Project Requirements - Registrant - Plumbing - Buildings

Buildings


Design ProfessionalsConstruction ProfessionalsLicensingbuilding UP

Project Guidelines: Skilled Trade/Registrant
Check License & Registration Status
Skilled Trades
Registrants

Project Guidelines: Skilled Trade/Registrant

Check License & Registration Status

Skilled Trades

Registrants


Registrant Project Requirements:
Plumbing Work & Inspections

During the course of completing plumbing installation and modification work of equipment, Licensed Master Plumbers (LMP) should check the following applicable notes to ensure regulatory and Code compliance with NYC Plumbing Code:

Roughing + Finishing, per PC section 107

Fernco couplings or Jim caps: Not permitted

Bottle, Bell + S Traps: Not permitted

Grease Traps (Interceptors): Both sides must be vented if on the floor, below the fixtures

Two + Three Compartment Food Preparation Sink Drains: Must have individual air gaps

Lavatory Sinks, No Overflow: 2” trap + grid strainer

Laundry Standpipes: Must be 18” – 42” (not 48”) per PC 406

Roughing Inspection: Tub/shower body and pressure-balancing valve piping must be completed

Roughing Inspection: Stall shower venting and traps required (shower pans are not)

Make-up Water, DDC, RPZ Connections: Must have air gap

Pressure Relief Valves: Piped down; unthreaded end not directly connected to house drainage or vent lines

Tub Connections: Separate inspection required if not inspected during the roughing inspection

PVC Waste + Vent Lines: Allowed in residential buildings five stories or less

NYC Fuel Gas Code: Gas Pipe Test Requirements, per FGC section 406

Meter Bars and/or Flanges: Must be installed

Future tees not permitted; appliance valves installed

System should have 5 PSI gauge with 3 PSI test for low pressure distribution systems

Test must include outlet side of meter to appliance, including any section isolations

New Gas Piping Risers: Drip leg prohibited, unless required by manufacturer; Branches taken off of a Riser shall have a minimum of two (2) elbow swing take-offs

Foundation, Footing or Bearing Wall Penetrations: Steel sleeve required (fire stopping for other penetrations)

Painted Gas Piping: 90 PSI test required

Approved Commercial Gas Flex: Commercial cooking equipment on wheels with restraints

Residential Stoves, Ovens + Dryers: Only these may use a gas flex; other equipment must be hard-piped.

NYC Fuel Gas Code: Gas Authorization, per FGC section 406

Flue, Make-up Air, Venting + Safety Control Wiring: Must be complete for dryers, hot water heaters, boilers, HVAC units

Fire Protection Inspections: Must be successfully completed when associated with a gas authorization request

Gas Test: Must not be more than one year old

Boiler Inspection Report or Boiler Work Type: Sign-off required

Non-residential Cooking Equipment: FDNY fire suppression letter required

Residential Stoves + Dryers (Not Installed Prior to Gas Authorization): LMP affidavit required

Welder affidavit (gas pipe welding only ) from approved agency

Color code: All gas piping in new or existing buildings shall be identified by a yellow label marked ‘Gas’ in black letters, at intervals not exceeding 5 feet. All labels must be in place at the time of the gas test. PC 401.5 (ASME A13.1)

NYC Energy Code: Commissioning replacement equipment >600kBTU/h

Commissioning preliminary report: Must be submitted to DOB prior to sign-off Commissioning final report: must be submitted to the Department 90 days after sign-off, as required by ECC section C408.

Special Inspections

Plumbing work may require, per Building Code Ch. 17, certain Special and Progress Inspections, and other construction requirements to be performed during, and at the end of construction, as per the table below. The Registered Design Professional is responsible for indicating which Special Inspections are required at application intake. The owner must engage the responsible Special Inspection Agencies, as required by Fuel Gas Code (FGC) Section 406, for such Special and Progress Inspections.

High Pressure Gas Piping

Per FGC Section 403.1.1, all welded gas distribution piping is subject to a special inspection.

Fire-resistance penetrations and joints

Per BC 1704.27, special inspections - all penetrations of walls must be sealed to maintain fire-rating; similarly piping joints and insulation may need to be fire-rated.

Seismic Isolation of Piping

Per BC 1707.8 – Compliance of piping with PC 106.5 to ensure earthquake protection of building and occupants.

Private on-site Sanitary / Storm Water Systems (Septic / Drywell)

When private on-site sanitary OR storm water disposal systems and detention (drywell and septic) are installed or repaired the following Special Inspections may be required per BC 1704.21and BC 1704.22:

(a) Design and construction standards for all types of systems.

Septic tanks - Concrete, Fiberglass and polyethylene tanks

Evaluation of existing system

Infiltration testing of existing individual private on-site sewage disposal systems

(b) Soil and groundwater testing.

Absorption test/percolation test (AT/PT)

Groundwater verification

AT/PT on sand column backfill material

Acceptance criteria for absorption tests

AT/PT termination

(c) Sand column construction.

Minimum depth of sand column

Serpentine rock

Backfilling the excavation

Post-Installed Anchors

Per BC 1704.32

The installation of post-installed mechanical anchors, adhesive anchors and screw anchors complying with Table 1704.32.

Special inspection shall include verification of compliance with the approved construction documents and standards

NYC Energy Code: Progress Inspections, as required by BC 110.3.5 and NYCECC

Penetrations through thermal envelope: must be sealed to minimize air leakage

Dampers integral to building envelope: outdoor air dampers must close when system is off

HVAC & Service Water heating equipment: meets sizing and efficiency requirements

HVAC & Service Water heating system controls: applicable part-load, reset, temperature controls

Piping insulation: minimum thickness of 1” to 4.5”, required on piping carrying fluids >105F

Maintenance Information: shall be furnished for installation of new equipment

Permanent Certificate: shall list type and efficiency of heating, cooling, and/or service water heating systems

Required Plumbing Inspections

Department inspections are required at various stages of completion of the plumbing work, as well as at the final completion. Based on the project’s scope of work, the following plumbing inspections may be required:

Underground Piping. Water/Sanitary, Gas, Storm, Medical/Gas

Roughing Piping in floors, ceilings and walls. Water/Sanitary, Gas, Storm, Medical/Gas, Sprinkler/Standpipe

Piping Test. Hydrostatic, Water/Sanitary, Pressure (water), Storm Water, Gas, Medical Gas

Finishes. Fixtures, Appliances and Equipment for Water/Sanitary, Gas, Sprinkler/Standpipe Finish, (PL) Storm, Medical/Gas

Final Inspection. Sign-off

LMP Self-Certification of Plumbing Inspections

For plumbing work, LMPs have the option to either require a Department Inspection or submit a self-certification of the completed work. LMPs must submit a notice of intent to self-certify, with the dates of these self-certified inspections to the Department, (online inspection requests) and follow-up with the submission of results for self-certified inspections (online inspection results).

The Plumbing Enforcement division conducts a random audit of all self-certified notices to ensure compliance of inspected work with code and regulations.

*Note: Plumbing installation and modifications that involves side walk heaters, micro turbines and jeweler torches in its scope of work cannot be self-certified by the Contractors.*

Inspection Requests

An online tool for scheduling appointments for required DOB inspections must be used. DOB NOW provides robust online accounts, making it easier to submit applications, make payments, schedule appointments, check the status of an application or inspection, pull permits, and make renewals.

Additional Requirements for Registrant

Plumbing Work & Site Requirements

Plumbing Allowable Work Without a RDP Submitting Construction Documents for Department Approval

More Building Systems Installation & Modifications

Contractor Project Checklists

Project Phases & Requirements for Registrant

Helpful Links

Project Categories

Key Points & Project Terms

Project Phases & Requirements

Project Checklists

Working on Your Project

Compliance & Violations

Insurance Guidelines

DOB NOW

Code Notes

Information for Master Plumbers & Master Fire Suppression Piping Contractors

Information for Contractors

Licensing Information