Project Requirements - Registrant - Mechanical - Buildings

Buildings


Design ProfessionalsConstruction ProfessionalsLicensingbuilding UP

Project Guidelines: Skilled Trade/Registrant
Check License & Registration Status
Skilled Trades
Registrants

Project Guidelines: Skilled Trade/Registrant

Check License & Registration Status

Skilled Trades

Registrants


Registrant Project Requirements:
Mechanical Work & Inspections

Special and Progress Inspections

Mechanical system work may require, per Building Code Ch. 17, certain Special and Progress Inspections, and other construction requirements to be performed during, and at the end of construction, as per the table below. The Registered Design Professional is responsible for indicating which Special Inspections are required at application intake. The owner must engage a Special Inspection Agencies, as required by AC Section 28-115, for such Special and Progress Inspections

Special / Progress Inspection

Description of Code Requirements

Final Inspection

There shall be a final inspection of all permitted work. Final inspections shall comply with AC 28-116.2.4.

Mechanical Systems

Mechanical systems requiring a certificate of compliance in accordance with AC 28-116.4.1 of the Administrative Code shall be inspected for conformance with the approved construction documents as per BC 1704.16.

Heating Systems

New and altered heating systems shall be tested in accordance with NYC MC 1011, and satisfactory operation within the existing system verified, as per NYC BC 1704.25.

Chimney

New and existing chimneys inspected for proper clearance and isolation from adjacent combustible construction in accordance with NYC MC 810 and NYC FGC 503.5.6, as per NYC BC 1704.26

Smoke Control Systems

Smoke control systems shall be tested by a special inspector in accordance with Sections BC 1704.15.1 and 909.

Structural Steel (welding, high strength bolting and details)

Provide special inspections with respect to any equipment that is mounted or hung from steel that is integral to the building, and/or mounted to rooftop dunnage, as per BC 1704.3.

Concrete – Cast-in-Place

Provide special inspection only if concrete is integral to mounting of equipment and is also relevant to the building’s structural system, as per BC 1704.4. Concrete Design Mix and Concrete Sampling and Testing may not be required if requirements in BC 1704.4.2 are satisfied.

Structural Stability – Existing Buildings

Mechanical work that may affect existing structural system, such as beams, bearing walls, floor system, roof system, etc. shall be inspected in accordance with BC 1704.20.6 to 1704.20.10.

Post-installed anchors

The installation of post-installed mechanical anchors, adhesive anchors, and screw anchors shall comply with Table BC 1704.32. The special inspection shall include the verification of compliance with approved construction documents and standards established by the commissioner pursuant to Section 28-113.2.2 of the Administrative Code and BB 2014-018, BB 2014-019.

Seismic isolation system

There shall be periodic special inspection during the fabrication and installation of isolator units and energy dissipation devices, if used as part of the seismic isolation system as per BC 1707.8.

Fire Resistance rated construction

As per BC 110.3.4, Fire-resistance-rated construction shall be inspected to determine compliance with the approved construction documents, including inspection of the following work:

Fire-resistance-rated partitions, floors, ceilings, shafts; and

Fire shutters

Sprayed fire-resistant materials

Special Inspections for sprayed fire-resistant materials applied to floor, roof and wall assemblies and structural members shall be in accordance with Sections BC 1704.11.1 through BC 1704.11.7. For example, this may be required if hangers are attached to steel components, which could adversely impact steel’s spray-on fire proofing.

Fire-resistant Penetration and Joists

Special Inspections for penetration of fire-resistant elements and assemblies; and related firestops in accordance with Sections BC 1704.27.1 and BC 1704.27.2.

Mastic and intumescent fire-resistant coatings.

Special inspections for mastic and intumescent fire-resistant coatings applied to structural elements and decks shall be in accordance with AWCI 12-B. Special inspections shall be based on the fire-resistance design as designated in the approved construction documents as per BC 1704.12.

Flood Zone Compliance

Special inspection for flood zone compliance shall be as required by BC Appendix G105.3.

NYC Energy Code: Progress Inspections, as required by BC 109.3.5 and NYCECC

Air sealing and insulation: penetrations through the thermal envelope must be sealed to minimize air leakage as per NYCECC R402.4.1 and C402.5.1.1.

Shutoff dampers: outdoor air dampers that penetrate the thermal envelope must close when system is off.

HVAC & Service Water heating equipment, per C406.2, exceeds by 10 percent the minimum sizing and efficiency requirements as per NYCECC Tables C403.2.3(1) through C403.2.3(7), C403.2.3(11), and C403.2.3(12) and Table C404.2.

HVAC & Service Water heating system controls: applicable part-load, reset, temperature controls as per NYCECC C403.2.4 and C404.6.

HVAC insulation and sealing: minimum R-6 insulation for ducts in unconditioned spaces and R-8 for insulation outside the building, per C403.2.7. Minimum thickness of 1” to 4.5”, required on piping carrying fluids >105F as per NYCECC Table C403.2.10 and C404.4

Maintenance Information: shall be furnished for installation of new equipment as per NYCECC R303.3 and C303.3

Permanent Certificate (1 or 2 Family homes only): shall list type and efficiency of heating, cooling, and/or service water heating systems as per NYCECC R401.3

Required Mechanical System Inspections

DOB inspections are typically performed only upon final completion of the mechanical system work. Based on the repair project’s scope of work, the following mechanical system inspections may be required:

Final Inspection

Prior to sign-off. The DOB Inspector shall check that the Equipment Certificates of Compliance have been submitted and match the installed equipment model number, capacities, etc.

Verification of SIA Final Inspection. DOB shall check that the SIA, or applicant of record with equivalent SIA credentials, has submitted the final inspection report (TR1). Such final inspection report (TR1) by SIA shall verify that the mechanical system installation is complete in accordance with the approved drawings and in compliance with all Code and Zoning requirements as outlined in AC 28-116.2.4.2.

Letter of Completion. After successful final inspection, a Letter of Completion may be issued.

Mechanical Work and Inspections

During the course of completing Mechanical System Work, Contractors should check the following to ensure regulatory and Code-compliance with NYC Mechanical and Building Code:

BC Chapter 7 – Fire Resistance rated Materials, e.g. penetrations of piping and ductwork

BC Chapter 9 – Fire Protection Systems, e.g. interconnection with fire alarm or smoke control systems

BC 1613 – Earthquake Loading

Mechanical Code (MC) in its entirety

During the course of completing Mechanical System Work, Contractors should check the following to ensure regulatory and Code-compliance with NYC Energy Conservation Code:

Commissioning is required on newly installed systems with a cumulative input heating capacity >600kBTU/h and/or cooling capacity > 480kBtu/h.

Commissioning preliminary report must be submitted to the Department prior to sign-off

Commissioning final report must be submitted to the department 18 months after Certificate of Completion, as required by ECC section C408.

Inspection Requests

An online tool for scheduling appointments for required DOB inspections must be used. DOB NOW provides robust online accounts, making it easier to submit applications, make payments, schedule appointments, check the status of an application or inspection, pull permits, and make renewals.

Additional Requirements for Registrant

Mechanical Work & Site Requirements

Mechanical: Allowable Work Without a Registered Design Professional

More Building Systems Installation & Modifications

Contractor Project Checklists

Project Phases & Requirements for Registrant

Helpful Links

Project Categories

Key Points & Project Terms

Project Phases & Requirements

Project Checklists

Working on Your Project

Compliance & Violations

Insurance Guidelines

DOB NOW

Code Notes

Information for Master Plumbers & Master Fire Suppression Piping Contractors

Information for Contractors

Licensing Information