Product: 12/2 UF-B Wire, Underground Feeder and Direct Earth Burial Cable (150ft Cut)
Brand: Stock Wire
Applications:
UF-B is an underground feeder and branch circuit wiring cable. It can be used as an underground feeder from an existing building to outdoor lighting fixtures, pumps, outbuildings and other equipment. Its applications are outlined in Article 340 NEC 2008 and NEC 2011. UF-B is rated at 600 volts. Although it is rated at a conductor temperature of 90ºC dry / wet, its ampacity is limited to 60ºC according to the NEC 2008 AND NEC 2011. UF-B may be directly buried or installed where exposed to sunlight. When used as an NM cable it must comply with the requirements in NEC 2008 and NEC 2011 Article 334.Standards:
ASTM - B3 and B-8
UL Standard 83
UL Standard 493
Federal Specification A-A-59544
National Electrical Code, NFPA 70, 2011 Edition
RoHS/REACHConstruction:
Insulation: Polyvinyl Chloride (PVC) with a nylon covering. Color coded phase identification.
Jacket:Sunlight and moisture resistant gray PVC.Specifications:
Size:12 AWG
Number of Conductors:2
PVC Insulation Thickness:0.030 inches
Ground Wire Size:12 AWG
Nylon Thickness:0.005 inches
Nominal Cable Dimensions:.463 inches x .183 inches
Weight per Foot: 0.95 lbs
Allowable Ampacity: 20 Amps
#12 AWG Wire with 2 Annealed (Soft) Copper (Cu) Conductors
Used Indoors for Wet or Corrosive Locations, Resistant to Light and Moisture
Used Outdoors for Direct Earth Burial, Resistant to Sunlight and Moisture
Has a Heat Capacity of 90 degreesC and is rated for 600-Volts, Has an Allowable Ampacity of 20 Amps
Color of Wire May not be the Same as the Picture Shown.

Search query: underground 12/2 wire
Relevance: Exact