Equal transfer processes-based distance protection of EHV transmission lines
Coupling capacitor voltage transformers can cause the distance relay overreach. We make the voltages and currents to have the same transfer links. We re-structure the voltage at the fault point. The virtual digital transfer method is used. The measuring error is within 5% at 15ms after fault occurrence.
coupling capacitor voltage transformer distance relay virtual digital transfer equal transfer process