reglab/statecodes huggingface dataset:
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › VENTILATION AND INDOOR AIR QUALITY › Section 296-150C-1490 - Appliances - Installation

Current through Register Vol. 24-14, July 15, 2024
In addition to requirements of the Washington State
				  Ventilation and Indoor Air Quality Code:
(1) The installation of each appliance must
				conform to the manufacturer's installation instructions. The manufacturer's
				instructions must be attached to the appliance.
(2) Combustion air inlets and flue gas
				outlets must be listed as components of the appliance and must be completely
				separated. The required separation may be obtained by:
(a) The installation of direct vent system
				(sealed combustion system) appliances; or
(b) The installation of appliances within
				enclosures so that the appliance combustion system and venting system are
				separate from the interior atmosphere of the commercial coach. There must not
				be any door, removable access panel, or other opening into the enclosure from
				inside the commercial coach. Any openings for ducts, piping, wiring, etc., must
				be sealed.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › VENTILATION AND INDOOR AIR QUALITY › Section 296-150C-1500 - Safety devices - Water heater relief valves

Current through Register Vol. 24-14, July 15, 2024
In addition to requirements of the Washington State
				  Ventilation and Indoor Air Quality Code:
(1) All water heaters must be installed with
				approved fully automatic valve or valves designed to provide temperature and
				pressure relief. Temperature and pressure relief valves must be tested and
				approved to ANSI Z21.22 standard or equal.
(2) Any temperature relief valve or combined
				pressure and temperature relief valve installed for this purpose must have the
				temperature sensing element immersed in the hottest water within the upper six
				inches of the tank. It must be set to start relieving at a pressure of 150 psi
				or the rated working pressure of the tank, whichever is lower, and at or below
				a water temperature of 210 degrees Fahrenheit.
(3) Relief valves must be provided with
				full-sized drains. Drains must be directed to the exterior sides of the unit,
				exiting at least six inches above the ground, and each drain pipe must exhaust
				with a ninety degree downward turn. Drain lines must be of a material approved
				for hot water distribution and must drain fully by gravity, must not be
				trapped, and must not have their outlets threaded.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150C-1500,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › VENTILATION AND INDOOR AIR QUALITY › Section 296-150C-1510 - Air ducts - Expandable or multiple commercial coach connections

Current through Register Vol. 24-14, July 15, 2024
In addition to the requirements of the International
				  Mechanical Code and the Washington State Energy Code air ducts for:
(1) An expandable or multiple commercial
				coach may have ducts of the heating system installed in the various units. The
				points of connection must be so designed and constructed that when the
				commercial coach is fully expanded or coupled, the resulting duct joint will
				conform to the requirements of this chapter.
(2) Installation instructions for supporting
				the crossover duct from the commercial coach must be provided for on-site
				installation. The duct must not touch the ground.
Statutory Authority:
					 Chapter
					 43.22 RCW and 2003 c 291.
					 05-01-102, § 296-150C-1510, filed 12/14/04, effective 2/1/05. Statutory
					 Authority:
					 RCW
					 43.22.340, [43.22.]355,
					 [43.22.]360,[43.22.]432 , [43.22.]440 and [43.22.]480. 96-21-146, §
					 296-150C-1510, filed 10/23/96, effective
					 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › VENTILATION AND INDOOR AIR QUALITY › Section 296-150C-1520 - Air ducts - Duct and plenum insulation

Current through Register Vol. 24-14, July 15, 2024
Every heating and cooling duct and plenum must be installed
				  according to the International Mechanical Code and the Washington State Energy
				  Code.
Statutory Authority:
					 Chapter
					 43.22 RCW and 2003 c 291.
					 05-01-102, § 296-150C-1520, filed 12/14/04, effective 2/1/05. Statutory
					 Authority:
					 RCW
					 43.22.340, [43.22.]355,
					 [43.22.]360,[43.22.]432 , [43.22.]440 and [43.22.]480. 96-21-146, §
					 296-150C-1520, filed 10/23/96, effective
					 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › PLUMBING › Section 296-150C-1530 - Plumbing - General

Current through Register Vol. 24-14, July 15, 2024
This chapter also applies to the installation of plumbing
				  equipment in any commercial coach bearing or required to bear a department
				  insignia. Plumbing fixtures, equipment, and installations in commercial coaches
				  must conform to the provisions of the Uniform Plumbing Code and the amendments
				  adopted by the State Building Code Council, except part 1, unless specifically
				  exempted or required by this section.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150C-1530,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › PLUMBING › Section 296-150C-1540 - Plumbing - Definitions

Current through Register Vol. 24-14, July 15, 2024
The definitions listed below, in addition to the Uniform
				  Plumbing Code definitions apply to this chapter.
"Drain outlet"
is the discharge end of the
				  commercial coach main drain to which a drain connector may be attached.
"Main drain"
is the principal artery of the
				  commercial coach drainage system to which drainage branches may be
				  connected.
"Water-supply connection"
is the fitting or
				  point of connection of the commercial coach water distribution system designed
				  for connection to a water connector.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150C-1540,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › PLUMBING › Section 296-150C-1545 - Does the department require a water system expansion tank be installed?

Current through Register Vol. 24-14, July 15, 2024
The department will only require that a tee be installed in
				  an accessible location for the future addition of an expansion tank where one
				  may be installed if required.
Statutory Authority:
					 RCW
					 43.22.340 and
					 43.22.480. 99-13-010, §
					 296-150C-1545, filed 6/4/99, effective
					 7/5/99.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › PLUMBING › Section 296-150C-1550 - Drainage - Cap or plug

Current through Register Vol. 24-14, July 15, 2024
Drain outlets must be equipped with a watertight cap or plug
				  that is permanently attached to the vehicle.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150C-1550,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › PLUMBING › Section 296-150C-1560 - Drainage - Clearance from drain outlet

Current through Register Vol. 24-14, July 15, 2024
The drain outlet and couplers must have a minimum clearance
				  of three inches in any direction from all parts of the structure or
				  appurtenances and at least eighteen inches unrestricted clearance directly in
				  front of the drain outlet.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150C-1560,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150C - Commercial coaches › PLUMBING › Section 296-150C-1570 - Water supply connection

Current through Register Vol. 24-14, July 15, 2024
(1)
				Each commercial coach equipped with a water distribution system must have a
				water-supply connection that terminates within eighteen inches of the outside
				wall of the commercial coach.
(2)
				Water-supply connections must be equipped with a watertight cap or plug that is
				permanently attached to the commercial coach.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150C-1570,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0010 - Authority, purpose, and scope

Current through Register Vol. 24-14, July 15, 2024
(1) This chapter is authorized by
			 RCW
			 43.22.420,
			 43.22.434 and
			 43.22.450 through
			 43.22.490, covering the
			 construction and approval of factory-built housing and commercial structures
			 before occupancy.
(2) This chapter
			 applies to the approval:
(a) Of factory-built
			 structures used for residences or commercial purposes; and
(b) After occupancy of a factory-built house
			 or commercial structure, all inspections are done by the local enforcement
			 agency.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0030 - How is this chapter enforced?

Current through Register Vol. 24-14, July 15, 2024
(1) To enforce this chapter, we or another
			 governmental inspection agency will inspect each factory-built house and
			 commercial structure that is sited in Washington. Inspections will be conducted
			 during normal work hours or at other reasonable times. (See WAC
			 296-150F-0070.)
(2) We will inspect each unit as required by
			 the codes. (See WAC
			 296-150F-0500.)
Statutory Authority:
				  RCW
				  43.22.340, [43.22.]355, [43.22.]360,
				  [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0030,
				  filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0040 - Will you keep my manufacturing information confidential?

Current through Register Vol. 24-14, July 15, 2024
We will only release manufacturing information such as design
				plans, specifications, and test results according to the requirements of the
				Public Records Act (see RCW 42.17.310(1)(h) ) unless we are ordered to do so by
				a court or otherwise required by law.
Statutory Authority:
				  RCW
				  43.22.340 and
				  43.22.420. 97-16-043, §
				  296-150F-0040, filed 7/31/97, effective 12/1/97. Statutory Authority:
				  RCW
				  43.22.340, [43.22.]355, [43.22.]360,
				  [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0040,
				  filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0050 - Can you prohibit the installation of factory-built housing and commercial structures?

Current through Register Vol. 24-14, July 15, 2024
(1) We
			 may prohibit the installation of factory-built housing and commercial
			 structures if they do not conform to the requirements of this chapter. (See
			 RCW
			 43.22.465.)
(2) If an inspection reveals that a
			 factory-built home or commercial structure violates this chapter, we may obtain
			 a temporary injunction enjoining the installation of any nonconforming
			 structure. The injunction may be made permanent at the discretion of the
			 court.
Statutory Authority:
				  RCW
				  43.22.340 and
				  43.22.480. 99-13-010, §
				  296-150F-0050, filed 6/4/99, effective
				  7/5/99.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0070 - Do you have reciprocal agreements with other states to inspect factory-built housing and commercial structures, and components?

Current through Register Vol. 24-14, July 15, 2024
(1) We have entered into reciprocal
			 agreements with states who have construction standards that are equal to or
			 greater than our standards for factory-built housing and commercial
			 structures.
(2) When we have a
			 reciprocal agreement with another state:
(a)
			 The reciprocal state inspects factory-built housing, commercial structures, and
			 components manufactured in that state before shipment into Washington to ensure
			 compliance with our laws. After inspection, the reciprocal state applies our
			 insignia.
(b) The department
			 inspects factory-built housing, commercial structures, and components
			 manufactured in Washington before shipment into the reciprocal state to ensure
			 compliance with their laws. After inspection, we apply the insignia of the
			 reciprocal state.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0080 - Do you allow a local enforcement agency to inspect factory-built housing, commercial structures, and components at the manufacturing location?

Current through Register Vol. 24-14, July 15, 2024
(1) A local
			 enforcement agency (city or county), under contract with us, can inspect
			 factory-built housing, commercial structures, and components. In some cases
			 their contract may be limited to specific portions of an inspection at
			 specified manufacturing locations.
(2) After approving a unit, the local
			 enforcement agency will attach the insignia, which indicates the unit has
			 passed inspection.
Statutory Authority:
				  RCW
				  43.22.340, [43.22.]355, [43.22.]360,
				  [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0080,
				  filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0090 - What are the requirements for certified plumbers and electricians?

Current through Register Vol. 24-14, July 15, 2024
Plumbers certified under chapter 18.106 RCW and electricians
				certified under
				chapter
				19.28 RCW are required for
				units constructed in Washington. For the purposes of construction at the
				manufacturing facility, the manufacturer is not required to be a licensed
				electrical contractor under
				chapter
				19.28 RCW or a registered
				contractor as required by
				chapter
				18.27 RCW. Manufacturers
				may hire registered plumbing contractors or licensed electrical contractors to
				meet this requirement.
Work performed outside the manufacturer's facility must be
				performed by a registered contractor under
				chapter
				18.27 RCW, electrical
				contractor and electricians under
				chapter
				19.28 RCW, and certified
				plumbers under chapter 18.106 RCW.
Statutory Authority:
				  Chapter
				  43.22 RCW. 12-15-061,
				  § 296-150F-0090, filed 7/17/12, effective
				  9/1/12.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0100 - What happens if I disagree with your decision regarding my compliance with this chapter?

Current through Register Vol. 24-14, July 15, 2024
(1) If we
			 determine you are in violation of this chapter, you will receive a notice of
			 noncompliance.
(2) If you disagree
			 with our decision, you can send us a written request for a hearing, stating why
			 you disagree.
(3) After we receive
			 your hearing request, we will:
(a) Schedule a
			 hearing within thirty days after we receive your request.
(b) Notify you of the time, date, and place
			 for the hearing. If you fail to appear, your case will be dismissed.
(c) Hear your case.
(d) Send you written notice of our decision.
If you disagree with our decision, you may appeal it under the
				Administrative Procedure Act (chapter 34.05 RCW).
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0110 - Do you have an advisory board to address factory-built housing and commercial structure issues?

Current through Register Vol. 24-14, July 15, 2024
The factory assembled structures (FAS) board advises us on
				issues relating to structural, plumbing, mechanical, electrical, installation,
				inspections, and rules for factory-assembled structures. (See
				RCW
				43.22.420.)
Statutory Authority:
				  RCW
				  43.22.340, [43.22.]355, [43.22.]360,
				  [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0110,
				  filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0120 - Where can I obtain technical assistance regarding factory-built housing and commercial structures?

Current through Register Vol. 24-14, July 15, 2024
We provide field technical service to factory-built housing and
				commercial structure manufacturers for an hourly fee. Field technical service
				may include an evaluation, consultation, plan examination, interpretation, and
				clarification of technical data relating to the application of our rules. It
				does not include inspections.
Statutory Authority:
				  RCW
				  43.22.340, [43.22.]355, [43.22.]360,
				  [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0120,
				  filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0130 - How do I register a complaint?

Current through Register Vol. 24-14, July 15, 2024
A person who believes that a structure or component does not
				meet the requirements of this chapter may register a complaint with the
				department. The complaint must be in writing and must specifically describe the
				alleged violations of this chapter. Upon receipt of the complaint, the
				department will forward a copy to the appropriate manufacturer and/or dealer
				and they shall have thirty days to respond to it. If the department determines
				that an inspection is necessary, the manufacturer/dealer shall pay the
				department for the cost of the inspection. The cost of the inspection is based
				upon the fee schedule in WAC
				296-150F-3000 and includes the
				hourly inspection fee, travel costs and other expenses incurred as a result of
				the inspection.
Statutory Authority:
				  Chapter
				  43.22 RCW. 98-14-078,
				  § 296-150F-0130, filed 6/30/98, effective
				  7/31/98.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › Section 296-150F-0140 - Do you allow the use of alternate materials, alternate design and method of construction?

Current through Register Vol. 24-14, July 15, 2024
An applicant may apply for the use of alternate materials,
				alternate design and methods of construction different from the requirements of
				this chapter by filing a written request with the department.
(1) Responsibilities of applicant. The
			 applicant must submit in writing the following information and sign and date
			 the request.
(a) The applicant's name,
			 address and phone number;
(b) The
			 specific requirement or requirements from which the alternate material,
			 alternate design or method of construction is requested;
(c) Justification that the requirements of
			 this chapter cannot be met without using alternate materials, alternate design
			 or method of construction;
(d) How
			 the use of alternate materials, alternate design or method of construction will
			 achieve the same result as the requirement and any specific alternative
			 measures to be taken to show the alternate provides the same level of
			 protection to life, safety and health as the requirements.
The department has a form that you may use for your request.
				Contact the department at the address shown in the definition section.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › INSIGNIA › Section 296-150F-0200 - Who must purchase factory-built housing and commercial structure insignia?

Current through Register Vol. 24-14, July 15, 2024
(1) You
				must obtain insignia from us for each factory-built house, commercial structure
				and component sited in Washington state.
(2) If you are a Washington state
				manufacturer, you do not need to purchase our insignia for your factory-built
				housing, commercial structures and components sold outside of Washington
				state.
(3) You must have an
				approved design plan and have passed inspection before an insignia can be
				attached to your factory-built home or commercial structure by us or our
				authorized agent.
(4) If a unit is
				damaged in transit after leaving the manufacturing location or during an
				on-site installation, and a repair is necessary, you must purchase an insignia
				from us. The insignia indicates that the unit was repaired.
Statutory Authority:
					 Chapter
					 43.22 RCW. 98-14-078,
					 § 296-150F-0200, filed 6/30/98, effective 7/31/98. Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432,[43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0200, filed
					 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › INSIGNIA › Section 296-150F-0210 - What are the insignia requirements?

Current through Register Vol. 24-14, July 15, 2024
(1) If you are applying for insignia for
				factory-built housing, commercial structures and components you must have your
				design plan approved and your units and components inspected and approved by
				us.
(2) We will attach the insignia
				after:
(a) We receive the required forms and
				fees from you (see WAC
				296-150F-3000 ); and
(b) Your unit or component has passed final
				inspection. (See WAC
				296-150F-0500.)
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › INSIGNIA › Section 296-150F-0220 - How do I obtain insignia information and the required forms?

Current through Register Vol. 24-14, July 15, 2024
Upon request, we will provide you with a packet of
				  information that includes the required forms.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0220,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › INSIGNIA › Section 296-150F-0230 - What are the insignia application requirements?

Current through Register Vol. 24-14, July 15, 2024
(1) If you are requesting insignia for units
				that you intend to manufacture under a
new design plan,
your
				completed application must include:
(a) A
				completed design plan approval request form;
(b) Two complete sets of design plans,
				specifications, engineering analysis, test procedures and results, plus one
				additional set for each manufacturing location where the design plan will be
				used;
(c) At least one set of
				design plans must have an original wet stamp from a professional engineer or
				architect licensed in Washington state. We will retain the set with the
				original wet stamp; and
(d) A
				one-time initial filing fee, the design plan fee (if we approve your design
				plan) and the fee for each insignia. (See WAC
				296-150F-3000.)
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › INSIGNIA › Section 296-150F-0250 - How do I replace lost or damaged insignia?

Current through Register Vol. 24-14, July 15, 2024
(1) If an insignia is lost or damaged after
				it is attached to your factory-built house, commercial structure, or component,
				you may obtain a replacement insignia.
(2) You should contact us and provide the
				following information:
(a) Your name,
				address, and telephone number;
(b)
				The name of the manufacturer;
(c)
				The serial number;
(d) The
				manufacturer number (M#), if available;
(e) The insignia number, if available;
				and
(f) The required fee. (See WAC
				296-150F-3000.)
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN PLAN › Section 296-150F-0300 - When is design plan approval required?

Current through Register Vol. 24-14, July 15, 2024
Design plans for factory-built housing and commercial
				  structures prior to installation at the building site in Washington must be
				  approved when:
(1) You build a new
				unit;
(2) You modify an approved
				design plan through an addendum; or
(3) You add options to an approved design
				plan through an addendum.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0300,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN PLAN › Section 296-150F-0310 - Who can approve design plans?

Current through Register Vol. 24-14, July 15, 2024
(1) Design plans can be approved by us or by
				a licensed professional or firm authorized by us (see WAC
				296-150F-0420 and
				296-150F-0430).
(2) All electrical design plans for new or
				altered electrical installations for educational, institutional, health care
				facilities, and other buildings (see WAC
				296-46B-900) must be reviewed and
				approved by us.
(3) All design
				plans submitted under a reciprocal agreement for multistate approval must be
				reviewed and approved by us.
Statutory Authority:
					 Chapter
					 43.22 RCW. 12-15-061,
					 § 296-150F-0310, filed 7/17/12, effective 9/1/12. Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355,
					 [43.22.]360,[43.22.]432 , [43.22.]440 and [43.22.]480. 96-21-146, §
					 296-150F-0310, filed 10/23/96, effective
					 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0320 - What must I provide with my request for design-plan approval by the department?

Current through Register Vol. 24-14, July 15, 2024
All requests for design-plan approval must include:
(1) A completed design-plan approval request
				form;
(2) Two complete sets of
				design plans, specifications, engineering analysis, test procedures and results
				plus one additional set for each manufacturing location where the design plan
				will be used (see WAC
				296-150F-0340 and
				296-150F-0350 );
(3) At least one set of design plans must
				have an original wet stamp from a professional engineer or architect licensed
				in Washington state. All new, renewed, and resubmitted plans, specifications,
				reports and structural calculations prepared by or prepared under his or her
				direct supervision shall be signed, dated and stamped with their seal.
				Specifications, reports, and structural calculations may be stamped only on the
				first sheet, provided this first sheet identifies all of the sheets that follow
				are included and identified in the same manner. Plans that have not been
				prepared by or under the engineer's or architect's supervision shall be
				reviewed by them and they shall prepare a report concerning the plans reviewed.
				This report shall:
(a) Identify which
				drawings have been reviewed by drawing number and date;
(b) Include a statement that the plans are in
				compliance with current Washington state regulations; and
(c) The report shall be stamped and signed by
				the reviewer.
Any deficiencies shall be corrected on the drawings before
				  submitting to the department or be included in the report and identify as to
				  how they are to be corrected. This report shall be attached to the plan(s) that
				  were reviewed. We will retain the set with the original wet stamp;
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0325 - What are the requirements for temporary built structures?

Current through Register Vol. 24-14, July 15, 2024
Structures built for temporary use must meet all the
				  requirements of this chapter.
Statutory Authority:
					 Chapter
					 43.22 RCW. 12-15-061,
					 § 296-150F-0325, filed 7/17/12, effective
					 9/1/12.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0340 - What must an engineering analysis for design plans include?

Current through Register Vol. 24-14, July 15, 2024
(1) The engineering
				analysis must show that the structural design meets the requirements of this
				chapter.
(2) An engineering
				analysis must be conducted according to accepted engineering practices and must
				be signed by a professional engineer or architect licensed in Washington
				state.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0340,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0350 - What must the test procedures and results for design plans include?

Current through Register Vol. 24-14, July 15, 2024
(1) Tests to a
				design for a factory-built home or commercial structure must be witnessed by a
				professional engineer or architect licensed in Washington state.
(2) Test reports must contain the following
				items:
(a) A description of the methods or
				standards that applied to the test;
(b) Drawings and a description of the item
				tested;
(c) A description of the
				test setup;
(d) The procedure used
				to verify the correct load;
(e) The
				procedure used to measure each condition;
(f) Test data, including applicable graphs
				and observations of the characteristics and behavior of the item tested;
				and
(g) Analysis, comments, and
				conclusion.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0380 - What happens if you approve my design plan?

Current through Register Vol. 24-14, July 15, 2024
(1) Your design plan will be approved if it
				meets the requirements of this chapter.
(2) We will send you an approved copy of the
				design plan with the design-plan approval number.
(3) You must keep copies of the approved
				design plan at each location where a factory-built house, commercial structure,
				or component is built.
(4) If your
				design plan is not approved, you will be notified in writing of plan
				deficiencies. You may send a corrected design plan to us. (See WAC
				296-150F-3000.)
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0380,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0390 - If my design plan is not approved, how much time do I have to submit a corrected design plan?

Current through Register Vol. 24-14, July 15, 2024
(1) You
				have ninety days to correct and resubmit your original design plan and send us
				the resubmittal fee after we notify you of plan deficiencies. After ninety
				days, your initial design plan is returned to you.
(2) If you submit your corrected design plan
				after ninety days, you must send the initial design plan fee instead of the
				resubmittal fee. (See WAC
				296-150F-3000.)
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0390,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0400 - What happens after my design plan is approved?

Current through Register Vol. 24-14, July 15, 2024
Once your design plan is approved, we will inspect each
				  related factory-built house, commercial structure, or
				  component.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0400,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0410 - When does my design plan expire?

Current through Register Vol. 24-14, July 15, 2024
Master design plan:
(1) Your master design plan expires when
				there is a code change. You must submit new design plans for approval when
				there is a State Building Code cycle change. You may use your approved master
				design plans to order insignia as long as they comply with the applicable
				codes.
One-year design plan:
(2) Your factory-built home or commercial
				structure one-year design plan expires either one year after approval or when
				there is a code change. You must submit new design plans for approval when
				there is a State Building Code cycle change. You may use your design plan to
				order insignia as long as they comply with the applicable codes.
(3) All National Electrical Code amendments
				may be incorporated by an addendum to your design plan.
Note:
The State Building Code is on a three-year code
								cycle which coincides with the State Building Code council amendment cycle. The
								National Electrical Code (NEC) cycle, however, does not coincide with the other
								code cycles.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355,
					 [43.22.]360,[43.22.]432 , [43.22.]440 and [43.22.]480. 96-21-146, §
					 296-150F-0410, filed 10/23/96, effective
					 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY THE DEPARTMENT › Section 296-150F-0415 - Who approves addendums to design plans approved by the department?

Current through Register Vol. 24-14, July 15, 2024
You must have us approve an addendum to a design plan, if we
				  initially approved your design plan.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0415,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0420 - Who can be authorized to approve design plans?

Current through Register Vol. 24-14, July 15, 2024
(1) A professional engineer, architect, or
				firm licensed by the state of Washington according to the Engineers
				Registration Act, chapter 18.43 RCW and/or the Architects Registration Act,
				chapter 18.08 RCW; or
(2) A
				professional engineer, architect, or firm licensed in another state that has
				licensing or certification requirements that meet or exceed Washington
				requirements;
(3) A professional
				engineer, architect, or firm who designs and certifies that the factory-built
				home or commercial structure design meets state requirements cannot also
				approve the design plan in the plan approval process;
(4) A professional engineer, architect, or
				firm cannot approve those electrical designs listed in WAC
				296-150F-0310(2);
				and
(5) A professional engineer,
				architect, or firm cannot approve plans submitted for multistate approval under
				a reciprocal agreement.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0420,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0430 - What information must a professional or firm provide to be authorized to approve design plans?

Current through Register Vol. 24-14, July 15, 2024
(1)
				Name, a copy of your certificate of registration or authority, and address of
				the professional engineer, architect, or firm; and
(2) A description of the services the
				professional engineer, architect, or firm will provide in the areas of
				structural, fire and life safety, energy, mechanical, plumbing, and electrical
				plan review for factory-built housing and commercial structures; and
(3) A summary of the professional's or firm's
				expertise and qualifications to review plans in the areas identified by the
				description of services.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0430,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0440 - How will I know whether I am authorized to approve design plans?

Current through Register Vol. 24-14, July 15, 2024
Within sixty days after you submit the information requested
				  in WAC 296-150F-0430, we will send you a
				  letter either approving or denying your authorization request.
(1) If we approve your request, your name is
				added to the list of licensed professionals and firms authorized to approve
				design plans.
(a) We will authorize a
				professional to approve portions of a design plan within his or her area of
				expertise; and
(b) We will
				authorize an engineering or architectural firm to approve plans if the firm
				employs or contracts with professionals within the area of expertise necessary
				for the design plan.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0450 - How long is a licensed professional or firms authorization effective?

Current through Register Vol. 24-14, July 15, 2024
Your authorization to approve design plans is effective until
				  your license expires, is revoked or suspended or until your authorization to
				  approve plans is revoked or suspended in accordance with subsection (3) or (4)
				  of this section.
(1) You must notify
				us of your license renewal at least 15 days before your license expires, to
				prevent your name from being removed from our licensed professional and firm
				list.
(2) You must notify us
				immediately if your license is revoked or suspended. Your name is then removed
				from the list of licensed professionals and firms authorized to approve design
				plans.
(3) Your authorization to
				approve plans may be revoked or suspended if during any one year we receive
				three or more approved plans that after audit are found to be incomplete or
				contain multiple code violations. Incomplete plans are those that do not meet
				the requirements of this chapter and our written plan review guidelines that we
				provided to you. If your authorization is revoked you may reapply for
				authorization in accordance with WAC
				296-150F-0430, after one year
				from the date of revocation. Suspensions may be up to one year. If you disagree
				with our decision, you can send us a written request for a hearing, stating why
				you disagree. (See WAC
				296-150F-0100.)
(4) Your authorization to approve plans may
				be revoked if we find the licensed professional has a conflict of interest. If
				your authorization is revoked you may reapply for authorization in accordance
				with WAC 296-150F-0430, after one year
				from the date of revocation. If you disagree with our decision, you can send us
				a written request for a hearing, stating why you disagree. (See WAC
				296-150F-0100.)
(5) If we revoke or suspend your
				authorization in accordance with subsection (3) or (4) of this section, your
				name will be removed from the list of licensed professionals and firms
				authorized to approve design plans.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0450,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0460 - What information must a manufacturer send to the department when a professional or firm does the design plan approval?

Current through Register Vol. 24-14, July 15, 2024
You must send us the following information in your approved
				  design plan:
(1) A completed
				departmental design plan approval request form;
(2) A set of the design plan drawings,
				specifications, engineering analysis, and test results and procedures necessary
				for a complete code evaluation of the design. These design plans must be sealed
				by the design professional(s) in accordance with chapters 196-23 and 308-12
				WAC;
(3) A cover sheet on the
				design plan noting which professional approved each portion of the design
				plan;
(4) A copy of the
				authorization letter from us; and
(5) The design plan fee for design plans
				approved by professionals or firms (see WAC
				296-150F-3000).
Statutory Authority:
					 Chapter
					 43.22 RCW. 98-14-078,
					 § 296-150F-0460, filed 6/30/98, effective 7/31/98. Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432,[43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0460, filed
					 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0470 - What happens after we receive the professional or firm approved design plan and information?

Current through Register Vol. 24-14, July 15, 2024
(1)
				After we receive your approved design plans and information, we will check the
				design plans and information to reasonably assure they contain the documents
				and plan information outlined in our written guidelines for plan reviews as
				provided to approved licensed professionals. Once accepted we will assign a
				plan approval number and send a copy of the design plan with the plan approval
				number to the manufacturer.
(2) If
				our check of the design plans and information finds that they are not
				acceptable we will notify you in writing of the reasons why. Unless being
				audited in accordance with subsection (3) of this section, design plans and
				information may be corrected and resubmitted for acceptance within 90 days of
				our notification. We may charge the applicant an additional hourly fee to
				process revised submittals (see WAC
				296-150F-3000).
(3) We may audit design plans approved by a
				professional engineer, architect, or firm to ensure compliance with this
				chapter and our written guidelines for plan reviews. Audits may be either
				random audits or they may be audits of plans that were not accepted in
				accordance with subsection (2) of this section. The department's audit should
				not be construed as certifying that the plans are safe.
(4) If the audit finds that the design plans
				approved by the professionals and firms do not comply with this chapter and our
				written guidelines for plan reviews, the applicant will be notified and may be
				required to pay our fees for review and approval of the design plans. (See WAC
				296-150F-3000.)
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0470,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0480 - Do you have a list of professionals or firms that are authorized to approve design plans?

Current through Register Vol. 24-14, July 15, 2024
Yes. We will maintain a list of the licensed professionals
				  and firms that are authorized to approve design plans for factory-built housing
				  and commercial structures.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0480,
					 filed 10/23/96, effective 11/25/96.
Washington Administrative Code › Title 296 - Labor and Industries, Department of › Chapter 296-150F - Factory-built housing and commercial structures › DESIGN-PLAN APPROVAL BY A LICENSED PROFESSIONAL OR FIRM › Section 296-150F-0490 - Who approves addendums to design plans approved by a professional or firm?

Current through Register Vol. 24-14, July 15, 2024
(1) You must
				have the professional or firm approve an addendum to a design plan, if they
				initially approved your design plan.
(2) If the professional or firm who approved
				your design plan is no longer on the department list you may have us approve
				your addendum.
Statutory Authority:
					 RCW
					 43.22.340, [43.22.]355, [43.22.]360,
					 [43.22.]432, [43.22.]440 and [43.22.]480. 96-21-146, § 296-150F-0490,
					 filed 10/23/96, effective 11/25/96.