reglab/statecodes huggingface dataset:
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter R - Underground Injection › Section NR 665.0430 - Applicability

Current through June 24, 2024
(1) Except as provided in sub. (2),
				  underground injection of any hazardous waste through a well is
				  prohibited.
(2) Underground
				  injection of contaminated groundwater that meets the definition of hazardous
				  waste or contains a hazardous waste may be allowed as part of a remedial action
				  necessary for the cleanup of soil or groundwater contamination, and is not
				  subject to the requirements of chs. NR 664 and 665 subchs. A to E, G, H and N,
				  and chs.
				  NR 668 and
				  670, provided that all of the
				  following requirements are met:
(a) A person
				  who proposes to perform the injection obtains written approval from the
				  department.
(b) The criteria in s.
				  NR
				  140.28(5) are met.
(c) The contaminated groundwater is treated
				  before it is injected.
(d) The
				  groundwater is injected into the same formation from which it was
				  withdrawn.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter W - Drip Pads › Section NR 665.0440 - Applicability

Current through June 24, 2024
(1) The requirements of this subchapter apply
				  to owners and operators of facilities that use new or existing drip pads to
				  convey treated wood drippage, precipitation or surface water run-off to an
				  associated collection system. Existing drip pads are those constructed before
				  June 1, 1995 and those for which the owner or operator has a design and has
				  entered into binding financial or other agreements for construction prior to
				  June 1, 1995. All other drip pads are new drip pads.
(2) The owner or operator of any drip pad
				  that is inside or under a structure that provides protection from precipitation
				  so that neither run-off nor run-on is generated is not regulated under s.
				  NR 665.0443(5)
				  or (6), as appropriate.
(3) The requirements of this subchapter are
				  not applicable to the management of infrequent and incidental drippage in
				  storage yards provided that the owner or operator maintains and complies with a
				  written contingency plan that describes how the owner or operator will respond
				  immediately to the discharge of the infrequent and incidental drippage. At a
				  minimum, the contingency plan shall describe how the facility will do all of
				  the following:
(a) Clean up the
				  drippage.
(b) Document the cleanup
				  of the drippage.
(c) Retain
				  documents regarding cleanup for 3 years.
(d) Manage the contaminated media in a manner
				  consistent with state rules.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter W - Drip Pads › Section NR 665.0441 - Assessment of existing drip pad integrity

Current through June 24, 2024
(1) For each
				  existing drip pad as defined in s.
				  NR
				  665.0440, the owner or operator shall evaluate the
				  drip pad and determine that it meets all of the requirements of this
				  subchapter, except the requirements for liners and leak detection systems of s.
				  NR
				  665.0443(2). No later than August 1,
				  2017, the owner or operator shall obtain and keep on file at the facility a
				  written assessment of the drip pad, reviewed and certified by a qualified
				  professional engineer that attests to the results of the evaluation. The
				  assessment shall be reviewed, updated and re-certified annually until all
				  upgrades, repairs or modifications necessary to achieve compliance with all of
				  the standards of s.
				  NR
				  665.0443 are complete. The evaluation shall document
				  the extent to which the drip pad meets each of the design and operating
				  standards of s.
				  NR
				  665.0443, except the standards for liners and leak
				  detection systems, specified in s.
				  NR
				  665.0443(2).
(2) The owner or operator shall develop a
				  written plan for upgrading, repairing and modifying the drip pad to meet the
				  requirements of s.
				  NR
				  665.0443(2), and submit the plan to
				  the department no later than 2 years before the date that all repairs, upgrades
				  and modifications are complete. This written plan shall describe all changes to
				  be made to the drip pad in sufficient detail to document compliance with all
				  the requirements of s.
				  NR
				  665.0443. The plan shall be reviewed and certified by
				  a qualified professional engineer.
(3) Upon completion of all upgrades, repairs
				  and modifications, the owner or operator shall submit to the department, the
				  as-built drawings for the drip pad together with a certification by a qualified
				  professional engineer attesting that the drip pad conforms to the
				  drawings.
(4) If the drip pad is
				  found to be leaking or unfit for use, the owner or operator shall comply with
				  the provisions of s.
				  NR
				  665.0443(13) or close the drip pad in
				  accordance with s.
				  NR
				  665.0445.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter W - Drip Pads › Section NR 665.0442 - Design and installation of new drip pads

Current through June 24, 2024
Owners and operators of new drip pads shall ensure that
					 the pads are designed, installed and operated in accordance with one of the
					 following:
(1) All of the applicable
				  requirements of s.
				  NR
				  665.0443 (except 665.0443(1)(d) ), s.
				  NR
				  665.0444 and s.
				  NR
				  665.0445.
(2) All of the applicable requirements of s.
				  NR
				  665.0443 (except 665.0443(2) ), s.
				  NR
				  665.0444 and s.
				  NR
				  665.0445.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter W - Drip Pads › Section NR 665.0443 - Design and operating requirements

Current through June 24, 2024
(1) Drip pads shall
				  comply with all of the following:
(a) Be
				  constructed of non-earthen materials, excluding wood and non-structurally
				  supported asphalt.
(b) Be sloped to
				  free-drain treated wood drippage, rain and other waters, or solutions of
				  drippage and water or other wastes to the associated collection
				  system.
(c) Have a curb or berm
				  around the perimeter.
(d)
1. Have a hydraulic conductivity of less than
				  or equal to 1×10-7 centimeters per second,
				  e.g., existing concrete drip pads shall be sealed, coated or covered with a
				  surface material with a hydraulic conductivity of less than or equal to
				  1×10 
				  -7 centimeters per second such that
				  the entire surface where drippage occurs or may run across is capable of
				  containing the drippage and mixtures of drippage and precipitation, materials
				  or other wastes while being routed to an associated collection system. This
				  surface material shall be maintained free of cracks and gaps that could
				  adversely affect its hydraulic conductivity, and the material shall be
				  chemically compatible with the preservatives that contact the drip pad. The
				  requirements of this provision apply only to existing drip pads and those drip
				  pads for which the owner or operator elects to comply with s.
				  NR
				  665.0442(2) instead of s.
				  NR
				  665.0442(1).
2. The owner or operator shall obtain and
				  keep on file at the facility a written assessment of the drip pad, reviewed and
				  certified by an independent, qualified registered professional engineer that
				  attests to the results of the evaluation. The assessment shall be reviewed,
				  updated and recertified annually. The evaluation shall document the extent to
				  which the drip pad meets the design and operating standards of this section,
				  except for sub. (2).
(e)
				  Be of sufficient structural strength and thickness to prevent failure due to
				  physical contact, climatic conditions, the stress of installation and the
				  stress of daily operations, including variable and moving loads such as vehicle
				  traffic or movement of wood.
Note: The department will generally consider applicable
					 standards established by professional organizations generally recognized by
					 industry such as the American Concrete Institute (ACI) and the American Society
					 of Testing Materials (ASTM) in judging the structural integrity requirement of
					 par. (e).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter W - Drip Pads › Section NR 665.0444 - Inspections

Current through June 24, 2024
(1) During construction or installation,
				  liners, and cover systems (for example, membranes, sheets, or coatings) shall
				  be inspected for uniformity, damage, and imperfections (for example, holes,
				  cracks, thin spots, or foreign materials). Immediately after construction or
				  installation, liners shall be inspected and certified as meeting the
				  requirements of s.
				  NR
				  665.0443 by a qualified professional engineer. The
				  certification shall be maintained at the facility as part of the facility
				  operating record. After installation, liners, and covers shall be inspected to
				  ensure tight seams and joints and the absence of tears, punctures, or
				  blisters.
(2) While a drip pad is
				  in operation, it shall be inspected weekly and after storms to detect evidence
				  of any of the following:
(a) Deterioration,
				  malfunctions or improper operation of run-on and run-off control
				  systems.
(b) The presence of
				  leakage in and proper functioning of the leakage detection system.
(c) Deterioration or cracking of the drip pad
				  surface.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter W - Drip Pads › Section NR 665.0445 - Closure

Current through June 24, 2024
(1) At closure, the owner or operator shall
				  remove or decontaminate all waste residues, contaminated containment system
				  components (such as pads and liners), contaminated subsoils, and structures and
				  equipment contaminated with waste and leakage, and manage them as hazardous
				  waste.
(2) If, after removing or
				  decontaminating all residues and making all reasonable efforts to effect
				  removal or decontamination of contaminated components, subsoils, structures and
				  equipment as required in sub. (1), the owner or operator finds that not all
				  contaminated subsoils can be practically removed or decontaminated, the owner
				  or operator shall close the facility and perform long-term care in accordance
				  with closure and long-term care requirements that apply to landfills (s.
				  NR
				  665.0310 ). For licensed units, the requirement to
				  have a license continues throughout the long-term care period.
(3)
(a) The
				  owner or operator of an existing drip pad, as defined in s.
				  NR
				  665.0440, that does not comply with the liner
				  requirements of s.
				  NR 665.0443(2)
				  (a) shall do all of the following:
1. Include in the closure plan for the drip
				  pad under s.
				  NR
				  665.0112 both a plan for complying with sub. (1) and a
				  contingent plan for complying with sub. (2) in case not all contaminated
				  subsoils can be practicably removed at closure.
2. Prepare a contingent long-term care plan
				  under s.
				  NR
				  665.0118 for complying with sub. (2) in case not all
				  contaminated subsoils can be practicably removed at closure.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter AA - Air Emission Standards for Process Vents › Section NR 665.1030 - Applicability

Current through June 24, 2024
(1) This subchapter applies to owners and
				  operators of facilities that treat, store or dispose of hazardous wastes
				  (except as provided in s.
				  NR
				  665.0001 ).
(2) Except for s.
				  NR 665.1034(4) and
				  (5), this subchapter applies to process vents
				  associated with distillation, fractionation, thin-film evaporation, solvent
				  extraction or air or steam stripping operations that manage hazardous wastes
				  with organic concentrations of at least 10 ppmw, if these operations are
				  conducted in one of the following:
(a) A unit
				  that is subject to the licensing requirements of ch. NR 670.
(b) A unit (including a hazardous waste
				  recycling unit) that is not exempt from licensing under s. NR 662.017 (i.e., a
				  hazardous waste recycling unit that is not a 90-day tank or container) and that
				  is located at a hazardous waste management facility otherwise subject to the
				  licensing requirements of ch. NR 670.
(c) A unit that is exempt from licensing
				  under s. NR 662.017 (i.e., a "90-day" tank or container) and is not a recycling
				  unit under s. NR 661.0006.
Note:
Sections
					 NR
					 665.1032 to 665.1035 apply to process vents on
					 hazardous waste recycling units previously exempt under s. NR 661.0006(3) (a).
					 Other exemptions under ss. NR 661.0004 and 665.0001(3) are not affected by
					 these requirements.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter AA - Air Emission Standards for Process Vents › Section NR 665.1031 - Definitions

Current through June 24, 2024
As used in this subchapter, all terms shall have the
					 meaning given them in s.
					 NR
					 664.1031, ch. 291, Stats., and chs. NR 660 to
					 666.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter AA - Air Emission Standards for Process Vents › Section NR 665.1032 - Standards: process vents

Current through June 24, 2024
(1) The owner or
				  operator of a facility with process vents associated with distillation,
				  fractionation, thin-film evaporation, solvent extraction or air or steam
				  stripping operations managing hazardous wastes with organic concentrations at
				  least 10 ppmw shall do any of the following:
(a) Reduce total organic emissions from all
				  affected process vents at the facility below 1.4 kg/h (3 lb/h) and 2.8 Mg/yr
				  (3.1 tons/yr).
(b) Reduce, by use
				  of a control device, total organic emissions from all affected process vents at
				  the facility by 95 weight percent.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter AA - Air Emission Standards for Process Vents › Section NR 665.1033 - Standards: closed-vent systems and control devices

Current through June 24, 2024
(1)
(a) Owners or operators of closed-vent
				  systems and control devices used to comply with provisions of this chapter
				  shall comply with this section.
(b)
1. The owner or operator of an existing
				  facility who cannot install a closed-vent system and control device to comply
				  with this subchapter on the effective date that the facility becomes subject to
				  this subchapter shall prepare an implementation schedule that includes dates by
				  which the closed-vent system and control device will be installed and in
				  operation. The controls shall be installed as soon as possible, but the
				  implementation schedule may allow up to 30 months after the effective date that
				  the facility becomes subject to this subchapter for installation and
				  startup.
2. Any unit that begins
				  operation after June 1, 1995, and is subject to this subchapter when operation
				  begins, shall comply with the rules immediately (i.e., shall have control
				  devices installed and operating on startup of the affected unit; the 30-month
				  implementation schedule does not apply).
3. The owner or operator of any facility in
				  existence on the effective date of a department rule amendment that renders the
				  facility subject to this subchapter shall comply with this subchapter as soon
				  as practicable but no later than 30 months after the amendment's effective
				  date. When control equipment required by this subchapter can not be installed
				  and begin operation by the effective date of the amendment, the facility owner
				  or operator shall prepare an implementation schedule that includes specific
				  calendar dates for award of contracts or issuance of purchase orders for the
				  control equipment, initiation of on-site installation of the control equipment,
				  completion of the control equipment installation and performance of any testing
				  to demonstrate that the installed equipment meets the applicable standards of
				  this subchapter. The owner or operator shall enter the implementation schedule
				  in the operating record or in a permanent, readily available file located at
				  the facility.
4. Owners and
				  operators of facilities and units that become newly subject to this subchapter
				  after August 1, 2006, due to an action other than those described in subd. 3.
				  shall comply with all applicable requirements immediately (i.e., shall have
				  control devices installed and operating on the date the facility or unit
				  becomes subject to this subchapter; the 30-month implementation schedule does
				  not apply).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter AA - Air Emission Standards for Process Vents › Section NR 665.1034 - Test methods and procedures

Current through June 24, 2024
(1) Each owner or
				  operator subject to this subchapter shall comply with the test methods and
				  procedures requirements in this section.
(2) When a closed-vent system is tested for
				  compliance with no detectable emissions, as required in s.
				  NR
				  665.1033(11), the test shall comply
				  with all of the following requirements:
(a)
				  Monitoring shall comply with Method 21 in appendix A of 40 CFR part 60,
				  incorporated by reference in s.
				  NR
				  660.11.
(b) The detection instrument shall meet the
				  performance criteria of Method 21 in appendix A of 40 CFR part 60, incorporated
				  by reference in s.
				  NR
				  660.11.
(c) The instrument shall be calibrated before
				  use on each day of its use by the procedures in Method 21 in appendix A of 40
				  CFR part 60, incorporated by reference in s.
				  NR
				  660.11.
(d) Calibration gases shall be all of the
				  following:
1. Zero air (less than 10 ppm of
				  hydrocarbon in air).
2. A mixture
				  of methane or n-hexane and air at a concentration of approximately, but less
				  than, 10,000 ppm methane or n-hexane.
(e) Determine the background level according
				  to Method 21 in appendix A of 40 CFR part 60, incorporated by reference in s.
				  NR
				  660.11.
(f) Traverse the instrument probe around all
				  potential leak interfaces as close to the interface as possible as described in
				  Method 21 in appendix A of 40 CFR part 60, incorporated by reference in s.
				  NR
				  660.11.
(g) Compare the arithmetic difference between
				  the maximum concentration indicated by the instrument and the background level
				  with 500 ppm for determining compliance.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter AA - Air Emission Standards for Process Vents › Section NR 665.1035 - Recordkeeping requirements

Current through June 24, 2024
(1)
(a) Each owner or operator subject to this
				  subchapter shall comply with this section.
(b) An owner or operator of more than one
				  hazardous waste management unit subject to this subchapter may comply with the
				  recordkeeping requirements for these hazardous waste management units in one
				  recordkeeping system if the system identifies each record by each hazardous
				  waste management unit.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1050 - Applicability

Current through June 24, 2024
(1) This subchapter applies to owners and
				  operators of facilities that treat, store or dispose of hazardous wastes
				  (except as provided in s.
				  NR
				  665.0001 ).
(2) Except as provided in s.
				  NR
				  665.1064(11), this subchapter applies
				  to equipment that contains or contacts hazardous wastes with organic
				  concentrations of at least 10 percent by weight that are managed in one of the
				  following:
(a) A unit that is subject to the
				  licensing requirements of ch. NR 670.
(b) A unit (including a hazardous waste
				  recycling unit) that is not exempt from licensing under s. NR 662.017 (i.e., a
				  hazardous waste recycling unit that is not a "90-day" tank or container) and
				  that is located at a hazardous waste management facility otherwise subject to
				  the licensing requirements of ch. NR 670.
(c) A unit that is exempt from licensing
				  under s. NR 662.017 (i.e., a "90-day" tank or container) and is not a recycling
				  unit under s. NR 661.0006.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1051 - Definitions

Current through June 24, 2024
As used in this subchapter, all terms shall have the
					 meaning given them in s.
					 NR
					 664.1031, ch. 291, Stats., and chs. NR 660 to
					 666.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1052 - Standards: pumps in light liquid service

Current through June 24, 2024
(1)
(a) Monitor each pump in light liquid service
				  monthly to detect leaks by the methods specified in s.
				  NR
				  665.1063(2), except as provided in
				  subs. (4) to (6).
(b) Check each
				  pump in light liquid service by visual inspection each calendar week for
				  indications of liquids dripping from the pump seal.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1053 - Standards: compressors

Current through June 24, 2024
(1) Equip each
				  compressor with a seal system that includes a barrier fluid system and that
				  prevents leakage of total organic emissions to the atmosphere, except as
				  provided in subs. (8) and (9).
(2)
				  Each compressor seal system as required in sub. (1) shall be one of the
				  following:
(a) Operated with the barrier
				  fluid at a pressure that is at all times greater than the compressor stuffing
				  box pressure.
(b) Equipped with a
				  barrier fluid system that is connected by a closed-vent system to a control
				  device that complies with s.
				  NR
				  665.1060.
(c) Equipped with a system that purges the
				  barrier fluid into a hazardous waste stream with no detectable emissions to
				  atmosphere.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1054 - Standards: pressure relief devices in gas or vapor service

Current through June 24, 2024
(1) Except during
				  pressure releases, operate each pressure relief device in gas or vapor service
				  with no detectable emissions, as indicated by an instrument reading of less
				  than 500 ppm above background, measured by the method specified in s.
				  NR
				  665.1063(3).
(2)
(a)
				  After each pressure release, return the pressure relief device to a condition
				  of no detectable emissions, as indicated by an instrument reading of less than
				  500 ppm above background, as soon as practicable, but no later than 5 calendar
				  days after each pressure release, except as provided in s.
				  NR
				  665.1059.
(b) No later than 5 calendar days after the
				  pressure release, monitor the pressure relief device to confirm the condition
				  of no detectable emissions, as indicated by an instrument reading of less than
				  500 ppm above background, measured by the method specified in s.
				  NR
				  665.1063(3).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1055 - Standards: sampling connection systems

Current through June 24, 2024
(1) Equip each
				  sampling connection system with a closed-purge, closed-loop or closed-vent
				  system. The system shall collect the sample purge for return to the process or
				  for routing to the appropriate treatment system. Gases displaced during filling
				  of the sample container are not required to be collected or captured.
(2) Each closed-purge, closed-loop or
				  closed-vent system required in sub. (1) shall meet one of the following
				  requirements:
(a) It returns the purged
				  process fluid directly to the process line.
(b) It collects and recycles the purged
				  process fluid.
(c) It is designed
				  and operated to capture and transport all the purged process fluid to a waste
				  management unit that complies with the applicable requirements of ss.
				  NR 665.1085 to
				  665.1087 or a control device that
				  complies with s.
				  NR
				  665.1060.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1056 - Standards: open-ended valves or lines

Current through June 24, 2024
(1)
(a) Equip each open-ended valve or line with
				  a cap, blind flange, plug or a second valve.
(b) The cap, blind flange, plug or second
				  valve shall seal the open end at all times except during operations requiring
				  hazardous waste stream flow through the open-ended valve or line.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1057 - Standards: valves in gas or vapor service or in light liquid service

Current through June 24, 2024
(1)
				  Monitor each valve in gas or vapor or light liquid service monthly to detect
				  leaks by the methods specified in s.
				  NR
				  665.1063(2) and comply with subs. (2)
				  to (5), except as provided in subs. (6) to (8) and ss.
				  NR
				  665.1061 and 665.1062.
(2) If an instrument reading of 10,000 ppm or
				  greater is measured, a leak is detected.
(3)
(a) Any
				  valve for which a leak is not detected for 2 successive months may be monitored
				  the first month of every succeeding quarter, beginning with the next quarter,
				  until a leak is detected.
(b) If a
				  leak is detected, monitor the valve monthly until a leak is not detected for 2
				  successive months.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1058 - Standards: pumps and valves in heavy liquid service, pressure relief devices in light liquid or heavy liquid service and flanges and other connectors

Current through June 24, 2024
(1)
				  Monitor pumps and valves in heavy liquid service, pressure relief devices in
				  light liquid or heavy liquid service and flanges and other connectors within 5
				  days by the method specified in s.
				  NR
				  665.1063(2) if evidence of a
				  potential leak is found by visual, audible, olfactory or any other detection
				  method.
(2) If an instrument
				  reading of 10,000 ppm or greater is measured, a leak is detected.
(3)
(a)
				  When a leak is detected, repair it as soon as practicable, but not later than
				  15 calendar days after it is detected, except as provided in s.
				  NR
				  665.1059.
(b) Make the first attempt at repair no later
				  than 5 calendar days after each leak is detected.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1059 - Standards: delay of repair

Current through June 24, 2024
(1) Delay of repair
				  of equipment for which leaks have been detected shall be allowed if the repair
				  is technically infeasible without a hazardous waste management unit shutdown.
				  In such a case, repair the equipment before the end of the next hazardous waste
				  management unit shutdown.
(2) Delay
				  of repair of equipment for which leaks have been detected shall be allowed for
				  equipment that is isolated from the hazardous waste management unit and that
				  does not continue to contain or contact hazardous waste with organic
				  concentrations at least 10 percent by weight.
(3) Delay of repair for valves shall be
				  allowed if all of the following conditions are met:
(a) The owner or operator determines that
				  emissions of purged material resulting from immediate repair are greater than
				  the emissions likely to result from delay of repair.
(b) When repair procedures are effected,
				  collect and destroy or recover the purged material in a control device
				  complying with s.
				  NR
				  665.1060.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1060 - Standards: closed-vent systems and control devices

Current through June 24, 2024
(1) Owners and
				  operators of closed-vent systems and control devices subject to this subchapter
				  shall comply with s.
				  NR
				  665.1033.
(2)
(a) The
				  owner or operator of an existing facility who can not install a closed-vent
				  system and control device to comply with this subchapter on the effective date
				  that the facility becomes subject to this subchapter shall prepare an
				  implementation schedule that includes dates by which the closed-vent system and
				  control device will be installed and in operation. Install the controls as soon
				  as possible, but the implementation schedule may allow up to 30 months after
				  the effective date that the facility becomes subject to this subchapter for
				  installation and startup.
(b) Any
				  units that begin operation after June 1, 1995, and are subject to this
				  subchapter when operation begins, shall comply with the rules immediately
				  (i.e., shall have control devices installed and operating on startup of the
				  affected unit; the 30-month implementation schedule does not apply).
(c) The owner or operator of any facility in
				  existence on the effective date of a department rule amendment that renders the
				  facility subject to this subchapter shall comply with this subchapter as soon
				  as practicable but no later than 30 months after the amendment's effective
				  date. When control equipment required by this subchapter can not be installed
				  and begin operation by the effective date of the amendment, prepare an
				  implementation schedule that includes specific calendar dates for award of
				  contracts or issuance of purchase orders for the control equipment, initiation
				  of on-site installation of the control equipment, completion of the control
				  equipment installation and performance of any testing to demonstrate that the
				  installed equipment meets the applicable standards of this subchapter. Enter
				  the implementation schedule in the operating record or in a permanent, readily
				  available file located at the facility.
(d) Owners and operators of facilities and
				  units that become newly subject to this subchapter after August 1, 2006 due to
				  an action other than those described in par. (c) shall comply with all
				  applicable requirements immediately (i.e., shall have control devices installed
				  and operating on the date the facility or unit becomes subject to this
				  subchapter; the 30-month implementation schedule does not apply).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1061 - Alternative standards for valves in gas or vapor service or in light liquid service: percentage of valves allowed to leak

Current through June 24, 2024
(1) An owner or
				  operator subject to s.
				  NR
				  665.1057 may elect to have all valves within a
				  hazardous waste management unit comply with an alternative standard which
				  allows no greater than 2 percent of the valves to leak.
(2) An owner or operator who decides to
				  comply with the alternative standard of allowing 2 percent of valves to leak
				  shall meet all of the following requirements:
(a) Conduct a performance test as specified
				  in sub. (3) initially upon designation, annually and at other times requested
				  by the department.
(b) If a valve
				  leak is detected, repair it according to s.
				  NR
				  665.1057(4) and (5).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1062 - Alternative standards for valves in gas or vapor service or in light liquid service: skip period leak detection and repair

Current through June 24, 2024
(1) An owner or
				  operator subject to s.
				  NR
				  665.1057 may elect for all valves within a hazardous
				  waste management unit to comply with one of the alternative work practices
				  specified in sub. (2) (b) and (c).
(2)
(a) An
				  owner or operator shall comply with the requirements for valves in s.
				  NR
				  665.1057, except as described in pars. (b) and
				  (c).
(b) After 2 consecutive
				  quarterly leak detection periods with the percentage of valves leaking equal to
				  or less than 2 percent, an owner or operator may begin to skip one of the
				  quarterly leak detection periods (i.e., monitor for leaks once every 6 months)
				  for the valves subject to s.
				  NR
				  665.1057.
(c) After 5 consecutive quarterly leak
				  detection periods with the percentage of valves leaking equal to or less than 2
				  percent, an owner or operator may begin to skip 3 of the quarterly leak
				  detection periods (i.e., monitor for leaks once every year) for the valves
				  subject to s.
				  NR
				  665.1057.
(d) If the percentage of valves leaking is
				  greater than 2 percent, the owner or operators shall monitor monthly in
				  compliance with s.
				  NR
				  665.1057, but may again elect to use this section
				  after meeting s.
				  NR
				  665.1057(3) (a).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1063 - Test methods and procedures

Current through June 24, 2024
(1) Each owner or
				  operator subject to this subchapter shall comply with the test methods and
				  procedures requirements in this section.
(2) Leak detection monitoring, as required in
				  ss.
				  NR
				  665.1052 to 665.1062, shall comply with all of the
				  following requirements:
(a) Monitoring shall
				  comply with Method 21 in appendix A of 40 CFR part 60, incorporated by
				  reference in s.
				  NR
				  660.11.
(b) The detection instrument shall meet the
				  performance criteria of Method 21.
(c) Calibrate the instrument before use on
				  each day of its use by the procedures in Method 21.
(d) Calibration gases shall be all of the
				  following:
1. Zero air (less than 10 ppm of
				  hydrocarbon in air).
2. A mixture
				  of methane or n-hexane and air at a concentration of approximately, but less
				  than, 10,000 ppm methane or n-hexane.
(e) Traverse the instrument probe around all
				  potential leak interfaces as close to the interface as possible as described in
				  Method 21.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter BB - Air Emission Standards for Equipment Leaks › Section NR 665.1064 - Recordkeeping requirements

Current through June 24, 2024
(1)
(a) Each owner or operator subject to this
				  subchapter shall comply with this section.
(b) An owner or operator of more than one
				  hazardous waste management unit subject to this subchapter may comply with the
				  recordkeeping requirements for these hazardous waste management units in one
				  recordkeeping system if the system identifies each record by each hazardous
				  waste management unit.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1080 - Applicability

Current through June 24, 2024
(1) This subchapter applies to owners and
				  operators of all facilities that treat, store or dispose of hazardous waste in
				  containers, tanks or surface impoundments subject to subch. I, J or K except as
				  s.
				  NR
				  665.0001 and sub. (2) provide otherwise.
(2) This subchapter does not apply to the
				  following waste management units at the facility:
(a) A waste management unit that holds
				  hazardous waste placed in the unit before June 1, 1998, and in which no
				  hazardous waste is added to the unit on or after June 1, 1998.
(b) A container that has a design capacity
				  less than or equal to 0.1 m3.
(c) A tank in which an owner or operator has
				  stopped adding hazardous waste and the owner or operator has begun implementing
				  or completed closure pursuant to an approved closure plan.
(d) A surface impoundment in which an owner
				  or operator has stopped adding hazardous waste (except to implement an approved
				  closure plan) and the owner or operator has begun implementing or completed
				  closure pursuant to an approved closure plan.
(e) A waste management unit that is used
				  solely for on-site treatment or storage of hazardous waste that is placed in
				  the unit as a result of implementing remedial activities required under the
				  corrective action authorities of
				  42
				  USC 6924(u) or (v),
				  6928(h)
				  or 9601 to
				  9675,
				  similar federal authorities or s.
				  291.37 or
				  292.11,
				  Stats.
(f) A waste management unit
				  that is used solely for the management of radioactive mixed waste according to
				  all applicable regulations under the authority of
				  42 USC
				  2011 to 2297 and
				  10101 to
				  10270.
Note: The U.S. code (USC) cites in this paragraph are also
					 known as the federal atomic energy act and the federal nuclear waste policy
					 act, respectively.
(g) A
				  hazardous waste management unit that the owner or operator certifies is
				  equipped with and operating air emission controls according to 40 CFR part 60,
				  61 or 63, or to corresponding provisions of ch. NR 440, subch. III of ch. NR
				  446 and chs.
				  NR
				  447 to
				  469. For the purpose of complying
				  with this paragraph, a tank for which the air emission control includes an
				  enclosure, as opposed to a cover, shall be in compliance with the enclosure and
				  control device requirements of s.
				  NR
				  665.1085(9), except as provided in s.
				  NR 665.1083(3)
				  (e).
(h) A tank that has a process vent as defined
				  in s.
				  NR
				  664.1031.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1082 - Schedule for implementation of air emission standards

Current through June 24, 2024
(1) Owners or
				  operators of facilities existing on June 1, 1998 and subject to subch. I, J or
				  K shall meet all of the following requirements:
(a) Install and begin operation of all
				  control equipment or waste management units required to comply with this
				  subchapter and complete modifications of production or treatment processes to
				  satisfy exemption criteria according to s.
				  NR
				  665.1083(3) by June 1, 1998, except
				  as provided for in par. (b).
(b)
				  When control equipment or waste management units required to comply with this
				  subchapter cannot be installed and in operation or modifications of production
				  or treatment processes to satisfy exemption criteria according to s.
				  NR
				  665.1083(3) cannot be completed by
				  June 1, 1998, the owner or operator shall do all of the following:
1. Install and begin operation of the control
				  equipment and waste management units, and complete modifications of production
				  or treatment processes as soon as possible but no later than June 1,
				  1999.
2. Prepare an implementation
				  schedule that includes specific calendar dates for award of contracts or
				  issuance of purchase orders for control equipment, waste management units and
				  production or treatment process modifications; initiation of on-site
				  installation of control equipment or waste management units, and modifications
				  of production or treatment processes; completion of control equipment or waste
				  management unit installation, and production or treatment process
				  modifications; and performance of testing to demonstrate that the installed
				  equipment or waste management units, and modified production or treatment
				  processes meet the applicable standards of this subchapter.
3. For facilities subject to the
				  recordkeeping requirements of s.
				  NR 665.0073, the
				  owner or operator shall enter the implementation schedule specified in subd. 2.
				  in the operating record no later than June 1, 1998.
4. For facilities not subject to s.
				  NR 665.0073, the
				  owner or operator shall enter the implementation schedule specified in subd. 2.
				  in a permanent, readily available file located at the facility no later than
				  June 1, 1998.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1084 - Waste determination procedures

Current through June 24, 2024
(1) PROCEDURE TO
				  DETERMINE AVERAGE VO CONCENTRATION OF A HAZARDOUS WASTE AT THE POINT OF WASTE
				  ORIGINATION.
(a) An owner or operator shall
				  determine the average VO concentration at the point of waste origination for
				  each hazardous waste placed in a waste management unit exempted under s.
				  NR 665.1083(3) (a)
				   from using air emission controls according
				  to the standards in ss.
				  NR 665.1085 to
				  665.1088, as applicable to the waste management unit. Make the determinations
				  according to all of the following:
1. Make an
				  initial determination of the average VO concentration of the waste stream
				  before the first time any portion of the material in the hazardous waste stream
				  is placed in a waste management unit exempted under s.
				  NR 665.1083(3)
				  (a) from using air emission controls, and
				  thereafter make an initial determination of the average VO concentration of the
				  waste stream for each averaging period that a hazardous waste is managed in the
				  unit.
2. Perform a new waste
				  determination whenever changes to the source generating the waste stream are
				  reasonably likely to cause the average VO concentration of the hazardous waste
				  to increase to a level that is equal to or greater than the VO concentration
				  limit in s.
				  NR 665.1083(3)
				  (a).