reglab/statecodes huggingface dataset:
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1085 - Standards: tanks

Current through June 24, 2024
(1) This section applies to the control of
				  air pollutant emissions from tanks for which s.
				  NR
				  665.1083(2) references the use of
				  this section for the air emission control.
(2) The owner or operator shall control air
				  pollutant emissions from each tank subject to this section according to one of
				  the following requirements, as applicable:
(a)
				  For a tank that manages hazardous waste that meets all of the following
				  conditions, control air pollutant emissions from the tank according to the Tank
				  Level 1 controls specified in sub. (3) or the Tank Level 2 controls specified
				  in sub. (4):
1. The hazardous waste in the
				  tank has a maximum organic vapor pressure which is less than the maximum
				  organic vapor pressure limit for the tank's design capacity category as
				  follows:
a. For a tank design capacity equal
				  to or greater than 151 m3, the maximum organic vapor
				  pressure limit for the tank is 5.2 kPa.
b. For a tank design capacity equal to or
				  greater than 75 m3 but less than 151
				  m3, the maximum organic vapor pressure limit for the
				  tank is 27.6 kPa.
c. For a tank
				  design capacity less than 75 m3, the maximum organic
				  vapor pressure limit for the tank is 76.6 kPa.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1086 - Standards: surface impoundments

Current through June 24, 2024
(1) This section
				  applies to the control of air pollutant emissions from surface impoundments for
				  which s.
				  NR
				  665.1083(2) references the use of
				  this section for the air emission control.
(2) The owner or operator shall control air
				  pollutant emissions from the surface impoundment by installing and operating
				  any of the following:
(a) A floating membrane
				  cover according to sub. (3).
(b) A
				  cover that is vented through a closed-vent system to a control device according
				  to sub. (4).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1087 - Standards: containers

Current through June 24, 2024
(1) APPLICABILITY.
				  This section applies to the control of air pollutant emissions from containers
				  for which s.
				  NR
				  665.1083(2) references the use of
				  this section for the air emission control.
(2) GENERAL REQUIREMENTS.
(a) The owner or operator shall control air
				  pollutant emissions from each container subject to this section according to
				  the following requirements, as applicable to the container, except when the
				  special provisions for waste stabilization processes specified in par. (b)
				  apply to the container.
1. For a container
				  having a design capacity greater than 0.1 m 3 and less than or equal to 0.46 m
				  3, control air pollutant emissions from the container according to the
				  Container Level 1 standards in sub. (3).
2. For a container having a design capacity
				  greater than 0.46 m 3 that is not in light material service, control air
				  pollutant emissions from the container according to the Container Level 1
				  standards in sub. (3).
3. For a
				  container having a design capacity greater than 0.46 m 3 that is in light
				  material service, control air pollutant emissions from the container according
				  to the Container Level 2 standards in sub. (4).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1088 - Standards: closed-vent systems and control devices

Current through June 24, 2024
(1) This section
				  applies to each closed-vent system and control device installed and operated by
				  the owner or operator to control air emissions according to the standards of
				  this subchapter.
(2) The
				  closed-vent system shall meet all of the following requirements:
(a) The closed-vent system shall route the
				  gases, vapors and fumes emitted from the hazardous waste in the waste
				  management unit to a control device that meets sub. (3).
(b) Design and operate the closed-vent system
				  according to s.
				  NR
				  665.1033(10).
(c) In the case when the closed-vent system
				  includes bypass devices that could be used to divert the gas or vapor stream to
				  the atmosphere before entering the control device, equip each bypass device
				  with either a flow indicator as specified in subd. 1. or a seal or locking
				  device as specified in subd. 2. For the purpose of complying with this
				  paragraph, low leg drains, high point bleeds, analyzer vents, open-ended valves
				  or lines, spring-loaded pressure relief valves and other fittings used for
				  safety purposes are not bypass devices.
1. If
				  a flow indicator is used to comply with this paragraph, install the indicator
				  at the inlet to the bypass line used to divert gases and vapors from the
				  closed-vent system to the atmosphere at a point upstream of the control device
				  inlet. For this paragraph, a flow indicator means a device which indicates the
				  presence of either gas or vapor flow in the bypass line.
2. If a seal or locking device is used to
				  comply with this paragraph, place the device on the mechanism by which the
				  bypass device position is controlled (e.g., valve handle, damper lever) when
				  the bypass device is in the closed position such that the bypass device cannot
				  be opened without breaking the seal or removing the lock. Examples of the
				  devices include, but are not limited to, a car-seal or a lock-and-key
				  configuration valve. Visually inspect the seal or closure mechanism at least
				  once every month to verify that the bypass mechanism is maintained in the
				  closed position.
(d)
				  Inspect and monitor the closed-vent system according to s.
				  NR
				  665.1033(11).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1089 - Inspection and monitoring requirements

Current through June 24, 2024
(1) The owner or
				  operator shall inspect and monitor air emission control equipment used to
				  comply with this subchapter according to the applicable requirements in ss.
				  NR 665.1085 to
				  665.1088.
(2) The owner or operator shall develop and
				  implement a written plan and schedule to perform the inspections and monitoring
				  required by sub. (1). The owner or operator shall incorporate this plan and
				  schedule into the facility inspection plan required under s.
				  NR
				  665.0015.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter CC - Air Emission Standards for Tanks, Surface Impoundments and Containers › Section NR 665.1090 - Recordkeeping requirements

Current through June 24, 2024
(1) Each owner or
				  operator of a facility subject to requirements in this subchapter shall record
				  and maintain the information specified in subs. (2) to (10), as applicable to
				  the facility. Except for air emission control equipment design documentation
				  and information required by subs. (9) and (10), maintain records required by
				  this section in the operating record for a minimum of 3 years. Maintain air
				  emission control equipment design documentation in the operating record until
				  the air emission control equipment is replaced or otherwise no longer in
				  service. Maintain information required by subs. (9) and (10) in the operating
				  record for as long as the waste management unit is not using air emission
				  controls specified in ss.
				  NR 665.1085 to
				  according 665.1088 to the conditions in s.
				  NR
				  665.1080(4) or (2) (g),
				  respectively.
(2) The owner or
				  operator of a tank using air emission controls according to s.
				  NR 665.1085
				  shall prepare and maintain records for the tank that include all of the
				  following information:
(a) For each tank
				  using air emission controls according to s.
				  NR 665.1085,
				  record all of the following:
1. A tank
				  identification number (or other unique identification description selected by
				  the owner or operator).
2. A record
				  for each inspection required by s.
				  NR 665.1085 that
				  includes all of the following information:
a.
				  Date inspection was conducted.
b.
				  For each defect detected during the inspection, the location of the defect, a
				  description of the defect, the date of detection and corrective action taken to
				  repair the defect. In the event that repair of the defect is delayed according
				  to s.
				  NR 665.1085,
				  also record the reason for the delay and the date that completion of repair of
				  the defect is expected.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter DD - Containment Buildings › Section NR 665.1100 - Applicability

Current through June 24, 2024
The requirements of this subchapter apply to owners or
					 operators who store or treat hazardous waste in units designed and operated
					 under s.
					 NR
					 665.1101. The owner or operator is not subject to the
					 definition of land disposal in s.
					 NR
					 668.02(3) provided that the unit
					 complies with all of the following:
(1) The unit is a completely enclosed,
				  self-supporting structure that is designed and constructed of manmade materials
				  of sufficient strength and thickness to support themselves, the waste contents
				  and any personnel and heavy equipment that operate within the unit, and to
				  prevent failure due to pressure gradients, settlement, compression, uplift,
				  physical contact with the hazardous wastes to which they are exposed, climatic
				  conditions and the stresses of daily operation, including the movement of heavy
				  equipment within the unit and contact of the equipment with containment
				  walls.
(2) The unit has a primary
				  barrier that is designed to be sufficiently durable to withstand the movement
				  of personnel and handling equipment within the unit.
(3) If the unit is used to manage liquids, it
				  has all of the following:
(a) A primary
				  barrier designed and constructed of materials to prevent migration of hazardous
				  constituents into the barrier.
(b)
				  A liquid collection system designed and constructed of materials to minimize
				  the accumulation of liquid on the primary barrier.
(c) A secondary containment system designed
				  and constructed of materials to prevent migration of hazardous constituents
				  into the barrier, with a leak detection and liquid collection system capable of
				  detecting, collecting and removing leaks of hazardous constituents at the
				  earliest possible time.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter DD - Containment Buildings › Section NR 665.1101 - Design and operating standards

Current through June 24, 2024
(1) All containment
				  buildings shall comply with all of the following design standards:
(a) The containment building shall be
				  completely enclosed with a floor, walls and a roof to prevent exposure to the
				  elements, (e.g., precipitation, wind, run-on), and to assure containment of
				  managed wastes.
(b) The floor and
				  containment walls of the unit, including the secondary containment system if
				  required under sub. (2), shall be designed and constructed of materials of
				  sufficient strength and thickness to support themselves, the waste contents and
				  any personnel and heavy equipment that operate within the unit, and to prevent
				  failure due to pressure gradients, settlement, compression, uplift, physical
				  contact with the hazardous wastes to which they are exposed, climatic
				  conditions and the stresses of daily operation, including the movement of heavy
				  equipment within the unit and contact of the equipment with containment walls.
				  The unit shall be designed so that it has sufficient structural strength to
				  prevent collapse or other failure. All surfaces to be in contact with hazardous
				  wastes shall be chemically compatible with those wastes. The department will
				  consider standards established by professional organizations generally
				  recognized by the industry such as the American Concrete Institute (ACI) and
				  the American Society of Testing Materials (ASTM) in judging the structural
				  integrity requirements of this paragraph. If appropriate to the nature of the
				  waste management operation to take place in the unit, an exception to the
				  structural strength requirement may be made for lightweight doors and windows
				  that meet both of the following criteria:
1.
				  They provide an effective barrier against fugitive dust emissions under sub.
				  (3) (a) 4.
2. The unit is designed
				  and operated in a fashion that assures that wastes will not actually come in
				  contact with these openings.
(c) Incompatible hazardous wastes or
				  treatment reagents may not be placed in the unit or its secondary containment
				  system if they could cause the unit or secondary containment system to leak,
				  corrode or otherwise fail.
(d) A
				  containment building shall have a primary barrier designed to withstand the
				  movement of personnel, waste and handling equipment in the unit during the
				  operating life of the unit and appropriate for the physical and chemical
				  characteristics of the waste to be managed.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter DD - Containment Buildings › Section NR 665.1102 - Closure and long-term care

Current through June 24, 2024
(1) At closure of a
				  containment building, the owner or operator shall remove or decontaminate all
				  waste residues, contaminated containment system components (liners, etc.),
				  contaminated subsoils and structures and equipment contaminated with waste and
				  leachate, and manage them as hazardous waste unless s. NR 661.0003(4) applies.
				  The closure plan, closure activities, cost estimates for closure and financial
				  responsibility for containment buildings shall meet all of the requirements
				  specified in subchs. G and H.
(2)
				  If, after removing or decontaminating all residues and making all reasonable
				  efforts to effect removal or decontamination of contaminated components,
				  subsoils, structures and equipment as required in sub. (1), the owner or
				  operator finds that not all contaminated subsoils can be practicably removed or
				  decontaminated, the owner or operator shall close the facility and perform
				  long-term care in accordance with the closure and long-term care requirements
				  that apply to landfills (s.
				  NR
				  665.0310 ). In addition, for the purposes of closure,
				  long-term care and financial responsibility, the containment building is then
				  considered to be a landfill, and the owner or operator shall meet all of the
				  requirements for landfills specified in subchs. G and H.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter EE - Hazardous Waste Munitions and Explosives Storage › Section NR 665.1200 - Applicability

Current through June 24, 2024
The requirements of this subchapter apply to owners or
					 operators who store munitions and explosive hazardous wastes, except as s.
					 NR
					 665.0001 provides otherwise.
Depending on explosive hazards, hazardous waste munitions
						and explosives may also be managed in other types of storage units, including
						containment buildings (subch. DD), tanks (subch. J) or containers (subch. I).
						See s.
						NR
						666.205 for storage of waste military munitions.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter EE - Hazardous Waste Munitions and Explosives Storage › Section NR 665.1201 - Design and operating standards

Current through June 24, 2024
(1) Hazardous waste
				  munitions and explosives storage units shall be designed and operated with
				  containment systems, controls and monitoring, that do all of the following:
(a) Minimize the potential for detonation or
				  other means of release of hazardous waste, hazardous constituents, hazardous
				  decomposition products or contaminated run-off to the soil, groundwater,
				  surface water and atmosphere.
(b)
				  Provide a primary barrier, which may be a container (including a shell) or
				  tank, designed to contain the hazardous waste.
(c) For wastes stored outdoors, provide that
				  the waste and containers will not be in standing precipitation.
(d) For liquid wastes, provide a secondary
				  containment system that assures that any released liquids are contained and
				  promptly detected and removed from the waste area, or vapor detection system
				  that assures that any released liquids or vapors are promptly detected and an
				  appropriate response taken (e.g., additional containment, such as overpacking,
				  or removal from the waste area).
(e) Provide monitoring and inspection
				  procedures that assure the controls and containment systems are working as
				  designed and that releases that may adversely impact human health or the
				  environment are not escaping from the unit.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Subchapter EE - Hazardous Waste Munitions and Explosives Storage › Section NR 665.1202 - Closure and long-term care

Current through June 24, 2024
(1) At closure of a
				  magazine or unit which stored hazardous waste under this subchapter, the owner
				  or operator shall remove or decontaminate all waste residues, contaminated
				  containment system components, contaminated subsoils, and structures and
				  equipment contaminated with waste, and manage them as hazardous waste unless s.
				  NR 661.0003(4) applies. The closure plan, closure activities, cost estimates
				  for closure and financial responsibility for magazines or units shall meet all
				  of the requirements specified in subchs. G and H, except that the owner or
				  operator may defer closure of the unit as long as it remains in service as a
				  munitions or explosives magazine or storage unit.
(2) If, after removing or decontaminating all
				  residues and making all reasonable efforts to effect removal or decontamination
				  of contaminated components, subsoils, structures and equipment as required in
				  sub. (1), the owner or operator finds that not all contaminated subsoils can be
				  practicably removed or decontaminated, the owner or operator shall close the
				  facility and perform long-term care in accordance with the closure and
				  long-term care requirements that apply to landfills (s.
				  NR
				  664.0310 ).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Appendix III - EPA INTERIM PRIMARY DRINKING WATER STANDARDS

Current through June 24, 2024
Parameter
Maximum level ( mg/L)
Arsenic . . . . . . . . . . . . . . . . . . . . . .
0.05
Barium . . . . . . . . . . . . . . . . . . . . . .
1.0
Cadmium . . . . . . . . . . . . . . . . . . . .
0.01
Chromium . . . . . . . . . . . . . . . . . . .
0.05
Fluoride . . . . . . . . . . . . . . . . . . . . .
1.4-2.4
Lead . . . . . . . . . . . . . . . . . . . . . . . .
0.05
Mercury . . . . . . . . . . . . . . . . . . . . .
0.002
Nitrate (as N) . . . . . . . . . . . . . . . . .
10
Selenium . . . . . . . . . . . . . . . . . . . .
0.01
Silver . . . . . . . . . . . . . . . . . . . . . . .
0.05
Endrin . . . . . . . . . . . . . . . . . . . . . .
0.0002
Lindane . . . . . . . . . . . . . . . . . . . . .
0.004
Methoxychlor . . . . . . . . . . . . . . . . .
0.1
Toxaphene . . . . . . . . . . . . . . . . . . .
0.005
2,4-D . . . . . . . . . . . . . . . . . . . . . . .
0.1
2,4,5-TP Silvex . . . . . . . . . . . . . . .
0.01
Radium . . . . . . . . . . . . . . . . . . . . . .
5 pCi/L
Gross Alpha . . . . . . . . . . . . . . . . . .
15 pCi/L
Gross Beta . . . . . . . . . . . . . . . . . . .
4 millirem/yr
Turbidity . . . . . . . . . . . . . . . . . . . .
1/TU
Coliform Bacteria . . . . . . . . . . . . .
1/100 ml
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 665 - Interim License Hazardous Waste Treatment, Storage And Disposal Facility Standards › Appendix IV - TESTS FOR SIGNIFICANCE

Current through June 24, 2024
As required in s.
				  NR
				  665.0093(2) the owner or operator
				  shall use the Student's t-test to determine statistically significant changes
				  in the concentration or value of an indicator parameter in periodic groundwater
				  samples when compared to the initial background concentration or value of that
				  indicator parameter. The comparison shall consider individually each of the
				  wells in the monitoring system. For 3 of the indicator parameters (specific
				  conductance, total organic carbon and total organic halogen) a single-tailed
				  Student's t-test shall be used to test at the 0.01 level of significance for
				  significant increases over background. The difference test for pH shall be a
				  2-tailed Student's t-test at the overall 0.01 level of significance.
The student's t-test involves calculation of the value of a
				  t-statistic for each comparison of the mean (average) concentration or value
				  (based on a minimum of 4 replicate measurements) of an indicator parameter with
				  its initial background concentration or value. The calculated value of the
				  t-statistic shall then be compared to the value of the t-statistic found in a
				  table for t-test of significance at the specified level of significance. A
				  calculated value of t which exceeds the value of t found in the table indicates
				  a statistically significant change in the concentration or value of the
				  indicator parameter.
Formulae for calculation of the t-statistic and tables for
				  t-test of significance can be found in most introductory statistics
				  texts.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter C - Recyclable Materials Used in a Manner Constituting Disposal › Section NR 666.020 - Applicability

Current through June 24, 2024
(1) This subchapter applies to recyclable
				  materials that are applied to or placed on the land in one of the following
				  ways:
(a) Without mixing with any other
				  substance.
(b) After mixing or
				  combination with any other substance or substances. These materials will be
				  referred to throughout this subchapter as "materials used in a manner that
				  constitutes disposal".
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter C - Recyclable Materials Used in a Manner Constituting Disposal › Section NR 666.021 - Standards applicable to generators and transporters of materials used in a manner that constitutes disposal

Current through June 24, 2024
Generators and transporters of materials that are used in a
					 manner that constitutes disposal are subject to the applicable requirements of
					 chs. NR 662 and 663, and the notification requirement under s.
					 NR
					 660.07.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter C - Recyclable Materials Used in a Manner Constituting Disposal › Section NR 666.022 - Standards applicable to storers of materials that are to be used in a manner that constitutes disposal who are not the ultimate users

Current through June 24, 2024
Owners or operators of facilities that store recyclable
					 materials that are to be used in a manner that constitutes disposal, but who
					 are not the ultimate users of the materials, are regulated under all applicable
					 provisions of subchs. A to L of ch. NR 664, all applicable provisions of
					 subchs. A to L of ch. NR 665, all applicable provisions of subchs. A to J of
					 ch. NR 667, all applicable provisions of NR 670 and the notification
					 requirement under s.
					 NR
					 660.07.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter C - Recyclable Materials Used in a Manner Constituting Disposal › Section NR 666.023 - Standards applicable to users of materials that are used in a manner that constitutes disposal

Current through June 24, 2024
(1) Owners or operators of facilities that
				  use recyclable materials in a manner that constitutes disposal are regulated
				  under all applicable provisions of subchs. A to N of chs.
				  NR 664 and 665, and chs.
				  NR 668 and 670 and the
				  notification requirement under s.
				  NR
				  660.07. (These requirements do not apply to products
				  which contain these recyclable materials under the provisions of s.
				  NR
				  666.020(2).)
(2) The use of waste or used oil or other
				  material, which is contaminated with dioxin or any other hazardous waste, for
				  dust suppression or road treatment is prohibited.
See s.
						NR
						679.82 regarding used oil as a dust
						suppressant.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter F - Recyclable Materials Used for Precious Metal Recovery › Section NR 666.070 - Applicability and requirements

Current through June 24, 2024
(1) This subchapter
				  applies to recyclable materials that are reclaimed to recover economically
				  significant amounts of gold, silver, platinum, palladium, iridium, osmium,
				  rhodium, ruthenium or any combination of these.
(2) Persons who generate, transport or store
				  recyclable materials that are regulated under this subchapter are subject to
				  all of the following requirements:
(a)
				  Notification requirements under s.
				  NR
				  660.07.
(b) Subchapter B of ch. NR 662 for
				  generators, ss.
				  NR 663.20 and
				  663.21 for transporters and ss.
				  NR
				  665.0071 and 665.0072 for persons who store.
Note:
Hazardous waste transportation licenses
					 are not required for transporting only recyclable materials regulated under
					 this subchapter.
(c) For
				  precious metals exported to or imported from other countries for recovery,
				  subch. H of ch. NR 662 and s.
				  NR
				  665.0012.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.101 - Management prior to burning

Current through June 24, 2024
(1) GENERATORS.
				  Generators of hazardous waste that is burned in a boiler or industrial furnace
				  are subject to ch. NR 662.
(2)
				  TRANSPORTERS. Transporters of hazardous waste that is burned in a boiler or
				  industrial furnace are subject to ch. NR 663.
(3) STORAGE AND TREATMENT FACILITIES.
(a) Owners and operators of facilities that
				  store or treat hazardous waste that is burned in a boiler or industrial furnace
				  are subject to the applicable provisions of chs.
				  NR 664, 665, 667 and 670, except
				  as provided by sub. (3) (b). These standards apply to storage and treatment by
				  the burner as well as to storage and treatment facilities operated by
				  intermediaries (processors, blenders, distributors, etc.) between the generator
				  and the burner.
(b) Owners and
				  operators of facilities that burn, in an on-site boiler or industrial furnace
				  exempt from regulation under the small quantity burner provisions of s.
				  NR
				  666.108, hazardous waste that they generate are exempt
				  from the regulations of chs.
				  NR 664, 665, 667 and 670
				  applicable to storage units for those storage units that store mixtures of
				  hazardous waste and the primary fuel to the boiler or industrial furnace in
				  tanks that feed the fuel mixture directly to the burner. Storage of hazardous
				  waste prior to mixing with the primary fuel is subject to regulation as
				  prescribed in par. (a).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.102 - License standards for burners

Current through June 24, 2024
(1) APPLICABILITY.
(a)
General
. Owners and
				  operators of boilers and industrial furnaces burning hazardous waste and not
				  operating under an interim license shall comply with this section and ss.
				  NR
				  670.022 and 670.066, unless exempt under the small
				  quantity burner exemption of s.
				  NR
				  666.108.
(b)
Applicability of ch. NR 664
				  standards
. Owners and operators of boilers and industrial furnaces
				  that burn hazardous waste are subject to the following provisions of ch. NR
				  664, except as provided otherwise by this subchapter:
1. In subch. A of ch. NR 664 (General), s.
				  NR
				  664.0004.
2. In subch. B of ch. NR 664 (General
				  facility standards), s.
				  NR 664.0011
				  to 664.0018.
3. In subch. C of ch.
				  NR 664 (Preparedness and prevention), ss.
				  NR
				  664.0031 to 664.0037.
4. In subch. D of ch. NR 664 (Contingency
				  plan and emergency procedures), ss.
				  NR
				  664.0051 to 664.0056.
5. In subch. E of ch. NR 664 (Manifest
				  system, recordkeeping and reporting), the applicable provisions of ss.
				  NR
				  664.0071 to 664.0077.
6. In subch. F of ch. NR 664 (Corrective
				  Action), ss.
				  NR
				  664.0090 and 664.0101.
7. In subch. G of ch. NR 664 (Closure and
				  post-closure), ss.
				  NR
				  664.0111 to 664.0115.
8. In subch. H of ch. NR 664 (Financial
				  requirements), ss.
				  NR
				  664.0141, 664.0142, 664.0143 and 664.0147 to 664.0151,
				  except that states and the federal government are exempt from s.
				  NR
				  664.0147.
9. Subchapter BB of ch. NR 664 (Air emission
				  standards for equipment leaks), except s.
				  NR
				  664.1050(1).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.103 - Interim license standards for burners

Current through June 24, 2024
(1) PURPOSE, SCOPE,
				  APPLICABILITY.
(a)
General.
1. The purpose of this section is to
				  establish minimum national standards for owners and operators of "existing"
				  boilers and industrial furnaces that burn hazardous waste where such standards
				  define the acceptable management of hazardous waste during the period of
				  interim license. The standards of this section apply to owners and operators of
				  existing facilities until either a license is issued under s.
				  NR
				  666.102(4) or until closure
				  responsibilities identified in this section are fulfilled.
2. "Existing" or "in existence" means a
				  boiler or industrial furnace that on or before August 21, 1991 is either in
				  operation burning or processing hazardous waste or for which construction
				  (including the ancillary facilities to burn or to process the hazardous waste)
				  has commenced. A facility has commenced construction if the owner or operator
				  has obtained the federal, state and local approvals or licenses necessary to
				  begin physical construction; and one of the following applies:
a. A continuous on-site, physical
				  construction program has begun.
b.
				  The owner or operator has entered into contractual obligations-which cannot be
				  canceled or modified without substantial loss-for physical construction of the
				  facility to be completed within a reasonable time.
3. If a boiler or industrial furnace is
				  located at a facility that already has a license or interim license, then the
				  facility shall comply with the applicable regulations dealing with license
				  modifications in s.
				  NR
				  670.042 or changes in interim license in s.
				  NR
				  670.072.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.105 - Standards to control particulate matter

Current through June 24, 2024
(1) A boiler or
				  industrial furnace burning hazardous waste may not emit particulate matter in
				  excess of 180 milligrams per dry standard cubic meter (0.08 grains per dry
				  standard cubic foot) after correction to a stack gas concentration of 7%
				  oxygen, using procedures prescribed in 40 CFR part 60, appendix A, methods 1 to
				  5, incorporated by reference in s.
				  NR
				  660.11, and ch. NR 666 Appendix IX.
(2) An owner or operator meeting s.
				  NR
				  666.109(2) for the low risk waste
				  exemption is exempt from the particulate matter standard.
(3) OXYGEN CORRECTION.
(a) Measured pollutant levels shall be
				  corrected for the amount of oxygen in the stack gas according to the formula:
Pc = Pm × 14 /( E - Y)
where:
Pc is the corrected concentration of the pollutant in the
					 stack gas, Pm is the measured concentration of the pollutant in the stack gas,
					 E is the oxygen concentration on a dry basis in the combustion air fed to the
					 device, and Y is the measured oxygen concentration on a dry basis in the
					 stack.
(b) For devices that
				  feed normal combustion air, E will equal 21%. For devices that feed
				  oxygen-enriched air for combustion (that is, air with an oxygen concentration
				  exceeding 21%), the value of E will be the concentration of oxygen in the
				  enriched air.
(c) Compliance with
				  all emission standards provided by this subchapter shall be based on correcting
				  to 7% oxygen using this procedure.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.106 - Standards to control metals emissions

Current through June 24, 2024
(1) GENERAL. The
				  owner or operator shall comply with the metals standards provided by subs. (2),
				  (3), (4), (5), or (6) for each metal listed in sub. (2) that is present in the
				  hazardous waste at detectable levels by using appropriate analytical
				  procedures.
(2) TIER I FEED RATE
				  SCREENING LIMITS. Feed rate screening limits for metals are specified in ch. NR
				  666 Appendix I as a function of terrain-adjusted effective stack height and
				  terrain and land use in the vicinity of the facility. Criteria for facilities
				  that are not eligible to comply with the screening limits are provided in par.
				  (g).
(a)
Noncarcinogenic
				  metals
. The feed rates of antimony, barium, lead, mercury, thallium
				  and silver in all feed streams, including hazardous waste, fuels, and
				  industrial furnace feed stocks may not exceed the screening limits specified in
				  ch. NR 666 Appendix I.
1. The feed rate
				  screening limits for antimony, barium, mercury, thallium and silver are based
				  on either of the following:
a. An hourly
				  rolling average as defined in s.
				  NR 666.102(5) (f)
				  1. b.
b. An instantaneous limit not to be exceeded
				  at any time.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.107 - Standards to control hydrogen chloride (HCl) and chlorine gas (Cl2) emissions

Current through June 24, 2024
(1) GENERAL. The owner or operator shall
				  comply with the hydrogen chloride (HCl) and chlorine (Cl2) controls provided by
				  sub. (2), (3) or (5).
(2) SCREENING
				  LIMITS.
(a)
Tier I feed rate
				  screening limits.
Feed rate screening limits are specified for total
				  chlorine in ch. NR 666 Appendix II as a function of terrain-adjusted effective
				  stack height and terrain and land use in the vicinity of the facility. The feed
				  rate of total chlorine and chloride, both organic and inorganic, in all feed
				  streams, including hazardous waste, fuels and industrial furnace feed stocks
				  may not exceed the levels specified.
(b)
Tier II emission rate screening
				  limits.
Emission rate screening limits for HCl and Cl2 are specified
				  in ch. NR 666 Appendix III as a function of terrain-adjusted effective stack
				  height and terrain and land use in the vicinity of the facility. The stack
				  emission rates of HCl and Cl2 may not exceed the levels specified.
(c)
Definitions and
				  limitations.
The definitions and limitations provided by s.
				  NR
				  666.106(2) for the following terms
				  also apply to the screening limits provided by this subsection:
				  terrain-adjusted effective stack height, good engineering practice stack
				  height, terrain type, land use and criteria for facilities not eligible to use
				  the screening limits.
(d)
Multiple stacks.
Owners and operators of facilities with more
				  than one on-site stack from a boiler, industrial furnace, incinerator or other
				  thermal treatment unit subject to controls on HCl or Cl2 emissions under an
				  operating license or interim license shall comply with the Tier I and Tier II
				  screening limits for those stacks assuming all hazardous waste is fed into the
				  device with the worst-case stack based on dispersion characteristics.
1. The worst-case stack is determined by
				  procedures provided in s.
				  NR
				  666.106(2) (f).
2. Under Tier I, the total feed rate of
				  chlorine and chloride to all subject devices may not exceed the screening limit
				  for the worst-case stack.
3. Under
				  Tier II, the total emissions of HCl and Cl2 from all subject stacks may not
				  exceed the screening limit for the worst-case stack.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.108 - Small quantity on-site burner exemption

Current through June 24, 2024
(1) EXEMPT
				  QUANTITIES. Owners and operators of facilities that burn hazardous waste in a
				  non-site boiler or industrial furnace are exempt from this subchapter if all of
				  the following conditions are met:
(a) The
				  quantity of hazardous waste burned in a device for a calendar month does not
				  exceed the limits provided in the following table based on the terrain-adjusted
				  effective stack height as defined in s.
				  NR
				  666.106(2) (c).
Terrain-adjusted effective stack height of device
								  (meters)
Allowable hazardous waste burning rate (gallons/
								  month)
Terrain-adjusted effective stack height of device
								  (meters)
Allowable hazardous waste burning rate
								  (gallons/month)
0 to 3.9
0
40.0 to 44.9
210
4.0 to 5.9
13
45.0 to 49.9
260
6.0 to 7.9
18
50.0 to 54.9
330
8.0 to 9.9
27
55.0 to 59.9
400
10.0 to 11.9
40
60.0 to 64.9
490
12.0 to 13.9
48
65.0 to 69.9
610
14.0 to 15.9
59
70.0 to 74.9
680
16.0 to 17.9
69
75.0 to 79.9
760
18.0 to 19.9
76
80.0 to 84.9
850
20.0 to 21.9
84
85.0 to 89.9
960
22.0 to 23.9
93
90.0 to 94.9
1,100
24.0 to 25.9
100
95.0 to 99.9
1,200
26.0 to 27.9
110
100.0 to 104.9
1,300
28.0 to 29.9
130
105.0 to 109.9
1,500
30.0 to 34.9
140
110.0 to 114.9
1,700
35.0 to 39.9
170
115.0 or greater
1,900
(b)
				  The maximum hazardous waste firing rate does not exceed at any time one percent
				  of the total fuel requirements for the device (hazardous waste plus other fuel)
				  on a total heat input or mass input basis, whichever results in the lower mass
				  feed rate of hazardous waste.
(c)
				  The hazardous waste has a minimum heating value of 5,000 Btu/lb, as
				  generated.
(d) The hazardous waste
				  fuel does not contain (and is not derived from) EPA hazardous waste numbers
				  F020, F021, F022, F023, F026 or F027.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.109 - Low risk waste exemption

Current through June 24, 2024
(1) WAIVER OF DRE
				  STANDARD. The DRE standard of s.
				  NR
				  666.104(1) does not apply if the
				  boiler or industrial furnace is operated in conformance with par. (a) and the
				  owner or operator demonstrates by procedures prescribed in par. (b) that the
				  burning will not result in unacceptable adverse health effects.
(a) The device shall be operated with all of
				  the following conditions:
1. A minimum of 50%
				  of fuel fired to the device shall be fossil fuel, fuels derived from fossil
				  fuel, tall oil, or, if approved by the department on a case-by-case basis,
				  other nonhazardous fuel with combustion characteristics comparable to fossil
				  fuel. Such fuels are termed primary fuel for purposes of this section. (Tall
				  oil is a fuel derived from vegetable and rosin fatty acids.) The 50% primary
				  fuel firing rate shall be determined on a total heat or mass input basis,
				  whichever results in the greater mass feed rate of primary fuel
				  fired.
2. Primary fuels and
				  hazardous waste fuels shall have a minimum as-fired heating value of 8,000
				  Btu/lb.
3. The hazardous waste
				  shall be fired directly into the primary fuel flame zone of the combustion
				  chamber.
4. The device shall
				  operate in conformance with the carbon monoxide controls provided by s.
				  NR
				  666.104(2) (a). Devices subject to
				  the exemption provided by this section are not eligible for the alternative
				  carbon monoxide controls provided by s.
				  NR
				  666.104(3).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 666 - Standards For Managing Specific Hazardous Wastes And Specific Types Of Hazardous Waste Management Facilities › Subchapter H - Hazardous Waste Burned in Boilers and Industrial Furnaces › Section NR 666.111 - Standards for direct transfer

Current through June 24, 2024
(1) APPLICABILITY.
				  The regulations in this section apply to owners and operators of boilers and
				  industrial furnaces subject to s.
				  NR
				  666.102 or 666.103 if hazardous waste is directly
				  transferred from a transport vehicle to a boiler or industrial furnace without
				  the use of a storage unit.
(2)
				  DEFINITIONS.
(a) When used in this section,
				  the following terms have the meanings given in subds. 1. and 2.:
1. "Direct transfer equipment" means any
				  device (including but not limited to, such devices as piping, fittings,
				  flanges, valves and pumps) that is used to distribute, meter or control the
				  flow of hazardous waste between a container (i.e., transport vehicle) and a
				  boiler or industrial furnace.
2.
				  "Container" means any portable device in which hazardous waste is transported,
				  stored, treated or otherwise handled, and includes transport vehicles that are
				  containers themselves (e.g., tank trucks, tanker-trailers and rail tank cars),
				  and containers placed on or in a transport vehicle.