reglab/statecodes huggingface dataset:
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part C - COMMERCIAL/INDUSTRIAL WASTE AND WASTEWATER FACILITIES › Section 11-26 - Discharge to Public Sewerage System

Current through July 13, 2024
The discharge of commercial/industrial wastewater to a
					 public sewerage system shall be allowed provided a letter of verification from
					 the public sewerage system manager is submitted to the Department of
					 Environmental Quality stating that the municipal system is capable of handling
					 the added organic and/or hydraulic loads. The applicant shall demonstrate (1)
					 that the wastewater will not adversely impact the treatment works and/or
					 discharge or (2) that pretreatment of the wastewater shall be provided to
					 eliminate the adverse impacts. The design and construction of any pretreatment
					 device shall reduce the pollutants to the limits imposed by the public sewerage
					 system manager.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part C - COMMERCIAL/INDUSTRIAL WASTE AND WASTEWATER FACILITIES › Section 11-27 - Domestic Wastes from Commercial/Industrial Facilities

Current through July 13, 2024
Commercial/industrial facilities that generate waste that
					 is entirely domestic waste shall be designed in compliance with Part B of
					 Chapter 11 or Chapter 25. When the commercial/industrial facility generates a
					 combined domestic and commercial/industrial waste, the facility may be designed
					 in compliance with Chapter 25 or Part B of this chapter provided the applicant
					 can demonstrate that the commercial/ industrial waste will not interfere or
					 adversely impact the treatment works or the discharge.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part C - COMMERCIAL/INDUSTRIAL WASTE AND WASTEWATER FACILITIES › Section 11-28 - Biological Treatment Ponds

Current through July 13, 2024
This section includes the standards for ponds that accept
					 commercial/ industrial waste and wastewater that is primarily organic and
					 utilizes biological organisms for treatment and do not meet the requirements of
					 Section 27. The presence of toxic wastes, hazardous substances, and/or
					 petroleum products shall not interfere or adversely impact the treatment
					 process or disposal system.
(a)
				  Location.
(i) Extraneous surface water and
				  groundwater shall be excluded from entering the wastewater pond or entering the
				  wastewater flow into the pond.
(ii)
				  Ponds shall not be located within the ordinary high water mark of perennial
				  rivers, streams, or creeks; nor in the bottoms of rivers, streams, creeks,
				  draws, coulees, or other natural drainages into which natural runoff may flow
				  and/or enter.
(iii) Ponds shall be
				  protected from structural damage during the 100-year flood event.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part C - COMMERCIAL/INDUSTRIAL WASTE AND WASTEWATER FACILITIES › Section 11-29 - Feedlots

Current through July 13, 2024
This section includes the standards for wastewater
					 retention systems for feedlot runoff. The basic concept of retention systems is
					 to intercept and collect runoff and wastes from the animal feeding area until
					 it can be disposed of via land application. Although retention systems are
					 usually the most economical method of treatment, other systems will be
					 evaluated on a case-by-case basis.
(a)
				  Location.
(i) Groundwater shall be excluded
				  from entering the wastewater pond or the wastewater flow into the
				  pond.
(ii) Ponds shall not be
				  located within the ordinary highwater mark of perennial rivers, streams, or
				  creeks. Ponds not containing hazardous or toxic wastes may be located within
				  the ordinary high water mark of intermit tent rivers, streams, creeks, draws,
				  coulees, or other natural drainages provided a by-pass ditch is installed
				  capable of passing the 24-hour - 100 -year precipitation event.
(iii) The wastewater retention system shall
				  be as near to the animal feeding operation as possible to keep construction to
				  a minimum. The retention ponds shall be located outside the pen area for safety
				  and maintenance purposes. Sufficient space must be left between streams or
				  drainage areas to allow construction of the necessary collection ditches and
				  retention ponds.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part C - COMMERCIAL/INDUSTRIAL WASTE AND WASTEWATER FACILITIES › Section 11-30 - Non-biological Treatment Ponds

Current through July 13, 2024
This section includes the standards for non-biological
					 treatment ponds or ponds that accept commercial/industrial waste or wastewater
					 that is primarily non-biological in nature and does not utilize biological
					 organisms for treatment. Radiological effects considered by the Nuclear
					 Regulatory Commission (NRC) from non-surface discharging treatment works within
					 a NRC licensed permit boundary are exempt from this section.
(a) Location.
(i) Extraneous surface water and groundwater
				  shall be excluded from entering the wastewater pond or entering the wastewater
				  flow into the pond.
(ii) Ponds
				  shall not be located within the ordinary high water mark of perennial rivers,
				  streams, or creeks. Ponds not containing hazardous or toxic wastes may be
				  located within the ordinary high water mark of intermit tent rivers, streams,
				  creeks, draws, coulees, or other natural drainages provided a by-pass ditch is
				  installed capable of passing the 24-hour - 100-year precipitation event. All
				  other ponds shall be protected from structural damage during the 100-year flood
				  event.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-32 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-33 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-34 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-35 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-36 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-37 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-38 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-39 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-40 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-41 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-42 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-43 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-44 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-45 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-46 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part D - SEPTIC TANK AND/OR SOIL ABSORPTION SYSTEMS AND OTHER SMALL WASTEWATER SYSTEMS › Section 11-47 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part E - STANDARDS FOR THE APPLICATION OF BIOSOLIDS AND THE REUSE OF TREATED NON-DOMESTIC WASTEWATER › Section 11-48 - General

Current through July 13, 2024
This part contains the minimum standards for the design and
					 construction of waste and wastewater land application facilities.
The permitting of biosolids facilities or the land
					 application of biosolids is regulated by the U.S. Environmental Protection
					 Agency (EPA) under the Code of Federal Regulations at 40 CFR Part 503. In cases
					 where the EPA does not issue a permit under 40 CFR 503, the Wyoming Department
					 of Environmental Quality, Water Quality Division (WDEQ/WQD) will issue a
					 permit. The WQD will require applicants to comply with the requirements of
					 40 CFR §
											503.12, §
										503.13, and
					 §
										503.14. The
					 permit applications and permits will be reviewed and processed according to
					 Chapter 3 of the Water Quality Rules and Regulations.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part E - STANDARDS FOR THE APPLICATION OF BIOSOLIDS AND THE REUSE OF TREATED NON-DOMESTIC WASTEWATER › Section 11-49 - Definitions Specific to Part E

Current through July 13, 2024
(a) "Overland flow
				  land application system" is a system in which treatment is accomplished by the
				  application of wastewater to a sloping, largely impermeable site. Treatment
				  mechanisms include filtration, sedimentation, microbial oxidation, and crop
				  uptake. Typical application rates range from 0.0392-0.3136
				  yd3/yd/hr.
(b) "Primary treatment level" (as related to
				  pathogenic organism reduction) is that level of fecal coliform reduction (a
				  minimum of 25 percent reduction) achievable by primary sedimentation in single
				  cell discharging lagoons operated within the limits described in Part B,
				  Section 13(c).
(c) "Biosolids" are
				  solid, semi-solid, or liquid residue generated during the treatment of domestic
				  sewage in a treatment works. Biosolids include, but are not limited to,
				  domestic septage; scum or solids removed in primary, secondary, or advanced
				  wastewater treatment processes; and a material derived from biosolids.
				  Biosolids do not include ash generated during the firing of biosolids in a
				  biosolids incinerator or grit and screenings generated during preliminary
				  treatment of domestic sewage in a treatment works.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part E - STANDARDS FOR THE APPLICATION OF BIOSOLIDS AND THE REUSE OF TREATED NON-DOMESTIC WASTEWATER › Section 11-51 - Pretreatment Water Quality Requirement

Current through July 13, 2024
Pretreatment of wastewater shall provide sufficient organic
					 and inorganic solids reduction, maintaining the estimated infiltration rate of
					 the soil surface.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part E - STANDARDS FOR THE APPLICATION OF BIOSOLIDS AND THE REUSE OF TREATED NON-DOMESTIC WASTEWATER › Section 11-52 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part E - STANDARDS FOR THE APPLICATION OF BIOSOLIDS AND THE REUSE OF TREATED NON-DOMESTIC WASTEWATER › Section 11-53 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part E - STANDARDS FOR THE APPLICATION OF BIOSOLIDS AND THE REUSE OF TREATED NON-DOMESTIC WASTEWATER › Section 11-54 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part F - MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Section 11-57 - General

Current through July 13, 2024
This part contains the minimum standards for the design and
					 construction of mobile home park and/or campground wastewater facilities and
					 public water supply systems.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part F - MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Section 11-58 - Sewage System Standards

Current through July 13, 2024
(a) If sewerage
				  system services are to be provided by a second person, a letter of verification
				  from the system manager stating that they are capable of handling added organic
				  and/or hydraulic loads shall be provided by the owner/operator of the
				  system.
(b) A mobile home park or
				  campground sewerage system, treatment works and disposal system shall comply
				  with Part A, B, C, and/or D of Chapter 11 except as follows:
(i) Mobile home park sewerage systems,
				  treatment works and disposal systems shall be designed on the basis of not less
				  than 350 gallons per site per day. Camp ground sewerage systems, treatment
				  works and disposal systems shall be designed on the basis of not less than 100
				  gallons per site per day for all sewered sites or 75 gallons per site per day
				  for all unsewered sites.
(ii)
				  Sanitary sewers shall not be smaller than six inches in diameter. They shall be
				  installed at a slope equal to or greater than 0.6 feet per 100 feet.
(iii) Not more than two mobile homes or
				  campground sites shall be served by a sanitary sewer service connection pipe of
				  a least four (4) inches in diameter, provided the main branch of the service
				  pipe is served by a cleanout and provided it is not longer than fifty (50)
				  feet. It shall be installed at a minimum slope of 1/4 inch per foot. The riser
				  portion of the service connection pipe shall be constructed of cast iron or
				  schedule 40 plastic pipe. The riser shall be terminated at least four (4)
				  inches above finished grade and shall not be located closer than five (5) feet
				  from a potable water service riser. The service connection pipe shall connect
				  to the sewerage system at a maximum 45-degree bend in the direction of sewage
				  flow.
(iv) Not more than one mobile
				  home shall be served by a sanitary sewer service riser pipe. The riser shall be
				  located so as to minimize the length of pipe required to connect the mobile
				  home drain. The riser pipe shall be capped or plugged when not in
				  use.
(v) The connection of the
				  mobile home drain to the riser pipe shall be sealed.
(vi) If sewer service is provided to sites in
				  a campground, the sanitary sewer service connection pipe shall comply with
				  subsections (iii) and (iv) above.
(vii) Service connection pipes for
				  campgrounds shall be trapped below the frost line.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-60 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-61 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-62 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-63 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-64 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-65 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-66 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-67 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-68 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-69 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part G - WELL CONSTRUCTION › Section 11-70 - Reserved

Current through July 13, 2024
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-71 - Authority and Purpose

Current through July 13, 2024
(a) These
				  regulations establish standards that address the primary health concerns
				  associated with the reuse of treated wastewater. The regulations establish
				  criteria to address the risk of pathogen exposure and infectious disease risks
				  associated with various specified uses of treated wastewater. The regulations
				  establish standards for the following:
(i) The
				  level of wastewater treatment required;
(ii) Treatment reliability
				  requirements;
(iii) Upper limits
				  for water quality parameters;
(iv)
				  Site access restrictions; and
(v)
				  Management practices.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-72 - Applicability

Current through July 13, 2024
(a) These
				  regulations apply to any person who prepares or applies treated waste-water
				  from domestic sewage.
(b) These
				  regulations are not applicable if the primary intent is to provide treatment
				  and/or disposal of a wastewater. Treatment and disposal are regulated under
				  appropriate sections of Chapter 11, Wyoming Water Quality Rules and
				  Regulations.
(c) If the reuse of
				  treated wastewater involves the construction of facilities for the
				  disinfection, delivery, storage or land application, a construction permit is
				  required in accordance with the provisions of Chapters 3 and 11, Wyoming Water
				  Quality Rules and Regulations. Such a permit constitutes approval to reuse the
				  treated wastewater. This permit is not an operational permit and does not
				  require periodic renewal. If there are no structural facilities requiring a
				  construction permit, the reuse of wastewater will be authorized by a land
				  application permit issued in accordance with these regulations. The land
				  application permit is not an operational permit and does not require periodic
				  renewal.
(d) These regulations are
				  not applicable to the discharge of a treated wastewater that is subject to a
				  discharge permit issued pursuant to Chapter 2, Wyoming Water Quality Rules and
				  Regulations.
(e) These regulations
				  are not applicable to treated wastewater reused at reclamation sites regulated
				  by the Land Quality Division under Article 4 of the Wyoming Environmental
				  Quality Act.
(f) These regulations
				  are not applicable to treated wastewater reused for irrigation of grass, shrubs
				  and trees at the treatment works.
(g) These regulations are not applicable to
				  the disposal of gray water.
(h)
				  These regulations are not applicable to groundwater recharge projects that are
				  regulated by the Underground Injection Control Program of the Department of
				  Environmental Quality, Water Quality Division.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-73 - Definitions Specific to Part H

Current through July 13, 2024
The following definitions supplement those definitions
					 contained in Section
											35-11-103
					 of the Wyoming Environmental Quality Act.
(a) "Agricultural land" is land on which a
				  food crop, a feed crop, or a fiber crop is grown. This includes range land and
				  land used as pasture.
(b)
				  "Agronomic rate" is the wastewater application rate designed to:
(1) provide the amount of nitrogen needed by
				  the food crop, feed crop, fiber crop, cover crop, or vegetation grown on the
				  land; and
(2) minimize the amount
				  of nitrogen in the treated wastewater that passes below the root zone of the
				  crop or vegetation grown on the land to the groundwater.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-74 - Compliance with Other Laws and Regulations

Current through July 13, 2024
Nothing in these regulations or the permits issued pursuant
					 to these regulations shall be construed to relieve the recipient of a permit of
					 the need to comply with any other law, rule or regulation. It is the duty of
					 the permittee to comply with all applicable federal, state and local laws or
					 regulations in the exercise of activities authorized pursuant to these
					 regulations.
Specifically, the permittee is responsible for complying
					 with the water right requirements of the Wyoming State Engineers Office.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-75 - Compliance Period

Current through July 13, 2024
(a) Compliance with
				  the standards in these regulations shall be achieved as expeditiously as
				  practicable, but in no case later than one (1) year after final adoption. When
				  compliance with the standards requires construction of new or modified
				  treatment facilities, compliance with the standards shall be achieved as
				  expeditiously as practicable, but in no case later than two years after final
				  adoption.
(b) Water reuse
				  facilities operating under authority granted by the Department of Environmental
				  Quality are required to notify the Department of the nature and requirements of
				  the existing authorization. Existing authorized facilities are not required to
				  comply with the requirements of these regulations unless the Administrator
				  determines it is necessary to revise the existing authorization in order to
				  protect public health and the environment. Existing facilities are required to
				  comply with the monitoring and reporting requirements of Sections 83, 84, 85
				  and 86.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-76 - Permits, Enforceability and Applications

Current through July 13, 2024
(a) The
				  requirements in these regulations may be implemented through:
(i) A land application permit issued by the
				  Department of Environmental Quality, Water Quality Division in accordance with
				  these regulations;
(ii) A
				  construction and operation permit issued by the Department of Environmental
				  Quality, Water Quality Division in accordance with Chapters 11 and 3, Wyoming
				  Water Quality Rules and Regulation; or
(iii) A general statewide operation permit
				  issued by the Water Quality Division, Department of Environmental Quality for
				  the Land Application of Treated Waste-water.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-77 - Exclusions

Current through July 13, 2024
(a) Treatment
				  processes. These regulations do not establish requirements for processes used
				  to treat wastewater.
(b) Selection
				  of a reuse practice. This chapter does not require the selection of a reuse
				  practice. The determination of the manner in which treated wastewater is to be
				  reused is a local determination.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-78 - General Management Practices

Current through July 13, 2024
(a) Treated
				  wastewater shall be applied for the purpose of beneficial reuse and shall not
				  exceed the irrigation need or demand of the vegetation at the site. Winter
				  irrigation is considered to be beneficial reuse.
(b) Treated wastewater shall not be applied
				  to agricultural land, forest, a public contact site, or a reclamation site at
				  an application rate that is greater than the agronomic rate for the vegetation
				  at the site.
(c) Treated wastewater
				  shall not be applied in a manner that will contaminate a groundwater
				  aquifer.
(d) Treated wastewater
				  will be applied in a manner and time that will not cause any surface runoff to
				  leave the application site and enter Surface Waters of the State.
(e) Direct human consumption food crops shall
				  not be harvested for thirty (30) days after application of treated
				  wastewater.
(f) Animals shall not
				  be allowed to graze on the land for thirty (30) days after application of Class
				  C treated wastewater.
(g) Fencing
				  and signing shall be provided at sites where Class B treated wastewater is
				  proposed for reuse on land with a moderate potential for public
				  exposure.
(h) Signing shall be
				  provided at sites where Class B or Class C treated wastewater is proposed for
				  reuse on land with a low potential for public exposure in order to protect the
				  health and safety of workers.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-79 - Site Isolation Requirements

Current through July 13, 2024
No person shall reuse treated wastewater on an application
					 site except in accordance with the restrictions specified below.
(a) Isolation of spray irrigation systems.
(i) Wind drift shall not leave the
				  application site.
(ii) If Class A
				  or Class B wastewater is reused for irrigation, a 30-foot buffer zone is
				  required between the reuse site and adjacent property lines. Public
				  right-of-ways may be utilized to meet this requirement for a buffer
				  zone.
(iii) If Class C wastewater
				  is reused for irrigation a 100-foot buffer zone is required between the reuse
				  site and adjacent property lines and any public right-of-way.
(iv) A 30-foot separation distance is
				  required between reuse sites and all surface waters.
(v) A 100-foot separation distance is
				  required between reuse sites and all potable water supply wells.
(vi) Surface runoff shall not leave the
				  application site.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-80 - Minimum Level of Wastewater Treatment

Current through July 13, 2024
Treated wastewater must receive the equivalent of primary
					 treatment and a maximum fecal coliform value of less than 1000/100 ml in order
					 to be reused in accordance with these regulations.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-81 - Treatment Reliability

Current through July 13, 2024
(a) The ability of
				  the treatment process to deliver the class of treated wastewater required for a
				  particular use will be considered by the permitting authority when approving or
				  denying wastewater reuse in accordance with Section 76. The criteria for
				  evaluating treatment reliability may include the following as appropriate:
(i) Multiple units and equipment;
(ii) Alternative power sources;
(iii) Alarm systems and
				  instrumentation;
(iv) Operator
				  certification and stand-by capability;
(v) Bypass and dewatering
				  capability;
(vi) Frequency of
				  sampling;
(vii) Hydraulic and
				  organic loading design capabilities; and
(viii) Emergency storage.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-82 - Authorized Reuse

Current through July 13, 2024
(a) Class A
				  wastewater may be used for the following purposes:
(i) Irrigation of land with a high potential
				  for public exposure;
(ii)
				  Irrigation of land with a moderate potential for public exposure;
(iii) Irrigation of land with a low potential
				  for public exposure;
(iv)
				  Irrigation of direct human consumption food crops; and
(v) Irrigation of indirect human consumption
				  food crops.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-83 - Monitoring

Current through July 13, 2024
(a) Sampling.
				  Representative samples of the treated wastewater that is to be reused shall be
				  collected and analyzed by the person who prepares the wastewater.
(b) Methods. Waste constituents shall be
				  analyzed in accordance with 40 CFR Part 136, Guidelines Establishing Test
				  Procedures for the Analysis of Pollutants.
(c) Parameters. The treated wastewater shall
				  be analyzed for the following:
(i) Fecal
				  coliform;
(ii) Nitrate as
				  N;
(iii) Ammonia as N;
(iv) pH;
(v) Parameters identified in 40 CFR Part 122,
				  Appendix D, Table III, when required by the NPDES permit; and
(vi) Other parameters identified in the
				  permit.
Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 11 - DESIGN AND CONSTRUCTION STANDARDS FOR SEWERAGE SYSTEMS, TREATMENT WORKS, DISPOSAL SYSTEMS OR OTHER FACILITIES CAPABLE OF CAUSING OR CONTRIBUTING TO POLLUTION AND MOBILE HOME PARK AND CAMPGROUND SEWERAGE AND PUBLIC WATER SUPPLY DISTRIBUTION SYSTEMS › Part H - STANDARDS FOR THE REUSE OF TREATED DOMESTIC WASTEWATER › Section 11-84 - Noncompliance Actions, Reporting and Monitoring Requirements

Current through July 13, 2024
In the event that the monitoring program identified in
					 Section 83 indicates noncompliance with the fecal coliform levels associated
					 with the class of wastewater and the appropriate authorized reuse identified in
					 Section 82, the responsible party shall take the following actions.
(a) Discontinue the reuse of treated
				  wastewater immediately. The responsible party may discharge in compliance with
				  the requirements of an NPDES permit or convert to any authorized reuse that is
				  consistent with the quality of the treated wastewater.
(b) Report the noncompliance to the
				  permitting authority as soon as possible, but no later than the next working
				  day.
(c) Initiate monitoring of the
				  parameter in noncompliance on a daily or more frequent basis in order to
				  adequately demonstrate that the treated wastewater can reliably meet the reuse
				  criteria.
(d) Report the results on
				  the noncompliance monitoring to the permitting authority. Upon adequate
				  demonstration by the responsible party that the reuse criteria can be reliably
				  met, the permitting authority may grant verbal and written authorization to
				  re-institute the discontinued reuse.
(e) The responsible party shall provide a
				  written report within fifteen (15) days of the resolution of the event that
				  will contain the following:
(i) A description
				  of the noncompliance and its cause;
(ii) The period of the noncompliance,
				  including dates and times;
(iii)
				  All monitoring data related to the noncompliance and the return to compliance;
				  and
(iv) Steps taken or planned to
				  reduce, eliminate or prevent reoccurrence of the noncompliance.