Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0014 - Storage Tanks › Chapter 1 - STORAGE TANKS › Part K - DELIVERY PROHIBITION AT NON-COMPLIANT FACILITIES › Section 1-44 - Delivery Prohibition

Current through July 13, 2024
(a)
Reasons
				  for Restricting Delivery.
Regulated substance delivery prohibition to
				  a storage tank system shall be required when the department becomes aware that:
(i) The owner and/or operator has not
				  performed leak detection on the tanks as required in Part D for any period
				  exceeding 60 days;
(ii) The most
				  recently required cathodic protection test has not been done within 90 days of
				  the due date as required by Section 11(b);
(iii) A cathodic protection test done in
				  accordance with Section 11 has failed and has not been repaired and re-tested
				  within 90 days of the date when the original failing result was
				  obtained;
(iv) The most recently
				  required pressure test of the lines has not been done as required by Section
				  14(g)(i)(B) or Section 14(g)(ii) (as applicable) within 90 days of the date
				  due;
(v) The most recently required
				  functional test of automatic line leak detectors has not been done as required
				  by Section 14(g)(i)(B) or Section 37 within 90 days of the date due;
(vi) The owner and/or operator has failed to
				  report a suspected release under Section 19 when required by Part D and/or
				  Section 19;
(vii) The owner and/or
				  operator has reported a suspected release under Section 19 but has failed to
				  initiate the release investigation required under Section 20 or 21;
(viii) The owner and/or operator has reported
				  a confirmed release, but repairs have not been made to the storage tank
				  system;
(ix) The owner and/or
				  operator has failed to pay the storage tank registration fee, which is due on
				  January 1 of each year, by April 1 of the year when due;
(x) The owner and/or operator has failed to
				  follow any Order issued by the department, unless that Order is under appeal to
				  the Environmental Quality Council;
(xi) Any required monitoring device has been
				  purposely tampered with or turned off (unless it is being repaired);
(xii) Any record required to be kept under
				  this Chapter has been falsified;
(xiii) Any regulated tank is discovered
				  without overfill and spill prevention devices in place as required by Sections
				  6(c) or 35(f);
(xiv) Any regulated
				  tank, or any piping or ancillary equipment that routinely contains product and
				  is not isolated from ground contact, is discovered without corrosion protection
				  or cathodic protection systems in place as required by Sections 6(a)(ii),
				  6(b)(ii), or 35(d);
(xv) Any
				  regulated AST has not been fully upgraded in accordance with Part I;
(xvi) The operator's annual inspection has
				  not been performed within 90 days of the due date as required by Section 13(g)
				  or Section 36(f);
(xvii) The
				  department becomes aware that there has been no licensed Class A or B Operator
				  for a facility for 90 days or more; or the Class B Operator has not been
				  retrained per Section 46(i) within 90 days of a Notice of Violation being
				  issued.
(xviii) Repaired tanks and
				  piping have not been tightness tested within 30 days of repair
				  completion;
(ixx) Cathodic
				  protection impressed current systems have not been inspected at least every 60
				  days;
(xx) A storage tank system
				  has been installed or substantially modified and is being operated without
				  written authorization by the department; or
(xxi) Spill prevention equipment, containment
				  sumps, or overfill prevention device testing has not been completed within 60
				  days of the due date as required in Section 10(d); or
(xxii) Pressurized piping is being operated
				  without an automatic line leak detector in accordance with Section
				  14(g)(i)(B).