reglab/statecodes huggingface dataset:
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-1500 - Chapter 15-Referenced standards

Current through Register Vol. 24-14, July 15, 2024
The following referenced standards are added to Chapter
				15.
AHAM
Association of Home Appliance Manufacturers
1111 19th St. N.W., #402
Washington D.C. 20036
AHAM-Certified Range Hood
Directory . . . . . . . . . . . . . . . . . . . . . . . . . . .
				. . . . . . . . . . . . . . . . . . . . . 403.4.7.3.1
HRH-2
Household Range Hoods . . . . . . . . . . .
				. . . . . . . . . . . . . 403.4.7.3.1
ANCE
UL/CSA/ANCE 60335-2-40-2019
Household and Similar
				Electrical Appliances - Safety - Part 2-40: Particular Requirements for
				Electrical Heat Pumps, Air Conditioners and Dehumidifiers . . . . . . . . . . .
				. . . . . . . . . . . . . 1101.2
ASHRAE
62.2-2019
Ventilation and Acceptable Indoor Air
				Quality in Low-Rise Residential Buildings 401.4, 403.4, 403.4.7.3.3, 403.4.11
ASTM
E3087-18:
Standard Test Method for Measuring
				Capture Efficiency of Domestic Range Hoods . . . . . . . . . . . . . . .
				403.4.7.3.2, Table 403.4.7.3.2
CSA
UL/CSA/ANCE 60335-2-40-2019
Household and Similar
				Electrical Appliances - Safety - Part 2-40: Particular Requirements for
				Electrical Heat Pumps, Air Conditioners and Dehumidifiers . . . . . . . . . . .
				. . . . 1101.2
HVI
address:
Home Ventilating Institute
1740 Dell Range Blvd., Suite H, PMB 450
Cheyenne, WY 82009
HVI Publication 911
Certified Home Ventilating
				Product Directory . . . . . . . . . . . . . . . . 403.4.7.3.4
HVI 915-2020
Procedure for Loudness Testing of
				Residential Fan Products . . . . . . . . . . . . . . . . 403.4.6.1, 403.4.6.2,
				403.4.7.2
HVI 916-2020
Air Flow Test Procedure .....
				403.4.6.1, 403.4.6. 2, 403.4.7.2
HVI 920-2020
Product Performance Certification
				Procedure Including Verification and Challenge ...... 403.4.6.1, 403.4.6.2,
				403.4.7.2
NFPA
110-22
Standard for Emergency and Standby Power
				Systems . . . . . . . . . . . . . . . . 915.3, 915.3.1, 915.3.2
111-22
Standard on Stored Electrical Energy
				Emergency and Standby Power Systems . . . . . . . . . . . . . . . . 915.3,
				915.4
UL
864-2014
Control Units and Accessories for Fire
				Alarm Systems with revisions through October 2018 . . . . . . . . . . . . . . .
				. 606.2.2
UL/CSA/ANCE 60335-2-40-2019
Household and Similar
				Electrical Appliances - Safety - Part 2-40: Particular Requirements for
				Electrical Heat Pumps, Air Conditioners and Dehumidifiers . . . . . . . . . . .
				. . . . . 1101.2
Statutory Authority:
				  RCW
				    19.27.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-053, §
				  51-52-1500, filed 2/1/13, effective 7/1/13. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 10-03-099, §
				  51-52-1500, filed 1/20/10, effective
				  7/1/10.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-21000 - International Fuel Gas Code

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27.031 and
				  19.27.074. 04-01-104, §
				  51-52-21000, filed 12/17/03, effective
				  7/1/04.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-21101 - Section 101 (IFGC)-General

Current through Register Vol. 24-14, July 15, 2024
101.2 Scope.
This code shall apply to the
				installation of fuel gas piping systems, fuel gas utilization equipment,
				gaseous hydrogen systems and regulated accessories in accordance with Section
				101.2.1 through 101.2.5.
EXCEPTIONS:
1. Detached one- and two-family dwellings and multiple
						  single-family dwellings (townhouses) not more than three stories high with
						  separate means of egress and their accessory structures shall comply with the
International Residential Code
.
2. The standards for liquefied petroleum gas
						  installations shall be the 2020 Edition of NFPA 58 (Liquefied Petroleum Gas
						  Code) and the 2021 Edition of ANSI Z223.1/NFPA 54 (National Fuel Gas
						  Code).
Statutory Authority:
				  RCW
				    19.27.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-053, §
				  51-52-21101, filed 2/1/13, effective 7/1/13. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 10-03-099, §
				  51-52-21101, filed 1/20/10, effective 7/1/10. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020, and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-092, §
				  51-52-21101, filed 12/19/06, effective
				  7/1/07.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-21116 - Section 116 (IFGC)-Stop work order

Current through Register Vol. 24-14, July 15, 2024
116.4 Failure to comply.
Any person who shall
				continue any work after having been served with a stop work order, except such
				work as that person is directed to perform to remove a violation or unsafe
				condition, shall be subject to fines established by the code official.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-21401 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-053, §
				  51-52-21401, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-21409 - Section 409 (IFGC)- Shutoff valves

Current through Register Vol. 24-14, July 15, 2024
Table 409.1.1
Natural Gas Valve Standards
Valve Standards
Appliance Shutoff Valve
							 Application Up to 1/2 psig Pressure
Other Valve
							 Applications
Up to 1/2 psig
							 Pressure
Up to 2 psig
							 Pressure
Up to 5 psig
							 Pressure
Up to 125 psig
							 Pressure
ANSI Z21.15/CGA 9.1
X
--
--
--
--
ASME B16.44
X
X
Xa
Xb
--
ASME B16.33
X
X
X
X
X
ASME B16.38
--
X
X
X
X
For SI: 1 pound per square inch gauge = 6.895 cPsa
a If labeled 2G.
b If labeled 5G.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-21601 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-053, §
				  51-52-21601, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-21800 - Chapter 8-Referenced standards

Current through Register Vol. 24-14, July 15, 2024
The following referenced standards are added to Chapter
				8.
ASME
B16. 38-2012(R2017):
Large Metallic Valves for Gas
				Distribution: Manually Operated, NPS 2 1/2 (DN 65) to NPS 12 (DN 300), 125 psig
				(8.6 bar) Maximum. . . . . . . . . . . . . . . . . . . . . Table 409.1.1
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-22000 - National Fuel Gas Code

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27.031 and
				  19.27.074. 04-01-104, §
				  51-52-22000, filed 12/17/03, effective
				  7/1/04.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-52 - State Building Code adoption and amendment of the 2021 edition of the International Mechanical Code › Section 51-52-22006 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020, and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-092, §
				  51-52-22006, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031 and
				  19.27.074. 04-01-104, §
				  51-52-22006, filed 12/17/03, effective
				  7/1/04.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-001 - Authority

Current through Register Vol. 24-14, July 15, 2024
These rules are adopted under the authority of
				chapter
				19.27
				RCW.
Statutory Authority: RCW 19.27A.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-001, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-002 - Purpose

Current through Register Vol. 24-14, July 15, 2024
The purpose of these rules is to implement the provisions of
				chapter
				19.27 RCW, which provides
				that the State Building Code Council shall maintain the State Building Code in
				a status which is consistent with the purpose as set forth in
				RCW
				  19.27.020. In maintaining the codes the
				council shall regularly review updated versions of the codes adopted under the
				act, and other pertinent information, and shall amend the codes as deemed
				appropriate by the council.
Statutory Authority: RCW 19.27A.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-002, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-003 - International Fire Code

Current through Register Vol. 24-14, July 15, 2024
The 2021 edition of the International Fire Code, published by
				the International Code Council is hereby adopted by reference with the
				following additions, deletions, and exceptions.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-003, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-007 - Exceptions

Current through Register Vol. 24-14, July 15, 2024
The exceptions and amendments to the International Fire Code
				contained in the provisions of chapter 19.27 RCW shall apply in case of
				conflict with any of the provisions of these rules.
Codes referenced which are not adopted through
				RCW
				  19.27.031 or chapter 19.27A RCW shall not
				apply unless specifically adopted by the authority having jurisdiction.
The provisions of this code do not apply to temporary growing
				structures used solely for the commercial production of horticultural plants
				including ornamental plants, flowers, vegetables, and fruits. "Temporary
				growing structure" means a structure that has the sides and roof covered with
				polyethylene, polyvinyl, or similar flexible synthetic material and is used to
				provide plants with either frost protection or increased heat retention. A
				temporary growing structure is not considered a building for purposes of this
				code.
The provisions of this code do not apply to the construction,
				alteration, or repair of temporary worker housing except as provided by rule
				adopted under chapter 70.114A RCW or chapter 37, Laws of 1998 (2SSB 6168).
				"Temporary worker housing" means a place, area, or piece of land where sleeping
				places or housing sites are provided by an employer for his or her employees or
				by another person, including a temporary worker housing operator, who is
				providing such accommodations for employees, for temporary, seasonal occupancy,
				and includes "labor camps" under RCW 70.54.110.
The manufacture, storage, handling, sale and use of fireworks
				shall be governed by chapter 70.77 RCW and by chapter 212-17 WAC and local
				ordinances consistent with chapter 212-17 WAC.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-007, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-008 - Implementation

Current through Register Vol. 24-14, July 15, 2024
The
International Fire Code
adopted by chapter
				51-54A WAC shall become effective in all counties and cities of this state on
				March 15, 2024.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-008, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0101 - Section 101 (Reserved)

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0101, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0105 - Permits

Current through Register Vol. 24-14, July 15, 2024
105.5.14.1
Lithium batteries.
An operational permit is required for an
			 accumulation of more than 15 cubic feet (0.42 m) of lithium-ion and lithium
			 metal batteries, where required by Section 322.1.
105.5.32
Mobile food preparation
			 vehicles.
A permit is required for mobile preparation vehicles equipped
			 with appliances that produce smoke or grease-laden vapors or utilize LP-gas
			 systems or CNG systems.
105.6.25
Underground supply piping for automatic sprinkler system.
A
			 construction permit is required for the installation of the portion of the
			 underground water supply piping, public or private, supplying a water-based
			 fire protection system. The permit shall apply to all underground piping and
			 appurtenances downstream of the first control valve on the lateral piping or
			 service line from the distribution main to 1 foot above finished floor of the
			 facility with the fire protection system. Maintenance performed in accordance
			 with this code is not considered to be a modification and does not require a
			 permit.
EXCEPTIONS:
1. When the underground piping is installed by the
						  aboveground piping contractor.
2. Underground piping that serves a fire protection
						  system installed in accordance with NFPA 13D.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0301 - Permits

Current through Register Vol. 24-14, July 15, 2024
301.2
Permits.
Permits shall be required as set forth in Section 105.5
			 for the activities or uses regulated by Sections 306, 307, 308, 315, 320, and
			 322.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0302 - Definitions

Current through Register Vol. 24-14, July 15, 2024
302.1
Definitions.
The following terms are defined in Chapter 2:
3D PRINTER;
ADDITIVE MANUFACTURING; BONFIRE; HI-BOY;
HIGH-VOLTAGE TRANSMISSION LINE;
MOBILE FOOD PREPARATION VEHICLE;
OPEN BURNING;
PORTABLE OUTDOOR FIREPLACE;
POWERED INDUSTRIAL TRUCK;
RECREATIONAL FIRE;
SKY LANTERN.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0307 - Open burning, recreational fires and portable outdoor fireplaces

Current through Register Vol. 24-14, July 15, 2024
307.2.1 Authorization.
Where required by state or
				local law or regulations, open burning shall only be permitted with prior
				approval from the state or local air and water quality management authority,
				provided that all conditions specified in the authorization are followed. See
				also chapter 173-425 WAC.
307.4.2 Recreational fires.
Recreational fires
				shall not be conducted within 25 feet of a structure or combustible material.
				Conditions which could cause a fire to spread within 25 feet of a structure
				shall be eliminated prior to ignition. See also chapter 173-425
				WAC.
Statutory Authority: RCW 19.27A.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0307, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0308 - Open flames

Current through Register Vol. 24-14, July 15, 2024
308.1.7
Religious
			 ceremonies.
Participants in religious ceremonies shall not be precluded
			 from carrying hand-held candles. See
			 RCW
			   19.27.031(3).
308.1.7.1
Aisles and exits.
Candles shall be prohibited in areas where occupants stand, or in an aisle or
			 exit.
EXCEPTION:
Candles used in religious ceremonies.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0314 - Indoor displays

Current through Register Vol. 24-14, July 15, 2024
314.4
Vehicles.
Liquid- or gas-fueled vehicles, boats, aircraft or other
			 motorcraft shall not be located indoors except as follows:
1. The engine starting system is made
			 inoperable or ignition batteries are disconnected except where the fire code
			 official requires that the batteries remain connected to maintain safety
			 features.
2. Fuel in fuel tanks
			 does not exceed any of the following:
2.1.
			 Class I, II, and III liquid fuel does not exceed one-quarter tank or 5 gallons
			 (19 L), whichever is less.
2.2. LP
			 gas does not exceed one-quarter tank or 6.6 gallons (25 L), whichever is
			 less.
2.3. CNG does not exceed
			 one-quarter tank or 630 cubic feet (17.8 m3),
			 whichever is less.
2.4. Hydrogen
			 does not exceed one-quarter tank or 2,000 cubic feet (0.57
			 m3), whichever is less.
3. Fuel tanks and fill openings are closed
			 and sealed to prevent tampering.
4.
			 Vehicles, aircraft, boats or other motorcraft equipment are not fueled or
			 defueled within the building.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0321 - Artificial combustible vegetation

Current through Register Vol. 24-14, July 15, 2024
321.1
Artificial
			 combustible vegetation on roofs and near buildings.
Artificial combustible vegetation exceeding 6 feet (1829 mm) in
				height and permanently installed outdoors within 5 feet (1524 mm) of a building
				or on the roof of a building shall comply with Section 807.4.1. The placement
				of artificial combustible vegetation shall also comply with Sections 806.3 and
				807.4.2.
EXCEPTIONS:
1. Artificial decorative vegetation located more than
						  30 feet (9144 mm) from the exterior wall of a building.
2. Artificial decorative vegetation used at structures
						  regulated by the International Residential Code.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0322 - Lithium batteries

Current through Register Vol. 24-14, July 15, 2024
322.1
General.
The storage of lithium-ion and lithium metal batteries shall
			 comply with Section 322.
EXCEPTIONS:
1. New or refurbished batteries installed in the
						  equipment, devices, or vehicles they are designed to power.
2. New or refurbished batteries packed for use with the
						  equipment, devices, or vehicles they are designed to power.
3. Batteries in original retail packaging that are
						  rated at 300 watt-hours or less for lithium-ion batteries or contain 25 grams
						  or less of lithium metal for lithium metal batteries.
4. Temporary storage of batteries or battery components
						  during the battery manufacturing process prior to completion of final quality
						  control checks.
5. Temporary storage of batteries during the vehicle
						  manufacturing or repair process.
322.2
Permits.
Permits shall be required for an accumulation of more
			 than 15 cubic feet (0.42 m3) of lithium-ion and
			 lithium metal batteries, other than batteries listed in the exceptions to
			 Section 322.1, as set forth in Section 105.5.14.1.
322.3
Fire safety plan.
A fire
			 safety plan shall be provided in accordance with Section 403.10.6. In addition,
			 the fire safety plan shall include emergency response actions to be taken upon
			 detection of a fire or possible fire involving lithium-ion or lithium metal
			 battery storage.
322.4
Storage requirements.
Lithium-ion and lithium metal batteries shall be
			 stored in accordance with Section 322.4.1, 322.4.2, or 322.4.3, as applicable.
322.4.1
Limited indoor storage in
			 containers.
Not more than 15 cubic feet (0.42
			 m3) of lithium-ion or lithium metal batteries shall
			 be permitted to be stored in containers in accordance with the following:
1. Containers shall be open-top and
			 constructed of noncombustible materials or shall be approved for battery
			 collection.
2. Individual
			 containers and groups of containers shall not exceed a capacity of 7.5 cubic
			 feet (0.21 m3).
3. A second container or group of containers
			 shall be separated by not less than 3 feet (914 mm) of open space, or 10 feet
			 (3048 mm) of space that contains combustible materials.
4. Containers shall be located not less than
			 5 feet (1524 mm) from exits or exit access doors.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0323 - Powered micromobility devices and powered industrial trucks

Current through Register Vol. 24-14, July 15, 2024
323.1
General.
Lithium-ion and lithium metal battery powered
			 micromo-bility devices and powered industrial trucks shall be operated and
			 maintained in accordance with this section.
EXCEPTIONS:
1. Storage, repair and charging in residential
						  occupancies of powered mobility devices, provided that such devices are for
						  personal use by its
owner
.
2. Charging of a single powered mobility device in any
						  occupancy by its
owner
.
323.1.1
Prohibited locations.
The use of a residential occupancy as a
			 business for the charging of commercially owned powered mobility devices or
			 powered industrial trucks as part of a rental or sales service shall not be
			 permitted.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0319 - Mobile food preparation vehicles

Current through Register Vol. 24-14, July 15, 2024
319.1
General.
Mobile food preparation vehicles
				that are equipped with appliances that produce smoke or grease-laden vapors or
				utilize LP-gas systems or CNG systems shall comply with this section.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0401 - General

Current through Register Vol. 24-14, July 15, 2024
401.2 Approval.
Where required by the fire code
				official, fire safety plans, emergency procedures and employee training
				programs shall be approved by the fire official.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0401, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0402 - Definitions

Current through Register Vol. 24-14, July 15, 2024
The following terms are defined in Chapter 2:
ALARM SIGNAL;
ALERT SIGNAL;
ALERT SYSTEM;
EMERGENCY EVACUATION DRILL;
LOCKDOWN;
SHELTER-IN-PLACE;
RECALL SIGNAL.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0402, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0403 - Emergency preparedness requirements

Current through Register Vol. 24-14, July 15, 2024
403.4.3
Assembly
			 points and fire operations.
Assembly points shall not be in areas likely
			 to be utilized for fire service operations.
403.9.2
Group R-2 occupancies.
Group R-2 occupancies shall comply with Sections 403.9.2.1 through 403.9.2.4.
403.9.2.4
Group R-2 assisted living and
			 residential care facilities.
Assisted living and residential care facilities licensed by the
				state of Washington shall comply with Section 403.7.1 as required for Group I-1
				Condition 2 occupancies.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0404 - Fire safety and evacuation plans

Current through Register Vol. 24-14, July 15, 2024
404.2.3 Lockdown plans.
This section is not
				adopted.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0404, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0405 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory
				Authority:
				RCW
				  19.27.031 and
				19.27.074. WSR 13-20-118, §
				51-54A-0405, filed 10/1/13, effective 11/1/13. Statutory Authority: RCW
				19.27A.031,
				
										19.27.074 and
				chapters
				19.27 and
				34.05 RCW. WSR 13-04-063, §
				51-54A-0405, filed 2/1/13, effective 7/1/13. WSR 13-20-001, § 51-54A-0405,
				filed 9/18/2013, effective 10/19/2013
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0406 - Employee training and response procedures

Current through Register Vol. 24-14, July 15, 2024
406.1
General.
Employees in the occupancies listed in Section 403 shall
			 be trained in the emergency procedures described in their emergency plans.
			 Training shall be based on these plans and as described in Sections 406.2
			 through 406.3.5.
406.2
Frequency.
Employees shall receive training in the contents of the
			 emergency plans and their duties as part of new employee orientation and at
			 least annually thereafter. Records shall be kept and made available to the fire
			 code official upon request.
406.3
Employee training program.
Employees shall be trained in fire
			 prevention, evacuation, sheltering-in-place, and fire safety in accordance with
			 Sections 406.3.1 through 406.3.5.
406.3.4
Emergency lockdown training.
This section is not
			 adopted.
406.3.5
Emergency
			 shelter-in-place training.
Where a facility has a shelter-in-place plan,
			 employees shall be trained on the alert and recall signals, communication
			 system, location of emergency supplies, the use of the incident notification
			 and alarm system, and their assigned duties and procedures in the event of an
			 alarm or emergency.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0408 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0408, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0503 - Fire apparatus access roads

Current through Register Vol. 24-14, July 15, 2024
503.1
Where
			 required.
Fire apparatus access roads shall be provided and maintained
			 in accordance with locally adopted street, road, and access standards.
503.1.1
Buildings and
			 facilities.
This section is not adopted.
503.1.2
Additional access.
This
			 section is not adopted.
503.1.3
High-piled storage.
This section is not adopted.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0507 - Fire protection water supplies

Current through Register Vol. 24-14, July 15, 2024
507.3
Fire
			 flow.
Fire flow requirements for buildings or portions of buildings and
			 facilities shall be determined by an approved method.
EXCEPTIONS:
1. Fire flow is not required for structures under 500
						  square feet (46 m2) with a B, U or R-1 occupancy
						  where structures are at least 30 feet (9144 mm) from any other structure and
						  are used only for ron.
2. Inuburban areas in which adequate and reliable water
						  supply systems do not exist, the fire
code official
is
						  authorized to utilize NFPA 1142 or the
International Wildland-Urban
						  Interface Code
.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0507, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0508 - Fire command center

Current through Register Vol. 24-14, July 15, 2024
508.1.2 Separation.
The fire command center shall
				be separated from the remainder of the building by not less than a 2hour fire
				barrier constructed in accordance with Section 707 of the International
				Building Code or horizontal assembly constructed in accordance with Section 711
				of the International Building Code, or both.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0508, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0605 - Fuel fired appliances

Current through Register Vol. 24-14, July 15, 2024
605.4.1.1
Approval.
Outdoor fuel oil storage tanks shall be in accordance
			 with UL 142, UL 142A, or UL 2085.
605.4.2.1
Approval.
Indoor fuel
			 oil storage tanks shall be in accordance with UL 80, UL 142, UL 142A, or UL
			 2085.
605.4.2.2
Quantity
			 limits.
One or more fuel oil storage tanks containing Class II or III
			 combustible liquid shall be permitted in a building. The aggregate capacity of
			 all tanks shall not exceed the following:
1.
			 660 gallons (2,498 L) in unsprinklered buildings, where stored in a tank
			 complying with UL 80, UL 142, UL 142A, or UL 2085.
2. 1,320 gallons (4,996 L) in buildings
			 equipped with an automatic sprinkler system in accordance with Section
			 903.3.1.1, where stored in a tank complying with UL 142 or UL 142A. The tank
			 shall be listed as a secondary containment tank, and the secondary containment
			 shall be monitored visually or automatically.
3. 3,000 gallons (11,356 L) in buildings
			 equipped with an automatic sprinkler system in accordance with Section
			 903.3.1.1, where stored in protected above-ground tanks complying with UL 2085
			 and Section 5704.2.9.7. The tank shall be listed as a secondary containment
			 tank, as required by UL 2085, and the secondary containment shall be monitored
			 visually or automatically.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0609 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Reviser's note:
The brackets and enclosed
				  material in the text of the above section occurred in the copy filed by the
				  agency and appear in the Register pursuant to the requirements of RCW
				    34.08.040.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0609, filed 2/1/13, effective 7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0806 - Decorative vegetation in new and existing buildings

Current through Register Vol. 24-14, July 15, 2024
806.1.1 Restricted occupancies.
Natural cut trees
				shall be prohibited in the following occupancies:
1.Group I; and
2.R-2 occupancies providing licensed care to clients in one of
				the categories listed in the International Building Code, Section 310.1,
				licensed by Washington state.
806.1.2 Support devices.
The support device that
				holds the tree in an upright position shall be of a type that is stable and
				that meets all of the following criteria:
1.The device shall hold the tree securely and be of adequate
				size to avoid tipping over of the tree.
2.The device shall be capable of containing a minimum supply of
				water in accordance with Table 806.1.2.
3.The water level, when full, shall cover the tree stem at
				least 2 inches (51 mm). The water level shall be maintained above the fresh cut
				and checked at least once daily.
Table 806.1.2 Support Stand Water Capacity
Tree Stem Diameter (inches)
Minimum Support Stand Water Capacity (gallons)
Typical Daily Water Transpiration Amount
							 (gallons)
Up to 4
1
1/4 to 1
4 to 6
1 1/2
1 1/4 to 1 1/2
7 to 8
2
1 3/4 to 2
9 to 12
3
2 1/4 to 3
13 and over
4
Over 3
Tree Stem Diameter (inches)
Minimum Support Stand Water Capacity (gallons)
Typical Daily Water Transpiration Amount (gallons)
Up to 4
1
1/4 to 1
4 to 6
1 1/2
1 1/4 to 1 1/2
7 to 8
2
1 3/4 to 2
9 to 12
3
2 1/4 to 3
13 and over
4
Over 3
Statutory Authority: RCW 19.27A.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0806, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0901 - General

Current through Register Vol. 24-14, July 15, 2024
901.4.2
Nonrequired fire protection systems and life safety systems.
A
fire protection
and
life safety system
or
			 portion thereof not required by this code or the
International Building
			 Code
shall be allowed to be furnished for partial or complete
			 protection provided such installed system meets the applicable requirements of
			 this code and the
International Building Code
. Such systems or
			 portion of system shall be provided with signage stating "NON-REQUIRED SYSTEM."
			 Signage shall be durable and permanent in nature, with contrasting color and
			 background, and with lettering of not less than 1 inch (25 mm) in height.
			 Location of such signage shall be approved.
901.8.2
Removal of existing
			 occupant-use hose lines.
The fire
code official
is
			 authorized to permit the removal of existing occupant-use hose lines where all
			 of the following conditions exist:
1.
			 Installation is not required by this code, the
International Building
			 Code
, or a previously approved alternative method.
2. The hose line would not be utilized by
			 trained personnel or the fire department.
3. The remaining outlets are compatible with
			 local fire department fittings.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0903 - Automatic sprinkler systems

Current through Register Vol. 24-14, July 15, 2024
903.2
Where
			 required.
Approved automatic sprinkler systems in new buildings and
			 structures shall be provided in the locations described in Sections 903.2.1
			 through 903.2.12.
EXCEPTIONS:
1. Spaces or areas in telecommunications buildings used
						  exclusively for telecommunications equipment, associated electrical power
						  distribution equipment, batteries and standby engines, provided that those
						  spaces or areas are equipped throughout with an automatic smoke detection
						  system in accordance with Section 907.2 and are separated from the remainder of
						  the building by not less than 1-hour
fire barriers
constructed
						  in accordance with Section 707 of the
International Building Code
or not less than 2-hour
horizontal assemblies
constructed in accordance with Section 711 of the
International
						  Building Code,
or both.
2. Bottom of the elevator hoistway in an enclosed and
						  noncombustible elevator shaft.
903.2.1.3
Group A-3.
An automatic sprinkler system shall be provided
			 throughout stories containing Group A-3 occupancies and throughout all stories
			 from the Group A-3 occupancy to and including the levels of exit discharge
			 serving that occupancy where one of the following conditions exists:
1. The fire area exceeds 12,000 square feet
			 (1115 m2).
2. The fire area has an occupant load of 300
			 or more.
3. The fire area is
			 located on a floor other than a level of exit discharge serving such
			 occupancies.
EXCEPTION:
For fixed guideway transit and passenger rail system
						  stations, an automatic sprinkler system shall be provided in accordance with
						  Section 4901.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0904 - Alternative automatic fire-extinguishing systems

Current through Register Vol. 24-14, July 15, 2024
904.1.1
Certification of service personnel for fire-extinguishing
			 equipment.
Service personnel performing system design, installation, or
			 conducting system maintenance or testing on automatic fire-extinguishing
			 systems, other than automatic sprinkler systems, shall possess the appropriate
			 ICC/NAFED certification.
904.1.1.1
Preengineered kitchen fire-extinguishing systems.
A current
			 ICC/NAFED certification for preengineered kitchen fire-extinguishing systems is
			 required when performing design, installation, inspection/testing or
			 maintenance on kitchen suppression systems.
904.1.1.2
Engineered fire suppression
			 systems.
A current ICC/NAFED certification for engineered fire
			 suppression systems is required when performing design, installation,
			 inspection/testing or maintenance on kitchen suppression systems.
904.1.1.3
Preengineered industrial
			 fire-extinguishing system.
A current ICC/NAFED certification for
			 preengineered industrial fire-extinguishing system is required when performing
			 design, installation, inspection/testing or maintenance on kitchen suppression
			 systems.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0908 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0908, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0909 - Section 909-Smoke control systems

Current through Register Vol. 24-14, July 15, 2024
909.21.12 Hoistway venting.
Hoistway venting need
				not be provided for pressurized elevator shafts.
909.21.13 Machine rooms.
Elevator machine rooms
				shall be pressurized in accordance with this section unless separated from the
				hoistway shaft by construction in accordance with Section 707 of the
International Building Code
.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-0909, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-0913 - Section 913-Fire pumps

Current through Register Vol. 24-14, July 15, 2024
913.2.1 Protection of fire pump rooms and access.
Fire pumps shall be located in rooms that are separated from all other areas of
				the building by 2-hour fire barriers constructed in accordance with Section 707
				of the
International Building Code
or 2-hour horizontal
				assemblies constructed in accordance with Section 711 of the
International Building Code
, or both. Fire pump rooms not
				directly accessible from the outside shall be accessible through an enclosed
				passageway from an interior exit stairway or exterior exit. The enclosed
				passageway shall have a
fire-resistance rating
not less than
				the
fire-resistance rating
of the fire pump room (see NFPA 20
				Section 4.14.2.1.2).
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-1003 - General means of egress

Current through Register Vol. 24-14, July 15, 2024
1003.7
Elevators, escalators, and moving walks.
Elevators, escalators, and
			 moving walks shall not be used as a component of a required means of egress
			 from any other part of the building.
EXCEPTIONS:
1. Elevators used as an accessible means of egress in
						  accordance with Section 1009.4.
2. Escalators used as a means of egress for fixed
						  transit and passenger rail systems in accordance with Section 4901.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-1005 - Means of egress sizing

Current through Register Vol. 24-14, July 15, 2024
1005.1 General.
All portions of the
means
				of egress
system shall be sized in accordance with this section.
EXCEPTIONS:
1. Aisles and aisle access ways in rooms or spaces used
						  for assembly purposes complying with Section 1030.
2. The capacity in inches, of means of egress
						  components for fixed guideway transit and passenger rail stations, shall meet
						  the requirements of Section 4901.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-1006 - Number of exits and exit access doorways

Current through Register Vol. 24-14, July 15, 2024
1006.2.1
Egress
			 based on occupant load and common path of egress travel distance.
Two
exits
or
exit
access doorways from any space
			 shall be provided where the design occupant load or the common path of egress
			 travel distance exceeds the values listed in Table 1006.2.1. The cumulative
occupant load
from adjacent rooms, areas or spaces shall be
			 determined in accordance with Section 1004.2.
EXCEPTIONS:
1. The number of
exits
from foyers,
						  lobbies, vestibules or similar spaces need not be based on cumulative
occupant loads
for areas discharging through such spaces, but
						  the capacity of the
exits
from such spaces shall be based on
						  applicable cumulative occupant loads.
2. Care suites in Group I-2 occupancies complying with
						  Section 407.4 of the
International Building Code.
3. Unoccupied mechanical rooms and penthouses are not
						  required to comply with the common path of egress travel distance
						  measurement.
4. The common path of travel for fixed transit and
						  passenger rail system stations shall be in accordance with Section
						  4901.
1006.2.1.1
Three or more exits or exit access doorways.
Three
exits
or
exit
access doorways shall be
			 provided from any space with an occupant load of 501 to 1,000. Four exits or
			 exit access doorways shall be provided from any space with an occupant load
			 greater than 1,000.
EXCEPTION:
The number of required exits for fixed transit and
						  passenger rail systems may be reduced by one at open stations.