Wisconsin Administrative Code › Department of Natural Resources › NR 400-499 - Environmental Protection - Air Pollution Control › Chapter NR 462 - National emission standards for hazardous air pollutants for industrial, commercial and institutional boilers and process heaters › Section NR 462.05 - Testing, fuel analyses and initial compliance requirements

Current through June 24, 2024
(1) WHAT ARE MY
				INITIAL COMPLIANCE REQUIREMENTS AND DEADLINES?
(a) For affected sources that elect to
				demonstrate compliance with any of the emission limits of this chapter through
				performance testing, your initial compliance requirements include conducting
				performance tests according to sub. (3) and Table 5 of this chapter, conducting
				a fuel analysis for each type of fuel burned in your boiler or process heater
				according to sub. (4) and Table 6 of this chapter, establishing operating
				limits according to sub. (7) and Table 7 of this chapter, and conducting CMS
				performance evaluations according to sub. (6).
(b) For affected sources that elect to
				demonstrate compliance with the emission limits for HCl, mercury or TSM through
				fuel analysis, your initial compliance requirement is to conduct a fuel
				analysis for each type of fuel burned in your boiler or process heater
				according to sub. (4) and Table 6 of this chapter and establish operating
				limits according to sub. (7) and Table 8 of this chapter.
(c) For affected sources that have an
				applicable work practice standard, your initial compliance requirements depend
				on the subcategory and rated capacity of your boiler or process heater. If your
				boiler or process heater is in any of the limited use subcategories or has a
				heat input capacity less than 100 mmBtu per hour, your initial compliance
				demonstration is conducting a performance test for carbon monoxide according to
				Table 5 of this chapter. If your boiler or process heater is in any of the
				large subcategories and has a heat input capacity of 100 mmBtu per hour or
				greater, your initial compliance demonstration is conducting a performance
				evaluation of your continuous emission monitoring system for carbon monoxide
				according to sub. (6) (a).
(d) For
				existing affected sources, you shall demonstrate initial compliance no later
				than 180 days after the compliance date that is specified for your source in s.
				NR
				462.01(5) and according to the
				applicable provisions in s.
				NR 460.06(1)
				(b) as cited in Appendix DDDDD in ch. NR
				460.
(e) If your new or
				reconstructed affected source commenced construction or reconstruction between
				January 13, 2003 and November 12, 2004, you shall demonstrate initial
				compliance with either the proposed emission limits and work practice standards
				or the promulgated emission limits and work practice standards no later than
				180 days after November 12, 2004 or within 180 days after startup of the
				source, whichever is later, according to s.
				NR 460.06(1)
				(b).
(f) If your new or reconstructed affected
				source commenced construction or reconstruction between January 13, 2003 and
				November 12, 2004, and you chose to comply with the proposed emission limits
				and work practice standards when demonstrating initial compliance, you shall
				conduct a second compliance demonstration for the promulgated emission limits
				and work practice standards within 3 years after November 12, 2004 or within 3
				years after startup of the affected source, whichever is later.
(g) If your new or reconstructed affected
				source commences construction or reconstruction after November 12, 2004, you
				shall demonstrate initial compliance with the promulgated emission limits and
				work practice standards no later than 180 days after startup of the
				source.