reglab/statecodes huggingface dataset:
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.1701 - Scope, application, and definitions

Current through June 24, 2024
(1) Substitute the
					 following informational notes for the requirements in ASME A17.1 section 1.1:
Note: See sections
						SPS 318.1002 and 318.1003
						for scope and application requirements.
Note: See ASME A18.1 and subchapter V for requirements
						relating to vertical and inclined platform lifts, and stairway chairlifts
						serving public buildings and places of employment.
(2) Substitute the following definitions for
					 the corresponding definitions specified in ASME A17.1 section 1.3:
(a) "Authority having jurisdiction" means the
					 department of safety and professional services, except as designated under s.
					 SPS
					 318.1012.
(b) "Rated speed, down" means all of the
					 following:
1. Prior to passing an acceptance
					 inspection, the speed at which the car, platform, or chair of an electric
					 elevator, dumbwaiter, material lift, vertical platform lift, inclined platform
					 lift, or stairway chairlift is designed to operate in the down direction with
					 rated load.
2. Upon acceptance
					 inspection, the actual speed at which the car, platform, or chair of an
					 electric elevator, dumbwaiter, material lift, vertical platform lift, inclined
					 platform lift, or stairway chairlift operates in the down direction with rated
					 load.
Note:
"Rated speed, down" applies to
						components where "rated speed" is used to describe the speed in the down
						direction for determining performance criteria for that code section. For the
						actual downspeed of a hydraulic elevator, dumbwaiter, or material lift, see the
						definition for "operating speed in the down direction."
(c) "Rated speed, up" means all of
					 the following:
1. Prior to passing an
					 acceptance inspection, the speed which the car, platform, or chair of an
					 elevator, dumbwaiter, material lift, vertical platform lift, inclined platform
					 lift, or stairway chairlift is designed to operate in the up direction with
					 rated load.
2. Upon acceptance
					 inspection, the actual speed at which the car, platform, or chair of an
					 elevator, dumbwaiter, material lift, vertical platform lift, inclined platform
					 lift, or stairway chairlift operates in the up direction with rated load.
Note:
"Rated speed, up" applies to
						components where "rated speed" is used to describe the speed in the up
						direction for determining performance criteria for that code section.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.1702 - Electric elevators

Current through June 24, 2024
(1) PIT DRAINS AND SUMPS.
(a) This is a department informational note
					 to be used under ASME A17.1 section 2.2.2.3:
Note: See ch. SPS 362 of the building code for hoistway
						drain and sump requirements for elevators in commercial buildings.
(b) Substitute the following
					 informational note for the requirements in ASME A17.1 section 2.2.2.5:
Note: See chapter
						SPS
						362 of the building code for hoistway drain and sump
						requirements for elevators in commercial buildings.
(bm) This is a department rule in addition to
					 the requirements in ASME A17.1 section 2.4.5: The data plate shall indicate the
					 minimum designed counterweight runby.
(c) This is a department informational note
					 to be used under ASME A17.1 section 2.7:
Note: See section
						SPS
						382.33 for prohibition of sumps and sump pumps in
						elevator machine rooms for elevators in commercial buildings.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.1703 - Hydraulic Elevators

Current through June 24, 2024
(1) HYDRAULIC JACKS. Substitute the following
					 wording for the requirements in ASME A17.1 section 3.18.3.8.3(b):
(a) The cylinder bottom and sides below the
					 pit floor shall be completely surrounded by a protective material designed to
					 withstand a static head of water from the ground level to the bottom of the
					 cylinder, based on the manufacturer's rating of the material.
(b) The top of the material shall be visible
					 at the pit floor.
(c) A means shall
					 be provided between the material and cylinder to monitor the space for the
					 entrance of water. The means to monitor shall comply with all of the following:
1. Extend from above the pit floor to below
					 the bottom of the jack.
2. Be open
					 on the bottom.
3. Be exposed and
					 visible at the pit floor.
4. Be
					 capped, plugged, or otherwise sealed at the top with a removable
					 means.
(d) The space
					 between the material, the means to monitor and the jack shall be sealed at or
					 near the pit floor to prevent the entrance of water from the pit.
(e) The material shall be one of the
					 following:
1. Rigid, non-metallic material
					 such as polyvinylchloride or high-density polyethylene, of a schedule that will
					 withstand the installation process.
2. Flexible material that is approved by the
					 department. Monitoring for the entrance of ground water shall be performed
					 according to the following schedule with findings recorded in the maintenance
					 record:
a. At the time of the acceptance
					 inspection.
b. Quarterly for the
					 first 2 years corresponding with quarterly checking of oil usage required by s.
					 SPS 318.17086(11) (a).
c. Annually
					 thereafter.
(f) If at any time water is found that cannot
					 be explained by some type of accidental entry, the material shall be replaced
					 within 6 months.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.1707 - Dumbwaiter and Type B material lifts

Current through June 24, 2024
(1) POWER AND HAND
					 DUMBWAITERS WITHOUT AUTOMATIC TRANSFER DEVICES. Substitute the following
					 wording for the requirements in ASME A17.1 Part 7, Scope: This part applies to
					 power dumbwaiters and Type B material lifts.
(2) HOISTWAY-ACCESS DOORS. This is a
					 department rule in addition to the requirements in ASME A17.1 section 7.1.11.5:
					 Hoistway access door panels for power dumbwaiters shall be provided with an
					 electric contact to remove power to the driving machine when the panel is not
					 in the closed position.
(3)
					 HOISTWAY-DOOR VISION PANELS. Substitute the following wording for the
					 requirements in ASME A17.l section 7.1.11.8: Vision panels shall be provided in
					 hoistway doors where position indicators are not provided. Vision panels shall
					 comply with the requirements in ASME A17.1 sections 2.11.7.1.2, 2.11.7.1.3,
					 2.11.7.1.4, and 2.11.7.1.6, and the total area of one or more vision panels in
					 any hoistway door may not be less than 4 square inches and not more than 25
					 square inches.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.1708 - Special application elevators (Repealed)

Current through June 24, 2024
The Department forms required in this chapter are
						  available for a nominal fee at telephone 800-DOC-SALE or 411
						  (Telecommunications Relay) or at docsales@doa.state.wi.us, or at no charge at
						  the Department's Web site at
http://dsps.wi.gov
through links to Division
						  of Industry Services forms.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.17081 - Security

Current through June 24, 2024
This is a department rule in addition to the
						requirements in ASME A17.1 section 8.1: Key access for installations after June
						1, 2020, as specified in this section, shall be verified by the department or
						agent municipality.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.17086 - Maintenance, repair, replacement, and testing

Current through June 24, 2024
(1) APPLICATION OF
					 ASME A17.1 SECTION 8.6. The introductory paragraph of ASME A17.1 section 8.6 is
					 not included as part of this chapter.
(2) DOCUMENTATION.
(a) These are department rules in addition to
					 the requirements in ASME A17.1 section 8.6.1.1.3:
1. A new or updated maintenance control
					 program, maintenance records, and wiring diagrams in electronic form shall be
					 transferred to a paper copy of the documents by the installing or service
					 contractor within 3 months of the associated maintenance, repair, replacement,
					 or alteration.
2. The maintenance
					 control program, including any devices and procedures needed to meet ASME A17.1
					 section 8.6.1.2.1(f), and the maintenance records and wiring diagrams are the
					 property of the conveyance owner, not a conveyance installer or service
					 company. They may be removed only with the permission of the owner.
3. An additional set of electrical wiring
					 diagrams may be securely located on the top of the car only if another complete
					 set is located in a place that is accessible by the owner or the owner's
					 agent.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.17087 - Alterations

Current through June 24, 2024
(1) This is a department rule in addition to
					 the requirements in ASME A17.1 section 8.7.2.8: Where sprinklers are added to
					 an existing elevator machine room, machinery space, control room, control
					 space, or top of hoistway, the installation shall comply with the requirements
					 in ASME A17.1 section 8.7.2.28(c) and (e), except as follows:
(a) Where the elevator already is equipped
					 with Phase I and Phase II firefighters' emergency operation and the existing
					 car operating panel will remain, the elevator is not required to have the
					 firefighters' emergency operation functions on the car operating panel behind a
					 locked cover, unless required by another part of ASME A17.1 section
					 8.7.
(b) Where the elevator already
					 is equipped with a Phase I key switch of the bypass-off-on type, the key switch
					 is not required to meet ASME A17.1 section 2.27.3.1 unless required by another
					 part of ASME A17.1 section 8.7.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.17089 - Code data plate

Current through June 24, 2024
Substitute the following wording for the requirements in
						the introductory paragraph of ASME A17.1 section 8.9: ASME A17.1 section 8.9
						contains requirements for all new equipment within the scope of this
						chapter.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.170810 - Acceptance inspections and tests, general requirements

Current through June 24, 2024
(1) PERSONS
					 AUTHORIZED TO MAKE ACCEPTANCE INSPECTIONS AND TESTS. Substitute the following
					 wording for the requirements in ASME A17.1 sections 8.10.1.1.1 and 8.10.1.1.3:
					 All acceptance inspections shall be performed by licensed elevator
					 inspectors.
(2) PERSONS INSTALLING
					 OR ALTERING EQUIPMENT. This is a department rule in addition to the
					 requirements in ASME A17.1 section 8.10.1.1.2: The installation may not be
					 placed in service until authorized by the department or agent
					 municipality.
(3) ACCEPTANCE TEST
					 REPORTS. This is a department rule in addition to the requirements in ASME
					 A17.1 section 8.10.1.1.5: The results of acceptance tests including those
					 required to be witnessed by the licensed elevator inspector shall be recorded
					 on forms of the department or agent municipality. Where witnessed, forms are
					 not required to be submitted to the department or agent municipality.
Note:
Forms required under this chapter are
						available on the department's website at
https://dsps.wi.gov
, or by request from the
						Department of Safety and Professional Services, P. O. Box 7302, Madison,
						Wisconsin 53708, or call (608) 266-2112.
(4) REPLACEMENT OF SPEED GOVERNOR INSPECTION
					 AND TEST REQUIREMENTS. This is a department rule in addition to the
					 requirements in ASME A17.1 section 8.10.2.3.2(f): Where a speed governor is
					 replaced, in accordance with 8.6.3.6.1, tests shall be performed as specified
					 in ASME A17.1 sections 8.10.2.2.2(hh) and 8.6.4.20.2(b).
(5) ELEVATORS USED FOR CONSTRUCTION. This is
					 a department rule in addition to the requirements in ASME A17.1 section
					 8.10.5.10: The department may conduct a maximum of 2 billable construction use
					 inspections in a 90-day period unless the department finds probable cause for
					 additional inspections.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.170811 - General requirements for periodic inspections and witnessing of tests

Current through June 24, 2024
(1)
					 PERSONS AUTHORIZED TO PERFORM PERIODIC INSPECTIONS AND TO WITNESS TESTS.
					 Substitute the following wording for the requirements in ASME A17.1 sections
					 8.11.1.1 and 8.11.1.1.1: Licensed elevator inspectors performing periodic
					 inspections shall comply with the applicable credentialing requirements in ch.
					 SPS 305.
(2) PERSONS AUTHORIZED TO
					 PERFORM PERIODIC TESTS. Substitute the following wording for the requirements
					 in ASME A17.1 section 8.11.1.1.2(a): Licensed or registered elevator personnel
					 performing periodic inspections and tests under ASME A17.1 section
					 8.11 shall comply
					 with ch. SPS 305. Licensed elevator inspectors may choose to witness
					 tests.
(3) PERIODIC TEST REPORTS.
					 Substitute the following wording for the requirements in ASME A17.1 section
					 8.11.1.1.2(b): Results of required tests shall be reported by the person
					 performing the test, on approved forms, where required.
Note:
Forms required under this chapter are
						available on the department's website at
https://dsps.wi.gov
, or by request from the
						Department of Safety and Professional Services, P.O. Box 7302, Madison,
						Wisconsin 53708, or call (608) 266-2112.
(4) PERIODIC INSPECTION AND TEST FREQUENCY.
					 Substitute the following wording for the requirements in ASME A17.1 section
					 8.11.1.3:
(a) Periodic inspections shall be
					 made at intervals not longer than one year.
(b) Except as provided in sub. (8), category
					 1 periodic tests shall be made at intervals not longer than one year.
(c) Category 3 periodic tests shall be made
					 at intervals not longer than 3 years.
(d) Category 5 periodic tests shall be made
					 at intervals not longer than 5 years.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter IV - Changes, Additions, or Omissions to ASME A17.1 › Section SPS 318.1709 - Reference codes, standards, and specifications

Current through June 24, 2024
(1) This is a
					 department rule in addition to the requirements in ASME A17.1 Part 9: Any code
					 or standard listed in section 9.1 without a specific year of issuance shall
					 mean the published edition of that code or standard which was available on May
					 30, 2017, except where a different edition is specified directly or indirectly
					 in the building code, that different edition applies.
(2)
(a)
					 Substitute chs.
					 SPS
					 361 to 366 for the reference to ICC/ANSI A117.1 in
					 ASME A17.1 section 9.1 and in any other ASME A17.1 section where that reference
					 appears.
(b) Substitute ch. SPS 316
					 for the reference to NFPA 70 in ASME A17.1 section 9.1 and in any other ASME
					 A17.1 section where that reference appears.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1800 - Platform lifts and stairway lifts

Current through June 24, 2024
(1) GENERAL.
					 Vertical platform lifts, inclined platform lifts, and stairway lifts shall be
					 designed, constructed, installed, operated, maintained, tested, and inspected
					 in accordance with ASME A18.1, except as otherwise provided in this chapter.
Note:
The commercial building code,
						chapters
						SPS
						361 to
						366, establishes standards for
						buildings and components that may be associated with platform lifts and
						stairway lifts, including ramps, ramp slopes, stairway egress width, and the
						location, clearances, or position of controls for people with
						disabilities.
(2) CHANGES,
					 ADDITIONS, AND OMISSIONS. Changes, additions, or omissions to ASME A18.1 are
					 specified in this subchapter and are rules of the department and are not
					 requirements in ASME A18.1.
The sections in this chapter are generally numbered to
						  correspond with the section numbering in ASME A18.1. For example, section
						  SPS
						  318.1801 corresponds to ASME A18.1 Section 1.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1801 - Scope, application, and definitions

Current through June 24, 2024
(1) SCOPE AND
					 APPLICATION. Substitute the following informational note for the requirements
					 in ASME A18.1 section 1.1:
Note: See sections
						SPS 318.1002 and 318.1003
						for scope and application requirements.
(2) DEFINITIONS.
(a) Substitute the following definitions for
					 the corresponding definitions specified in ASME A18.1 section 1.3:
1. "Authority having jurisdiction" means the
					 department of safety and professional services, except as designated under s.
					 SPS
					 318.1012.
2. "Building code" means chs.
					 SPS
					 361 to 366.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1802 - Vertical platform lifts

Current through June 24, 2024
(1) RUNWAY
					 ENCLOSURE PROVIDED.
(a) This is a department
					 rule in addition to the requirements in ASME A18.1 sections 2.1.1.2 and
					 2.1.1.3: The clearance between the platform and the glazing in a fire-rated
					 runway door shall be not more than 1 1/4 inches. The shear condition at the top
					 of any glazing in the door shall be beveled at not less than 45
					 degrees.
(b) This is a department
					 rule in addition to the requirements in ASME A18.1 section 2.1.1.7: Where the
					 platform enclosure extends less than 79 inches above the platform, the
					 horizontal clearance between the platform enclosure on a side not containing an
					 entrance and the adjacent runway enclosure wall or the vertical surface of the
					 machine tower may not exceed 4 inches. The horizontal clearance between the
					 platform enclosure and the runway enclosure walls on either side of the machine
					 tower may not exceed 12 inches. These maximum clearances do not apply to spaces
					 above the machine tower or to any point more than 42 inches above the top
					 landing.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1803 - Inclined platform lifts

Current through June 24, 2024
(1) RUNWAYS.
					 Substitute the following wording for the requirements in ASME A18.1 section
					 3.1.1: Inclined platform lifts shall be installed so that the necessary means
					 of egress is maintained as required in the building code. For new
					 installations, the egress width shall be measured with the inclined platform
					 lift in the unfolded, usable position. For replacement of a previously approved
					 inclined platform lift, the egress width may remain as it has been with the
					 original lift in place, but may not be reduced by the replacement.
(2) LOWER LEVEL ACCESS RAMPS AND PITS.
(a) Substitute the following wording for the
					 requirements in ASME A18.1 section 3.1.4.1: Ramping inclinations for
					 floor-mounted ramps shall be in accordance with the building code.
Note:
Under the building code, a floor
						surface steeper than 1:48 within the required wheelchair-maneuvering clearances
						at a lift entrance is a ramp, and a lift entrance at a ramp must have a
						power-opening device. Clearances to the lift call and door-opener button must
						also meet the building code.
(b) Substitute the following wording for the
					 requirements in the last sentence and pars. (a) to (e) of ASME A18.1 section
					 3.1.4.2: When in use, the inclination of retractable ramps shall be in
					 accordance with the building code.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1804 - Inclined stairway chair lifts

Current through June 24, 2024
Substitute the following wording for the requirements in
						ASME A18.1 section 4.1.1: Stairway chairlifts shall be installed so that the
						required means of egress is maintained as required in the building code. For
						new installations, the egress width shall be measured with the stairway chair
						lift in the unfolded, usable position. For replacement of a previously approved
						stairway chair lift, the egress width may remain as it has been with the
						original lift in place, but may not be reduced by the
						replacement.
Stairway chairlifts complying with this section may be
						  installed as a convenience for individuals but are not recognized by the
						  building code as providing accessibility due to the inability of a wheelchair
						  user to use them without assistance.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1808 - Hydraulic driving means

Current through June 24, 2024
These are department rules in addition to the
						requirements in ASME A18.1 section 8.1:
(1) SHUTOFF VALVE.
(a) A manually operated shutoff valve shall
					 be provided between the hydraulic pump unit and the hydraulic
					 cylinder.
(b) For a lift with a
					 machine room, the shutoff valve under par. (a) shall be located inside the
					 machine room and adjacent to the hydraulic pump unit.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1809 - Rope sockets

Current through June 24, 2024
This is a department rule in addition to the requirements
						in ASME A18.1 section 9.8: Where wedge rope sockets are provided, they shall
						conform to the requirements in ASME A17.1 section 2.20.9.5.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1810 - Routine, periodic, and acceptance inspections and tests

Current through June 24, 2024
(1) INSPECTORS. The
					 requirements in ASME A18.1 sections 10.1.1 to 10.1.4 are not included as part
					 of this chapter.
Note:
See s.
						SPS
						318.1011 for additional requirements relating to
						inspections
(2)
					 APPLICABILITY OF INSPECTION AND TEST REQUIREMENTS. Substitute the following
					 wording for the requirements in ASME A18.1 section 10.1.5: Inspections and
					 tests required by subs. (4) to (8) are to determine whether the equipment
					 conforms to whichever of the following are applicable:
(a) The standard in effect on the contract
					 date for the original installation.
(b) For altered components, the standard in
					 effect on the contract date for the alteration.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter V - Changes, Additions, or Omissions to ASME A18.1 › Section SPS 318.1811 - Maintenance logs

Current through June 24, 2024
(1) WEEKLY OPERATION PROCEDURE. The
					 requirements in ASME A18.1 section 11.1.2(c) are not included as part of this
					 chapter.
(2) ON-SITE DOCUMENTATION.
					 This is a department rule in addition to the requirements in ASME A18.1 part
					 11.3: For a lift having an inspection and test panel, the inside cover of the
					 inspection and test panel shall provide instructions for locating the on-site
					 documentation. Instructions shall be permanently legible with lettering not
					 less than 1/8 inch in height.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4200 - Entertainment technology

Current through June 24, 2024
(1) GENERAL.
					 Orchestra pit lifts shall be designed, constructed, installed, operated,
					 maintained, tested, and inspected in accordance with ANSI E1.42, except as
					 otherwise provided in this subchapter.
(2) CHANGES, ADDITIONS, AND OMISSIONS.
					 Changes, additions, or omissions to ANSI E1.42 are specified in this subchapter
					 and are rules of the department and are not requirements in ANSI E1.42.
Note:
The sections in this subchapter are
						generally numbered to correspond with the chapter numbering in ANSI E1.42. For
						example, section SPS 318.4201 corresponds to ANSI E1.42 Chapter 1.
(3) RETROACTIVITY. The operation,
					 testing, maintenance, and periodic inspection requirements of this subchapter
					 apply to all orchestra pit lifts existing prior to June 1, 2020.
(4) PIT ACCESS. Orchestra pit lifts installed
					 after June 1, 2020, in accordance with this subchapter shall include a means to
					 access the pit for use when the lift is at the lowest landing.
(5) STAGE FALL PROTECTION PLAN. An orchestra
					 pit lift owner shall develop and implement a protection plan to address the
					 hazard of stage edge falls.
An example of a stage edge fall protection plan is
						  available in ANSI E1.42 Annex B.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4201 - Scope and application

Current through June 24, 2024
(1) The statement
					 in ANSI E1.42 section 1.1.1.1 is not included as part of this
					 subchapter.
(2) This is a
					 department rule in addition to the requirements in ANSI E1.42 section 1.1.2:
					 This subchapter covers the design, construction, operation, inspection,
					 testing, maintenance, alteration, and repair of orchestra pit lifts and the
					 associated parts, rooms, spaces, and hoistways.
(3) This is a department rule in addition to
					 the requirements in ANSI E1.42 section 1.1.4: An orchestra pit lift that is not
					 covered by this subchapter shall be subject to s.
					 SPS
					 318.1700(1).
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4202 - Reference codes, standards, and specifications

Current through June 24, 2024
Substitute the following requirement for ANSI E1.42
						section 2.1: All references listed in ANSI E1.42 section 2.2are informational
						only and are not requirements of this subchapter.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4203 - Definitions

Current through June 24, 2024
(1) Substitute the following definitions for
					 the corresponding definitions specified in ANSI E1.42 chapter 3:
(a) "Authority having jurisdiction" means the
					 department of safety and professional services, except as designated under s.
					 SPS
					 318.1012.
(b) "Lifting load" means the load that the
					 equipment is designed and installed to lift at the rated speed.
(c) "Qualified person" means one who is
					 licensed for the corresponding work by the department under s.
					 SPS
					 305.991.
(d) "Static load" means the live load that
					 the orchestra pit lift is designed and installed to support while the lift
					 platform is not in motion as provided by the manufacturer upon installation or
					 as approved by the department.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4204 - Design requirements

Current through June 24, 2024
(1) Substitute the following wording for the
					 requirements in ANSI E1.42 section 4.3.3: The horizontal gaps between the edges
					 of the lift platform floor and fixed floors shall be greater than zero, in
					 order to avoid direct contact, and not greater than 3/4 inch.
(2) This is a department rule in addition to
					 the requirements in ANSI E1.42 section 4.1.4.1: The means of stopping and
					 preventing unintended movement of the lift platform shall be tested at 100% of
					 rated load.
(3) Substitute the
					 following wording for the requirements in ANSI E1.42 section 4.1.4.1.2: An
					 inherently self-locking gear reducer or actuator that resists motion by a
					 restraining force 150% or greater than the applied force may be permitted for
					 use as secondary means against uncontrolled or unintended movement, where
					 available from the manufacturer. Where the secondary means is installed, it
					 shall be inspected by a qualified person.
(4) This is a department rule in addition to
					 requirements in ANSI E1.42 section 4.3.3.1: The horizontal gaps shall be
					 measured between the edge of the lift platform surface and the edge of the
					 fixed floor.
(5) This is a
					 department rule in addition to requirements in ANSI E1.42 section 4.6.1: The
					 illumination levels shall be a minimum of 19 foot candles at the controller
					 with the door open or closed, at the main disconnect location, and at the drive
					 machines. The remainder of the pit floor shall be a minimum of 10 foot candles,
					 including at access levels, the route to controller and disconnect location,
					 and any other Group 2 areas, in accordance with ASME A17.1, section 2.2.5, as
					 applicable.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4205 - Control systems

Current through June 24, 2024
(1) This is a department informational note
					 to be used under ANSI E1.42 section 5.1.3:
Note:
See s.
						SPS
						316.620 and NEC 620 for additional
						requirements.
(2)
					 Substitute the following wording for the requirements in ANSI E1.42 section
					 5.5.4: When actual and stored position data differ, setting or restoring
					 position data for the lift shall only be done by qualified or competent
					 persons.
(3) Substitute the
					 following wording for the requirements in ANSI E1.42 section 5.6.1.2: The
					 circumstances requiring the override shall be investigated by a competent
					 person before an override is engaged and may only be performed by an authorized
					 person in communication with the operator. Override devices shall be located in
					 a position so as to provide the authorized person a clear line of sight to the
					 condition requiring the override. Indicators at all operator positions shall
					 change state to inform the operator that the override has been engaged. The
					 override device may not initiate motion without the direct action of the lift
					 operator and shall limit speed and direction of travel while engaged.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4206 - Safety systems

Current through June 24, 2024
(1) This is a department rule in addition to
					 requirements in ANSI E1.42 section 6.3.1.2: Suitable active guarding mechanisms
					 shall be per manufacturer's recommendations or as approved by the
					 department.
(2) This is a
					 department rule in addition to requirements in ANSI E1.42 section 6.4.6: The
					 emergency unlocking or unlatching release systems shall be accessible only to
					 competent persons.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4207 - Installation and inspections

Current through June 24, 2024
(1) Substitute the
					 following for the requirements in ANSI E1.42 section 7.1.1: Orchestra pit lifts
					 shall be tested in accordance with the applicable criteria in ASME A17.1
					 section 8.6.
(2) The requirement in
					 ANSI E1.42 section 7.1.4 is not included as part of this subchapter.
(3) Substitute the following for the
					 requirements in ANSI E1.42 section 7.2.2: Compliance testing may be observed by
					 the department.
(4) Substitute the
					 following wording for the requirements in ANSI E1.42 section 7.9.7.5: Any
					 additional issues as identified by the manufacturer's instructions or noted by
					 the department during previous inspections.
(5) These are department rules in addition to
					 requirements in ANSI E1.42 chapter 7:
(a)
					 Periodic inspections shall be made at intervals not longer than one
					 year.
(b) Periodic tests in
					 conformance with ANSI E1.42 sections 7.3, 7.4, 7.5, and 7.8 shall be made at
					 intervals not longer than one year.
(c) Periodic tests in conformance with ANSI
					 E1.42 sections 7.6, 7.7, 7.9, and
					 7.10 shall be made
					 at intervals not longer than 5 years.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-319 - General, Part I › Chapter SPS 318 - Elevators, Escalators, and Lift Devices › Subchapter VI - Changes, Additions, or Omissions to ANSI E1.42 › Section SPS 318.4208 - Operation, maintenance, and repair

Current through June 24, 2024
(1) Substitute the
					 following wording for the requirements in ANSI E1.42 section 8.1.2: A written
					 record of all trainings for competent persons and authorized persons, including
					 the names of the competent persons, the names of the authorized persons, the
					 names and affiliations of the trainers, and the dates of any training received
					 from the trainers shall be maintained and shall be made available for
					 inspection on request.
(2)
					 Substitute the following wording for the requirements in ANSI E1.42 section
					 8.2.4: If a fault, malfunction, damage, unusual sound, or other unusual
					 performance of the orchestra pit lift occurs, then the operator shall stop the
					 lift and evaluate the lift status. If corrective action cannot be taken within
					 the authority of the operator, then the lift shall be taken out of service and
					 referred to a competent person. Any such event and resulting actions shall be
					 reported in accordance with section 8.3.4.
(3) Substitute the following wording for the
					 requirements in ANSI E1.42 section 8.3.3: For new installations, the initial
					 maintenance control program shall be provided by the equipment manufacturer.
					 For existing equipment undergoing any alteration, repair, or replacement, the
					 maintenance control program for the altered, repaired, or replaced components
					 shall be provided by the person or firm performing the work. The maintenance
					 control program shall be made available at the scheduled time for service,
					 tests, or inspection.
(4) This is a
					 department rule in addition to requirements in ANSI E1.42 section 8.3.4: A
					 paper copy of the record shall be available.
(5) Substitute the following wording for the
					 requirements in ANSI E1.42 section 8.4.1.2: Alterations and repairs to
					 orchestra pit lifts manufactured to this standard shall be performed or
					 supervised by qualified persons, in accordance with s.
					 101.984,
					 Stats.
(6) Substitute the following
					 wording for the requirements in ANSI E1.42 section 8.4.6.1: Orchestra pit lifts
					 subject to this subchapter shall be inspected and operationally tested in
					 accordance with ANSI E1.42 by a qualified person after any alterations,
					 replacements, or repairs listed in table
					 SPS
					 318.1007 -1, as applicable. An orchestra pit lift may
					 not be returned to service until it is in compliance with ANSI E1.42 section
					 8.4.6.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 301-366 - Commercial Building Code › Chapter SPS 366 - Existing Buildings › Subchapter I - Purpose, Scope and Application › Section SPS 366.1401 - Performance compliance methods

Current through June 24, 2024
(1) APPLICABILITY.
					 Substitute the following wording for the requirements in IEBC section
					 1401.2: The provisions of
					 sections 1401.2.1 through
					 1401.2.5 shall apply to existing
					 occupancies that will continue to be, or are proposed to be, in Groups A, B, E,
					 F, M, R, and S. These provisions may not apply to buildings with occupancies in
					 Group H or Group I.
(2)
					 ACCESSIBILITY REQUIREMENTS. Substitute the following wording for the
					 requirements in IEBC section
					 1401.2.5: All portions of the
					 buildings proposed for change of occupancy or being altered shall conform to
					 the accessibility provisions of IEBC section 410.
(3) OTHER CODES. The requirements in IEBC
					 section 1401.3.2 are not included as
					 part of chs.
					 SPS 361 to
					 366.
(4) MINIMUM PLUMBING FIXTURES. This is a
					 department rule in addition to the requirements in IEBC section
					 1401.2: Where the occupant load
					 of a story is increased by more than 20 percent, plumbing fixtures for the
					 story shall be provided in quantities specified in the IBC based on the
					 increased occupant load.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 320-325 - Uniform Dwelling Code › Chapter SPS 320 - Administration And Enforcement › Subchapter I - Purpose and Scope › Section SPS 320.01 - Purpose

Current through June 24, 2024
(1) The purpose of this code is to establish
					 uniform statewide construction standards and inspection procedures for one- and
					 2-family dwellings and modular homes in accordance with the requirements of ss.
					 101.60 and
					 101.70, Stats.
(2) The purpose of this code is to establish
					 uniform installation and inspection procedures for manufactured homes in
					 accordance with the requirements of s.
					 101.96,
					 Stats.
Other agencies may have regulations that affect the
						  design, construction or placement of the dwelling and accessory structures or
						  systems serving the dwelling. The regulations may necessitate additional
						  administrative procedures or inspections for compliance.
Note:
The design and construction of
						  manufactured homes is regulated by the federal Department of Housing and Urban
						  Development under Title 24 CFR Part 3280.
Note:
See ch. SPS 305 for licensing
						  requirements for manufactured home manufacturers and manufactured home
						  installers.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 320-325 - Uniform Dwelling Code › Chapter SPS 320 - Administration And Enforcement › Subchapter I - Purpose and Scope › Section SPS 320.03 - Effective date

Current through June 24, 2024
The effective date of ch. SPS 322 is December 1, 1978.
						The effective date of chs.
						SPS
						320, 321, 323, 324 and 325 is June 1,
						1980.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 320-325 - Uniform Dwelling Code › Chapter SPS 320 - Administration And Enforcement › Subchapter I - Purpose and Scope › Section SPS 320.04 - Applications

Current through June 24, 2024
(1) NEW DWELLINGS.
(a) This code applies to all dwellings,
					 dwelling units and foundations for dwelling units, for which the building
					 permit application was made or construction commenced on or after the effective
					 date of this code.
(b) All
					 dwellings covered under par. (a) shall meet the requirements of ch. SPS
					 321.
(c)
1. The installation of heating, air
					 conditioning, plumbing or electrical systems is not required.
2. If any of the systems under subd. 1. are
					 installed, the systems and their installation shall comply with this
					 code.
3. If a heating or air
					 conditioning system is installed, the dwelling shall comply with ch. SPS
					 322.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 320-325 - Uniform Dwelling Code › Chapter SPS 320 - Administration And Enforcement › Subchapter II - Jurisdiction › Section SPS 320.06 - Procedure for municipalities

Current through June 24, 2024
(1) MUNICIPAL
					 JURISDICTION.
(a)
General.
1. Except as provided in ss.
					 101.65(1c)
					 and
					 101.651(1)
					 and (2m), Stats., cities, villages and towns
					 shall exercise jurisdiction over the construction and inspection of new
					 dwellings.
Note:
Section
						101.65(1c),
						Stats., reads as follows:
101.65 Municipal authority.
Except as
						provided by s.
						101.651,
						cities, villages, towns and counties:
(1c) May not make or enforce an ordinance
					 under sub. (1) that is applied to a dwelling and that does not conform to this
					 subchapter and the uniform dwelling code adopted by the department under this
					 subchapter or is contrary to an order of the department under this subchapter.
					 If any provision of a contract between a city, village, town, or county and an
					 owner requires the owner to comply with an ordinance that does not conform to
					 this subchapter or the uniform dwelling code adopted by the department under
					 this subchapter or is contrary to an order of the department under this
					 subchapter, the owner may waive the provision, and the provision, if waived, is
					 void and unenforceable.
Note:
Sections
						101.651(1)
						and (2m), Stats., read as follows.
(1) DEFINITION. In this section,
					 "municipality" means a city, village or town with a population of 2,500 or
					 less.
(2m) ENFORCEMENT OPTIONS. A
					 municipality shall exercise jurisdiction over the construction and inspection
					 of new one- and 2-family dwellings by enacting ordinances under s.
					 101.65(1)
					 (a) or shall exercise the jurisdiction
					 granted under s.
					 101.65(1)
					 (a) jointly under s.
					 101.65(1)
					 (b), unless any of the following conditions
					 are met:
(a) The municipality adopts a
					 resolution requesting under sub. (3) (a) that a county enforce this subchapter
					 or an ordinance enacted under s.
					 101.65(1)
					 (a) throughout the municipality and that a
					 county provide inspection services in the municipality to administer and
					 enforce this subchapter or an ordinance enacted under s.
					 101.65(1)
					 (a).
(c) Under sub. (3) (b), the department
					 enforces this subchapter throughout the municipality and provides inspection
					 services in the municipality to administer and enforce this
					 subchapter.