reglab/statecodes huggingface dataset:
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-5706 - Special operations

Current through Register Vol. 24-14, July 15, 2024
5706.5.4.5 Commercial, industrial, governmental or
				manufacturing.
Dispensing of Class II and III motor vehicle fuel from
				tank vehicles into the fuel tanks of motor vehicles located at commercial,
				industrial, governmental or manufacturing establishments is allowed where
				permitted, provided such dispensing operations are conducted in accordance with
				the following: (Those sections not noted here remain unchanged.)
12.Fuel delivery vehicles shall be equipped with spill clean-up
				supplies in accordance with the department of ecology's Source Control Best
				Management Practices. Such supplies shall be readily available for deployment
				by the operator at all times and include nonwater absorbents capable of
				absorbing 15 gallons (56.76 L) of diesel fuel, storm drain plug or cover kit, a
				nonwater absorbent containment boom of a minimum 10 foot long (3038 mm) length
				with a 12-gallon (45.41 L) absorbent capacity, a nonmetallic shovel, and two
				5-gallon (19 L) buckets with lids.
Statutory Authority: RCW 19.27A.031,
				  19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-5706, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-6108 - Fire protection

Current through Register Vol. 24-14, July 15, 2024
6108.1 General.
Storage, handling and
				transportation of liquefied petroleum gas (LP-gas) and the installation of
				LP-gas equipment pertinent to systems for such uses shall comply with this
				chapter and NFPA 58. Properties of LP-gas shall be determined in accordance
				with Appendix B of NFPA 58.
EXCEPTION:
The use and storage of listed propane fired barbeque
						grills on R-2 decks and balconies with an approved container not exceeding a
						water capacity of 20 pounds (9 kg) that maintain a minimum clearance of 18
						inches on all sides, unless listed for lesser clearances.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-6108, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-8000 - Referenced standards

Current through Register Vol. 24-14, July 15, 2024
NFPA 13-19: Standard for the Installation of Sprinkler Systems
				(except 9.3. 6.3(5)) ........................ 903.3.1.1, 903.3. 2, 903.3.8.2,
				903.3.8.5, 904.13, 905.3.4, 907.6.4, 914.3.2, 1019.3, 1103.4.8, 3201.1, 3204.2,
				3205.5, Table 3206.2, 3206.4.1, 3206.10, 3207.2, 3207.2.1, 3208.2.2,
				3208.2.2.1, 3208.4, 3210.1, 3401.1, 5104.1, 5104.1.1, 5106.5.7, 5704.3.3.9,
				Table 5704.3.6.3(7), 5704.3.7.5.1, 5704.3.8.4
NFPA 33-18 Membrane Enclosures ............ 2404.3.5
NFPA 96-21 Standard for Ventilation Control and Fire Protection
				of Commercial Cooking Operations ................ 606.2, 606. 3, 904.13
NFPA 130-20 Standard for Fixed Guideway Transit and Passenger
				Rail Systems ........................... 4901.1
NFPA 855-23 Standard for the Installation of Stationary Energy
				Storage Systems ........................... 1201.1
UL 142A-2018: Special Purpose Above ground Tanks for Specific
				Flammable or Combustible Liquids ................... 605.4
UL 2272-2016: Electrical Systems for Personal E-Mobility
				Devices ............................ 323.2
UL 2849-2020: Electrical Systems for eBikes ..........
				323.2
Reviser's note:
The bracketed material preceding
				  the section above was supplied by the code reviser's office.
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-8000, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-54A - State Building Code adoption and amendment of the 2021 edition of the International Fire Code › Section 51-54A-8100 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority: RCW 19.27A.031,
				  
											19.27.074 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-063, §
				  51-54A-8100, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-002 - Purpose

Current through Register Vol. 24-14, July 15, 2024
The purpose of these rules is to implement the provisions of
				chapter 19.27 RCW, which provides that the state building code council shall
				maintain the state building code in a status which is consistent with the
				purpose as set forth in
				RCW
				  19.27.020. In maintaining the codes the
				council shall regularly review updated versions of the codes adopted under the
				act, and other pertinent information, and shall amend the codes as deemed
				appropriate by the council.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-003 - International Wildland-Urban Interface Code

Current through Register Vol. 24-14, July 15, 2024
The 2021 edition of the
International Urban-Interface
				Code
, published by the International Code Council, is hereby adopted
				by reference with the following additions, deletions, and
				exceptions.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-008 - Implementation

Current through Register Vol. 24-14, July 15, 2024
The International Wildland-Urban Interface Code adopted by this
				chapter shall become effective in all counties and cities of this state on
				March 15, 2024.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-100 - Scope and administration

Current through Register Vol. 24-14, July 15, 2024
101 Scope and general requirements.
101.2 Scope.
The provisions of this code shall
				apply to the construction, alteration, movement, repair, maintenance and use of
				any building, structure, or premises within the wildland-urban interface areas
				in this jurisdiction.
Buildings or conditions in existence at the time of the
				adoption of this code are allowed to have their use or occupancy continued, if
				such condition, use or occupancy was legal at the time of the adoption of this
				code, provided that such continued use does not constitute an egregious danger
				to life or property.
Buildings or structures moved into or within the jurisdiction
				shall comply with the provisions of this code for new buildings or
				structures.
101.4 Retroactivity.
The provisions of the code
				shall apply to conditions arising after the adoption thereof, conditions not
				legally in existence at the adoption of this code and conditions that, as
				determined by the code official, constitute an egregious hazard to life or
				property.
EXCEPTION:
Provisions of this code that specifically apply to
							 existing conditions are retroactive.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-0200 - Chapter 2-Definitions

Current through Register Vol. 24-14, July 15, 2024
202 Definitions.
ACCESSORY STRUCTURE.
A building or structure used
				to shelter or support any material, equipment, chattel or occupancy other than
				a habitable building, or a habitable building or structure that is accessory to
				and incidental to that of the dwelling(s) and that is located on the same
				lot.
BUILDING OFFICIAL.
Not adopted.
EGREGIOUS DANGER.
A danger that if left
				unmitigated, places the occupants or property in immediate danger.
FUEL, HEAVY.
Vegetation consisting of round wood 3
				to 8 inches (76 to 203 mm) in diameter. See Fuel Models G, I, J, K, and U
				described in Chapter 9.
FUEL, LIGHT.
Vegetation consisting of herbaceous
				plants and round wood less than 1/4-inch (6.4 mm) in diameter. See Fuel Models
				A, C, E, L, N, P, R, and S described in Chapter 9.
FUEL, MEDIUM.
Vegetation consisting of round wood
				1/4 to 3 inches (6.4 mm to 76 mm) in diameter. See Fuel Models B, D, F, H, O,
				Q, and T described in Chapter 9.
HIGH-DENSITY VEGETATED AREA.
An area defined by a
				square determined in accordance with Section 302.3.1, with 75 percent or more
				vegetation.
WASHINGTON WILDLAND-URBAN INTERFACE MAP (WA-WUI).
The Washington department of natural resources map designating urban areas,
				wildland-urban interface, wild-land-urban intermix, wildlands, and long-term
				nonbuildable areas, designated as the Washington wildland-urban interface as
				mapped for 2019 by the Washington state department of natural
				resources-wildfire and forest health divisions under consultation from the USFS
				Rocky Mountain Research Station.
WILDLAND-URBAN INTERFACE/INTERMIX AREA.
That
				geographical area where structures and other human development meets or
				intermingles with wildland or vegetative fuels.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-0600 - Fire protection requirements

Current through Register Vol. 24-14, July 15, 2024
602 Automatic sprinkler systems.
602.1 General.
An
approved
automatic sprinkler system shall be installed when required by the authority
				having jurisdiction.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-0700 - Chapter 7-Vegetation management plan

Current through Register Vol. 24-14, July 15, 2024
User note:
About this chapter: The purpose
				of this chapter is to provide criteria for submitting vegetation management
				plans, specifying their content and establishing a criterion for considering
				vegetation management as being a fuel modification.
701 General.
701.1 Scope.
Vegetation management plans shall be
				submitted to the
code official where required
for review and
				approval as part of the plans required for a permit.
701.2 Plan content.
Vegetation management plans
				shall describe all actions that will be taken to prevent a fire from being
				carried toward or away from the building. A vegetation management plan shall
				include the following information:
1.
			 A copy of the site plan.
2. Methods
			 and timetables for controlling, changing or modifying areas on the property.
			 Elements of the plan shall include removal of slash, snags, vegetation that may
			 grow into overhead electrical lines, other ground fuels, ladder fuels and dead
			 trees, and the thinning of live trees.
3. A plan for maintaining the proposed
			 fuel-reduction measures.
701.3 Fuel modification.
To be considered a
fuel modification
for purposes of this code, continuous
				maintenance of the clearance is required.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-0800 - Chapter 8-Fire hazard severity form

Current through Register Vol. 24-14, July 15, 2024
User note:
About this chapter: The purpose
				of this chapter is to provide an alternative methodology to using Table 502.1
				for analyzing the fire hazard severity of building sites using a preassigned
				value/scoring system for each feature that impacts the hazard level of a
				building site. Included in the evaluation are site access, types and management
				of vegetation, percentage of defensible space on the site, site topography,
				class of roofing and other construction materials used on the building
				(existing or to be constructed on the site), fire protection water supply, and
				whether utilities are installed above or below ground.
801 Fire hazard severity form.
Where adopted,
				Table 801.1 is permitted to be used as an alternative to Table 502.1 for
				analyzing the fire hazard severity of building sites.
TABLE 801.1
FIRE HAZARD SEVERITY FORM
(No change to the table)
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-55 - State Building Code adoption and amendment of the 2021 edition of the Wildland-Urban Interface Code › Section 51-55-1000 - Chapter 10-Referenced standards

Current through Register Vol. 24-14, July 15, 2024
ASTM E2632-2020: Standard Test Method for Evaluating the
				Under-Deck Fire Test Response of Deck Materials 501.6
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-001 - Authority

Current through Register Vol. 24-14, July 15, 2024
These rules are adopted under the authority of
				chapter
				19.27
				RCW.
Statutory Authority:
				  RCW
				  19.27.031,
				  19.27.074. 02-01-114, §
				  51-56-001, filed 12/18/01, effective
				  7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-002 - Purpose

Current through Register Vol. 24-14, July 15, 2024
The purpose of these rules is to implement the provisions of
				chapter
				19.27 RCW, which provides
				that the state building code council shall maintain the State Building Code in
				a status which is consistent with the purpose as set forth in
				RCW
				  19.27.020. In maintaining the codes, the
				council shall regularly review updated versions of the codes adopted under the
				act, and other pertinent information, and shall amend the codes as deemed
				appropriate by the council.
Statutory Authority:
				  RCW
				  19.27.031,
				  19.27.074. 02-01-114, §
				  51-56-002, filed 12/18/01, effective
				  7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-003 - Uniform Plumbing Code

Current through Register Vol. 24-14, July 15, 2024
The 2021 edition of the Uniform Plumbing Code, including
				Appendices A, B, I, and M, published by the International Association of
				Plumbing and Mechanical Officials, is hereby adopted by reference with the
				following additions, deletions and exceptions: Provided that chapters 12 and 14
				of this code are not adopted. Provided further, that those requirements of the
				Uniform Plumbing Code relating to venting and combustion air of fuel fired
				appliances as found in chapter 5 and those portions of the code addressing
				building sewers are not adopted.
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-003, filed 2/1/13, effective 7/1/13; 10-03-101, § 51-56-003, filed
				  1/20/10, effective 7/1/10. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020 and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-094, §
				  51-56-003, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031 and
				  19.27.074. 04-01-110, §
				  51-56-003, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-56-003, filed
				  12/18/01, effective 7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-004 - Conflicts between Appendix I and the manufacturer's installation instructions

Current through Register Vol. 24-14, July 15, 2024
Where a conflict exists between the provisions of Appendix I
				and the manufacturer's installation instructions, the conditions of the listing
				and the manufacturer's installation instructions shall apply.
Statutory Authority:
				  RCW
				  19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-004, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-007 - Exceptions

Current through Register Vol. 24-14, July 15, 2024
The exceptions and amendments to the model codes contained in
				the provisions of
				chapter
				19.27 RCW shall apply in
				cases of conflict with any of the provisions of these rules.
Codes referenced which are not adopted through
				RCW
				  19.27.031 or
				chapter
				19.27A RCW shall not
				apply unless specifically adopted by the authority having
				jurisdiction.
Statutory Authority:
				  RCW
				  19.27.031 and
				  19.27.074. 04-01-110, §
				  51-56-007, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-56-007, filed
				  12/18/01, effective 7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-008 - Implementation

Current through Register Vol. 24-14, July 15, 2024
The Uniform Plumbing Code adopted by chapter 51-56 WAC shall
				become effective in all counties and cities of this state on March 15,
				2024.
Statutory Authority:
				  RCW
				    19.27.074 and
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-008, filed 2/1/13, effective 7/1/13; 10-03-101, § 51-56-008, filed
				  1/20/10, effective 7/1/10. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020 and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-094, §
				  51-56-008, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031 and
				  19.27.074. 04-01-110, §
				  51-56-008, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-56-008, filed
				  12/18/01, effective 7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-0100 - Chapter 1-Administration

Current through Register Vol. 24-14, July 15, 2024
102.1 Conflict Between Codes.
Delete
				paragraph.
103.3.1 Certification.
State rules and
				regulations concerning certification shall apply.
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-0100, filed 2/1/13, effective 7/1/13. Statutory Authority:
				  RCW
				    19.27.031 and
				  19.27.074. 04-01-110, §
				  51-56-0100, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-56-0100,
				  filed 12/18/01, effective 7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-0300 - Chapter 3-General regulations

Current through Register Vol. 24-14, July 15, 2024
301.2.2 Standards.
Standards listed or referred to
				in this chapter or other chapters cover materials which will conform to the
				requirements of this code, when used in accordance with the limitations imposed
				in this or other chapters thereof and their listing. Where a standard covers
				materials of various grades, weights, quality, or configurations, the portion
				of the listed standard that is applicable shall be used. Design and materials
				for special conditions or materials not provided for herein shall be permitted
				to be used by special permission of the authority having jurisdiction after the
				authority having jurisdiction has been satisfied as to their adequacy in
				accordance with Section 301.2.
310.4 Use of Vent and Waste Pipes.
Except as
				hereinafter provided in Sections 908.0 through 911.0 and Appendix C, no vent
				pipe shall be used as a soil or waste pipe, nor shall any soil or waste pipe be
				used as a vent.
312.6 Freezing Protection.
No water, soil, or
				waste pipe shall be installed or permitted outside of a building, in attics or
				crawl spaces, or in an exterior wall unless, where necessary, adequate
				provision is made to protect such pipe from freezing. All hot and cold water
				pipes installed outside the conditioned space shall be insulated to meet the
				minimum requirements of the Washington State Energy Code.
312.7 Fire-Resistant Construction.
All pipe
				penetrating floor/ceiling assemblies and fire-resistance rated walls or
				partitions shall be protected in accordance with the requirements of the
				building code.
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-0300, filed 2/1/13, effective 7/1/13; 10-03-101, § 51-56-0300, filed
				  1/20/10, effective 7/1/10. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020 and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-094, §
				  51-56-0300, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031 and
				  19.27.074. 04-01-110, §
				  51-56-0300, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-56-0300,
				  filed 12/18/01, effective 7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-0400 - Chapter 4-Plumbing fixtures and fixture fittings

Current through Register Vol. 24-14, July 15, 2024
402.5
Setting.
Fixtures shall be set level and in proper alignment with
			 reference to adjacent walls. No water closet or bidet shall be set closer than
			 fifteen (15) inches (381 mm) from its center to any side wall or obstruction
			 nor closer than thirty (30) inches (762 mm) center to center to any similar
			 fixture. The clear space in front of any water closet or bidet shall be not
			 less than twenty-four (24) inches (610 mm). No urinal shall be set closer than
			 twelve (12) inches (305 mm) from its center to any side wall or partition nor
			 closer than twenty-four (24) inches (610 mm) center to center.
EXCEPTIONS:
1. The clear space in front of a water closet, lavatory
						  or bidet in dwelling units and sleeping units shall be not less than 21 inches
						  (533 mm).
2. The installation of paper dispensers or
						  accessibility grab bars shall not be considered obstructions.
405.4
Application.
No individual, public or private corporation, firm,
			 political subdivision, government agency, or other legal entity, may, for
			 purposes of use in the state of Washington, distribute, sell, offer for sale,
			 import, install, or approve for installation any plumbing fixtures or fittings
			 unless the fixtures or fittings meet the standards as provided for in this
			 chapter.
407.1
Application.
Lavatories shall comply with ASME A112.19.1/CSA
			 B45.2, ASME A112.19.2/CSA B45.1, ASME A112.19.3/CSA B45.4, ASME A112.19.12, CSA
			 B45.5/IAPMO Z124, CSA B45.8/IAPMO Z403, CSA B45.11/IAPMO Z401 or CSA
			 B45.12/IAPMO Z402. Group wash fixtures shall comply with the requirements of
			 Section 401.2. Every 20 inches (508 mm) of rim space of a group wash fixture
			 shall be considered as one lavatory for determining the number of lavatories
			 required in accordance with the International Building Code Table 2902.1.
Lavatory assemblies with automatic soap dispensers, faucets, or
				hand dryers shall comply with IAPMO IGC 127.
407.2
Water Consumption.
The
			 maximum water flow rate of faucets shall comply with Section 407.2.1 through
			 407.2.2.
407.2.1
Maximum Flow
			 Rate.
The maximum flow rate for public lavatory faucets shall not exceed
			 0.5 gpm at 60 psi (1.9 L/m at 414 kPa).
407.2.1.1
Residential Lavatory
			 Faucets.
The maximum flow rate of residential lavatory faucets shall not
			 exceed 1.2 gallons (4.54 L) per minute at 60 psi. The minimum flow rate of
			 residential lavatory faucets shall not be less than 0.8 gallons (3.03 L) per
			 minute at 20 psi.
407.2.1.2
Lavatory Faucets in Common and Public Use Areas.
The maximum flow
			 rate of lavatory faucets, installed in common and public use areas (outside of
			 dwellings or sleeping units) in residential buildings, shall not exceed 0.5
			 gallons (1.89 L) per minute at 60 psi.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-0500 - Chapter 5-Water heaters

Current through Register Vol. 24-14, July 15, 2024
501.1
Applicability.
The regulations of this chapter shall govern the
			 construction, location, and installation of fuel burning and other types of
			 water heaters heating potable water. The minimum capacity for water heaters
			 shall be in accordance with the first hour rating listed in Table 501.1(2). See
			 the Mechanical Code for combustion air and installation of all vents and their
			 connectors. No water heater shall be hereinafter installed that does not comply
			 with the manufacturer's installation instructions and the type and model of
			 each size thereof approved by the authority having jurisdiction. A list of
			 accepted water heater appliance standards is referenced in Table 501.1(1).
			 Listed appliances shall be installed in accordance with the manufacturer's
			 installation instructions. Unlisted water heaters shall be permitted in
			 accordance with Section 504.3.2.
TABLE 501.1 (2)1,3
Number of Bathrooms
1 to 1.5
2 to 2.5
3 to 3.5
Number of Bedrooms
1
2
3
2
3
4
5
3
4
5
6
First Hour Rating2,
						  Gallons
38
49
49
49
62
62
74
62
74
74
74
Notes:
1The first hour rating is
						  found on the "Energy Guide" label.
2Nonstorage and solar water
						  heaters shall be sized to meet the appropriate first hour rating as shown in
						  the table, and shall be capable of delivering hot water at the maximum system
						  demand flow, as calculated in Section 610.0 or Appendix A, as
						  applicable.
3For replacement water
						  heaters, see Section 102.4.
501.1.2
Consumer Electric Storage Water Heater Requirements.
Consumer
			 electric storage water heaters must have a modular demand response
			 communications port compliant with the March 2018 version of the
			 ANSI/CTA-2045-A communication interface standard, or equivalent and the March
			 2018 version of the ANSI/CTA-2045-A application layer requirements. The
			 interface standard and application layer requirements required in this
			 subsection are the versions established on March 16, 2018.
EXCEPTIONS:
1. Water heaters manufactured prior to January 1,
						  2021.
2. Electric storage water heaters other than heat pump
						  type water heaters manufactured prior to January 1, 2022.
501.1.3
Mini-tank Electric Water Heaters.
The standby energy consumption
			 of hot water dispensers and mini-tank electric water heaters manufactured on or
			 after January 1, 2010, shall be not greater than 35 watts. Mini-tank electric
			 water heaters shall be tested in accordance with the method specified in the
			 California Code of 39 Regulations, Title 20, section 1604 in effect as of July
			 26, 2009.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-0700 - Chapter 7-Sanitary drainage

Current through Register Vol. 24-14, July 15, 2024
701.2
Drainage
			 Piping.
Materials for drainage piping shall be in accordance with one of
			 the referenced standards in Table 701.1 except that:
1. No galvanized wrought-iron or galvanized
			 steel pipe shall be used underground and shall be kept not less than 6 inches
			 (152 mm) above ground.
2. ABS and
			 PVC DWV piping installations shall be installed in accordance with applicable
			 standards in Table 1701.1. Except for individual single family dwelling units,
			 materials exposed within ducts or plenums shall have a maximum flame-spread
			 index of 25 and a maximum smoke developed index of 50, when tested in
			 accordance with ASTM E-84 and UL 723.
3. No vitrified clay pipe or fittings shall
			 be used above ground or where pressurized by a pump or ejector. They shall be
			 kept not less than 12 inches (305 mm) below ground.
4. Copper tube for drainage and vent piping
			 shall have a weight of not less than that of copper drainage tube type
			 DWV.
5. Stainless steel 304 pipe
			 and fittings shall not be installed underground and shall be kept not less than
			 6 inches (152 mm) above ground.
6.
			 Cast-iron soil pipe and fittings shall be listed and tested in accordance with
			 standards referenced in Table 701.2. Such pipe and fittings shall be marked
			 with country of origin and identification of the original manufacturer in
			 addition to markings required by referenced standards.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-0800 - Chapter 8 - Indirect wastes

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27.190,
				  19.27.020 and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-094, §
				  51-56-0800, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031,
				  19.27.074. 02-01-114, §
				  51-56-0800, filed 12/18/01, effective
				  7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-0900 - Chapter 9-Vents

Current through Register Vol. 24-14, July 15, 2024
911.1 Circuit Vent Permitted.
A maximum of eight
				fixtures connected to a horizontal branch drain shall be permitted to be
				circuit vented. Each fixture drain shall connect horizontally to the horizontal
				branch being circuit vented. The horizontal branch drain shall be classified as
				a vent from the most downstream fixture drain connection to the most upstream
				fixture drain connection to the horizontal branch. Given its grease-producing
				potential, restaurant kitchen equipment shall not be connected to a circuit
				vented system. Each trap arm shall connect horizontal to the horizontal branch
				being circuit vented in accordance with Table 1002.2.
EXCEPTION:
Back-outlet and wall-hung water closets shall be
						  permitted to be circuit vented provided that no floor-outlet fixtures are
						  connected to the same horizontal branch.
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-0900, filed 2/1/13, effective 7/1/13; 10-03-101, § 51-56-0900, filed
				  1/20/10, effective 7/1/10. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020 and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-094, §
				  51-56-0900, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031,
				  19.27.074. 02-01-114, §
				  51-56-0900, filed 12/18/01, effective
				  7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-1000

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-1000, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-1300 - Chapter 13-Health care facilities and medical gas and vacuum systems

Current through Register Vol. 24-14, July 15, 2024
Part II Medical Gas and Vacuum Systems
1303.8 Water Mains for Hospitals.
Hospitals shall
				be provided with not less than two
approved potable water
mains that are installed in such a manner as to prevent the interruption of
				water service.
1305.3 Minimum Station Outlets/Inlets.
Station
				outlets and inlets for medical gas and medical vacuum systems for facilities
				licensed or certified by Washington state department of health (DOH) or
				Washington state department of social and health services (DSHS) shall be
				provided as listed in chapters 246-320 and 246-330 WAC as required by the
				applicable licensing rules as applied by DOH construction review services. All
				other medical gas and medical vacuum systems shall be provided as listed in
				Table 1305.3.
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-1300, filed 2/1/13, effective 7/1/13; 10-03-101, § 51-56-1300, filed
				  1/20/10, effective 7/1/10. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020 and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-094, §
				  51-56-1300, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031 and
				  19.27.074. 04-01-110, §
				  51-56-1300, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-56-1300,
				  filed 12/18/01, effective 7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-1400 - Chapter 14-Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-1400, filed 2/1/13, effective 7/1/13; 10-03-101, § 51-56-1400, filed
				  1/20/10, effective 7/1/10. Statutory Authority:
				  RCW
				    19.27.190,
				  19.27.020 and
				  chapters
				  19.27 and
				  34.05 RCW. 07-01-094, §
				  51-56-1400, filed 12/19/06, effective 7/1/07. Statutory Authority:
				  RCW
				    19.27.031 and
				  19.27.074. 04-01-110, §
				  51-56-1400, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-56-1400,
				  filed 12/18/01, effective 7/1/02.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-1500 - Chapter 15-Alternate water sources for nonpotable applications

Current through Register Vol. 24-14, July 15, 2024
1501.1 Applicability.
The provisions of this
				chapter and the Washington state department of health shall apply to the
				construction, alteration, and repair of alternate water source systems for
				nonpotable applications.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-1600 - Chapter 16- Nonpotable rainwater catchment systems

Current through Register Vol. 24-14, July 15, 2024
1601.1 Applicability.
The provisions of this
				chapter and the Washington state department of health shall apply to the
				construction alteration and repair of nonpotable rainwater catch
				systems.
Statutory
				Authority:
				RCW
				  19.27.074,
				19.27.031 and
				chapters
				19.27 and
				34.05 RCW. WSR 13-04-054, §
				51-56-1600, filed 2/1/13, effective 7/1/13. Statutory Authority:
				RCW
				  19.27.031,
				19.27.035,
				19.27.074, and
				chapters
				19.27 and
				34.05 RCW. WSR 12-07-018, §
				51-56-1600, filed 3/12/12, effective 4/12/12. Statutory Authority:
				RCW
				  19.27.074,
				19.27.031 and
				chapters
				19.27 and
				34.05 RCW. WSR 10-03-101, §
				51-56-1600, filed 1/20/10, effective 7/1/10. Statutory Authority:
				RCW
				  19.27.190,
				19.27.020 and
				chapters
				19.27 and
				34.05 RCW. WSR 07-01-094, §
				51-56-1600, filed 12/19/06, effective 7/1/07. WSR 13-23-007, § 51-56-1600,
				filed 11/7/2013, effective 12/8/2013
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-1700 - Chapter 17-Referenced standards

Current through Register Vol. 24-14, July 15, 2024
Referenced Standards.
TABLE 1701.1
Standards for Materials, Equipment, Joints and
				Connections
Where more than one standard has been listed for the same
				material or method, the relevant portions of all such standards shall
				apply.
Add the following standard to those listed in Table
				1701.1:
Standard Number
Standard Title
Application
WAC
						246-290-490
Washington State Department of Health Cross-connection
						Control Requirements
Backflow Protection
Statutory
				Authority:
				RCW
				  19.27.074,
				19.27.031 and
				chapters
				19.27 and
				34.05 RCW. WSR 13-04-054, §
				51-56-1700, filed 2/1/13, effective 7/1/13. WSR 13-23-007, § 51-56-1700,
				filed 11/7/2013, effective 12/8/2013
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-90700 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-90700, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-90800 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-90800, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-56 - State Building Code adoption and amendment of the 2021 edition of the Uniform Plumbing Code › Section 51-56-92000 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27.074,
				  19.27.031 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-054, §
				  51-56-92000, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 60 - Beef Commission › Chapter 60-12 - Washington Beef Commission Act rules › Section 60-12-005 - Promulgation

Current through Register Vol. 24-14, July 15, 2024
This is a new order relating to
				RCW
				16.67.120.
I, Gary F. Strohmaier, director of agriculture of the state of
				Washington, after public notice and hearing held at Olympia, Washington, on
				April 26, 1977, by virtue of authority vested in me under chapter 34.04 RCW and
				RCW
				16.67.120, do hereby find and declare that
				the assessment of twenty cents per head on Washington cattle be continued
				beyond July 1, 1977.
Order 1527, § 60-12-005, filed
				  5/11/77, effective 7/1/77.
Washington Administrative Code › Title 60 - Beef Commission › Chapter 60-12 - Washington Beef Commission Act rules › Section 60-12-010 - Levy of assessment

Current through Register Vol. 24-14, July 15, 2024
(1)
			 Pursuant to the National Beef Promotion and Research Program, 7 USC S 2901, et
			 seq., RCW
			 16.67.120 and
			 16.67.122, the Washington state
			 beef commission levies an assessment of one dollar and fifty cents per head on
			 all Washington cattle sold in this state or elsewhere, provided that no
			 assessment shall be collected with reference to the following:
(a) Sales by a person who purchased cattle
			 solely for resale when such resale occurs within ten days from such person's
			 purchase of the cattle and when any assessment due in connection with that
			 original purchase has been paid. In order to qualify for this exception, such
			 persons additionally must present the designated collecting person with their
			 certification of nonproducer status form, along with a brand inspection
			 certificate, a bill of sale or other documentation establishing the date of
			 their purchase of the cattle. Such documentation must be presented at the time
			 of sale to the designated collection person.
(b) Sales of cattle where the cattle that
			 have been transported into Washington from another state for the purpose of
			 sale and the sale takes place within thirty days of the cattle entering the
			 state unless the assessment has not been paid in the state of origin.
Washington Administrative Code › Title 60 - Beef Commission › Chapter 60-12 - Washington Beef Commission Act rules › Section 60-12-010 - Levy of assessment

Current through Register Vol. 24-14, July 15, 2024
(1) Pursuant to
			 the National Beef Promotion and Research Program, 7 U.S.C. S 2901, et seq.,
			 RCW
			 16.67.120 and
			 16.67.122, the Washington state
			 beef commission levies an assessment of up to $3.00 ($2.00 of which goes to the
			 state beef checkoff and $1.00 to the federal beef checkoff) per head to be
			 implemented as prescribed in subsection (2) of this section on all Washington
			 cattle sold in this state or elsewhere, provided that no assessment shall be
			 collected with reference to the following:
(a)
			 Sales by a person who purchased cattle solely for resale when such resale
			 occurs within 10 days from such person's purchase of the cattle and when any
			 assessment due in connection with that original purchase has been paid. In
			 order to qualify for this exception, such persons additionally must present the
			 designated collecting person with their certification of nonproducer status
			 form, along with a brand inspection certificate, a bill of sale or other
			 documentation establishing the date of their purchase of the cattle. Such
			 documentation must be presented to the designated collection person at the time
			 of sale.
(b) Sales of cattle where
			 the cattle that have been transported into Washington from another state for
			 the purpose of sale and the sale takes place within 30 days of the cattle
			 entering the state unless the assessment has not been paid in the state of
			 origin.
Washington Administrative Code › Title 60 - Beef Commission › Chapter 60-12 - Washington Beef Commission Act rules › Section 60-12-020 - Collection of assessment

Current through Register Vol. 24-14, July 15, 2024
(1)
			 Collection of the federal beef check-off assessment shall be accomplished as
			 set forth in the Beef Promotion and Research Act of 1985, 7 USC §§
			 2901-11 and the federal Beef Promotion and Research Order,
			 7 C.F.R. §§
									1260.301 -
			 1260.316 (Subpart B), referred to
			 in chapter 16.67 RCW as "the federal order."
(2) Procedures for collecting
			 state-authorized assessments are not covered by the federal order and shall be
			 as set forth in
			 RCW
			 16.67.120(2),
			 16.67.122,
			 16.67.130 and this rule.
(3) All state-authorized assessments levied
			 under chapter 16.67 RCW shall be due and payable on the 15th day of the month
			 following the month in which the assessed transaction occurred.
(4) Pursuant to
			 RCW
			 16.67.130, in the event a person who owes a
			 state-authorized assessment fails to pay the full amount within the time set
			 forth in subsection (3) of this section, the commission is authorized to and
			 shall add an amount of ten percent to the unpaid assessments to defray the cost
			 of collecting the assessment.
(5)
			 Interest at the rate of one percent per month shall accrue on past due
			 assessments pursuant to
			 RCW
			 43.17.240, starting on the date the
			 assessment became past due.
(6) The
			 commission may assign past due assessments to a state-contracted collection
			 agency to pursue collection. Under
			 RCW
			 19.16.500, at least thirty days prior to
			 assigning a past due assessment to a collection agency, the commission shall
			 attempt to advise the person who owes the assessment of the existence of the
			 debt and that the debt may be assigned to a collection agency for collection if
			 the debt is not paid.
(7) The
			 commission may bring a civil action under
			 RCW
			 16.67.130 against any person who owes a past
			 due state-authorized assessment in a state court of competent jurisdiction for
			 the collection thereof, together with ten percent late fee, interest from the
			 date the debt became past due and any other necessary reasonable costs
			 including attorney's fees.
(8) Any
			 civil action for the collection of past due assessments may be combined with an
			 action to collect any past due Washington state department of agriculture brand
			 inspection fees imposed under chapter 16.57 or 16.65 RCW or 16-610 WAC when
			 owed from the same person.
Statutory Authority: RCW 43.17.240,
				  chapters 16.67 and 34.05 RCW. 10-21-057, § 60-12-020, filed 10/15/10,
				  effective 11/15/10.
Washington Administrative Code › Title 60 - Beef Commission › Chapter 60-12 - Washington Beef Commission Act rules › Section 60-12-025 - Refunds

Current through Register Vol. 24-14, July 15, 2024
(1) Chapter 16.67
			 RCW provides that of the assessments levied in
			 RCW
			 16.67.120, a producer or owner of cattle from
			 whom an assessment is collected, except for assessments collected at the first
			 point of sale of green tag calves not subject to the assessment increases
			 provided in
			 RCW
			 16.67.120(2), has the right
			 to request a refund of not more than $1.00 per head beginning July 1, 2024, not
			 more than $1.50 per head beginning January 1, 2025, and not more than $2.00 per
			 head beginning January 1, 2026. Refund requests must be mailed to the
			 commission within 90 calendar days of the assessment and include the following
			 information:
(a) Name and address of the
			 producer or owner;
(b) Name and
			 address of the entity collecting the assessment (brand inspector or livestock
			 market);
(c) Number of head on
			 which a refund is requested;
(d)
			 Total amount of refund requested;
(e) Date of assessment;
(f) Producer's signature; and
(g) Proof of payment of the
			 assessment.