Wyoming Administrative Code › Agency 020 - Environmental Quality, Dept. of › Sub-Agency 0011 - Water Quality › Chapter 17 - STORAGE TANKS › Part K - PROHIBITION OF DELIVERIES AT NON-COMPLIANT FACILITIES › Section 17-44 - Prohibition of Deliveries

Current through July 13, 2024
(a)
Reasons for Restricting Delivery.
Prohibition of delivery of
				  regulated substances to a storage tank system shall be required when the
				  department becomes aware that:
(i) The owner
				  and/or operator has not performed leak detection on the tanks as required in
				  Part D of this chapter for any period exceeding sixty (60) days;
(ii) The most recently required cathodic
				  protection test has not been done within ninety (90) days of the date when due
				  under Section 11(b) of this chapter;
(iii) A cathodic protection test done in
				  accordance with Section 11 has failed and has not been repaired and re-tested
				  within ninety (90) days of the date when the original failing result was
				  obtained;
(iv) The most recently
				  required pressure test of the lines has not been done as required under
				  Sections 14(g)(i)(B) or Section 14(g)(ii) of this chapter (as applicable)
				  within sixty (60) days of the date due;
(v) The most recently required functional
				  test of automatic line leak detectors has not been done as required under
				  Sections 14(g)(i)(B), Section 37(a), or Section 37(b) of this chapter within
				  sixty (60) days of the date due;
(vi) The owner and/or operator has failed to
				  report a suspected release under Section 19 when required by Sections 14(b),
				  15(a)(iv), 16(a) (viii), 16(b), 16(c)(ii), 16(d)(viii), 16(e)(x), 16(f)(iv),
				  16(g)(v), 16(h)(vii), or 19 of this chapter;
(vii) The owner and/or operator has reported
				  a suspected release under Section 19 but has failed to initiate the release
				  investigation required under Section 20 of this chapter;
(viii) The owner and/or operator has reported
				  a confirmed release, but repairs have not been made to the storage tank
				  system;
(ix) The owner and/or
				  operator has failed to pay the storage tank registration fee which is due on
				  January 1 of each year by September 1 of the year when due;
(x) The owner and/or operator has failed to
				  follow any Order issued by the department, unless that Order is under appeal to
				  the Environmental Quality Council;
(xi) Any required monitoring device has been
				  purposely tampered with or turned off (except if it is being worked on); or any
				  record required to be kept under this chapter has been falsified;
(xii) Any regulated tank is discovered
				  without overfill and spill prevention devices in place as required by Section
				  6(c) of this chapter;
(xiii) Any
				  regulated tank is discovered without cathodic protection equipment in place as
				  required by Sections 6(a)(ii) or 6(b)(ii) of this chapter;
(xiv) Any regulated above ground storage tank
				  has not been fully upgraded under Part I of this chapter after October 1,
				  2007;
(xv) The operator's annual
				  inspection has not been performed, as required by Section 13(e) or Section
				  36(f) of this chapter, within ninety (90) days of the date when due;
(xvi) The department becomes aware that there
				  has been no Licensed Class B Operator for a facility for ninety (90) days or
				  more;
(xvii) Repaired tanks and
				  piping have not been tightness tested within thirty (30) days of repair
				  completion; or
(xviii) Cathodic
				  protection impressed current systems have not been inspected at least every
				  sixty (60) days.