reglab/statecodes huggingface dataset:
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40503 - Section C405.2.10-Parking garage lighting control

Current through Register Vol. 24-14, July 15, 2024
C405.2.10
Parking
			 garage lighting control.
Parking garage lighting shall be controlled by
			 an
occupant sensor
complying with Section C405.2.1.1 or a
time-switch control
complying with Section C405.2.2.1.
			 Additional lighting controls shall be provided as follows:
1. Lighting power of each luminaire shall be
			 automatically reduced by not less than 30 percent when there is no activity
			 detected within a lighting zone for 20 minutes. Lighting zones for this
			 requirement shall be not larger than 3,600 square feet (334.5
			 m2).
2.
			 Where lighting for eye adaptation is provided at covered vehi-cle entrances and
			 exits from buildings and parking structures, such lighting shall be separately
			 controlled by a device that automatically reduces lighting power by at least 50
			 percent from sunset to sunrise.
3.
			 The power to luminaires within 20 feet (6096 mm) of perimeter wall openings
			 shall automatically reduce in response to daylight by at least 50 percent.
EXCEPTIONS TO ITEM 3:
1. Daylight transition lighting for covered vehicle
						  entrances and exits from buildings and parking structures; each transition zone
						  shall not exceed a depth of 66 feet inside the structure and a width of 50
						  feet.
2. Where permanent screens or architectural elements
						  obstruct more than 50 percent of the opening.
3. Where the top of any existing adjacent structure or
						  natural object is at least twice as high above the openings as its horizontal
						  distance from the opening.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-405030 - Section C405.3-Lighting for plant growth and maintenance

Current through Register Vol. 24-14, July 15, 2024
C405.3
Lighting
			 for plant growth and maintenance.
All permanently installed luminaires
			 used for plant growth and maintenance shall have a
photosynthetic
			 photon efficacy
measured at the lamp for luminaires with serviceable
			 or removable lamps or at the luminaire for integrated, nonserviceable
			 luminaires of not less than 1.7 µmol/J for greenhouses and not less than
			 1.9 µmol/J for all other indoor growing spaces as defined in accordance
			 with ANSI/ASABE S640.
EXCEPTIONS:
Buildings with no more than 10 kW of aggregate
						  horticultural lighting load.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40504 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40504, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40505 - Section C405.4-Interior lighting power requirements

Current through Register Vol. 24-14, July 15, 2024
C405.4 Interior lighting power requirements .
A
				building complies with this section if its total connected interior lighting
				power calculated under Section C405.4.1 is no greater than the interior
				lighting power allowance calculated under Section C405.4.2.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40505, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-405052 - Section C405.4.2-Interior lighting power requirements

Current through Register Vol. 24-14, July 15, 2024
C405.4.2
Interior
			 lighting power allowance.
The total interior lighting power allowance
			 (watts) for an entire building shall be determined according to Table
			 C405.4.2(1) using the Building Area Method, or Table C405.4.2(2) using the
			 Space-by-Space Method. The interior lighting power allowance for projects that
			 involve only portions of a building shall be determined according to Table
			 C405.4.2(2) using the Space-by-Space Method. Buildings with unfinished spaces
			 shall use the Space-by-Space Method.
C405.4.2.1
Building area method.
For the Building Area Method, the interior lighting power allowance is
			 calculated as follows:
1. For each building
			 area type inside the building, determine the applicable building area type and
			 the allowed lighting power density for that type from Table C405.4.2(1). For
			 building area types not listed, select the building area type that most closely
			 represents the use of that area. For the purposes of this method, an "area"
			 shall be defined as all contiguous spaces that accommodate or are associated
			 with a single building area type.
2. Determine the floor area for each building
			 area type listed in Table C405.4.2(1) and multiply this area by the applicable
			 value from Table C405.4.2(1) to determine the lighting power (watts) for each
			 building area type.
3. The total
			 interior lighting power allowance (watts) for the entire building is the sum of
			 the lighting power from each building area type.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-405053 - Table C405.4.2(1)-Interior lighting power allowances-Building area method

Current through Register Vol. 24-14, July 15, 2024
Table C405.4.2(1)
Interior Lighting Power Allowances-Building Area
				Method
Building Area Type
LPD (w/
						  ft2)
Automotive facility
0.64
Convention center
0.64
Court house
0.79
Dining: Bar lounge/leisure
0.79
Dining: Cafeteria/fast food
0.72
Dining: Family
0.71
Dormitory
0.46
Exercise center
0.67
Fire station
0.54
Gymnasium
0.75
Health care clinic
0.70
Hospital
0.84
Hotel/motel
0.56
Library
0.83
Manufacturing facility
0.82
Motion picture theater
0.44
Multiple family
0.41
Museum
0.55
Office
0.64
Parking garage
0.14
Penitentiary
0.65
Performing arts theater
0.84
Police station
0.66
Post office
0.65
Religious building
0.67
Retail
0.84
School/university
0.70
Sports arena
0.62
Town hall
0.69
Transportation
0.50
Warehouse
0.40
Workshop
0.91
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-405053, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40506 - Section C405.5-Exterior lighting

Current through Register Vol. 24-14, July 15, 2024
C405.5 Exterior lighting power
				requirements.
The total connected exterior lighting power calculated in
				accordance with Section C405.5.2 shall not be greater than the exterior
				lighting power allowance calculated in accordance with Section
				C405.5.3.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40506, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-405061 - Section C405.5.1-Exterior building grounds lighting

Current through Register Vol. 24-14, July 15, 2024
C405.5.1
Exterior
			 building grounds lighting.
All exterior building grounds luminaires that
			 operate at greater than 25 watts shall have a minimum efficacy of 100 lumens
			 per watt.
EXCEPTIONS:
1. Luminaires controlled by a motion sensor.
2. Luminaires that qualify for one of the exceptions
						  under Section C405.5.2.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-405061, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-405062 - Section C405.5.2-Exterior building lighting power

Current through Register Vol. 24-14, July 15, 2024
C405.5.2
Total
			 connected exterior building lighting power.
The total exterior connected
			 lighting power shall be the total maximum rated wattage of all exterior
			 lighting that is powered through the energy service for the building.
EXCEPTION:
Lighting used for the following applications shall not
						  be included:
1. Lighting approved because of safety
						  considerations;
2. Emergency lighting automatically off during normal
						  business operation;
3. Exit signs;
4. Specialized signal, directional and marker lighting
						  associated with transportation;
5. Advertising signage or directional signage;
6. Integral to equipment or instrumentation and is
						  installed by its manufacturer;
7. Theatrical purposes, including performance, stage,
						  film production and video production;
8. Athletic playing areas;
9. Temporary lighting;
10. Industrial production, material handling,
						  transportation sites and associated storage areas;
11. Theme elements in theme/amusement parks;
12. Lighting integrated within or used to highlight
						  features of art, public monuments and the national flag;
13. Lighting for water features and swimming pools;
						  and
14. Lighting that is controlled from within dwelling
						  units, where the lighting complies with Section R404.1.
C405.5.3
Exterior lighting power
			 allowance.
The exterior lighting power allowance (watts) is calculated
			 as follows:
1. Determine the Lighting Zone
			 (LZ) for the building according to Table C405.5.3(1), unless otherwise
			 specified by the code official.
2.
			 For each exterior area that is to be illuminated by lighting that is powered
			 through the energy service for the building, determine the applicable area type
			 from Table C405.5.3(2). For area types not listed, select the area type that
			 most closely represents the proposed use of the area. Covered parking garage
			 lighting is not considered exterior lighting for the purposes of this
			 calculation.
3. Determine the total
			 area or length of each area type and multiply by the value for the area type in
			 Table C405.5.3(2) to determine the lighting power (watts) allowed for each area
			 type.
4. The total exterior
			 lighting power allowance (watts) is the sum of the base site allowance
			 determined according to Table C405.5.3(2), plus the watts from each area
			 type.
C405.5.3.1
Additional
			 exterior lighting power.
Additional exterior lighting power allowances
			 are available for the specific lighting applications listed in Table
			 C405.5.3(3). These additional power allowances shall be used only for the
			 luminaires serving these applications and shall not be used to increase any
			 other lighting power allowance.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-405063 - Table C405.5.3(1)-Exterior lighting zones

Current through Register Vol. 24-14, July 15, 2024
Table C405.5.3(1)
Exterior Lighting Zones
Lighting Zone
Description
1
Developed areas of national parks, state parks, forest
						land, and rural areas
2
Areas predominantly consisting of residential zoning,
						neighborhood business districts, light industrial with limited nighttime use
						and residential mixed use areas
3
All other areas not classified as lighting zone 1, 2, or 4
4
High-activity commercial districts in major metropolitan
						areas as designated by the local land use planning authority
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-405063, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40509 - Section C405.9-Vertical and horizontal transportation systems

Current through Register Vol. 24-14, July 15, 2024
C405.9
Vertical
			 and horizontal transportation systems and equipment.
Vertical and
			 horizontal transportation systems and equipment shall comply with this section.
C405.9.1
Elevator cabs.
For the
			 luminaires in each elevator cab, not including signals and displays, the sum of
			 the lumens divided by the sum of the watts shall be no less than 35 lumens per
			 watt. Ventilation fans in elevators that do not have their own air conditioning
			 system shall not consume more than 0.33 watts/cfm at the maximum rated speed of
			 the fan. Controls shall be provided that will deenergize ventilation fans and
			 lighting systems when the elevator is stopped, unoccupied and with its doors
			 closed for over 15 minutes.
C405.9.2
Escalators and moving
			 walks.
Escalators and moving walks shall comply with ASME A17.1/CSA B44
			 and shall have automatic controls that reduce speed as permitted speed in
			 accordance with ASME A17.1/CSA B44 and applicable local code when not conveying
			 passengers.
EXCEPTION:
A variable voltage drive system that reduces operating
						  voltage in response to light loading conditions is allowed to be provided in
						  lieu of the variable speed function.
C405.9.2.1
Energy recovery.
Escalators shall be designed to recover
			 electrical energy when resisting overspeed in the down direction.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40510 - Section C405.10-Controlled receptacles

Current through Register Vol. 24-14, July 15, 2024
C405.10
Automatic
			 receptacle control.
2
The following shall have automatic receptacle control complying
				with Section C405.10.1:
1. At least 50
			 percent of all 125V, 15- and 20-amp receptacles installed in enclosed offices,
			 conference rooms, rooms used primarily for copy or print functions, breakrooms,
			 classrooms and individual workstations, including those installed in modular
			 partitions and module office workstation systems.
2. At least 50 percent of branch circuit
			 feeders installed for modular furniture not shown on the construction
			 documents.
C405.10.1
Automatic receptacle control function.
Automatic receptacle
			 controls shall comply with the following:
1.
			 Either split controlled receptacles shall be provided with the top receptacle
			 controlled, or a controlled receptacle shall be located within 12 inches (304.8
			 mm) of each uncontrolled receptacle.
2. One of the following methods shall be used
			 to provide control:
2.1. A scheduled basis
			 using a time-of-day operated control device that turns receptacle power off at
			 specific programmed times and can be programmed separately for each day of the
			 week. The control device shall be configured to provide an independent schedule
			 for each portion of the building of not more than 5,000 square feet (464.5
			 m2) override an area for not more than 2 hours. Any
			 individual override switch shall control the receptacles of not more than 5,000
			 feet (1524 m).
2.2. An occupant
			 sensor control that shall turn off receptacles within 20 minutes of all
			 occupants leaving a space.
2.3. An
			 automated signal from another control or alarm system that shall turn off
			 receptacles within 20 minutes after determining that the local area is
			 unoccupied.
3. All
			 controlled receptacles shall be permanently marked in accordance with NFPA 70
			 and be uniformly distributed throughout the space.
4. Plug-in devices shall not comply.
EXCEPTION:
Automatic receptacle controls are not required for the
						  following:
1. Receptacles specifically designated for equipment
						  requiring continuous operation (24 hours per day, 365 days per year).
2. Spaces where an automatic control would endanger
						  the safety or security of the room or building occupants.
3. Within a single modular office workstation,
						  noncontrolled receptacles are permitted to be located more than 12 inches
						  (304.8 mm), but not more than 72 inches (1828 mm) from the controlled
						  receptacles serving that workstation.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40511 - Section C405.11-Voltage drop

Current through Register Vol. 24-14, July 15, 2024
C405.11
Voltage
			 drop.
The total voltage drop across the combination of customer-owned
			 service conductors, feeder conductors and branch circuit conductors shall not
			 exceed five percent.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40511, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40512 - Section C405.12- Alternating current-output uninterruptible power supplies (AC-output UPS)

Current through Register Vol. 24-14, July 15, 2024
AC-output UPS
systems serving a
computer room
shall meet or exceed the calculation and testing
				requirements identified in ENERGY STAR Program Requirements for Uninterruptible
				Power Supplies (UPSs) - Eligibility Criteria Version 2.0.
EXCEPTION:
AC-output UPC that utilizes standardized NEMA-1-15P or
						  NEMA 5-15P input plug, as specified in ANSI/NEMA WD 6.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40512, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40513 - Section C405.13-Electrical commissioning

Current through Register Vol. 24-14, July 15, 2024
C405.13
Commissioning.
Controlled receptacles and lighting systems shall
			 be commissioned in accordance with Section C408.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40513, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40621 - Section C406.2.1-Dwelling unit HVAC measures

Current through Register Vol. 24-14, July 15, 2024
C406.2.1
Dwelling
			 unit HVAC controls.
HVAC systems serving
dwelling units
or
sleeping units
shall be controlled with a programmable
thermostat
that is configured to automatically activate a
			 setback condition of at least 5°F (3°C) for both heating and cooling.
			 The programmable
thermostat
shall be configured to provide
			 setback during occupied sleep periods. The unoccupied setback mode shall be
			 configured to operate in conjunction with one of the following:
1. A manual main control device by each
dwelling unit
main entrance that initiates setback for all
			 HVAC units in the
dwelling unit
and is clearly identified as
			 "Heating/Cooling Master Setback."
2. Occupancy sensors in each room of the
dwelling unit
combined with a door switch to initiate setback
			 for all HVAC units in the dwelling within 20 minutes of all spaces being vacant
			 immediately following a door switch operation. Where separate room HVAC units
			 are used, an individual occupancy sensor on each unit that is configured to
			 provide setback shall meet this requirement.
3. An advanced learning thermostat that
			 senses occupant presence and automatically creates a schedule for occupancy and
			 provides a dynamic setback schedule based on when the spaces are generally
			 unoccupied.
4. An automated control
			 and sensing system that uses geographic sensing connected to the
dwelling unit
occupants' cell phones and initiates the setback
			 condition when all occupants are away from the building.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40623 - Section C406.2.3-Lighting measures

Current through Register Vol. 24-14, July 15, 2024
C406.2.3
Reduced
			 lighting power.
Interior lighting within the whole project shall achieve
			 credits by complying with Section C406.2.3.1 or C406.2.3.2. In Group R-1 and
			 Group R-2 occupancies, dwelling and sleeping units shall comply with Section
			 C406.2.3.3 and all other areas shall comply with section C406.2.3.1 or
			 C406.2.3.2. Credits apply to the whole Group R-1 or Group R-2 area.
C406.2.3.1
Reduced lighting power
			 option 1.
The total connected interior lighting power calculated in
			 accordance with Section C405.4.1 shall be 90 percent or less of the lighting
			 power values specified in Table C405.4.2(1) times the floor area for the
			 building types, or 90 percent or less of the total interior lighting power
			 allowance calculated in accordance with Section C405.4.2.
C406.2.3.2
Reduced lighting power
			 option 2.
The total connected interior lighting power calculated in
			 accordance with Section C405.4.1 shall be 80 percent or less of the lighting
			 power values specified in Table C405.4.2(1) times the floor area of the
			 building types, or 80 percent or less of the total interior lighting power
			 allowance calculated in accordance with Section C405.4.2.
C406.2.3.3
Lamp efficacy.
No
			 less than 95 percent of the permanently installed light fixtures in dwelling
			 units and sleeping units shall be provided by lamps with a minimum efficacy of
			 90 lumens per watt.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40624 - Section C406.2.5-Renewable energy measures

Current through Register Vol. 24-14, July 15, 2024
C406.2.5
On-site
			 and off-site renewable energy.
Projects installing on-site or off-site
			 renewable energy systems with a capacity of at least 0.1 watts per gross square
			 foot (1.08 W/m2) of building area in addition to the
			 renewable energy capacity required elsewhere in this code shall achieve energy
			 credits for this measure. Renewable energy systems achieving energy credits
			 shall not be used to satisfy other requirements of this code. Off-site
			 renewable energy systems shall comply with Sections C411.2.2 and C411.2.3.
			 Credits shall be prorated from the table value in accordance with Equation
			 4-17.
Click
				here to view image
Click
				here to view image
Informative Note
:
On-site renewable energy may include thermal service
						water heating or pool water heating, in which case ratings in Btu/h can be
						converted to W where W = Btu/h / 3.413.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40626 - Section C406.2-Envelope measures

Current through Register Vol. 24-14, July 15, 2024
C406.2.12
Enhanced envelope performance.
The Proposed Total UA of the
			 thermal envelope of the project shall be 15 percent lower than the Allowable
			 Total UA determined in accordance with Section C402.1.5 and Equation
			 4-2.
C406.2.13
Reduced air
			 leakage.
Energy credits shall be achieved where measured air leakage of
			 the total
conditioned floor area
of the whole building, fully
			 isolated building addition or tenant space is determined in accordance with
			 Section C402.5.1.2 and complies with the maximum leakage in either Section
			 C406.2.13.1 or C406.2.13.2.
C406.2.13.1
Base reduced air leakage.
Measured air leakage shall not exceed 68
			 percent of the maximum leakage allowed by Section C402.5.1.2.
C406.2.13.2
Enhanced reduced air
			 leakage.
Measured air leakage shall not exceed 33 percent of the maximum
			 leakage allowed by Section C402.5.1.2.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40627 - Section C406.2-Other measures

Current through Register Vol. 24-14, July 15, 2024
C406.2.14
Enhanced commercial kitchen equipment.
For buildings or areas
			 designated as Group A-2, or facilities whose primary business type involves the
			 use of a commercial kitchen with at least one gas or electric fryer, all
			 fryers, dishwashers, steam cookers and ovens shall comply with all of the
			 following:
1. Achieve the ENERGY STAR label
			 in accordance with the specifications current as of January 1, 2022.
2. Be installed prior to the issuance of the
			 certificate of occupancy.
3. Have
			 the ENERGY STAR qualified model number listed on the construction documents
			 submitted for permitting.
Energy efficiency credits for efficient commercial kitchen
				equipment shall be determined based on Equation 4-19, rounded to the nearest
				whole number.
Click
				here to view image
Click
				here to view image
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40700 - Section C407 - Total building performance

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40700, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40701 - Section C407.1-Scope

Current through Register Vol. 24-14, July 15, 2024
C407.1 Scope.
This section establishes criteria
				for compliance using total building performance. All systems and loads shall be
				included in determining the total building performance including, but not
				limited to: Heating systems, cooling systems, service water heating, fan
				systems, lighting power, receptacle loads and process loads.
EXCEPTION
Energy used to recharge or refuel vehicles that are used
						for on-road and off-site transportation purposes
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40701, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-407031 - Tables for Section C407.3

Current through Register Vol. 24-14, July 15, 2024
Table C407.3(1)
Reserved
Table C407.3(2)
Building Performance Factors (BPF) to be used for
				Compliance with Section C407.3
Building Area Type
Building Performance
						  Factor
Multifamily
0.51
Health care/hospital
0.70
Hotel/motel
0.51
Office
0.44
Restaurant
0.33
Retail
0.41
School
0.35
Warehouse
0.18
All others
0.43
Table C407.3(3)
Site Energy Performance Targets to be used for Compliance
				with Section C407.3
Building Area Type
Site Energy Performance
						  Targets
Multifamily
0.59
Health care/hospital
0.72
Hotel/motel
0.62
Office
0.58
Restaurant
0.59
Retail
0.46
School
0.52
Warehouse
0.29
All others
0.55
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40704 - Section C407.4-Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40704, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40705 - Section C407.5-Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40705, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-407051 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-407051, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-407052 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-407052, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-407053 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Reviser's note:
The brackets and enclosed
				  material in the text of the above section occurred in the copy filed by the
				  agency and appear in the Register pursuant to the requirements of RCW
				    34.08.040.
Reviser's note:
The brackets and enclosed
				  material in the text of the above section occurred in the copy filed by the
				  agency and appear in the Register pursuant to the requirements of
				  RCW
				    34.08.040.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-407054 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-407054, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-407055 - Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-407055, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40706 - Section C407.6- Reserved

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40706, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40800 - Section C408 - System commissioning

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40800, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40801 - Section C408.1-General

Current through Register Vol. 24-14, July 15, 2024
C408.1
General.
A building commissioning process led by a
certified commissioning professional
and functional testing
			 requirements shall be completed for mechanical systems in Section C403; service
			 water heating systems in Section C404; controlled receptacle and lighting
			 control systems in Section C405; equipment, appliances and systems installed to
			 comply with Sections C406 or C407; energy metering in Section C409; and
			 refrigeration systems in Section C410.
EXCEPTION:
Buildings, or portions thereof, which are exempt from
						  Sections C408.2 through C408.7 may be excluded from the commissioning
						  process.
1. Mechanical systems that are not required to comply
						  with Section C403.3.5 are exempt from the commissioning process where the
						  installed total mechanical equipment capacity is less than 180,000 Btu/h (15
						  tons) cooling capacity and less than 240,000 Btu/h (20 tons) heating capacity
						  and energy recovery ventilation (ERV) equipment is less than 300 cfm
						  capacity.
2. Service water heating systems are exempt from the
						  commissioning process in buildings where the largest service water heating
						  system capacity is less than 200,000 Btu/h and where there are any of the
						  following:
2.1. No pools or permanent spas.
2.2. No solar thermal water heating.
2.3. No recirculation pumps.
2.4. No heat pump water heaters, except fully-packaged
						  for individual residential dwelling unit use.
3. Lighting control systems are exempt from the
						  commissioning process in buildings where both the total installed lighting load
						  is less than 10 kW and the lighting load controlled by occupancy sensors or
						  automatic daylighting controls is less than 5 kW.
4. Refrigeration systems are exempt from the
						  commissioning process in buildings if they are limited to self-contained
						  units.
C408.1.1
Commissioning in construction documents.
Construction documents shall
			 clearly indicate provisions for commissioning process. The construction
			 documents shall minimally include the following:
1. A narrative description of the activities
			 that will be accomplished during the commissioning process. At a minimum, the
			 commissioning process is required to include:
1.1. Development and execution of the
			 commissioning plan, including all subsections of Section C408.1.2;
1.2. The
certified commissioning
			 professional's
review of the building documentation and close out
			 submittals in accordance with Section C103.6; and
1.3. The commissioning report in accordance
			 with Section C408.1.3.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40803 - Section C408.3- Service water heating systems commissioning

Current through Register Vol. 24-14, July 15, 2024
C408.3 Service water heating systems
				commissioning.
Service water heating equipment and controls subject to
				Section C404 shall be included in the commissioning process required by Section
				C408.1. The commissioning process shall minimally include equipment and
				components installed to meet all energy code requirements for devices to
				"start," "automatically turn off," "automatically adjust," "limit operation,"
				and "limit the temperature" and "be configured to."
C408.3.1 System testing.
Functional performance
				testing shall demonstrate that heaters, piping, distribution systems, and
				system-to-system interfacing relationships are installed and operate in
				accordance with approved construction documents. Testing shall include the
sequence of operation
, and be conducted under at least 50
				percent water heating load, part-load and the following conditions:
1. Normal operation;
2. Redundant or automatic back-up
			 mode;
3. Performance of alarms;
			 and
4. Mode of operation upon a
			 loss of power and restoration of power.
Statutory
				Authority:
				RCW
				  19.27A.020,
				19.27A.025 and
				chapters
				19.27 and
				34.05 RCW. WSR 13-04-056, §
				51-11C-40803, filed 2/1/13, effective 7/1/13. WSR 13-23-007, §
				51-11C-40803, filed 11/7/2013, effective
				12/8/2013
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40804 - Section C408.4- Controlled receptacle and lighting control system commissioning

Current through Register Vol. 24-14, July 15, 2024
C408.4 Controlled receptacle and lighting control system
				commissioning.
Controlled receptacles and lighting control systems
				subject to Section C405 shall be included in the commissioning process required
				by Section C408.1. The configuration and function of controlled receptacles and
				lighting control systems required by this code shall be tested and shall comply
				with Section C408.4.1.
EXCEPTION:
Lighting control systems are exempt from the
						  commissioning process in buildings where:
1. The total installed lighting load is less than 20
						  kW; and
2. The lighting load controlled by occupancy sensors or
						  automatic daylighting controls is less than 10 kW.
C408.4.1 System testing.
Functional performance testing shall demonstrate that occupant
				sensors, time switches, manual overrides, night sweep-off, daylight responsive
				control, and controlled receptacles are installed and operate in accordance
				with approved construction documents. Testing shall include the
sequence of operation
and be conducted under the following
				conditions:
1. Normal
			 operation;
2. Redundant or
			 automatic back-up mode;
3.
			 Performance of alarms; and
4. Mode
			 of operation upon a loss of power and restoration of power.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40804, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-408045 - Section C408.5-Other systems commissioning

Current through Register Vol. 24-14, July 15, 2024
C408.5 Systems installed to meet Section C406 or
				C407.
Equipment, components, controls or configuration settings for
				systems which are included in the project to comply with Section C406 or C407
				shall be included in the commissioning process required by Section
				C408.1.
C408.5.1 System testing.
Functional performance
				testing for these appliances, equipment, components, controls and/or
				configuration settings shall demonstrate operation, function and maintenance
				serviceability for each of the commissioned systems in accordance with the
				approved construction documents.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40805 - Section C408.6-Metering system commissioning

Current through Register Vol. 24-14, July 15, 2024
C408.6 Metering system commissioning.
Energy
				metering systems required by Section C409 shall comply with Section C408.6 and
				be included in the commissioning process required by Section C408.1. The
				commissioning process shall include all energy metering equipment and controls
				required by Section C409.
C408.6.1 System testing.
Functional performance testing shall demonstrate that energy
				source meters, end-use meters, data acquisition systems, and energy displays
				are installed and operate in accordance with approved construction documents.
				At a minimum, testing shall confirm that:
1. The metering system devices and components
			 work properly under low and high load conditions.
2. The metered data is delivered in a format
			 that is compatible with the data collection system.
3. The energy display is in a location with
access
to building operation and management
			 personnel.
4. The energy display
			 meets code requirements regarding views required in Section C409.4.3. The
			 display shows energy data in identical units (e.g., kWh).
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40805, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40807 - Section C408.7-Refrigeration system commissioning

Current through Register Vol. 24-14, July 15, 2024
C408.7 Refrigeration system commissioning.
All
				installed refrigeration systems subject to Section C410 shall be included in
				the commissioning process required by Section C408.1.
EXCEPTIONS:
1. Self-contained refrigeration systems are exempt from
						  the commissioning process.
2. Total installed capacity for refrigeration is equal
						  to or less than 240 kBtu/h.
C408.7.1 System testing.
Functional performance
				testing shall demonstrate that compressors, heat exchangers, piping,
				distribution systems, and system-to-system interfacing relationships are
				installed and operate in accordance with approved construction documents.
				Testing shall include the sequence of operation and be conducted under
				full-load at, part-load and the following conditions:
1. Normal mode;
2. Redundant or automatic back-up
			 mode;
3. Performance of alarms;
			 and
4. Mode of operation upon a
			 loss of power and restoration of power.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-40900 - Section C409 - Energy metering and energy consumption management

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-40900, filed 2/1/13, effective
				  7/1/13.