reglab/statecodes huggingface dataset:
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61060 - Section A106 - On-grade slab floors

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61060, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61061 - Section A106.1 - General

Current through Register Vol. 24-14, July 15, 2024
A106.1 General.
Table A106.1 lists heat loss
				coefficients for heated on-grade slab floors, in units of Btu/h . °F per
				lineal foot of perimeter.
Table A106.1 Default F -factors for On-Grade
				Slabs
Insulation Type
R-0
R-5
R-10
R-15
R-20
R-30
Unheated Slab
Uninsulated slab
0.73
--
--
--
--
--
2 ft. Horizontal (No thermal break)
--
0.70
0.70
0.69
--
--
4 ft. Horizontal (No thermal break)
--
0.67
0.64
0.63
--
--
2 ft. Vertical
--
0.58
0.54
0.52
--
--
4 ft. Vertical
--
0.54
0.48
0.45
--
--
Fully insulated slab*
--
--
0.36
0.31
0.26
0.21
Heated Slab
Uninsulated slab
0.84
--
--
--
--
--
Fully insulated slab*
--
0.74
0.55
0.44
0.39
0.32
R-5 Center (With perimeter insulation)
--
--
0.66
0.62
--
--
R-10 Center (With perimeter insulation)
--
--
--
0.51
--
--
3 ft. Vertical
--
--
0.78
--
--
--
*Edge insulation R-10 regardless of the below slab
							 insulation level.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61061, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61062 - Section A106.2 - Component description

Current through Register Vol. 24-14, July 15, 2024
A106.2 Component description.
All on-grade slab
				floors are assumed to be 6 inch concrete poured directly onto the earth. The
				bottom of the slab is assumed to be at grade line. Monolithic and floating
				slabs are not differentiated.
Soil is assumed to have a conductivity of 0.75 Btu/h .
				ft2 . °F. Slabs 2 feet or more below grade
				should use basement coefficients.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61062, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61063 - Section A106.3 - Insulation description

Current through Register Vol. 24-14, July 15, 2024
A106.3 Insulation description.
Coefficients are
				provided for the following three configurations:
1.
Two foot (or four foot)
			 vertical:
Insulation is applied directly to the slab exterior, extending
			 downward from the top of the slab to a depth of 2 feet (or 4 feet) below
			 grade.
2.
Two foot (or four
			 foot) horizontal:
Insulation is applied directly to the underside of the
			 slab, and run horizontally from the perimeter inward for 2 feet (or 4 feet).
			 The slab edge is exposed in this configuration.
Note:
A horizontal installation with a thermal break of at
							 least R-5 at the slab edge should use the vertical-case F-factors.
3.
Fully insulated slab:
Insulation extends from the top of the slab, along the entire perimeter, and
			 completely covers the area under the slab. Thicker perimeter insulation covers
			 the slab edge and extends 2 feet under the slab.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61063, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61070 - Section A107 - Default U-factors for doors

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61070, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61071 - Section A107.1 - Doors without NFRC certification

Current through Register Vol. 24-14, July 15, 2024
A107.1 Doors without NFRC certification.
Doors
				that do not have NFRC certification shall be assigned the appropriate U-factor
				from Tables A107.1(1) through A107.1(4).
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61071, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-610711 - Table A107.1(1)Default U-factors for doors

Current through Register Vol. 24-14, July 15, 2024
Table A107.1(1)
Default U-factors for Doors
Door Type
No
Glazed Fenestration
Single Glazing
Double
Glazing
with 1/4
						in.
Airspace
Double Glazing with 1/2
in.
						Airspace
Double Glazing with e = 0.10, 1/2 in. Argon
Swinging Doors (Rough opening - 38 in. x
						82 in.)
Slab Doors
Wood slab in wood framea
0.46
6% glazed fenestration (22 in. x 8 in. lite)
-
0.48
0.47
0.46
0.44
25% glazed fenestration (22 in. x 36 in. lite)
-
0.58
0.48
0.46
0.42
45% glazed fenestration (22 in. x 64 in. lite)
-
0.69
0.49
0.46
0.39
More than 50% glazed fenestration
Use Table C303.1.3(1)/R303.1.3(1) as
						appropriate
Insulated steel slab with wood edge in wood
						framea
0.16
6% glazed fenestration (22 in. x 8 in. lite)
-
0.21
0.20
0.19
0.18
25% glazed fenestration (22 in. x 36 in. lite)
-
0.39
0.28
0.26
0.23
45% glazed fenestration (22 in. x 64 in. lite)
-
0.58
0.38
0.35
0.26
More than 50% glazed fenestration
Use Table C303.1.3(1)/R303.1.3(1) as
						appropriate
Foam insulated steel slab with metal edge in steel
						frameb
0.37
6% glazed fenestration (22 in. x 8 in. lite)
-
0.44
0.42
0.41
0.39
25% glazed fenestration (22 in. x 36 in. lite)
-
0.55
0.50
0.48
0.44
45% glazed fenestration (22 in. x 64 in. lite)
-
0.71
0.59
0.56
0.48
More than 50% glazed fenestration
Use Table C303.1.3(1)/R303.1.3(1) as
						appropriate
Cardboard honeycomb slab with metal edge in steel
						frameb
0.61
Style and Rail Doors
Sliding glass doors/French doors
Use Table C303.1.3(1)/R303.1.3(1) as
						appropriate
Site-Assembled Style and Rail
						Doors
Aluminum in aluminum frame
-
1.32
0.99
0.93
0.79
Aluminum in aluminum frame with thermal break
-
1.13
0.80
0.74
0.63
Note: Appendix A Tables A107.1(2) through A107.1(4) may also be
				used if applicable.
aThermally broken sill
							 (add 0.03 for nonthermally broken sill)
bNonthermally broken
							 sill
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-610711, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-610712 - Table A107.1(2) - Default U-factors for revolving doors

Current through Register Vol. 24-14, July 15, 2024
Table A107.1(2) Default U-factors for Revolving
				Doors
Revolving Doors
Size (W x H)
U-Factor
3-wing
8 ft. x 7 ft.
10 ft. x 8 ft.
0.79
0.80
4-wing
7 ft. x 6.5 ft.
7 ft. x 7.5 ft.
0.63
0.64
Open
82 in. x 84 in.
1.32
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-610712, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-610713 - Table A107.1(3) - Default U-factors for steel emergency doors

Current through Register Vol. 24-14, July 15, 2024
Table A107.1(3) Default U-factors for Steel Emergency
				Doors
Double-skin Steel Emergency Exit
							 Doors
Core Insulation
3 ft. x 6 ft. 8 in.
6 ft. x 6 ft. 8 in.
1-3/8 in. thickness
Honeycomb kraft paper
Mineral wool, steel ribs
Polyurethane foam
0.57
0.44
0.34
0.52
0.36
0.28
1-3/4 in. thickness
Honeycomb kraft paper
Mineral wool, steel ribs
Polyurethane foam
0.57
0.41
0.31
0.54
0.33
0.26
1-3/8 in. thickness
Honeycomb kraft paper
Mineral wool, steel ribs
Polyurethane foam
0.60
0.47
0.37
0.55
0.39
0.31
1-3/4 in. thickness
Honeycomb kraft paper
Mineral wool, steel ribs
Polyurethane foam
0.60
0.44
0.34
0.57
0.37
0.30
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-610713, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-610714 - Table A107.1(4)-Default U-factors for steel garage and hangar doors

Current through Register Vol. 24-14, July 15, 2024
Table A107.1(4)
Default U-factors for Steel Garage and Hangar
				Doors
Double-skin Steel Garage and Aircraft
						Hangar Doors
One-piece tilt-upa
Sectional tilt-upb
Aircraft hangar
Insulatione
8 ft. x 7 ft.
16 ft. x 7 ft.
9 ft. x 7 ft.
72 ft. x 12 ft.c
240 ft. x 50 ft.d
1-3/8 in. thickness XPS, steel ribs EPS, steel ribs
0.36 0.33
0.33 0.31
0.34 - 0.39 0.31 - 0.36
2 in. thickness XPS, steel ribs EPS, steel ribs
0.31 0.29
0.28 0.26
0.29 - 0.33 0.27 - 0.31
3 in. thickness XPS, steel ribs EPS, steel ribs
0.26 0.24
0.23 0.21
0.25 - 0.28 0.24 - 0.27
4 in. thickness XPS, steel ribs EPS, steel ribs
0.23 0.21
0.20 0.19
0.23 - 0.25 0.21 - 0.24
6 in. thickness XPS, steel ribs EPS, steel ribs
0.20 0.19
0.16 0.15
0.20 - 0.21 0.19 - 0.21
4 in. thickness Noninsulated Expanded polystyrene Mineral
						wool, steel ribs Extruded polystyrene
1.10 0.25 0.25 0.23
1.23 0.16 0.16 0.15
6 in. thickness Noninsulated Expanded polystyrene Mineral
						wool, steel ribs Extruded polystyrene
1.10 0.21 0.23 0.20
1.23 0.13 0.13 0.12
Uninsulated All products
1.15
a Values are for thermally
							 broken or thermally unbroken doors.
b Lower values are for
							 thermally broken doors; upper values are for doors with no thermal
							 break.
c Typical size for a small
							 private airplane (single-engine or twin).
d Typical hangar door for
							 a midsize commercial jet airliner.
e XPS is extruded
							 polystyrene, EPS is expanded polystyrene.
Statutory Authority:
				  RCW
				    19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-610714, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61080 - Section A108 - Air infiltration

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61080, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-61081 - Section A108.1 - General

Current through Register Vol. 24-14, July 15, 2024
A108.1 General.
Tables A108.1(1) and A108.1(2)
				list effective air change rates and heat capacities for heat loss due to
				infiltration for Single-Family Residential.
The estimated seasonal average infiltration rate in air changes
				per hour (ACH) is given for standard air-leakage control (see Section R402.4
				for air leakage requirements for Single-Family Residential). The effective air
				change rate shall be used in calculations for compliance under either the
				Component Performance or Systems Analysis approaches.
Heat loss due to infiltration shall be computed using the
				following equation:
Qinfil
=
ACHeff * HCP
Where:
Qinfil
=
Heat loss due to air infiltration.
ACHeff
=
The effective air infiltration rate in Table
							 A108.1(1)
HCP
=
The Heat Capacity Density Product for the appropriate
							 elevation or climate zone as given below.
Table A108.1(1) Assumed Effective Air Changes per
				Hour
Air-Leakage
Air Changes per Hour
Control Package
Natural
Effective
Standard
0.35
0.35
Table A108.1(2) Default Heat Capacity/Density Product for
				Air
Zone
Average Elevation
Heat Capacity/Density
1
Mean Sea Level
0.0180 Btu/h . °F
2
2000
0.0168 Btu/h . °F
3
3000
0.0162 Btu/h . °F
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-61081, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-70000 - Appendix B - Default internal load values and schedules

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-70000, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71010 - Section B101 - General

Current through Register Vol. 24-14, July 15, 2024
B101.1 Scope.
The following default internal load
				values and schedules shall apply to Section C407.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71010, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71020 - Section B102 - Default tables of internal loads

Current through Register Vol. 24-14, July 15, 2024
B102 Default tables of internal loads.
Default
				occupancy densities, receptacle power densities and service hot water
				consumption are included in Table B102.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71020, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71021 - Table B102 - Acceptable occupancy densities, receptacle power densities and service hot water consumption

Current through Register Vol. 24-14, July 15, 2024
TABLE B102 Acceptable Occupancy Densities, Receptacle
				Power Densities and Service Hot Water
				Consumptiona
Building Type
Occupancy Densityb
							 ft2/Person (Btu/h .
							 ft2)
Receptacle Power
							 Densityc, Watts/ft2
							 (Btu/h . ft2)
Service Hot Water
							 Quantitiesd Btu/h per person
Assembly
50 (4.60)
0.25 (0.85)
215
Health/Institutional
200 (1.15)
1.00 (3.41)
135
Hotel/Motel
250 (0.92)
0.25 (0.85)
1,110
Light Manufacturing
750 (0.31)
0.20 (0.68)
225
Office
275 (0.84)
0.75 (2.56)
175
Parking Garage
NA
NA
NA
Restaurant
100 (2.30)
0.10 (0.34)
390
Retail
300 (3.07)
0.25 (0.85)
135
School
75 (3.07)
0.50 (1.71)
215
Warehouse
15,000 (0.02)
0.10 (0.34)
225
aThe occupancy densities,
							 receptacle power densities, and service hot water consumption values are from
							 ASHRAE Standard 90.1-1989 and addenda.
bValues are in square feet
							 of conditioned floor area per person. Heat generation in Btu per person per
							 hour is 230 sensible and 190 latent. Figures in parenthesis are equivalent Btu
							 per hour per square foot.
cValues are in watts per
							 square foot of conditioned floor area. Figures in parenthesis are equivalent
							 Btu per hour per square foot. These values are the minimum acceptable. If other
							 process loads are not input (such as for computers, cooking, refrigeration,
							 etc.), it is recommended that receptacle power densities be increased until
							 total process energy consumption is equivalent to 25 percent of the
							 total.
dValues are in Btu per
							 person per hour.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71021, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71030 - Section B103 - Default schedules

Current through Register Vol. 24-14, July 15, 2024
B103 Default schedules.
Default schedules for
				occupancy, lighting, receptacles, HVAC, service hot water, and elevators are
				included in Tables B103(1) through B103(10).
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71030, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71031 - Table B103(1) - Assembly occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(1) Assembly
				Occupancya
Schedule for Occupancy
Schedule for
							 Lightingb/ Receptacle
Schedule for Service
Hot Water
Schedule for Elevator
Hour of Day (time)
Percent of
Maximum Load
Percent of
Maximum Load
Schedule for HVAC
System
Percent of
Maximum Load
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
0
0
0
5
5
5
Off
Off
Off
0
0
0
0
0
0
2
(1-2am)
0
0
0
5
5
5
Off
Off
Off
0
0
0
0
0
0
3
(2-3am)
0
0
0
5
5
5
Off
Off
Off
0
0
0
0
0
0
4
(3-4am)
0
0
0
5
5
5
Off
Off
Off
0
0
0
0
0
0
5
(4-5am)
0
0
0
5
5
5
Off
Off
Off
0
0
0
0
0
0
6
(5-6am)
0
0
0
5
5
5
On
Off
Off
0
0
0
0
0
0
7
(6-7am)
0
0
0
35/40
5
5
On
On
On
0
0
0
0
0
0
8
(7-8am)
0
0
0
35/40
30
30
On
On
On
0
0
0
0
0
0
9
(8-9am)
20
20
10
35/40
30
30
On
On
On
0
0
0
0
0
0
10
(9-10am)
20
20
10
65/75
40/50
30
On
On
On
5
5
5
0
0
0
11
(10-11am)
20
20
10
65/75
40/50
30
On
On
On
5
5
5
0
0
0
12
(11-12pm)
80
60
10
65/75
40/50
30
On
On
On
35
20
10
0
0
0
13
(12-1pm)
80
60
10
65/75
40/50
55/65
On
On
On
5
0
0
0
0
0
14
(1-2pm)
80
60
70
65/75
40/50
55/65
On
On
On
5
0
0
0
0
0
15
(2-3pm)
80
60
70
65/75
40/50
55/65
On
On
On
5
0
0
0
0
0
16
(3-4pm)
80
60
70
65/75
40/50
55/65
On
On
On
5
0
0
0
0
0
17
(4-5pm)
80
60
70
65/75
40/50
55/65
On
On
On
5
0
0
0
0
0
18
(5-6pm)
80
60
70
65/75
40/50
55/65
On
On
On
0
0
0
0
0
0
19
(6-7pm)
20
60
70
65/75
40/50
55/65
On
On
On
0
0
0
0
0
0
20
(7-8pm)
20
60
70
65/75
40/50
55/65
On
On
On
0
65
65
0
0
0
21
(8-9pm)
20
60
70
65/75
40/50
55/65
On
On
On
0
30
30
0
0
0
22
(9-10pm)
20
80
70
65/75
40/50
55/65
On
On
On
0
0
0
0
0
0
23
(10-11pm)
10
10
20
25
40/50
5
On
On
On
0
0
0
0
0
0
24
(11-12am)
0
0
0
5
5
5
Off
Off
Off
0
0
0
0
0
0
Total/Day
710
750
700
1010/
1155
660/
800
745/845
1800
1700
1700
70
125
115
0
0
0
Total/Week
50.50
hours
64.55/
74.20
hours
124
hours
5.9
hours
0
hours
Total/Year
2633
hours
3357/
3869
hours
6465
hours
308
hours
0
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system, and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
bLighting profiles are
							 modified to reflect the requirement for occupancy sensors in Section
							 C405.2.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71031, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71032 - Table B103(2) - Health occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(2) Health
				Occupancya
Schedule for Occupancy
Schedule for
							 Lightingb/ Receptacle
Schedule for Service
Hot Water
Schedule for Elevator
Hour of Day (time)
Percent of
Maximum Load
Percent of
Maximum Load
Schedule for HVAC System
Percent of
Maximum Load
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
2
(1-2am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
3
(2-3am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
4
(3-4am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
5
(4-5am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
6
(5-6am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
7
(6-7am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
8
(7-8am)
10
10
0
45/50
20
5
On
On
On
17
1
1
2
2
0
9
(8-9am)
50
30
5
80/90
35/40
10
On
On
On
58
20
1
75
46
2
10
(9-10am)
80
40
5
80/90
35/40
10
On
On
On
66
28
1
100
70
2
11
(10-11am)
80
40
5
80/90
35/40
10
On
On
On
78
30
1
100
70
2
12
(11-12pm)
80
40
5
80/90
35/40
10
On
On
On
82
30
1
100
70
2
13
(12-1pm)
80
40
5
80/90
35/40
10
On
On
On
71
24
1
75
51
2
14
(1-2pm)
80
40
5
80/90
35/40
10
On
On
On
82
24
1
100
51
2
15
(2-3pm)
80
40
5
80/90
35/40
10
On
On
On
78
23
1
100
51
2
16
(3-4pm)
80
40
5
80/90
35/40
10
On
On
On
74
23
1
100
51
2
17
(4-5pm)
80
40
0
30
35/40
5
On
On
On
63
23
1
100
51
0
18
(5-6pm)
50
10
0
30
35/40
5
On
On
On
41
10
1
100
25
0
19
(6-7pm)
30
10
0
30
10
5
On
On
On
18
1
1
52
2
0
20
(7-8pm)
30
0
0
30
10
5
On
On
On
18
1
1
52
0
0
21
(8-9pm)
20
0
0
30
10
5
On
On
On
18
1
1
52
0
0
22
(9-10pm)
20
0
0
30
10
5
On
On
On
10
1
1
28
0
0
23
(10-11pm)
0
0
0
30
10
5
On
On
On
1
1
1
0
0
0
24
(11-12am)
0
0
0
10
10
5
On
On
On
1
1
1
0
0
0
Total/Day
850
380
40
975/
1060
500/
550
160
2400
2400
2400
783
249
24
1136
540
16
Total/Week
46.70
hours
55.35/
60.10
hours
168
hours
41.88
hours
62.36
hours
Total/Year
2435
hours
2878/
3134
hours
8760
hours
2148
hours
3251
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system, and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
bLighting profiles are
							 modified to reflect the requirement for occupancy sensors in Section
							 C405.2.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71032, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71033 - Table B103(3) - Hotel/motel occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(3) Hotel/Motel
				Occupancya
Schedule for
Occupancy
Schedule for Lighting/ Receptacle
Schedule for Service
Hot Water
Schedule for Elevator
Hour of Day (time)
Percent of
Maximum Load
Percent of
Maximum Load
Schedule for HVAC System
Percent of
Maximum Load
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
90
90
70
20
20
30
On
On
On
20
20
25
40
44
55
2
(1-2am)
90
90
70
15
20
30
On
On
On
15
15
20
33
35
55
3
(2-3am)
90
90
70
10
10
20
On
On
On
15
15
20
33
35
43
4
(3-4am)
90
90
70
10
10
20
On
On
On
15
15
20
33
35
43
5
(4-5am)
90
90
70
10
10
20
On
On
On
20
20
20
33
35
43
6
(5-6am)
90
90
70
20
10
20
On
On
On
25
25
30
33
35
43
7
(6-7am)
70
70
70
40
30
30
On
On
On
50
40
50
42
40
52
8
(7-8am)
40
50
70
50
30
40
On
On
On
60
50
50
42
32
52
9
(8-9am)
40
50
50
40
40
40
On
On
On
55
50
50
52
45
65
10
(9-10am)
20
30
50
40
40
30
On
On
On
45
50
55
52
45
65
11
(10-11am)
20
30
50
25
30
30
On
On
On
40
45
50
40
42
53
12
(11-12pm)
20
30
30
25
25
30
On
On
On
45
50
50
51
60
60
13
(12-1pm)
20
30
30
25
25
30
On
On
On
40
50
40
51
65
53
14
(1-2pm)
20
30
20
25
25
20
On
On
On
35
45
40
51
65
51
15
(2-3pm)
20
30
20
25
25
20
On
On
On
30
40
30
51
65
50
16
(3-4pm)
30
30
20
25
25
20
On
On
On
30
40
30
51
65
44
17
(4-5pm)
50
30
30
25
25
20
On
On
On
30
35
30
63
65
64
18
(5-6pm)
50
50
40
25
25
20
On
On
On
40
40
40
80
75
62
19
(6-7pm)
50
60
40
60
60
50
On
On
On
55
55
50
86
80
65
20
(7-8pm)
70
60
60
80
70
70
On
On
On
60
55
50
70
80
63
21
(8-9pm)
70
60
60
90
70
80
On
On
On
50
50
40
70
75
63
22
(9-10pm)
80
70
80
80
70
60
On
On
On
55
55
50
70
75
63
23
(10-11pm)
90
70
80
60
60
50
On
On
On
45
40
40
45
55
40
24
(11-12am)
90
70
80
30
30
30
On
On
On
25
30
20
45
55
40
Total/Day
1390
1390
1300
855
785
810
2400
2400
2400
915
930
900
1217
1303
1287
Total/Week
96.40
hours
58.70
hours
168.0
hours
64.05
hours
86.75
hours
Total/Year
5026
hours
3061
hours
8760
hours
3340
hours
4523
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system, and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71033, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71034 - Table B103(4) - Light manufacturing occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(4) Light Manufacturing
				Occupancya
Schedule for Occupancy
Schedule for
							 Lightingb/ Receptacle
Schedule for Service
Hot Water
Schedule for Elevator
Hour of Day (time)
Percent of
Maximum Load
Percent of
Maximum Load
Schedule for HVAC System
Percent of
Maximum Load
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
2
(1-2am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
3
(2-3am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
4
(3-4am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
5
(4-5am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
6
(5-6am)
0
0
0
10
5
5
Off
Off
Off
8
8
7
0
0
0
7
(6-7am)
10
10
5
10
10
5
On
On
Off
7
7
4
0
0
0
8
(7-8am)
20
10
5
30
10
5
On
On
Off
19
11
4
35
16
0
9
(8-9am)
95
30
5
85/90
30
5
On
On
Off
35
15
4
69
14
0
10
(9-10am)
95
30
5
85/90
30
5
On
On
Off
38
21
4
43
21
0
11
(10-11am)
95
30
5
85/90
30
5
On
On
Off
39
19
4
37
18
0
12
(11-12pm)
95
30
5
85/90
30
5
On
On
Off
47
23
6
43
25
0
13
(12-1pm)
50
10
5
75/80
15
5
On
On
Off
57
20
6
58
21
0
14
(1-2pm)
95
10
5
85/90
15
5
On
On
Off
54
19
9
48
13
0
15
(2-3pm)
95
10
5
85/90
15
5
On
On
Off
34
15
6
37
8
0
16
(3-4pm)
95
10
5
85/90
15
5
On
On
Off
33
12
4
37
4
0
17
(4-5pm)
95
10
5
85/90
15
5
On
On
Off
44
14
4
46
5
0
18
(5-6pm)
30
5
5
50
5
5
On
On
Off
26
7
4
62
6
0
19
(6-7pm)
10
5
0
30
5
5
On
Off
Off
21
7
4
20
0
0
20
(7-8pm)
10
0
0
30
5
5
On
Off
Off
15
7
4
12
0
0
21
(8-9pm)
10
0
0
20
5
5
On
Off
Off
17
7
4
4
0
0
22
(9-10pm)
10
0
0
20
5
5
On
Off
Off
8
9
7
4
0
0
23
(10-11pm)
5
0
0
10
5
5
Off
Off
Off
5
5
4
0
0
0
24
(11-12am)
5
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
Total/Day
920
200
60
995/
1040
280
120
1600
1200
0
537
256
113
555
151
0
Total/Week
48.60
hours
53.75/
56.00
hours
92.00
hours
30.54
hours
29.26
hours
Total/Year
2534
hours
2795/
2920
hours
4797
hours
1592
hours
1526
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system, and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
bLighting profiles are
							 modified to reflect the requirement for occupancy sensors in Section
							 C405.2.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71034, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71035 - Table B103(5) - Office occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(5) Office
				Occupancya
Schedule for Occupancy
Schedule for
							 Lightingb/ Receptacle
Schedule for Service Hot Water
Schedule for Elevator
Hour of Day (time)
Percent of
Maximum Load
Percent of
Maximum Load
Schedule for HVAC System
Percent of
Maximum Load
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
2
(1-2am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
3
(2-3am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
4
(3-4am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
5
(4-5am)
0
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
6
(5-6am)
0
0
0
10
5
5
Off
Off
Off
8
8
7
0
0
0
7
(6-7am)
10
10
5
10
10
5
On
On
Off
7
7
4
0
0
0
8
(7-8am)
20
10
5
30
10
5
On
On
Off
19
11
4
35
16
0
9
(8-9am)
95
30
5
65/90
30
5
On
On
Off
35
15
4
69
14
0
10
(9-10am)
95
30
5
65/90
30
5
On
On
Off
38
21
4
43
21
0
11
(10-11am)
95
30
5
65/90
30
5
On
On
Off
39
19
4
37
18
0
12
(11-12pm)
95
30
5
65/90
30
5
On
On
Off
47
23
6
43
25
0
13
(12-1pm)
50
10
5
55/80
15
5
On
On
Off
57
20
6
58
21
0
14
(1-2pm)
95
10
5
65/90
15
5
On
On
Off
54
19
9
48
13
0
15
(2-3pm)
95
10
5
65/90
15
5
On
On
Off
34
15
6
37
8
0
16
(3-4pm)
95
10
5
65/90
15
5
On
On
Off
33
12
4
37
4
0
17
(4-5pm)
95
10
5
65/90
15
5
On
On
Off
44
14
4
46
5
0
18
(5-6pm)
30
5
5
35/50
5
5
On
On
Off
26
7
4
62
6
0
19
(6-7pm)
10
5
0
30
5
5
On
On
Off
21
7
4
20
0
0
20
(7-8pm)
10
0
0
30
5
5
On
Off
Off
15
7
4
12
0
0
21
(8-9pm)
10
0
0
20
5
5
On
Off
Off
17
7
4
4
0
0
22
(9-10pm)
10
0
0
20
5
5
On
Off
Off
8
9
7
4
0
0
23
(10-11pm)
5
0
0
10
5
5
Off
Off
Off
5
5
4
0
0
0
24
(11-12am)
5
0
0
5
5
5
Off
Off
Off
5
5
4
0
0
0
Total/Day
920
200
60
800/
1040
280
120
1600
1200
0
537
256
113
555
151
0
Total/Week
48.60
hours
44.00/56.00
hours
92.00
hours
30.54
hours
29.26
hours
Total/Year
2534
hours
2288/
2920
hours
4797
hours
1592
hours
1526
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system, and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
bLighting profiles are
							 modified to reflect the requirement for occupancy sensors in Section
							 C405.2.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71035, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71036 - Table B103(6) - Parking garage occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(6) Parking Garage
				Occupancya
Hour of Day
(time)
Schedule for
Occupancy
Percent of
Maximum Load
Schedule for
Lightingb/
Receptacle
Percent of
Maximum Load
Schedule for
HVAC System
Schedule for
Service Hot
							 Water
Percent of
Maximum Load
Schedule for
Elevator
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
50/100
50/100
50/100
2
(1-2am)
50/100
50/100
50/100
3
(2-3am)
50/100
50/100
50/100
4
(3-4am)
50/100
50/100
50/100
5
(4-5am)
50/100
50/100
50/100
6
(5-6am)
50/100
50/100
50/100
7
(6-7am)
100
100
50/100
8
(7-8am)
100
100
50/100
9
(8-9am)
100
100
50/100
10
(9-10am)
100
100
50/100
Based
Included
11
(10-11am)
100
100
50/100
on
with
12
(11-12pm)
N/A
100
100
50/100
likely
N/A
other
13
(12-1pm)
100
100
50/100
use
occupancies
14
(1-2pm)
100
100
50/100
15
(2-3pm)
100
100
50/100
16
(3-4pm)
100
100
50/100
17
(4-5pm)
100
100
50/100
18
(5-6pm)
100
50/100
50/100
19
(6-7pm)
100
50/100
50/100
20
(7-8pm)
100
50/100
50/100
21
(8-9pm)
100
50/100
50/100
22
(9-10pm)
100
50/100
50/100
23
(10-11pm)
50/100
50/100
50/100
24
(11-12am)
50/100
50/100
50/100
Total/Day
2000/
2400
1750/
2400
1200/
2400
Total/Week
129.50/
168
hours
Total/Year
6734/
8760
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
bLighting profiles are
							 modified to reflect the requirement for occupancy sensors in Section C405.2.
							 For parking garage lighting, the schedule has been revised to accompany the
							 office schedule: The lighting in the parking garage is set to be on at 100
							 percent for all hours when the building occupancy is 10 percent or greater, but
							 reduced to 50 percent (per Section C405.2) for all hours when the building
							 occupancy is less than 10 percent. For a parking garage serving a use other
							 than office, it is acceptable to modify the parking garage schedule to parallel
							 that use.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71036, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71037 - Table B103(7) - Restaurant occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(7) Restaurant
				Occupancya
Schedule for Occupancy
Schedule for
							 Lightingb/
Receptacle
Schedule for Service Hot Water
Schedule for Elevator
Hour of Day
(time)
Percent of
Maximum Load
Percent of
Maximum Load
Schedule for
HVAC System
Percent of
Maximum Load
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
15
30
20
15
20
20
On
On
On
20
20
25
0
0
0
2
(1-2am)
15
25
20
15
15
15
On
On
On
15
15
20
0
0
0
3
(2-3am)
5
5
5
15
15
15
On
On
On
15
15
20
0
0
0
4
(3-4am)
0
0
0
15
15
15
Off
Off
Off
0
0
0
0
0
0
5
(4-5am)
0
0
0
15
15
15
Off
Off
Off
0
0
0
0
0
0
6
(5-6am)
0
0
0
20
15
15
Off
Off
Off
0
0
0
0
0
0
7
(6-7am)
0
0
0
35/40
30
30
Off
Off
Off
0
0
0
0
0
0
8
(7-8am)
5
0
0
35/40
30
30
On
Off
Off
60
0
0
0
0
0
9
(8-9am)
5
0
0
55/60
55/60
45/50
On
Off
Off
55
0
0
0
0
0
10
(9-10am)
5
5
0
55/60
55/60
45/50
On
On
Off
45
50
0
0
0
0
11
(10-11am)
20
20
10
85/90
75/80
65/70
On
On
On
40
45
50
0
0
0
12
(11-12pm)
50
45
20
85/90
75/80
65/70
On
On
On
45
50
50
0
0
0
13
(12-1pm)
80
50
25
85/90
75/80
65/70
On
On
On
40
50
40
0
0
0
14
(1-2pm)
70
50
25
85/90
75/80
65/70
On
On
On
35
45
40
0
0
0
15
(2-3pm)
40
35
15
85/90
75/80
65/70
On
On
On
30
40
30
0
0
0
16
(3-4pm)
20
30
20
85/90
75/80
65/70
On
On
On
30
40
30
0
0
0
17
(4-5pm)
25
30
25
85/90
75/80
55/60
On
On
On
30
35
30
0
0
0
18
(5-6pm)
50
30
35
85/90
85/90
55/60
On
On
On
40
40
40
0
0
0
19
(6-7pm)
80
70
55
85/90
85/90
55/60
On
On
On
55
55
50
0
0
0
20
(7-8pm)
80
90
65
85/90
85/90
55/60
On
On
On
60
55
50
0
0
0
21
(8-9pm)
80
70
70
85/90
85/90
55/60
On
On
On
50
50
40
0
0
0
22
(9-10pm)
50
65
35
85/90
85/90
55/60
On
On
On
55
55
50
0
0
0
23
(10-11pm)
35
55
20
45/50
45/50
45/50
On
On
On
45
40
40
0
0
0
24
(11-12am)
20
35
20
30
30
30
On
On
On
25
30
20
0
0
0
Total/Day
750
740
485
1370/
1455
1290/
1365
1040/
1115
2000
1800
1700
790
730
625
0
0
0
Total/Week
49.75
hours
91.80/
97.55
hours
135
hours
53.05
hours
0
hours
Total/Year
2594
hours
4774/
5086
hours
7039
hours
2766
hours
0
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
bLighting profiles are
							 modified to reflect the requirement for occupancy sensors in Section
							 C405.2.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71037, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-71038 - Table B103(8) - Retail occupancy

Current through Register Vol. 24-14, July 15, 2024
Table B103(8) Retail
				Occupancya
Schedule for
Occupancy
Schedule for
Lightingb/
Receptacle
Schedule for Service Hot Water
Schedule for
Elevator
Hour of Day (time)
Percent of
Maximum Load
Percent of
Maximum Load
Schedule for HVAC System
Percent of
Maximum Load
Percent of
Maximum Load
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
Wk
Sat
Sun
1
(12-1am)
0
0
0
5
5
5
Off
Off
Off
4
11
7
0
0
0
2
(1-2am)
0
0
0
5
5
5
Off
Off
Off
5
10
7
0
0
0
3
(2-3am)
0
0
0
5
5
5
Off
Off
Off
5
8
7
0
0
0
4
(3-4am)
0
0
0
5
5
5
Off
Off
Off
4
6
6
0
0
0
5
(4-5am)
0
0
0
5
5
5
Off
Off
Off
4
6
6
0
0
0
6
(5-6am)
0
0
0
5
5
5
Off
Off
Off
4
6
6
0
0
0
7
(6-7am)
0
0
0
5
5
5
On
On
Off
4
7
7
0
0
0
8
(7-8am)
10
10
0
20
10
5
On
On
Off
15
20
10
12
9
0
9
(8-9am)
20
20
0
50
30
10
On
On
On
23
24
12
22
21
0
10
(9-10am)
50
50
10
85/90
55/60
10
On
On
On
32
27
14
64
56
11
11
(10-11am)
50
60
20
85/90
85/90
40
On
On
On
41
42
29
74
66
13
12
(11-12pm)
70
80
20
85/90
85/90
40
On
On
On
57
54
31
68
68
35
13
(12-1pm)
70
80
40
85/90
85/90
55/60
On
On
On
62
59
36
68
68
37
14
(1-2pm)
70
80
40
85/90
85/90
55/60
On
On
On
61
60
36
71
69
37
15
(2-3pm)
70
80
40
85/90
85/90
55/60
On
On
On
50
49
34
72
70
39
16
(3-4pm)
80
80
40
85/90
85/90
55/60
On
On
On
45
48
35
72
69
41
17
(4-5pm)
70
80
40
85/90
85/90
55/60
On
On
On
46
47
37
73
66
38
18
(5-6pm)
50
60
20
85/90
85/90
40
On
On
Off
47
46
34
68
58
34
19
(6-7pm)
50
20
10
55/60
50
20
On
On
Off
42
44
25
68
47
3
20
(7-8pm)
30
20
0
55/60
30
5
On
On
Off
34
36
27
58
43
0
21
(8-9pm)
30
20
0
50
30
5
On
On
Off
33
29
21
54
43
0
22
(9-10pm)
0
10
0
20
10
5
Off
On
Off
23
22
16
0
8
0
23
(10-11pm)
0
0
0
5
5
5
Off
Off
Off
13
16
10
0
0
0
24
(11-12am)
0
0
0
5
5
5
Off
Off
Off
8
13
6
0
0
0
Total/Day
750
750
280
1060/1115
940/ 985
500/ 525
1500
1600
900
662
690
459
844
761
288
Total/Week
46.30
hours
67.40/
70.85
hours
100
hours
44.59
hours
52.69
hours
Total/Year
2414
hours
3505/ 3694
hours
5214
hours
2325
hours
2747
hours
Wk = Weekday
aSchedules for occupancy,
							 lighting, receptacle, HVAC system and service hot water are from ASHRAE
							 Standard 90.1-1989 and addendums, except that 5 percent emergency lighting has
							 been added for all off hours. Elevator schedules, except for restaurants, are
							 from the U.S. Department of Energy Standard Evaluation Techniques except
							 changed to 0 percent when occupancy is 0 percent.
These values may be
							 used only if actual schedules are not known.
bLighting profiles are
							 modified to reflect the requirement for occupancy sensors in Section
							 C405.2.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-71038, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-80000 - Appendix C - Exterior design conditions

Current through Register Vol. 24-14, July 15, 2024
As required by Sections C302.2 and R302.2, the heating or
				cooling outdoor design temperatures shall be selected from Table
				C-1.
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-80000, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11C - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Commercial › Section 51-11C-80100 - Table C-1 - Outdoor design temperatures for Washington

Current through Register Vol. 24-14, July 15, 2024
Table C-1 Outdoor Design Temperatures
Outdoor Design Temp. Heating
Outdoor Design Temp. Cooling
Location
(°F)
(°F)
Aberdeen 20 NNE
25
83
Anacortes
24
72
Anatone
-4
89
Auburn
25
84
Battleground
19
91
Bellevue
24
83
Bellingham 2 N
19
78
Blaine
17
73
Bremerton
29
83
Burlington
19
77
Chehalis
21
87
Chelan
10
89
Cheney
4
94
Chesaw
-11
81
Clarkston
10
94
Cle Elum
1
91
Colfax 1 NW
2
94
Colville AP
-2
92
Concrete
19
83
Connell 4 NNW
6
100
Cougar 5 E
25
93
Dallesport AP
14
99
Darrington RS
13
85
Davenport
5
92
Edmonds
24
82
Ellensburg AP
2
90
Elma
24
88
Ephrata AP
7
97
Everett Paine AFB
21
79
Forks 1 E
23
81
Glacier RS
13
82
Glenoma (Kosmos)
18
89
Goldendale
7
94
Grays River Hatchery
24
86
Greenwater
1.4
84
Grotto
21
84
Hoquiam AP
26
79
Inchelium 2 NW
0
92
John Day Dam
19
100
Kent
21
85
Kirkland
17
83
La Grande
23
88
Leavenworth
-3
93
Little Goose Dam
22
101
Long Beach 3 NNE
25
77
Longview
24
87
Lower Granite Dam
14
98
Lower Monument Dam
18
103
Marysville
23
79
Metaline Falls
-1
89
Methow 2 W
1
89
Nespelem 2 S
-4
93
Newhalem
19
89
Newport
-5
92
Northport
2
92
Oak Harbor
16
74
Odessa
7
100
Olga 2 SE
24
71
Olympia, AP
17
85
Omak 2 NW
3
90
Oroville
5
93
Othello
9
98
Packwood
16
90
Plain
-3
89
Pleasant View
16
98
Pomeroy
3
95
Port Angeles
28
75
Port Townsend
25
76
Prosser
12
97
Puyallup
19
86
Quilcene 2 SW
23
83
Quinault RS
25
84
Rainier, Longmire
15
85
Paradise RS
8
71
Raymond
28
81
Redmond
17
83
Republic
-9
87
Richland
11
101
Ritzville
6
99
Satus Pass
10
90
Seattle: Sea-Tac AP
24
83
Sedro Woolley 1 E
19
78
Sequim
23
78
Shelton
23
85
Smyrna
8
102
Snohomish
21
81
Snoqualmie Pass
6
80
Spokane AP
4
92
Spokane CO
10
96
Stampede Pass
7
76
Stehekin 3 NW
12
85
Stevens Pass
6
77
Tacoma CO
29
82
Tatoosh Island
31
63
Toledo AP
17
84
Vancouver
22
88
Vashon Island
28
78
Walla Walla AP
6
96
Waterville
1
88
Wellpinit
1
93
Wenatchee CO
10
92
Whidbey Island
11
71
Willapa Harbor
26
81
Wilson Creek
3
96
Winthrop 1 WSW
-12
91
Yakima AP
11
94
ABBREVIATIONS:
AFB Air Force Base
AP Airport
CO City Office
RS Ranger Station
Typical: "4(miles)NE"
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.025 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-056, §
				  51-11C-80100, filed 2/1/13, effective
				  7/1/13.
Washington Administrative Code › Title 51 - Enterprise Services, Department of (Building Code Council) › Chapter 51-11R - State Building Code adoption and amendment of the 2021 edition of the International Energy Conservation Code, Residential › Section 51-11R-10000 - Chapter 1 RE - Scope and administration

Current through Register Vol. 24-14, July 15, 2024
Statutory Authority:
				  RCW
				  19.27A.020,
				  19.27A.045 and
				  chapters
				  19.27 and
				  34.05 RCW. 13-04-055, §
				  51-11R-10000, filed 2/1/13, effective 7/1/13.
Reviser's note:
The brackets and enclosed
				  material in the text of the above section occurred in the copy filed by the
				  agency.