reglab/statecodes huggingface dataset:
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0191 - What are the required design and construction standards for new tank systems or components?

Current through June 24, 2024
Ensure that the foundation, structural support, seams,
					 connections, and pressure controls (if applicable) are adequately designed and
					 that the tank system has sufficient structural strength, compatibility with the
					 waste or wastes to be stored or treated and corrosion protection to ensure that
					 it will not collapse, rupture, or fail. Obtain a written assessment, reviewed
					 and certified by a qualified professional engineer, following s.
					 NR
					 670.011(4), attesting that the tank
					 system has sufficient structural integrity and is acceptable for the storing
					 and treating of hazardous waste. This assessment shall include, at a minimum,
					 the following information:
(1) Design
				  standards for the construction of tank or tanks and any ancillary
				  equipment.
(2) Hazardous
				  characteristics of the waste or wastes to be handled.
(3) For new tank systems or components in
				  which the external shell of a metal tank or any external metal component of the
				  tank system will be in contact with the soil or with water, a determination by
				  a corrosion expert of:
(a) Factors affecting
				  the potential for corrosion, such as:
1. Soil
				  moisture content.
2. Soil
				  pH.
3. Soil sulfides
				  level.
4. Soil
				  resistivity.
5. Structure to soil
				  potential.
6. Existence of stray
				  electric current.
7. Existing
				  corrosion-protection measures (for example, coating, cathodic
				  protection).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0192 - What handling and inspection procedures shall I follow during installation of new tank systems?

Current through June 24, 2024
(1) Ensure that you
				  follow proper handling procedures to prevent damage to a new tank system during
				  installation. Before placing a new tank system or component in use, an
				  independent, qualified installation inspector or an independent, qualified,
				  registered professional engineer, either of whom is trained and experienced in
				  the proper installation of tank systems or components shall inspect the system
				  for the presence of any of the following items:
(a) Weld breaks.
(b) Punctures.
(c) Scrapes of protective coatings.
(d) Cracks.
(e) Corrosion.
(f) Other structural damage or inadequate
				  construction or installation.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0193 - What testing shall I do?

Current through June 24, 2024
Test all new tanks and ancillary equipment for tightness
					 before you place them in use. If you find a tank system that is not tight,
					 perform all repairs necessary to remedy the leak or leaks in the system before
					 you cover, enclose or place the tank system into use.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0194 - What installation requirements shall I follow?

Current through June 24, 2024
(1) Support and
				  protect ancillary equipment against physical damage and excessive stress due to
				  settlement, vibration, expansion or contraction.
(2) Provide the type and degree of corrosion
				  protection recommended by an independent corrosion expert, based on the
				  information provided under s.
				  NR
				  667.0191(3), to ensure the integrity
				  of the tank system during use of the tank system. An independent corrosion
				  expert shall supervise the installation of a corrosion protection system that
				  is field fabricated to ensure proper installation.
(3) Obtain and keep at the facility written
				  statements by those persons required to certify the design of the tank system
				  and to supervise the installation of the tank system as required in subs. (1)
				  and (2) and ss.
				  NR
				  667.0192 and 667.0193. The written statement shall
				  attest that the tank system was properly designed and installed and that you
				  made repairs under ss.
				  NR
				  667.0192 and 667.0193. These written statements shall
				  also include the certification statement as required in s.
				  NR
				  670.011(4).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0195 - What are the secondary containment requirements?

Current through June 24, 2024
To prevent the release of hazardous waste or hazardous
					 constituents to the environment, provide secondary containment that meets the
					 requirements of this section for all new and existing tank systems.
(1) Secondary containment systems shall be:
(a) Designed, installed and operated to
				  prevent any migration of wastes or accumulated liquid out of the system to the
				  soil, groundwater, or surface water at any time during the use of the tank
				  system.
(b) Capable of detecting
				  and collecting releases and accumulated liquids until the collected material is
				  removed.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0196 - What are the required devices for secondary containment and what are their design, operating and installation requirements?

Current through June 24, 2024
(1) Secondary
				  containment for tanks shall include one or more of the following:
(a) A liner (external to the tank).
(b) A double-walled tank.
(c) An equivalent device. Maintain
				  documentation of equivalency at the facility.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0197 - What are the requirements for ancillary equipment?

Current through June 24, 2024
Provide ancillary equipment with secondary containment (for
					 example, trench, jacketing double-walled piping) that meets the requirements of
					 s.
					 NR
					 667.0195, except for:
(1) Above ground piping (exclusive of
				  flanges, joints, valves, and other connections) that are visually inspected for
				  leaks on a daily basis.
(2) Welded
				  flanges, welded joints, and welded connections that are visually inspected for
				  leaks on a daily basis.
(3) Seal
				  less or magnetic coupling pumps and seal less valves, that are visually
				  inspected for leaks on a daily basis.
(4) Pressurized above ground piping systems
				  with automatic shut-off devices (for example, excess flow check valves, flow
				  metering shutdown devices, loss of pressure actuated shut-off devices) that are
				  visually inspected for leaks on a daily basis.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0198 - What are the general operating requirements for my tank systems?

Current through June 24, 2024
(1) You
				  may not place hazardous wastes or treatment reagents in a tank system if they
				  could cause the tank, its ancillary equipment or the containment system to
				  rupture, leak, corrode, or otherwise fail.
(2) Use appropriate controls and practices to
				  prevent spills and overflows from tank or containment systems. These include,
				  at a minimum:
(a) Spill prevention controls
				  (for example, check valves, dry disconnect couplings).
(b) Overfill prevention controls (for
				  example, level sensing devices, high level alarms, automatic feed cutoff, or
				  bypass to a standby tank).
(c)
				  Sufficient freeboard in uncovered tanks to prevent overtopping by wave or wind
				  action or by precipitation.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0199 - What inspection requirements shall I meet?

Current through June 24, 2024
Comply with the following requirements for scheduling,
					 conducting, and documenting inspections.
(1) Develop and follow a schedule and
				  procedure for inspecting overfill controls.
(2) Inspect at least once each operating day:
(a) Aboveground portions of the tank system
				  to detect corrosion or releases of waste.
(b) Data gathered from monitoring and leak
				  detection equipment (for example, pressure or temperature gauges, monitoring
				  wells) to ensure that the tank system is being operated according to its
				  design.
(c) The construction
				  materials and the area immediately surrounding the externally accessible
				  portion of the tank system, including the secondary containment system (for
				  example, dikes) to detect erosion or signs of releases of hazardous waste (for
				  example, wet spots, dead vegetation).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0200 - What shall I do in case of a leak or a spill?

Current through June 24, 2024
If there has been a leak or a spill from a tank system or
					 secondary containment system, or if either system is unfit for use, remove the
					 system from service immediately and satisfy the following requirements:
(1) Immediately stop the flow of hazardous
				  waste into the tank system or secondary containment system and inspect the
				  system to determine the cause of the release.
(2) Remove the waste from the tank system or
				  secondary containment system.
(a) If the
				  release was from the tank system, within 24 hours after detecting the leak,
				  remove as much of the waste as is necessary to prevent further release of
				  hazardous waste to the environment and to allow inspection and repair of the
				  tank system to be performed.
(b) If
				  the material released was to a secondary containment system, remove all
				  released materials within 24 hours or as quickly as possible to prevent harm to
				  human health and the environment.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0201 - What shall I do when I stop operating the tank system?

Current through June 24, 2024
When you close a tank system, remove or decontaminate all
					 waste residues, contaminated containment system components (for example,
					 liners), contaminated soils and structures and equipment contaminated with
					 waste, and manage them as hazardous waste, unless s. NR 661.0003(4) applies.
					 The closure plan, closure activities, cost estimates for closure, and financial
					 responsibility for tank systems shall meet all of the requirements specified in
					 subchs. G and H.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0202 - What special requirements shall I meet for ignitable or reactive wastes?

Current through June 24, 2024
(1) You
				  may not place ignitable or reactive waste in tank systems, unless:
(a) You treat, render, or mix the waste
				  before or immediately after placement in the tank system so that:
1. You comply with s.
				  NR
				  667.0017(2).
2. The resulting waste, mixture or dissolved
				  material no longer meets the definition of ignitable or reactive waste under s.
				  NR 661.0021 or 661.0023.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0203 - What special requirements shall I meet for incompatible wastes?

Current through June 24, 2024
(1) You may not
				  place incompatible wastes, or incompatible wastes and materials, in the same
				  tank system, unless you comply with s.
				  NR
				  667.0017(2).
(2) You may not place hazardous waste in a
				  tank system that has not been decontaminated and that previously held an
				  incompatible waste or material, unless you comply with s.
				  NR
				  667.0017(2).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter J - Tank Systems › Section NR 667.0204 - What air emission standards apply?

Current through June 24, 2024
Manage all hazardous waste placed in a tank following the
					 requirements of subchs. AA, BB, and CC of ch. NR 664. Under a standardized
					 license, the following control devices are permissible: Thermal vapor
					 incinerator, catalytic vapor incinerator, flame, boiler, process heater,
					 condenser, and carbon absorption unit.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1100 - Does this subchapter apply to me?

Current through June 24, 2024
This subchapter applies to you if you own or operate a
					 facility that treats or stores hazardous waste in containment buildings under a
					 subch. J of ch. NR 667 standardized license, except as provided in s.
					 NR
					 667.0001(2). Storage or treatment in
					 your containment building is not land disposal as defined in s.
					 NR
					 668.02 if your unit meets the requirements of ss.
					 NR
					 667.1101, 667.1102, and 667.1103.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1101 - What design and operating standards shall my containment building meet?

Current through June 24, 2024
Comply with the design and operating standards in this
					 section. The department shall consider standards established by professional
					 organizations generally recognized by the industry such as the American
					 Concrete Institute (ACI) and the American Society of Testing Materials (ASTM)
					 in judging the structural integrity requirements of this section.
(1) The containment building shall be
				  completely enclosed with a floor, walls, and a roof to prevent exposure to the
				  elements, (for example, precipitation, wind, run-on), and to assure containment
				  of managed wastes.
(2) The floor
				  and containment walls of the unit, including the secondary containment system,
				  if required under s.
				  NR
				  667.1103, shall be designed and constructed of manmade
				  materials of sufficient strength and thickness to:
(a) Support themselves, the waste contents,
				  and any personnel and heavy equipment that operates within the unit.
(b) Prevent failure due to:
1. Pressure gradients, settlement,
				  compression, or uplift.
2. Physical
				  contact with the hazardous wastes to which they are exposed.
3. Climatic conditions.
4. Stresses of daily operation, including the
				  movement of heavy equipment within the unit and contact of such equipment with
				  containment walls.
5. Collapse or
				  other failure.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1102 - What other requirements shall I meet to prevent releases?

Current through June 24, 2024
Use controls and practices to ensure containment of the
					 hazardous waste within the unit, and at a minimum:
(1) Maintain the primary barrier to be free
				  of significant cracks, gaps, corrosion, or other deterioration that could cause
				  hazardous waste to be released from the primary barrier.
(2) Maintain the level of the stored or
				  treated hazardous waste within the containment walls of the unit so that the
				  height of any containment wall is not exceeded.
(3) Take measures to prevent personnel or by
				  equipment used in handling the waste from tracking hazardous waste out of the
				  unit. Designate an area to decontaminate equipment and collect and properly
				  manage any rinsate.
(4) Take
				  measures to control fugitive dust emissions such that any openings (such as
				  doors, windows, vents, and cracks) exhibit no visible emissions (see 40 CFR
				  part 60, Appendix A, Method 22-Visual Determination of Fugitive Emissions from
				  Material Sources and Smoke Emissions from Flares). In addition, operate and
				  maintain all associated particulate collection devices (for example, fabric
				  filter, electrostatic precipitator) with sound air pollution control practices.
				  Effectively maintain this state of no visible emissions at all times during
				  routine operating and maintenance conditions, including when vehicles and
				  personnel are entering and exiting the unit.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1103 - What additional design and operating standards apply if liquids will be in my containment building?

Current through June 24, 2024
If your containment building will be used to manage
					 hazardous wastes containing free liquids or treated with free liquids, as
					 determined by the paint filter test, by a visual examination or by other
					 appropriate means, you shall include:
(1) A primary barrier designed and
				  constructed of materials to prevent the migration of hazardous constituents
				  into the barrier (for example, a geomembrane covered by a concrete wear
				  surface).
(2) A liquid collection
				  and removal system to minimize the accumulation of liquid on the primary
				  barrier of the containment building.
(a) The
				  primary barrier shall be sloped to drain liquids to the associated collection
				  system.
(b) Collect and remove
				  liquids and waste to minimize hydraulic head on the containment system at the
				  earliest practicable time.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1104 - How may I obtain a waiver from secondary containment requirements?

Current through June 24, 2024
Notwithstanding any other provision of this subchapter, the
					 department may waive requirements for secondary containment for a licensed
					 containment building where:
(1) You
				  demonstrate that the only free liquids in the unit are limited amounts of dust
				  suppression liquids required to meet occupational health and safety
				  requirements.
(2) Containment of
				  managed wastes and dust suppression liquids can be assured without a secondary
				  containment system.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1105 - What shall I do if my containment building contains areas both with and without secondary containment?

Current through June 24, 2024
For these containment buildings, you shall:
(1) Design and operate each area in
				  accordance with the requirements specified in ss.
				  NR
				  667.1101 to 667.1103.
(2) Take measures to prevent the release of
				  liquids or wet materials into areas without secondary containment.
(3) Maintain in the facility's operating log
				  a written description of the operating procedures used to maintain the
				  integrity of areas without secondary containment.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1106 - What shall I do if I detect a release?

Current through June 24, 2024
Throughout the active life of the containment building, if
					 you detect a condition that could lead to or has caused a release of hazardous
					 waste, repair the condition promptly, according to the following
					 procedures:
(1) Upon detection of a
				  condition that has led to a release of hazardous waste (for example, upon
				  detection of leakage from the primary barrier), you shall:
(a) Enter a record of the discovery in the
				  facility operating record.
(b)
				  Immediately remove the portion of the containment building affected by the
				  condition from service.
(c)
				  Determine what steps you are required to take to repair the containment
				  building, to remove any leakage from the secondary collection system and to
				  establish a schedule for accomplishing the cleanup and repairs.
(d) Within 7 days after the discovery of the
				  condition, notify the department of the condition and within 14 working days,
				  provide a written notice to the department with a description of the steps
				  taken to repair the containment building and the schedule for accomplishing the
				  work.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1107 - Can a containment building itself be considered secondary containment?

Current through June 24, 2024
Containment buildings may serve as secondary containment
					 systems for tanks placed within the building under certain conditions.
(1) A containment building may serve as an
				  external liner system for a tank, provided it meets the requirements of s.
				  NR
				  667.0196(1).
(2) The containment building shall also meet
				  the requirements of ss.
				  NR
				  667.0195(1) and 667.0195(2) (a) and
				  (b) to be considered an acceptable secondary containment system for a
				  tank.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 667 - Standards For Owners And Operators Of Hazardous Waste Facilities Operating Under A Standardized License › Subchapter DD - Containment Buildings › Section NR 667.1108 - What shall I do when I stop operating the containment building?

Current through June 24, 2024
When you close a containment building, remove or
					 decontaminate all waste residues, contaminated containment system components
					 (such as liners), contaminated subsoils and structures, and equipment
					 contaminated with waste and leachate, and manage them as hazardous waste unless
					 s. NR 661.0003(4) applies. The closure plan, closure activities, cost estimates
					 for closure, and financial responsibility for containment buildings shall meet
					 all of the requirements specified in subchs. G and H.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter A - General › Section NR 668.01 - Purpose, scope and applicability

Current through June 24, 2024
(1) This chapter
				  identifies hazardous wastes that are restricted from land disposal and defines
				  those limited circumstances under which an otherwise prohibited waste may
				  continue to be land disposed.
(2)
				  Except as specifically provided otherwise in this chapter or ch. NR 661, the
				  requirements of this chapter apply to persons who generate or transport
				  hazardous waste and owners and operators of hazardous waste treatment, storage
				  and disposal facilities.
(3)
				  Restricted wastes may continue to be land disposed if any of the following
				  conditions are met:
(a) The EPA administrator
				  has granted an extension to the effective date of a prohibition under
				  40 CFR
				  268.5 with respect to those wastes covered by
				  the extension.
(b) The EPA
				  administrator has granted an exemption from a prohibition pursuant to a
				  petition under
				  40
				  CFR 268.6, with respect to those wastes and
				  units covered by the petition.
(c)
				  Wastes that are hazardous only because they exhibit a hazardous characteristic,
				  and which are otherwise prohibited under this chapter or 40 CFR part 148 are
				  not prohibited if the wastes meet all of the following:
1. The wastes are disposed into a
				  nonhazardous or hazardous injection well as defined under
				  40 CFR
				  146.6(a).
2. The wastes at the point of injection do
				  not exhibit any prohibited characteristic of hazardous waste as identified in
				  subch. C of ch. NR 661.
(d) The wastes are hazardous only because
				  they exhibit a hazardous characteristic, unless the wastes are subject to a
				  specified method of treatment other than DEACT in s.
				  NR
				  668.40, or are D003 reactive cyanide and the wastes
				  meet subds. 1. or 2. or 3. and subd. 4.
1.
				  The wastes are managed in a treatment system which subsequently discharges to
				  waters of the state pursuant to a permit issued under ch. 283, Stats.
2. The wastes are treated for purposes of the
				  pretreatment requirements of ch. 283, Stats.
3. The wastes are managed in a zero discharge
				  system engaged in CWA-equivalent treatment as defined in s.
				  NR
				  668.37.
4.
				  The wastes no longer exhibit a prohibited characteristic at the point of land
				  disposal (i.e., placement in a surface
				  impoundment).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter A - General › Section NR 668.03 - Dilution prohibited as a substitute for treatment

Current through June 24, 2024
(1) Except as
				  provided in sub. (2), no generator, transporter, handler, or owner or operator
				  of a treatment, storage, or disposal facility may in any way dilute a
				  restricted waste or the residual from treatment of a restricted waste as a
				  substitute for adequate treatment to achieve compliance with subch. D, to
				  circumvent the effective date of a prohibition in subch. C, to otherwise avoid
				  a prohibition in subch. C, or to circumvent a land disposal prohibition imposed
				  by
				  42
				  USC 6924.
(2) Dilution of wastes that are hazardous
				  only because they exhibit a characteristic in treatment systems which include
				  land-based units which treat wastes subsequently discharged to a water of the
				  State pursuant to a permit issued under section s.
				  283.31,
				  Stats., or which treat wastes in a CWA-equivalent treatment system, or which
				  treat wastes for the purposes of pretreatment requirements under ss.
				  283.11
				  and
				  283.21,
				  Stats., is not impermissible dilution for purposes of this section unless a
				  method other than DEACT has been specified in s.
				  NR
				  668.40 as the treatment standard, or unless the waste
				  is a D003 reactive cyanide wastewater or nonwastewater.
(3) Combustion of the hazardous waste codes
				  listed in ch. NR 668 Appendix XI is prohibited, unless the waste, at the point
				  of generation, or after any bona fide treatment such as cyanide destruction
				  prior to combustion, complies with one or more of the criteria in pars. (a) to
				  (f), and is not otherwise specifically prohibited from combustion:
(a) The waste contains hazardous organic
				  constituents or cyanide at levels exceeding the constituent-specific treatment
				  standard found in s.
				  NR
				  668.48.
(b) The waste consists of organic,
				  debris-like materials, for example, wood, paper, plastic, or cloth,
				  contaminated with an inorganic metal-bearing hazardous waste.
(c) The waste, at point of generation, has
				  reasonable heating value, for example, greater than or equal to 5000 BTU per
				  pound.
(d) The waste is
				  co-generated with wastes for which combustion is a required method of
				  treatment.
(e) The waste is subject
				  to federal or Wisconsin requirements necessitating reduction of organics,
				  including biological agents.
(f)
				  The waste contains greater than one% total organic carbon (TOC).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter A - General › Section NR 668.06 - Petitions to allow land disposal of a waste prohibited under subch. C

Current through June 24, 2024
(1) Any person
				  seeking an exemption from a prohibition under subch. C of ch. NR 668 for the
				  disposal of a restricted hazardous waste in a particular unit or units shall
				  submit a petition under
				  40
				  CFR 268.6 to the EPA administrator
				  demonstrating, to a reasonable degree of certainty, that there will be no
				  migration of hazardous constituents from the disposal unit or injection zone
				  for as long as the wastes remain hazardous. The EPA administrator retains the
				  authority to implement all requirements of
				  40
				  CFR 268.6.
(2) Prior to the EPA administrator's
				  decision, the applicant shall comply with all restrictions on land disposal
				  under this chapter once the effective date for the waste has been
				  reached.
(3) The petition granted
				  by the EPA administrator does not relieve the petitioner of the petitioner's
				  responsibilities in the management of hazardous waste under chs. NR 660 to
				  670.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter B - Schedule for Land Disposal Prohibition and Establishment of Treatment Standards › Section NR 668.14 - Surface impoundment exemptions

Current through June 24, 2024
(1) This section
				  defines additional circumstances under which an otherwise prohibited waste may
				  continue to be placed in a surface impoundment.
(2) Wastes which are newly identified or
				  listed under
				  42 USC
				  6921 after November 8, 1984, and stored in a
				  surface impoundment that is newly subject to ch. 291, Stats., and chs. NR 660
				  to 673 as a result of the additional identification or listing, may continue to
				  be stored in the surface impoundment for 48 months after the promulgation of
				  the additional listing or characteristic, not withstanding that the waste is
				  otherwise prohibited from land disposal, if the surface impoundment is in
				  compliance with the requirements of subch. F of ch. NR 665 within 12 months
				  after promulgation of the new listing or characteristic.
(3) Wastes which are newly identified or
				  listed under
				  42 USC
				  6921 after November 8, 1984, and treated in a
				  surface impoundment that is newly subject to ch. 291, Stats., and chs. NR 660
				  to 673 as a result of the additional identification or listing, may continue to
				  be treated in that surface impoundment, not withstanding that the waste is
				  otherwise prohibited from land disposal, if the surface impoundment is in
				  compliance with subch. F of ch. NR 665 within 12 months after the promulgation
				  of the new listing or characteristic. In addition, if the surface impoundment
				  continues to treat hazardous waste after 48 months from promulgation of the
				  additional listing or characteristic, it must then be in compliance with s.
				  NR
				  668.04.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter C - Prohibitions on Land Disposal › Section NR 668.20 - Waste specific prohibitions - Dyes or pigments production wastes

Current through June 24, 2024
(1) Effective August
				  23, 2005, the waste specified in ch. NR 661 and 40 CFR part 261 as hazardous
				  waste number K181, and soil and debris contaminated with this waste,
				  radioactive wastes mixed with this waste and soil and debris contaminated with
				  radioactive wastes mixed with this waste are prohibited from land
				  disposal.
(2) The requirements of
				  sub. (1) do not apply if:
(a) The wastes meet
				  the applicable treatment standards specified in subch. D of ch. NR
				  668.
(b) The facility has been
				  granted an exemption from a prohibition pursuant to a petition under s.
				  NR
				  668.06, with respect to those wastes and units covered
				  by the petition.
(c) The wastes
				  meet the applicable treatment standards established pursuant to a petition
				  granted under s.
				  NR
				  668.44.
(d) Hazardous debris has met the treatment
				  standards in s.
				  NR
				  668.40 or the alternative treatment standards in s.
				  NR
				  668.45.
(e) The facility has been granted an
				  extension to the effective date of a prohibition pursuant to s.
				  NR
				  668.05, with respect to these wastes covered by the
				  extension.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter C - Prohibitions on Land Disposal › Section NR 668.30 - Waste specific prohibitions - wood preserving wastes

Current through June 24, 2024
(1) Effective August
				  11, 1997, the wastes specified in ch. NR 661 as EPA Hazardous Waste numbers
				  F032, F034, and F035 are prohibited from land disposal.
(2) Effective May 12, 1999, soil and debris
				  contaminated with F032, F034, F035; and radioactive wastes mixed with EPA
				  Hazardous waste numbers F032, F034, and F035 are prohibited from land
				  disposal.
(3) Between May 12, 1997
				  and May 12, 1999, soil and debris contaminated with F032, F034, F035; and
				  radioactive waste mixed with F032, F034, and F035 may be disposed in a landfill
				  or surface impoundment only if the unit is in compliance with the requirements
				  specified in
				  40 CFR
				  268.5(h)(2).
(4) The requirements of sub. (1) and (2) do
				  not apply if any of the following conditions are met:
(a) The wastes meet the applicable treatment
				  standards specified in subch. D.
(b) Persons have been granted an exemption
				  from a prohibition pursuant to a petition under
				  40
				  CFR 268.6, with respect to those wastes and
				  units covered by the petition.
(c)
				  The wastes meet the applicable alternate treatment standards established
				  pursuant to a petition granted under
				  40 CFR
				  268.44(a) to (g) or s.
				  NR 668.44(8) to
				  (13).
(d) Persons have been granted an extension to
				  the effective date of a prohibition pursuant to
				  40 CFR
				  268.5, with respect to those wastes covered
				  by the extension.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter C - Prohibitions on Land Disposal › Section NR 668.31 - Waste specific prohibitions - dioxin-containing wastes

Current through June 24, 2024
(1) Effective
				  November 8, 1988, the dioxin-containing wastes specified in s. NR 661.0031 as
				  EPA hazardous waste numbers F020, F02l, F022, F023, F026, F027, and F028, are
				  prohibited from land disposal, unless the F020 to F023 and F026 to F028
				  dioxin-containing waste is contaminated soil and debris resulting from a
				  response action taken under
				  42 USC 9604
				  or
				  9606 or a
				  corrective action taken under ch. 292, Stats.
(2) Effective November 8, 1990, the F020-F023
				  and F026-F028 dioxin-containing wastes listed in sub. (1) are prohibited from
				  land disposal.
(3) Between November
				  8, 1988, and November 8, 1990, wastes included in sub. (1) may be disposed in a
				  landfill or surface impoundment only if the unit complies with
				  40 CFR
				  268.5(h)(2) and all other
				  applicable requirements of chs.
				  NR 664 and 665.
(4) The requirements of subs. (1) and (2) do
				  not apply if any of the following conditions are met:
(a) The wastes meet the standards of subch.
				  D.
(b) Persons have been granted an
				  exemption from a prohibition pursuant to a petition under
				  40
				  CFR 268.6, with respect to those wastes and
				  units covered by the petition.
(c)
				  Persons have been granted an extension to the effective date of a prohibition
				  pursuant to
				  40 CFR
				  268.5, with respect to those wastes covered
				  by the extension.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter C - Prohibitions on Land Disposal › Section NR 668.32 - Waste specific prohibitions - soils exhibiting the toxicity characteristic for metals and containing PCBs

Current through June 24, 2024
(1) Effective
				  December 26, 2000, any volumes of soil exhibiting the toxicity characteristic
				  solely because of the presence of metals (D004 to D011) and containing PCBs,
				  are prohibited from land disposal.
(2) The requirements of sub. (1) do not apply
				  if any of the following conditions are met:
(a) The wastes contain halogenated organic
				  compounds in total concentration less than 1,000 mg/kg and meet the treatment
				  standards specified in subch. D for EPA hazardous waste numbers D004 to D011,
				  as applicable.
(b) The wastes
				  contain halogenated organic compounds in total concentration less than 1,000
				  mg/kg and meet the alternative treatment standards specified in s.
				  NR
				  668.49 for contaminated soil.
(c) Persons have been granted an exemption
				  from a prohibition pursuant to a petition under
				  40
				  CFR 268.6, with respect to those wastes and
				  units covered by the petition.
(d)
				  The wastes meet the applicable alternate treatment standards established
				  pursuant to a petition granted under
				  40 CFR
				  268.44(a) to (g) or s.
				  NR 668.44(8) to
				  (13).
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter C - Prohibitions on Land Disposal › Section NR 668.33 - Waste specific prohibitions - chlorinated aliphatic wastes

Current through June 24, 2024
(1) Effective May 8,
				  2001, the wastes specified in ch. NR 661 as EPA hazardous wastes numbers K174
				  and K175, soil and debris contaminated with these wastes, radioactive wastes
				  mixed with these wastes, and soil and debris contaminated with radioactive
				  wastes mixed with these wastes are prohibited from land disposal.
(2) The requirements of sub. (1) do not apply
				  if any of the following conditions are met:
(a) The wastes meet the applicable treatment
				  standards specified in subch. D.
(b) Persons have been granted an exemption
				  from a prohibition pursuant to a petition under
				  40
				  CFR 268.6, with respect to those wastes and
				  units covered by the petition.
(c)
				  The wastes meet the applicable alternate treatment standards established
				  pursuant to a petition granted under
				  40 CFR
				  268.44(a) to (g) or s.
				  NR 668.44(8) to
				  (13).
(d) Hazardous debris has met the treatment
				  standards in s.
				  NR
				  668.40 or the alternative treatment standards in s.
				  NR
				  668.45.
(e) Persons have been granted an extension to
				  the effective date of a prohibition pursuant to
				  40 CFR
				  268.5, with respect to these wastes covered
				  by the extension.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter C - Prohibitions on Land Disposal › Section NR 668.34 - Waste specific prohibitions - toxicity characteristic metal wastes

Current through June 24, 2024
(1) Effective
				  August 24, 1998, the newly identified wastes specified in ch. NR 661 as EPA
				  hazardous waste numbers D004 to D011 (i.e. wastes, soil, or debris identified
				  as hazardous by the toxic characteristic leaching procedure but not the
				  extraction procedure), and waste, soil, or debris from mineral processing
				  operations that is identified as hazardous by the specifications at ch. NR
				  661are prohibited from land disposal.
(2) Effective November 26, 1998, slag from
				  secondary lead smelting which exhibits the toxicity characteristic due to the
				  presence of one or more metals is prohibited from land disposal.
(3) Effective May 26, 2000, newly identified
				  characteristic wastes from elemental phosphorus processing; radioactive wastes
				  mixed with newly identified wastes specified in EPA hazardous waste numbers
				  D004 to D011 (i.e., wastes, soil, or debris identified as hazardous by the
				  toxic characteristic leaching procedure but not the extraction procedure); or
				  mixed with newly identified characteristic mineral processing wastes, soil, or
				  debris are prohibited from land disposal.
(4) Between May 26, 1998 and May 26, 2000,
				  newly identified characteristic wastes from elemental phosphorus processing,
				  radioactive waste mixed with D004 to D011 wastes that are newly identified
				  (i.e., wastes, soil, or debris identified as hazardous by the toxic
				  characteristic leaching procedure but not the extraction procedure), or mixed
				  with newly identified characteristic mineral processing wastes, soil, or debris
				  may be disposed in a landfill or surface impoundment only if the unit is in
				  compliance with
				  40 CFR
				  268.5(h).
(5) The requirements of subs. (1) and (2) do
				  not apply if:
(a) The wastes meet the
				  applicable treatment standards specified in subch. D.
(b) EPA has granted an exemption from a
				  prohibition pursuant to a petition under
				  40
				  CFR 268.6, with respect to those wastes and
				  units covered by the petition.
(c)
				  The wastes meet the applicable alternate treatment standards established
				  pursuant to a petition granted under
				  40 CFR
				  268.44.
(d) EPA has granted an extension to the
				  effective date of a prohibition pursuant to
				  40 CFR
				  268.5, with respect to these wastes covered
				  by the extension.
Wisconsin Administrative Code › Department of Natural Resources › NR 600-699 - Environmental Protection - Hazardous Waste Management › Chapter NR 668 - Hazardous Waste Land Disposal Restrictions › Subchapter C - Prohibitions on Land Disposal › Section NR 668.35 - Waste specific prohibitions - petroleum refining wastes

Current through June 24, 2024
(1) Effective
				  February 8, 1999, wastes specified in ch. NR 661 as EPA hazardous waste numbers
				  K169, K170, K171, and K172, soils and debris contaminated with these wastes,
				  radioactive wastes mixed with these wastes, and soils and debris contaminated
				  with these radioactive mixed wastes are prohibited from land
				  disposal.
(2) The requirements of
				  sub. (1) do not apply if any of the following conditions are met:
(a) The wastes meet the applicable treatment
				  standards specified in subch. D.
(b) EPA has granted an exemption from a
				  prohibition pursuant to a petition under
				  40
				  CFR 268.6, with respect to those wastes and
				  units covered by the petition.
(c)
				  The wastes meet the applicable treatment standards established pursuant to a
				  petition granted under
				  40 CFR
				  268.44(a) to (g) or s.
				  NR 668.44(8) to
				  (13).
(d) Hazardous debris have met treatment
				  standards in s.
				  NR
				  668.40 or the alternative treatment standards in s.
				  NR
				  668.45.
(e) EPA has granted an extension to the
				  effective date of a prohibition pursuant to
				  40 CFR
				  268.5, with respect to these wastes covered
				  by the extension.