Wisconsin Administrative Code › Department of Natural Resources › NR 400-499 - Environmental Protection - Air Pollution Control › Chapter NR 462 - National emission standards for hazardous air pollutants for industrial, commercial and institutional boilers and process heaters › Section NR 462.04 - General compliance requirements

Current through June 24, 2024
(1) WHAT ARE MY
				GENERAL REQUIREMENTS FOR COMPLYING WITH THIS CHAPTER?
(a) You shall be in compliance with the
				emission limits, including operating limits, and the work practice standards in
				this chapter at all times, except during periods of startup, shutdown and
				malfunction.
(b) You shall always
				operate and maintain your affected source, including air pollution control and
				monitoring equipment, according to the provisions in s.
				NR
				460.05(4) (a) 1.
(c) You may demonstrate compliance with any
				applicable emission limit using fuel analysis if the emission rate calculated
				according to s.
				NR
				462.05(7) (d) is less than the
				applicable emission limit. Otherwise, you shall demonstrate compliance using
				performance testing.
(d) If you
				demonstrate compliance with any applicable emission limit through performance
				testing, you shall develop a site-specific monitoring plan according to the
				requirements in subds. 1. to 4. This requirement also applies to you if you
				petition the EPA administrator for alternative monitoring parameters under
				40 CFR
				63.8(f).
Note: The authority to approve alternative monitoring
				  parameters is retained by the administrator and is not delegated to the
				  department.
1. For each continuous
				monitoring system (CMS) required in this subsection, you shall develop and
				submit to the department for approval a site-specific monitoring plan that
				addresses subd. 1. a. to c. You shall submit this site-specific monitoring plan
				at least 60 days before your initial performance evaluation of your CMS. The
				plan shall include all of the following:
a.
				Installation of the CMS sampling probe or other interface at a measurement
				location relative to each affected process unit such that the measurement is
				representative of control of the exhaust emissions, such as on or downstream of
				the last control device.
b.
				Performance and equipment specifications for the sample interface, the
				pollutant concentration or parametric signal analyzer and the data collection
				and reduction systems.
c.
				Performance evaluation procedures and acceptance criteria, such as
				calibrations.
2. In your
				site-specific monitoring plan you shall also address subd. 2. a. to c.
a. Ongoing operation and maintenance
				procedures in accordance with the general requirements of s.
				NR 460.07(3) (a), (c) and
				(d) 2.
b. Ongoing data quality assurance procedures
				in accordance with the general requirements of s.
				NR
				460.07(4).
c. Ongoing recordkeeping and reporting
				procedures in accordance with the general requirements of s.
				NR
				460.09(3) (a) and (5) (a) and (b)
				1.
3. You shall conduct a performance evaluation
				of each CMS in accordance with your site-specific monitoring plan.
4. You shall operate and maintain the CMS in
				continuous operation according to the site-specific monitoring plan.
(e) If you have an applicable
				emission limit or work practice standard, you shall develop and implement a
				written startup, shutdown and malfunction plan (SSMP) according to the
				provisions in s.
				NR
				460.05(4) (c).