reglab/statecodes huggingface dataset:
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.63 - Jump harness

Current through June 24, 2024
(1) GENERAL. A jump harness shall be either a
					 full body harness, a sit harness with shoulder straps, or an ankle
					 harness.
(2) JUMP HARNESSES.
(a) All harnesses used in bungee jumping
					 shall be:
1. Full-body-designed either as a
					 full body harness or a waist harness worn in conjunction with a chest harness;
					 or
2. Ankle-designed either as an
					 ankle harness or an ankle strapping that is tied off to secure the jumper to
					 the bungee cord end connection. The ankle harness or strapping shall provide
					 evidence of redundancy. A link to a waist harness or "swami belt" shall be
					 required. A harness shall not cause bruising.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.64 - Ropes

Current through June 24, 2024
All ropes for holding or lowering the jumper shall have a
						minimum breaking strength of at least 6,000 pounds.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.65 - Hardware and equipment

Current through June 24, 2024
(1) GENERAL. All hardware and equipment used
					 for the purpose of bungee jumping shall be approved for that purpose by the
					 original manufacturer.
(2)
					 CARABINERS. Carabiners shall be the screw gate type, manufactured of hardened
					 steel, with a minimum breaking strength of at least 6,000 pounds.
(3) PULLEYS AND SHACKLES. Pulleys and
					 shackles shall be manufactured of hardened steel and shall have a minimum
					 breaking strength of at least 6,000 pounds. All pulleys shall be compatible
					 with the rope size.
(4) WEBBING.
					 Webbing shall be flat or tubular mountaineering webbing or equivalent with a
					 minimum breaking strength of at least 6,000 pounds. If military specification
					 bungee cords are used, all webbing shall have redundant connections.
(5) ANCHORS.
(a) There shall be 2 anchors that attach the
					 bungee cord to the structure. Each shall have a minimum breaking strength of at
					 least 8,000 pounds or shall be designed with a factor of safety of 5, whichever
					 is greater. There shall be a carabiner that attaches each anchor to the bungee
					 cord end. The 2 carabiners shall not be connected to each other.
(b) Where wire rope is used, it shall have
					 swaged ends with a thimble eye or be continuous. Other connection systems are
					 acceptable if they meet the strength specifications in par. (a). Wire clips are
					 not acceptable.
(c) All materials
					 used for anchoring systems shall be manufactured by an organization approved to
					 manufacture similar devices.
(d)
					 Daily inspections of the anchors shall be conducted by the jump master, and any
					 equipment showing signs of excessive wear shall be removed from service
					 immediately.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.66 - Testing and inspection

Current through June 24, 2024
(1) GENERAL. All jump rigging, harnesses,
					 lowering system and safety gear shall be regularly inspected and tested as set
					 forth in the operating manual. Inspections, findings and corrective action
					 shall be recorded in the site log.
(2) HARDWARE. Hardware subject to abnormal
					 loadings, impacts against hard surfaces or having surface damage shall be
					 replaced immediately.
(3) ROPES AND
					 WEBBING. All ropes, webbing and bindings shall be inspected visually and by
					 feel for signs of wear, fraying, or damage by corrosive substances in
					 accordance with the site operating manual.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.67 - Replacement equipment

Current through June 24, 2024
(1) AVAILABLE EQUIPMENT. Replacement
					 equipment available at the site shall include bungee cords and binding, all
					 ropes, rigging hardware, ankle strapping for jumpers, jump harnesses, safety
					 harnesses, and life lines and clips.
(2) WHEN TO REPLACE. Items of equipment,
					 rigging or personal protective equipment found to be defective shall be
					 replaced immediately.
(3) CEASE
					 JUMPING. Jumping shall cease immediately when a defective item cannot be
					 replaced.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.68 - Identification of rigging, bungee cords and safety equipment

Current through June 24, 2024
(1) PERMANENT
					 NUMBER. All rigging, bungee cords and safety equipment shall have a permanent
					 identification number.
(2) FORM.
					 The form of identification shall not affect the performance of the
					 material.
(3) VISIBILITY. The
					 identification shall be clearly visible to the operators during daily
					 operations.
(4) RECORDING. The
					 identification shall be recorded in the site operating manual.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.69 - Landing and recovery areas

Current through June 24, 2024
(1) JUMPS OVER
					 LAND. The following requirements apply where the landing area is over land:
(a) A net or air bag shall be used. The net
					 or air bag shall be designed to provide adequate coverage of the jump zone, and
					 its specifications shall be included in the site operating manual. The net or
					 air bag shall be rated for the maximum free fall height possible from the
					 platform during operation.
(b) The
					 net or air bag shall be in position before jumper preparation commences on the
					 platform.
(c) Air bags shall be
					 equipped with an audible alarm in case of loss of air bag pressure.
(d) Upon completion of a jump, the jumper
					 shall be lowered onto the net, air bag or landing pad.
(e) The landing area shall be free of
					 spectators at all times.
(f) The
					 landing area shall be free of any equipment or staff when a jumper is being
					 prepared on the jump platform and until the bungee cord is at its static
					 extended state.
(g) A place for the
					 jumper to sit and recover shall be provided close to, but outside, the landing
					 area.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.70 - Site requirements

Current through June 24, 2024
(1) STORAGE. Adequate storage shall be
					 provided to protect equipment from physical, chemical and ultra-violet ray
					 damage. The storage area shall be secured against unauthorized entry.
(2) COMMUNICATIONS. There shall be a public
					 address system in operation during all hours of business. Voice, telephone,
					 radio or other communications shall be maintained between all operations
					 personnel involved with the actual jump.
(3) FENCE. The site shall be enclosed by a
					 fence at least 42 inches in height. The fence shall be designed and constructed
					 to prevent people, animals and objects from entering the site.
(4) STAFF IDENTIFICATION. All staff shall be
					 identified so that they can be readily recognized by the public.
(5) STAFF BRIEFING. Staff shall be briefed
					 for each day's operation, including the assignment of the designated jump
					 master where more than one jump master is on site.
(6) EMERGENCY SERVICES. There shall be a
					 means of communication to local emergency services within 200 feet of the
					 operation.
(7) JUMP CONTROL. Owners
					 of bungee jumping facilities shall allow jumps only under the direct control of
					 a jump master.
(8) JUMPER WEIGHT.
					 The weight of the jumper shall be checked by 2 independent scales at the jump
					 site. Scales shall be calibrated at least 3 times each year, or when in doubt
					 as to accuracy. Adjustments for the weight of each jumper shall be made by the
					 jump master's selection of bungee cord and the length of webbing or rope
					 attached to the bungee cord.
(9)
					 JUMPER INSTRUCTIONS AND RESTRICTIONS. A clearly visible sign shall be posted at
					 the site that lists instructions to jumpers and all medical, age and weight
					 restrictions for jumpers.
(10)
					 JUMPER REGISTRATION. Jumpers shall register with the registration clerk before
					 jumping. Registration information shall include the jumper's name, address,
					 city, county, state, zip code, telephone number, medical factors, age and
					 weight.
(11) JUMPER PREPARATION.
					 The area where the jumper is prepared for jumping shall be separate from the
					 jump zone. Jumper preparation shall include information to the jumper on
					 jumping, landing, lowering, and recovery procedures; completing harness or
					 binding activities; final inspection by jump master; return of the jumper to
					 the public area; and retrieval of the bungee cord to the platform or storage
					 location.
(12) SAFE OPERATION. The
					 jump master shall stop the jumping operation when the wind speed or other
					 conditions affect safe operation of the jump platform or the recovery
					 area.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.71 - Safety and loss control management

Current through June 24, 2024
(1) COORDINATOR. A
					 jump master shall be designated safety, health and loss control
					 coordinator.
(2) KNOWLEDGE OF
					 REGULATIONS. The jump master shall be thoroughly familiar with the bungee
					 jumping regulations in this subchapter.
(3) EMERGENCY PLAN. A comprehensive written
					 emergency plan shall be developed, practiced, maintained and posted at the site
					 entrance.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.72 - Staff and duties

Current through June 24, 2024
(1) MINIMUM AGE. The minimum age for
					 employment at a bungee jumping site shall be 18 years.
(2) JUMP MASTER QUALIFICATIONS.
(a) To qualify as a jump master for a bungee
					 jumping site, a person shall have completed a minimum of 25 jumps and 30 hours
					 of training, including 10 hours of site operating manual training, 10 hours of
					 on-the-job experience and 4 hours of procedural review and additional
					 education.
(b) A jump master shall
					 have a knowledge of rescue procedures and ground operator procedures, as well
					 as emergency procedures for an accident or illness, for unruly or hysterical
					 jumpers, and for any failure before or after the bungee jump.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.73 - Site operating manual

Current through June 24, 2024
(1) CONTENTS OF MANUAL. The site operating
					 manual shall describe the system of operation to be used and shall include, but
					 not be limited to, a complete description of the following:
(a) A site plan containing a plan view of the
					 site with all components in place, with fencing and the jump zone
					 defined.
(b) A site plan containing
					 a profile of the jump zone.
(c) All
					 components in the rigging system which shall include a manufacturer's
					 specification or laboratory test certificate of each component.
(d) All operator, jumper and passenger safety
					 equipment.
(e) All rescue
					 equipment.
(f) Jobs of all
					 personnel employed on the site with the minimum qualifications of each person
					 and complete detail of work periods required.
(g) Personnel selection criteria and the
					 process for verifying the qualifications of job applicants.
(h) Rules concerning the health and safety of
					 staff, patrons and the public.
(i)
					 The owner's requirements regarding personnel use of drugs or alcohol and
					 testing procedures which may be required.
(j) The training program of
					 personnel.
(k) Standard operating
					 procedures.
(L) Emergency
					 procedures to be taken in all possible scenarios which may occur.
(m) The rescue training and qualifications
					 required for all staff where the site includes moving water or swift
					 water.
(n) The reporting to
					 authorities of incidents resulting in injury.
(o) The reporting procedures for any
					 incidents which do not result in injury but which were not in accord with
					 normal operating procedures.
(p)
					 Equipment inspection procedures and the logging of those inspections.
(q) Maintenance procedures.
(r) Redundancy criteria and procedures for
					 all equipment.
(s) Purchasing
					 procedures.
(t) The method of
					 identifying or labeling all equipment.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 334 - Amusement Rides › Subchapter VIII - Bungee Jumping › Section SPS 334.74 - Emergency provisions and procedures

Current through June 24, 2024
(1) EMERGENCY PLAN.
					 Each site shall have an emergency plan.
(2) FIRST AID KIT. A first aid kit and
					 blankets shall be maintained on site.
(3) FIRST AID CERTIFICATION. All jump masters
					 shall have current first aid and CPR certification and complete an annual
					 refresher course.
(4) LIFE SAVING
					 CERTIFICATION. At sites where the jump or recovery is over water, the jump
					 master and all landing and recovery staff shall be holders of a current life
					 saving certificate and shall have passed the equivalent for in-water rescue of
					 injured persons.
(5) EMERGENCY
					 LIGHTING. Emergency lighting shall be provided at all jump sites that operate
					 one-half hour prior to sunset until one-half hour after sunrise. The emergency
					 lighting system shall illuminate the jump platform, the jump zone and the
					 landing area. The emergency lighting system shall have its own power
					 source.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 335 - Infectious agents › Section SPS 335.001 - Purpose

Current through June 24, 2024
The purpose of this chapter is to identify, by
					 administrative rules, those infectious agents relevant to the Employees' Right
					 to Know Law, ss.
					 101.58
					 to
					 101.599,
					 Stats.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 335 - Infectious agents › Section SPS 335.01 - Definitions

Current through June 24, 2024
In this chapter:
(1) "Department" means the department of
				  safety and professional services.
(2) "Infectious agents" has the meaning set
				  forth in s.
				  101.58(2)
				  (f), Stats.
The statutory definition for infectious agents reads:
						"Infectious agent" means a bacterial, mycoplasmal, fungal, parasitic or viral
						agent identified by the department by rule as causing illness in humans or
						human fetuses or both, which is introduced by an employer to be used, studied
						or produced in the workplace. "Infectious agent" does not include such an agent
						in or on the body of a person who is present in the workplace for diagnosis or
						treatment.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter I - Purpose, Scope and Application › Section SPS 340.11 - Scope and application

Current through June 24, 2024
(1) GENERAL.
(a) This chapter applies to the design,
					 construction, installation, inspection, operation, testing, maintenance, repair
					 and alteration of gas systems for fueling purposes, such as for heating
					 appliances or engines.
(b) All of
					 the following gases are regulated by this chapter:
1. Liquefied petroleum gas.
2. Liquefied natural gas.
3. Compressed natural gas.
4. Gaseous hydrogen.
5. Liquefied hydrogen.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter I - Purpose, Scope and Application › Section SPS 340.12 - Local requirements

Current through June 24, 2024
This chapter does not limit the power of cities, villages
						and towns to make or enforce additional or more stringent requirements,
						provided the requirements do not conflict with this chapter, any other rule of
						the department, or law.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter II - Definitions › Section SPS 340.20 - Definitions

Current through June 24, 2024
(1)"Alteration" means a change in a gas
					 system that involves an extension or addition for, or involves the arrangement,
					 type or purpose of, the existing installation or component.
(2)"Approved" means acceptable to the
					 department.
Note:
The Department will ordinarily accept
						items approved by a nationally recognized testing laboratory.
(3)"Certified inspector" means an individual
					 who holds a valid credential issued by the department as a certified
					 boiler-pressure vessel inspector.
(4)"Container" means a vessel such as a tank,
					 cylinder, bottle or drum used for storing of a gas or liquid.
(5)"Department" means the department of
					 safety and professional services.
(6)"First class city" means a city of the
					 first class, as established under s.
					 62.05, Stats.
Note:
As of September 1, 2011, only the
						City of Milwaukee had become a first class city.
(7)"Gas systems" means assemblies for
					 storing, conveying, or dispensing the gases regulated by this
					 chapter.
(8)"Liquefied petroleum
					 gas" has the meaning given in s.
					 101.16(1)
					 (b), Stats.
Note:
Section
						101.16(1)
						(b) of the Statutes reads as follows: "
						`Liquefied petroleum gas' means any material which is composed predominantly
						of, or any mixtures of, any of the following hydrocarbons including their
						isomers:
1. Propane.
2. Propylene.
3. Butane.
4. Butylene."
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.31 - Certificate of installation

Current through June 24, 2024
(1)Every person,
					 firm, association or corporation installing a gas system shall complete a
					 certificate of installation form, SBD-9656-E. The form shall be completed at
					 the time of installation and shall be provided to the owner of the system. A
					 copy of the form shall be kept at the installation site and available for
					 review by an authorized representative of the department or the first class
					 city. A copy of the form shall be submitted to the local fire department within
					 10 business days of the installation, except as provided in sub. (2).
(2)Submitting form SBD-9656-E to the fire
					 department is not required for liquefied petroleum gas installations that are
					 exempt from plan approval under s.
					 SPS
					 340.30.
The Department forms required in this chapter are
						  available for a nominal fee at telephone 800-DOC-SALE or 411
						  (Telecommunications Relay) or at docsales@doa.state.wi.us, or at no charge at
						  the Department's Web site at
www.dsps.wi.gov
through links to Division of
						  Industry Services forms.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.32 - Revisions, alterations and piping upgrades

Current through June 24, 2024
(1) PLAN REVISIONS.
(a) The changes specified in par. (b) to
					 approved plans for gas systems, that are made before commencement of system
					 operation, shall be submitted for review and approval as a revision. Revised
					 plans submitted to the department for review shall include the department plan
					 number for the original plans.
(b)
					 Plans shall be submitted to the department or a first class city for review and
					 approval of any changes in tank location or capacity, piping arrangement or
					 material, safety setback clearance, point of transfer location, design of
					 indoor fueling operation, and gas detection or monitoring equipment
					 location.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.33 - Revocation of approval

Current through June 24, 2024
The department or the first class city may revoke any
						approval issued under this chapter for any false statements or
						misrepresentation of facts upon which the approval was based.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.34 - Enforcement and inspections

Current through June 24, 2024
(1) ENFORCEMENT.
(a) This chapter shall be enforced by the
					 department and by all local officials or bodies having jurisdiction to approve
					 plans or specifications or issue permits for construction, alterations or
					 installations within the scope of this chapter.
Note:
Local fire departments have statutory
						authority to investigate and eliminate any fire hazards relating to the gas
						systems regulated by this chapter. Under section
						101.14(2)
						(a) of the Statutes, "The chief of the fire
						department in every city, village or town, except cities of the 1st class, is
						constituted a deputy of the department." Under section
						101.14(1)
						(b) of the Statutes, "The [department]
						secretary and any deputy may at all reasonable hours enter into and upon all
						buildings, premises and public thoroughfares excepting only the interior of
						private dwellings, for the purpose of ascertaining and causing to be corrected
						any condition liable to cause fire, or any violation of any law or order
						relating to the fire hazard or to the prevention of fire."
(b) Where a first class city administers and
					 enforces this chapter, a regulated item or activity shall be directed to or
					 addressed by the first class city before requesting input from the department.
Note:
Under section
						SPS
						340.11(7), the Department reserves
						the right to interpret the requirements in this chapter and in all codes and
						standards adopted herein.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.35 - Fees

Current through June 24, 2024
Fees shall be submitted to the department as specified in
						ch. SPS 302. Fees shall be submitted at the time the application for approval
						is submitted. No plan examinations, approvals or inspections may be made until
						the fees are received.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.36 - Appeals

Current through June 24, 2024
As specified in s.
						227.12,
						Stats., any municipality, corporation or any 5 or more persons having an
						interest in an administrative rule may appeal to the department requesting the
						adoption, amendment or repeal of the rule.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.37 - Petition for variance

Current through June 24, 2024
The department shall consider and may grant a variance to
						a provision of this chapter in accordance with ch. SPS 303. The petition for
						variance shall include a position statement from the fire department having
						jurisdiction, and from any other local governmental unit having jurisdiction to
						enforce this chapter under s.
						SPS
						340.34.
Chapter
						  SPS
						  303 requires the submittal of a petition for variance
						  form (SBD-9890-X) and a fee, and that an equivalency is established in the
						  petition for variance that meets the intent of the rule being petitioned.
						  Chapter
						  SPS
						  303 also requires the Department to process regular
						  petitions within 30 business days and priority petitions within 10 business
						  days.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.38 - Penalties

Current through June 24, 2024
Penalties for violations of this chapter shall be
						assessed in accordance with ss.
						101.02(12)
						and (13) and
						101.16(5),
						Stats.
Section
						  101.02(13)
						  (a) of the Statutes provides that penalties
						  will be assessed against any employer, employee, owner or other person who
						  fails or refuses to perform any duty lawfully enjoined, within the time
						  prescribed by the Department, for which no penalty has been specifically
						  provided, or who fails, neglects or refuses to comply with any lawful order
						  made by the Department, or any judgment or decree made by any court in
						  connection with sections
						  101.01 to
						  101.599
						  of the Statutes. For each such violation, failure or refusal, such employee,
						  owner or other person must forfeit and pay into the state treasury a sum not
						  less than $10 nor more than $100 for each violation.
Section
						  101.02(12)
						  of the Statutes provides that every day during which any person, persons,
						  corporation or any officer, agent or employee thereof, fails to observe and
						  comply with an order of the Department will constitute a separate and distinct
						  violation of such order.
Section
						  101.16(5)
						  of the Statutes provides that any person, firm, association or corporation who
						  violates s.
						  101.16,
						  Stats., or any standard, rule or regulation adopted by the Department under
						  that section, or who issues a false installation statement under section
						  101.16(4)
						  of the Statutes will be fined not less than $10 nor more than $2000, or
						  imprisoned not less than 30 days nor more than 6 months.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter III - Administration and Enforcement › Section SPS 340.39 - Reporting of accidents

Current through June 24, 2024
If a gas system component fails and causes injuries to
						any person that require more than first aid treatment, the owner or user shall
						report in writing on form SBD-10789-E the facts involved to the department
						within the following 24 hours. The owner or user may not remove or disturb the
						gas system equipment or any of its components nor permit any such removal or
						disturbance prior to receiving authorization from the department or first class
						city, except for the purpose of saving human life or preventing further
						property damage. This section applies to those gas systems that are required to
						obtain department plan approval under s.
						SPS
						340.30.
The address for reporting accidents to the Department
						  is the Division of Industry Services, Gas Systems Program, P.O. Box 7302,
						  Madison, WI 53707-7302; and the fax number is 608-283-7420.
The Department can be contacted at 262/548-8617 during
						  normal business hours. The State Division of Emergency Management can be
						  contacted at 800/943-0003 during non-business hours.
The Department forms required in this chapter are
						  available for a nominal fee at telephone 800-DOC-SALE or 411
						  (Telecommunications Relay) or at docsales@doa.state.wi.us, or at no charge at
						  the Department's Web site at
www.dsps.wi.gov
through links to Division of
						  Industry Services forms.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IV - Standards and General Requirements › Section SPS 340.40 - Adoption of standards by reference

Current through June 24, 2024
(1) PRIMARY
					 STANDARDS. The following standards are hereby incorporated by reference into
					 this chapter, subject to the modifications specified in this chapter:
(a) American Petroleum Institute, 1220 L
					 Street Northwest, Washington D.C. 20005:
Design and Construction of
					 Liquefied Petroleum Gas Installations
, API standard 2510, 8th edition,
					 May 2001.
(b) National Fire
					 Protection Association, 1 Batterymarch Park, Quincy, MA 02169-7471, telephone
					 800-344-3555,
www.nfpa.org:
1. Code for Motor Fuel Dispensing Facilities
					 and Repair Garages, NFPA® 30A, 2008 edition.
2. Vehicular Gaseous Fuel Systems Code,
					 NFPA® 52, 2010 edition.
3.
					 National Fuel Gas Code, ANSI Z223.1-2009/NFPA® 54-2009.
4. Liquefied Petroleum Gas Code, NFPA®
					 58, 2011 edition.
5. Production,
					 Storage, and Handling of Liquefied Natural Gas (LNG), NFPA®59A, 2009
					 edition.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IV - Standards and General Requirements › Section SPS 340.41 - Secondhand pressure vessels

Current through June 24, 2024
The use of secondhand pressure vessels, having a water
						capacity in excess of 2,000 gallons, is prohibited, unless all of the following
						conditions are satisfied:
(1)MANUFACTURER'S DATA REPORT. The original
					 manufacturer's data report is available. If the original manufacturer's data
					 report is unavailable, documentation acceptable to the department or first
					 class city shall be submitted.
(2)ALTERATIONS AND REPAIRS BY WELDING. All
					 alterations and repairs by welding are documented in writing to verify
					 compliance with ch. SPS 341.
(3)INSPECTIONS. An inspection of the
					 secondhand pressure vessel has been performed at its new location by a
					 certified inspector.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IV - Standards and General Requirements › Section SPS 340.42 - Vehicle-fuel dispensing systems

Current through June 24, 2024
All vehicle-fuel dispensing systems shall comply with
						whichever of the following are applicable:
(1)NFPA 30A section 4.3.7.2 and chapter 12,
					 if Class I or Class II liquids are dispensed as motor fuels along with a fuel
					 gas regulated by this chapter.
(2)NFPA 52, if liquefied natural gas,
					 compressed natural gas, gaseous hydrogen or liquefied hydrogen are dispensed in
					 the absence of Class I and Class II liquids.
(3)NFPA 58, if liquefied petroleum gas is
					 dispensed in the absence of Class I and Class II liquids.
Class I and II liquids are classified in NFPA 30A as
						  having a flash point below 140°F.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IV - Standards and General Requirements › Section SPS 340.43 - Dispensing to vehicle fuel tanks, recreational equipment and containers

Current through June 24, 2024
(1) PUBLIC
					 SELF-SERVICE PROHIBITED. Self-service dispensing by the general public of any
					 gas regulated by this chapter is prohibited, except trained members of the
					 general public may fuel compressed natural gas motor vehicles through a fueling
					 connection that complies with ANSI NGV1-2006.
Note:
The ANSI NGV1-2006 standard contains
						construction and performance criteria for compressed natural gas vehicle
						fueling connection devices consisting of (1) a receptacle (mounted on the
						vehicle), (2) a nozzle (mounted on fueling dispenser), and/or (3) a three-way
						valve (internal or external to the nozzle), having design pressures of 2400,
						3000 or 3600 psig. Nozzle design will not permit gas flow until positively
						engaged to the receptacle and will not release the receptacle until gas flow
						has ceased and captured gas is safely vented. Intermating components are
						standardized. Nozzle and receptacle design prevent the fueling of a vehicle
						with lower service pressure by a dispenser with a higher service
						pressure.
(2)GENERAL. No
					 person, except for the following, may dispense any gas regulated by this
					 chapter unless the dispensing is through approved dispensing devices:
(a) A trained and authorized employee of a
					 bulk storage plant, container charging plant or service station.
(b) A trained and authorized employee of an
					 entity operating a commercial fleet of motor vehicles.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IV - Standards and General Requirements › Section SPS 340.44 - U.S. department of transportation vessels

Current through June 24, 2024
Pressure vessels bearing the stamping of the United
						States department of transportation are not permitted as permanent storage
						containers, except they may be used either as cylinders for storage of
						compressed natural gas or gaseous hydrogen, or as replaceable service
						cylinders.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IV - Standards and General Requirements › Section SPS 340.45 - Welded repairs and alterations for containers and pressure vessels

Current through June 24, 2024
Any repair or alteration that includes any welding on
						ASME containers or pressure vessels or their fittings, settings or
						appurtenances shall conform to the applicable standards adopted in this chapter
						and to the requirements for welded repairs and alterations in ch. SPS
						341.
See subchapter VI of chapter
						  SPS
						  341 for the referenced requirements.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter V - Liquefied Petroleum Gas Systems › Section SPS 340.50 - Scope

Current through June 24, 2024
(1)
					 APPLICATION. This subchapter applies to the storage, handling and use of
					 liquefied petroleum gas, and to the transportation of liquefied petroleum gas
					 by tank truck or tank trailer.
(2)EXEMPTIONS. This subchapter does not apply
					 to any of the following:
(a) Liquefied
					 petroleum gas systems owned and operated by utilities when the systems are part
					 of the distribution facilities for the utility and are subject to the
					 provisions of ch. PSC 135.
(b) The
					 transportation of liquefied petroleum gas by railroads engaged in interstate
					 commerce or to equipment used by them.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter V - Liquefied Petroleum Gas Systems › Section SPS 340.51 - Design, construction, installation, operation and maintenance of liquefied petroleum gas systems

Current through June 24, 2024
Liquefied petroleum gas systems shall be designed,
						constructed, installed, operated and maintained as specified in the following
						standards, except as otherwise provided in this chapter:
(1)API 2510.
(2)ANSI Z223.1/NFPA 54 and NFPA 58.
Section
						  SPS
						  340.42 contains requirements for vehicle-fuel
						  dispensing systems.
Section
						  101.16(4)
						  (b) of the Statutes contains the following
						  requirements: "(b) 1. A person who owns, leases, or uses a propane gas system
						  and who is a customer of a retail supplier shall notify the retail supplier of
						  propane gas for the propane gas system of any interruption in the operation of
						  the propane gas system due to the replacement, modification, repair, or
						  servicing of the propane gas system by any person other than the retail
						  supplier. The customer shall provide the notice at least 7 days in advance of
						  the interruption in the operation of the propane gas system, except as provided
						  in subd. 2. The retail supplier, or the person replacing, modifying, repairing,
						  or servicing the propane gas system, shall perform a check for leaks or other
						  defects in the propane gas system before placing the propane gas system back
						  into operation in the manner required by rule.
2. If the interruption of a propane gas system subject
						  to subd. 1. is due to emergency repair or servicing, the customer shall provide
						  the notice to the retail supplier as soon as possible and no later than 24
						  hours after the repair or servicing is completed."
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter V - Liquefied Petroleum Gas Systems › Section SPS 340.53 - Fuel supply tanks for liquefied petroleum cargo tank trucks

Current through June 24, 2024
No liquefied petroleum gas cargo tank that exists on or
						after September 1, 2011, may be connected in any way to a liquefied petroleum
						gas fuel supply tank for a motor vehicle.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter VI - Liquefied Natural Gas Systems › Section SPS 340.60 - Scope

Current through June 24, 2024
(1)
					 APPLICATION. This subchapter applies to the storage, handling and use of
					 liquefied natural gas.
(2)EXEMPTIONS. This subchapter does not apply
					 to any of the following:
(a) Liquefied natural
					 gas systems owned and operated by utilities when the systems are part of the
					 distribution facilities for the utility and are subject to the provisions of
					 ch. PSC 135.
Note:
Liquefied natural gas systems owned
						and operated for utility purposes by utilities are regulated by the Public
						Service Commission and are subject to chapter
						PSC 135, and the Natural Gas
						Pipeline Safety Act of 1968 ( 49 USC 1675, 49 CFR 192 - et seq.).
(b) The transportation of
					 liquefied natural gas.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter VI - Liquefied Natural Gas Systems › Section SPS 340.61 - Design, construction, installation, operation and maintenance of liquefied natural gas systems

Current through June 24, 2024
Liquefied natural gas systems shall be designed,
						constructed, installed, operated and maintained as specified in NFPA 52 and
						59A, except as otherwise provided in this chapter.
Section
						  SPS
						  340.42 contains requirements for vehicle-fuel
						  dispensing systems.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter VII - Compressed Natural Gas Systems › Section SPS 340.70 - Scope

Current through June 24, 2024
(1)
					 APPLICATION. This subchapter applies to the storage, handling and use of
					 compressed natural gas.
(2)EXEMPTIONS. This subchapter does not apply
					 to any of the following:
(a) Compressed
					 natural gas systems owned and operated by utilities when the systems are part
					 of the distribution facilities for the utility and are subject to the
					 provisions of ch. PSC 135.
Note:
Compressed natural gas systems owned
						and operated for utility purposes by utilities are regulated by the Public
						Service Commission and are subject to chapter
						PSC 135, and the Natural Gas
						Pipeline Safety Act of 1968 ( 49 USC 1675, 49 CFR 192 - et seq.).
(b) The transportation of
					 compressed natural gas.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter VII - Compressed Natural Gas Systems › Section SPS 340.71 - Design, construction, installation, operation and maintenance of compressed natural gas systems

Current through June 24, 2024
Compressed natural gas systems shall be designed,
						constructed, installed, operated and maintained as specified in NFPA 52, except
						as otherwise provided in this chapter.
Section
						  SPS
						  340.42 c ontains requirements for vehicle-fuel
						  dispensing systems.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter VIII - Gaseous Hydrogen Systems › Section SPS 340.80 - Scope

Current through June 24, 2024
(1)
					 APPLICATION. This subchapter applies to the storage, handling and use of
					 gaseous hydrogen.
(2)EXEMPTIONS.
					 This subchapter does not apply to any of the following:
(a) Gaseous hydrogen systems owned and
					 operated by utilities when the systems are part of the distribution facilities
					 for the utility and are subject to the provisions of ch. PSC 135.
Note:
Gaseous hydrogen systems owned and
						operated for utility purposes by utilities are regulated by the Public Service
						Commission and are subject to chapter
						PSC 135, and the Natural Gas
						Pipeline Safety Act of 1968 ( 49 USC 1675, 49 CFR 192 - et seq.).
(b) The transportation of gaseous
					 hydrogen.
Note:
The transportation of gaseous
						hydrogen is subject to the regulations of the federal Department of
						Transportation under Title 49 CFR Parts 171 - 179.
(c) Process gaseous hydrogen storage
					 installations.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter VIII - Gaseous Hydrogen Systems › Section SPS 340.81 - Design, construction, installation, operation and maintenance of gaseous hydrogen systems

Current through June 24, 2024
Gaseous hydrogen systems shall be designed, constructed,
						installed, operated and maintained as specified in NFPA 52, except as otherwise
						provided in this chapter.
Section
						  SPS
						  340.42 contains requirements for vehicle-fuel
						  dispensing systems.
See chapter
						  SPS
						  341 for registration and inspections of gaseous
						  hydrogen pressure vessels that are not within the scope of this chapter.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IX - Liquefied Hydrogen Systems › Section SPS 340.90 - Scope

Current through June 24, 2024
(1)
					 APPLICATION. This subchapter applies to the storage, handling and use of
					 liquefied hydrogen.
(2) EXEMPTIONS.
					 This subchapter does not apply to any of the following:
(a) Liquefied hydrogen systems owned and
					 operated by utilities when the systems are part of the distribution facilities
					 for the utility and are subject to the provisions of ch. PSC 135.
Note: Liquefied hydrogen systems owned and operated for
						utility purposes by utilities are regulated by the Public Service Commission
						and are subject to chapter
						PSC 135, and the Natural Gas
						Pipeline Safety Act of 1968 ( 49 USC 1675, 49 CFR 192 - et seq.).
(b) The transportation of
					 liquefied hydrogen.
Note: The transportation of liquefied hydrogen is subject
						to the regulations of the federal Department of Transportation under Title 49
						CFR Parts 171 - 179.
(c)
					 Process liquefied hydrogen storage installations.
Wisconsin Administrative Code › Department of Safety and Professional Services › SPS 301-399 - Safety, Buildings, and Environment › SPS 326-360 - General, Part II › Chapter SPS 340 - Gas systems › Subchapter IX - Liquefied Hydrogen Systems › Section SPS 340.91 - Design, construction, installation, operation and maintenance of liquefied hydrogen systems

Current through June 24, 2024
Liquefied hydrogen systems shall be designed,
						constructed, installed, operated and maintained as specified in NFPA 52, except
						as otherwise provided in this chapter.
Section
						  SPS
						  340.42 contains requirements for vehicle-fuel
						  dispensing systems.
Note: See chapter
						  SPS
						  341 for registration and inspections of gaseous
						  hydrogen pressure vessels that are not within the scope of this chapter.