reglab/statecodes huggingface dataset:
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.116 - Vehicular Sally Port

Current through Reg. 49, No. 28; July 12, 2024
A facility should have a vehicular sally port located
					 inside or abutting the building so that inmates may board or disembark from a
					 vehicle. Space should be sufficient to accommodate anticipated transportation
					 vehicles.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.117 - Inmate Entrance

Current through Reg. 49, No. 28; July 12, 2024
The inmate entrance should be from the vehicular sally port
					 through a safety vestibule into the processing area. This entrance shall allow
					 for passage of patient evacuation equipment between interlocking doors. The
					 entrance shall be designed and constructed to allow observation and
					 identification of persons approaching the inmate entrance. Electronic
					 surveillance equipment may be used.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.118 - Weapon Storage

Current through Reg. 49, No. 28; July 12, 2024
Separate secure storage space shall be provided at all
					 entrances to the security perimeter for weapons and
					 ammunition.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.119 - Processing Area

Current through Reg. 49, No. 28; July 12, 2024
Facilities shall have a processing area located inside the
					 security perimeter, but away from the inmate housing areas. The processing area
					 shall be designed to readily permit the booking, shakedown, identification, and
					 dressing of inmates. A telephone shall be available for detainees' use.
					 Processing areas should be provided with access to drinking fountains and
					 toilets. Panels or partitions may be erected in the booking area to provide
					 privacy and separation of inmates.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.120 - Identification

Current through Reg. 49, No. 28; July 12, 2024
Space shall be provided for photographing, fingerprinting
					 and identification procedures for inmates.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.121 - Visiting Areas

Current through Reg. 49, No. 28; July 12, 2024
Visiting areas shall be provided and shall be designed to
					 provide adequate visitation for the capacity of the facility. Visitation areas
					 shall be designed for the degree of security sought to be achieved. Audible
					 communications shall be provided between the inmate and visitor. Visiting areas
					 for maximum and medium custody inmates shall be designed to prevent passage of
					 contraband. Provisions shall be made for disabled visitors and inmates. Seating
					 should be provided for both inmates and visitors. A secure visiting area should
					 be provided for contact visits from law enforcement officers, attorneys,
					 clergy, and probation and parole officers. Provisions shall be made for passage
					 of legal paper between inmates and attorneys.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.122 - Jailer Stations

Current through Reg. 49, No. 28; July 12, 2024
A sufficient number of jailer stations shall be provided on
					 each floor where inmates are housed. Staff toilets and lavatories should be
					 provided in close proximity to jailer stations.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.123 - Kitchen

Current through Reg. 49, No. 28; July 12, 2024
A kitchen of adequate size and properly equipped shall be
					 provided within the system and shall include the following.
(1) Functions. Kitchen space and equipment
				  shall allow for the efficient operations of receiving, storage, processing,
				  preparation, cooking, baking, serving, dish washing, cleaning, menu
				  preparation, record keeping, personal hygiene, and removal of waste and
				  garbage. Kitchen functions shall be performed without compromising the security
				  of the facility. The kitchen should not be designed as a passageway for nonfood
				  handling persons.
(2) Storage.
				  Adequate dry and cold storage shall be provided appropriate for the size of
				  kitchen. Separate storage shall be provided for nonfood items.
(3) Surfaces. The kitchen floor shall be
				  properly pitched to adequate floor drains and allow for proper cleaning. Floor
				  finish should prevent slipping. The junction between floors and walls shall be
				  covered. Walls and ceilings shall be finished with smooth washable light
				  colored surfaces.
(4) Light.
				  Adequate lighting shall be provided on all work surfaces.
(5) Ventilation. Food service areas shall be
				  adequately ventilated to control disagreeable odors and moisture. All openings
				  to the outside shall be secured and provided with insect screens.
(6) Water. Adequate hot and cold water shall
				  be provided for food preparation, cleaning, and dish washing. Hot water
				  equipment shall be of sufficient size and capacity to meet the needs of the
				  facility.
(7) Codes. Kitchens shall
				  comply with state health codes.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.124 - Dining Space

Current through Reg. 49, No. 28; July 12, 2024
Group dining may be provided. Group dining should avoid
					 concentrations of more than 24 inmates (48 for direct
					 supervision).
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.125 - Laundry Facilities

Current through Reg. 49, No. 28; July 12, 2024
A laundry, or an acceptable laundry vendor contract, or
					 both, shall be maintained to provide clean clothing, bedding, and supplies.
					 Adequate, separated storage space, commensurate with facility capacity, shall
					 be provided for both clean and soiled laundry and laundry supplies. Where
					 applicable, space shall be provided for washers, extractors and dryers. A
					 toilet and lavatory should be provided nearby.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.126 - Commissary

Current through Reg. 49, No. 28; July 12, 2024
Space appropriate to the capacity of the facility should be
					 provided for an inmate commissary, or a written program shall be established.
					 (See Chapter 291 of this title (relating to Services and
					 Activities)).
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.127 - Storage Area Capacities

Current through Reg. 49, No. 28; July 12, 2024
Storage areas based upon facility capacity should be
					 provided as follows:
(1) Inmate
				  property; two cubic feet per inmate;
(2) Inmate uniforms and linens: three cubic
				  feet per inmate;
(3) Inmate
				  mattresses: raised perforated storage in the amount of five and one-fourth
				  cubic feet per mattress for 25% of total capacity.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.128 - Janitorial Storage Space

Current through Reg. 49, No. 28; July 12, 2024
Adequate, secured, well ventilated storage for janitorial
					 supplies and equipment should be provided within the security perimeter and
					 administrative area. Sufficient broom and mop racks should be
					 provided.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.129 - Medical Space and Equipment

Current through Reg. 49, No. 28; July 12, 2024
Adequate space for first aid equipment shall be provided.
					 Space and equipment for medical examination, treatment, and convalescent care
					 shall be provided or provisions contained in the health services plan.
					 Adequate, secure storage for medical supplies and drugs shall be
					 provided.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.130 - Infirmary

Current through Reg. 49, No. 28; July 12, 2024
An infirmary should be provided for facilities of 200 or
					 more capacity. When an infirmary is provided, the following minimum components
					 shall be included:
(1) nurses
				  station;
(2) locked medication
				  station with storage for individually filled prescriptions;
(3) utility room with sink and storage for
				  linens and equipment;
(4)
				  refrigerated storage;
(5) utility
				  room with double tub sink and clinical service sink with flushing
				  rim;
(6) 80 square feet of floor
				  space per bed;
(7) at least one
				  single occupancy room or cell with 80 square feet of floor space;
(8) doors, through which patients and
				  equipment are to be moved, of adequate width to allow turning of wheeled chairs
				  and tables normally used in medical facilities;
(9) a lavatory with a gooseneck inlet and
				  wrist controls accessible to each ward;
(10) janitor closet;
(11) toilet, lavatory, and shower for use of
				  inmates in the infirmary;
(12)
				  additional elements as dictated by the facility health care director.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.131 - Multipurpose Rooms

Current through Reg. 49, No. 28; July 12, 2024
One or more multipurpose rooms should be provided. These
					 multipurpose rooms may be used for group assembly, conferences, contact
					 visitation, counseling, religious services, education, or other special
					 uses.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.132 - Exercise Area

Current through Reg. 49, No. 28; July 12, 2024
One or more secure exercise areas shall be provided. Where
					 outdoor exercise areas are provided, alternate areas should be provided for
					 exercise during inclement weather. Outdoor exercise areas should be covered
					 with a security enclosure. A toilet and drinking fountain should be readily
					 available. Consideration shall be given to the requirement for inmates to be
					 allowed access to sunlight for one hour per week after ten days
					 confinement.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.133 - Single Cells

Current through Reg. 49, No. 28; July 12, 2024
Single cells shall not be less than eight feet high from
					 finished floor to ceiling and not less than five feet wide from wall to wall.
					 They shall contain not less than 40 square feet of floor space. They shall have
					 one bunk, toilet, lavatory, table, and seat. Single cells should comprise at
					 least 50% of the total inmate capacity of the facility, but in no event shall
					 comprise less than 30% of the total capacity of the facility.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.134 - Multiple Occupancy Cells

Current through Reg. 49, No. 28; July 12, 2024
Multiple occupancy cells shall contain two to eight bunks
					 and not less than 40 square feet of floor space for the first bunk plus 18
					 square feet of floor space for each additional bunk. Each multiple occupancy
					 cell shall have one toilet and lavatory. Multiple occupancy cells should not be
					 provided in direct supervision facilities.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.135 - Dormitories

Current through Reg. 49, No. 28; July 12, 2024
Dormitories shall contain nine to 24 bunks, except direct
					 supervision dormitories which may contain up to 48 bunks. Dormitories shall
					 contain not less than 40 square feet of floor space for the first bunk plus 18
					 square feet of floor space for each additional bunk. Each dormitory shall have
					 adequate toilets and lavatories. Not more than 40% of the inmate capacity of
					 the facility shall be designed for dormitories.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.136 - Day Rooms

Current through Reg. 49, No. 28; July 12, 2024
All single cells, multiple occupancy cells, and dormitories
					 shall be provided with day rooms. Separation cells, violent cells, holding
					 cells, detoxification cells, and medical cells are exempt from this
					 requirement. Day rooms shall be designed for no more than 24 inmates, except
					 direct supervision day rooms may be designed for up to 48 inmates. Based on the
					 design capacity of the cells served, the day rooms shall contain not less than
					 40 square feet of floor space for the first inmate plus 18 square feet of floor
					 space for each additional inmate; adequate toilets, lavatories, mirrors,
					 showers, seating and tables. A utility sink should be provided. Day rooms may
					 be contiguous with inmate living areas provided that space requirements for
					 living areas and day rooms are met. Convenient electrical receptacles circuited
					 with ground fault protection should be provided. Power to receptacles should be
					 individually controlled outside of the cell.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.137 - Separation Cells

Current through Reg. 49, No. 28; July 12, 2024
A facility shall have one or more single occupancy
					 separation cells which shall include the following features and
					 equipment.
(1) Furnishings. Each cell
				  shall be provided with a table, seat, mirror and bunk. A shelf and clothes hook
				  may be provided. Convenient electrical receptacles circuited with ground fault
				  protection should be provided. Power to receptacles, when provided, shall be
				  individually controlled outside of the cell.
(2) Plumbing. Cells shall be provided with a
				  toilet, lavatory, shower, and floor drain.
(3) Cell Size. Cells shall contain not less
				  than 40 square feet of floor space.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.138 - Holding Cells

Current through Reg. 49, No. 28; July 12, 2024
(a) One or more
				  holding cells should be provided to hold inmates pending booking, court
				  appearance, identification, housing assignment, discharge, or other reason for
				  temporary housing. Inmates shall not be held for more than 48 hours and the
				  cell shall include the following features.
(1) Seating. A stationary bench or benches
				  abutting the walls shall be provided. Benches shall be 14" to 18" above the
				  finished floor and not less than 12" wide. Seating shall be sufficient to
				  provide not less than 24 linear inches per inmate at cell capacity;
(2) Plumbing. Cells shall be provided with
				  adequate toilets, lavatories, and floor drains. The floor shall be properly
				  pitched to drains;
(3) Cell Size.
				  The size of the cell shall be determined by the anticipated maximum number of
				  inmates to be confined at any one time. Cells shall be constructed to house
				  from 1 to 24 inmates and shall contain not less than 40 square feet of floor
				  space for 1 inmate and 18 square feet of floor space for each additional inmate
				  to be confined;
(4) Surfaces.
				  Floor, wall, and ceiling material shall be durable and easily
				  cleaned;
(5) Supervision. The cell
				  should be located and constructed to facilitate supervision of the cell area
				  and to materially reduce noise.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.139 - Detoxification Cells

Current through Reg. 49, No. 28; July 12, 2024
Any facility that anticipates the housing of intoxicated
					 persons should provide one or more detoxification cells for the detention of
					 persons during the detoxification process. These cells shall include the
					 following features and equipment.
(1)
				  Seating. A stationary bench or benches abutting the walls shall be provided.
				  Benches shall be not higher than eight inches above the finished
				  floor.
(2) Plumbing. Cells should
				  be provided with one or more vandal resistive flushing floor drains with
				  outside controls, or vandal resistive toilet, lavatory, and standard floor
				  drains. The floor shall be properly pitched to drains. Drinking fountains or
				  lavatories capable of providing drinking water should be provided.
(3) Cell Size. The size of the cell shall be
				  determined by the anticipated maximum number of intoxicated inmates to be
				  confined at any one time. Cells shall be constructed to house from one to 12
				  inmates and shall contain not less than 40 square feet of floor space for one
				  inmate and 18 square feet of floor space for each additional inmate to be
				  confined.
(4) Surfaces. Floor, wall
				  and ceiling material shall be durable and easily cleaned.
(5) Supervision. The cell shall be located
				  and constructed to facilitate supervision of the cell area and to materially
				  reduce noise.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.140 - Violent Cells

Current through Reg. 49, No. 28; July 12, 2024
A facility may contain one or more single occupancy cells
					 for the temporary holding of violent persons. Violent cells shall include the
					 following features and equipment.
(1)
				  Furnishings. The cell shall be equipped with a hammock, not less than two
				  feet-three inches wide and six feet-three inches long, made of an elastic or
				  fibrous fabric. A bench abutting the wall, the length or width of the cell, at
				  least two feet-three inches wide and six feet-three inches long and not more
				  than eight inches above the floor may be provided in lieu of a
				  hammock.
(2) Plumbing. Flushing
				  type floor drains with outside controls shall be provided.
(3) Cell Size. Cell shall contain not less
				  than 40 square feet of floor space.
(4) Padding. Walls, floor and bench shall be
				  completely covered with a material to protect the inmate from self injury. The
				  type of material used to cover the walls, floor, and bench shall be fire
				  resistive and nontoxic.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.141 - Dimensions

Current through Reg. 49, No. 28; July 12, 2024
All cells and day rooms shall be not less than eight feet
					 from finished floor to ceiling and five feet from wall to wall. Cells
					 containing over/under bunk units shall be measured from center line of units to
					 wall. Corridors shall be not less than four feet wide.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.142 - Safety Vestibules

Current through Reg. 49, No. 28; July 12, 2024
Safety vestibules shall be provided for each inmate living
					 area and day room used for confinement of three or more inmates.
(1) Safety vestibules shall have one or more
				  interior doors and a main entrance door.
(2) Doors shall be arranged to be locked and
				  unlocked by control means located outside of the inmate living area and safety
				  vestibule.
(3) Where doors have an
				  interlocking security feature, provisions should be made for an override
				  capability in the event an emergency requires both doors to be opened
				  simultaneously.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.143 - Furnishings for Inmate Housing Areas

Current through Reg. 49, No. 28; July 12, 2024
(a)
				  Bunks. Bunks shall be fire resistive and securely anchored. The mattress
				  surface of the bunk shall measure not less than two feet-three inches wide and
				  six feet-three inches long.
(b)
				  Toilets and Lavatories. Detention type toilets and lavatories shall be provided
				  in cells and day rooms. In direct supervision living areas, they shall be
				  constructed in such manner and of such material so as to resist vandalism.
				  Based on design capacity, each cell and day room shall provide one toilet and
				  lavatory capable of providing drinking water for each group or increment of 12
				  inmates.
(c) Showers. Shower areas
				  shall be not less than two feet-six inches square per showerhead and not less
				  than seven feet high. Construction shall be of vandal resistive materials and
				  should be of materials which resist the action of soap and water. Drying areas
				  of not less than two feet-six inches square sloped to a drain should be
				  provided adjoining the shower entrance. Based on design capacity, each
				  separation cell and day room shall provide one shower for each group or
				  increment of 12 inmates.
(d) Tables
				  and Seating. Tables and seating shall be constructed of materials which will
				  resist vandalism. They shall be fire resistive, securely anchored, and
				  reasonably remote from toilet areas. Tables and seating in direct supervision
				  day rooms are not required to be anchored. Tables and benches shall be not less
				  than 12 inches wide, and linear seating shall be not less than 18 inches per
				  person. Stools shall be not less than 12 inches in diameter. Seating height of
				  14 inches to 18 inches shall be provided.
(e) Privacy Shields. Inmate toilet areas in
				  holding cells shall be configured or equipped to provide reasonable privacy
				  from exposure to persons outside the cell. Privacy shields should extend from
				  about 15 inches above the finished floor to about four feet-six inches high and
				  shall be securely anchored.
(f)
				  Mirrors. Mirrors shall be constructed of unbreakable material. Mirrors shall be
				  provided above lavatories in separation cells.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.144 - Walls

Current through Reg. 49, No. 28; July 12, 2024
Walls should be constructed to resist vandalism and
					 facilitate ease of maintenance. Walls shall be constructed with due
					 consideration to the security sought to be achieved.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.145 - Floors

Current through Reg. 49, No. 28; July 12, 2024
Floors should provide a high resistance to wear and
					 moisture. A nonslip surface should be provided at the entrance to all shower
					 areas.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.146 - Ceilings

Current through Reg. 49, No. 28; July 12, 2024
Ceilings within the security perimeter shall be constructed
					 of material not easily damaged and shall be commensurate with the security
					 level of the adjacent walls.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.147 - Vermin Control

Current through Reg. 49, No. 28; July 12, 2024
Facility construction shall protect against the entrance
					 and infestation of vermin. Materials and construction design shall contribute
					 to efficient maintenance and housekeeping.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.148 - Windows and Screens

Current through Reg. 49, No. 28; July 12, 2024
Operable windows shall be equipped with insect screens. The
					 security level of windows in inmate occupied areas shall be commensurate with
					 the security of the walls. Windows or skylights should be provided in inmate
					 living and activity areas.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.149 - Vent Grilles

Current through Reg. 49, No. 28; July 12, 2024
Vent grilles in walls and ceilings shall be commensurate
					 with the security sought to be achieved. Vent grilles shall be securely
					 anchored.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.150 - Food Passes

Current through Reg. 49, No. 28; July 12, 2024
Food passes should not be less than 15 inches wide and four
					 and one-half inches high. Lockable shutters should be provided to prevent
					 passage of contraband.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.151 - Detention Doors

Current through Reg. 49, No. 28; July 12, 2024
Hollow metal doors shall be constructed of 12 to 14 gauge
					 steel inside the security perimeter. Eighteen gauge hollow metal doors may be
					 used outside the security perimeter. Plate doors shall be constructed of
					 material not less than 3/16 inch thick. The security quality of each detention
					 door shall be determined by the level of security sought to be achieved.
					 Detention doors shall be equipped with detention hardware and
					 accessories.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.152 - Door Stops

Current through Reg. 49, No. 28; July 12, 2024
Door stops shall be provided for all detention doors. Door
					 closers manufactured with integral door stops may be used.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.153 - Door Closers

Current through Reg. 49, No. 28; July 12, 2024
Where used, door closers for all detention swinging doors
					 shall be appropriate for the weight of the door.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.154 - Keys and Locks

Current through Reg. 49, No. 28; July 12, 2024
Keys and locks for detention doors shall be manufactured
					 especially for detention use and shall be commensurate with the security sought
					 to be achieved. An additional set of keys shall be maintained by the
					 operator.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.155 - Key Cabinets

Current through Reg. 49, No. 28; July 12, 2024
Secured key cabinets should be provided at suitable
					 locations.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.156 - Power Operated Locks

Current through Reg. 49, No. 28; July 12, 2024
Power operated locks, where used, shall be motor, solenoid,
					 or pneumatic type and provide electrical control unlocking, key unlocking by
					 manual operation, and automatic mechanical deadlocking of doors upon closing. A
					 door position switch and door position indicator shall be provided for all
					 doors equipped with power operated locks. Heavy-duty detention type door
					 closers should be provided on all swinging doors equipped with power operated
					 locks.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.157 - Remote Controls

Current through Reg. 49, No. 28; July 12, 2024
Doors to single cells, multiple occupancy cells,
					 dormitories, and day rooms shall be capable of being locked and unlocked
					 individually by control means located remote from the cell area. Single cells
					 with contiguous day room and separation cells which open directly on an exiting
					 corridor are exempt from this requirement. All remote door controls should be
					 secure.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.158 - Emergency Operation of Doors

Current through Reg. 49, No. 28; July 12, 2024
All doors to cells and day rooms shall be capable of being
					 unlocked by a manual means at the door or a remote location.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.159 - Access Doors

Current through Reg. 49, No. 28; July 12, 2024
All plumbing and mechanical access doors and panels shall
					 be constructed and secured with locks commensurate to the security sought to be
					 achieved.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.160 - Temperature Control

Current through Reg. 49, No. 28; July 12, 2024
Temperature levels shall be reasonably maintained between
					 65 degrees Fahrenheit and 85 degrees Fahrenheit in all occupied
					 areas.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.161 - Air Flow

Current through Reg. 49, No. 28; July 12, 2024
Ventilation shall be sufficient to admit fresh air and
					 remove disagreeable odors. A sufficient number of windows capable of being
					 opened, or a mechanical ventilation system provided with emergency electrical
					 power, shall be provided in order to allow for sufficient ventilation in case
					 of breakdown in the normal ventilation system or normal power
					 failure.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.162 - Plumbing

Current through Reg. 49, No. 28; July 12, 2024
Plumbing work shall meet the requirements of the Southern
					 Standard Building Code, or equivalent. Warm and cold water should be provided
					 at all lavatories and warm water shall be provided at all showers. Warm water
					 temperature shall be between 100 and 120 degrees Fahrenheit. All plumbing in
					 inmate occupied areas should have quick shut off capability.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.163 - Sinks

Current through Reg. 49, No. 28; July 12, 2024
Sufficient mop sinks with hot and cold water should be
					 provided within the security perimeter and administrative
					 area.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.164 - Faucets

Current through Reg. 49, No. 28; July 12, 2024
Cold water faucets with standard hose connections should be
					 provided in plumbing access space or corridors.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.165 - Floor Drains

Current through Reg. 49, No. 28; July 12, 2024
Floor drains shall be located throughout the facility so as
					 to reduce the possibility of flooding. Floor drains shall be provided in every
					 area where toilets, lavatories, or showers are located. Drain covers should be
					 provided and securely anchored with vandal proof screws.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.166 - Lighting

Current through Reg. 49, No. 28; July 12, 2024
Adequate illumination shall be provided throughout the
					 cells and day rooms. An illumination level of 20 foot candles shall be provided
					 at mirrors and tables. Master light controls for cells and day rooms and
					 electrical conduit shall be out of reach of inmates. Inmates should be capable
					 of controlling some lighting; override capability shall be provided. All
					 lighting fixtures in cells and day rooms shall be detention type. Night lights
					 sufficient to permit continuous observation shall be provided. Control areas
					 and means of egress shall be continuously illuminated. Exteriors of buildings
					 and all entrances shall be lighted sufficiently to observe approaching
					 persons.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.167 - Audible Communication

Current through Reg. 49, No. 28; July 12, 2024
Two-way voice communication shall be available at all times
					 between inmates and jailers.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.168 - Television Monitoring

Current through Reg. 49, No. 28; July 12, 2024
Closed circuit television monitoring may be provided to
					 supplement control and security functions. Closed circuit television monitoring
					 of toilet and shower areas shall not be allowed except in medical and special
					 observation areas.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.169 - Electrical Power

Current through Reg. 49, No. 28; July 12, 2024
Electrical installation shall comply with state and local
					 codes and ordinances. Facilities should have adequate electrical receptacles in
					 corridors or chases for food carts, janitorial, and maintenance
					 equipment.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.170 - Emergency Electrical Power

Current through Reg. 49, No. 28; July 12, 2024
An emergency electrical power system for quick recovery to
					 maintain essential services, security, and safety should be provided to meet
					 the life safety requirements as required by Chapter 263 of this title (relating
					 to Life Safety). If installed, such system shall be tested operationally not
					 less than weekly and a record kept of this testing.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter A - EXISTING MAXIMUM SECURITY DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.171 - Applicability

Current through Reg. 49, No. 28; July 12, 2024
The provisions of this section apply only to facilities
					 existing and being operated as county facilities on December 23,
					 1976.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.200 - Lockup Operation Concept

Current through Reg. 49, No. 28; July 12, 2024
A facility shall be planned to receive unclassified
					 persons, hold pretrial persons, and allow for processing, classifying, and
					 releasing persons at all times. Inmates shall not be confined in a lockup in
					 excess of 72 hours.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.201 - Lockup Facilities

Current through Reg. 49, No. 28; July 12, 2024
A facility shall consist of one or more single cells and
					 may include multiple occupancy cells or dormitories.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.202 - Lockup Security Requirements

Current through Reg. 49, No. 28; July 12, 2024
Facility security should be planned to protect inmates from
					 one another, protect staff and visitors from inmates, and deter or prevent
					 escapes.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.203 - Special Security

Current through Reg. 49, No. 28; July 12, 2024
A facility shall be constructed and maintained as a special
					 security unit. The integrity of the security perimeter shall not be compromised
					 by other functions.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.204 - Construction Materials

Current through Reg. 49, No. 28; July 12, 2024
Inmate housing areas and day rooms shall be constructed of
					 metal, masonry, concrete, or other comparable materials. The level of security
					 desired should determine the selection of appropriate
					 materials.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.205 - Public Areas

Current through Reg. 49, No. 28; July 12, 2024
Public areas shall be located outside the security
					 perimeter. Public access to the security perimeter shall be controlled. A
					 public lobby or waiting area should be provided for the convenience of the
					 public, including seating, drinking fountains, and rest rooms and should
					 include lockers or storage for visitor's articles. Provisions shall be made for
					 disabled visitors.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.206 - Vision into Inmate Areas

Current through Reg. 49, No. 28; July 12, 2024
Design and construction shall preclude direct vision into
					 inmate occupied areas by the public.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.207 - Administrative Space

Current through Reg. 49, No. 28; July 12, 2024
The facility shall provide sufficient space for
					 administrative, program, and clerical needs. Adequate space for equipment and
					 supplies shall be provided to meet established and projected needs. These
					 spaces should be located outside the inmate housing areas. Evidence storage
					 should not be located within the security perimeter.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.208 - Squad Rooms

Current through Reg. 49, No. 28; July 12, 2024
Locker space, toilets, lavatories, showers, dressing rooms,
					 and classroom space should be provided for staff and shall be located outside
					 the security perimeter. Break and dining space should be provided in the
					 facility.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.209 - Arsenal

Current through Reg. 49, No. 28; July 12, 2024
An arsenal or secure storage area for weapons and tactical
					 equipment should be provided outside the security perimeter.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.210 - Inmate Movement Into and Out of Lockup

Current through Reg. 49, No. 28; July 12, 2024
Construction should provide for movement of an inmate or
					 detainee into and out of the facility without exposing the individual to
					 contact with the public.
Texas Administrative Code › Title 37 - PUBLIC SAFETY AND CORRECTIONS › Part 9 - TEXAS COMMISSION ON JAIL STANDARDS › Chapter 261 - EXISTING CONSTRUCTION RULES › Subchapter B - EXISTING LOCKUP DESIGN, CONSTRUCTION AND FURNISHING REQUIREMENTS › Section 261.211 - Inmate Movement inside Lockup

Current through Reg. 49, No. 28; July 12, 2024
The design should provide for the orderly movement of
					 inmates and services.