Oklahoma Administrative Code › Title 748 - Oklahoma Uniform Building Code Commission › Chapter 20 - Adopted Codes › Subchapter 16 - IPC[®] 2018 › Section 748:20-16-8 - IPC[®] 2018 Chapter 3 General Regulations

Current through Vol. 41, No. 20, July 1, 2024
Chapter 3 of the Oklahoma adopted IPC® 2018 is adopted
				  with the following modifications:
(1)
				Section 305.3 Pipes through foundations walls. This section has been modified
				to require the relieving arch or pipe sleeve pipe to conform with the materials
				and standards listed in Table 702.2 or as approved by the authority having
				jurisdiction. This section has been modified to read: 305.3 Pipes through
				foundation walls. Any pipe that passes through a foundation wall shall be
				provided with a relieving arch or pipe sleeve pipe shall be built into the
				foundation wall. The relieving arch or pipe sleeve shall conform to one of the
				materials and standards listed in Table 702.2, or as approved. The sleeve shall
				be two pipe sizes greater than the pipe passing through the wall.
(2) Section 305.4.1 Sewer depth. This section
				has been modified to include a depth for the septic tank connection unless
				otherwise approved by the authority having jurisdiction. This section has been
				modified to read: 305.4.1 Sewer depth. Building sewers that connect to private
				sewage disposal systems shall be a minimum of 12 inches (305 mm) or as approved
				by the authority having jurisdiction below finished grade at the point of
				septic tank connection. Building sewers shall be a minimum of 12 inches (305
				mm) below grade.
(3) Section 305.6
				Protection against physical damage. This section has been modified to change
				distance in concealed locations where piping, other than cast-iron or
				galvanized steel, is installed through holes or notches in studs, joists,
				rafters or similar members from less than 1 and a quarter inches to less than 1
				and one half inches from the nearest edge of the member or the pipe will be
				protected by steel shield plates. This section has been modified to read: 305.6
				Protection against physical damage. In concealed locations, where piping, other
				than cast-iron or galvanized steel, is installed through holes or notches in
				studs, joists, rafters or similar members less than 1 and one-half inches (38
				mm) from the nearest edge of the member, the pipe shall be protected by steel
				shield plates. Such shield plates shall have a thickness of not less than
				0.0575 inch (1.463 mm) (No. 16 gage). Such plates shall cover the area of the
				pipe where the member is notched or bored, and shall extend not less than 2
				inches (51 mm) above sole plates and below top plates.
(4) Section 312.2 Drainage and vent water
				test. This section has been modified to change the test from a requirement of a
				10 foot (3048 mm) head of water to a requirement of a 5 foot (1524 mm) head of
				water. This section has been modified to read: 312.2 Drainage and vent water
				test. A water test shall be applied to the drainage system either in its
				entirety or in sections. If applied to the entire system, all openings in the
				piping shall be tightly closed, except the highest opening, and the system
				shall be filled with water to the point of overflow. If the system is tested in
				sections, each opening shall be tightly plugged except the highest openings of
				the section under test, and each section shall be filled with water, but no
				section shall be tested with less than a 5 foot (1524 mm) head of water. In
				testing successive sections, at least the upper 5 feet (1524 mm) of the next
				preceding section shall be tested so that no joint or pipe in the building,
				except the uppermost 5 feet (1524 mm) of the system, shall have been submitted
				to a test of less than a 5 foot (1524 mm) head of water. This pressure shall be
				held for at least 15 minutes. The system shall then be tight at all points.
(5) Section 312.3 Drainage and
				vent air test. This section has been modified to change the equivalent pressure
				for the inches of mercury to match the feet of water change made for the
				drainage and vent test. This section has been modified to read: 312.3 Drainage
				and vent air test. Plastic piping shall not be tested using air. An air test
				shall be made by forcing air into the system until there is a uniform gauge
				pressure of 2.5 psi (17.25 kPa) or sufficient to balance a 5-inch (127 mm)
				column of mercury. This test shall be held for a period of not less than 15
				minutes. Any adjustments to the test pressure required because of changes in
				ambient temperatures or the seating of gaskets shall be made prior to the
				beginning of the test period.
(6)
				312.6 Gravity sewer test. This section has been modified to allow the authority
				having jurisdiction to determine if this test is required and change the test
				from a 10 foot (3048 mm) head of water test to a 5 foot (1024 mm) head of water
				test. This section has been modified to read: 312.6 Gravity sewer test. Where
				required, gravity sewer tests shall consist of plugging the end of the building
				sewer at the point of connection with the public sewer, filling the building
				sewer with water, testing with not less than a 5 foot (1024 mm) head of water
				and maintaining such pressure for 15 minutes.
(7) Section 312.10.1 Inspections. This
				section has been modified to allow for third-party inspections to be accepted
				by the code official. This section has been modified to read: 312.10.1
				Inspections. Annual inspections shall be made of all backflow prevention
				assemblies and air gaps to determine whether they are operable, in accordance
				with Chapter 1, Sections 104.3 and 105.3.2.
(8) Section 314.2.1 Condensate disposal. This
				section has been modified to allow condensate drains to terminate to an
				approved pit or French drain. This section has been modified to read: 314.2.1
				Condensate disposal. Condensate from all cooling coils and evaporators shall be
				conveyed from the drain pain outlet to an approved place of disposal. Such
				piping shall maintain a horizontal slope in the direction of discharge of not
				less than one-eighth unit vertical in 12 units horizontal (1-percent slope).
				Condensate drains shall be allowed to terminate to an approved pit or French
				drain consisting of a minimum of 24 inches by 24 inches by 24 inches (610 mm by
				610 mm by 610 mm), or equivalent; of 1 inch (25 mm) washed rock. Such pits or
				French drains shall be located 30 inches (762 mm) minimum from outer edge of
				foundation to nearest edge of pit or French drain. Condensate shall not
				discharge into a street, alley or other areas so as to cause a nuisance.
(9) Section 314.2.3.1 Water-level
				monitoring devices. This section has been modified to add an exception for when
				the section shall not apply. This section has been modified to read: 314.2.3.1
				Water-level monitoring devices. On down-flow units and all other coils that do
				not have a secondary drain or provisions to install a secondary or auxiliary
				drain pan, a water- level monitoring device shall be installed inside the
				primary drain pan. This device shall shut off the equipment served in the event
				that the primary drain becomes restricted. Devices installed in the drain line
				shall not be permitted. Exception: This section shall not apply to appliances
				installed in areas outside on the ground or elevated structure where condensate
				overflow will not damage building components or contents.