Rhode Island Code of Regulations › Title 450 - Fire Safety Code Board of Appeal and Review › Chapter 00 - N/A › Subchapter 00 - N/A › Part 7 - RI Fire Code › Section 450-RICR-00-00-7.1 - Fire Code

Current through June 14, 2024
Pursuant to R.I. Gen. Laws §
										23-28.3-3, the NFPA  1   - Fire Code of the National Fire Protection Association, Inc., 2018 edition, with annexes, except those portions specifically reserved, deleted, altered, added to, or otherwise amended as outlined in this Part herein, and including all of the specific amendments to NFPA 1 - Fire Code, as outlined in this Part herein, is hereby adopted by reference as the Rhode Island Fire Code. Copies of NFPA 1 - Fire Code, 2018 edition, are available from the National Fire Protection Association, 1 Batterymarch Park, Quincy, Massachusetts 02169-7471. The National Fire Protection Association's telephone number is 617-770-0700.
Electronic copies of the reservations, deletions, alterations, additions and other amendments to this code, also known as the Rhode Island Fire Code Part 7, will be initially made available on the Fire Board's website at
http://www.fsc.ri.gov/
. Copies shall subsequently be available from LexisNexis/Matthew Bender & Co., 701 E. Water Street, Charlottesville, VA 22902. The LexisNexis telephone number is 1-800-446-3410.
The State Fire Marshal is the sole authority having jurisdiction for the strict enforcement of the Rhode Island Fire Code. The Fire Safety Code Board of Appeal and Review is the sole authority having jurisdiction for administration of the Rhode Island Fire Code.
Except as outlined below, the Fire Safety Code Board of Appeal and Review is the sole authority having jurisdiction to grant variances, waivers, and amendments from, or to review and accept any proposed fire safety equivalencies and alternatives to, the strict adherence to the provisions of the Rhode Island Fire Code and all referenced standards therein. Notwithstanding the above, the State Fire Marshal and his or her designees are hereby authorized to approve dimensional relief within the egress systems of any existing building in accordance with NFPA 101 and its annexes. Such dimensional relief shall be known as "AHJ modifications." All "AHJ modifications" must be in writing and recorded by the State Fire Marshal's Office. Once recorded by the State Fire Marshal's Office, the "AHJ modification" shall remain as permanent relief for the building as long as the use and/or occupancy of the building remains the same. Any change of use and/or occupancy shall subject the building to review under the relevant codes and reconsideration of the "AHJ modification" in light of the new use or occupancy.
For the purposes of uniform administration, and with the exception of "AHJ modifications" as outlined above, all other exceptions listed in the Rhode Island NFPA 1 - Fire Code and its referenced standards, allowing for a discretionary waiver by the authority having jurisdiction, shall be referred directly to the Fire Safety Code Board of Appeal and Review as outlined in Fire Safety Code §1.7.1 of this Subchapter et
seq
. The only official formal and binding interpretations of the provisions of the Rhode Island NFPA 1 - Fire Code and its referenced standards are those approved and published by the Fire Safety Code Board of Appeal and Review pursuant to the procedures outlined in Fire Safety Code, §1.7.1(C) of this Subchapter et
seq
.
All new buildings and structures, for which a building permit was issued on or after July 1, 2021, shall be subject to the provisions of the Rhode Island Fire Code addressing the new occupancy unless this requirement is specifically modified by the issuance of a blanket variance by the Fire Safety Code Board of Appeal and Review to allow a grace period for plans, submitted after the above date, to be reviewed under the prior Code.
All existing buildings and structures, and those buildings and structures for which a building permit was issued prior to July 1, 2021, shall be subject to the provisions of the Rhode Island Fire Code addressing the existing occupancy.
Any existing required building or structure, subject to the provisions of the Rehabilitation Building and Fire Code for Existing Buildings and Structures, shall also comply with the existing occupancy provisions of the Rhode Island Fire Code addressing the current or proposed occupancy.
All existing fire protection systems, such as sprinklers, fire alarms, emergency lighting and exit signs, installed in existing buildings, shall continue to be properly maintained. Non-required systems shall either be maintained, or have the devices removed or marked in such a manner to immediately notify the public of the lack of fire protection. Prior to the removal or marking of any non-required system, the system's owner must first comply with the procedures outlined in the Rhode Island Life Safety Code, (NFPA 101) 2018 Edition, §4.6.12.2 .1. The above marking of any de-activated system shall be at the direction and to the satisfaction of the State Fire Marshal or his or her designee.
The provisions of NFPA 1, 2018 edition, as amended and referenced below, and incorporated herein as the "Rhode Island Fire Code", shall be preceded by the acronym "RIFC". All of the remaining provisions of NFPA 1, 2018 edition, adopted as the "Rhode Island Fire Code", but not specifically addressed below, shall likewise be identified by the acronym "RIFC" preceding it. (Accordingly, "Chapter 1" below would be identified as "RIFC 1". Likewise, "§1.1.2 " below would be identified as "RIFC 1.1.2 ".)
7.1.1
CHAPTER 1 - ADMINISTRATION
(Amd) 1.1.2 Title.
The title of this Code shall be the "Rhode Island Fire Code" and may be cited as such.
(Add) 1.1.3
The "Rhode Island Fire Code" is hereby adopted pursuant to R.I. Gen. Laws Chapter 23-28.1.
(Add) 1.3.3.3
When a conflict between the language of the original 2018 Edition of the Fire Code and any specific Rhode Island amendment occurs, the Rhode Island amendment shall apply exclusively.
(Amd) 1.4.1 Equivalencies.
Nothing in this Code is intended to prevent the use of systems, methods, or devices of equivalent or superior quality, strength, fire resistance, effectiveness, durability, and safety, as determined by the Fire Safety Code Board of Appeal and Review, to those prescribed in this Code, provided a request for variance is submitted to the Fire Safety Code Board of Appeal and Review along with technical documentation to demonstrate equivalency and the system, method, or device is approved for the intended purpose.
(Amd) 1.4.2 Alternatives.
The specific requirements of this Code may be modified by the Fire Safety Code Board of Appeal and Review to allow alternative arrangements that will secure as nearly equivalent fire safety as practical.
(Amd) 1.4.3 Modifications.
The State Fire Marshal and his or her designees are hereby authorized to approve dimensional relief within the egress systems of any existing building in accordance with NFPA 101 and its annexes. Such dimensional relief shall be known as "AHJ modifications." All "AHJ modifications" must be submitted to the State Fire Marshal's Office for recording. Once recorded by the State Fire Marshal's Office, the "AHJ modification" shall remain as permanent relief for the building as long as the use and/or occupancy of the building remains the same. Any change of use and/or occupancy shall subject the building to review under the relevant codes and reconsideration of the "AHJ modification" in light of the new use or occupancy.
(Amd) 1.4.4
Buildings with alternative fire protection features approved by the Fire Safety Code Board of Appeal and Review shall be considered as conforming with this Code.
(Amd) 1.4.5
Each application for variance to allow for an alternative fire protection feature shall be filed with the Fire Safety Code Board of Appeal and Review pursuant to the provisions of the Fire Safety Code §1.7.1 of this Subchapter
et seq
. and R.I. Gen. Laws Chapter 23-28.3. Each application shall further be accompanied by such evidence, letters, statements, results of tests, or other supporting information as may be required to justify the request. The Fire Safety Code Board of Appeal and Review shall keep a record of all actions on such applications in accordance with its records retention schedule. A written comprehensive Decision shall be signed by both the Chairperson, or the Board Member who chaired the hearing, and the Executive Director who drafted the Decision for the Board's approval. A signed Decision shall be forwarded to the Applicant, the State Fire Marshal and the local fire officials. Unless specifically noted to the contrary, the effective date of the Decision shall be the mailing date listed therein.
(Amd) 1.4.6 Approval.
The Fire Safety Code Board of Appeal and Review may approve such alternative construction systems, materials, or methods of design when it is substantiated that the standards of this Code are at least comparable. If, in the opinion of the Fire Safety Code Board of Appeal and Review, the standards of this Code shall not be made comparable by the alternative requested, the requested relief shall not be granted. Consideration shall also be given to test or prototype installations.
(Amd) 1.6 Enforcement.
This Code shall be administered by the Fire Safety Code Board of Appeal and Review and enforced by the State Fire Marshal.
(Add) 1.6.1 Enforcement Jurisdiction.
The State Fire Marshal is the sole authority having jurisdiction for the strict enforcement of the provisions of this code. The State Fire Marshal shall have authority to appoint and certify as many Deputy State Fire Marshals and Assistant Deputy State Fire Marshals as are deemed necessary to strictly enforce the provisions of this Code. All such Deputy State Fire Marshals and Assistant Deputy State Fire Marshals maintain their certification at the pleasure of the State Fire Marshal. Accordingly, all Deputy State Fire Marshals and Assistant Deputy State Fire Marshals shall be allowed to enforce this code as long as they maintain their certification in the above positions by the State Fire Marshal.
(Amd) 1.7.1 Administration Jurisdiction.
The Fire Safety Code Board of Appeal and Review is the sole authority having jurisdiction for the administration of this Code. Accordingly, the Fire Safety Code Board of Appeal and Review is the sole authority having jurisdiction to grant variances, waivers and amendments from, or to review and accept any proposed fire safety equivalencies and alternatives to, the strict adherence to the provisions of this Code and all referenced standards herein. With the exception of "AHJ Modifications" as outlined in §1.4.3 above, all other exceptions listed in this Code, and its referenced standards, allowing for a discretionary waiver by the authority having jurisdiction, shall be referred directly to the Fire Safety Code Board of Appeal and Review as outlined in Fire Safety Code, §1.7.1 of this Subchapter
et seq
.
(Amd) 1.7.3.1 The Fire Safety Code Board of Appeal and Review is the sole authority to render interpretations of this Code and to make Rules and supplemental Regulations in order to carry out the application and intent of its provisions.
(Amd) 1.7.5 Delegation of Authority.
The State Fire Marshal may delegate to his or her Deputy State Fire Marshals, Division Chiefs, other members of the staff, and any other qualified individuals, such powers as are necessary for the proper enforcement of the Code. The Fire Safety Code Board of Appeal and Review may delegate to its appointed staff such powers as are necessary for the proper administration of this Code.
(Amd) 1.7.7.1
The State Fire Marshal is authorized to inspect, at all reasonable times, any building or premises for dangerous or hazardous conditions or materials as set forth in this Code and the general provisions of the Fire Safety Code. The State Fire Marshal may order any person(s) to remove or remedy such dangerous or hazardous condition or material. Any person(s) failing to comply with such an order shall be in violation of the Fire Safety Code. Any person so charged with a violation of the Fire Safety Code shall have the right to appeal the order of the State Fire Marshal to the Fire Safety Code Board of Appeal and Review. An appeal shall automatically stay the State Fire Marshal's order. However, where the State Fire Marshal, or his or her designee, advises that such an automatic stay would endanger the public and/or the owner's tenants or employees, the chairperson of the board, or his or her designee, may, for such good cause shown, suspend the automatic stay of the State Fire Marshal's order pending review by the full Board.
(Amd) 1.7.7.2 Abatement.
The State Fire Marshal, or his or her designee within the division, or an Assistant Deputy State Fire Marshal in accordance with the guidelines established by the State Fire Marshal, has the authority to summarily abate any condition which presents immediate danger to life. The conditions that present an "immediate danger to life" are outlined under the definition of "abatement or to abate a condition" found in fire safety code §
											1.5     of this Subchapter. A failure to abate a condition that presents a clear and immediate danger to life shall be grounds for the person issuing the order to abate, to require that the premises be vacated. Any such order to vacate the premises shall be approved in writing by either the State Fire Marshal or a designee of the State Fire Marshal who has been given advanced written authority by the State Fire Marshal to approve such actions.
(Add) 1.7.7.2.1 Appeal of Abatement.
Any person subject to the abatement procedure as outlined in §1.7.6.2, shall have the right to appeal the order of the State Fire Marshal to the Fire Safety Code Board of Appeal and Review. An appeal does not automatically stay the State Fire Marshal's order. However, the Chairperson of the Board, or his or her designee, may, for good cause shown, stay the order of the State Fire Marshal pending review by the full Board.
(Amd) 1.7.7.6
Persons authorized to enter and inspect buildings, marine vessels and premises as herein set forth shall be identified by credentials recognized by the State Fire Marshal.
(Amd) 1.10 Fire Safety Code Board of Appeal and Review.
(Amd) 1.10.1
The Fire Safety Code Board of Appeal and Review was originally created in 1966 as the Fire Safety Code Commission and is currently authorized and maintained pursuant to R.I. Gen. Laws §
											23-28.3-2.
(Amd) 1.10.1.1.1
The members of the Fire Safety Code Board of Appeal and Review are appointed pursuant to R.I. Gen. Laws §
											23-28.3-2(a)  and Fire Safety Code §
											1.6(A)     of this Subchapter.
(Amd) 1.10.1.1.2
The current composition of the Fire Safety Code Board of Appeal and Review is outlined in R.I. Gen. Laws §
											23-28.3-2(a)  and Fire Safety Code §
											1.6(A)     of this Subchapter.
(Amd) 1.10.1.1.2.1
Procedures, adopted by the Fire Safety Code Board of Appeal and Review, addressing administrative appeals, are outlined in Fire Safety Code, §1.7.1 of this Subchapter.
(Amd) 1.10.1.1.3
Procedures, adopted by the Fire Safety Code Board of Appeal and Review, addressing administrative hearings and court appeals, are outlined in Fire Safety Code §§1.7.2(A) through (BB) of this Subchapter.
(Amd) 1.10.1.1.4
Procedures, adopted by the Fire Safety Code Board of Appeal and Review, addressing the Fire Board's rulemaking authority, are outlined in Fire Safety Code §1.7.3 of this Subchapter.
(Amd) 1.10.1.1.5
Procedures, adopted by the Fire Safety Code Board of Appeal and Review, addressing code interpretation by the Fire Board, are outlined in Fire Safety Code §1.7.4 of this Subchapter.
(Amd) 1.10.1.1.5.1
Members of the Fire Safety Code Board of Appeal and Review shall comply with the Rhode Island Code of Ethics, as outlined in R.I. Gen. Laws §
											36-14-1
et seq
., and all relevant advisory opinions and/or decisions rendered by the Rhode Island Ethics Commission.
(Amd) 1.10.1.1.5.2
Members of the Fire Safety Code Board of Appeal and Review shall be residents of the State.
(Amd) 1.10.1.1.5.3
Members of the Fire Safety Code Board of Appeal and Review shall be composed of individuals experienced in the fields and professions as outlined in Fire Safety Code, §
											1.6(A)     of this Subchapter.
(Amd) 1.10.1.1.6
Members of the Fire Safety Code Board of Appeal and Review shall be selected and appointed pursuant to R.I. Gen. Laws §
											23-28.3-2.
(Amd) 1.10.1.1.7
Members of the Fire Safety Code Board of Appeal and Review shall not sit in judgment and vote on any case in which the member, personally, is directly interested or has a potential conflict of interest. If the actual interest of the member is unclear, the member should recuse and not participate, and then request an advisory opinion from State Ethics Commission prior to participating in comparable cases in the future.
(Amd) 1.10.1.1.8
The Governor shall designate one (1) member as Chairperson pursuant to R.I. Gen. Laws §
											23-28.3-2. The Chairperson shall then designate one (1) member as Vice Chairperson subject to confirmation by the Board.
(Amd) 1.10.3.4
The Fire Safety Code Board of Appeal and Review shall have the authority to waive any requirement(s) of the code pursuant to a comprehensive plan of action as outlined in a written Decision after a hearing and vote on the matter.
(Amd) 1.10.4.1
Any building owner or operator of any regulated process or hazardous activity may request a variance from the Fire Safety Code Board of Appeal and Review in accordance with R.I. Gen. Laws §
											23-28.3-5 and its referenced standards.
(Amd) 1.10.4.2
An appeal shall be submitted to the Fire Safety Code Board of Appeal and Review pursuant to the Fire Board procedures outlined in Section 6 of the Fire Safety Code, Part 1 of this Subchapter and R.I. Gen. Laws §
											23-28.3-5.
(Amd) 1.10.4.3
Any documentation that either the Applicant or the AHJ wishes to rely upon during their scheduled hearing shall be submitted to the Fire Board, and the opposing side, at least seven (7) calendar days prior to their scheduled Fire Safety Code Board of Appeal and Review hearing. This requirement may be either shortened or waived by the Fire Board for good cause shown.
(Amd) 1.10.5.1
Depending upon its case load, the Fire Safety Code Board of Appeal and Review generally meets at least once each week in formal session and throughout the year in subcommittee sessions. All formal meetings are conducted pursuant to the Rhode Island Administrative Procedures Act (R.I. Gen. Laws §
											42-35-1
et seq
.) and notice is provided pursuant to the Rhode Island Open Meetings Act (R.I. Gen. Laws §
											42-46-1
et seq
.)
(Amd) 1.10.5.1.1
Notice is hereby provided, pursuant to R.I. Gen. Laws §
											42-46-6(a), that the formal meetings of the Fire Safety Code Board of Appeal and Review are currently scheduled on Tuesday afternoons at 1:00 P.M. The time and location of the meetings are subject to change in the future. Accordingly, please consult the board website at
www.fsc.ri.gov
for specific public notice and any additional information regarding the formal weekly hearings. Hearings are also posted on the Rhode Island Secretary of State's website at
http://sos.ri.gov/
.
(Amd) 1.10.5.4
The Fire Board of Appeal and Review shall keep records of its examinations, correspondence, files, meeting minutes, decisions and other official actions in accordance with its approved Records Retention Schedule.
(Amd) 1.10.5.6
A quorum of the Board shall consist of not less than five (5) members.
(Amd) 1.10.5.7
In varying the application of any provision of this Code, or in modifying an order of the AHJ, a majority vote by members present with at least five (5) members in accord shall be required.
(Amd) 1.10.6.4
Copies of the Decision shall be sent by mail or delivered in person to the Applicant, the State Fire Marshal's Office, and the local Fire Marshal or Department having territorial jurisdiction over the subject property or process.
(Amd) 1.11.1
The State Fire Marshal shall maintain a properly indexed record of all variances, issued on or after January 1, 2004, in his or her office pursuant to R.I. Gen. Laws §
											23-28.3-5(b). This record shall be open to the public for inspection.
(Add) 1.11.2.1
Enforcement powers of Deputy State Fire Marshals and Assistant Deputy State Fire Marshals shall be exercised in such a manner as to avoid duplication of effort by the building owner. The Deputy State Fire Marshals and Assistant Deputy State Fire Marshals shall provide the building owner with a single written inspection report detailing the fire safety requirements necessary to bring the building into full compliance with the Rhode Island Fire Safety Code. If a building owner receives an initial written inspection report listing all of the cited fire safety deficiencies in the building, and new non-abatable deficiencies are detected within the subsequent twelve (12) months, upon written notification thereof, the building owner is urged to correct such deficiencies as soon as practical, but shall have a period of twelve (12) months from the original inspection report to correct said newly detected deficiencies. The above time extension shall not apply to the issuance of "citations" pursuant to R.I. Gen. Laws §
											23-28.2-14 or issues being addressed by the abatement procedure outlined in §1.7.6.2.
(Add) 1.11.2.2
The State Fire Marshal shall make quarterly continuing educational programs available to all Assistant Deputy State Fire Marshals who shall be required to annually attend a minimum of two (2) such continuing educational programs in order to maintain their Assistant Deputy State Fire Marshal status. The above quarterly continuing educational programs shall be in addition to any training sessions deemed mandatory by the State Fire Marshal. The quarterly continuing educational programs may be conducted by outside groups with the approval of the State Fire Marshal.
(Add) 1.11.2.3
The State Fire Marshal shall provide all Assistant Deputy State Fire Marshals with sufficient copies of a brochure explaining the inspection process and outlining the obligations and rights, including all appeal rights, of building owners under the State Fire Code. The Assistant Deputy State Fire Marshal shall provide the building owner, or onsite representative, with a copy of this brochure during the initial inspection of the building. A second (2nd) copy of the brochure shall accompany the initial written inspection report generated as a result of the above building inspection.
(Amd) 1.12.6.1
Only the State Fire Marshal, and those Deputies and Assistant Deputy State Fire Marshals specifically authorized by the office of the State Fire Marshal, shall be granted the authority to issue the permits listed under this Code. The State Fire Marshal shall not be required to issue any of the permits listed under this Code unless he or she first determines that listed permit is necessary and that there are sufficient fiscal and personnel resources available for the uniform and consistent administration of the specific permit program.
(Amd) 1.14.1
Construction documents shall be submitted, reviewed, and approved for all new construction, modification, or rehabilitation, projects prior to the start of such work as provided in §1.14, unless any or all of these requirements are specifically waived herein. These requirements may also be waived by the AHJ.
(Amd) 1.14.2
Unless specifically waived in writing by the AHJ, the applicant shall be responsible to ensure that the following conditions are met:
1. The construction documents include all of the fire protection requirements.
2. The shop drawings are correct and in compliance with the applicable codes and standards.
3. The contractor maintains an approved set of construction documents on site.
4. Up to five (5) sets of paper drawings and a project manual shall be submitted to the AHJ unless this requirement is specifically waived by the State Fire Marshal's Office or the AHJ conducting the plan review.
(Amd) 1.14.3
Applications for plan review shall be made in the system designated by the State Fire Marshal's Office.
(Add) 1.14.3.1
The Application for plan review by the State Fire Marshal's Office shall be accompanied by a plan review fee in accordance with either §1.14.3.2 for one (1), two (2), and three (3) family homes or §1.14.3.3 for commercial projects.
(Add) 1.14.3.2
Plan review and inspection for the installation of smoke detection and/or carbon monoxide detection in any new and existing private dwelling occupied by one (1), two (2), and three (3) families shall be in accordance with R.I. Gen. Laws §
												23-28.1-2(b)(2)(ii).
(Add) 1.14.3.3
Every request for plan review by the State Fire Marshal's Office, under the provisions of the Rhode Island Fire Safety Code, shall be accompanied by the fee prescribed in accordance with R.I. Gen. Laws §
												23-28.2-26.
(Add) 1.14.3.3.1
All fees collected by the State Fire Marshal pursuant to §§1.14.3.2 or 1.14.3.3 shall be deposited as outlined in R.I. Gen. Laws §
												23-28.2-26.
(Add) 1.14.3.4
Plan review fees, not exceeding the amounts listed in §§1.14.3.2 and 1.14.3.3, may be collected by the Assistant Deputy Fire Marshals of the municipal fire departments and/or fire districts, pursuant to municipal ordinance, only upon their completion of the plan review process. All such fees shall be utilized exclusively for supporting the operations of the municipal fire prevention bureau. Nothing herein shall preclude an AHJ, performing an inspection, pursuant to either Rhode Island Life Safety Code (RILSC) §§24.6.3.1 .3.1 or 25.2.2.3.1, from being paid at the time of that inspection.
(Add) 1.14.3.5
At the request of either the applicant or the AHJ, a preliminary meeting shall be held with the applicant and the AHJ at the time of the submittal. The purpose of the meeting is to discuss the scope of the project, check that the correct codes were used, check that the plans have been stamped, and to ensure that all necessary paperwork is included with the submittal. At this time, if all of the above are not correct, the plans shall not be accepted by the AHJ and the AHJ shall immediately advise the applicant in writing of the specific deficiencies which must be addressed prior to re-submittal.
(Amd) 1.14.4
The AHJ shall either approve or render a written report to the applicant stating all of the reason(s) why the submitted construction documents cannot be approved within the following timeframes:
(Add) 1.14.4.1
One (1), two (2), and three (3) family homes shall be completed within fifteen (15) business days of receipt.
(Add) 1.14.4.2
All fire alarm plans shall be reviewed and either approved or disapproved, with full explanation, within fifteen (15) business days of submission of the plans. Fire alarm plans for existing buildings shall be limited to that portion of the building either under construction or renovation unless the State Fire Marshal specifically approves, in writing, an expanded scope of plan review. If the plans are not reviewed and approved within the above fifteen (15) business day period the project shall be allowed to proceed. The AHJ shall immediately submit written notification to the building official overseeing the project and advise that a building permit should issue pursuant to the understanding that the owner and/or contractor may proceed with the project at his or her own risk.
(Add) 1.14.4.3
Projects meeting all the requirements of §§1.14.4.3(1) through 1.14.4.3(5) shall be completed within twenty (20) business days of receipt:
1. Overall construction cost of under five hundred thousand dollars ($500,000.00);
2. No change in occupancy;
3. No change in square footage of the building or occupant load;
4. Renovations not affecting egress routes and/or exits;
5. Life safety systems are compliant with no major alterations proposed.
(Add) 1.14.4.3.1
For purposes of §1.14.4.3(5) a compliant fire alarm system is defined as a system allowed to be maintained in the facility pursuant to RILSC Chapter 9.6 and its referenced standards.
(Add) 1.14.4.3.2
For purposes of §1.14.4.3(5) major alterations are defined as:
1. Twenty (20) or more sprinkler heads being added or relocated;
2. Ten (10) or more fire alarm devices or appliances being added or relocated;
3. Ceiling heights being reconfigured.
(Add) 1.14.4.4
Projects that have an overall cost of construction of five hundred thousand dollars ($500,000.00) or more but less than ten million dollars ($10,000,000.00) shall be completed within thirty (30) business days of receipt.
(Add) 1.14.4.5
All other projects, not meeting §§1.14.4.1, 1.14.4.2, 1.14.4.3 or 1.14.4.4, shall be completed within forty (40) business days of receipt.
(Add) 1.14.4.6
When required by the AHJ, revised construction documents or shop drawings shall be prepared and submitted for review and approval to illustrate corrections as required by the written report in §1.14.4 . The corrections shall be re-reviewed by the AHJ within ten (10) business days of receipt.
(Add) 1.14.4.7
For good cause shown, the State Fire Marshal may extend any of the timelines, outlined in §§1.14.4.1 through 1.14.4.6, provided that such an extension is reduced to writing and issued to both the applicant and the AHJ. In the absence of such an extension, the project shall be allowed to proceed once the above applicable time limit for plan review has been reached. Specifically, at the conclusion of the above applicable time limit, the AHJ shall immediately submit written notification to the building official overseeing the project and advise that a building permit should issue pursuant to the understanding that the owner and/or contractor may proceed with the project at his or her own risk.
(Add) 1.14.4.8
Review and approval by the AHJ, or default submission to the building official pursuant to §§1.14.4.2 or 1.14.4.7, shall not relieve the applicant of the responsibility of full compliance with this Code and/or any other codes or Regulations which must be met by the applicant prior to the completion of the project.
(Add) 1.14.4.9
The AHJ shall have the discretion to waive the examination and approval of drawings when plans for the erection or alteration of a building, or its fire protection systems, are prepared by a professional engineer or registered architect who is either licensed or registered by the State of Rhode Island, and the professional engineer or architect has stated in writing that he or she has supervised the preparation of all design and technical documents and that he or she will review and approve all work drawings for the construction, and that the document shall, to the best of his or her knowledge, conform to all provisions of this code and all rules and regulations adopted under its provisions. In such a case, where the AHJ chooses to waive examination of the plans, the AHJ shall immediately submit written notification to the building official overseeing the project and advise that a building permit should be issued pursuant to the understanding that the owner and/or contractor may proceed with the project at his or her own risk as outlined above.
(Add) 1.14.4.10
The AHJ may waive the detailed department field inspection when the abovedescribed professional engineer or architect certifies that the construction work will be built under his or her field observations and in accordance with the approved contract documents, and that he or she will certify to the best of his or her knowledge, Information and belief that the construction is in compliance with the approved plans and the code.
(Add) 1.14.7
Where phased approval or approval in part is sought by the applicant pursuant to 510-RICR- 00-00-1, SBC-  1, §106.3.3 or other applicable sections of the Building Code, a plan review letter of approval shall not be required for a fire protection system in order to obtain phased approval status from the Building Code Official. However, plans or shop drawings shall be submitted, reviewed, and approved prior to the start of work on those fire protection systems. The holder of a phased approval permit for the foundation or other parts of a building or structure shall proceed at the holder's own risk with the building operation and without assurance that a permit or plan review approval for fire code compliance will be granted. Phased approval shall not relieve the applicant of the responsibility of providing such temporary fire protection as may be required by other sections of the State Fire Safety Code.
(Add) 1.14.7
When any plan review is appealed, or when any variance request relates to a current or proposed future plan review, the State or local Fire Marshal conducting, or ultimately responsible for, the plan review shall, upon request of the Fire Safety Code Board of Appeal and Review, appear before the Board and advise the Board as to the position of the applicable State or local Fire Marshal's Office. In this case, if a written plan review is not currently available, the State or local Fire Marshal shall not be required to submit written documentation for the case to proceed.
(Amd) 1.15.1
Where pre-approved by the State Fire Marshal, the AHJ shall be permitted to require a review by an approved independent third (3rd) party with expertise in the matter to be reviewed at the submitter's expense.
(Amd) 1.16.4.1
Any person who fails to comply with the provisions of this Code, fails to carry out an order made pursuant to this Code, or violates any condition attached to a permit, approval or certificate shall be subject to the penalties set forth in the Rhode Island State Fire Safety Code.
(Res) 1.16.4.2
Reserved for future consideration by the Fire Safety Code Board of Appeal and and Review.
(Res) 1.16.4.3
Reserved for future consideration by the Fire Safety Code Board of Appeal and and Review.
(Amd) 1.16.5
Where a violation creates an imminent danger, the AHJ is authorized to abate such hazard in accordance with §1.7.7.2.
(Res) 1.17
Reserved for future consideration by the Fire Safety Code Board of Appeal and Review.