reglab/statecodes huggingface dataset:
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:46 - Repair of minor cracks and imperfections

Current through Register Vol. 51, page 10, July 15, 2024
Minor cracks, isolated pits, and small plate imperfections must be examined to determine the extent of the defect and whether or not repair by welding is required. Prior to repair by welding, the defects must be removed to sound metal.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:47 - Repair of cracks radiating from holes

Current through Register Vol. 51, page 10, July 15, 2024
Cracks radiating from staybolt or rivet holes may be repaired if the plate is not seriously damaged.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:48 - Repair of welded butt joints

Current through Register Vol. 51, page 10, July 15, 2024
Welded butt joints must have complete penetration and fusion for the full length of the weld. The surfaces of the weld may be left as welded, if they are sufficiently free from coarse ripples and valleys to avoid stress concentration points. The owner may not overlay a weakened area with a patch.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:49 - Repair of wasted surfaces

Current through Register Vol. 51, page 10, July 15, 2024
Wasted surfaces in stayed or unstayed areas may be built up by welding if, in the judgment of the inspector, the structural strength will be adequate.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:50 - Welding on butt straps

Current through Register Vol. 51, page 10, July 15, 2024
Welding may be used to restore the original dimensions of the edges of butt straps, plated laps, or connections attached by riveting; however, prior approval by the inspector is required.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:51 - Staybolt replacement

Current through Register Vol. 51, page 10, July 15, 2024
Threaded staybolts may be replaced by welded-in stays if, in the judgment of the inspector, the area adjacent to the staybolt has not been seriously weakened by deterioration.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:52 - Inspection of welds

Current through Register Vol. 51, page 10, July 15, 2024
Completed welds must be inspected for appearance and unsatisfactory conditions, such as cracks, excessive reinforcement, and undercutting.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:53 - Approval of major repairs and report

Current through Register Vol. 51, page 10, July 15, 2024
All major repairs must be approved by the inspector before the start of the work. The inspector may inspect the work while it is in progress. Any defects in the repair work must be discussed with the owner, and recommendations for corrective action must be made at this time and noted in the Report of Welded or Riveted Repairs. The inspector shall forward this report to the Office of the Fire Marshal, the chief boiler inspector, and the owner of the boiler.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:54 - Requirements for construction of new boilers

Current through Register Vol. 51, page 10, July 15, 2024
Each new boiler shall conform to Section I, 2021
ASME Boiler & Pressure Vessel Code
. A record must be maintained by the owner of all materials used in the construction of any portion of the boiler that is under pressure. These records must include the type of welding rod and welding equipment used, the source of the boiler plate and rivets, and the thickness of the materials used.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
Section I, 2021
ASME Boiler & Pressure Vessel Code
. Copies may be obtained from the American Society of Mechanical Engineers, Two Park Avenue, New York, NY 10016. Cost is $508 plus handling charges.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Section 61:08:09:55 - Qualifications of inspectors

Current through Register Vol. 51, page 10, July 15, 2024
Anyone who holds a commission as an inspector pursuant to RCI-1, 2021
National Board Inspection Code
, may obtain authority to inspect historic boilers in South Dakota by providing written evidence of the commission to the State Fire Marshal's Office. Authority to inspect historic boilers in South Dakota expires upon expiration of the inspector's National Board commission.
General Authority:
SDCL  34-29A-14.1.
Law Implemented:
SDCL  34-29A-14.1.
2021
National Board Inspection Code
. Copies may be obtained from the National Board of Boiler and Pressure Vessel Inspectors, 1055 Crupper Avenue, Columbus, OH 43229-1183. Cost is $325 plus shipping and handling charges.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:08 - Boilers › Chapter 61:08:09 - Historic power boilers › Appendix A - Guide to Riveted Joint Efficiencies

Current through Register Vol. 51, page 10, July 15, 2024
APPENDIX A
A GUIDE TO RIVETED JOINT EFFICIENCIES
The following table of efficiencies shows the
average
for the different types of joints. The values are only approximate because the efficiency depends on the ultimate strength of the plate and rivet, the thickness of the plates, and the diameter of the rivets.
Type of Riveting
Lap
Butt
Single
58
Double
70
82
Triple
74
88
Quadruple
94
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:01 - Conformity with national standards

Current through Register Vol. 51, page 10, July 15, 2024
The standards of fire safety set forth in the
International Building Code
, 2015 edition;
International Fire Code
, 2015 edition; and the
International Mechanical Code
, 2015 edition; and referenced standards, except as modified, amended, or deleted in this chapter, are the rules of the South Dakota Department of Public Safety authorized by SDCL  34-29B-2.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
International Mechanical Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $72.00 for members and $96.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:02 - Deletions from the International Fire Code

Current through Register Vol. 51, page 10, July 15, 2024
Sections 102.5, 103 to 106.4, inclusive, sections 903.2.6 are deleted from the
International Fire Code
, 2015 edition.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:03 - Deletions from the International Building Code

Current through Register Vol. 51, page 10, July 15, 2024
Sections 101.4 to 101.4.5, inclusive, 103 to 106.3, inclusive, 109 to 113.3, inclusive, and 903.2.6 are deleted from the
International Building Code
, 2015 edition.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:05 - Amendments to the International Building Code

Current through Register Vol. 51, page 10, July 15, 2024
Amendments to the
International Building Code
, 2015 edition, are as follows:
(1) Where the International Building Code references NFPA 13, "Standard for the Installation of Sprinkler Systems," the 2013 edition is the standard to be used;
(2) Where the International Building Code references NFPA 14, "Standard for the Installation of Standpipe and Hose Systems," the 2013 edition is the standard to be used; and
(3) Where the International Building Code references NFPA 13R, "Standard for the Installation of Sprinkler Systems in Residential Occupancies Up to and Including Four Stories in Height," the 2013 edition is the standard to be used.
(4) Where the International Building Code references the "International Energy Conservation Code" the 2009 edition is the standard to be used.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
NFPA 13, "Standard for the Installation of Sprinkler Systems," 2013 edition, National Fire Protection Association. Copies may be obtained from the National Fire Protection Association, 1 Batterymarch Park, Quincy, Massachusetts 02169-9101; $92.70 for members and $103.00 for nonmembers.
NFPA 14, "Standard for the Installation of Standpipe and Hose Systems," 2013 edition, National Fire Protection Association. Copies may be obtained from the National Fire Protection Association, 1 Batterymarch Park, Quincy, Massachusetts 02169-9101; $41.40 for members and $46.00 for nonmembers.
NFPA 13R, "Standard for the Installation of Sprinkler Systems in Residential Occupancies Up to and Including Four Stories in Height," 2013 edition, National Fire Protection Association. Copies may be obtained from the National Fire Protection Association, 1 Batterymarch Park, Quincy, Massachusetts 02169-9101; $41.40 for members and $46.00 for nonmembers.
International Energy Conservation Code,
2009 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $32.00 for members and $42.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:06 - Fire safety for flammable liquids and liquefied petroleum gases

Current through Register Vol. 51, page 10, July 15, 2024
The manufacture, transportation, storage, and use of combustible and flammable liquids and liquefied petroleum gases shall conform to the requirements specified in chapter 61:15:03 and in chapter 57 and chapter 61 of the
International Fire Code
, 2015 edition.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:08 - Residential flammable liquid storage tanks and liquefied petroleum gas installations

Current through Register Vol. 51, page 10, July 15, 2024
Residential combustible liquid storage tanks and liquefied petroleum gas installations of less than 2,000 gallons water capacity are not required to submit plans for review by the Department of Public Safety. This does not relieve the installer from meeting the requirements for installation as specified by the
International Mechanical Code
, 2015 edition, the
International Fire Code
, 2015 edition, or more stringent local requirements.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Mechanical Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $72.00 for members and $96.00 for nonmembers. Telephone: 1-888-422 -7233.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:09 - Maintenance of exits and emergency escapes

Current through Register Vol. 51, page 10, July 15, 2024
The number of required exits for a building or each level of a building shall meet the requirements of section 1031 of the International Fire Code, 2015 edition. Each exit conforming to the requirements of the building code under the exit was constructed may be considered as a complying exit if, in the opinion of the authority having jurisdiction, the exit does not constitute a distinct hazard to life. The fire-resistive rating of any wall, ceiling, or opening that is part of an exit shall meet the minimum requirements of this chapter. No obstruction, including storage, may be placed in the required width of an exit. No exit may be obstructed in any manner. Each exit shall remain free of any material or matter whose presence would make the exit hazardous.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:10 - Exit requirements for existing buildings other than high-rise buildings

Current through Register Vol. 51, page 10, July 15, 2024
Every floor above the first story used for human occupancy in existing buildings other than high-rise buildings shall have access to at least two separate exits, one of which may be an exterior fire escape complying with this chapter. In all occupancies, except day care, second stories with an occupant load of 10 or less may have one exit. All required stairs shall have a minimum run of 9 inches and a maximum rise of 8 inches and shall have a minimum width of 30 inches exclusive of handrails. Every stairway shall have at least one handrail. A landing having a minimum 30-inch run in the direction of travel shall be provided at each point of access to the stairway. Fire escape stairs shall be of noncombustible construction.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:12 - Existing fire escapes

Current through Register Vol. 51, page 10, July 15, 2024
Existing fire escapes which, in the opinion of the fire official, comply with the intent of this chapter, may be used as one of the required exits. Fire escapes shall comply with the following:
(1) All openings in the exterior wall below and within 10 feet of a fire escape stair serving a building over two stories high shall be protected by a self-closing fire assembly having a 3/4-hour fire protection rating;
(2) Egress from the building shall be by a clear opening of not less than 20 inches wide, 24 inches high, and 5.7 square feet in area. The bottom of the opening shall be not more than 44 inches above the floor of the building or balcony;
(3) Fire escape stairways and balconies shall support the dead load plus a live load of not less than 100 pounds per square foot and shall be provided with a top and intermediate handrail on each side. The pitch of the stairway may not exceed 60 degrees with a minimum width of 18 inches. Treads may not be less than 4 inches wide and the rise between treads may not exceed 10 inches. All stair and balcony railings shall support a horizontal force of not less than 50 pounds per lineal foot of railing;
(4) Balconies shall be not less than 44 inches wide with no floor openings other than the stairway opening greater than 5/8 inch wide. Stairway openings in such balconies shall be at least 22 inches by 44 inches. The balustrade of each balcony shall be not less than 36 inches high with not more than 9 inches between balusters;
(5) Fire escapes shall extend to the roof or provide an approved gooseneck ladder between the top floor landing and the roof when serving buildings four or more stories high having roofs with less than 4:12 slope. Fire escape ladders shall be designed and connected to the building to withstand a horizontal force of 100 pounds per lineal foot; each rung shall support a concentrated load of 500 pounds placed anywhere on the rung. All ladders shall be at least 15 inches wide, located within 12 inches of the building, and shall be placed flat to the face of the building. Ladder rungs shall be 3/4 inch in diameter and shall be located 12 inches on center. Openings for roof access ladders through cornices and similar projections shall have minimum dimensions of 30 inches by 33 inches;
(6) The lowest balcony shall be not more than 18 feet from the ground. Fire escapes shall extend to the ground or be provided with counterbalanced stairs reaching to the ground;
(7) Fire escapes may not take the place of stairways required by the codes under which the building was constructed;
(8) Fire escapes shall be kept clear and unobstructed at all times and maintained in good working order.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:13 - The abatement of unsafe buildings or structures

Current through Register Vol. 51, page 10, July 15, 2024
The abatement of unsafe buildings or structures covered by this chapter shall be in accordance with section 116 of the
International Building Code
, 2015 edition. Local jurisdictions may make inspections and take actions as required to enforce the provisions of this section. The Department of Public Safety may provide technical assistance as required to enforce the provisions of this section.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-10,  34-29B-11.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:14 - Smoke detectors required

Current through Register Vol. 51, page 10, July 15, 2024
Each sleeping room of a lodging establishment, as defined in subdivision (7) of SDCL  34-18-1, shall contain smoke detectors installed in accordance with the manufacturer's instructions. In new construction, smoke detectors shall receive their primary power from the building wiring and shall be equipped with a battery backup. The detector shall emit a signal when the batteries are low. Wiring shall be permanent and without a disconnecting switch other than those required for overcurrent protection. Smoke detectors may be solely battery-operated when installed in existing lodging establishments.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:15 - Smoke detectors required in multifamily residences

Current through Register Vol. 51, page 10, July 15, 2024
Each family living unit of a multifamily residence which houses six or more families shall contain at least one smoke detector installed in accordance with the manufacturer's instructions and this section. A smoke detector shall be located on the ceiling or wall of the main room or sleeping room in each dwelling unit of an existing multifamily residence. In new construction each smoke detector shall receive primary power from the building wiring and shall be equipped with a battery backup. Wiring shall be permanent and without a disconnecting switch other than as required for overcurrent protection. If a violation of this section is found, a written notice confirming such findings shall be issued and served upon the owner, operator, or other person responsible for the violation. Any notice or order issued pursuant to this section shall require compliance within 30 days of the date of notice. However, in an existing lodging establishment, each smoke detector may be solely battery-operated.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:16 - Municipal conformity

Current through Register Vol. 51, page 10, July 15, 2024
Nothing in this chapter prohibits municipalities or local fire officials from adopting alternative requirements for
International Fire Code
, 2015 edition, chapters 20, 21, 24 to 27, inclusive, 29, 32, and 51, provided that the alternative requirement meets the intent and spirit of the code.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:17 - Egress requirements

Current through Register Vol. 51, page 10, July 15, 2024
Exits for new hotels, motels, multifamily residences which house six or more families, and congregate residences shall be as specified in chapter 10 of the
International Building Code
, 2015 edition. Access to and egress from buildings required to be accessible to persons with disabilities shall be provided as specified in chapter 11 of the
International Building Code
, 2015 edition. Emergency escape and rescue openings shall be provided as specified in section 1030 of the
International Building Code
, 2015 edition.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:18 - Required draft stops

Current through Register Vol. 51, page 10, July 15, 2024
Draft stops shall be installed in the attics, mansards, overhangs, false fronts set out from walls, and similar concealed spaces of new multifamily residences housing six or more families, hotels, motels, and congregate residences. Such draft stops shall meet the requirements outlined in section 718.4.2 of the
International Building Code
, 2015 edition.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club, Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:01 - Fire safety standards › Section 61:15:01:19 - Automatic sprinkler system requirements

Current through Register Vol. 51, page 10, July 15, 2024
An automatic sprinkler system shall be installed throughout any new hotel, motel, and multi-family residence housing six or more families as specified in section 903 of the International Building Code, 2015 edition.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2,  34-29B-10.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club, Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:02 - School construction requirements › Section 61:15:02:01 - Responsibility of governing boards

Current through Register Vol. 51, page 10, July 15, 2024
The governing board of a school covered by SDCL chapter 13-25 shall inform the Department of Public Safety of its intention to alter or remodel existing structures or to build new facilities to be used for school purposes.
General Authority:
SDCL  13-25-2.
Law Implemented:
SDCL  13-25-1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:02 - School construction requirements › Section 61:15:02:02 - Approval of proposed construction required

Current through Register Vol. 51, page 10, July 15, 2024
The governing body shall advertise no plans and specifications for proposed construction or alteration of school buildings until the plans and specifications have been reviewed by a representative of the Department of Public Safety and approved in writing. Drawings shall be drawn to scale and shall clearly show plot plan sections, elevations, structural details, floor plan, electrical, mechanical, and any other details the department requires.
General Authority:
SDCL  13-25-2.
Law Implemented:
SDCL  13-25-1.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:02 - School construction requirements › Section 61:15:02:03 - Requirements for plans and specifications - New construction

Current through Register Vol. 51, page 10, July 15, 2024
All plans and specifications for new construction shall be in accordance with the
International Building Code
, 2015 edition; the
International Fire Code
, 2015 edition; the
International Mechanical Code
, 2015 edition, and referenced standards, except as modified, amended, or deleted in this chapter. The cover sheet shall clearly state the occupancy group, division, and building type. Failure to designate these is cause for rejection of the plans.
General Authority:
SDCL  13-25-2.
Law Implemented:
SDCL  13-25-1.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
International Mechanical Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $72.00 for members and $96.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:02 - School construction requirements › Section 61:15:02:04 - Requirements for plans and specifications - Remodeling - Unsafe conditions

Current through Register Vol. 51, page 10, July 15, 2024
Any addition, alteration, or repair may be made to any building or structure without requiring the existing building or structure to comply with all the requirements of the
International Building Code
, 2015 edition, if the addition, alteration, or repair conforms to that required for a new building or structure. Any addition or alteration that will cause the existing building or structure to become unsafe may not be made to an existing building or structure. An unsafe condition is considered to have been created if the addition or alteration causes the building or structure to become structurally unsafe or overloaded, will not provide sufficient egress or will obstruct existing exits, will create a fire hazard, will reduce required fire resistance, or will otherwise create conditions dangerous to human life.
General Authority:
SDCL  13-25-2.
Law Implemented:
SDCL  13-25-1.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:02 - School construction requirements › Section 61:15:02:05 - Deletions from International Building Code

Current through Register Vol. 51, page 10, July 15, 2024
Sections 101.4 to 101.4.6, inclusive, 103 to 106.3, inclusive, 109 to 113.3, inclusive, and 903.2.6 are deleted from the
International Building Code
, 2015 edition.
General Authority:
SDCL  13-25-2.
Law Implemented:
SDCL  13-25-1.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:02 - School construction requirements › Section 61:15:02:06 - Deletions from the International Fire Code

Current through Register Vol. 51, page 10, July 15, 2024
Sections 102.5, 103 to 106.4, inclusive, sections 903.2.6 are deleted from the
International Fire Code
, 2015 edition.
General Authority:
SDCL  13-25-2.
Law Implemented:
SDCL  13-25-1.
International Fire Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $92.00 for members and $123.00 for nonmembers. Telephone: 1-888-422 -7233.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:02 - School construction requirements › Section 61:15:02:08 - Amendments to the International Building Code

Current through Register Vol. 51, page 10, July 15, 2024
Amendments to the
International Building Code
, 2015 edition, are as follows:
(1) Where the International Building Code references NFPA 13, "Standard for the Installation of Sprinkler Systems," the 2013 edition is the standard to be used;
(2) Where the International Building Code references NFPA 14, "Standard for the Installation of Standpipe and Hose Systems," the 2013 edition is the standard to be used; and
(3) Where the International Building Code references NFPA 13R, "Standard for the Installation of Sprinkler Systems in Residential Occupancies Up to and Including Four Stories in Height," the 2013 edition is the standard to be used.
General Authority:
SDCL  13-25-2.
Law Implemented:
SDCL  13-25-1.
International Building Code
, 2015 edition, International Code Council. Copies may be obtained from the International Code Council, 4051 West Flossmoor Road, Country Club Hills, IL 60478; $114.00 for members and $152.00 for nonmembers. Telephone: 1-888-422 -7233.
NFPA 13, "Standard for the Installation of Sprinkler Systems," 2013 edition, National Fire Protection Association. Copies may be obtained from the National Fire Association, 1 Batterymarch Park, Quincy, Massachusetts 02169-9101; $92.70 for members and $103.00 for nonmembers.
NFPA 14, "Standard for the Installation of Standpipe and Hose Systems," 2013 edition, National Fire Protection Association. Copies may be obtained from the National Fire Protection Association, 1 Batterymarch Park, Quincy, Massachusetts 02169-9101; $41.40 for members and $46.00 for nonmembers.
NFPA 13R, "Standard for the Installation of Sprinkler Systems in Residential Occupancies Up to and Including Four Stories in Height," 2013 edition, National Fire Protection Association. Copies may be obtained from the National Fire Protection Association, 1 Batterymarch Park, Quincy, Massachusetts 02169-9101; $41.40 for members and $46.00 for nonmembers.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:01 - Blueprints of installations required

Current through Register Vol. 51, page 10, July 15, 2024
Except as provided in §
									61:15:03:06, duplicate copies of drawings or blueprints for any construction or installation for the storage, handling, or use of flammable or combustible liquids or liquefied petroleum gas shall be submitted to the Department of Public Safety for approval. The drawings or blueprints must be drawn to scale and include structural, electrical, plumbing, and mechanical features. Approval is required before any construction or installation may be undertaken in aboveground storage for retail sales, bulk plants, service stations, and processing plants. Within 20 days after receipt of the application with drawings or blueprints, a representative of the Department of Public Safety shall examine them. If the drawings or blueprints conform to the applicable requirements of this chapter, the representative shall approve the application, retain one copy for the files, and return the other copy to the applicant, plus any additional copies submitted by the applicant. If the drawings or blueprints do not conform to the applicable requirements, the representative shall notify the applicant.
General Authority:
SDCL  34-29B-2,  34-38-35.
Law Implemented:
SDCL  34-29B-2,  34-38-24,  34-38-25,  34-38-26.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:02 - Information required on blueprint

Current through Register Vol. 51, page 10, July 15, 2024
Blueprints or drawings shall show the name of the person, firm, or corporation proposing the installation, the location of the installation, and the adjacent streets or highways.
General Authority:
SDCL  34-29B-2,  34-38-35.
Law Implemented:
SDCL  34-29B-2,  34-38-25.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:03 - Drawing requirements for aboveground storage

Current through Register Vol. 51, page 10, July 15, 2024
For aboveground storage, the drawings shall show:
(1) The capacity of each tank;
(2) The dimensions of each tank;
(3) The class of liquid to be stored in each tank;
(4) The type of tank supports;
(5) The clearances between tanks;
(6) The type of venting and pressure relief used and the combined capacity of all venting and pressure relief valves on each tank;
(7) The tank control valves;
(8) The location and type of pump;
(9) Electrical schematic;
(10) Vehicle access;
(11) Method of storage and dispensing; and
(12) Distances from tanks and dispensers to property lines and buildings, fire appliances, collision barriers, and emergency controls.
General Authority:
SDCL  34-29B-2,  34-38-35.
Law Implemented:
SDCL  34-29B-2,  34-38-24,  34-38-25,  34-38-26.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:04 - Drawing requirements for underground storage

Current through Register Vol. 51, page 10, July 15, 2024
For underground systems, the drawings shall show the location and capacity of each tank, and the class of liquid to be stored in the tanks, together with the clearances and requirements and the location of fill, gauge, and vent pipes and other openings.
General Authority:
SDCL  34-29B-2,  34-38-35.
Law Implemented:
SDCL  34-29B-2,  34-38-24,  34-38-25.
Conformity with national standards, §
											61:15:01:01.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:05 - Detail required on drawings and blueprints

Current through Register Vol. 51, page 10, July 15, 2024
Drawings or blueprints for installations for storage, handling, or use of flammable liquids within buildings or enclosures at any establishment or occupancy covered by this section shall show in detail whether applicable requirements are met.
General Authority:
SDCL  34-29B-2,  34-38-35.
Law Implemented:
SDCL  34-29B-2,  34-38-24,  34-38-25.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:06 - Role of local jurisdictions

Current through Register Vol. 51, page 10, July 15, 2024
Drawings or blueprints of a proposed installation shall be first submitted to the applicable local official or governing body. The local official or governing body shall require compliance with the applicable requirements of this chapter and may require compliance with more stringent local requirements. Local approval must be in writing and signed by the head of the local governing body. After local approval has been given, the applicant shall send the approval letter, plans, and specifications to the Department of Public Safety for approval pursuant to §
									61:15:03:01.
General Authority:
SDCL  34-29B-2,  34-38-35.
Law Implemented:
SDCL  34-29B-2,  34-38-25.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:07 - Reasons for denial

Current through Register Vol. 51, page 10, July 15, 2024
In addition to failure to meet the applicable provisions provided by statute, failure to meet the applicable provisions in this article, failure to obtain any variance required by statute, or failure to comply with local regulations, the Department of Public Safety may deny approval for use of aboveground storage tanks at retail locations if there is a false statement or misrepresentation of a material fact in the request or plans on which the request was based or the proposed location is in an area where undue hazard to the safety of the general public can be expected.
General Authority:
SDCL  34-38-35.
Law Implemented:
SDCL  34-38-24,  34-38-25,  34-38-35.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:08 - Delegation of authority to grant uncontested variance

Current through Register Vol. 51, page 10, July 15, 2024
If no petition in opposition is filed pursuant to §
									61:15:03:09, the Department of Public Safety may grant a variance pursuant to SDCL  34-38-39. A variance may be granted no sooner than 20 days after publication of the variance notice. Petitions filed in support of a variance may not result in a hearing; however, the petitioner will receive notice if a hearing is to be held.
General Authority:
SDCL  34-38-35.
Law Implemented:
SDCL  34-38-25,  34-38-35,  34-38-39.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:03 - Flammable gases and liquids blueprints › Section 61:15:03:09 - Deadline to file petitions

Current through Register Vol. 51, page 10, July 15, 2024
Petitions filed to oppose or support a variance request must be served by first class mail or personally delivered to the Department of Public Safety and the variance applicant. Mail must be postmarked or personal delivery must occur at least 10 days before the published date of the hearing. If the 10th day is a Saturday, Sunday, or legal holiday, petitions must be postmarked or personally delivered to the Department of Public Safety by the next working day.
General Authority:
SDCL  34-38-35.
Law Implemented:
SDCL  34-38-25,  34-38-35,  34-38-39.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:04 - Automatic school fire alarm tie-in › Section 61:15:04:01 - Requirements for signaling devices for public school attendance centers

Current through Register Vol. 51, page 10, July 15, 2024
Public school attendance centers with fire alarm systems shall be monitored by a central, proprietary, or remote station service or a local alarm which gives audible and visual signals at a constantly attended location.
General Authority:
SDCL  13-25-2,  13-25-13.
Law Implemented:
SDCL  13-25-11 to  13-25-13.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:04 - Automatic school fire alarm tie-in › Section 61:15:04:03 - Alternative requirements for signaling devices for public school attendance centers

Current through Register Vol. 51, page 10, July 15, 2024
To comply with SDCL  13-25-11 to  13-25-13, inclusive, public school attendance centers may either install signaling devices that comply with §
									61:15:04:01  or automatic telephone dialing devices directly connected to the local fire department dispatch system. Automatic telephone dialing devices used to transmit an emergency alarm may not be connected to any fire department telephone number unless the connection is approved by the fire chief.
General Authority:
SDCL  13-25-2,  13-25-13.
Law Implemented:
SDCL  13-25-11 to  13-25-13.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:04 - Automatic school fire alarm tie-in › Section 61:15:04:04 - Automatic telephone dialing device defined

Current through Register Vol. 51, page 10, July 15, 2024
An automatic telephone dialing device is a device located at the protected premise to which initiation devices are connected. When an initiation device activates the dialer, the dialer must seize a telephone line, dial a preselected number, and transmit a voice message over the telephone line.
General Authority:
SDCL  13-25-2,  13-25-13.
Law Implemented:
SDCL  13-25-11 to  13-25-13.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:05 - Day care center construction requirements › Section 61:15:05:01 - Definition of day care center

Current through Register Vol. 51, page 10, July 15, 2024
A day care center is any facility as defined in SDCL  26-6-14(3)  providing group care and supervision for 21 or more children.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:05 - Day care center construction requirements › Section 61:15:05:02 - Responsibility of day care proprietors

Current through Register Vol. 51, page 10, July 15, 2024
A day care proprietor intending to alter, remodel, or build new facilities to be used for day care purposes shall inform the Office of the State Fire Marshal and the Department of Social Services of that intention.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:05 - Day care center construction requirements › Section 61:15:05:03 - Approval of proposed construction required

Current through Register Vol. 51, page 10, July 15, 2024
A day care proprietor may not begin proposed construction until the plans and specifications have been reviewed locally and by a representative of the Department of Public Safety and approved in writing. Drawings shall be drawn to scale and shall clearly show plot plan sections, elevations, structural details, floor plan, electrical, mechanical, and any other details the department may require.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2.
South Dakota Administrative Rules › Title 61 - Department of Public Safety › Article 61:15 - Fire safety › Chapter 61:15:05 - Day care center construction requirements › Section 61:15:05:04 - Construction requirements

Current through Register Vol. 51, page 10, July 15, 2024
New construction of and any addition to a day care center, remodeling of an existing day care center, and remodeling of any existing building to be used as a day care center must be in accordance with this chapter.
General Authority:
SDCL  34-29B-2.
Law Implemented:
SDCL  34-29B-2.