reglab/statecodes huggingface dataset:
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 1 - General Provisions › Part 19 - OPERATOR TRAINING › Section 165:25-1-120 - Training requirements

Current through Vol. 41, No. 20, July 1, 2024
Each underground storage tank system or group of
					 underground storage tank systems at a facility must have a Class A, Class B,
					 and Class C operator designated. Separate individuals may be designated for
					 each class of operator or an individual may be designated to more than one of
					 the operator classes. A Class A and Class B operator are required for TOU
					 tanks.
Added at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 1 - General Provisions › Part 19 - OPERATOR TRAINING › Section 165:25-1-122 - Operator Class designations

Current through Vol. 41, No. 20, July 1, 2024
(a) A Class A operator has primary
				  responsibility to operate and maintain the underground storage tank system in
				  the broader aspects of the statutory and regulatory requirements to achieve and
				  maintain compliance.
(b) A Class B
				  operator implements applicable requirements and standards for one or more
				  facilities to monitor day-to-day aspects of operation and recordkeeping.
(c) A Class C operator is an
				  onsite employee responsible for responding to alarms or emergencies caused by
				  spills or release from underground storage tank systems. An operator with at
				  least a Class C Certification must be onsite during fueling operations at
				  attended facilities.
Added at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 1 - General Provisions › Part 19 - OPERATOR TRAINING › Section 165:25-1-124 - Frequency and proof of training

Current through Vol. 41, No. 20, July 1, 2024
(a) Each operator class must obtain initial
				  certification from a PSTD-approved training provider no later than July 1,
				  2011. A Class A or Class B operator may train a Class C operator.
(b) Class A and Class B operators must be
				  trained within 30 days after assuming operation and maintenance
				  responsibilities for an underground storage tank system. Class C operators must
				  be trained before assuming responsibility for responding to
				  emergencies.
(c) Class A and Class
				  B operators must be recertified every 3 years.
(d) Class B operators must be recertified
				  within 30 days in any areas (e.g. spill, overfill, corrosion protection) that
				  are determined to be out of compliance with EPA and PSTD requirements for
				  release prevention and/or release detection.
(e) Owners or operators must provide PSTD
				  with documentation for all operator classes.
Added at 25 Ok Reg
					 1867, eff 7-1-08; Amended at 26 Ok Reg 1826, eff
					 7-1-09
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 1 - General Provisions › Part 19 - OPERATOR TRAINING › Section 165:25-1-126 - Enforcement of operator training requirements

Current through Vol. 41, No. 20, July 1, 2024
Failure to have in place any active certified operator
					 class or comply with requirements of this Part will result in fines and/or
					 formal enforcement action.
Added at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 1 - CODES AND STANDARDS › Section 165:25-2-1 - Sources of standards

Current through Vol. 41, No. 20, July 1, 2024
The standards referenced in this Chapter are available for
					 inspection at the offices of the Petroleum Storage Division during regular
					 business hours and from the following sources. New editions of codes and
					 standards supersedes all previous editions.
(1) American Petroleum Institute (API), 1220
				  L. Street, N.W., Washington, D.C. 20005. Telephone (202) 682-8375.
(2) National Association of Corrosion
				  Engineers (NACE), P.O. Box 218340, Houston, Texas 77218. Telephone (713)
				  492-0535, ext. 810.
(3) National
				  Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts
				  02269. Telephone (800) 344-3555.
(4) American Society for Testing and
				  Materials (ASTM), 1916 Race Street, Philadelphia, Pennsylvania 19103. Telephone
				  (610) 832-9500.
(5) Underwriter's
				  Laboratory (UL), 333 Pfingston Road, Northbrook, Illinois 60062. Telephone
				  (708) 272-8800, ext. 42612.
(6)
				  Petroleum Equipment Institute (PEI), P.O. Box 2380, Tulsa, Oklahoma 74101.
				  Telephone (918) 464-9696.
(7) Steel
				  Tank Institute (STI), 570 Oakwood Road, Lake Zurich, Illinois, 60047. Telephone
				  (847) 438-8265.
(8) American
				  Society of Mechanical Engineers (ASME/ANSI), 22 Law Drive, Fairfield, New
				  Jersey 07007. Telephone (800) 843-2763.
Added at 21 Ok Reg
					 2036, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 1 - CODES AND STANDARDS › Section 165:25-2-2 - Incorporated codes and standards

Current through Vol. 41, No. 20, July 1, 2024
Specific references to documents are made in this Chapter.
					 Each of these documents or part thereof is included by reference as a standard.
					 New editions of codes and standards supersede all previous editions. Commission
					 rules will supersede in all conflicts between PSTD rules and any industry
					 standard. These codes and standards will be updated periodically through a
					 formal rulemaking procedure initiated by PSTD to reflect any substantive or
					 relevant changes.
(1) National Fire
				  Protection Association Standards:
(A)
				  Standard Number 30, 2021, "Flammable and Combustible Liquids Code."
(B) Standard Number 329, 2020, "Handling
				  Releases of Flammable and Combustible Liquids and Gases."
(C) Standard Number 385, 2022, "Tank Vehicles
				  for Flammable and Combustible Liquids."
(D) Standard Number 326, 2020, "Safeguarding
				  Tanks and Containers for Entry, Cleaning and Repair."
(E) Standard Number 30A, 2021, "Motor Fuel
				  Dispensing Facilities and Repair Garages."
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 1 - CODES AND STANDARDS › Section 165:25-2-3 - Other standards and regulations [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Revoked at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 1 - CODES AND STANDARDS › Section 165:25-2-4 - Financial responsibility

Current through Vol. 41, No. 20, July 1, 2024
An owner/operator must satisfy the requirements of Title
					 40 Code of Federal Regulations (CFR) 280, Subpart H by use of the Oklahoma
					 Petroleum Storage Tank Indemnity Fund (Indemnity Fund) (ref: Okla. Stat. Tit.
					 17 § 327.3 ). Compliance may also be satisfied by use of any of the
					 mechanisms outlined in 40 CFR 280, Subpart H, including, but not limited to
					 Self-insurance, Guarantee, Insurance, Surety Bond, Letter of Credit, Trust fund
					 or standby trust fund, Securities pledge, Cash or cash equivalent pledge. Use
					 of the Indemnity Fund requires a co-pay.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 1 - CODES AND STANDARDS › Section 165:25-2-6 - Lender liability

Current through Vol. 41, No. 20, July 1, 2024
PSTD incorporates by reference the lender liability
					 requirements specified in 40 CFR 280, Subpart I.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-31 - Underground storage tank installation

Current through Vol. 41, No. 20, July 1, 2024
All tanks, piping, and associated equipment used in
					 conjunction with a UST installation shall be installed by personnel possessing
					 appropriate skills, experience, manufacturer's certification, and required PSTD
					 license to complete the installation in accordance with recognized industry
					 standards and this Chapter. A licensed UST installer must be present at all
					 times during the installation. The PSTD Fuel Specialist monitoring the
					 installation must be contacted before underground piping is backfilled so
					 piping and sump tests may be observed and/or inspected. Photos of the
					 installation of tank(s) and line(s) must accompany a completed registration
					 form within thirty (30) days of installation and tanks fees must be paid before
					 a permit is issued.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-32 - Compatibility

Current through Vol. 41, No. 20, July 1, 2024
(a) Owners and
				  operators of all underground storage tank systems must use an underground
				  storage tank system that is made of or lined with materials that are compatible
				  with the substance stored in the system.
(b) Owners and operators of underground
				  storage tanks that contain regulated substances greater than ten percent (10%)
				  ethanol or twenty percent (20%) biodiesel must demonstrate compatibility of the
				  tank system, piping, containment sumps, pumping equipment, release detection
				  equipment, as well as spill and overfill equipment by using one of the
				  following methods:
(1) Certification or
				  listing of underground petroleum storage tank system equipment or components by
				  a nationally recognized, independent testing laboratory for use with the
				  regulated substance stored; or
(2)
				  Manufacturer's approval. The manufacturer's approval must be in writing,
				  indicating an affirmative statement of compatibility, specify the range of
				  biofuel blends the equipment or component is compatible with, and originate
				  from the equipment or component manufacturer.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-33 - Approved tanks, tank design

Current through Vol. 41, No. 20, July 1, 2024
(a) Tanks must be properly designed and
				  constructed, and any portion underground that routinely contains a regulated
				  substance must be protected from corrosion as specified in referenced codes and
				  standards. All new or replacements tanks except those excluded by regulation in
				  this Chapter must be double wall or jacketed secondarily contained in
				  construction to prevent the release of regulated substances to the environment
				  during the operational life of the system.
(1) Fiberglass-reinforced plastic tanks must
				  conform to the standards contained in UL 1316 or ASTM D4021-86.
(2) Steel tanks clad with
				  fiberglass-reinforced plastic must conform to the standards contained in UL
				  1746, ACT-100 F894, ACT-100-U F961, or STI F922.
(3) Tanks constructed of steel and
				  cathodically protected must conform to the standards in UL 58, UL 1746,
				  STI-P3®, STI F841, and NACE RP-0285 and must be
				  protected in the following manner:
(A) The
				  tank must be coated with a suitable dielectric material.
(B) Field-installed cathodic protection
				  systems must be designed by a corrosion expert.
(C) Impressed current systems must be
				  designed to allow determination of current operating status as required by this
				  Chapter and manufacturer's specifications.
(D) Cathodic protection systems must be
				  operated and maintained according to this Chapter and manufacturer's
				  specifications.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-34 - Compliance with nationally recognized code of practice and manufacturer's instructions [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Revoked at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-35 - Pre-installation

Current through Vol. 41, No. 20, July 1, 2024
All installers of underground storage tank systems must
					 perform an analysis of the installation site prior to the system's construction
					 and installation and submit with the scheduling form. The analysis must
					 include, at a minimum, the following:
(1) A determination of local soil
				  conditions.
(2) The level of the
				  water table in the area.
(3)
				  Drainage conditions.
(4) The
				  presence of any underground utility lines or conduits.
Added at 21 Ok Reg
					 2036, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-36 - Tank system installation

Current through Vol. 41, No. 20, July 1, 2024
(a)
Backfill material.
Backfill material used below, around, and/or
				  above a new underground storage tank system installation must be clean, unused,
				  non-corrosive porous material such as sand, crushed rock or pea gravel
				  specified by the tank manufacturer. The Licensed UST Installer must be present
				  and continuously supervise backfilling operations to ensure that proper
				  procedures are followed.
(b)
UST installation.
(1)
				  Owners/operators of all underground storage tank systems must notify PSTD at
				  least forty-eight (48) hours prior to the installation of underground storage
				  tanks and/or lines by submitting the PSTD scheduling form and receiving
				  confirmation of the installation and the Temporary Authorization for Receipt of
				  Fuel from PSTD. Following the required forty-eight (48) hour notification of
				  new UST installations, an on-site inspection may be required at critical
				  junctures. The PSTD Fuel Specialist monitoring the installation must be
				  contacted prior to initiating the following so it may be observed or inspected:
(A) The air/soap test of tanks.
(B) The tank pit prior to the placement of
				  tank(s).
(C) The backfilling of the
				  lower quadrant of tank(s).
(D) The
				  air/soap test, layout of piping, and hydrostatic testing of sumps prior to
				  backfilling.
(E) The tightness test
				  of tanks and piping, and leak detector tests prior to startup.
(F) Backfilling of all piping.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-37 - Storage tank spacing

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Underground storage tanks must be at least thirty-six inches (36") from a
				  property line boundary of the property on which they are installed.
(b) Fiberglass and steel underground storage
				  tanks must be spaced in accordance with manufacturer's instructions.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-38 - Fill pipe requirements

Current through Vol. 41, No. 20, July 1, 2024
(a) Fill
				  pipes that enter the top of a tank must have drop tubes installed and terminate
				  within 6 inches (6", or 15 cm) of the bottom of the tank.
(b) Fill pipes should be installed or
				  arranged so that vibration is minimized.
(c) Each fill pipe must be labeled by a
				  permanent marking to identify the product stored. The marking must be
				  maintained in legible condition throughout the life of the tank installation.
				  Color coding of the tank fill riser lids set forth in OAC
				  165:15-13-1 must also be used.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-39 - Spill and overfill protection

Current through Vol. 41, No. 20, July 1, 2024
(a) Owners and operators of underground
				  storage tank systems, their employees or agents, as well as those who transport
				  regulated substances to these systems must do everything reasonably possible to
				  ensure that releases due to spilling and overfilling do not occur.
(b) Owners, operators, their employees or
				  agents, or transporters must ensure that the volume available in the tank
				  (ullage) is greater than the volume of product to be transferred to the tank
				  before the transfer is made and that the transfer operation is monitored
				  constantly to prevent overfilling and spilling.
(c) Tight fill connections must be used on
				  all deliveries made to underground storage tanks.
(d) Tampering with overfill protection is not
				  permitted. Any violation of this Section will be subject to the enforcement
				  procedures of this Chapter resulting in fines, contempt proceedings, and/or
				  shutdown of operations as provided by law.
(e) Except as provided in (e) of this
				  Section, in order to prevent spilling and overfilling associated with product
				  transfer to the petroleum storage tank system, the following prevention
				  equipment must be used:
(1) Spill prevention
				  equipment that will prevent release of product to the environment when the
				  transfer hose is detached from the fill pipe (for example, a spill
				  bucket).
(2) Overfill prevention
				  equipment that will automatically shut off flow into the tank when the tank is
				  no more than ninety-five percent (95%) full.
(A) A drop tube with overfill device is
				  required on all tank systems installed after July 1, 2001.
(B) Tanks installed before July 1, 2001, must
				  be upgraded to meet these standards before July 1, 2002, unless equipped with
				  an operational ball float overfill device. Use of ball floats is prohibited
				  with suction systems. Staff may require a ball float functionality
				  test.
(C) Ball float valves that
				  are inoperable cannot be repaired and instead must be replaced with a drop tube
				  with flapper valve, or
(D) A
				  mechanism to prevent overfilling by sounding an alarm when the liquid level in
				  the tank reaches ninety percent (90%) of capacity and by automatically stopping
				  the delivery of liquid to the tank when the level in the tank reaches
				  ninety-five percent (95%) of capacity.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-40 - Installation testing

Current through Vol. 41, No. 20, July 1, 2024
(a) All tanks
				  must be tested with air pressure prior to installation, and/or tested according
				  to manufacturer's specifications. Pressure must not exceed 5 pounds per square
				  inch (psi). The entire tank must be soaped during this period and inspected for
				  bubbling.
(b) All suction piping
				  must be tested while disconnected from the tank, pumps, and dispensing units.
				  The piping must be subjected to an air test with the following specifications:
(1) The piping must be subjected to an air
				  test of at least 50 psi for a period of one hour.
(2) All piping joints must be soaped while
				  the system is under pressure, in order to detect any possible leaks.
(3) As an alternative to the preceding
				  methods in (1) and (2) above, the piping may be subjected to a vacuum test
				  while connected to tanks, pumps and dispensing units.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-41 - Installation drawing

Current through Vol. 41, No. 20, July 1, 2024
As built drawings, showing the location(s) of tanks, piping
					 and associated underground storage tank equipment, monitoring wells and
					 dispensing units, must be prepared by the installer and submitted to the
					 Commission with the tank registration form.
Added at 21 Ok Reg
					 2036, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 3 - DESIGN AND INSTALLATION › Section 165:25-2-42 - Certification of installation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 23 Ok Reg 2261, eff 7-1-06; Revoked at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 5 - PROTECTION AGAINST CORROSION › Section 165:25-2-51 - Corrosion protection

Current through Vol. 41, No. 20, July 1, 2024
Any portion of a metallic tank or piping system in contact
					 with the soil must be protected from corrosion. A cathodic protection system
					 must be designed by a corrosion expert, installed and maintained in accordance
					 with recognized standards of design. One of the following codes of practice
					 shall be used to comply with this section:
(1) NACE International Test Method TM 0101,
				  "Measurement Techniques Related to Criteria for Cathodic Protection of
				  Underground Storage Tank Systems";
(2) NACE International Test Method TM 0497,
				  "Measurement Techniques Related to Criteria for Cathodic Protection on
				  Underground or Submerged Metallic Piping Systems";
(3) Steel Tank Institute Recommended Practice
				  R051, "Cathodic Protection Testing Procedures for
				  STI-P3® Underground Storage Tanks";
(4) NACE International Standard Practice SP
				  0169, "Control of External Corrosion on Underground or Submerged Metallic
				  Piping Systems"; or
(5) NACE
				  International Standard Practice SP 0285, "External Control of Underground
				  Storage Tank Systems by Cathodic Protection.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 5 - PROTECTION AGAINST CORROSION › Section 165:25-2-52 - Compliance with corrosion protection requirements and manufacturer's specifications

Current through Vol. 41, No. 20, July 1, 2024
Corrosion protection systems shall be operated and
					 maintained in accordance with manufacturer's instructions and specifications to
					 provide continuous corrosion protection to the metal components of the storage
					 tank system that routinely contain regulated substances and are in contact with
					 the ground.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff
					 7-1-05
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 5 - PROTECTION AGAINST CORROSION › Section 165:25-2-53 - Frequency and criteria of inspections and tests

Current through Vol. 41, No. 20, July 1, 2024
(a) All cathodic protection systems must be
				  tested within 6 months of installation and/or repair, and at least every three
				  (3) years thereafter.
(b) Cathodic
				  protection testing, repair, or three (3) year recertification must be scheduled
				  at least 24 hours before by submitting the PSTD scheduling form and PSTD staff
				  may be present.
(c) Every 60 days
				  impressed current cathodic protection systems must be inspected by the owner or
				  owner's designated representative to ensure the equipment is working properly.
(d) The criteria that are used to
				  determine whether cathodic protection is adequate must be in accordance with a
				  code of practice developed by a nationally recognized organization, such as
				  NACE RP-0285.
(e) All personnel
				  performing cathodic protection system testing must have the required education,
				  current corrosion certification, experience, knowledge and competence to
				  correctly perform testing services in accordance with a certified course and
				  applicable industry standards or codes.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 5 - PROTECTION AGAINST CORROSION › Section 165:25-2-53.1 - Underground storage tank internal lining requirements

Current through Vol. 41, No. 20, July 1, 2024
(a) A previously lined steel tank that fails
				  precision tightness testing or an internal lining inspection shall not be
				  repaired and must be removed.
(b)
				  Tank lining may not be used as a method of repair for an unlined
				  tank.
(c) Within 10 years after
				  lining, and every five years thereafter, lined USTs must be internally
				  inspected and found to be structurally sound, with the lining still performing
				  in accordance with original design specifications.
(d) Standards that must be referenced during
				  the periodic inspection of lined USTs:
(1)
				  American Petroleum Institute (API) Publication 1631.
(2) Ken Wilcox Associates, Inc. "Recommended
				  Practices for Inspecting Buried Lined Steel Tanks Using a Video Camera," First
				  Edition, 1999, Methods A and D.
(3)
				  National Leak Prevention Association Standard 631.
(4) PSTD Internal Tank Lining Guidance
				  document and PSTD Interior Lining Inspection Formare available on the
				  Commission website.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 5 - PROTECTION AGAINST CORROSION › Section 165:25-2-54 - Underground storage tank piping materials [AMENDED AND RENUMBERED TO 165:25-2-55.1]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended and renumbered to 165:25-2-55.1 at 23 Ok Reg 2261,
					 eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 5 - PROTECTION AGAINST CORROSION › Section 165:25-2-55 - Underground storage tank internal lining requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Revoked at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 6 - PIPING › Section 165:25-2-55.1 - Underground storage tank piping materials

Current through Vol. 41, No. 20, July 1, 2024
(a) All new or
				  replacement underground pressurized piping must be installed as follows:
(1) Nonmetallic;
(2) Double-walled;
(3) A tracer locator wire must be installed
				  in all piping trenches; and
(4)
				  Tank, dispenser, and transition sumps must be installed and monitored per
				  165:25-3-6.29.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 6 - PIPING › Section 165:25-2-55.2 - Vent piping requirements

Current through Vol. 41, No. 20, July 1, 2024
(a) Where vent pipes installed prior to July,
				  2003, from tanks storing gasoline are adjacent to buildings or public ways,
				  they must be located not less than twelve feet (12') (3.6 meters) above the
				  adjacent ground level or three feet (3') above the roof line at the highest
				  point of attachment. Newly installed vent pipes must be five feet (5') above
				  the roof or canopy. All vent pipes buried below ground must be a minimum of
				  eighteen inches (18").
(b) In order
				  to aid in dispersion, vapors must be discharged upward. Vent outlets must be
				  located so that flammable vapors will not accumulate to an unsafe location or
				  trapped under eaves and shall be at least five feet (5') (1.5 meters) from
				  building openings and fifteen feet (15') (4.5 meters from powered ventilation
				  air intake devices).
(c) All new or
				  replacement underground vent piping must be non-metallic. Aboveground vent
				  risers must be steel pipe.
(d) Vent
				  risers must be located or protected and anchored, to prevent damage from
				  traffic, wind, or testing procedures.
Added at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 7 - DISPENSERS › Section 165:25-2-71 - Dispensers

Current through Vol. 41, No. 20, July 1, 2024
(a) A control must
				  be provided that will permit the dispenser to operate only when a dispensing
				  nozzle is removed from its bracket or normal position with respect to the
				  dispensing device and only when the switch on this dispensing device is
				  manually activated. This control must also stop the dispenser when all nozzles
				  have been returned either to their brackets or to the normal non-dispensing
				  position.
(b) A Underwriter's
				  Laboratory ("UL") listed emergency breakaway device designed to retain liquid
				  on both sides of the breakaway point must be installed on each hose. These
				  devices must be installed and maintained in accordance with the manufacturer's
				  instructions. Where hoses are attached to a hose-retrieving mechanism, the
				  listed emergency breakaway device must be installed between the point of
				  attachment of the hose-retrieving mechanism to the hose and the hose nozzle
				  valve.
(c) If a submersible pump
				  system is used, a UL listed emergency shutoff/shear valve must be installed at
				  each dispensing device. Both the emergency shutoff/shear valve and dispensing
				  device shall be rigidly anchored in place.
(d) Liquids must be transferred from storage
				  tanks by means of fixed dispensers designed and equipped to allow control of
				  the flow and prevent leakage or accidental discharge.
(e) Dispensing devices for Class I and Class
				  II liquids must be listed.
(1) Existing
				  listed or labeled dispensing devices may be modified provided the modifications
				  made are "Listed by Report" by an approved testing laboratory or as otherwise
				  pre-approved by PSTD.
(2)
				  Modification proposals must contain a description of the component parts used
				  in the modification and the recommended methods of installation on specific
				  dispensing devices, and they must be made available to PSTD for approval prior
				  to installation.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 7 - DISPENSERS › Section 165:25-2-72 - Dispenser hose

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Underwriters Laboratory (UL) Listed hose assemblies must be used to dispense
				  fuel.
(1) Hose length at facilities must not
				  exceed eighteen feet (18', or 5.5 m).
(2) Hose at facilities must be checked daily
				  for evidence of blistering, carcass saturation or separation, cuts, nicks or
				  abrasions that expose reinforcement material and for slippage, misalignment or
				  leaks at couplings. If any of the defects are present, the defective hose must
				  be removed from service immediately.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 7 - DISPENSERS › Section 165:25-2-73 - Nozzles

Current through Vol. 41, No. 20, July 1, 2024
At any installation where the normal flow of product may be
					 stopped other than by the hose nozzle valve e.g., at pre-pay stations, the
					 system must include UL listed equipment with a feature that causes or requires
					 the closing of the hose nozzle valve before product flow can be resumed or
					 before the hose nozzle valve can be replaced in its normal position in the
					 dispenser.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 7 - DISPENSERS › Section 165:25-2-75 - Required signs

Current through Vol. 41, No. 20, July 1, 2024
(a) Warning
				  signs must be conspicuously posted in the dispensing area incorporating the
				  following or equivalent wording:
(1)
				  WARNING
(2) It is unlawful and
				  dangerous to dispense gasoline into unapproved containers.
(3) No smoking.
(4) Stop motor.
(5) No filling of portable containers in or
				  on a motor vehicle.
(6) Place
				  container on ground before filling.
(7) Discharge your static electricity before
				  fueling by touching a metal surface away from the nozzle.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 7 - DISPENSERS › Section 165:25-2-75.1 - Display on dispenser

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Every dispenser or delivery device regulated by the Commission used for the
				  sale of motor fuel to the public must legibly display the type of motor fuel
				  offered for sale.
(b) Any motor
				  fuel must be displayed in accordance with
				  16
				  CFR Part 306.0 through
				  306.12, including
				  Appendices; and sold as provided for by Commission rules and National Institute
				  of Standards and Technology (NIST) Handbook 44, "Specifications, Tolerances,
				  and Other Technical Requirements for Weighing and Measuring Devices".
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 7 - DISPENSERS › Section 165:25-2-76 - Sources of ignition

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Smoking materials, including but not limited to matches and lighters, must not
				  be used within 20 feet (20', or 6 m) of areas used for fueling, servicing fuel
				  systems for internal combustion engines, or receiving or dispensing of Class I
				  liquids.
(b) At least one fire
				  extinguisher must be readily accessible in the pump area, as well as at the
				  service bay(s), where applicable.
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 7 - DISPENSERS › Section 165:25-2-77 - Electrical equipment [AMENDED AND RENUMBERED TO 165:25-2-91]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended and renumbered
					 to 165:25-2-91 at 23 Ok Reg 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 9 - ELECTRICAL › Section 165:25-2-91 - Electrical requirements

Current through Vol. 41, No. 20, July 1, 2024
(a) All
				  electrical work must be performed by a licensed electrician.
(b) All electrical wiring and electrical
				  equipment must be of a type specified by and must be installed in accordance
				  with NFPA 30A and NEC 70, National Electrical Code.
(c) Clearly identified and easily accessible
				  switch(es) or circuit breaker(s) must be provided at a location remote from
				  dispensing devices, including remote pumping systems, to shut off the power to
				  all dispensing devices in the event of an emergency.
(d) Electrical equipment that was installed
				  in compliance with an earlier state or national code will not require
				  modification unless the equipment is hazardous to people or property.
Amended and renumbered
					 from 165:25-2-77 at 23 Ok Reg 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 11 - REPAIRS TO UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-111 - Repairs to underground storage tank systems

Current through Vol. 41, No. 20, July 1, 2024
(a) Repairs to underground storage tank
				  systems must prevent releases due to structural failure or corrosion for the
				  remaining operational life of the system.
(b) Repairs shall be conducted by qualified
				  personnel possessing the appropriate skills, experience, competence, and any
				  required license or certification to complete the work in accordance with
				  provisions of this Chapter.
(c)
				  Any repair shall be properly conducted in accordance with a standard or code of
				  practice developed by a nationally recognized association or independent
				  testing laboratory.
(d)
				  Requirements of this Section do not apply to routine and minor maintenance
				  activities related to the tank and piping system.
(e) Following completion of repairs, a tank
				  or line tightness test must be performed by a certified tester and is required
				  prior to returning tank or line to service.
(f) Repairs to secondary containment areas of
				  tanks and piping used for interstitial monitoring and repairs to containment
				  sumps used for interstitial monitoring of piping must have the secondary
				  containment tested for tightness within thirty (30) days following completion
				  of the repair. This testing must be conducted according to the manufacturer's
				  instructions or a code or practice developed by a nationally recognized
				  association or independent testing laboratory.
(g) A tightness test of spill prevention
				  equipment must be performed within thirty (30) days following repairs to such
				  spill prevention equipment. This testing must be conducted according to the
				  manufacturer's instructions or a code or practice developed by a nationally
				  recognized association or independent testing laboratory.
(h) Overfill prevention equipment must be
				  inspected within thirty (30) days following repairs to it to ensure it is
				  operating properly. This inspection must be conducted according to the
				  manufacturer's instructions or a code or practice developed by a nationally
				  recognized association or independent testing laboratory.
Added at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-131 - Tank removal and closure

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Owners/operators of all underground storage tank systems must notify PSTD at
				  least fourteen (14) days prior to the removal or permanent closure of
				  underground storage tanks and/or lines by submitting the PSTD scheduling form
				  and receiving confirmation of the scheduled removal from PSTD. If events
				  require a change in the date of removal, PSTD shall be given forty-eight (48)
				  hours notice prior to the new date.
(b) An authorized agent of PSTD may be
				  present to observe the removal and to inspect the closed tank system and the
				  surrounding environment prior to backfilling.
(c) Tanks and lines must be removed upon
				  closure unless a Commission order grants a variance that allows the tanks
				  and/or lines to be closed in place. Tank systems that are removed from the
				  ground must be transported from the site and whether sold to a scrap dealer or
				  disposed of at an acceptable facility, sufficient holes should be made in the
				  tanks to render the tank(s) unfit for further use. A certificate of destruction
				  must be submitted to PSTD with the UST Closure Report. When scheduling a
				  removal, a site map of where samples are to be taken should be attached to the
				  scheduling form. After closure activities are completed, the excavation must be
				  backfilled no later than seven (7) days upon completion of tank removal.
				  Backfill material shall be earth, gravel, rock, sand or combinations thereof,
				  backfill shall predominate in the finer sizes and present no isolated voids,
				  silt pockets or areas of large stones. Refer to OAC
				  165:29-3-65
				  when backfilling. Exceptions to backfilling within seven (7) days may be made
				  when a new tank system is scheduled to be installed in the same tank
				  pit.
(d) The Licensed UST Remover
				  must be on the job site during all removal activities, beginning with break-out
				  of concrete. This includes Licensed UST Remover presence during cutting and
				  removing concrete over any part of the tank system.
(e) Photos must be taken of tank(s), line(s)
				  and soil at removal. In the event there is a hole in tank(s) or line(s),
				  further photographic evidence is required. If tank(s), line(s) or excavated
				  soil show evidence of a release, photos of the apparent release must be taken
				  that indicate the release source.
Added at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-132 - Compliance with removal and closure requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 23 Ok Reg
					 2261, eff 7-1-06; Revoked at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-133 - Temporary removal from service

Current through Vol. 41, No. 20, July 1, 2024
(a) When an underground storage tank system
				  is taken temporarily out of service for three (3) months or less, the owner or
				  operator must meet the following requirements :
(1) Continue the operation, testing, and
				  maintenance of corrosion protection as required by this Chapter. Electricity
				  must be maintained for an impressed current CP system to be operational.
(2) Continue to monitor for leaks
				  by performing release detection and release detection testing as required by
				  this Chapter.
(3) Perform annual
				  inspections and testing of release detection equipment.
(4) Perform thirty (30) day walkthrough
				  inspections.
(5) Perform three (3)
				  year containment sump testing on containment sumps used for interstitial
				  monitoring of piping.
(6) Comply
				  with the requirements of this Chapter concerning release reporting and
				  corrective action.
(7) Notify PSTD
				  of a change in service within thirty (30) days on the prescribed TOU form.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-134 - Requirements for returning to service/use

Current through Vol. 41, No. 20, July 1, 2024
When an underground storage tank system is returned to
					 service/use a tank tightness test, line tightness test, and a leak detector
					 test must be performed by a certified tester, and must be completed on the
					 underground portion of temporarily closed systems prior to returning the system
					 to service if it has been out of service/use for more than twelve (12) months.
					 Any system failure will require either closure or upgrade of the failed
					 portion. Additional testing shall be required on any portion of the tank system
					 considered detrimental to release detection depending upon the type of tank
					 system installed. Notify PSTD on the prescribed "Return to Service" form when
					 returning a system to service/use along with copies of all testing and the tank
					 registration fees.
Added at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-135 - Permanent closure

Current through Vol. 41, No. 20, July 1, 2024
All underground storage tanks and associated piping out of
					 service/use for more than twelve (12) months must be removed if they do not
					 comply with the requirements as stated in
					 165:25-2-133
					 and
					 165:25-2-134.
					 A variance to close a tank and/or associated piping in place with a PSTD
					 approved inert material must be made by application and administrative review
					 in accordance with OAC
					 165:5-21-3.1.
					 For a closure in place variance solely on the basis of financial concerns
					 between the cost to remove and the cost to close in place, applicant must
					 submit three (3) bids to remove and three (3) bids to close in place with their
					 variance application. A variance is effective on order
					 issuance.
Added at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08