reglab/statecodes huggingface dataset:
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-56 - Open-ended valves or lines - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
(1)
									Each open-ended valve or line shall be equipped with a
			 cap, blind flange, plug, or a second valve.
(2)
									The cap, blind
			 flange, plug, or second valve shall seal the open end at all times, except
			 during operations requiring hazardous waste stream flow through the open-ended
			 valve or line.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-57 - Valves in gas or vapor service or in light liquid service - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
								Each valve in gas or vapor or light liquid service
			 shall be monitored monthly to detect leaks by the methods specified in
			 paragraph (B) of rule
			 3745-205-63 of the
			 Administrative Code and shall comply with paragraphs (B) to (E) of this rule,
			 except as provided in paragraphs (F), (G), and (H) of this rule, and rules
			 3745-205-61 and
			 3745-205-62 of the
			 Administrative Code.
(B)
								If an instrument reading of ten thousand parts per
			 million (ppm) or greater is measured, a leak is detected.
(C)
(1)
									Any valve for which a leak is not detected for two
			 successive months may be monitored the first month of every succeeding quarter,
			 beginning with the next quarter, until a leak is detected.
(2)
									If a leak is
			 detected, the valve shall be monitored monthly until a leak is not detected for
			 two successive months.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-58 - Pumps and valves in heavy liquid service, pressure relief devices in light liquid or heavy liquid service, and flanges and other connectors - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
								Pumps and valves in heavy liquid service, pressure
			 relief devices in light liquid or heavy liquid service, and flanges and other
			 connectors shall be monitored within five days by the method specified in
			 paragraph (B) of rule
			 3745-205-63 of the
			 Administrative Code if evidence of a potential leak is found by visual,
			 audible, olfactory, or any other detection method.
(B)
								If an instrument
			 reading of ten thousand parts per million or greater is measured, a leak is
			 detected.
(C)
(1)
									When a leak is
			 detected, the leak shall be repaired as soon as practicable, but not later than
			 fifteen calendar days after the leak is detected, except as provided in rule
			 3745-205-59 of the
			 Administrative Code.
(2)
									The first attempt at repair shall be made no later than
			 five calendar days after each leak is detected.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-59 - Delay of repair - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
								Delay of repair
			 of equipment for which leaks have been detected will be allowed if the repair
			 is technically infeasible without a hazardous waste management unit shutdown.
			 In such a case, repair of this equipment shall occur before the end of the next
			 hazardous waste management unit shutdown.
(B)
								Delay of repair
			 of equipment for which leaks have been detected will be allowed for equipment
			 that is isolated from the hazardous waste management unit and that does not
			 continue to contain or contact hazardous waste with organic concentrations at
			 least ten per cent by weight.
(C)
								Delay of repair
			 for valves will be allowed if:
(1)
									The owner or operator determines that emissions of
			 purged material resulting from immediate repair are greater than the emissions
			 likely to result from delay of repair.
(2)
									When repair
			 procedures are completed, the purged material is collected and destroyed or
			 recovered in a control device complying with rule
			 3745-205-60 of the
			 Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-61 - Alternative standards for valves in gas or vapor service or in light liquid service; percentage of valves allowed to leake-quipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
								An owner or operator subject to the requirements of
			 rule 3745-205-57 of the
			 Administrative Code may elect to have all valves within a hazardous waste
			 management unit comply with an alternative standard that allows no greater than
			 two per cent of the valves to leak.
(B)
								The following
			 requirements shall be met if an owner or operator decides to comply with the
			 alternative standard of allowing two per cent of valves to leak:
(1)
									A performance
			 test as specified in paragraph (C) of this rule shall be conducted initially
			 upon designation, annually, and at other times requested by the
			 director.
(2)
									If a valve leak is detected, the leak shall be repaired
			 in accordance with paragraphs (D) and (E) of rule
			 3745-205-57 of the
			 Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-62 - Alternative standards for valves in gas or vapor service or in light liquid service; skip period leak detection and repair - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
								An owner or operator subject to the requirements of
			 rule 3745-205-57 of the
			 Administrative Code may elect for all valves within a hazardous waste
			 management unit to comply with one of the alternative work practices specified
			 in paragraphs (B)(2) and (B)(3) of this rule.
(B)
(1)
									An owner or operator shall comply with the requirements
			 for valves, as described in rule
			 3745-205-57 of the
			 Administrative Code, except as described in paragraphs (B)(2) and (B)(3) of
			 this rule.
(2)
									After two consecutive quarterly leak detection periods
			 with the percentage of valves leaking equal to or less than two per cent, an
			 owner or operator may begin to skip one of the quarterly leak detection periods
			 (i.e., monitor for leaks once every six months) for the valves subject to the
			 requirements in rule
			 3745-205-57 of the
			 Administrative Code.
(3)
									After five consecutive quarterly leak detection periods
			 with the percentage of valves leaking equal to or less than two per cent, an
			 owner or operator may begin to skip three of the quarterly leak detection
			 periods (i.e., monitor for leaks once every year) for the valves subject to the
			 requirements in rule
			 3745-205-57 of the
			 Administrative Code.
(4)
									If the percentage of valves leaking is greater than two
			 per cent, the owner or operator shall monitor monthly in compliance with the
			 requirements in rule
			 3745-205-57 of the
			 Administrative Code, but may again elect to use this rule after meeting the
			 requirements of paragraph (C)(1) of rule
			 3745-205-57 of the
			 Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-63 - Test methods and procedures - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
								Each owner or
			 operator subject to rules
			 3745-205-50 to
			 3745-205-65 of the
			 Administrative Code shall comply with the test methods and procedures
			 requirements provided in this rule.
(B)
								Leak detection
			 monitoring, as required in rules
			 3745-205-52 to
			 3745-205-62 of the
			 Administrative Code, shall comply with the following requirements:
(1)
									Monitoring shall
			 comply with reference method 21 in 40 CFR Part 60.
(2)
									The detection
			 instrument shall meet the performance criteria of reference method
			 21.
(3)
									The instrument shall be calibrated before use on each
			 day of its use by the procedures specified in reference method
			 21.
(4)
									Calibration gases shall be:
(a)
										Zero air (less
			 than ten parts per million (ppm) of hydrocarbon in air).
(b)
										A mixture of
			 methane or n-hexane and air at a concentration of approximately, but less than,
			 ten thousand ppm methane or n-hexane.
(5)
									The instrument
			 probe shall be traversed around all potential leak interfaces as close to the
			 interface as possible as described in reference method 21.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-64 - Recordkeeping - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
(1)
									Each owner or operator subject to rules
			 3745-205-50 to
			 3745-205-65 of the
			 Administrative Code shall comply with the recordkeeping requirements of this
			 rule.
(2)
									An owner or operator of more than one hazardous waste
			 management unit subject to rules
			 3745-205-50 to
			 3745-205-65 of the
			 Administrative Code may comply with the recordkeeping requirements for these
			 hazardous waste management units in one recordkeeping system if the system
			 identifies each record by each hazardous waste management unit.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-65 - Reporting - equipment leaks

Current through all regulations passed and filed through July 1, 2024
(A)
								A semiannual
			 report shall be submitted by owners and operators subject to the requirements
			 of rules
			 3745-205-50 to
			 3745-205-65 of the
			 Administrative Code to the director by dates specified by the director. The
			 report shall include the following information:
(1)
									The U.S. EPA
			 identification number, name, and address of the facility.
(2)
									For each month
			 during the semiannual reporting period:
(a)
										The equipment
			 identification number of each valve for which a leak was not repaired as
			 required in paragraph (D) of rule
			 3745-205-57 of the
			 Administrative Code.
(b)
										The equipment identification number of each pump for
			 which a leak was not repaired as required in paragraphs (C) and (D)(6) of rule
			 3745-205-52 of the
			 Administrative Code.
(c)
										The equipment identification number of each compressor
			 for which a leak was not repaired as required in paragraph (G) of rule
			 3745-205-53 of the
			 Administrative Code.
(3)
									Dates of
			 hazardous waste management unit shutdowns that occurred within the semiannual
			 reporting period.
(4)
									For each month during the semiannual reporting period,
			 dates when the control device installed as required by rule
			 3745-205-52,
			 3745-205-53,
			 3745-205-54, or
			 3745-205-55 of the
			 Administrative Code exceeded or operated outside of the design specifications
			 as described in paragraph (E) of rule
			 3745-205-64 of the
			 Administrative Code and as indicated by the control device monitoring required
			 by rule 3745-205-60 of the
			 Administrative Code and was not corrected within twenty-four hours, the
			 duration and cause of each exceedance, and any corrective measures
			 taken.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-80 - Applicability and definitions - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								Rules
			 3745-205-80 to
			 3745-205-90 of the
			 Administrative Code apply to owners and operators of all facilities that treat,
			 store, or dispose of hazardous waste in tanks, surface impoundments, or
			 containers subject to either rules
			 3745-55-70 to
			 3745-55-79,
			 3745-55-90 to
			 3745-55-100, or
			 3745-56-20 to
			 3745-56-32 of the Administrative
			 Code except as rule
			 3745-54-01 of the Administrative
			 Code and paragraph (B) of this rule provide otherwise.
(B)
								Rules
			 3745-205-80 to
			 3745-205-90 of the
			 Administrative Code do not apply to the following waste management units at the
			 facility:
(1)
									A
			 waste management unit that holds hazardous waste placed in the unit before
			 December 6, 1996, and in which no hazardous waste is added to the unit on or
			 after December 6, 1996.
(2)
									A container that has a design capacity less than or
			 equal to 0.1 cubic meters
			 (m3).
(3)
									A tank in which
			 an owner or operator has stopped adding hazardous waste and the owner or
			 operator has begun implementing or completed closure pursuant to an approved
			 closure plan.
(4)
									A surface impoundment in which an owner or operator has
			 stopped adding hazardous waste (except to implement an approved closure plan)
			 and the owner or operator has begun implementing or completed closure pursuant
			 to an approved closure plan.
(5)
									A waste
			 management unit that is used solely for on-site treatment or storage of
			 hazardous waste that is placed in the unit as a result of implementing remedial
			 activities required under the corrective action authorities of RCRA Sections
			 3004(u), 3004(v), or 3008(h); CERCLA authorities; or similar federal or state
			 authorities.
(6)
									A waste management unit that is used solely for the
			 management of radioactive mixed waste in accordance with all applicable
			 regulations under the authority of the Atomic Energy Act and the Nuclear Waste
			 Policy Act.
(7)
									A hazardous waste management unit that the owner or
			 operator certifies is equipped with and operating air emission controls in
			 accordance with the requirements of an applicable Clean Air Act regulation
			 codified under 40 CFR Part
			 60, Part 61, or Part
			 63. For the purpose of complying
			 with this paragraph, a tank for which the air emission control includes an
			 enclosure, as opposed to a cover, shall be in compliance with the enclosure and
			 control device requirements of paragraph (I) of rule
			 3745-205-84 of the
			 Administrative Code, except as provided in paragraph (C)(5) of rule
			 3745-205-82 of the
			 Administrative Code.
(8)
									A tank that has a "process vent" as defined in rule
			 3745-205-31 of the
			 Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-83 - Waste determination procedures - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								Waste
			 determination procedure to determine average volatile organic (VO)
			 concentration of a hazardous waste at the point of waste origination.
(1)
									An owner or
			 operator shall determine the average VO concentration at the point of waste
			 origination for each hazardous waste placed in a waste management unit exempted
			 under paragraph (C)(1) of rule
			 3745-205-82 of the
			 Administrative Code from using air emission controls in accordance with
			 standards specified in rules
			 3745-205-84 to
			 3745-205-87 of the
			 Administrative Code, as applicable to the waste management unit.
(a)
										An initial
			 determination of the average VO concentration of the waste stream shall be made
			 before the first time any portion of the material in the hazardous waste stream
			 is placed in a waste management unit exempted under paragraph (C)(1) of rule
			 3745-205-82 of the
			 Administrative Code from using air emission controls, and thereafter an initial
			 determination of the average VO concentration of the waste stream shall be made
			 for each averaging period that a hazardous waste is managed in the unit;
			 and
(b)
										Perform a new waste determination whenever changes to
			 the source generating the waste stream are reasonably likely to cause the
			 average VO concentration of the hazardous waste to increase to a level that is
			 equal to or greater than the applicable VO concentration limits specified in
			 rule 3745-205-82 of the
			 Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-84 - Tanks - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								This rule applies to the control of air pollutant
			 emissions from tanks for which paragraph (B) of rule
			 3745-205-82 of the
			 Administrative Code references the use of this rule for such air emission
			 control.
(B)
								The owner or operator shall control air pollutant
			 emissions from each tank subject to this rule in accordance with the following
			 requirements as applicable:
(1)
									For a tank that manages hazardous waste that meets all
			 of the conditions specified in paragraphs (B)(1)(a) to (B)(1)(c) of this rule,
			 the owner or operator shall control air pollutant emissions from the tank in
			 accordance with the "Tank Level 1" controls specified in paragraph (C) of this
			 rule or the "Tank Level 2" controls specified in paragraph (D) of this
			 rule.
(a)
										The
			 hazardous waste in the tank has a maximum organic vapor pressure which is less
			 than the maximum organic vapor pressure limit for the tank's design capacity
			 category as follows:
(i)
											For a tank design capacity equal to or greater than one
			 hundred fifty-one cubic meters (m3), the maximum
			 organic vapor pressure limit for the tank is
			 5.2 kilopascals
			 (kPa).
(ii)
											For a tank design capacity equal to or greater than
			 seventy-five m3 but less than one hundred fifty-one
			 m3, the maximum organic vapor pressure limit for the
			 tank is 27.6 kPa.
(iii)
											For a tank
			 design capacity less than seventy-five m3, the
			 maximum organic vapor pressure limit for the tank is
			 76.6 kPa.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-85 - Surface impoundments - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								This rule applies to the control of air pollutant
			 emissions from surface impoundments for which paragraph (B) of rule
			 3745-205-82 of the
			 Administrative Code references the use of this rule for such air emission
			 control.
(B)
								The owner or operator shall control air pollutant
			 emissions from the surface impoundment by installing and operating either of
			 the following:
(1)
									A floating membrane cover in accordance with the
			 provisions specified in paragraph (C) of this rule; or
(2)
									A cover that is
			 vented through a closed-vent system to a control device in accordance with the
			 provisions specified in paragraph (D) of this rule.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-86 - Containers - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								This rule applies to the control of air pollutant
			 emissions from containers for which paragraph (B) of rule
			 3745-205-82 of the
			 Administrative Code references the use of this rule for such air emission
			 control.
(B)
								General requirements.
(1)
									The owner or
			 operator shall control air pollutant emissions from each container subject to
			 this rule in accordance with the following requirements, as applicable to the
			 container, except when the special provisions for waste stabilization processes
			 specified in paragraph (B)(2) of this rule apply to the container.
(a)
										For a container
			 having a design capacity greater than
			 0.1 cubic meters
			 (m3) and less than or equal to
			 0.46
			 m3, the owner or operator shall control air
			 pollutant emissions from the container in accordance with the "Container Level
			 1" standards specified in paragraph (C) of this rule.
(b)
										For a container
			 having a design capacity greater than
			 0.46
			 m3 that is not in light material service, the owner
			 or operator shall control air pollutant emissions from the container in
			 accordance with the "Container Level 1" standards specified in paragraph (C) of
			 this rule.
(c)
										For a container having a design capacity greater than
			 0.46
			 m3 that is in light material service, the owner or
			 operator shall control air pollutant emissions from the container in accordance
			 with the "Container Level 2" standards specified in paragraph (D) of this
			 rule.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-87 - Closed-vent systems and control devices - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								This rule applies
			 to each closed-vent system and control device installed and operated by the
			 owner or operator to control air emissions in accordance with standards of
			 rules 3745-205-80 to
			 3745-205-90 of the
			 Administrative Code.
(B)
								The closed-vent system shall meet the following
			 requirements:
(1)
									The closed-vent system shall route the gases, vapors,
			 and fumes emitted from the hazardous waste in the waste management unit to a
			 control device that meets the requirements specified in paragraph (C) of this
			 rule.
(2)
									The closed-vent system shall be designed and operated
			 in accordance with the requirements specified in paragraph (K) of rule
			 3745-205-33 of the
			 Administrative Code.
(3)
									In the case when the closed-vent system includes bypass
			 devices that could be used to divert the gas or vapor stream to the atmosphere
			 before entering the control device, each bypass device shall be equipped with
			 either a flow indicator as specified in paragraph (B)(3)(a) of this rule or a
			 seal or locking device as specified in paragraph (B)(3)(b) of this rule. For
			 the purpose of complying with this paragraph, low leg drains, high point
			 bleeds, analyzer vents, open-ended valves or lines, spring loaded pressure
			 relief valves, and other fittings used for safety purposes are not considered
			 to be bypass devices.
(a)
										If a flow indicator is used to comply with paragraph
			 (B)(3) of this rule, the indicator shall be installed at the inlet to the
			 bypass line used to divert gases and vapors from the closed-vent system to the
			 atmosphere at a point upstream of the control device inlet. For this paragraph,
			 a flow indicator means a device which indicates the presence of either gas or
			 vapor flow in the bypass line.
(b)
										If a seal or
			 locking device is used to comply with paragraph (B)(3) of this rule, the device
			 shall be placed on the mechanism by which the bypass device position is
			 controlled (e.g., valve handle, damper lever) when the bypass device is in the
			 closed position such that the bypass device cannot be opened without breaking
			 the seal or removing the lock. Examples of such devices include, but are not
			 limited to, a car-seal or a lock-and-key configuration valve. The owner or
			 operator shall visually inspect the seal
(4)
									The closed-vent
			 system shall be inspected and monitored by the owner or operator in accordance
			 with the procedure specified in paragraph (L) of rule
			 3745-205-33 of the
			 Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-88 - Inspection and monitoring - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								The owner or operator shall inspect and monitor air
			 emission control equipment used to comply with rules
			 3745-205-80 to
			 3745-205-90 of the
			 Administrative Code in accordance with the applicable requirements specified in
			 rules 3745-205-84 to
			 3745-205-87 of the
			 Administrative Code.
(B)
								The owner or operator shall develop and implement a
			 written plan and schedule to perform the inspections and monitoring required by
			 paragraph (A) of this rule. The owner or operator shall incorporate this plan
			 and schedule into the facility inspection plan required under rule
			 3745-54-15 of the Administrative
			 Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-89 - Recordkeeping - air emission standards for tanks, surface impoundments, and containers

Current through all regulations passed and filed through July 1, 2024
(A)
								Each owner or operator of a facility subject to
			 requirements of rules
			 3745-205-80 to
			 3745-205-90 of the
			 Administrative Code shall record and maintain the information specified in
			 paragraphs (B) to (J) of this rule, as applicable to the facility. Except for
			 air emission control equipment design documentation and information required by
			 paragraphs (I) and (J) of this rule, records required by this shall be
			 maintained in the operating record for a minimum of three years. Air emission
			 control equipment design documentation shall be maintained in the operating
			 record until the air emission control equipment is replaced or otherwise no
			 longer in service. Information required by paragraphs (I) and (J) of this rule
			 shall be maintained in the operating record for as long as the waste management
			 unit is not using air emission controls specified in rules
			 3745-205-84 to
			 3745-205-87 of the
			 Administrative Code in accordance with the conditions specified in paragraph
			 (B)(7) or (D) of rule
			 3745-205-80 of the
			 Administrative Code, respectively.
(B)
								The owner or
			 operator of a tank using air emission controls in accordance with the
			 requirements of rule
			 3745-205-84 of the
			 Administrative Code shall prepare and maintain records for the tank that
			 include the following information:
(1)
									For each tank using air emission controls in accordance
			 with the requirements of rule
			 3745-205-84 of the
			 Administrative Code, the owner or operator shall record:
(a)
										A tank
			 identification number (or other unique identification description as selected
			 by the owner or operator).
(b)
										A record for each
			 inspection required by rule
			 3745-205-84 of the
			 Administrative Code that includes the following information:
(i)
											Date inspection
			 was conducted.
(ii)
											For each defect detected during the inspection, the
			 location of the defect, a description of the defect, the date of detection, and
			 corrective action taken to repair the defect. In the event that repair of the
			 defect is delayed in accordance with the requirements of rule
			 3745-205-84 of the
			 Administrative Code, the owner or operator also shall record the reason for the
			 delay and the date that completion of repair of the defect is
			 expected.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-100 - Applicability- containment buildings

Current through all regulations passed and filed through July 1, 2024
Rules 3745-205-100 to
				3745-205-102
				of the Administrative Code apply to owners or operators who store or treat
				hazardous waste in units designed and operated under rule
				3745-205-101
				of the Administrative Code. The owner or operator is not subject to the
				definition of "land disposal" in rule
				3745-270-02
				of the Administrative Code, provided that the unit meets the following
				requirements:
(A) Is a completely
			 enclosed, self-supporting structure that is designed and constructed of
			 man-made materials of sufficient strength and thickness to support the
			 materials, the waste contents, and any personnel and heavy equipment that
			 operate within the unit; and to prevent failure due to pressure gradients,
			 settlement, compression, uplift, physical contact with the wastes to which the
			 materials are exposed, climatic conditions, and the stresses of daily operation
			 (including the movement of heavy equipment within the unit and contact of such
			 equipment with containment walls).
(B) Has a primary barrier that is designed to
			 be sufficiently durable to withstand the movement of personnel, wastes, and
			 handling equipment within the unit.
(C) If used to manage a hazardous waste
			 containing free liquids (the presence of which is determined by the paint
			 filter test, a visual examination, or other appropriate means), has the
			 following:
(1) A primary barrier designed and
			 constructed of materials to prevent migration of hazardous constituents into
			 the barrier.
(2) A liquid
			 collection system designed and constructed of materials to minimize the
			 accumulation of liquid on the primary barrier.
(3) A secondary containment system designed
			 and constructed of materials to prevent migration of hazardous constituents
			 into the barrier, with a leak detection and liquid collection system capable of
			 detecting, collecting, and removing leaks of hazardous constituents at the
			 earliest practicable time, unless the unit was granted a variance from the
			 secondary containment system requirements under paragraph (B)(4) of rule
			 3745-205-101
			 of the Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-101 - Design and operating standards for containment buildings

Current through all regulations passed and filed through July 1, 2024
(A) All containment buildings shall comply
			 with the following design standards:
(1) The
			 containment buildings shall be completely enclosed with a floor, walls, and a
			 roof to prevent exposure to the elements (e.g., precipitation, wind, run-on),
			 and to assure containment of managed wastes.
(2) The floor and containment walls of the
			 unit, including the secondary containment system if required under paragraph
			 (B) of this rule, shall be designed and constructed of
			  materials of sufficient strength
			 and thickness to support such floor and walls, the waste contents, and any
			 personnel and heavy equipment that operate within the unit, and to prevent
			 failure due to pressure gradients, settlement, compression, uplift, physical
			 contact with the wastes to which such floor and walls are exposed, climatic
			 conditions, and the stresses of daily operation (including the movement of
			 heavy equipment within the unit and contact of such equipment with containment
			 walls). The unit shall be designed so that the unit has sufficient structural
			 strength to prevent collapse or other failure. All surfaces to be in contact
			 with hazardous wastes shall be chemically compatible with those wastes. Ohio
			 EPA will consider standards established by professional organizations generally
			 recognized by the industry such as the American concrete institute (ACI) and
			 the American society of testing materials (ASTM) in judging the structural
			 integrity requirements of paragraph (A)  of this rule. If appropriate to the nature of the waste
			 management operation to take place in the unit, an exception to the structural
			 strength requirement may be made for light-weight doors and windows that meet
			 the following criteria:
(a) The doors and
			 windows provide an effective barrier against fugitive dust emissions under
			 paragraph (C)(1)(d) of this rule.
(b) The unit is designed and operated in a
			 manner that assures that wastes will not actually come in contact with these
			 openings.
(3)
			 Incompatible hazardous wastes or treatment reagents shall not be placed in the
			 unit or the unit's secondary containment system if such substances could cause
			 the unit or secondary containment system to leak, corrode, or otherwise
			 fail.
(4) A containment building
			 shall have a primary barrier designed to withstand the movement of personnel,
			 waste, and handling equipment in the unit during the operating life of the unit
			 and appropriate for the physical and chemical characteristics of the waste to
			 be managed.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-102 - Closure and post-closure care of containment buildings

Current through all regulations passed and filed through July 1, 2024
(A) At closure of a
			 containment building, the owner or operator must remove or decontaminate all
			 waste residues, contaminated containment system components (liners, etc.),
			 contaminated subsoils, and structures and equipment contaminated with waste and
			 leachate, and must manage them as hazardous waste unless paragraph (D) of rule
			 3745-51-03
			 of the Administrative Code applies. The closure plan, closure activities, cost
			 estimate for closure, and financial responsibility for containment buildings
			 must meet all of the requirements specified in rules
			 3745-55-10
			 to
			 3745-55-20
			 and
			 3745-55-40
			 to
			 3745-55-51
			 of the Administrative Code.
(B) If,
			 after removing or decontaminating all residues and making all reasonable
			 efforts to effect removal or decontamination of contaminated components,
			 subsoils, structures, and equipment as required in paragraph (A) of this rule,
			 the owner or operator finds that not all contaminated subsoils can be
			 practicably removed or decontaminated, he must close the facility and perform
			 post-closure care in accordance with the closure and post-closure requirements
			 that apply to landfills (see rule
			 3745-57-10
			 of the Administrative Code). In addition, for the purposes of closure,
			 post-closure, and financial responsibility, such a containment building is
			 considered to be a landfill, and the owner or operator must meet all of the
			 requirements for landfills specified in rules
			 3745-55-10
			 to
			 3745-55-20
			 and
			 3745-55-40
			 to
			 3745-55-51
			 of the Administrative Code.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-200 - Applicability - military munitions

Current through all regulations passed and filed through July 1, 2024
Rules 3745-205-200 to 3745-205-202 of the
				Administrative Code apply to owners or operators who store hazardous waste
				munitions and hazardous waste explosives, except as rule
				3745-54-01 of the Administrative
				Code provides otherwise.
[Comment: Depending on explosive hazards, hazardous waste
				munitions and hazardous waste explosives may also be managed in other types of
				storage units, including containment buildings (rules
				3745-205-100 to
				3745-205-102 of the
				Administrative Code), tanks (rules
				3745-55-90 to
				
								3745-55-100 of the Administrative Code), or containers
				(rules 3745-55-70 to
				
								3745-55-79 of the Administrative Code). See rule
				3745-266-205 of the
				Administrative Code for storage of waste military munitions.]
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-201 - Design and operating standards for military munitions

Current through all regulations passed and filed through July 1, 2024
(A) Hazardous waste
			 munitions and hazardous waste explosives storage units must be designed and
			 operated with containment systems, controls, and monitoring, that:
(1) Minimize the potential for detonation or
			 other means of release of hazardous waste, hazardous constituents, hazardous
			 decomposition products, or contaminated run-off, to the soil, ground water,
			 surface water, and atmosphere;
(2)
			 Provide a primary barrier, which may be a container (including a shell) or
			 tank, designed to contain the hazardous waste;
(3) For wastes stored outdoors, provide that
			 the waste and containers will not be in standing precipitation;
(4) For liquid wastes, provide a secondary
			 containment system that assures that any released liquids are contained and
			 promptly detected and removed from the waste area, or vapor detection system
			 that assures that any released liquids or vapors are promptly detected and an
			 appropriate response taken (e.g., additional containment, such as overpacking,
			 or removal from the waste area); and
(5) Provide monitoring and inspection
			 procedures that assure the controls and containment systems are working as
			 designed and that releases that may adversely impact human health or the
			 environment are not escaping from the unit.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-205 - Hazardous Waste Containment Buildings, Munitions or Explosives › Section 3745-205-202 - Closure and post-closure care of military munitions

Current through all regulations passed and filed through July 1, 2024
(A) At closure of a magazine or unit which
			 stored hazardous waste under rules
			 3745-205-200
			 to 3745-205-202 of the Administrative Code, the owner or operator must remove
			 or decontaminate all waste residues, contaminated containment system
			 components, contaminated subsoils, and structures and equipment contaminated
			 with waste, and manage them as hazardous waste unless paragraph (D) of rule
			 3745-51-03
			 of the Administrative Code applies. The closure plan, closure activities, cost
			 estimates for closure, and financial responsibility for magazines or units must
			 meet all of the requirements specified in rules
			 3745-55-10
			 to
			 3745-55-20
			 and
			 3745-55-40
			 to
			 3745-55-51
			 of the Administrative Code, except that the owner or operator may defer closure
			 of the unit as long as it remains in service as a munitions or explosives
			 magazine or storage unit.
(B) If,
			 after removing or decontaminating all residues and making all reasonable
			 efforts to effect removal or decontamination of contaminated components,
			 subsoils, structures, and equipment as required in paragraph (A) of this rule,
			 the owner or operator finds that not all contaminated subsoils can be
			 practicably removed or decontaminated, he must close the facility and perform
			 post-closure care in accordance with the closure and post-closure requirements
			 that apply to landfills (see rule
			 3745-57-10
			 of the Administrative Code).
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-218 - Containment Buildings for Hazardous Wastes Meeting No Visible Emissions Standard › Section 3745-218-01 - Applicability of rules 3745-218-01 to 3745-218-02 of the Administrative Code. [Rescinded]

Current through all regulations passed and filed through July 1, 2024
Rescinded eff 12-7-04
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-248 - Containment Buildings for Hazardous Wastes › Section 3745-248-01 - Applicability of rules 3745-248-01 to 3745-248-02 of the Administrative Code. [Rescinded]

Current through all regulations passed and filed through July 1, 2024
Rescinded eff 12-7-04
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-256 - Containment Buildings, Military Munitions › Section 3745-256-30 - Applicability and definitions - air emission standards for process vents

Current through all regulations passed and filed through July 1, 2024
(A)
								Applicability. Rules
			 3745-256-30 to
			 3745-256-35 of the
			 Administrative Code apply to owners and operators of facilities that treat,
			 store, or dispose of hazardous wastes (except as provided in rule
			 3745-65-01 of the Administrative
			 Code).
(B)
								Except for paragraphs (D) and (E) of rule
			 3745-256-34 of the
			 Administrative Code, rules
			 3745-256-30 to
			 3745-256-35 of the
			 Administrative Code apply to process vents associated with distillation,
			 fractionation, thin-film evaporation, solvent extraction, or air or steam
			 stripping operations that manage hazardous wastes with organic concentrations
			 of at least ten parts per million by weight, if these operations are conducted
			 in one of the following:
(1)
									A unit that is subject to the permitting requirements
			 of rules
			 3745-50-40 to
			 3745-50-235 of the
			 Administrative Code; or
(2)
									A unit (including a hazardous waste recycling unit)
			 that is not exempt from permitting under the rule
			 3745-52-17 of the Administrative
			 Code (i.e., a hazardous waste recycling unit that is not a ninety-day tank or
			 container) and that is located at a hazardous waste management facility
			 otherwise subject to the permitting requirements of rules
			 3745-50-40 to
			 3745-50-235 of the
			 Administrative Code; or
(3)
									A unit that is exempt from permitting under rule
			 3745-52-17 of the Administrative
			 Code (i.e., a "ninety-day" tank or container) and is not a recycling unit under
			 the requirements of rule
			 3745-51-06 of the Administrative
			 Code.
[Comment: Rules 3745-256-32 to
				3745-256-35 of the Administrative Code apply to process vents on hazardous
				waste recycling units previously exempt under paragraph (C)(1) of rule
				3745-51-06 of the Administrative Code. Other exemptions under rule 3745-51-04
				and paragraph (C) of rule
				3745-65-01 of the Administrative
				Code are not affected by these requirements.]
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-256 - Containment Buildings, Military Munitions › Section 3745-256-32 - Process vents - air emission standards for process vents

Current through all regulations passed and filed through July 1, 2024
(A)
								The owner or operator of a facility with process vents
			 associated with distillation, fractionation, thin-film evaporation, solvent
			 extraction or air or steam stripping operations managing hazardous wastes with
			 organic concentrations at least ten parts per million by weight shall
			 either:
(1)
									Reduce total organic emissions from all affected process
			 vents at the facility below
			 1.4 kilograms per hour (kg/h)
			 [three pounds per hour (lb/h)] and
			 2.8 megagrams per year (Mg/yr)
			 [3.1 ton per year (tons/yr)];
			 or
(2)
									Reduce, by use of a control device, total organic
			 emissions from all affected process vents at the facility by ninety-five weight
			 per cent.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-256 - Containment Buildings, Military Munitions › Section 3745-256-34 - Test methods and procedures - process vents

Current through all regulations passed and filed through July 1, 2024
(A)
								Each owner or
			 operator subject to rules
			 3745-256-30 to
			 3745-256-35 of the
			 Administrative Code shall comply with the test methods and procedures
			 requirements provided in this rule.
(B)
								When a
			 closed-vent system is tested for compliance with no detectable emissions, as
			 required in paragraph (K) of rule
			 3745-256-33 of the
			 Administrative Code, the test shall comply with the following
			 requirements:
(1)
									Monitoring shall comply with reference method 21 in 40
			 CFR Part 60.
(2)
									The detection instrument shall meet the performance
			 criteria of reference method 21.
(3)
									The instrument
			 shall be calibrated before use on each day of its use by the procedures
			 specified in reference method 21.
(4)
									Calibration gases
			 shall be:
(a)
										Zero air (less than ten parts per million (ppm) of
			 hydrocarbon in air).
(b)
										A mixture of methane or n-hexane and air at a
			 concentration of approximately, but less than, ten thousand ppm methane or
			 n-hexane.
(5)
									The background level shall be determined as provided in
			 reference method 21.
(6)
									The instrument probe shall be traversed around all
			 potential leak interfaces as close to the interface as possible as described in
			 reference method 21.
(7)
									The arithmetic difference between the maximum
			 concentration indicated by the instrument and the background level is compared
			 with five hundred ppm for determining compliance.
Ohio Administrative Code › Title 3745 - Ohio Environmental Protection Agency › Chapter 3745-256 - Containment Buildings, Military Munitions › Section 3745-256-35 - Recordkeeping - process vents

Current through all regulations passed and filed through July 1, 2024
(A)
(1)
									Each owner or operator subject to rules
			 3745-256-30 to
			 3745-256-35 of the
			 Administrative Code shall comply with the recordkeeping requirements of this
			 rule.
(2)
									An owner or operator of more than one hazardous waste
			 management unit subject to rules
			 3745-256-30 to
			 3745-256-35 of the
			 Administrative Code may comply with the recordkeeping requirements for these
			 hazardous waste management units in one recordkeeping system if the system
			 identifies each record by each hazardous waste management unit.