reglab/statecodes huggingface dataset:
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-6 - Walkways or decks

Current through Vol. 41, No. 20, July 1, 2024
(a)
Width.
A walkway shall entirely surround the pool. It shall not be
				less than four (4) feet wide at indoor pools. The walk area about outdoor pools
				and within the fence shall be equivalent to that provided by a walk at least
				eight (8) feet wide around the pool. In no case shall the minimum width of the
				walk be less than four (4) feet at outdoor pools. Where an outdoor pool is
				covered for cold weather use, the walkway requirements for indoor pools shall
				govern the size of cover.
(b)
Slope.
All walks, decks and terraces shall have a minimum slope of
				one-fourth (1/4) inch per foot to drains or points at which the water will have
				a free, unobstructed flow to points of disposal at all times. Drainage
				connections to the recirculation system, scum gutter or suitable waste are
				acceptable. Drainage into the pool is prohibited.
(c)
Finish.
(1) It is recommended that decks adjoining
				the pool at public bathing places be constructed of concrete or other
				impervious material, have a slip-resistant finish, be easily cleanable, not
				allow standing water, and not cause discomfort to bare feet. Epoxied gravel
				should not be used as deck material unless the interstices are filled with a
				stable, inert material.
(2) Wooden
				decks or walkways are prohibited adjoining the pool at public bathing places
				open to the general public but may be approved at public bathing places not
				open to the general public, indoors where such decks are sealed by a resin or
				other waterproof material, and outdoors where the design provides for adequate
				cleaning, sanitation, safety, and exposure to the drying action of the sun and
				wind.
(3) Indoor/outdoor carpets,
				absorbent or adsorbent coverings or similar deck materials are not recommended
				for use on the deck or walkways around outdoor public bathing places and
				prohibited at all indoor public bathing places. If carpeting or other porous
				materials are used as deck covering at outdoor pools, the substrate supporting
				the covering, and all ancillary features, shall comply with the recommendations
				of paragraph one of this chapter and with 310:315-7-6.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-8 - Ventilation

Current through Vol. 41, No. 20, July 1, 2024
(a)
Indoor areas.
Indoor pools,
				shower rooms, dressing rooms, and toilets of all public bathing places shall be
				properly ventilated, with the further provision that the ventilating system for
				indoor pools be so designed as to prevent direct drafts on the
				bathers.
(b)
Interior
				rooms.
All interior rooms shall be ventilated so that they do not remain
				excessively damp.
(c)
Toilet
				rooms.
Toilet rooms shall be ventilated to the outside so that no odor
				nuisance may develop.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-9 - Wading pools

Current through Vol. 41, No. 20, July 1, 2024
(a)
Wading
				pools used by children.
Since wading pools will be used by children, who
				are more susceptible to disease than adults, the standards of sanitation shall
				be equal, or superior, to those for swimming pools. The maximum depth of all
				wading pools cannot exceed eighteen (18) inches. A reasonably non-slip surface
				shall be provided. Bottom slopes shall not exceed one (1) foot in twelve (12)
				feet. Bathing water shall meet all of the water quality requirements as
				specified for all artificially constructed bathing places.
(b)
Recirculation.
Wading pools
				shall have a minimum of one (1) turnover every four (4) hours (two (2) hours is
				strongly recommended). Unless a separate recirculation system is provided for
				the wading pool, the main pool recirculation system shall be designed for the
				additional flow. All recirculation piping to and from the wading pool shall be
				valved utilizing valves designed for proportioning flows. Rate of flow
				indicators shall be installed to indicate the flow rate to the wading pool. The
				piping, fittings, and hydraulic requirements shall be in accordance with OAC
				310:315-7-14.
(1)
Inlets, outlets.
Adjustable
				inlets shall be provided for wading pools based on a minimum of one (1) inlet
				for each twenty (20) feet, or fraction thereof, of pool perimeter except that
				wading pools with twenty (20) feet or less of perimeter shall have a minimum of
				two (2) equally spaced adjustable inlets. Submerged suction outlets shall meet
				the requirements of OAC
				310:315-7-14(h).
(2)
Surface skimmers.
One (1)
				surface skimmer shall be provided for each four hundred (400) square feet of
				surface area or fraction thereof. Multiple skimmers shall be equally spaced and
				shall meet all the requirements of OAC
				310:315-7-14.
(3)
Emergency drainage.
All
				wading pools shall have drainage to waste (with indirect connection) through a
				quick opening valve to facilitate emptying the wading pools should accidental
				bowel or other discharge occur.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-10 - Spray pools [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 26 Ok Reg
				  2003, eff 6-25-09
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-11 - Public spas

Current through Vol. 41, No. 20, July 1, 2024
(a)
Spas.
Spas shall be made of concrete or other impervious materials
				with a finish adapted to the needs of the facility. Spas shall be of such shape
				and size as to be operated and maintained in a safe and sanitary manner. In
				addition to the requirements of this section, compliance is required with all
				other applicable sections of this chapter.
(b)
Water depths and floor
				slopes.
The maximum water depth of a spa is four (4) feet. The spa floor
				shall slope uniformly to a main drain and cannot exceed one (1) foot in twelve
				(12) feet (1:12).
(c)
Steps.
Steps shall be provided for adequate entrance to and exit
				from the spa. The number of sets of steps required equals one (1) for each
				fifty (50) feet, or major fraction thereof, of spa perimeter. They shall be
				constructed of an easily cleaned impervious materials having a slip resistant
				finish. Step sets for spas with more than two hundred (200) square feet of spa
				water surface area shall comply with OAC
				310:315-7-5(a).
				Step sets for spas with two hundred (200) square feet or less of spa water
				surface area shall comply with the following:
(1) Step treads have a minimum continuous
				tread length of twelve (12) inches and a minimum tread width of ten (10)
				inches.
(2) Step riser heights do
				not exceed twelve (12) inches, except that when the bottom step is used for a
				bench or seat, the bottom riser may be a maximum of fourteen (14)
				inches.
(3) Intermediate treads and
				risers between the top and bottom treads and risers are uniform in width and
				height, respectively.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-13 - Chemicals and chemical storage

Current through Vol. 41, No. 20, July 1, 2024
(a)
Chemical storage and equipment.
For chemicals necessary in water
				treatment, disinfection, and pH control, provision shall be made for dry
				storage of at least a two (2) weeks supply. Equipment shall be provided for
				batch preparation of chemicals sufficient for twenty-four (24) hours
				feeding.
(b)
Storage room
				marking.
All rooms or areas used for storage of pool chemicals shall be
				plainly marked on the outside door. This may be done as follows:
(1) A sign stating "POOL
				CHEMICALS".
(2) A sign approved by
				the local fire officials which indicates that the contents are potentially
				dangerous.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-14 - Recirculation system

Current through Vol. 41, No. 20, July 1, 2024
(a)
General
				considerations.
(1) A circulation
				system shall be provided which will include pumps, hair-catcher, and filters,
				together with all necessary piping connections to the inlets and outlets of the
				pool, including features, such as the water heater, chlorinator, and suction
				cleaner, etc. The entire system and all component parts of swimming pools shall
				be designed to provide a minimum of three (3) replacements of the bathing water
				volume every twenty-four (24) hours (four (4) turnovers are recommended), with
				maximum frictional resistance. At pools and spas with skimmers, the required
				skimmer flow, rather than turnover, may determine the minimum flow. Design is
				based on main drain flow at thirty (30) percent of the total recirculation, and
				thirty (30) gpm through each skimmer. This is represented as 0.3Q + 30n = Q =
				total recirculation flow rate and n = number of skimmers. (Main drain flow is
				0.3Q.) These criteria, plus the maximum allowable filter flux (15 gpm/ft2 for
				rapid sand filters) and the maximum total dynamic head loss calculated assuming
				a "dirty" filter ready for backwash, comprise the basic design requirements for
				pools and spas.
(2) A collector
				tank or other means for accommodating surge capacity shall be provided for all
				pools using overflow gutters connected to the recirculation
				system.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-17 - Testing equipment

Current through Vol. 41, No. 20, July 1, 2024
(a)
Test
				kits.
Test kits are required at all pools to determine free active
				chlorine and total or combined available chlorine (using D.P.D. reagents), or
				bromine, total alkalinity, calcium hardness, and pH.
(b)
Cyanuric acid test kits.
Cyanuric acid test kits are required at all pools in which cyanurates or
				cyanuric acid stabilized chlorine products are used. The concentration of
				cyanuric acid in the pool water shall not exceed one hundred (100)
				ppm.
(c)
Sodium chloride test
				kits.
Sodium chloride test kits are required at all pools which utilize
				accepted electrolytic chlorine generators which require sodium chloride
				concentrations in the pool water. The concentration of sodium chloride in the
				pool water shall be maintained in the range specified by the electrolytic
				chlorine generator manufacturer.
(d)
Thermometers.
All facilities
				heating the water to temperatures over 90 
				oF shall maintain on the premises, in
				the pool or pool enclosure, a thermometer to take the temperature of the water.
				Those facilities requiring the ambient air temperature to be monitored shall
				maintain a suitable thermometer with a Fahrenheit scale at deck level in the
				pool room to monitor air temperature.
(e)
Test kits, spas.
In addition
				to fulfilling the foregoing requirements of this section, spa facilities shall
				be equipped to test for concentrations of total dissolved solids, copper, and
				iron.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-18 - Lighting

Current through Vol. 41, No. 20, July 1, 2024
(a)
Artificial lighting.
A
				complete system of artificial lighting shall be provided for all pools, rest
				rooms, toilet rooms, shower rooms, store rooms, and other areas of public
				bathing places.
(b)
Arrangement.
The arrangement and design of the lighting shall be
				such that attendants may clearly observe every part of the pool, spring boards,
				towers, floats, or other appurtenances. The lighting system of outdoor pools
				shall be designed with sources of illumination located so as to prevent insects
				attracted by the lights from falling into the water.
(c)
Underwater lights.
Where
				underwater lighting is used, it is recommended that the minimum illumination be
				eight (8) foot-candles at any point in the pool. Such lights shall be spaced to
				provide illumination so that all portions of the pool and pool bottom may be
				seen without glare.
(d)
Area
				lighting.
Area lighting shall provide a minimum of ten (10) foot-candles
				at all points on the deck.
(e)
Interior rooms.
All rooms shall be provided with sufficient light
				so that all sections may be observed and are easily visible for cleaning
				purposes. A minimum of ten (10) foot-candles shall be provided in all interior
				rooms.
(f)
Emergency
				lighting.
Emergency lighting shall be provided at all indoor bathing
				facilities, in accordance with the requirements of the current edition of the
				NFPA 101 Life Safety Code, unless assurance can be provided that the facility
				will always be locked and not used at night.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 315 - Public Bathing Place Facility Standards › Subchapter 7 - Construction and Operation › Section 310:315-7-19 - Electrical requirements

Current through Vol. 41, No. 20, July 1, 2024
(a)
Wiring
				standards.
All wiring in connection with requirements for a swimming
				pool for lighting or power shall conform with the National Electrical Code of
				the National Underwriters Laboratories.
(b)
Grounding.
In addition to
				the grounding requirements for electrical equipment and circuits by the
				National Electrical Code, all metal water and other metal piping to and from
				the public bathing place, including inlet and outlet pipes, shall be
				metallically bonded together and adequately connected to the same grounding
				electrode used to ground the neutral conductor of the electrical system. Where
				metal fence is used, it shall be grounded at both sides of the entrance
				gate.
(c)
Electrical
				devices.
All electrical devices such as portable announcing systems,
				radios, and soft drink dispensers that might be used around the pool deck and
				immediate environment shall be prohibited within reach of bathers. Further
				special grounding of such fixtures must be provided.
(d)
Overhead conductors.
No
				electrical wiring shall pass overhead within twenty (20) feet of the pool
				enclosure.
(e)
Ground fault
				interrupter type circuit breakers.
Ground fault interrupter type circuit
				breakers shall be provided for all outlets within fifteen (15) feet of the pool
				and those located in the bathhouse and pump room.
(f)
Underwater light assemblies.
All underwater light assemblies shall comply with 310:315-7-19 and shall be
				connected in one of the following manners.
(1)
				Using a low-voltage twelve (12) volt system with three hundred (300) watt or
				less underwater light(s).
(2) New
				one hundred-ten (110) volt systems will have an approved junction box (deck
				box) in excess of eight (8) inches above the deck level and must have a ground
				fault interrupter installed at the main panel.
(3) All existing underwater lighting systems
				using one hundred-ten (110) volts shall have a ground fault interrupter
				installed at the main panel.
(4)
				Low water cutoffs are strongly recommended.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 1 - General Provisions › Section 310:320-1-1 - Purpose

Current through Vol. 41, No. 20, July 1, 2024
The Public Bathing Place Operational Regulations are minimum
				  design criteria and will be used as such by the State Department of Health.
				  Nothing in these operational regulations should be construed as preventing the
				  consulting engineer from recommending, or the reviewing authority from
				  approving, more effective treatment where local conditions dictate such
				  action.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 1 - General Provisions › Section 310:320-1-3 - Operational license

Current through Vol. 41, No. 20, July 1, 2024
(a) No person,
				municipality, or entity shall operate a public bathing place without obtaining
				a license from the Commissioner of Health pursuant to 63 §
				1-1013.1.
(b) A license to operate
				a public bathing place is not required for
those public or semipublic
				baths where the main object is the external cleansing of the body,
"Private Pools",
or to bathing places owned or managed by a group or
				association of the owners of thirty or fewer homes, the use of which is limited
				to the homeowner group and their nonpaying guests.
(c) A public bathing place may be inspected
				by representatives of the Department at any reasonable time to determine if the
				public bathing place complies with applicable statutes and rules administered
				by the Department [63 O.S. § 1-1018].
Added at 26 Ok Reg 1491,
				  eff 6-11-09
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-1 - Life saving equipment

Current through Vol. 41, No. 20, July 1, 2024
(a)
Adequate life saving equipment.
Adequate life saving equipment
				shall be provided at all public bathing places where the water is sufficiently
				deep for swimming and diving, to minimize the danger of drowning and of
				injuries to bathers from falls or collisions.
(b)
Lifeguard chairs.
Each
				public bathing place open to the general public shall have at least one (1)
				elevated lifeguard chair. This shall be presumed to be adequate for two
				thousand (2000) square feet of pool surface area with an additional lifeguard
				chair being provided for each additional area of two thousand (2000) square
				feet or fraction thereof. Lifeguard chairs shall be located so that a lifeguard
				is not required to protect a segment in excess of one hundred-eighty (180)
				degrees. Where a pool is provided with more than one (1) lifeguard chair and
				the pool width is forty (40) feet or more, chairs shall be located on each side
				of the pool. See OAC
				310:315-7-3
				and OAC
				310:320-3-2.
(c)
Small pools.
Every public
				pool having a horizontal dimension that is thirty (30) feet or less or a
				surface area less than sixteen hundred (1600) square feet shall provide:
(1) One (1) or more poles each at least
				sixteen (16) feet in length. These shall end in a shepherd's crook with an
				opening of at least eighteen (18) inches and shall be constructed of light
				sturdy material such as aluminum or bamboo and used according to the
				manufacturer's instructions.
(2)
				Two (2) or more ring-buoys fifteen (15) to eighteen (18) inches in diameter,
				constructed of light material, with at least one-quarter (1/4) inch rope
				attached to reach the length of the pool, not to exceed forty (40)
				feet.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-3 - Rules and precautions for patrons

Current through Vol. 41, No. 20, July 1, 2024
(a)
Rules for pools.
Rules governing the use of pools, spas, and other
				public bathing places shall be displayed on signs large enough for easy reading
				which are posted at the entrance to the pool, dressing rooms, or other
				appropriate places. Sign shall provide, in similar language, that:
(1) A cleansing shower bath, using warm water
				and soap, must be taken before entering the pool.
(2) Persons with open wounds, bandages, or
				any symptom of communicable disease shall be prevented from entering the
				pool.
(3) Swimming alone is
				prohibited.
(4) At pools which do
				not have attendants or lifeguards on duty, children under twelve (12) years of
				age must be accompanied by an adult responsible for that individual child at
				the pool side.
(5) Running and
				rough play are prohibited in and around the pool.
(6) "Cut-offs" should be hemmed.
(7) Excess body lotions should be removed
				prior to entering the water.
(8)
				Bathing load limits shall be posted and enforced. See Standards Section
				310:315-7-3.
(9) "NO LIFEGUARD OR ATTENDANT ON DUTY" where
				appropriate. See OAC
				310:320-3-2.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-4 - Safety provisions

Current through Vol. 41, No. 20, July 1, 2024
(a)
Emergency
				telephone numbers.
Every bathing place shall provide, immediately
				adjacent to its telephone, anotice to dial 911 in the event of an
				emergency.
(b)
Bathing
				load.
The bathing load must be observed and enforced by pool personnel
				and shall not exceed design standards as per OAC
				310:315-7-3.
				The bathing load limit shall be posted in plain sight at all pools.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-5 - Swimming suits and towels furnished by management

Current through Vol. 41, No. 20, July 1, 2024
(a)
Suits and towels.
All
				swimming suits and towels used by and maintained for public use shall be
				thoroughly washed with hot water and soap or detergent, rinsed, and thoroughly
				dried and sterilized by heat each time they are used, or an equivalent approved
				process shall be used.
(b)
Clean suits and towels.
Clean swimming suits and towels cannot
				come in contact with unwashed suits and towels or be stored on shelves or in
				baskets which have been used for storing dirty swimming suits and towels. The
				issuing of clean suits and towels at the same counters where dirty towels and
				suits are turned in shall be prevented.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-6 - Wading pool operation

Current through Vol. 41, No. 20, July 1, 2024
(a)
Operation.
All artificially constructed bathing places, including
				wading pools using recirculation systems, shall be free of turbidity, algae,
				and slime or floating matter, and the water quality shall comply with the same
				standards as all other artificially constructed bathing places.
(b)
Supervision.
A supervisor
				shall be present at all times when a wading pool is in use. The supervisor's
				main duties consist of maintaining proper conduct and guarding against
				accidents. Children over twelve (12) years of age should be permitted to enter
				the enclosure but not the pool. Children with open sores or cuts, bruises,
				etc., or any contagious disease should not be admitted to the pool. The pool
				should be operated on definite hours on prescribed days. This supervisor
				replaces lifeguards and other safety requirements.
(c)
Drains.
Wading pool drains
				shall have grates or covers complying with OAC
				310:315-7-14.
				This stipulation shall apply to all existing wading pools with recirculation
				systems, as well as those to be constructed.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-7 - Quality of Bathing Water

Current through Vol. 41, No. 20, July 1, 2024
The pool water of all artificially constructed public
				  bathing places shall undergo treatment necessary to comply with the standards
				  set forth in OAC
				  310:320-3-8.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-8 - Table

Current through Vol. 41, No. 20, July 1, 2024
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-9 - Sampling and testing procedures

Current through Vol. 41, No. 20, July 1, 2024
(a)
Bathing place operators.
All bathing place operators shall know
				how to perform the following:
(1) Collect a
				sample for bacterial analysis.
(2)
				Collect at proper places, a representative sample for determination of
				applicable chemical and operational parameters required by OAC
				310:320-3-9.
(3) Be able to perform
				all applicable chemical analyses and operational determinations required by OAC
				310:320-3-9. The D.P.D. method should be used for free and combined chlorine
				determination. Orthotolidine (OTO) is not an acceptable method for
				determination of free chlorine.
(4)
				Observe the proper procedure of turbidity determination. Close pool any time
				the main drain cannot be seen from the sidewalk. Determine cause and reduce
				turbidity to acceptable level before reopening pool.
(5) Observe the water temperature in hot
				water pools and spas.
(6) Balance
				the pool water in relation to pH, total alkalinity, and calcium hardness as per
				OAC
				310:320-3-7
				(see OAC
				310:320-5-2
				for Tables).
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-10 - Satisfactory compliance of records

Current through Vol. 41, No. 20, July 1, 2024
(a) The
				management of a facility is responsible for maintaining records only on those
				line items of the report that apply to their bathing place. All bathing places
				must maintain information on turbidity, pH, and chlorine residual; and for
				pools using stabilized chlorine compounds, cyanuric acid
(b) Records shall be submitted to the county
				health department, or for those counties without a county health department, to
				the appropriate sanitarian upon request.
(c)
Records forms.
Public
				bathing place operation record forms may be obtained from the Department. The
				information must be filled in completely for each day the public bathing place
				is open. Forms tailored to suit the needs of the management may be substituted
				for Department forms provided that all information required by these standards
				is included and the forms are submitted to the Department for approval prior to
				use.
(d)
Laboratory
				reports.
The laboratory reports covering any chemical or bacteriological
				examination of the water in a public bathing place must be kept on the premises
				and made accessible to authorized representatives of the Department.
(e)
Operation report form.
The
				public bathing place operation record forms are designed to cover one (1) full
				week of operation. A copy shall be forwarded to the appropriate health
				department upon request.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-11 - Winterizing and securing outdoor pools

Current through Vol. 41, No. 20, July 1, 2024
When the pool is closed, all gates shall be locked. All
				  outdoor pools shall be secured in one of the following approved methods:
(1)
Draining.
Drained
				and kept drained until put back into service; or
(2)
Pools not drained or
				covered.
Turbidity shall be controlled so that the main drain is visible
				from the pool deck. Maintaining disinfectant concentrations will suppress algae
				growthand maintaining water balance will protect concrete and metal
				surfaces.
(3)
Covering.
Provide a pool cover of a type that is securely anchored
				to the deck area with bolts or similar hardware and capable of supporting a
				minimum of one thousand (1000) pounds. Water must not be allowed to accumulate
				on the top. Swimming in the pool with a partial cover is prohibited. If water
				is left in the pool, it should be drained below the tile and skimmers (eighteen
				(18) to twenty-four (24) inches) and kept chlorinated. The air should be blown
				out of the skimmer and fill lines. Lights should be stored on the deck or in
				the bottom of the pool and with switches taped in the off position.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-12 - Special conditions

Current through Vol. 41, No. 20, July 1, 2024
Should special conditions exist or circumstances be such that
				  in the opinion of the manager or operator, certain items listed as requirements
				  would not be applicable, then alternate items shall be submitted in writing to
				  the Department for appraisal as an acceptable substitute for the requirement,
				  and upon approval may be used.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 3 - Operational Provisions › Section 310:320-3-13 - Subsequent examination, investigation, and inspection

Current through Vol. 41, No. 20, July 1, 2024
Subsequent to examination, investigation, and inspection by
				  the State Commissioner of Health or his representative, any public bathing
				  place found to be in non-compliance with the requirements of this chapter and
				  therefore constituting a public nuisance, shall be reinspected within a
				  reasonable time to determine if the public bathing place has been brought into
				  compliance with the requirements of this chapter.
A $125.00 reinspection fee may apply in cases when the
				  applicant fails an initial licensure inspection due to items not found to be on
				  site or operational as reported by the applicant during the pre-inspection
				  assessment.
Added at 22 Ok Reg 2393,
				  eff 7-11-05
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 5 - Forms and Tables › Section 310:320-5-1 - Portable pools

Current through Vol. 41, No. 20, July 1, 2024
(a)
Conditions
				governing operation.
The following conditions govern operation of
				portable pools:
(1) To be used for
				instructional purposes.
(2) For
				installation only at public buildings where adequate toilet and other sanitary
				facilities are conveniently available.
(3) The pool(s) to have continuous
				supervision by instructors or supervisors certified as lifeguards per OAC
				310:320-3-2.
(4) Instruction classes to be sized on the
				basis of one (1) pupil for each four hundred (400) gallons of pool
				volume.
(5) Use of the pool(s) to
				be limited to daylight hours unless the lighting requirements of these
				standards are met.
(6) The pool(s)
				to be covered and locked whenever unattended or out of use.
(7) The pool(s) installation at each location
				to be authorized by a permit issued by the Department for a scheduled period,
				preferably about two (2) weeks, extendable at the option of the Department,
				upon receipt of a written request giving justification for the time
				extension.
(8) The operations of
				the pool(s) to be coordinated with the county health department for the
				purposes of inspections and supervision.
(9) Pool(s) to be located on paved surface
				with paved area and walkway from shower and toilet facilities to the
				pool.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 5 - Forms and Tables › Section 310:320-5-2 - Water balance and water balance tables

Current through Vol. 41, No. 20, July 1, 2024
Water balance recommended values are:
(1) pH 7.2 to 7.8
(2) Total alkalinity 80-120 ppm (pools)
				100-150 ppm (spas)
(3) Calcium
				hardness 100-150 ppm (pools) 150-300 ppm (spas)
(4) Temperature: 75-90 °F for pools and
				90-105° F for spas. See Appendix B.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 5 - Forms and Tables › Section 310:320-5-5 - Application for license [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 26 Ok Reg
				  1491, eff 6-11-09
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 5 - Forms and Tables › Section 310:320-5-5.1 - Application for license

Current through Vol. 41, No. 20, July 1, 2024
(a) The applicant
				shall file an application for a license to operate a public bathing place on
				the forms provided by the Department, as set forth in this Chapter with the
				filing fee payable to the Oklahoma State Department of Health, prior to
				operating a public bathing place. The filing fee is established by rule in
				Chapter 310:250 of the Oklahoma Administrative Code, Fee Schedule For Consumer
				Health Services.
(b) The
				application for a license to operate a public bathing place must include a copy
				of the permit to construct the public bathing place for which the applicant
				seeks a license, or reference the construction permit in the application, in
				order to be eligible for a license to operate a public bathing place.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 5 - Forms and Tables › Section 310:320-5-6 - Application guidelines for permits to construct and licenses to operate public bathing places [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 22 Ok Reg
				  2393, eff 7-11-05
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 320 - Public Bathing Place Operations › Subchapter 5 - Forms and Tables › Section 310:320-5-6.1 - Application guidelines for licenses to operate public bathing places

Current through Vol. 41, No. 20, July 1, 2024
(a)
Applicant requirements.
An
				applicant shall be an owner/operator of the public bathing place, as defined in
				63 O.S. Section 1-1013 et. Seq. complying with the requirements of this
				chapter, agree to permit access to the public bathing places, provide required
				information, and pay the applicable license fee and submit application on a
				form provided by the Department.
(b)
Application contents.
The
				application shall include:
(1) The name,
				mailing address, telephone number, approximate number of employees, and
				signature of the person applying for the license and the name, mailing address
				and location of the public bathing places;
(2) Information about the legal entity for
				the public bathing places; and
(3)
				Information about the type of public bathing places.
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 1 - General Provisions [Revoked] › Section 310:325-1-1 - Purpose [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 1 - General Provisions [Revoked] › Section 310:325-1-2 - Definitions [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 1 - General Provisions [Revoked] › Section 310:325-1-3 - Permits: public or private entities; eligibility [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-1 - Plan documents [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-2 - Preliminary report [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-3 - Engineer's report [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-4 - Plans [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-5 - Specifications [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-6 - Design criteria [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-7 - Revisions to approved plans [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 3 - Plan Documents [Revoked] › Section 310:325-3-8 - As built plans [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-1 - Design considerations [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-2 - New processes, methods, and equipment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-3 - Plant layout [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-4 - Building layout [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-5 - Location of structures [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-6 - Electrical controls [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-7 - Standby power [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-8 - Shop space and storage [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-9 - Laboratory equipment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-10 - Flow monitoring: raw and finished water [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-11 - Sample taps [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-12 - Facility water supply [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-13 - Sanitary facilities [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-14 - Piping and conduits [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-15 - Piping color code [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-16 - Disinfection [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-17 - Bypasses [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-18 - Drains [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-19 - Operating equipment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-20 - Operation and maintenance of water systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 5 - General Design Considerations [Revoked] › Section 310:325-5-21 - Other considerations [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 7 - Source Development [Revoked] › Section 310:325-7-1 - Source development [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 7 - Source Development [Revoked] › Section 310:325-7-2 - Surface water [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 7 - Source Development [Revoked] › Section 310:325-7-3 - Springs [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 7 - Source Development [Revoked] › Section 310:325-7-4 - Ground water [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95
Oklahoma Administrative Code › Title 310 - Oklahoma State Department of Health › Chapter 325 - Public Water Supply Facility Standards [Revoked] › Subchapter 7 - Source Development [Revoked] › Section 310:325-7-5 - Purchase water [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 12 Ok Reg
				  2343, eff 6-26-95