reglab/statecodes huggingface dataset:
Ohio Administrative Code › Title 1301:6 - Division of Securities › Chapter 1301:6-3 - Registration of Securities; Licensing › Section 1301:6-3-23 - Enforcement powers

Current through all regulations passed and filed through July 1, 2024
(A) Hearings conducted by the division
			 pursuant solely to section
			 1707.23 of the Revised Code
			 shall be investigative in nature with attendance restricted by the division to
			 those persons whose presence is necessary for the efficient conduct of the
			 hearing, and shall be conducted by an attorney designated by the division who
			 is admitted to the practice of law in Ohio.
(B) The division may, in its sole discretion,
			 prepare a transcript of any investigative hearing at its expense. A copy of any
			 transcript prepared at the expense of the division shall be furnished to the
			 witness at the expense of the witness upon written request. No photographic
			 recording or transceiving devices except those acceptable to the division shall
			 be permitted at investigative hearings.
(C) Every witness in an investigative hearing
			 shall be afforded an opportunity to make a statement. The witness shall be
			 advised of the right to secure legal counsel and to have counsel present during
			 questioning.
(D) The rules of
			 evidence applicable in judicial proceedings shall apply to investigative
			 hearings by the division so far as practicable, taking into consideration the
			 investigative and administrative character of such hearings and the powers of
			 investigation of the division.
(E)
			 No rule or adjudication of the division shall result from an investigative
			 hearing unless an opportunity for a hearing is afforded in accordance with
			 sections 119.01 to
			 119.13 of the Revised Code.
(F) For the purposes of division
			 (C) of section 1707.23 of the Revised Code,
			 "party" or "parties" to an investigative hearing are those persons required by
			 the division to testify at the hearing.
Five Year Review (FYR) Dates:
				06/08/2015 and
				06/08/2020
Promulgated
				Under: 119.03
Statutory
				Authority: 1707.20
Rule
				Amplifies: 1707.23
Prior
				Effective Dates: 2/22/80, 12/31/75,
				1/17/92
Ohio Administrative Code › Title 1301:6 - Division of Securities › Chapter 1301:6-3 - Registration of Securities; Licensing › Section 1301:6-3-39.1 - Retroactive exemption, qualification or registration

Current through all regulations passed and filed through July 1, 2024
(A) An application
			 may be made pursuant to section
			 1707.391 of the
			 Revised Code to exempt, qualify or register securities when the only deficiency
			 is a failure to timely file or a failure to properly file with the division the
			 appropriate form due to excusable neglect and the issuer is not otherwise in
			 violation of section
			 1707.13
			 of the Revised Code.
(1) For the purposes of
			 this rule, "failure to timely file" means the failure to file an application to
			 exempt, qualify or register securities within the time required by the
			 applicable section of the Ohio Securities Act or the rules adopted
			 thereunder.
(2) For the purposes of
			 this rule, "failure to properly file" means the filing of an application to
			 exempt, qualify or register securities which was not proper because the
			 application was incomplete, because there was a clerical error made in
			 completing the application, because an error was made regarding the facts
			 underlying the application, or because the application was made on the wrong
			 form.
(3) For the purposes of this
			 rule, "date of sale," will be the
			 earlier of the date that a subscription agreement or its equivalent is signed
			 by the purchaser or the date that the purchaser transfers or loses control of
			 the purchase funds, or the date of disbursement of funds subject to an escrow
			 agreement specifically approved by the division or established in accordance
			 with the administrative rules of the division.
Ohio Administrative Code › Title 1301:6 - Division of Securities › Chapter 1301:6-3 - Registration of Securities; Licensing › Section 1301:6-3-48 - Records retention

Current through all regulations passed and filed through July 1, 2024
(A) The division shall draft schedules for
			 the retention of consents to service of process filed with the division, in any medium filed with, or retained by, the
			 division, as part of a registration by description, a registration by
			 qualification, a registration by coordination, a filing to claim an exemption,
			 or a notice filing, the scheduled retention period of which shall be no less
			 than eight years.
(B) The division
			 shall draft schedules for the retention, in any medium
			 filed with, or retained by, the division, of the originals or copies of
			 documents filed with the division as license applications for investment
			 advisers, investment adviser representatives, dealers,
			  salespersons, state retirement system investment officers, and the bureau
			 of workers compensation chief investment officer, and the originals or
			 copies of documents filed with the division, in any
			 medium filed with, or retained by, the division, as notice filings
			 submitted by federally registered investment advisers, the scheduled retention
			 period of which shall be no less than five years.
(C) The division shall draft schedules for
			 the retention of all documents, testimony transcripts, investigative reports,
			 and investigative notes that the division has compiled in original or copy
			 form, electronic or in any medium, the scheduled
			 retention period of which shall be no less than five years from the date the
			 enforcement file containing this documentation is deemed closed by the
			 division.
(D)
								 The division may receive documents electronically. If
			 the division converts documents into electronic copies, the original may be
			 destroyed upon conversion and the electronic document shall be retained
			 according to the retention schedule as though it was the
			 original.
Effective: 9/26/2015
Five Year
				Review (FYR) Dates: 06/08/2015 and
				06/08/2020
Promulgated
				Under: 119.03
Statutory
				Authority: 1707.20
Rule
				Amplifies: 1707.48
Prior
				Effective Dates: 1-28-00, 11-27-00
Ohio Administrative Code › Title 1301:6 - Division of Securities › Chapter 1301:6-3 - Registration of Securities; Licensing › Section 1301:6-3-471 - Ohio investor recovery fund

Current through all regulations passed and filed through July 1, 2024
(A)
								Reviewing applications for restitution assistance
			 awards
(1)
									The
			 claimant needs to produce a copy of a valid identification showing Ohio
			 residency of the claimant or the victim on the date the pecuniary loss was
			 incurred and the following to demonstrate that the claimant and loss are
			 properly identified:
(a)
										The court order: or
(b)
										The
			 administrative order.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-02 - Definitions

Current through all regulations passed and filed through July 1, 2024
(A)
Section 201 General
(1)
201.1
			 Scope.
Unless otherwise expressly stated,
			 the following words and terms shall, for the purposes of this code, have the
			 meanings shown in this
rule.
(2)
201.2
			 Interchangeability.
Words used in the
			 present tense include the future; words stated in the masculine gender include
			 the feminine and neuter; the singular number includes the plural and the
			 plural, the singular.
(3)
201.3 Terms defined in other codes.
Where terms are not defined in this code
			 and are defined in the
building code,
International Fuel Gas
			 Code,
mechanical code
or
plumbing code as listed in
			 rule
			 1301:7-7-80
			 of the Administrative Code,
such terms shall have the meanings
			 ascribed to them as in those codes.
(4)
201.4 Terms
			 not defined.
Where terms are not defined
			 through the methods authorized by this
paragraph,
such terms
			 shall have ordinarily accepted meanings such as the context implies. "Merriam
			 Webster's Collegiate Dictionary, 11th Edition,"
			 shall be considered as providing ordinarily accepted
			 meanings.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-03 - General requirements

Current through all regulations passed and filed through July 1, 2024
(A)
Section 301
			 General
(1)
301.1 Scope.
The
			 provisions of this
rule
shall govern the occupancy and
			 maintenance of all structures and premises for precautions against fire and the
			 spread of fire and general requirements of fire safety.
(2)
301.2
			 Permits.
Permits shall be required as set
			 forth in
rule
			 1301:7-7-01
			 of the Administrative Code
for the activities or uses regulated by
paragraphs
(F)(306), (G)(307), (H)(308) and (O)(315)
of this rule.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-04 - Emergency planning and preparedness

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 401
			 General
(1)
									401.1 Scope. Reporting of emergencies, coordination with
			 emergency response forces, emergency plans, and procedures for managing or
			 responding to emergencies shall comply with the provisions of this
			 paragraph.
Exception: Firms that have approved
				on-premises fire-fighting organizations and that are in compliance with
				approved procedures for fire reporting.
(2)
									401.2 Approval.
			 Where required by this code, fire safety plans, emergency procedures and
			 employee training programs shall be approved by the fire code
			 official.
(3)
									401.3 Emergency responder notification. Notification of
			 emergency responders shall be in accordance with paragraphs (A)(3)(a)(401.3.1)
			 to (A)(3)(c)(401.3.3) of this rule.
(a)
										401.3.1 Fire events. In the event an unwanted fire
			 occurs on a property, the owner or occupant shall immediately report such
			 condition to the fire department.
(b)
										401.3.2 Alarm
			 activations. Upon activation of a fire alarm signal, employees or staff shall
			 immediately notify the fire department.
(c)
										401.3.3 Delayed
			 notification. A person shall not, by verbal or written directive, require any
			 delay in the reporting of a fire to the fire department.
(4)
									401.4
			 Required plan implementation. In the event an unwanted fire is detected in a
			 building or a fire alarm activates, the emergency plan shall be
			 implemented.
(5)
									401.5 Making false report. A person shall not give,
			 signal or transmit a false alarm.
(6)
									401.6 Emergency
			 evacuation drills. The sounding of a fire alarm signal and the carrying out of
			 an emergency evacuation drill in accordance with the provisions of paragraph
			 (E)(405) of this rule shall be allowed.
(7)
									401.7 Unplanned
			 evacuation. Evacuations made necessary by the unplanned activation of a fire
			 alarm system or by any other emergency shall not be substituted for a required
			 evacuation drill.
(8)
									401.8 Interference with fire department operations. It
			 shall be unlawful to interfere with, attempt to interfere with, conspire to
			 interfere with, obstruct or restrict the mobility of or block the path of
			 travel of a fire department emergency vehicle in any way, or to interfere with,
			 attempt to interfere with, conspire to interfere with, obstruct or hamper any
			 fire department operation.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-05 - Fire service features

Current through all regulations passed and filed through July 1, 2024
(A)
Section 501
			 General
(1)
501.1 Scope.
Fire
			 service features for buildings, structures and premises shall comply with this
rule.
(2)
501.2 Permits.
A permit shall be required as set forth in
rule
			 1301:7-7-01
			 of the Administrative Code.
(3)
501.3
			 Construction documents.
Construction
			 documents for proposed fire apparatus access, location of fire lanes, security
			 gates across fire apparatus access and construction documents and hydraulic
			 calculations for fire hydrant systems shall be submitted to the fire department
			 for review and approval prior to construction.
(4)
501.4
			 Timing of installation.
Where fire
			 apparatus access roads or a water supply for fire protection are required to be
			 installed, such protection shall be installed and made serviceable prior to and
			 during the time of construction except when approved alternative methods of
			 protection are provided. Temporary street signs shall be installed at each
			 street intersection where construction of new roadways allows passage by
			 vehicles in accordance with
paragraph
(E)(2)( 505.2 )
of this rule.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-06 - Building services and systems

Current through all regulations passed and filed through July 1, 2024
(A)
Section 601
			 General
(1)
601.1 Scope.
The provisions of this
rule
shall apply to the installation, operation and
			 maintenance of fuel-fired appliances and heating systems, emergency and standby
			 power systems, electrical systems and equipment, mechanical refrigeration
			 systems, elevator recall, stationary storage battery systems and commercial
			 kitchen equipment.
(2)
601.2 Permits.
Permits shall be obtained
			 for refrigeration systems, battery systems and solar photovoltaic power systems
			 as set forth in
rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-07 - Fire and smoke protection features

Current through all regulations passed and filed through July 1, 2024
(A)
Section 701
			 General
(1)
701.1 Scope.
The
			 provisions of this
rule
shall govern maintenance of the
			 materials, systems and assemblies used for structural fire resistance and
			 fire-resistance-rated construction separation of adjacent spaces to safeguard
			 against the spread of fire and smoke within a building and the spread of fire
			 to or from buildings. New buildings shall comply with the
building code
			 as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
(2)
701.2
			 Unsafe conditions.
Where any components in
			 this
rule
are not maintained and do not function as intended
			 or do not have the fire resistance required by the code under which the
			 building was constructed, remodeled or altered, such component(s) or portion
			 thereof shall be deemed an unsafe condition, in accordance with
paragraph
(J)(1)(a)(110.1.1)
of rule
			 1301:7-7-01
			 of the Administrative Code.
Components or portions thereof determined
			 to be unsafe shall be repaired or replaced to conform to that code under which
			 the building was constructed, remodeled, altered or this
rule,
as deemed appropriate by the fire code official.
Where the extent of the conditions of
				components is such that any building, structure or portion thereof presents an
				imminent danger to the occupants of the building, structure or portion thereof,
				the fire code official shall act in accordance with
section
				3737.44 of the Revised Code and
				paragraphs (I)(1)(a)(109.1.1) and (J)(1)(a)(110.1.1) of rule
				1301:7-7-01
				of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-08 - Interior finish, decorative materials and furnishings

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 801 General
(1)801.1 Scope. The
			 provisions of this rule shall govern interior finish, interior trim, furniture,
			 furnishings, decorative materials and decorative vegetation in buildings.
			 Existing buildings shall comply with paragraphs (C)(803) to (H) (808) of this
			 rule. New buildings shall comply with paragraphs (D)(804) to (H)(808) of this
			 rule and section 803 of the building code as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-10 - Means of egress

Current through all regulations passed and filed through July 1, 2024
(A)
Section
			 1001 General
(1)
1001.1 General.
Buildings or portions thereof shall be provided with a means
			 of egress system as required by this
rule and in compliance with
			 accessibility requirements as set forth in chapter 11 of the building code as
			 listed in rule
			 1301:7-7-80
			 of the Administrative Code.
The provisions of this
rule
shall control the design, construction and arrangement of
			 means of egress components required to provide an approved means of egress from
			 structures and portions thereof.
Paragraphs
(C)(1003)
to
(DD)(1030)
of this rule
shall apply to new
			 construction.
The new construction requirements of this rule for the
			 means of egress in structures regulated by the building code as listed in rule
			 1301:7-7-80
			 of the Administrative Code submitted for plan review in accordance with this
			 paragraph are subject to and do not supersede or otherwise conflict with the
			 requirements of paragraph
(D)(2)(a)(104.2.1)
of rule
			 1301:7-7-01
			 of the Administrative Code. Paragraph
(EE)(1031)
of this
			 rule
shall apply to existing buildings.
Except for maintenance
			 requirements contained in paragraph
(EE)(1031)
of this rule,
			 the provisions of this rule for a means of egress system in existing buildings
			 shall apply only in accordance with paragraph
(B)(1)(c)( 102.1 )
of rule
			 1301:7-7-01
			 of the Administrative Code.
(2)
1001.2
			 Minimum requirements.
It shall be unlawful
			 to alter a building or structure in a manner that will reduce the number of
			 exits or the capacity of the means of egress to less than required by this
			 code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-11 - Construction requirements for existing buildings

Current through all regulations passed and filed through July 1, 2024
(A)
Section
			 1101 General
(1)
1101.1 Scope.
The
			 provisions of this
rule
shall apply to existing buildings
			 constructed prior to the adoption of this code
in accordance with
			 paragraph (B)(1)(c)( 102.1 ) of rule
			 1301:7-7-01
			 of the Administrative Code. The provisions of this rule shall not apply to
			 existing buildings unless the conditions at the building constitute a distinct
			 hazard to life or property in the opinion of the fire code official in
			 accordance with paragraph (B)(1)(c)( 102.1 ) of rule
			 1301:7-7-01
			 of the Administrative Code.
Exceptions:
1.
The
			 provisions of paragraph (D)(1104) of this rule shall apply to all existing
			 buildings.
2.
The provisions of paragraph
(C)(9)( 1103.9 )
of this rule shall apply to
			 all existing occupancies identified in paragraph
(C)(9)( 1103.9 )
of this rule.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-20 - Aviation facilities

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2001
			 General
(1)2001.1 Scope. Airports, heliports, helistops and aircraft
			 hangars shall be in accordance with this rule.
(2)
									2001.2
			 Regulations not covered. Regulations not specifically contained herein
			 pertaining to airports, aircraft maintenance, aircraft hangars and appurtenant
			 operations shall be in accordance with nationally recognized
			 standards.
(3)
									2001.3 Permits. For permits to operate
			 aircraft-refueling vehicles, application of flammable or combustible finishes
			 and hot work, see rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-21 - Dry cleaning

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2101
			 General
(1)2101.1 Scope. Dry cleaning plants and their operations shall
			 comply with the requirements of this rule.
(2)
									2101.2 Permit
			 required. Permits shall be required as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-22 - Combustible dust-producing operations

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2201
			 General
(1)2201.1 Scope. The equipment, processes and operations
			 involving dust explosion hazards shall comply with the provisions of this
			 rule.
(2)
									2201.2 Permits. Permits shall be required for
			 combustible dust-producing operations as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-23 - Motor fuel-dispensing facilities and repair garages

Current through all regulations passed and filed through July 1, 2024
(A)
Section 2301 General
(1)
2301.1
			 Scope.
Automotive motor fuel-dispensing
			 facilities, marine motor fuel-dispensing facilities, fleet vehicle motor
			 fuel-dispensing facilities,
service stations at bulk plants,
aircraft motor-vehicle fuel-dispensing facilities and repair garages shall be
			 in accordance with this
rule, NFPA 30, NFPA 30A,
the
			 International Fuel Gas Code, the
building code,
and the
mechanical code as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
Such operations shall include both those
			 that are accessible to the public and private operations.
(a)
2301.1.1.
Notwithstanding paragraphs
(B)(1)( 102.1 )
and
(B)(2)( 102.2 )
of rule
			 1301:7-7-01
			 of the Administrative Code and unless otherwise noted in this rule, the
			 provisions of this rule shall not apply to facilities, equipment, structures or
			 installations existing or approved for construction or installation prior to
			 the effective date of this rule, except in those cases where the fire code
			 official demonstrates by a preponderance of the evidence that the existing
			 facility, equipment, structure or installation creates a distinct hazard to
			 life or adjacent property.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-24 - Flammable finishes

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2401
			 General
(1)2401.1 Scope. This rule shall apply to locations or areas
			 where any of the following activities are conducted:
(a)
										The application
			 of flammable finishes to articles or materials by means of spray
			 apparatus.
(b)
										The application of flammable finishes by dipping or
			 immersing articles or materials into the contents of tanks, vats or containers
			 of flammable or combustible liquids for coating, finishing, treatment or
			 similar processes.
(c)
										The application of flammable finishes by applying
			 combustible powders to articles or materials utilizing powder spray guns,
			 electrostatic powder spray guns, fluidized beds or electrostatic fluidized
			 beds.
(d)
										Floor surfacing or finishing operations using Class I
			 or II liquids in areas exceeding 350 square feet ( 32.5
			 m2).
(e)
										The application
			 of flammable finishes consisting of dual-component coatings or Class I or II
			 liquids when applied by brush or roller in quantities exceeding 1 gallon (4
			 L).
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-25 - Fruit and crop ripening

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2501
			 General
(1)2501.1 Scope. Ripening processes where ethylene gas is
			 introduced into a room to promote the ripening of fruits, vegetables and other
			 crops shall comply with this rule.
Exception: Mixtures of ethylene and one
				or more inert gases in concentrations that prevent the gas from reaching
				greater than 25 per cent of the lower explosive limit (LEL) when released to
				the atmosphere.
(2)
									2501.2 Permits. Permits shall be required as set forth
			 in rule
			 1301:7-7-01
			 of the Administrative Code.
(3)
									2501.3 Ethylene
			 generators. Approved ethylene generators shall be operated and maintained in
			 accordance with paragraph (F)(2506) of this rule.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-26 - Fumigation and insecticidal fogging

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2601
			 General
(1)
									2601.1 Scope. Fumigation and insecticidal fogging operations
			 within buildings, structures and spaces shall comply with this
			 rule.
(2)
									2601.2 Permits. Permits shall be required as set forth
			 in rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-27 - Semiconductor fabrication facilities

Current through all regulations passed and filed through July 1, 2024
(A)
Section
			 2701 General
(1)
2701.1 Scope.
Semiconductor fabrication facilities and comparable research
			 and development areas classified as Group H-5 shall comply with this
rule
and the
building code as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
The use, storage and handling of hazardous
			 materials in Group H-5 shall comply with this
rule,
other
			 applicable provisions of this code and the
building code as listed in
			 rule
			 1301:7-7-80
			 of the Administrative Code.
(2)
2701.2
			 Application.
The requirements set forth in
			 this
rule
are requirements specific only to Group H-5 and
			 shall be applied as exceptions or additions to applicable requirements set
			 forth elsewhere in this code.
(3)
2701.3
			 Multiple hazards.
Where a material poses
			 multiple hazards, all hazards shall be addressed in accordance with
paragraph
(A)(1)( 5001.1 )
of rule
			 1301:7-7-50
			 of the Administrative Code.
(4)
2701.4
			 Existing buildings and existing fabrication areas.
Existing buildings and existing fabrication areas shall
			 comply with this
rule,
except that transportation and handling
			 of HPM in corridors and enclosures for stairways and ramps shall be allowed
			 where in compliance with
paragraph
(E)(3)(b)(2705.3.2)
of this rule
and the
building code as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
(5)
2701.5
			 Permits.
Permits shall be required as set
			 forth in
rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-28 - Lumber yards and agro-industrial, solid biomass and woodworking facilities

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2801 General
(1)
									2801.1 Scope. The
			 storage, manufacturing and processing of solid biomass feedstock, timber,
			 lumber, plywood, veneers and agro-industrial byproducts shall be in accordance
			 with this rule.
(2)
									2801.2 Permit. Permits shall be required as set forth
			 in rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-29 - Manufacture of organic coatings

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 2901
			 General
(1)
									2901.1 Scope. Organic coating manufacturing processes shall
			 comply with this rule except that this rule shall not apply to processes
			 manufacturing nonflammable or water-thinned coatings or to operations applying
			 coating materials.
(2)
									2901.2 Permits. Permits shall be required as set forth
			 in rule
			 1301:7-7-01
			 of the Administrative Code.
(3)
									2901.3
			 Maintenance. Structures and their service equipment shall be maintained in
			 accordance with this code and NFPA 35 as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-30 - Industrial ovens

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3001
			 General
(1)
									3001.1 Scope. This rule shall apply to the installation and
			 operation of industrial ovens and furnaces. Industrial ovens and furnaces shall
			 comply with the applicable provisions of NFPA 86, the International Fuel Gas
			 Code, the mechanical code as listed in rule
			 1301:7-7-80
			 of the Administrative Code and this rule. The terms "ovens" and "furnaces" are
			 used interchangeably in this rule.
(2)
									3001.2 Permits.
			 Permits shall be required as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-31 - Tents and other membrane structures

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3101
			 General
(1)
									3101.1 Scope. Tents, temporary stage canopies and membrane
			 structures shall comply with this rule. The provisions of paragraph (C)(3103)
			 of this rule are applicable only to temporary tents and membrane structures.
			 The provisions of paragraph (D)(3104) of this rule are applicable to temporary
			 and permanent tents and membrane structures. Other temporary structures shall
			 comply with the building code as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-32 - High-piled combustible storage

Current through all regulations passed and filed through July 1, 2024
(A)
Section
			 3201 General
(1)
3201.1 Scope.
High-piled combustible storage shall be in accordance with
			 this
rule.
In addition to the requirements of this
rule,
the following material-specific requirements shall
			 apply:
(a)
										Aerosols shall be in accordance with
rule
			 1301:7-7-51 of the
			 Administrative Code.
(b)
										Flammable and
			 combustible liquids shall be in accordance with
rule
			 1301:7-7-57
			 of the Administrative Code.
(c)
										Hazardous
			 materials shall be in accordance
with rule
			 1301:7-7-50
			 of the Administrative Code.
(d)
										Storage of
			 combustible paper records shall be in accordance with NFPA 13
as listed
			 in rule
			 1301:7-7-80
			 of the Administrative Code.
(e)
										Storage of
			 combustible fibers shall be in accordance with
rule
			 1301:7-7-37 of
			 the Administrative Code.
(f)
										General storage
			 of combustible material shall be in accordance with
rule
			 1301:7-7-03
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-33 - Fire safety during construction and demolition

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3301
			 General
(1)
									3301.1 Scope. This rule shall apply to structures in the
			 course of construction, alteration or demolition, including those in
			 underground locations. Compliance with NFPA 241 as listed in rule
			 1301:7-7-80
			 of the Administrative Code is required for items not specifically addressed
			 herein.
(2)
									3301.2 Purpose. This rule prescribes minimum safeguards
			 for construction, alteration and demolition operations to provide reasonable
			 safety to life and property from fire during such operations.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-34 - Tire rebuilding and tire storage

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3401
			 General
(1)
									3401.1 Scope. Tire rebuilding plants, tire storage and tire
			 byproduct facilities shall comply with this rule, other applicable requirements
			 of this code and NFPA 13 as listed in rule
			 1301:7-7-80
			 of the Administrative Code. Tire storage in buildings shall also comply with
			 rule
			 1301:7-7-32
			 of the Administrative Code.
(2)
									3401.2 Permit
			 required. Permits shall be required as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-35 - Welding and other hot work

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3501
			 General
(1) 
									3501.1 Scope. Welding, cutting, open torches and other hot
			 work operations and equipment shall comply with this rule.
(2)
									3501.2 Permits.
			 Permits shall be required as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.
(3)
									3501.3 Restricted
			 areas. Hot work shall only be conducted in areas designed or authorized for
			 that purpose by the personnel responsible for a "Hot Work Program." Hot work
			 shall not be conducted in the following areas unless approval has been obtained
			 from the fire code official:
(a)
										Areas where the sprinkler system is
			 impaired.
(b)
										Areas where there exists the potential of an explosive
			 atmosphere, such as locations where flammable gases, liquids or vapors are
			 present.
(c)
										Areas with readily ignitable materials, such as storage
			 of large quantities of bulk sulfur, baled paper, cotton, lint, dust or loose
			 combustible materials.
(d)
										On board ships at dock or ships under construction or
			 repair.
(e)
										At other locations as specified by the fire code
			 official.
(4)
									3501.4 Cylinders and containers. Compressed gas
			 cylinders and fuel containers shall comply with this rule and rule
			 1301:7-7-53 of
			 the Administrative Code.
(5)
									3501.5 Design and installation of oxygen-fuel gas
			 systems. An oxygen-fuel gas system with two or more manifolded cylinders of
			 oxygen shall be in accordance with NFPA 51 as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-36 - Marinas

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3601 Scope
(1)
									3601.1 Scope.
			 Marina facilities shall be in accordance with this rule.
(2)
									3601.2 Plans and
			 approvals. Plans for marina fire protection facilities shall be approved prior
			 to installation. The work shall be subject to final inspection and approval
			 after installation.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-37 - Combustible fibers

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3701
			 General
(1)
									3701.1 Scope. The equipment, processes and operations
			 involving combustible fibers shall comply with this rule.
(2)
									3701.2
			 Applicability. Storage of combustible fibers in any quantity shall comply with
			 this paragraph.
(3)
									3701.3 Permits. Permits shall be required as set forth
			 in rule
			 1301:7-7-01
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-39 - Plant processing and extraction facilities

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 3901
			 General
(1)
									3901.1 Scope. Plant processing or extraction facilities
			 shall comply with this rule and the building code as listed in rule
			 1301:7-7-80
			 of the Administrative Code. The extraction process includes the act of
			 extraction of the oils and fats by use of a solvent, desolventizing of the raw
			 material, production of the miscella, distillation of the solvent from the
			 miscella and solvent recovery. The use, storage, transfilling and handling of
			 hazardous materials in these facilities shall comply with this rule, other
			 applicable provisions of this code and the building code as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
(2)
									3901.2 Existing
			 buildings or facilities. Existing buildings or facilities used for the
			 processing of plants or where the medium of extraction or solvent is changed
			 shall comply with this rule.
(3)
									3901.3 Permits.
			 Permits shall be required as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.
(4)
									3901.4. All plant
			 processing or extraction facilities subject to both this rule and Chapter 3796.
			 of the Revised Code shall be inspected by the state fire marshal to determine
			 facility and operational compliance with this code. Such inspections shall
			 initially occur in coordination with the medical marijuana processor license
			 application process described in division 3796:3 of the Administrative Code and
			 recur at least annually thereafter. Fire code officials may conduct other
			 inspections of facilities subject to this rule in accordance with section
			 3737.14 of the Revised Code and
			 this code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-51 - Aerosols

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 5101 General
(1)
									5101.1 Scope. The
			 provisions of this rule, the building code and NFPA 30B as listed in rule
			 1301:7-7-80
			 of the Administrative Code shall apply to the manufacturing, storage and
			 display of aerosol products. Manufacturing of aerosol products using hazardous
			 materials shall also comply with rule
			 1301:7-7-50
			 of the Administrative Code.
(2)
									5101.2 Permit
			 required. Permits shall be required as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.
(3)
									5101.3 Material
			 Safety Data Sheets. Material Safety Data Sheet (MSDS) information for aerosol
			 products displayed shall be kept on the premises at an approved
			 location.
(4)
									5101.4 Containers. Metal aerosol containers shall be
			 limited to a maximum size of 33.8 fluid ounces (1000 ml). Plastic aerosol
			 containers shall be limited to a maximum 4 fluid ounces (118 ml) except as
			 provided in paragraph (D)(1)(a)(5104.1.1) of this rule. Glass aerosol
			 containers shall be limited to a maximum 4 fluid ounces (118
			 ml).
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-53 - Compressed gases

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 5301
			 General
(1)
									5301.1 Scope. Storage, use and handling of compressed gases
			 in compressed gas containers, cylinders, tanks and systems shall comply with
			 this rule and NFPA 55 as listed in rule
			 1301:7-7-80
			 of the Administrative Code, including those gases regulated elsewhere in this
			 code. Partially full compressed gas containers, cylinders or tanks containing
			 residual gases shall be considered as full for the purposes of the controls
			 required.
Liquefied natural gas for use as a
				vehicular fuel shall also comply with NFPA 52 and NFPA 59A as listed in rule
				1301:7-7-80
				of the Administrative Code.
Compressed gases classified as
				hazardous materials shall also comply with rule
				1301:7-7-50
				of the Administrative Code for general requirements and rules addressing
				specific hazards, including rule
				1301:7-7-58(flammable
				gases), rule
				1301:7-7-60(highly
				toxic and toxic materials), rule
				1301:7-7-63(oxidizers,
				oxidizing gases and oxidizing cryogenic fluids), and rule
				1301:7-7-64(pyrophoric
				materials) of the Administrative Code.
Compressed hydrogen (CH2) for use as a
				vehicular fuel shall also comply with rules 1301:7-7-23 and 1301:7-7-58 of the
				Administrative Code, the International Fuel Gas Code and NFPA 2 as listed in
				rule
				1301:7-7-80
				of the Administrative Code.
Cutting and welding gases shall also
				comply with rule
				1301:7-7-35
				of the Administrative Code.
LP-gas shall also comply with rule
				1301:7-7-61 of the Administrative Code and the International Fuel Gas Code as
				listed in rule
				1301:7-7-80
				of the Administrative Code.
Exceptions:
1.
										Gases used as
			 refrigerants in refrigeration systems (see paragraph (F)(606) of rule
			 1301:7-7-06
			 of the Administrative Code).
2.
										Compressed natural
			 gas (CNG) for use as a vehicular fuel shall comply with rule
			 1301:7-7-23
			 of the Administrative Code, NFPA 52 and the International Fuel Gas Code as
			 listed in rule
			 1301:7-7-80
			 of the Administrative Code.
3.
										Cryogenic fluids
			 shall comply with rule
			 1301:7-7-55 of
			 the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-54 - Corrosive materials

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 5401
			 General
(1)
									5401.1 Scope. The storage and use of corrosive materials
			 shall be in accordance with this rule. Compressed gases shall also comply with
			 rule
			 1301:7-7-53 of
			 the Administrative Code.
Exceptions:
1.
										Display and
			 storage in Group M and storage in Group S occupancies complying with paragraph
			 (C)(11)(500311) of rule
			 1301:7-7-50
			 of the Administrative Code.
2.
										Stationary storage
			 battery systems in accordance with paragraph (H)(608) of rule
			 1301:7-7-06
			 of the Administrative Code.
3.
										This rule shall
			 not apply to R-717 (ammonia) where used as a refrigerant in a refrigeration
			 system (see paragraph (F)(606) of rule
			 1301:7-7-06
			 of the Administrative Code).
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-55 - Cryogenic fluids

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 5501
			 General
(1)
									5501.1 Scope. Storage, use and handling of cryogenic fluids
			 shall comply with this rule and NFPA 55 as listed in rule
			 1301:7-7-80
			 of the Administrative Code. Cryogenic fluids classified as hazardous materials
			 shall also comply with the general requirements of rule
			 1301:7-7-50
			 of the Administrative Code. Partially full containers containing residual
			 cryogenic fluids shall be considered as full for the purposes of the controls
			 required.
Exceptions:
1.
										Fluids used as
			 refrigerants in refrigeration systems (see paragraph (F)(606) of rule
			 1301:7-7-06
			 of the Administrative Code.)
2.
										Liquefied natural
			 gas (LNG), which shall comply with NFPA 59A as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
Oxidizing cryogenic fluids, including
				oxygen, shall comply with rule
				1301:7-7-63
				of the Administrative Code, as applicable.
Flammable cryogenic fluids, including
				hydrogen, methane and carbon monoxide, shall comply with rules
				1301:7-7-23
				and
				1301:7-7-58
				of the Administrative Code, as applicable.
Inert cryogenic fluids, including
				argon, helium and nitrogen, shall comply with ANSI/CGA P-18 as listed in rule
				1301:7-7-80
				of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-57 - Flammable and combustible liquids

Current through all regulations passed and filed through July 1, 2024
(A)
Section
			 5701 General
(1)
5701.1 Scope and application.
Prevention, control and mitigation of dangerous conditions
			 related to storage, use, dispensing, mixing and handling of flammable and
			 combustible liquids shall be in accordance with
NFPA 30, the building
			 code and mechanical code as listed in rule
			 1301:7-7-80
			 of the Administrative Code, rule
			 1301:7-7-50
			 of the Administrative Code and this rule.
(a)
5701.1.1
Notwithstanding paragraphs
(B)(1)( 102.1 )
and
(B)(2)( 102.2 )
of rule
			 1301:7-7-01
			 of the Administrative Code and unless otherwise noted in this rule, the
			 provisions of this rule shall not apply to facilities, equipment, structures or
			 installations existing or approved for construction or installation prior to
			 the effective date of this rule, except in those cases where the fire code
			 official demonstrates by a preponderance of the evidence that the existing
			 facility, equipment, structure or installation creates a distinct hazard to
			 life or adjacent property.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-58 - Flammable gases and flammable cryogenic fluids

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 5801
			 General
(1)
									5801.1 Scope. The storage and use of flammable gases and
			 flammable cryogenic fluids shall be in accordance with this rule and rule
			 1301:7-7-55 of
			 the Administrative Code. Compressed gases shall also comply with rule
			 1301:7-7-53 of
			 the Administrative Code and cryogenic fluids shall also comply with rule
			 1301:7-7-55 of
			 the Administrative Code. Flammable cryogenic fluids shall comply with paragraph
			 (F)(5806) of this rule. Hydrogen motor fuel-dispensing stations and repair
			 garages and their associated above-ground hydrogen storage systems shall also
			 be designed, constructed and maintained in accordance with rule
			 1301:7-7-23
			 of the Administrative Code and NFPA 2 as listed in rule
			 1301:7-7-80
			 of the Administrative Code.
Exceptions:
1.
										Gases used as
			 refrigerants in refrigeration systems (see paragraph (F)(606) of rule
			 1301:7-7-06
			 of the Administrative Code).
2.
										Liquefied
			 petroleum gases and natural gases regulated by rule
			 1301:7-7-61
			 of the Administrative Code.
3.
										Fuel-gas systems
			 and appliances regulated under the International Fuel Gas Code as listed in
			 rule
			 1301:7-7-80
			 of the Administrative Code other than gaseous hydrogen systems and
			 appliances.
4.
										Pyrophoric gases in accordance with rule
			 1301:7-7-64
			 of the Administrative Code.
Ohio Administrative Code › Title 1301:7 - Division of State Fire Marshal › Chapter 1301:7-7 - Ohio Fire Code › Section 1301:7-7-59 - Flammable solids

Current through all regulations passed and filed through July 1, 2024
(A)
								Section 5901
			 General
(1)
									5901.1 Scope. The storage and use of flammable solids shall
			 be in accordance with this rule.
(2)
									5901.2 Permits.
			 Permits shall be required as set forth in rule
			 1301:7-7-01
			 of the Administrative Code.