reglab/statecodes huggingface dataset:
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 3 - General Program Requirements › Section 252:633-3-19 - Construction phase

Current through Vol. 41, No. 20, July 1, 2024
(a)
Awarding
				construction contracts.
The recipient shall be responsible for assuring
				that every appropriate procedure and incidental legal requirement is observed
				in advertising for bids and awarding the construction contract. The text of the
				construction contract shall not vary from the text of the DEQ approved plans
				and specifications and addenda to the plans and specifications for which the
				Permit to Construct has been issued.
(b)
Engineering during
				construction.
During the building phase of the project, the recipient
				shall provide engineering services necessary to assure completion of the
				project according to the loan agreement and the approved plans and
				specifications.
(c)
Resident
				inspection.
After the construction contract is awarded, the recipient
				shall provide for adequate full-time resident inspection of the project and
				require assurance that the work is being performed in a satisfactory manner
				according to the approved plans and specifications, approved alterations, and
				sound engineering principles and building practices. The DEQ shall, to the
				extent practicable, alert the recipient and the project engineer of any
				variances from the approved plans and specifications. The recipient and the
				project engineer shall immediately initiate necessary action rectifying
				construction deficiencies.
(d)
Quality of materials.
The applicant shall ensure that materials
				used by their contractors meet or exceed the requirements of the approved
				specifications.
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Amended at 15 Ok
				  Reg 1957, eff 6-1-98; Amended at 25 Ok Reg 1140, eff
				  7-1-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 3 - General Program Requirements › Section 252:633-3-20 - Project changes

Current through Vol. 41, No. 20, July 1, 2024
(a) After an
				application for financial assistance has been approved by the OWRB and the DEQ
				has approved the plans and specifications for the project, no change from the
				approved plans and specifications which would materially or significantly
				affect total project or cost, estimated revenues, or design shall be made
				without the prior written approval. Additionally, the amount of the funding
				provided may only be increased through an amended application for financial
				assistance.
(b) The recipient must
				receive approval from the DEQ before implementing changes which:
(1) Alter the project performance
				standards;
(2) Alter the type of
				water treatment provided by the project;
(3) Significantly delay or accelerate the
				project schedule; or,
(4)
				Substantially alter the design drawings and specifications, or the location,
				size, capacity, or quality of any major part of the project.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 3 - General Program Requirements › Section 252:633-3-21 - Building phase submittals

Current through Vol. 41, No. 20, July 1, 2024
The following submittal and accompanying actions by the
				  recipient are required during and upon the completion of the construction of
				  the project;
(1) Any change order
				shall be submitted to the DEQ for approval;
(2) Once construction is completed, notice
				shall be submitted to the DEQ; and
(3) A complete set of as-built drawings shall
				be submitted to the DEQ upon completion of construction.
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Amended at 15 Ok
				  Reg 1957, eff 6-1-98; Amended at 25 Ok Reg 1140, eff
				  7-1-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 3 - General Program Requirements › Section 252:633-3-22 - Progress payments

Current through Vol. 41, No. 20, July 1, 2024
Certified requests for payment and documentation shall be
				  submitted to the DEQ monthly.
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Amended at 15 Ok
				  Reg 1957, eff 6-1-98; Amended at 25 Ok Reg 1140, eff
				  7-1-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 3 - General Program Requirements › Section 252:633-3-23 - Retainage [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 3 - General Program Requirements › Section 252:633-3-24 - Post building phase responsibilities of the recipient [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 3 - General Program Requirements › Section 252:633-3-25 - Accounting

Current through Vol. 41, No. 20, July 1, 2024
(a)
Instrument.
The recipient
				shall agree to the following:
(1) That
				project accounts shall be maintained in accordance with standards set forth by
				the Governmental Accounting Standards, the OWRB and the DEQ;
(2) A fund in the project account shall be
				secured in the manner provided by law for the security of county funds or city
				funds, as appropriate;
(3) All
				proceeds acquired by the recipient to plan, design and construct the project
				shall be placed in the project account;
(4) All proceeds in the project account shall
				be used for the sole purpose of planning, designing and building the project as
				approved by the OWRB and the DEQ;
(5) That an annual audit of the recipient,
				prepared by a certified public accountant, be provided to the OWRB;
(6) That the recipient shall maintain
				adequate insurance coverage on the project in an amount adequate to protect the
				State's interest;
(7) That the
				recipient will comply with any special conditions specified by the DEQ
				environmental determination, required pursuant to OAC
				252:633-7-1,
				until all financial obligations to the State have been discharged;
				and
(8) That the recipient
				covenants to continually abide by the terms of the financial assistance
				agreement and relevant State statutes and regulations for operation and
				maintenance of the facility.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 5 - Miscellaneous Provisions › Section 252:633-5-1 - Inspection of works, books and records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 5 - Miscellaneous Provisions › Section 252:633-5-2 - Project modifications [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 5 - Miscellaneous Provisions › Section 252:633-5-3 - Public records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 5 - Miscellaneous Provisions › Section 252:633-5-4 - Application fees

Current through Vol. 41, No. 20, July 1, 2024
Loan applications are subject to an OWRB filing, review and
				  processing fee at the time of filing the application. All application fees
				  charged by OWRB are eligible and may be included in the eligible project
				  costs.
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Amended at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 5 - Miscellaneous Provisions › Section 252:633-5-5 - Project or water project completion, inspection and audit

Current through Vol. 41, No. 20, July 1, 2024
(a)
Notification.
Upon
				completion of any project, the applicant shall notify the DEQ in
				writing.
(b)
Final
				inspection.
Upon receipt of such notification, the DEQ shall conduct a
				final on-site inspection of the project and may conduct an audit of all
				financial assistance funds furnished to the applicant.
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Amended at 15 Ok
				  Reg 1957, eff 6-1-98; Amended at 25 Ok Reg 1140, eff
				  7-1-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 5 - Miscellaneous Provisions › Section 252:633-5-6 - Return of funds to the Board [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 5 - Miscellaneous Provisions › Section 252:633-5-7 - Approval and notification regardin certain proposed action of an eligible entity [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 7 - Environmental Review Process › Section 252:633-7-1 - Requirement of environmental review

Current through Vol. 41, No. 20, July 1, 2024
The DEQ Water Quality Division Director shall conduct an
				  interdisciplinary environmental review consistent with the National
				  Environmental Policy Act of the project proposed for funding through the
				  Drinking Water Treatment Revolving Loan Account (DWTRLA). This review will
				  ensure that the project will comply with the applicable local, state and
				  federal laws and DEQ regulations and procedures relating to the protection and
				  enhancement of the environment. As necessary, the determination will include
				  mitigative provisions as a condition of financial assistance for building and
				  no financial assistance will be provided until a final environmental
				  determination has been made. The DEQ will establish procedures for the
				  environmental review process. Nothing in this Part shall prohibit any public,
				  private or governmental party from seeking administrative or legal relief from
				  the determinations of the DEQ.
(1)
Basic environmental determination.
There are three (3) basic
				environmental determinations that will apply to projects proposed to be
				implemented with assistance from the Drinking Water Treatment Revolving Loan
				Account. These are:
(A) a determination to
				categorically exclude a project from a formal environmental review;
(B) a Finding of No Significant Impact (FNSI)
				based upon a formal environmental review supported by an Environmental
				Information Document (EID); and
(C)
				a determination to provide or not to provide financial assistance based upon a
				Record of Decision following the preparation of an Environmental Impact
				Statement (EIS).
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 7 - Environmental Review Process › Section 252:633-7-2 - Environmental information required by the Department [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Subchapter 7 - Environmental Review Process › Section 252:633-7-3 - Environmental review by the Department [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1139,
				  eff 3-18-97 (emergency); Added at 14 Ok Reg 1690, eff 6-2-97; Revoked at 15 Ok
				  Reg 1957, eff 6-1-98
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 633 - Drinking Water State Revolving Fund › Appendix A - Funding Priority Formula

Current through Vol. 41, No. 20, July 1, 2024
Figure
				1
Figure
				2
Figure
				3
Figure
				4
Added at 14 Ok Reg 1139,
				eff 3-18-97 (emergency) ; Added at 14 Ok Reg 1690, eff 6-2-97; Revoked and
				reenacted at 15 Ok Reg 1957, eff 6-1-98; Revoked and reenacted at 25 Ok Reg
				2312, eff 7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 1 - General Provisions [Revoked] › Section 252:635-1-1 - Purpose [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 1 - General Provisions [Revoked] › Section 252:635-1-2 - Applicability [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 1 - General Provisions [Revoked] › Section 252:635-1-3 - Exclusions [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 1 - General Provisions [Revoked] › Section 252:635-1-4 - Definitions [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-1 - Sewage and wastewater storage, treatment and disposal devices and equipment for marine toilets [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-2 - Solid waste disposal [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-3 - Dumping and storage of solid wastes [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-4 - Wastewater treatment, storage and disposal systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-5 - Water supply systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-6 - Approval of plans for systems required [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-7 - Other rules applicable [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 635 - Reservoir Sanitation [Revoked] › Subchapter 3 - Sanitation and Other Requirements for Pollution Prevention [Revoked] › Section 252:635-3-8 - Penalties [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 2155,
				  eff 5-26-94; Revoked at 18 Ok Reg 1613, eff
				  6-1-01
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-1 - Purpose [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-2 - Definitions [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-3 - Applicability [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 13 Ok
				Reg 2087, eff 7-1-96; Amended at 14 Ok Reg 1045, eff 1-16-97 (emergency);
				Amended at 14 Ok Reg 1709, eff 6-2-97; Revoked at 16 Ok Reg 1863, eff
				6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-4 - Residential development requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-5 - Septic tank systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-6 - Lift station [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-7 - House sewer and other solid pipe [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-8 - Subsurface absorption field [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-9 - Percolation tests [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-10 - Requirements for on-site sewage disposal systems: lagoons [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-11 - Requirements for on-site sewage disposal systems: Evapotranspiration/absorption (ET/A) systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-12 - Requirements for individual sewage disposal systems: Alternative/experimental sewage systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 13 Ok
				Reg 2087, eff 7-1-96; Amended at 14 Ok Reg 1045, eff 1-16-97 (emergency);
				Amended at 14 Ok Reg 1709, eff 6-2-97; Revoked at 16 Ok Reg 1863, eff
				6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-13 - Inspection, operation, repairs, complaints and maintenance of on-site sewage disposal systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 11 Ok
				Reg 4637, eff 8-15-94 (emergency); Amended at 12 Ok Reg 3021, eff 7-27-95;
				Amended at 14 Ok Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709,
				eff 6-2-97; Revoked at 16 Ok Reg 1863, eff
				6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-14 - Water usage and septic tank care [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Revoked at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Revoked at 14 Ok Reg 1709, eff
				6-2-97
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-15 - On-site sewage disposal fees [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 11 Ok Reg 1317,
				eff 3-10-94 (emergency); Added at 11 Ok Reg 2159, eff 5-26-94; Amended at 14 Ok
				Reg 1045, eff 1-16-97 (emergency); Amended at 14 Ok Reg 1709, eff 6-2-97;
				Revoked at 16 Ok Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-16 - Existing systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 13 Ok Reg 2087,
				eff 7-1-96; Revoked at 16 Ok Reg 1863, eff
				6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 640 - Individual and Small Public Sewage Disposal [Revoked] › Section 252:640-1-17 - Location of on-site sewage disposal systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg 1045,
				eff 1-16-97 (emergency); Added at 14 Ok Reg 1709, eff 6-2-97; Revoked at 16 Ok
				Reg 1863, eff 6-11-99
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 1 - General Provisions › Section 252:641-1-1 - Purpose, authority and applicability

Current through Vol. 41, No. 20, July 1, 2024
(a)
Purpose.
The purpose of this
				Chapter is to ensure that sewage is properly treated in order to protect the
				waters of the State, the public health and the environment. This Chapter
				establishes requirements for the design, construction, installation and
				operation of individual and small public on-site sewage treatment systems. This
				Chapter also establishes requirements for persons seeking certification as
				installers of on-site sewage treatment systems and for persons seeking
				certification to perform soil profile descriptions to be used to design on-site
				sewage treatment systems.
(b)
Authority.
This Chapter is authorized by 27A O.S. Section(s)
				2-2-101, 2-2-201, 2-6-402 and 403; and 59 O.S. Section(s) 1158.
(c)
Applicability.
The rules in
				this Chapter apply to:
(1) Any person who
				owns, designs, constructs, installs, modifies, repairs or operates an on-site
				sewage treatment system;
(2) Any
				person who seeks certification from the DEQ to install, modify or repair
				on-site sewage treatment systems; and/or
(3) Any person who seeks certification from
				the DEQ to perform soil profile descriptions to be used to design on-site
				sewage treatment systems.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 1 - General Provisions › Section 252:641-1-2.1 - Authorizations and permits for on-site sewage treatment systems

Current through Vol. 41, No. 20, July 1, 2024
(a)
Requirement for authorizations and
				permits.
Before installing a new or modifying an existing on-site sewage
				treatment system, the installer shall first obtain either:
(1) DEQ authorization to construct an on-site
				sewage treatment system under the general permit, the terms of which are the
				rules of this Chapter; or
(2) an
				individual permit to construct an alternative on-site sewage treatment
				system.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 1 - General Provisions › Section 252:641-1-3 - General requirements for on-site sewage treatment systems

Current through Vol. 41, No. 20, July 1, 2024
(a)
Inspections.
All new
				installations of, modifications to and/or repairs to on-site sewage treatment
				systems shall be inspected and approved by the DEQ, or installed,
				self-inspected and approved by a certified installer before new installations,
				modifications or repairs can be backfilled and/or before the system may be
				placed into operation. The installer shall be responsible for requesting any
				required DEQ inspections.
(b)
Treatment.
On-site sewage treatment systems shall only be used for
				treatment of sewage, as defined in
				252:641-1-2. All
				sewage must be treated and dispersed according to the rules in this
				Chapter.
(c)
Ownership.
An on-site sewage treatment system shall be located
				only where:
(1) all components of an
				individual on-site sewage treatment system, which includes tanks, pumps,
				dispersal fields and collection line(s), are or will be located on property
				that is:
(A) owned by the owner of the
				on-site sewage treatment system; and/or
(B) dedicated in a recorded easement for the
				installation and operation of the on-site sewage system to the owner of the
				on-site sewage treatment system; or
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 1 - General Provisions › Section 252:641-1-4 - Operation, repairs and maintenance

Current through Vol. 41, No. 20, July 1, 2024
(a)
Proper operation.
The owner of an on-site sewage treatment system
				shall ensure that the system is maintained and operated properly so that:
(1) sewage or effluent from the system is
				properly treated and does not surface, pool, flow across the ground or
				discharge to surface waters;
(2)
				septic tanks, lift stations, low pressure dosing tanks, flow equalization
				tanks, aerobic treatment units and lagoons shall be maintained so that they do
				not leak or overflow; and
(3) the
				required security measures are intact (e.g., required fences, septic tank lids
				, manhole covers are properly secured).
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 1 - General Provisions › Section 252:641-1-5 - Enforcement

Current through Vol. 41, No. 20, July 1, 2024
Violations of this Chapter are subject to enforcement
				  actions and penalties set forth in 27A O.S. Section(s) 2-3-502, 2-3-504 and
				  2-6-206.
Added at 16 Ok Reg 1895,
				  eff 6-11-99; Amended at 19 Ok Reg 1704, eff 6-13-02; Amended at 25 Ok Reg 2318,
				  eff 7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 3 - Soil Tests › Section 252:641-3-1 - General provisions

Current through Vol. 41, No. 20, July 1, 2024
(a)
Requirement for soil test.
A soil test, performed in accordance
				with this Subchapter, shall be used to identify the dispersal site for all
				modifications to on-site sewage treatment systems and/or to identify the
				dispersal site and size the dispersal field for new installations of on-site
				sewage treatment systems except for:
(1)
				lagoons; and
(2) aerobic treatment
				systems that utilize spray irrigation when sized for Group 5 soil in the
				corresponding net evaporation zone.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 3 - Soil Tests › Section 252:641-3-2 - Soil Percolation test

Current through Vol. 41, No. 20, July 1, 2024
(a)
Use of percolation tests.
A percolation test may only be used to
				identify dispersal sites for conventional subsurface absorption fields.
				Percolation tests, including pre-existing ones, may not be used to identify
				dispersal sites for on-site sewage systems:
(1) in scenic river corridors, unless
				documentation that the site is not located within the scenic river watershed is
				provided to DEQ; and
(2) in Zone 2
				of a water body protection area.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 3 - Soil Tests › Section 252:641-3-3 - Linear feet requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 16 Ok Reg 1895,
				  eff 6-11-99; Revoked at 19 Ok Reg 1704, eff
				  6-13-02
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 3 - Soil Tests › Section 252:641-3-4 - Soil profile description

Current through Vol. 41, No. 20, July 1, 2024
(a)
Test hole requirements.
Test holes may be augered borings,
				continuous core borings, or excavated pits.
(1)
Borings.
If borings are
				used, three test holes shall be placed in the proposed dispersal site at the
				approximate corners of an isosceles triangle having two (2) sides fifty feet
				(50') long and one side seventy-five feet (75') long. If the dispersal field
				will cover an area larger than ten thousand square feet (10,000 ft 
				2), then one additional test hole shall
				be used for each additional five thousand square feet (5,000 ft 
				2). Additional test holes shall not be
				placed within fifty feet of any other test hole and shall be located between
				fifty to seventy-five feet (50-75') from one of the other test holes. The DEQ
				may approve or require alternative configurations. Borings shall allow for the
				classification of the soil in six-inch intervals and shall be bored to a
				minimum depth of forty-eight inches (48") or until one of the following is
				encountered first:
(A) a layer that is
				impervious to boring;
(B) a
				six-inch interval classified as a Group 5 soil; or
(C) water saturated soil.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 5 - Building Sewer and Collection Systems › Section 252:641-5-1 - General provisions

Current through Vol. 41, No. 20, July 1, 2024
All solid pipe used in the conveyance of wastewater from a
				  structure (home or business) shall comply with the following:
(1) Oklahoma Uniform Building Code Commission
				Rules- Title 748 Uniform Building Code Commission Adopted Codes (with
				Amendments);
(2) OAC 158:30
				Plumbing Industry Regulations; and
(3) Oklahoma Statute Title 59 Sections 1001
				through 1023.
Added at 16 Ok Reg 1895,
				  eff 6-11-99; Amended at 25 Ok Reg 2318, eff
				  7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 5 - Building Sewer and Collection Systems › Section 252:641-5-2 - Installation [Revoked]

Current through Vol. 41, No. 20, July 1, 2024
Added at 16 Ok Reg 1895,
				  eff 6-11-99; Amended at 19 Ok Reg 1704, eff 6-13-02; Amended at 21 Ok Reg 1618,
				  eff 6-11-04; Amended at 25 Ok Reg 2318, eff
				  7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 7 - Septic Tanks › Section 252:641-7-1 - General provisions

Current through Vol. 41, No. 20, July 1, 2024
(a) Once installed,
				septic tanks shall have no more than one inch (1") variation in elevation from
				side to side and end to end.
(b)
				Septic tanks shall be constructed to prevent sewage from leaking out of the
				tank and to prevent the infiltration of water into the tank.
(c) The bottom of the inlet pipe of a septic
				tank shall be at least one-eighth inch (1/8") per foot below the bottom of the
				building sewer pipe unless the wastewater is mechanically lifted.
(d) Appendix I illustrates the requirements
				for a septic tank.
Added at 16 Ok Reg 1895,
				  eff 6-11-99; Amended at 25 Ok Reg 2318, eff
				  7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 7 - Septic Tanks › Section 252:641-7-2 - Types of tanks

Current through Vol. 41, No. 20, July 1, 2024
(a)
Concrete
				tanks.
Concrete tanks shall be reinforced with rebar or fiber, and
				constructed of a mix which demonstrates a twenty-eight-day compressive strength
				of four (4) thousand pounds per square inch (4,000 psi). They may be poured in
				place or precast, but, in either case, shall be monolithically poured and
				mechanically vibrated.
(b)
Fiberglass and plastic tanks.
Fiberglass and plastic tanks shall
				meet either IAPMO or CSA standards for septic tanks and shall be installed
				according to the manufacturer's recommendations. If the tank does not bear the
				IAPMO or CSA mark, then DEQ will require the installer to submit documentation
				from IAPMO or CSA stating the tank meets the above standards.
Added at 16 Ok Reg 1895,
				  eff 6-11-99; Amended at 19 Ok Reg 1704, eff 6-13-02; Amended at 21 Ok Reg 1618,
				  eff 6-11-04; Amended at 25 Ok Reg 2318, eff
				  7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 7 - Septic Tanks › Section 252:641-7-3 - Design

Current through Vol. 41, No. 20, July 1, 2024
(a)
Compartments.
A septic tank
				may consist of one (1) or two (2) compartments. All septic tanks shall have a
				removable lid or a manhole opening of at least twenty inches (20") in diameter
				or, if rectangular, having no side less than twenty inches (20") in length over
				each compartment. All lids and manholes shall be sealed to prevent leakage.
(b)
Two-compartment
				tanks.
The passage in the common wall of two-compartment tanks shall be
				located between twenty percent (20%) to forty percent (40%) of the liquid
				depth. There shall be a vent through the common wall.
(c)
Inlets and outlets.
The
				outlet of the septic tank shall be two inches (2") lower than the inlet of the
				septic tank. Baffles for inlets and outlets shall be constructed and located as
				follows:
(1)
Construction.
Baffles shall be used on all inlet and outlet lines. Cleanout openings shall be
				located directly above the inlet and outlet baffles. Inlets and outlets shall
				have a watertight seal.The inlet cleanout shall have an opening of sufficient
				size to allow for maintenance that extends a minimum of two inches (2") above
				ground elevation. The cover for the opening shall have a lock, locking bolt or
				some type of tamper-resistant fastener, or require a tool for removal.
(2)
Location.
All
				baffles shall extend to within two inches (2") of the top of the septic tank.
(A)
Inlet.
Inlet baffles shall
				extend at least six inches (6") below the liquid depth of the septic tank.
(B)
Outlet.
Outlet
				baffles shall extend below the liquid level by twenty percent (20%) to forty
				percent (40%) of the liquid depth.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 7 - Septic Tanks › Section 252:641-7-4 - Liquid capacity

Current through Vol. 41, No. 20, July 1, 2024
(a)
Individual on-site sewage treatment system.
A septic tank used in
				an individual on-site sewage treatment system for a residential unit with four
				(4) or fewer bedrooms shall have a liquid capacity of at least one thousand
				(1,000) gallons. An additional two hundred and fifty (250) gallons of capacity
				must be added for each additional bedroom.
(b)
Small public sewage system.
The liquid capacity for a septic tank used in a small public sewage system
				shall be equal to or greater than the average daily flow plus fifty percent
				(50%), but in no case shall it be less than one thousand (1,000)
				gallons.
(c)
Two-compartment
				tanks.
The capacity of the influent compartment of a two-compartment
				tank shall not be less than one-half (1/2) nor more than two-thirds (2/3) of
				the total required liquid capacity of the tank.
(d)
All septic tanks.
All septic
				tanks shall be designed to have:
(1) a liquid
				depth of at least three feet (3') but not more than six and one-half feet
				(6-1/2'); and
(2) an air space of
				eight inches (8") or more inside the tank.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 9 - Pump Tanks › Section 252:641-9-1 - General provisions

Current through Vol. 41, No. 20, July 1, 2024
(a)
Primary
				settling.
All sewage entering a pump tank (i.e., a lift station, a flow
				equalization tank or a low pressure dosing tank) must first pass through a
				septic tank or a trash tank for primary settling.
(b)
Pump tank design and
				construction.
Pump tanks shall:
(1) be
				constructed to prevent sewage from leaking out of the tank and to prevent the
				infiltration of water into the tank;
(2) when made of concrete, meet the
				requirements of
				252:641-7-2(a);
(3) have a manhole opening of at least twenty
				inches (20") in diameter or, if rectangular, having no side less than twenty
				inches (20") in length. The manhole cover shall have a lock, locking bolt, or
				some type of tamper-resistant fastener, or require tools for removal. The
				manhole opening shall extend a minimum of two inches (2") above ground
				elevation;
(4) have a threaded
				union installed in the discharge line located within eighteen inches (18") of
				the manhole opening so that the pump can be removed without entering the pump
				tank; and
(5) have a check valve
				installed in the discharge line after the threaded union. The check valve shall
				be the same diameter as the discharge line.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 9 - Pump Tanks › Section 252:641-9-2 - Sizing

Current through Vol. 41, No. 20, July 1, 2024
Pump tanks shall be sized as follows:
(1)
Lift stations.
The lift
				station pump tank shall have a minimum liquid storage capacity of one thousand
				(1,000) gallons.
(A)
Daily flow over 500
				gallons.
For systems with average daily flows over five hundred (500)
				gallons, the liquid capacity of the pump tank shall be at least twice the
				highest daily flow.
(B)
Daily
				flow over 2,000 gallons.
For systems with an average daily flow over two
				thousand (2,000) gallons, the liquid capacity of the pump tank may be reduced
				to one-half (1/2) of the average daily flow, if a backup pump is available on
				site.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 9 - Pump Tanks › Section 252:641-9-3 - Pump controls

Current through Vol. 41, No. 20, July 1, 2024
The pump controls shall be set as follows:
(1)
Lift stations.
The following
				control settings apply to lift stations:
(A)
Never more than 1/2 full.
The pump controls shall be set so that
				the pump tank is never more than one-half (1/2) full.
(B)
Alarm.
There shall be an
				alarm set to activate and alert the owner/operator if the pump tank becomes
				more than one-half (1/2) full.
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 9 - Pump Tanks › Section 252:641-9-4 - Dosing requirements [AMENDED AND RENUMBERED TO 252:641-9-3]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg 1618,
				  eff 6-11-04; Amended and renumbered to 252:641-9-3 at 25 Ok Reg 2318, eff
				  7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 10 - Aerobic Treatment Systems › Section 252:641-10-1 - Sewage treatment

Current through Vol. 41, No. 20, July 1, 2024
Aerobic treatment systems shall only be used for treatment
				  of sewage and cannot be used when the average daily flow is less than one
				  hundred (100) gallons per day or greater than one thousand five hundred (1,500)
				  gallons per dayor generates wastewater with a total Biochemical Oxygen Demand
				  (BOD) greater than one and one half (1.5) pounds per day. All other system
				  designs must be permitted as alternative systems as described in OAC
				  252:641-1-2.1(c)
				  (e.g., hospitals, laundromats, restaurants, etc).
Added at 25 Ok Reg 2318,
				  eff 7-11-08
Oklahoma Administrative Code › Title 252 - Department of Environmental Quality › Chapter 641 - Individual and Small Public On-Site Sewage Treatment Systems › Subchapter 10 - Aerobic Treatment Systems › Section 252:641-10-2 - Design and installation

Current through Vol. 41, No. 20, July 1, 2024
(a)
Fluctuating flows.
If the daily flow fluctuates so that the flow
				on any given day during the week exceeds the aerobic treatment unit's daily
				capacity, then an aerobic treatment system may not be used unless a flow
				equalization tank, which meets the requirements of 252:641-9, is installed
				between the trash tank and the aerobic treatment unit.
(b)
Components of aerobic treatment
				systems.
Aerobic treatment systems shall be comprised of the following
				components:
(1)
Trash tank.
There shall be a trash tank that meets the requirements of NSF/ANSI Standard 40
				or
				252:641-7-2. The
				trash tank shall:
(A) be constructed to
				prevent sewage from leaking out of the tank and to prevent the infiltration of
				water into the tank;
(B) have a
				minimum liquid capacity of three hundred (300) gallons or the average daily
				flow, whichever is greater, except that the minimum liquid capacity shall not
				be less than what was used in the NSF/ANSI certification process;
(C) have a removable lid or a manhole opening
				of sufficient size to allow for maintenance. The lid or manhole shall be sealed
				to prevent leakage and extend a minimum of two inches (2") above ground
				elevation. The cover for the opening shall have a lock, locking bolt or some
				type of tamper-resistant fastener, or require a tool for removal;
(D) have baffles installed at its inlet and
				the outlet. The baffles shall extend to within two inches (2") of the top of
				the trash tank; and
(i)
Inlet.
Inlet baffles shall extend at least six inches (6") below the liquid depth of
				the trash tank.
(ii)
Outlet.
Outlet baffles shall extend below the liquid level by
				twenty percent (20%) to forty percent (40%) of the liquid depth.
(E) meet the requirements of
				252:641-7-1(c).