New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1112 - REPORTING

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and
				operators shall provide to the department all reports as required in 20.5.111
				NMAC within 60 days of completion of the tests.
B. Owners and operators shall report any test
				or inspection results that are anything other than a "pass" or "normal" result
				to the department within 24 hours of completion of the test or inspection in
				accordance with 20.5.118.1801 NMAC.
C. Owners and operators shall ensure all
				reports required in 20.5.111 NMAC contain, at a minimum, the following:
(1) facility name and address;
(2) facility ID number;
(3) owner and operator name and
				address;
(4) owner ID
				number;
(5) date report was
				completed;
(6) date of the
				test;
(7) duration of the
				test;
(8) brand name and model
				number of equipment being tested or sufficient description to allow
				identification of the equipment;
(9) type of equipment being tested;
(10) type of test, including test procedures
				and methods;
(11) results of the
				test;
(12) name of the person who
				performed the inspection or test and their qualifications as specified in
				20.5.105 NMAC;
(13) brand name and
				model number of the testing equipment used during the test and the date the
				testing equipment was last calibrated;
(14) for inspections and testing of automatic
				tank gauge systems as required in 20.5.111.1104 NMAC, a completed copy of the
				automatic tank gauge operation inspection form in
Petroleum Equipment
				Institute Publication RP 1200, "Recommended Practices for the Testing and
				Verification of Spill, Overfill, Leak Detection and Secondary Containment
				Equipment at UST Facilities"
;
(15) for testing of automatic line leak
				detectors:
(a) serial number of the leak
				detector;
(b) description of
				storage tank system;
(c) detected
				leak rate in gallons per hour;
(d)
				line pressure and functional element holding pressure in pounds per square
				inch;
(e) type, diameter and length
				of piping; and
(f) test results,
				including the following:
(i) whether flow is
				restricted by a mechanical line leak detector when a leak is
				detected;
(ii) whether the turbine
				shuts down, an alarm is triggered, or both, when a simulated leak is induced
				during the testing of an electronic line leak detector;
(16) for testing of sensors used
				for monitoring secondary containment and interstitial spaces:
(a) the information in the liquid sensor
				functionality testing form in the
Petroleum Equipment Institute
				Publication RP 1200, "Recommended Practices for the Testing and Verification of
				Spill, Overfill, Leak Detection and Secondary Containment Equipment at UST
				Facilities"
; and
(b)
				information on whether each individual sensor used for interstitial monitoring
				meets automatic shutdown requirements in 20.5.111 NMAC; and
(17) for line tightness testing:
(a) leak rate;
(b) testing pressure;
(c) bleed back;
(d) piping type;
(e) piping diameter; and
(f) length of piping.