New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 108 - RELEASE DETECTION FOR UNDERGROUND STORAGE TANK SYSTEMS › Section 20.5.108.816 - REPORTING

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and
				operators shall provide to the department all reports as required in 20.5.108
				NMAC within 60 days of completion of the tests.
B. Owners and operators shall report any test
				or inspection results that are anything other than a "pass" or "normal" result
				to the department within 24 hours of completion of the test or inspection in
				accordance with 20.5.118 NMAC.
C.
				Owners and operators shall ensure all reports required in 20.5.108 NMAC
				contain, at a minimum, the following:
(1)
				facility name and address;
(2)
				facility ID number;
(3) owner and
				operator name and address;
(4)
				owner ID number;
(5) date report
				was completed;
(6) date of the
				test;
(7) duration of the
				test;
(8) brand name and model
				number of equipment being tested or sufficient description to allow
				identification of the equipment;
(9) type of equipment being tested;
(10) type of test, including test procedures
				and methods;
(11) results of the
				test;
(12) name of the person who
				performed the inspection or test, and their qualifications as specified in
				20.5.105 NMAC;
(13) brand name and
				model number of the testing equipment used during the test and the date the
				testing equipment was last calibrated (only applies to tests performed in
				accordance with 20.5.108.800 NMAC, 20.5.108.804 NMAC, 20.5.108.806 NMAC,
				20.5.108.807 NMAC, 20.5.108.808 NMAC, 20.5.108.810 NMAC through 20.5.108.813
				NMAC);
(14) monitoring well number
				and instrument reading in parts per million (only applies to tests performed in
				accordance with 20.5.108.807 NMAC);
(15) monitoring well number, depth to
				groundwater and confirmation that free product was observed or not (only
				applies to tests performed in accordance with 20.5.108.807 NMAC);
(16) a completed copy of the automatic tank
				gauge operation inspection form in
Petroleum Equipment
Institute Publication RP 1200,
"Recommended Practices
				for the Testing
and Verification of Spill, Overfill,
Leak
Detection and
Secondary
Containment
Equipment at UST Facilities"
(only applies to tests performed in accordance with 20.5.108.805
				NMAC);
(17) for testing of
				automatic line leak detectors:
(a) serial
				number of the leak detector;
(b)
				description of storage tank system;
(c) detected leak rate in gallons per
				hour;
(d) line pressure and
				functional element holding pressure in pounds per square inch;
(e) type, diameter and length of
				piping;
(f) test results, including
				the following:
(i) whether flow is restricted
				by a mechanical line leak detector when a leak is detected;
(ii) whether the turbine shuts down when a
				leak is detected by an electronic line leak detector;
(18) for testing of sensors used
				for monitoring secondary containment and interstitial spaces:
(a) the information in the liquid sensor
				functionality testing form in the
Petroleum Equipment
Institute Publication RP 1200,
"Recommended Practices
				for the Testing
and Verification of Spill, Overfill,
Leak
Detection and
Secondary
Containment
Equipment at UST Facilities"
;
				and
(b) information on whether each
				individual sensor meets automatic shutdown requirements in 20.5.108.811 NMAC
				and 20.5.108.813 NMAC; and
(19) for line tightness testing:
(a) leak rate;
(b) testing pressure;
(c) bleed back;
(d) piping type;
(e) piping diameter; and
(f) length of piping.