reglab/statecodes huggingface dataset:
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.16 - CHAPTER 7 SANITARY DRAINAGE PART I - DRAINAGE SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UPC except as provided below.
A.
704.0 Fixture connections
				(drainage). 704.3 Commercial Sinks.
Delete the text this section of the
				UPC and substitute with the following: pot sinks, scullery sinks, dishwashing
				sinks, silverware sinks, commercial dishwashing machines, silverware washing
				machines, and other similar fixtures shall not be connected directly to the
				drainage system. Such equipment or fixtures shall be drained by means of
				indirect waste pipes, as defined in chapter 2 of the UPC, and all wastes
				drained by them shall discharge through an airgap into an open floor sink or
				other approved type receptor that is properly connected to the drainage system.
				Food waste disposal units shall be connected directly to the drainage system. A
				floor drain shall be provided adjacent to the disposal unit, and the disposal
				unit shall be connected on the sewer side of the floor drain trap, provided
				that no other drainage line is connected between the floor drain waste
				connection and the disposal unit drain. The floor drain shall be trapped and
				vented as required in this code.
B.
712.1 Media.
See this section of the UPC except add the following
				text to the end: When testing during weather conditions that could result in
				damage to piping, adequate provisions shall be made to protect such piping from
				freezing.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.17 - CHAPTER 7 SANITARY DRAINAGE PART II - BUILDING SEWERS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UPC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.19 - CHAPTER 9 VENTS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UPC except as provided below.
906.1 Roof Termination.
See this section of the UPC except add the
				  following to the end: "Exception: When approved by the authority having
				  jurisdiction, a fixture or fixture branch may be permitted to be vented by the
				  use of an approved Air Admittance Valve (AAV) in accordance with its listing
				  when conventional venting termination methods are not
				  available."
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.21 - CHAPTER 11 STORM DRAINAGE

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UPC except as follows:
1101.6
				  Subsoil drains.
See this section of the UPC except after the words
				  "Subsoil drains shall be provided" in the first sentence add the following
				  text: "as required by the NMCBC, 14.7.2 NMAC".
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.22 - CHAPTER 12 FUEL PIPING

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UPC except as provided below.
A.
1208.6.3.2 Copper and copper alloy
				pipe.
Delete this section of the UPC and substitute: Copper and brass
				pipe shall not be used. Threaded aluminum alloy pipe shall not be used with
				gases corrosive to such material.
B.
1208.6.10.5 Metallic pipe fittings
				(including valves, strainers, filters).
See this section of the UPC
				except delete "(3) fittings used with copper or copper alloy pipe shall be
				copper or copper alloy."
D.
1210.9.3 Emergency shutoff valves.
See this section of the UPC
				except delete the following: "The emergency shutoff valves shall be plainly
				marked as such and their locations posted as required by the authority having
				jurisdiction" and replace with the following text: "For purposes of isolation
				and safety, an additional approved gas shut off valve shall be installed
				downstream of the serving supplier gas meter prior to any distribution of gas
				into the gas piping system."
E.
1211.0 Electrical bonding and grounding.
Delete this section of
				the UPC and see 14.10.4 NMAC the New Mexico electrical code (NMEC).
F.
1212.11 Liquefied petroleum gas
				facilities and piping.
Delete this section of the UPC and substitute the
				following: Liquefied petroleum gas facilities shall comply with Sections
				70-5-1
				through
				70-5-23
				NMSA 1978, the LPG and CNG Act and with 19.15.40 NMAC, liquefied petroleum gas
				standards.
G.
12.13.3 Test
				pressure.
See this section of the UPC except add the following:
				Exception: An existing gas piping system may be tested at a test pressure equal
				to one and one-half times the operating pressure of the system, but in no case
				shall it be tested at less than 3 psi.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.23 - CHAPTER 13 HEALTH CARE FACILITIES AND MEDICAL GAS AND VACUUM SYSTEMS PART I - SPECIAL REQUIREMENTS FOR HEALTH CARE FACILITIES [RESERVED]

Current through Register Vol. 35, No. 13, July 16, 2024
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.24 - CHAPTER 13 HEALTH CARE FACILITIES AND MEDICAL GAS AND VACUUM SYSTEMS PART II - MEDICAL GAS AND VACUUM SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
See 14.9.5 NMAC and this chapter of the
				  UPC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.26 - CHAPTER 15 ALTERNATE WATER SOURCES FOR NONPOTABLE APPLICATIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UPC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 2 - 2021 NEW MEXICO PLUMBING CODE › Section 14.8.2.27 - CHAPTER 16 NONPOTABLE RAINWATER CATCHMENT SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UPC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.1 - ISSUING AGENCY

Current through Register Vol. 35, No. 13, July 16, 2024
Construction Industries Division (CID) of the Regulation and
				  Licensing Department.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
This rule applies to all contracting work performed on
				  swimming pools, spas, and hot tubs in New Mexico on or after May 1, 2015, that
				  is subject to the jurisdiction of CID, unless performed pursuant to a permit
				  for which an application was received by CID before that
				  date.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
Section
				  60-13-9 NMSA
				  1978.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.5 - EFFECTIVE DATE

Current through Register Vol. 35, No. 13, July 16, 2024
May 1, 2015, unless a later date is cited at the end of a
				  section.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The purpose of this rule is to establish minimum standards
				  for the construction of swimming pools, spas and hot tubs in New
				  Mexico.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.7 - DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See 14.5.1 NMAC, General Provisions and Chapter 2 of the 2012
				  Uniform Swimming Pool, Spa, and Hot Tub Code (USPSHTC) as Adopted by this
				  part.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.8 - ADOPTION OF THE 2012 UNIFORM SWIMMING POOL, SPA, AND HOT TUB CODE

Current through Register Vol. 35, No. 13, July 16, 2024
A. This rule
				adopts, by reference, the 2012 USPSHTC, as Adopted by this rule.
B. In this rule, each provision is numbered
				to correspond with the numbering of the USPSHTC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.9 - CHAPTER 1 ADMINISTRATION

Current through Register Vol. 35, No. 13, July 16, 2024
A.
101.0 General.
(1)
101.1
				Title.
Delete this section of the USPC and substitute: This code shall
				be known as the 2012 New Mexico Swimming Pool, Spa, and Hot Tub Code
				(NMSPSHTC).
(2)
101.2 Scope.
Delete this section of the USPSHTC and see 14.8.3.2 NMAC.
(3)
101.3 Purpose.
Delete this
				section of the USPSHTC substitute: The purpose of this code is to establish
				minimum standards for all swimming pools, spas and hot tub construction in New
				Mexico.
(4)
101.4
				Unconstitutional.
Delete this section of the USPSHTC and see 14.5.1
				NMAC.
(5)
101.5 Validity.
Delete this section of the USPSHTC and see 14.5.1 NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.10 - CHAPTER 2 DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the USPSHTC, except as provided
				  below.
A.
203.0 Authority
				having jurisdiction
. Delete the text of this definition and substitute:
				The authority having jurisdiction is the CID and the bureau chief of the
				mechanical and plumbing bureau of CID.
B.
214.0 Listing agency
. See
				this definition in the UPC and Section
				60-13-44
				of the CILA.
C.
221.0 Shall.
Delete this text of this definition and see Section 221.0 of the
				UPC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.11 - CHAPTER 3 GENERAL REQUIREMENTS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the USPSHTC except as provided below.
302.6 Alternate materials and methods equivalency.
Delete this
				  section and see
				  14.8.2.11
				  NMAC and
				  14.5.1.11
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.12 - CHAPTER 4 DESIGN, MATERIALS, AND METHODS OF CONSTRUCTION

Current through Register Vol. 35, No. 13, July 16, 2024
See this section of the USPSHTC except as provided
				  below.
A.
403.3 Markings.
Delete this section of the USPSHTC.
B.
403.4 Maximum bather load.
Delete this section of the USPSHTC.
C.
404.0 Wading pools.
See this
				section of the USPSHTC except as provided below.
(1)
404.1 General.
Delete this
				section of the USPSHTC.
(2)
404.2 Gates.
Delete this section of the USPSHTC.
(3)
404.5 Markings.
Delete this
				section of the USPSHTC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.13 - CHAPTER 5 WATER QUALITY

Current through Register Vol. 35, No. 13, July 16, 2024
See this section of the USPSHTC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.14 - CHAPTER 6 EQUIPMENT

Current through Register Vol. 35, No. 13, July 16, 2024
See this section of the USPSHTC except as provided
				  below.
A.
603.0 Electrical
				systems.
Delete this section of the USPSHTC and see 14.10.4
				NMAC.
B.
606.0 Diving
				equipment.
Delete this section of the USPSHTC.
C.
607.0 Slides.
Delete this
				section of the USPSHTC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.15 - CHAPTER 7 WATER HEATING EQUIPMENT AND VENTS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the USPSHTC except as provided as
				  follows:
712.2.18 Chimneys and vents.
See this section of the
				  USPSHTC except delete the following language: "Where vents extend outdoors
				  above the roof more than 5 feet (1524 mm) higher than required by Table
				  509.6.2, and where vents terminate in accordance with Section 509.6.2(1), the
				  outdoor portion of the vent shall be enclosed as required by this section for
				  vents not considered to be exposed to the outdoors or such venting shall be
				  engineered."
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.16 - CHAPTER 8 FUEL GAS PIPING

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the USPSHTC except as provided
				  below.
A.
809.5.2.3 Copper and
				brass.
Delete this section of the USPSHTC and substitute: Copper and
				brass pipe shall not be used. Threaded aluminum alloy pipe shall not be used
				with gases corrosive to such material.
B.
809.5.3.2 Copper and brass.
Delete this section of the USPSHTC and substitute: Copper and brass pipe
				shall not be used.
C.
810.12
				Electrical bonding and grounding.
Delete this section of the USPSHTC and
				see NMAC 14.10.4.
D.
810.13
				Electrical circuits.
Delete this section of the USPSHTC and see 14.10.4
				NMAC.
E.
810.14 Electrical
				connections.
Delete this section of the USPSHTC and see 14.10.4
				NMAC.
F.
812.0 Liquefied
				petroleum gas facilities and piping.
Delete this section of the USPSHTC
				and substitute the following: Liquefied petroleum gas facilities shall comply
				with 19.15.40 NMAC, liquefied petroleum gas standards, and
				70-5-1 to
				-23 NMSA 1978, liquefied and compressed gasses.
G.
813.3 Test pressure.
See
				this section of the USPSHTC except add the following: Exception: An existing
				gas piping system may be tested at a test pressure equal to one and one-half
				times them operating pressure of the system, but in no case shall it be tested
				at less than 3 psi.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.17 - CHAPTER 9 SAFETY

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the USPSHTC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.18 - CHAPTER 10 REFERENCED STANDARDS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the USPSHTC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 8 - PLUMBING CODES › Part 3 - 2009 NEW MEXICO SWIMMING POOL, SPA AND HOT TUB CODE › Section 14.8.3.19 - APPENDICES

Current through Register Vol. 35, No. 13, July 16, 2024
See this section of the USPSHTC except delete appendix A and
				  appendix C.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
This rule applies to all contracting work performed in New
				  Mexico on or after May 15, 2018, that is subject to the jurisdiction of CID,
				  unless performed pursuant to a permit for which an application was received by
				  CID before that date.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
Sections
				  60-13-9,
				  60-13-44,
				  60-13-45,
				  60-13-46
				  and
				  60-13-47
				  NMSA 1978.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.5 - EFFECTIVE DATE

Current through Register Vol. 35, No. 13, July 16, 2024
May 15, 2018, unless a later date is cited at the end of a
				  section. From the date of publication of this rule in the New Mexico register,
				  until September 10, 2022, permits may be issued under either the previously
				  adopted rule, or this rule. After September 10, 2022, permits may be issued
				  only under this rule.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The purpose of this rule is to establish minimum standards
				  for the installation, repair, and replacement of mechanical systems including
				  equipment, appliances, fixtures, fittings and appurtenances including
				  ventilating, heating, cooling, air conditioning, and refrigeration systems,
				  incinerators, and other energy related systems in New Mexico.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.7 - DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See 14.5.1 NMAC, General Provisions and Chapter 2 of the 2021
				  Uniform Mechanical Code (UMC) as amended in
				  14.9.2.10
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.8 - ADOPTION OF THE 2021 UNIFORM MECHANICAL CODE

Current through Register Vol. 35, No. 13, July 16, 2024
A. This rule adopts by reference the 2021
				UMC, as amended by this rule.
B. In
				this rule, each provision is numbered to correspond with the numbering of the
				2021 UMC.
C. This rule shall apply
				in conjunction with the provisions of all applicable New Mexico construction
				codes, laws and standards.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.9 - CHAPTER 1 ADMINISTRATION

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
A.
101.0 General.
(1)
101.1 Title
Delete this
				section of the UMC and substitute: This code shall be known as 14.9.2 NMAC, the
				2021 New Mexico Mechanical Code (NMMC).
(2)
101.2 Scope.
Delete this
				section of the UMC and see
				14.9.2.2
				NMAC.
(3)
101.3
				Purpose.
Delete this section of the UMC and see
				14.9.2.6
				NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.10 - CHAPTER 2 DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
A.
203.0 Authority having
				jurisdiction.
Delete the text of this definition and substitute: The
				authority having jurisdiction is the CID and the mechanical-plumbing trade
				bureau chief for adoption, enactment, interpretation and enforcement of the
				state adopted mechanical code as the minimum requirement in the
				state.
B.
214.0 Listed (Third
				Party Certified).
See this definition in the UMC and add the following
				provision at the end of the definition: A manufacturer may select the
				independent certification organization of its choice to certify its products,
				provided that the certification organization has been accredited by the
				American national standards institute (ANSI), or another certification
				organization that CID has approved in writing.
C.
217.0 Occupiable Space
.
				Delete this section and see 14.7.2 NMAC and 14.7.3 NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.11 - CHAPTER 3 GENERAL REQUIREMENTS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
A.
304.3 Access to equipment and
				appliances on roofs. 304.3.1 Access.
See this section of the UMC except
				after the words "in height" add the following: except those designated as R-3
				occupancies.
B.
305.1
				Installation in garages.
At the end of the last sentence delete the
				following text: "unless listed as a flammable vapor ignition
				resistant.
C.
305.5 Drainage
				Pan.
See this section of the UMC except after each term "water heater"
				add the following: or hot-water-heating boiler.
D.
311.0 Heating and cooling air
				system.
See this section of the UMC except as follows:
311.3
				Prohibited source.
See this section of the UMC except delete the text of
				subsection (5) and replace with the following: a closet, bathroom, laundry
				room, toilet room, kitchen; or where it will pick up objectionable odors,
				fumes, or flammable vapors.
E.
314.0 Balancing.
Delete this section of the UMC and insert:
				Heating, ventilating, and air-conditioning systems (including hydronic systems)
				shall be balanced in accordance with the standards pursuant to UMC chapter
				17.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.12 - CHAPTER 4 VENTILATION AIR

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
A.
405.3 Bathroom Exhaust.
See
				this section of the UMC except add the following:
Exception: Residential Occupancies with an operable window
				  located in the same room.
B.
405.4 Kitchen Exhaust.
See
				this section of the UMC except after the words "directly to the outdoors" add
				the following: unless listed for recirculation.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.13 - CHAPTER 5 EXHAUST SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
511.3 Makeup Air.
See this section of the UMC except add the
				  following: windows and doors shall not be used for the purpose of providing
				  makeup air. The exhaust and makeup air systems shall be connected by an
				  electrical interlocking switch. A device to sense continued air movement within
				  the makeup air plenum shall be installed initiating a complete system shut-down
				  if air-flow is interrupted.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.14 - CHAPTER 6 DUCT SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
A.
603.11 Underground
				installation.
See this section of the UMC and add the following to the
				last sentence, "and be installed so as to support the weight of the concrete
				during encasement."
B.
609.0
				Automatic shutoffs. 609.1 Air-moving systems and smoke detectors.
See
				this section of the UMC and add the following to the exceptions: (6) automatic
				shutoffs are not required on evaporative coolers that derive all of their air
				from outside the building.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.16 - CHAPTER 8 CHIMNEYS AND VENTS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
803.1.10 Chimney and Vents.
See this section of the UMC except
				  delete the following language: "Where vents extend outdoors above the roof more
				  than 5 feet (1524mm) higher than required by Table 802.6.1, and where vents
				  terminate in accordance with Section 802.6.1 (1)(b), the outdoor portion of the
				  vent shall be enclosed as required by this section for vents not considered to
				  be exposed to the outdoors or such venting shall be
				  engineered."
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.17 - CHAPTER 9 INSTALLATION OF SPECIFIC APPLIANCES

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
907.2 Location.
See this section of the UMC except add the
				  following to the end: unlisted wall furnaces shall be installed with clearances
				  to combustible material of not less than eighteen (18) inches (460
				  mm).
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.20 - CHAPTER 12 HYDRONICS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
1205.2 Pressure testing.
See this section of the UMC except delete
				  the first sentence and substitute: system piping shall be tested with a
				  hydrostatic pressure or an air test of not less than 1.5 times operating
				  pressure.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 2 - 2021 NEW MEXICO MECHANICAL CODE › Section 14.9.2.21 - CHAPTER 13 FUEL GAS PIPING

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the UMC except as provided below.
A.
1308.5.2.2 Copper and copper alloy
				pipe.
Delete this section and substitute with the following: Copper and
				copper alloy pipe shall not be used. Aluminum alloy pipe shall not be used with
				gases corrosive to such material.
B.
1310.11.2 Emergency shutoff
				valves.
See this section of the UMC except delete the following: the
				emergency shutoff valves shall be plainly marked as such and their locations
				posted as required by the authority having jurisdiction. Add the following to
				the end: For purposes of isolation and safety, an additional approved gas shut
				off valve shall be installed downstream of the serving supplier gas meter prior
				to any distribution of gas into the gas piping system
C.
1311.0 Electrical bonding and
				grounding.
Delete this section of the UMC and see subsection G of
				14.10.4.11
				NMAC.
D.
1312.11 Liquefied
				petroleum gas facilities and piping.
Delete this section of the UMC and
				substitute the following: Liquefied petroleum gas facilities shall comply with
				Sections
				70-5-1
				through
				70-5-23
				NMSA 1978, the LPG and CNG Act and with 19.15.40 NMAC liquefied petroleum gas
				standards.
E.
1313.3 Test
				pressure.
See this section of the UMC except add the following:
				Exception: An existing gas piping system may be tested at a test pressure equal
				to one and one-half times them operating pressure of the system, but in no case
				shall it be tested at less than 3 psi.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 3 - 1997 UNIFORM MECHANICAL CODE › Section 14.9.3.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
A. This rule
				applies to all persons engaged in the construction activities, including
				inspectors and code enforcement officials, in the state of New
				Mexico.
B. 14 NMAC.9.3 [now 14.9.3
				NMAC] has a broad scope, with provisions that apply to the erection,
				installation, alteration, addition, repair, relocation, replacement,
				maintenance, of any mechanical system for the regulation and control of any
				heating, ventilating, cooling or refrigeration systems, incinerators, design
				construction, quality of materials and providing for the issuance of permits
				and inspections.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 3 - 1997 UNIFORM MECHANICAL CODE › Section 14.9.3.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
A. Pursuant
				to Section 60-13-9(F) NMSA 1978 of the Construction Industries Licensing Act,
				the construction industries division of the regulation and licensing department
				has adopted 14 NMAC 9.3 [now 14.9.3 NMAC]. This section provides as follows:
				"The division shall adopt all building codes and minimum standards as
				recommended by the trade bureaus and approved by the commission so that the
				public welfare is protected, uniformity is promoted and conflicting provisions
				are avoided."
B. Section
				60-13-44(B) NMSA 1978 of the Construction Industries Licensing Act states: "The
				mechanical bureau shall recommend to the commission minimum standards for the
				installation of all fixtures, consumers' gas pipe, appliances and materials
				installed in the course of a mechanical installation. The recommendations shall
				be in substantial conformity with the Uniform Mechanical Code published by the
				international conference of building officials and the Uniform Plumbing Code
				published by the international association of mechanical and plumbing
				officials."
C. Pursuant to Section
				60-13-44(F) NMSA 1978 of the Construction Industries Licensing Act, this rule
				and the materials adopted pursuant to this rule set the minimum building
				standards for the state of New Mexico. This provision specifically states: "All
				political subdivisions of the state are subject to the provisions of codes
				adopted and approved under the Construction Industries Licensing Act. Such
				codes constitute the minimum requirements for codes of political
				subdivisions."
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 3 - 1997 UNIFORM MECHANICAL CODE › Section 14.9.3.5 - EFFECTIVE DATE

Current through Register Vol. 35, No. 13, July 16, 2024
Compiler's note: The words or paragraph, above, are no
					 longer applicable. Later dates are now cited only at the end of sections, in
					 the history notes appearing in brackets.
12/31/98; Recompiled
					 10/01/01
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 3 - 1997 UNIFORM MECHANICAL CODE › Section 14.9.3.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The objective of 14 NMAC 9.3 [now 14.9.3 NMAC] is to promote
				  the general welfare of the people of the state of New Mexico by providing for
				  the protection of life and property through standards that, when complied with,
				  will result in an installation essentially free from hazards. Further, this
				  code is intended to provide uniformity in mechanical
				  standards.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 3 - 1997 UNIFORM MECHANICAL CODE › Section 14.9.3.8 - ADOPTION OF 14 NMAC 9.3 [now 14.9.3 NMAC]

Current through Register Vol. 35, No. 13, July 16, 2024
Adoption of the 1997 Uniform Mechanical Code (14 NMAC 9.3)
				  [now 14.9.3 NMAC] was recommended by the mechanical bureau and formally
				  approved by the construction industries commission on August 17, 1998 and
				  September 25, 1998.
A. This part
				supersedes Rule No. MB-UMC-91-1, the 1991 Uniform Mechanical Code, filed with
				the state records center on July 28, 1992.
B. This part adopts by reference the 1997
				Uniform Mechanical Code, except as amended by the 1997 New Mexico Plumbing and
				Mechanical Code at 14 NMAC 9.2 [now 14.9.2 NMAC].
C. This part shall be referred to as the 1997
				Uniform Mechanical Code, and cited in short form as 14 NMAC 9.3 [now 14.9.3
				NMAC].
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
A. This rule
				applies to all individuals performing alteration, repair and installation
				working on boilers in the state of New Mexico.
B. These boiler rules and regulations address
				the following: permits, insurance requirements and inspections, licensing,
				licensing of boiler operators and repairmen, installers and repair
				organizations, the issuing of boiler certificates of inspection, authorization
				for alterations and enforcement by the mechanical bureau.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
Pursuant to Section
				  60-13-9.(F.) of
				  the Construction Industries Licensing Act (NMSA 1978) the construction
				  industries division has adopted 14 NMAC 9.4 [now 14.9.4 NMAC]. Section
				  61-13-9.
				  (F.), NMSA 1978 provides as follows: "The division shall adopt all building
				  codes and minimum standards as recommended by the trade bureaus and approved by
				  the commission so that the public welfare is protected, uniformity is promoted
				  and conflicting provision are avoided."
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The objective of 14 NMAC 9.4 [now 14.9.4 NMAC] is to promote
				  the general welfare of the people of New Mexico by providing for the protection
				  of life and property through standards that, when complied with, will result in
				  an installation essentially free from hazards.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.8 - ADOPTED PUBLICATIONS

Current through Register Vol. 35, No. 13, July 16, 2024
The commission has adopted the following publications as the
				  rules for construction, installation, operation, inspection, repair and
				  alterations of all existing boilers.
A. Uniform Plumbing Code, 1991 Edition, 14
				NMAC 11.3 (MB-UPC-91-1) [now 14.11.3 NMAC].
B. Uniform Mechanical Code, 1991 Edition, 14
				NMAC 9.3 (MB-UMC-91-1) [now 14.9.3 NMAC].
C. NOTE: The above referenced documents are
				included in the edition adopted by construction industries division and the
				construction industries commission that is currently on file with the state
				records and archives center. Future editions will be adopted in the NMAC
				format. The NMAC reference for the Uniform Plumbing Code is 14 NMAC 11.3
				(MB-UPC-91-1) [now 14 11.3 NMAC]. The NMAC reference for the Uniform Mechanical
				Code is 14 NMAC 9.3 (MB-UMC-91-1) [now 14.9.3 NMAC].
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.9 - PERMIT REQUIRED

Current through Register Vol. 35, No. 13, July 16, 2024
A. It shall be
				unlawful to install or reinstall any boiler without first obtaining a permit to
				do so from the mechanical bureau, subject to all provisions of the construction
				industries division rules and regulations.
B. Owner/user inspectors are not required to
				have permits issued for repairs, alterations or installations.
C. Each application for a boiler permit
				(installation and/or re-installation) may require one set of plans and
				specifications as determined necessary by the mechanical bureau to describe
				adequately the proposed installation.
D. It shall be the responsibility of the
				organization making the installation to provide for a permit, inspection,
				documentation and certification of the work and to ensure prior acceptance of
				the procedures for the work.
E.
				Emergency boiler installation may be performed during non-business hours
				provided a permit is requested on the next regular business day.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.10 - ANNUAL PERMITS

Current through Register Vol. 35, No. 13, July 16, 2024
Section 5, 14 NMAC 5.2 [now
				  14.5.2.5 NMAC]
				  (permits) of the construction industries division rules and regulations does
				  not apply to boilers.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.11 - VIOLATIONS AND PENALTIES

Current through Register Vol. 35, No. 13, July 16, 2024
Violation(s) of this code and/or the technical codes may
				  result in one or more of the following:
A. The construction industries division may
				assess the licensee an administrative penalty provided under the provisions of
				the Construction Industries Licensing Act and the LPG Act, (NMSA 1978), or its
				rules and regulations.
B. The
				division may require a double permit fee when any work is started prior to
				acquiring the necessary permit as stated in the provisions of the Construction
				Industries Licensing Act and LPG Act, (NMSA 1978) or its rules and
				regulations.
C. Whenever any work
				is being done contrary to the provisions of these rules or the technical codes,
				the director may order the work stopped by notice in writing served on a person
				engaged in doing or causing such work to be done, and that person shall
				forthwith stop such work until authorized by the director or the mechanical
				bureau chief to proceed with the work.
D. Pursuant to Section 6 [now 14.9.4.6 NMAC]
				(inspections) of the construction industries rules and regulations, failure of
				a licensee to call for final inspection may result in the commission assessing
				up to a five hundred dollar ($500.00) penalty for each failure.
E. Pursuant to Section 6 [now 14.9.4.6 NMAC]
				(inspection[s]) of the construction industries division rules and regulations,
				failure of a licensee to cure any cited violation within 90 days may result in
				the commission assessing up to a two hundred fifty dollar ($250.00) penalty for
				each such code violation.
F. The
				alteration of any safety device by a licensee may be subject to a penalty
				assessed by the commission.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.12 - NEW CONSTRUCTION AND INSTALLATION OF BOILERS

Current through Register Vol. 35, No. 13, July 16, 2024
A. All boiler installations shall conform to
				minimum requirements for safety from structural and mechanical failure and
				excessive pressure, as established by the mechanical bureau in accordance with
				the ASME Boiler and Pressure Vessel Codes, Sections I, IV, and IX, with the
				addenda and interpretations thereto made, and the National Board of Boiler and
				Pressure Vessel Inspection Code.
B.
				All installations after the adoption of the boiler rules shall be designed,
				constructed, inspected and stamped in accordance with the ASME Code, as adopted
				herein and the latest addenda thereto, in effect. In addition, all boilers,
				except cast iron boilers, shall be registered with the national board of boiler
				and pressure vessel inspectors and be assigned a national board registration
				number.
C. The mechanical bureau
				may inspect any boiler installations in the state of New Mexico with sufficient
				notice to the owners/operators of such equipment. All inspections are to be
				conducted in accordance with the latest accepted edition of the National Board
				Inspection Code.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.13 - EXISTING BOILERS

Current through Register Vol. 35, No. 13, July 16, 2024
A. All existing
				boilers shall be maintained and operated in compliance with the manufacturer's
				requirements and all existing codes at the time of installation. All existing
				boilers installed prior to 1973 shall, within two (2) years, meet the minimum
				requirements of the Uniform Mechanical Code, 1973. (Reference Appendix B,
				Chapter 21, - Table No. 21-C.)
B.
				All boilers which are re-located with or without a change of ownership shall be
				installed in compliance with ASME as a new installation. Following such
				reinstallation of a boiler, a hydrostatic test in compliance with Section 27
				[now 14.9.4.27 NMAC] (preparation of boilers) of these rules may be required by
				the state mechanical bureau chief inspector, deputy state inspector, city
				inspector, or an [sic] national board commissioned inspector.
C. Used boilers from within New Mexico,
				another state or country must be approved by the mechanical bureau. Such
				boilers shall bear the standard stamping of ASME and the national board
				registration number.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.14 - EXEMPTIONS: BOILERS NOT SUBJECT TO THE MECHANICAL BUREAU RULES AND REGULATIONS

Current through Register Vol. 35, No. 13, July 16, 2024
A. Listed
				and approved potable water heaters with a nominal capacity of 120 gallons or
				less having a heat input of 200,000 Btu/h or less used for hot-water supply at
				pressures of 160 psi or less and at temperatures not exceeding 250 degrees F,
				as regulated by the New Mexico Plumbing Code.
B. Tanks connected to sprinkler(s).
C. Portable unfired pressure vessels, which
				are constructed to D.O.T. and I.C.C. regulations and are used in such
				service.
D. Containers for
				liquefied petroleum gases, bulk oxygen and medical gas, which are regulated by
				the Fire Code or by the New Mexico LPG Act, (NMSA 1978).
E. Unfired pressure vessels having a volume
				of 5 cubic feet or less and operated at pressures not exceeding 250
				psi.]
F. Pressure vessels used in
				refrigeration systems, which are regulated by the Uniform Mechanical
				Code.
G. Pressure tanks used in
				conjunction with coaxial cables, telephone cables, power cables, and other
				similar humidity-control systems.
H. Any boiler subjected to regular inspection
				by federal inspectors or licensed by federal authorities.
I. Hydronic panel heating systems as
				described in the Uniform Mechanical Code, Chapter 23.
J. Public utilities, rural electric
				cooperatives, mining process (administration facilities are NOT exempt),
				refinery processing, gas processing (administration facilities are NOT exempt)
				and lumber industries (sawmill only).
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.15 - CITY AND LOCAL JURISDICTION

Current through Register Vol. 35, No. 13, July 16, 2024
Cities that have adopted a boiler code in substantial
				  compliance with the State Boiler Code may enforce the provisions of the city
				  code within their jurisdictions.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.16 - REPAIRS/ALTERATIONS OF BOILERS AND SAFETY/SAFETY RELIEF VALVES

Current through Register Vol. 35, No. 13, July 16, 2024
A. Repair organizations making repairs to
				boilers shall have an ASME qualified welders certificate or national board "R"
				stamp.
B. All repairs of boilers
				shall be in compliance with these rules. A report of welder repair/alteration
				and the completed work may be subject to the approval of the insurance company
				insuring the unit. The mechanical bureau may make random field site
				inspections.
C. Safety valves and
				safety relief valves shall be repaired only by organizations having a
				certificate of authorization code symbol stamp, ASME, "V", "HV", "UV", "NV" or
				a national board "VR" (repair of pressure relief valves) symbol stamp.
				Additionally, such repair firms when located within or doing business within
				the state of New Mexico shall be a New Mexico licensed contractor.
D. No repair/alteration by welding shall be
				made without the approval of the mechanical bureau or by a national board
				commissioned inspector holding a valid national board commission. If the
				mechanical bureau or special inspector determine a hydrostatic test is
				required, such test shall be applied after the repair/alteration have been
				completed.
E. A boiler shall be
				removed from service if a lap seam crack is discovered along a longitudinal
				riveted joint. Repairs are prohibited.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.17 - ACCIDENT REPORTING

Current through Register Vol. 35, No. 13, July 16, 2024
In case of boiler accident (fire or waterside) or other
				  serious damage to a boiler, the mechanical bureau and the insurance company
				  shall be notified immediately by the owner/user. No parts or appurtenances
				  shall be removed or their positions changed unless necessary for the protection
				  of life or limb until the state or a national board commissioned inspector has
				  made an investigation.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 9 - MECHANICAL CODES › Part 4 - BOILERS › Section 14.9.4.18 - CERTIFICATE OF COMPLIANCE/OPERATING PERMIT

Current through Register Vol. 35, No. 13, July 16, 2024
A. All boilers and steam generators as
				stipulated in Section 26 [now 14.9.4.26 NMAC] (Inspections and fees) of these
				rules shall be inspected. Upon successful inspection, a certificate of
				inspection shall be issued by the mechanical bureau or insurance company. Such
				certificate may take any format approved for use by the mechanical bureau
				chief.
B. If, upon making the
				internal and/or external inspection, the Inspector finds the boiler to be in
				safe working order, provided with the appurtenances necessary for safety, and
				properly set up, the mechanical bureau or insurance company, upon receipt of an
				inspection report from the Inspector, shall issue to the owner or user thereof
				a certificate of inspection. Upon receipt of the certificate of inspection,
				such owner or user may operate the boiler described in the certificate until
				the date of expiration unless such certificate shall be withdrawn or
				revoked.
C. The certificate of
				compliance shall state the name of the owner or user; location; manufacturer's
				serial number, and the national board registration number; date of inspection;
				date of expiration of the certificate of compliance; the maximum allowable
				working pressure at which the boiler may operate; name of the manufacturer;
				type of boiler and insurance company with the name and national board
				commission number of the national board commissioned inspector or mechanical
				bureau inspector doing the inspection.
D. The certificate of compliance operating
				permit or a copy shall be conspicuously placed so it can be readily identified
				with the boiler and must be posted in the boiler or mechanical room. The
				certificate of compliance operating permit for a portable boiler shall be
				attached to the boiler and shall be accessible at all times.