reglab/statecodes huggingface dataset:
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 17 - TANK FILLING PROCEDURES › Section 165:26-6-73 - Emergency controls

Current through Vol. 41, No. 20, July 1, 2024
(a) Each
				  fuel system must have means for quickly and completely shutting off the flow of
				  fuel in an emergency. This requirement is in addition to the requirement for a
				  deadman control of fuel flow.
(b)
				  The emergency fuel shutoff system must include shutoff stations located outside
				  of probable spill areas and near the route that normally is used to leave the
				  spill area or to reach the fire extinguishers provided for the protection of
				  the area.
Added at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 19 - DISPENSING PROCEDURES › Section 165:26-6-80 - Dispensing fuel into aircraft

Current through Vol. 41, No. 20, July 1, 2024
Aircraft being fueled from a stationary dispenser must be
					 positioned so that aircraft fuel system vents or fuel tank openings are not
					 closer than 25 ft. (8 m) from any terminal building, hangar, service building
					 or enclosed passenger concourse other than a loading walkway. Aircraft being
					 fueled must not be positioned so that the vent or tank openings are within 50
					 ft. (15 m) of any combustion and ventilation air-intake to any boiler, heater
					 or incinerator room.
Added at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 19 - DISPENSING PROCEDURES › Section 165:26-6-81 - Static protection and bonding

Current through Vol. 41, No. 20, July 1, 2024
(a) Dispensing devices or cabinets must be
				  designed so that a proper bond between the aircraft and the fueling equipment
				  can be established.
(b) Conductive
				  hose must be used to prevent electrostatic discharge but not to accomplish
				  required bonding.
Added at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-6-85 - Fencing [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-6-86 - Required signs

Current through Vol. 41, No. 20, July 1, 2024
Entrances to fueling areas must be posted with signs that
					 state:
(1) No Smoking.
(2) Shut engines off.
Added at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-6-87 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-6-88 - Fire extinguishers

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Extinguishers specified for protection of fuel servicing operations should be
				  located along the fence, near dispensers or at emergency remote control
				  stations of airport fixed-fuel systems.
(b) Extinguishers should be located near but
				  not in probable spill areas.
Added at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-6-89 - Sources of ignition [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-6-90 - Monitoring requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 23 - RECORDKEEPING [Revoked] › Section 165:26-6-95 - Inventory records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 6 - Requirements for Aboveground Storage Tank Systems Utilized by Airports Open to the Public › Part 23 - RECORDKEEPING [Revoked] › Section 165:26-6-96 - Spill prevention control and countermeasure plan [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 1 - DESIGN, CONSTRUCTION, AND INSTALLATION [Revoked] › Section 165:26-7-1 - General standards [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 15 Ok Reg 3020, eff 7-15-98; Revoked at 17 Ok Reg
					 2875, eff 17-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 1 - DESIGN, CONSTRUCTION, AND INSTALLATION [Revoked] › Section 165:26-7-2 - Construction and design standards for tank systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 17-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 1 - DESIGN, CONSTRUCTION, AND INSTALLATION [Revoked] › Section 165:26-7-3 - Construction and design standards for piping and ancillary equipment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 15 Ok Reg 3020, eff 7-15-98; Revoked at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 1 - DESIGN, CONSTRUCTION, AND INSTALLATION [Revoked] › Section 165:26-7-4 - Construction and design standards for the control of spillages and releases [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 1 - DESIGN, CONSTRUCTION, AND INSTALLATION [Revoked] › Section 165:26-7-5 - Construction and design standards for physical and safety protection [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 3 - RELEASE DETECTION [Revoked] › Section 165:26-7-11 - Tanks [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 3 - RELEASE DETECTION [Revoked] › Section 165:26-7-12 - Piping [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 15 Ok Reg
					 3020, eff 7-15-98; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 3 - RELEASE DETECTION [Revoked] › Section 165:26-7-13 - Methods of release detection for piping [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 15 Ok Reg
					 3020, eff 7-15-98; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 3 - RELEASE DETECTION [Revoked] › Section 165:26-7-14 - Testing or monitoring for vapors [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 15 Ok Reg
					 3020, eff 7-15-98; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 7 - Requirements for New Aboveground Storage Tanks Systems [Revoked] › Part 3 - RELEASE DETECTION [Revoked] › Section 165:26-7-15 - Testing and monitoring for liquids on the groundwater [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 15 Ok Reg
					 3020, eff 7-15-98; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-8-1 - Application

Current through Vol. 41, No. 20, July 1, 2024
(a) This Subchapter
				  applies to the storage, handling and use of regulated substances kept in
				  aboveground storage tanks at marinas.
(b) Subchapters 1 General Provisions, 2
				  General Requirements for AST's, 3 Release Prevention and Detection, and 4
				  Inspections, Penalties, and Field Citations shall also apply in addition to
				  this Subchapter.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Amended at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-8-2 - Timeframes for registration and compliance with rules

Current through Vol. 41, No. 20, July 1, 2024
(a) Tanks that are greater than 110 gallons
				  must be registered with PSTD. The tank and piping system must come in
				  compliance with the rules of this Chapter and Subchapter before July 1, 2009.
				  Compliance may be required sooner for any part of a system which poses a threat
				  to property, people, or to the environment.
(b) All new underground piping at existing
				  facilities must be installed in accordance with
				  165:26-2-55, "Underground piping
				  materials," and with
				  165:26-3-20.2, "Installation and
				  monitoring requirements for underground piping."
(c) All dock or pier product piping from the
				  shoreline to the dispensers at new facilities must be installed according to
				  165:26-8-40.1 "Over-water piping
				  at marinas" and
				  165:26-8-40.2 "Installation
				  requirements for over-water piping".
(d) All dock or pier product piping from the
				  shoreline to the dispensers at existing facilities must be upgraded before the
				  deadline date of July 1, 2009 according to
				  165:26-8-40.1 "Over-water piping
				  at marinas" and
				  165:26-8-40.2 "Installation
				  requirements for over-water piping".
(e) Temporary tanks may not be used at
				  marinas.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Amended at 23 Ok Reg 144, eff 10-6-05 (emergency); Amended at
					 23 Ok Reg 2297, eff 7-1-06; Amended at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-8-2.1 - Release detection requirements for marinas

Current through Vol. 41, No. 20, July 1, 2024
Monitoring requirements, at a minimum, must consist of an
					 annual line tightness test conducted no later than April
					 1st of each year.
Added at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Added at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-8-3 - Codes and standards [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-8-4 - Local jurisdiction [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-8-5 - Consultation of Petroleum Storage Tank Division [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-9 - Approved tanks, tank design [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-10 - Maximum capacity for tanks

Current through Vol. 41, No. 20, July 1, 2024
Aboveground storage tanks storing gasoline and diesel fuel
					 at an individual site must be limited to a maximum capacity of 12,000 gal.
					 (45,600 L) and an aggregate capacity of 40,000 gal. (152,000 L). Local
					 jurisdictions may have more stringent regulations.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-11 - Emergency pressure release [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-12 - Aboveground storage tank spacing [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-13 - Location of aboveground storage tanks at marinas

Current through Vol. 41, No. 20, July 1, 2024
(a) Tanks supplying marinas and pumps not
				  integral with the dispensing device must be onshore.
(b) All new aboveground storage tanks located
				  at marinas must be located above the flood stage level.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-14 - Distance to be kept around tanks [REVOKED)

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-15 - Requirements on fill pipes [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-16 - Collision barriers [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-17 - Spill and overfill prevention [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-8-18 - Corrosion protection [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 5 - SECONDARY CONTAINMENT REQUIREMENTS [Revoked] › Section 165:26-8-25 - Double-walled tanks [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 5 - SECONDARY CONTAINMENT REQUIREMENTS [Revoked] › Section 165:26-8-26 - Secondary containment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 7 - EQUIPMENT AND MATERIALS [Revoked] › Section 165:26-8-30 - Aboveground storage tank piping materials [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 7 - EQUIPMENT AND MATERIALS [Revoked] › Section 165:26-8-31 - Electrical equipment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-35 - Piping protection [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-36 - Piping and gravity flow [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-37 - Valves on piping [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-38 - External piping protection [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-39 - Underground piping materials [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 19 Ok Reg 1616, eff 6-13-02; Revoked at 21 Ok Reg
					 2079, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-40 - Aboveground piping at marinas [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Revoked at 23 Ok Reg 144, eff 10-6-05 (emergency); Revoked at
					 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-40.1 - Over-water piping at marinas

Current through Vol. 41, No. 20, July 1, 2024
(a) The design, fabrication, assembly, test,
				  and inspection of the piping system from the fuel tank to the fuel dispensers
				  must be in accordance with NFPA 30 and NFPA 30A.
(b) The piping must be installed according to
				  the manufacturers installation recommendations and instructions.
(c) Piping must be listed and approved by the
				  manufacturer for aboveground installations.
Added at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Added at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-40.2 - Installation requirements for over-water piping

Current through Vol. 41, No. 20, July 1, 2024
(a)
Steel piping.
(1) Piping shall be installed with proper
				  support and strain relief in order to eliminate the physical stress on the
				  piping and piping connections caused by the constant movement of the water and
				  floating dock. Fuel piping and electrical conduit shall be rigidly attached to
				  the dock before the piping enters the sump area, in order to prevent strain on
				  the entry boots and primary pipe fittings.
(2) Steel flex connectors must be used
				  between the shore piping and the piping on the floating structure and between
				  separate sections of the floating structure to allow for movement of the dock
				  and changes in water levels.
(3)
				  Onshore piping must be rigidly anchored in place to prevent movement when water
				  levels are elevated.
(4) A listed
				  emergency breakaway device designed to retain liquid on both sides of the
				  breakaway point must be installed on each line serving the dock. The breakaway
				  device shall be located where the dock piping will separate from the shore or
				  secured ramp piping. The piping shall be secured at both ends of the breakaway
				  device so that the piping will withstand the forces and pressures exerted upon
				  it.
(5) There must be a normally
				  closed explosion proof solenoid valve with built-in pressure relief or a
				  normally closed explosion proof solenoid valve and a pressure relief valve
				  installed in each product line at the shoreline.
(6) A ball valve must be installed at the
				  shoreline in order to manually shut off the flow of fuel.
(7) Containment sumps must be installed under
				  all dispensers and monitored with sensors. If a pressure system is used all
				  sump sensors must automatically control the electricity to both the solenoid
				  valves and submerged pump. If a suction system is used the sump sensors should
				  automatically control the electricity to both the solenoid valve and suction
				  pump motor.
(8) If the onshore
				  piping is double walled a transition sump is required at the shoreline in order
				  to contain a release from the onshore piping. The transition sump must contain
				  the ball valve and solenoid valve and be rigidly anchored in place.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 9 - OVER-WATER PIPING REQUIREMENTS › Section 165:26-8-41 - Installation and monitoring requirements for piping [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Revoked at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Revoked at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 11 - VAULT REQUIREMENTS [Revoked] › Section 165:26-8-45 - Vaults [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 11 - VAULT REQUIREMENTS [Revoked] › Section 165:26-8-50 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 13 - VENTING AND VENTING SPECIFICATIONS [Revoked] › Section 165:26-8-51 - Vent piping size [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 13 - VENTING AND VENTING SPECIFICATIONS [Revoked] › Section 165:26-8-52 - Vent piping height [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 15 - DISPENSER REQUIREMENTS › Section 165:26-8-60 - Dispensers [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 15 - DISPENSER REQUIREMENTS › Section 165:26-8-61 - Dispenser hose

Current through Vol. 41, No. 20, July 1, 2024
Listed hose assemblies must be used to dispense fuel. Where
					 hose length exceeds 18 ft (5.5m), the hose shall be secured so as to protect it
					 from damage, such as a hose reel, and in no case shall the hose exceed 50 ft
					 (15m) in length.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Amended at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 15 - DISPENSER REQUIREMENTS › Section 165:26-8-62 - Nozzles

Current through Vol. 41, No. 20, July 1, 2024
Dispensing nozzles used at marinas must be the automatic
					 closing type. Hold-open latch devices from nozzles for marina service are not
					 allowed.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Amended at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 15 - DISPENSER REQUIREMENTS › Section 165:26-8-63 - Dispenser location at marinas

Current through Vol. 41, No. 20, July 1, 2024
Dispensing devices at marinas may be located on open piers,
					 wharves, floating docks, shores or on piers of the solid-fill type, but must be
					 located apart from other structures to provide room for safe ingress and egress
					 of watercraft for fueling. Dispensing devices must be in all cases at least 20
					 ft. (6 m) from any activity involving fixed sources of
					 ignition.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 22 Ok Reg 1752, eff
					 7-1-05
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 15 - DISPENSER REQUIREMENTS › Section 165:26-8-64 - Specific requirements for dispensers at marinas; maintenance

Current through Vol. 41, No. 20, July 1, 2024
When maintenance of a Class I dispenser is necessary the
					 following precautions must be taken before maintenance begins:
(1) Only persons knowledgeable in performing
				  the required maintenance can perform the work.
(2) All electrical power to the dispenser,
				  the dispensing pump, and all associated circuits must be shut off at the main
				  electrical panel.
(3) The emergency
				  shutoff valve at the dispenser, if installed, must be closed.
(4) All unauthorized persons are prohibited
				  from coming within 20 ft (6 m) of the dispenser while the maintenance work is
				  being done.
Added at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 17 - TANK FILLING PROCEDURES [Revoked] › Section 165:26-8-70 - Tank filling operation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 17 - TANK FILLING PROCEDURES [Revoked] › Section 165:26-8-71 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 17 - TANK FILLING PROCEDURES [Revoked] › Section 165:26-8-72 - Tightfill connection requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 17 - TANK FILLING PROCEDURES [Revoked] › Section 165:26-8-73 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 19 - DISPENSING PROCEDURES › Section 165:26-8-80 - Attendants at marinas

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Marinas may have an attendant or supervisor on duty when the marina is open for
				  business. The attendant's primary function will be to supervise, observe, and
				  control the dispensing of fuels to insure that all safety requirements are met,
				  and to insure that the waters of the state are not contaminated by
				  fuel.
(b) At unattended marine
				  facilities an emergency shut off device must be installed to meet the following
				  requirements:
(1) Installed between 20 to 100
				  feet from the fuel dispensing devices that they serve.
(2) Device must shut down the fuel dispensing
				  system in the event of an emergency.
(3) Must be readily accessible to
				  patrons.
(4) Emergency instructions
				  must be conspicuously posted.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 19 - DISPENSING PROCEDURES › Section 165:26-8-81 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-8-85 - Fencing [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-8-86 - Required signs

Current through Vol. 41, No. 20, July 1, 2024
All marinas must have a sign printed in 1/4 to ½
					 inch text in black or red block capital letters on a white background
					 conspicuously posted and easily readable from the dispensing area which
					 says:
(1) BEFORE FUELING:
(A) Stop all engines and
				  auxiliaries.
(B) Shut off all
				  electricity, open flames and heat sources.
(C) Check all bilges for fuel
				  vapors.
(D) Extinguish all smoking
				  materials.
(E) Close access
				  fittings and openings to prevent fuel vapors from entering enclosed spaces of
				  the vessel.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-8-87 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-8-88 - Fire extinguishers

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Each marina must have a 40B:C fire extinguisher.
(b) A minimum of three (3) extinguishers must
				  be located at the fuel dock and one or more located so they will be within
				  fifty feet (50') or fifteen meters (15 m) of each pump, dispenser, and
				  underground fill pipe opening.
(c)
				  Piers which extend more than five hundred feet (500') or one hundred fifty-two
				  meters (152 m) in travel distance from shore must have a Class III standpipe
				  installed in accordance with NFPA 14, Standard for the Installation of
				  Standpipe and Hose Systems.
(d)
				  There must be a knife at the fuel dock for quickly cutting mooring lines in an
				  emergency and a push pole for shoving away a boat.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Amended at 23 Ok Reg 144, eff 10-6-05 (emergency); Amended at
					 23 Ok Reg 2297, eff 7-1-06; Amended at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-8-89 - Sources of ignition [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 21 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-8-90 - Monitoring requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 23 - RECORDKEEPING [Revoked] › Section 165:26-8-95 - Inventory records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 8 - Requirements for Aboveground Storage Tank Systems Utilized by Marinas › Part 23 - RECORDKEEPING [Revoked] › Section 165:26-8-96 - Spill Prevention Control and Countermeasure Plan [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 1 - INSPECTIONS [Revoked] › Section 165:26-9-1 - Owner/operator cooperation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 1 - INSPECTIONS [Revoked] › Section 165:26-9-2 - Authority of the Commission [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 1 - INSPECTIONS [Revoked] › Section 165:26-9-3 - Completion of inspections [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 1 - INSPECTIONS [Revoked] › Section 165:26-9-4 - Recordkeeping [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 1 - INSPECTIONS [Revoked] › Section 165:26-9-5 - Inspection for compliance [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 3 - FEES [Revoked] › Section 165:26-9-11 - Fees [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 5 - PENALTIES [Revoked] › Section 165:26-9-21 - Penalties [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 9 - Inspections, Fees, and Penalties [Revoked] › Part 7 - FIELD CITATION [Revoked] › Section 165:26-9-25 - Field citations [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg
					 2515, eff 7-1-97; Amended at 15 Ok Reg 3020, eff 7-15-98; Revoked at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 10 - Requirements for Aboveground Storage Tank Systems Utilized by Retail Facilities › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-10-1 - Application

Current through Vol. 41, No. 20, July 1, 2024
(a) This Subchapter
				  applies to the storage, handling and use of all regulated substances which are
				  kept in aboveground storage tanks, at facilities which engage in the retail
				  sale of a Regulated Substance.
(b)
				  Subchapters 1 General Provisions, 2 General Requirements for AST's, 3 Release
				  Prevention and Detection, and 4 Inspections, Penalties, and Field Citations
				  shall also apply in addition to this Subchapter.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Amended at 25 Ok Reg 2187, eff 7-11-08; Amended at 26 Ok Reg
					 1831, eff 7-1-09
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 10 - Requirements for Aboveground Storage Tank Systems Utilized by Retail Facilities › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-10-2 - Timeframes for registration and compliance with rules

Current through Vol. 41, No. 20, July 1, 2024
(a) Tanks at retail facilities that are
				  greater than 110 gallons must be registered with PSTD.
(b) Temporary tanks may not be used at retail
				  facilities.
Added at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Amended at 23 Ok Reg 2297, eff 7-1-06; Amended at 24 Ok Reg
					 1479, eff 7-1-07; Amended at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 10 - Requirements for Aboveground Storage Tank Systems Utilized by Retail Facilities › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-10-3 - Codes and standards [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 10 - Requirements for Aboveground Storage Tank Systems Utilized by Retail Facilities › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-10-4 - Local jurisdiction [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 10 - Requirements for Aboveground Storage Tank Systems Utilized by Retail Facilities › Part 1 - GENERAL APPLICATION AND COMPLIANCE PROVISIONS › Section 165:26-10-5 - Consultation of Petroleum Storage Tank Division [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 10 - Requirements for Aboveground Storage Tank Systems Utilized by Retail Facilities › Part 3 - TANK DESIGN, CONSTRUCTION, CAPACITY AND LOCATION REQUIREMENTS › Section 165:26-10-9 - Approved tanks, tank design [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Revoked at 21 Ok Reg 2079, eff
					 7-1-04