reglab/statecodes huggingface dataset:
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1207 - ANIMALS IN RESERVOIR

Current through Register Vol. 39, No. 2, July 15, 2024
The watering, washing or wallowing of any horses, mules,
					 cattle, or domestic animals shall not be permitted in any class I or class II
					 reservoir. The supplier of water may permit domestic animals within 50 feet of
					 normal pool elevation if the animal is under direct supervision by a person and
					 the activity is regulated by the supplier of water to ensure that water quality
					 is not adversely affected.
Authority
					 G.S.
					 130A-315;
					 130A-320;
					 P.L.
					 93-523;
Eff. January 1,
					 1977;
Readopted Eff. December 5, 1977;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1304 Eff. April 4, 1990;
Amended Eff. July 1, 1994;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1208 - CONTROLLING THE DRAINAGE OF WASTES

Current through Register Vol. 39, No. 2, July 15, 2024
Precautions shall be taken on the watershed of class I and
					 class II reservoirs and water intakes located on unimpounded streams to control
					 the drainage of wastes from animal and poultry pens or lots, into such
					 sources.
Authority
					 G.S.
					 130A-315;
					 130A-320;
					 P.L.
					 93-523;
Eff. January 1,
					 1977;
Readopted Eff. December 5, 1977;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1305 Eff. April 4, 1990;
Amended Eff. September 1, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1209 - UNTREATED DOMESTIC SEWAGE OR INDUSTRIAL WASTES

Current through Register Vol. 39, No. 2, July 15, 2024
No treated or untreated domestic sewage, treated or
					 untreated industrial waste or by-products shall be stored on the watershed of
					 or discharged into any public water supply reservoir or stream tributary to
					 that reservoir whose waters are classified as WS-I. No untreated domestic
					 sewage or industrial waste by-products shall be discharged into any public
					 water supply reservoir or stream classified as WS-II, WS-III, WS-IV, or WS-V.
					 No hazardous waste, industrial by-products, treated or untreated domestic
					 sewage shall be stored in the watershed of a Class I or Class II water supply
					 reservoir. No hazardous waste or industrial by-products shall be stored in the
					 watershed of a WS-II, WS-III, WS-IV, or WS-V stream unless precautions are
					 taken to prevent its being spilled into or otherwise entering the raw water
					 supply.
Authority
					 G.S.
					 130A-315;
					 130A-320;
					 P.L.
					 93-523;
Eff. January 1,
					 1977;
Readopted Eff. December 5, 1977;
Amended Eff.
					 February 1, 1987;
Transferred and Recodified from
					 10 NCAC
					 10D .1306 Eff. April 4, 1990;
Amended Eff. July 1, 1994; September 1, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1210 - SEWAGE DISPOSAL

Current through Register Vol. 39, No. 2, July 15, 2024
Any residence, place of business or public assembly,
					 located on a watershed shall be provided with a sanitary means of sewage
					 disposal.
Authority
					 G.S.
					 130A-315;
					 130A-320;
Eff.
					 January 1, 1977;
Readopted Eff. December 5, 1977;
Transferred and Recodified from
					 10 NCAC
					 10D .1309 Eff. April 4, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1211 - EXPIRED - GROUND ABSORPTION SEWAGE COLLECTION: TREATMENT/DISP SYSTEMS

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-315;
					 130A-320;
					 P.L.
					 93-523;
Eff. February 1,
					 1987;
Amended Eff. December 1, 1988;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1313 Eff. April 4, 1990;
Amended Eff. July 1, 1994; September 1, 1990;
Expired Eff. December
					 1, 2015 pursuant to
					 G.S.
					 150B-21.3A.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1212 - BURIAL OF CARCASSES

Current through Register Vol. 39, No. 2, July 15, 2024
The carcass of any dead animal found within the watershed
					 shall be buried by the owner or person in charge of the animal or the person
					 owning or in charge of the land upon which the animal dies with a covering of
					 at least three feet of earth or the carcass shall be burned or removed from the
					 watershed and buried as required by
					 G.S.
					 106-403. In no case shall dead animals be
					 placed in the reservoir.
Authority
					 G.S.
					 130A-315;
					 130A-320;
					 P.L.
					 93-523;
Eff. January 1,
					 1977;
Readopted Eff. December 5, 1977;
Transferred and
					 Recodified
					 10 NCAC
					 10D .1307 Eff. April 4, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1213 - BURIAL GROUND

Current through Register Vol. 39, No. 2, July 15, 2024
No burial ground shall be established on any watershed
					 within 1,500 feet upstream from a public water supply intake on an unimpounded
					 stream or within 300 feet of any class I or class II
					 reservoir.
Authority
					 G.S.
					 130A-315;
					 130A-320;
					 P.L.
					 93-523;
Eff. January 1,
					 1977;
Readopted Eff. December 5, 1977;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1308 Eff. April 4, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1200 - PROTECTION OF FILTERED WATER SUPPLIES › Section 18C .1214 - DISPOSAL OF ANY SUBSTANCE

Current through Register Vol. 39, No. 2, July 15, 2024
Any person who intends to dispose of or store any substance
					 that may adversely affect the quality of the water, to the point of rendering
					 the water unsuitable as a source for a public water system, shall notify the
					 Division prior to disposal or storage. The notification shall be in writing and
					 shall list any substances that will be disposed of or stored. No substances
					 shall be disposed of or stored without the Division's approval. The owner of
					 the water supply shall be responsible for maintaining surveillance of the
					 reservoirs and watersheds to insure protection of the water quality and shall
					 notify the Department of any activities that may endanger water
					 quality.
Authority
					 G.S.
					 130A-315;
					 130A-320;
					 P.L.
					 93-523;
Eff. January 1,
					 1977;
Readopted Eff. December 5, 1977;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1310 Eff. April 4, 1990;
Amended Eff. September 1, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1300 - OPERATION OF PUBLIC WATER SUPPLIES › Section 18C .1301 - GENERAL REQUIREMENTS

Current through Register Vol. 39, No. 2, July 15, 2024
(a) For the
				  purposes of this Section,
(1) A "facility" is
				  defined as any individual operational unit or a combination of operational
				  units that a public water system uses in the treatment or distribution of
				  drinking water.
(2) Any "operator"
				  referenced in this Section shall hold a valid certificate issued by the North
				  Carolina Water Treatment Facility Operators Certification Board. An "Operator
				  in Responsible Charge (ORC)" designated for each facility shall hold a grade of
				  certification corresponding to or higher than the classification of the
				  facility.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1300 - OPERATION OF PUBLIC WATER SUPPLIES › Section 18C .1304 - WATER SYSTEM OPERATION AND MAINTENANCE

Current through Register Vol. 39, No. 2, July 15, 2024
(a) Water
				  systems shall be operated and maintained in accordance with applicable approved
				  engineering plans and specifications, Water System Management Plan and
				  Operation and Maintenance Plan.
(b)
				  Water systems shall be operated and maintained in accordance with
				  15A NCAC
				  18D, Rules Governing Water Treatment Facility
				  Operators, Rule .0206 and
				  G.S.
				  90A-29.
Authority
					 G.S.
					 90A-29;
					 130A-315;
					 P.L.
					 93-523;
Temporary Adoption Eff.
					 October 1, 1999;
Eff. August 1, 2000;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1300 - OPERATION OF PUBLIC WATER SUPPLIES › Section 18C .1305 - SOURCE WATER PROTECTION PLANNING

Current through Register Vol. 39, No. 2, July 15, 2024
(a) In
				  compliance with
				  G.S.
				  130A-320, every supplier of water operating a
				  public water system treating and furnishing water from a surface water source
				  shall create and implement a Source Water Protection Plan. For purposes of this
				  Rule, the Source Water Protection Plan required by
				  G.S.
				  130A-320 shall be referred to as a Source
				  Water Resiliency and Response Plan (SWRRP).
(b) The SWRRP shall include a list of
				  potential contaminant sources (PCSs) that have potential to reach surface
				  waters, both provided by the Department and supplemented by the water system if
				  additional PCSs are known to exist by the supplier of water. The listed PCSs
				  will be located in the following areas as defined in Classifications and Water
				  Quality Standards Applicable to Surface Waters and Wetlands of North Carolina,
				  15A NCAC
				  02B .0200, which is hereby incorporated by
				  reference, including subsequent amendments and editions:
(1) within the entire watershed for waters
				  classified as WS-I;
(2) within the
				  critical area and 1,000 feet from perennial streambanks within the protected
				  area for waters classified as WS-II and WS-III;
(3) within the critical area and 1,000 feet
				  from perennial streambanks within the protected area for waters classified as
				  WS-IV;
(4) within ½ mile
				  from the normal pool elevation in which the intake is located, or to the ridge
				  line of the watershed, whichever comes first, for a reservoir within waters
				  classified as WS-V; and
(5) within
				  ½ mile, measured as a straight line, upstream from and draining to the
				  intake located directly in the stream or river, or to the ridge line of the
				  watershed, whichever comes first, for a direct-stream intake within waters
				  classified as WS-V.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1401 - POLICY

Current through Register Vol. 39, No. 2, July 15, 2024
Upon receipt of an application from a community water
					 system to fluoridate its water supply, the Department will approve the
					 application provided the rules for fluoridation pursuant to this Section are
					 followed.
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Readopted Eff. December 5, 1977;
Amended Eff.
					 September 1, 1990; September 1, 1979;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1402 - FORMAL APPLICATION

Current through Register Vol. 39, No. 2, July 15, 2024
(a) Fluoride shall
				  not be added to a community water system until a formal application has been
				  submitted to and written approval is granted by the Secretary of the
				  Department.
(b) Such approval will
				  be considered upon written application and after adequate investigation has
				  been made to determine if the policy adopted by the Division has been satisfied
				  and the facilities, their accuracy and the proposed method of control are
				  satisfactory and meet the requirements hereafter stated.
(c) The application shall include a
				  resolution by the unit of local government or the governing body operating the
				  community water system. The resolution shall state that the local board of
				  health has approved the proposed fluoridation procedure.
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Readopted Eff. December 5, 1977;
Amended Eff.
					 July 1, 1993; September 1, 1990; September 1, 1979;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1403 - REPEALED - RESOLUTION

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Readopted Eff. December 5, 1977;
Repealed Eff.
					 July 1, 1990 in accordance with
					 G.S.
					 150B-59(c).
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1404 - FEEDING EQUIPMENT

Current through Register Vol. 39, No. 2, July 15, 2024
Accurate feeding equipment shall be provided for applying
					 fluoride. Either gravimetric or volumetric dry-feed equipment or positive
					 displacement liquid-feed equipment with accuracy within five percent shall be
					 required.
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Readopted Eff. December 5, 1977;
Amended Eff.
					 September 1, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1405 - PROTECTION OF OPERATORS

Current through Register Vol. 39, No. 2, July 15, 2024
(a) Special
				  precautions shall be taken to protect the operators from inhaling fluoride dust
				  when handling this chemical and while charging the hoppers of the
				  feeders.
(b) Dry feeders shall be
				  equipped with dust collectors consisting of bag filters operating under
				  positive air pressure and vented to the outside air.
(c) Each operator who handles fluoride shall
				  be provided with his individual toxic dust respirator to be used only when
				  handling the chemical.
(d) When
				  liquid or solution feed equipment is used, special precautions against
				  siphonage and improper chemical mixing must be provided after consultation with
				  and approval by the Department.
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Readopted Eff. December 5, 1977;
Amended Eff.
					 September 1, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1406 - CONTROL OF FLUORIDE PROCESS

Current through Register Vol. 39, No. 2, July 15, 2024
(a)
				  Fluoride Levels. Fluoride levels shall not exceed the MCL set forth in Rule
				  .1510 of this Subchapter. A supplier of water that is adding fluoride to the
				  treated water shall maintain the following fluoride levels:
(1) an operational control range for fluoride
				  of 0.6 mg/l to 1.0 mg/l shall be established;
(2) the monthly average of the daily
				  measurements at the entry point to the distribution system shall be within the
				  operational control range; and
(3)
				  80 percent of the daily measurements at the entry point to the distribution
				  system shall be within the operational control range.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1407 - APPROVAL MAY BE RESCINDED

Current through Register Vol. 39, No. 2, July 15, 2024
Failure to thoroughly and effectively carry out the
					 requirements governing the application of fluoride, or for other good cause,
					 shall be considered sufficient cause to rescind the approval of the Department
					 and to withdraw the authorization granted for the permission to add fluoride to
					 a community water system.
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Readopted Eff. December 5, 1977;
Amended Eff.
					 September 1, 1990; September 1, 1979;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1408 - REPEALED - SEVERABILITY

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Readopted Eff. December 5, 1977;
Repealed Eff.
					 July 1, 1990 in accordance with
					 G.S.
					 150B-59(c).
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1400 - FLUORIDATION OF PUBLIC WATER SUPPLIES › Section 18C .1409 - REPEALED - REFERENCE RULES

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-316;
Eff. February 1,
					 1976;
Amended Eff. January 1, 1977;
Readopted Eff.
					 December 5, 1977;
Amended Eff. December 17, 1979;
Repealed Eff. September 1, 1990.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1501 - REPEALED - PURPOSE

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Transferred and Recodified from
					 10 NCAC
					 10D .1610 Eff. April 4, 1990;
Repealed Eff. September 1, 1990.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1502 - MONITORING OF CONSECUTIVE PUBLIC WATER SYSTEMS

Current through Register Vol. 39, No. 2, July 15, 2024
(a) When
				  a public water system supplies water to one or more other public water systems
				  the Department may modify the monitoring requirements imposed by this Section
				  to the extent that the interconnection of the systems justifies treating them
				  as a single system for monitoring purposes. Any modified monitoring shall be
				  conducted pursuant to a schedule specified by the Department and concurred in
				  by the Administrator of the U.S. Environmental Protection Agency.
(b) All public water systems which purchase
				  water for resale and which do not provide any treatment except booster
				  chlorination will be required to perform bacteriological monitoring in
				  accordance with Rule .1534 of this Section.
(c) The Department may exempt a public water
				  system that obtains treated water from another public water system serving more
				  than 10,000 persons from conducting compliance monitoring for the organic
				  chemicals under
				  15A NCAC
				  18C .1518(a), provided that
				  the system from which the water is obtained has conducted the analyses required
				  under 15A NCAC 18C
				  .1518(a). Exempted public water
				  systems which disinfect are required to monitor under
				  15A NCAC
				  18C .1516.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. June 1, 1988;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1628 Eff. April 4, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1503-1504

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. March 1, 1989; December 1, 1988; March 31, 1981;
					 December 19, 1979;
15A NCAC
					 18C .1503 was Transferred and Recodified from
					 10 NCAC
					 10D .1622
Eff. April 4,
					 1990;
15A NCAC
					 18C .1504 was Transferred and Recodified from
					 10 NCAC
					 10D .1613
Eff. April 4,
					 1990;
Amended Eff. September 1, 1990;
Repealed Eff.
					 January 1, 1991.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1505 - TURBIDITY SAMPLING AND ANALYSIS

Current through Register Vol. 39, No. 2, July 15, 2024
The requirements of this Rule shall apply only to public
					 water systems that use water obtained in whole or in part from surface sources.
					 The provisions of 40 C.F.R.
					 141.22 are hereby incorporated by reference
					 including any subsequent amendments and editions. Copies are available for
					 public inspection as set forth in Rule .0102 of this Subchapter. Any dates set
					 forth in the federal rule shall be applicable.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. March 31, 1981; December 19, 1979;
Transferred and Recodified from
					 10 NCAC
					 10D .1623 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; January 1, 1991; September 1,
					 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1506 - MAXIMUM CONTAMINANT LEVELS FOR TURBIDITY

Current through Register Vol. 39, No. 2, July 15, 2024
The requirements of this Rule shall apply to public water
					 systems that use water obtained in whole or in part from surface water sources.
					 The provisions of 40 C.F.R.
					 141.13 are hereby incorporated by reference
					 including any subsequent amendments and editions. Copies are available for
					 public inspection as set forth in Rule .0102 of this Subchapter. Any dates set
					 forth in the federal rule shall be applicable.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Transferred and Recodified from
					 10 NCAC
					 10D .1614 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; January 1, 1991; September 1,
					 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1507 - CORROSION CONTROL AND LEAD AND COPPER MONITORING

Current through Register Vol. 39, No. 2, July 15, 2024
(a)
				  Control and adjustment of pH shall be provided for community water systems
				  having water with a pH below 6.5. This control and adjustment shall be approved
				  by the Department pursuant to the rules in Section .0300 of this Subchapter. If
				  the community water system is also required to install corrosion control
				  treatment to comply with (c) of this Rule, it shall meet the minimum pH level
				  required pursuant to Paragraph (c) of this Rule.
(b) The provisions of
				  40 C.F.R.
				  141.42 are incorporated by reference,
				  including subsequent amendments and editions. Copies may be obtained as set
				  forth in Rule .0102(b) of this Subchapter.
(c) The provisions of
				  40 C.F.R.
				  141, Subpart I - Control of Lead and Copper
				  are incorporated by reference, including subsequent amendments and editions.
				  Copies may be obtained as set forth in Rule .0102(b) of this
				  Subchapter.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. October 1, 1982; February 27, 1982;
Transferred and Recodified from
					 10 NCAC
					 10D .1621 Eff. April 4, 1990;
Amended Eff. April 1, 2014; July 1, 1994; October 1, 1992; December 1,
					 1991;
Readopted Eff. July 1,
					 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1508 - INORGANIC CHEMICAL SAMPLING AND ANALYSIS

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.23 are incorporated by reference,
					 including subsequent amendments and editions. Copies may be obtained as set
					 forth in Rule .0102(b) of this Subchapter. In addition, two or more water
					 systems that are adjacent, that are owned or operated by the same supplier of
					 water, and that together serve 15 or more service connections or 25 or more
					 persons shall submit samples every three years from each section of the water
					 system that is supplied from a separate source.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. March 1, 1989; February 1, 1987; October 1,
					 1986; April 1, 1983;
Transferred and Recodified from
					 10 NCAC
					 10D .1625 Eff. April 4, 1990;
Amended Eff. April 1, 2014; July 1, 1994; April 1, 1992; December 1,
					 1991;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23, 2015;
Amended Eff.
					 July 1, 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1509 - SPECIAL MONITORING FOR SODIUM

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.41 are incorporated by reference,
					 including subsequent amendments and editions. Copies may be obtained as set
					 forth in Rule .0102(a) and (b) of this Subchapter.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. February 27,
					 1982;
Transferred and Recodified from
					 10 NCAC
					 10D .1636 Eff. April 4, 1990;
Amended Eff. April 1, 2014; July 1, 1994; September 1, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23, 2015;
Amended Eff.
					 July 1, 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1510 - MAXIMUM CONTAMINANT LEVELS FOR INORGANIC CHEMICALS

Current through Register Vol. 39, No. 2, July 15, 2024
(a) The provisions of
				  40 C.F.R.
				  141.11 are hereby incorporated by reference
				  including any subsequent amendments and editions, except the maximum
				  contaminant level for arsenic shall be regulated as set forth in Paragraph (c)
				  of this Rule. Copies are available for public inspection as set forth in Rule
				  .0102 of this Subchapter.
(b) The
				  provisions of 40 C.F.R.
				  141.62 are hereby incorporated by reference
				  including any subsequent amendments and editions. Copies are available for
				  public inspection as set forth in Rule .0102 of this Subchapter.
(c) Effective January 1, 2002, the maximum
				  contaminant level for arsenic applies to community and non-transient
				  non-community water systems are as follows:
(1) The maximum contaminant level for arsenic
				  is 0.010 milligrams per liter, until such time as the USEPA revises the
				  standard to a level lower than 0.010 milligrams per liter at which time the
				  more stringent level shall apply.
(2) Sampling, analytical requirements, and
				  compliance calculations for arsenic shall be conducted as specified for
				  contaminants in Rule .1508 of this Subchapter.
(3) Certified laboratories must report
				  quantifiable results down to at least 0.005 milligrams per liter.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1511 - CONCENTRATION OF IRON

Current through Register Vol. 39, No. 2, July 15, 2024
The requirements of this Rule shall apply only to community
					 water systems. A community water system that has an iron concentration in
					 excess of 0.30 mg/l shall provide treatment to control the water quality.
					 Analysis of samples shall be made on an as needed basis determined by the
					 Department and shall include the addition of a new well or other raw water
					 source, an approval of a new community water system, an approval of an existing
					 system not previously approved, or problems and complaints of water quality
					 normally associated with iron concentration.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Transferred and Recodified from
					 10 NCAC
					 10D .1619 Eff. April 4, 1990;
Amended Eff. July 1, 1994;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23, 2015;
Amended Eff.
					 July 1, 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1512 - CONCENTRATION OF MANGANESE

Current through Register Vol. 39, No. 2, July 15, 2024
The requirements of this Rule shall apply only to community
					 water systems. A community water system that has a manganese concentration in
					 excess of 0.05 mg/l shall provide treatment to control the water quality.
					 Analysis of samples shall be made on an as needed basis determined by the
					 Department and shall include the addition of a new well or other raw water
					 source, an approval of a new community water system, an approval of an existing
					 system not previously approved, or problems and complaints of water quality
					 normally associated with manganese concentration.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. September 9, 1980;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1620 Eff. April 4, 1990;
Amended Eff. July 1, 1994;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23, 2015;
Amended Eff.
					 November 1, 2020; July 1, 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1513 - EXPIRED - TOTAL TRIHALOMETHANES SAMPLING AND ANALYSIS: 10,000 OR MORE

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 CFR
					 141;
Eff. September 30,
					 1980;
Amended Eff. April 1, 1983;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1635 Eff. April 4, 1990;
Amended Eff. August 1, 2000; August 1, 1990;
Expired Eff. December
					 1, 2015 pursuant to
					 G.S.
					 150B-21.3A.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1514 - EXPIRED - TREATMENT TECHNIQUES FOR TOTAL TRIHALOMETHANES

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-315;
					 P. L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. October 1,
					 1983;
Transferred and Recodified from
					 10 NCAC
					 10D .1637 Eff. April 4, 1990;
Amended Eff. August 1, 1990;
Expired Eff. December 1, 2015 pursuant
					 to G.S.
					 150B-21.3A.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1515 - ORGANIC CHEMICALS OTHER THAN TTHM, SAMPLING AND ANALYSIS

Current through Register Vol. 39, No. 2, July 15, 2024
(a) The requirements of this Rule shall apply
				  to community and non-transient non-community water systems. The provisions of
				  40 C.F.R.
				  141.24 are incorporated by reference,
				  including subsequent amendments and editions. Copies may be obtained as set
				  forth in Rule .0102(b) of this Subchapter.
(b) If the result of an analysis made
				  pursuant to Paragraph (a) of this Rule indicates that the level of any
				  contaminant regulated under this Subchapter exceeds the maximum contaminant
				  level, the supplier of water shall report to the Department within 48 hours of
				  receipt of the analytical result.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. November 1, 1989; December 1, 1988; June 1,
					 1988; October 1, 1982;
Transferred and Recodified from
					 10 NCAC
					 10D .1624 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; April 1, 1992; December 1, 1991;
					 September 1, 1990;
Readopted Eff. July 1,
					 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1516 - SPECIAL MONITORING FOR UNREGULATED CONTAMINANTS

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.40 are incorporated by reference
					 including subsequent amendments and editions. Copies are available for public
					 inspection as set forth in Rule .0102(b) of this Subchapter.
Authority
					 G.S.
					 130A-313;
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. June 1,
					 1988;
Amended Eff. November 1, 1989;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1638 Eff. April 4, 1990;
Amended Eff. April 1, 2014; July 1, 1994; April 1, 1992; December 1, 1991;
					 August 1, 1990;
Readopted Eff. July 1,
					 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1517 - EXPIRED - MAXIMUM CONTAMINANT LEVELS FOR ORGANIC CHEMICALS

Current through Register Vol. 39, No. 2, July 15, 2024
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. September 30, 1980;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1615 Eff. April 4, 1990;
Amended Eff. April 1, 2014; April 1, 1992; August 1, 1990;
Expired
					 Eff. December 1, 2015 pursuant to
					 G.S.
					 150B-21.3A.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1518 - MAXIMUM CONTAMINANT LEVELS FOR ORGANIC CONTAMINANTS

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.61 are hereby incorporated by reference
					 including any subsequent amendments and editions. Copies are available for
					 public inspection as set forth in Rule .0102 of this
					 Subchapter.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. June 1,
					 1988;
Transferred and Recodified from
					 10 NCAC
					 10D .1639 Eff. April 4, 1990;
Amended Eff. April 1, 2014; April 1, 1992;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1519 - MONITORING FREQUENCY FOR RADIOACTIVITY

Current through Register Vol. 39, No. 2, July 15, 2024
The requirements of this Rule shall apply to community
					 water systems and community adjacent water systems, as defined in
					 G.S.
					 130A-315(b2). The provisions
					 of 40 C.F.R.
					 141.26 are incorporated by reference,
					 including subsequent amendments and editions. Copies may be obtained as set
					 forth in Rule .0102(b) of this Subchapter.
Authority
					 G.S.
					 130A-313;
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. March 1, 1989; September 9, 1980; December 19,
					 1979;
Transferred and Recodified from
					 10 NCAC
					 10D .1627 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; July 1, 1994;
Pursuant
					 to G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23, 2015;
Amended Eff.
					 July 1, 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1520 - MAXIMUM CONTAMINANT LEVELS FOR RADIONUCLIDES

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.66 are hereby incorporated by reference
					 including any subsequent amendments and editions. Copies are available for
					 public inspection as set forth in Rule .0102 of this
					 Subchapter.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Transferred and Recodified from
					 10 NCAC
					 10D .1617 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; July 1, 1994;
Pursuant
					 to G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1521 - MAXIMUM CONTAMINANT LEVEL GOALS FOR RADIONUCLIDES

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.55 are hereby incorporated by reference
					 including any subsequent amendments and editions. Copies are available for
					 public inspection as set forth in Rule .0102 of this
					 Subchapter.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Transferred and Recodified from
					 10 NCAC
					 10D .1618 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; July 1, 1994;
Pursuant
					 to G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1522 - ANALYTICAL METHODS FOR RADIOACTIVITY

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.25 are hereby incorporated by reference
					 including any subsequent amendments and editions. Copies are available for
					 public inspection as set forth in Rule .0102 of this
					 Subchapter.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. September 1,
					 1979;
Amended Eff. March 31, 1981; March 31, 1980;
Transferred and Recodified from
					 10 NCAC
					 10D .1626 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; September 1, 1990;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23,
					 2015.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1523 - PUBLIC NOTIFICATION REQUIREMENTS

Current through Register Vol. 39, No. 2, July 15, 2024
(a) The
				  provisions of 40 C.F.R.
				  141, Subpart Q - Public Notification of
				  Drinking Water Violations are incorporated by reference, including subsequent
				  amendments and editions. As authorized by
				  40 C.F.R.
				  141.205(c)(2), the
				  Department has determined that multi-lingual notice shall be given if 30
				  percent or more of the consumers served by the system are non-English speaking.
				  Copies may be obtained as set forth in Rule .0102(b) of this
				  Subchapter.
(b) Special
				  notification for distribution system samples. The requirements of this
				  Paragraph shall be in addition to the public notice requirements set forth in
				  Paragraph (a) of this Rule and to the reporting requirements contained in Rule
				  .1525 of this Subchapter. If a distribution sample that is required to be
				  reported to the Division is taken from the plumbing of a school or daycare,
				  place of residence, or location supplying permanent or temporary housing, the
				  supplier of water shall notify the billing customer at the sampled address if
				  any individual water sample exceeds an action level, maximum contaminant level,
				  or maximum residual disinfectant level established in this Subchapter or if any
				  individual sample is positive for E. coli or any other fecal indicator, as
				  follows:
(1) For a contaminant listed as Tier
				  1 in Appendix A to 40 C.F.R.
				  141, Subpart Q, notice shall be provided
				  within 24 hours of receipt of analytical results. If the initial contact is by
				  telephone, written notice by mail or direct delivery shall also be provided
				  within 48 hours of analytical results. The written notice shall include the
				  analytical results and appropriate health effects language as required by
				  Appendix B to 40 C.F.R.
				  141, Subpart Q.
(2) For a contaminant listed as Tier 2 or
				  Tier 3 in Appendix A to 40
				  C.F.R. 141, Subpart Q, notice shall be
				  provided within 48 hours of receipt of analytical results. Written notice shall
				  be provided by mail or direct delivery and shall include the analytical results
				  and appropriate health effects language as required by Appendix B to
				  40 C.F.R.
				  141, Subpart Q.
(3) The supplier of water shall submit a copy
				  of the written notice and certification of delivery to the Department within 10
				  days of completing notification.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1524 - REPORTING FOR UNREGULATED CONTAMINANT MONITORING RESULTS

Current through Register Vol. 39, No. 2, July 15, 2024
The provisions of
					 40 C.F.R.
					 141.35 are incorporated by reference,
					 including subsequent amendments and editions. Copies may be obtained as set
					 forth in Rule .0102(b) of this Subchapter.
Authority
					 G.S.
					 130A-315;
					 P.L.
					 93-523;
					 40 C.F.R.
					 141;
Eff. June 1,
					 1988;
Amended Eff. November 1, 1989;
Transferred and
					 Recodified from
					 10 NCAC
					 10D .1640 Eff. April 4, 1990;
Readopted Eff. July 1, 2019.
North Carolina Administrative Code › Title 15A - Environmental Quality › Chapter 18 - ENVIRONMENTAL HEALTH › Subchapter C - WATER SUPPLIES › Section .1500 - WATER QUALITY STANDARDS › Section 18C .1525 - REPORTING REQUIREMENTS

Current through Register Vol. 39, No. 2, July 15, 2024
(a) The
				  requirements of this Rule shall apply to all public water systems. The
				  provisions of 40 C.F.R.
				  141.31 are incorporated by reference,
				  including subsequent amendments and editions. Copies may be obtained as set
				  forth in Rule .0102(b) of this Subchapter. Any dates set forth in the federal
				  rule shall be applicable.
(b) If a
				  certified laboratory analyzes a compliance sample for a supplier of water, the
				  certified laboratory shall report the results to both the Department and to the
				  supplier of water or his or her designated representative within the periods
				  set forth in 40 C.F.R.
				  141.31, except that electronic reporting
				  conducted in accordance with 40 C.F.R.
				  141.31(a) shall be completed
				  within seven days of completion of the analysis. The laboratory reporting to
				  the Department shall include analytical results for any maximum contaminant
				  level exceedance within the timeframes applicable to the system owner.
				  Reporting shall be in a format, including electronic reporting, established by
				  the Department and shall be filled out completely. If a certified laboratory
				  fails to report compliance sample results in accordance with this Paragraph,
				  the supplier of water shall report results to the Department as required by
				  this Rule.
Authority
					 G.S.
					 130A-315;
					 130A-324;
					 130A-329;
					 40 C.F.R
					 141;
Eff. September 1,
					 1979;
Amended Eff. February 1, 1987; October 1, 1984; March 31,
					 1981; March 31, 1980;
Transferred and Recodified from
					 10 NCAC
					 10D .1631 Eff. April 4, 1990;
Amended Eff. April 1, 2014; August 1, 2002; January 1, 1991;
Pursuant to
					 G.S.
					 150B-21.3A, rule is necessary without
					 substantive public interest Eff. November 23, 2015;
Amended Eff.
					 July 1, 2019.