reglab/statecodes huggingface dataset:
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 110 - GENERAL OPERATING REQUIREMENTS FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.110.1016 - REPORTING

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of a storage tank system shall
				  cooperate fully with inspections, monitoring and testing conducted by the
				  department, as well as requests for document submission, testing, and
				  monitoring by the owner or operator.
A. Owners and operators shall provide the
				following information to the department:
(1)
				registration for all storage tank systems in accordance with 20.5.102 NMAC,
				which includes certification of installation for new AST systems in accordance
				with Subsection C of 20.5.109.919 NMAC;
(2) reports of all releases in accordance
				with 20.5.102 NMAC and the requirements in 20.5.18 NMAC for reporting suspected
				releases, spills and overfills and confirmed releases;
(3) corrective actions planned or taken as
				required by 20.5.119 NMAC and 20.5.200 NMAC;
(4) notification before storage tank system
				installation, replacement, repair or modification in accordance with 20.5.109
				NMAC and 20.5.110 NMAC; notification when any person assumes ownership of a
				storage tank system in accordance with 20.5.102 NMAC and notification before
				permanent closure or change in service in accordance with 20.5.115 NMAC; it may
				not be feasible for owners and operators to provide advance notice of emergency
				repairs; however, owners and operators shall provide notice of emergency
				repairs as soon as possible after completing emergency repairs;
(5) notification prior to storage tank
				systems changing to certain regulated substances in accordance with Subsection
				A of 20.5.110.1009 NMAC; and
(6)
				updated project drawings for any addition, replacement or modification of a
				storage tank system.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
This part applies to owners and operators of above ground
				  storage tanks as provided in 20.5.101 NMAC. If the owner and operator of a
				  storage tank are separate persons, only one person is required to comply with
				  the requirements of this part, including any notice and reporting requirements;
				  however, both parties are liable in the event of noncompliance. Release
				  detection requirements for above ground storage tank emergency generator
				  systems are listed in 20.5.112 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
This part is promulgated pursuant to the provisions of the
				  Hazardous Waste Act, Sections
				  74-4-1
				  through
				  74-4-14
				  NMSA 1978, and the general provisions of the Environmental Improvement Act,
				  Sections
				  74-1-1
				  through
				  74-1-17
				  NMSA 1978.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.5 - EFFECTIVE DATE

Current through Register Vol. 35, No. 13, July 16, 2024
July 24, 2018, unless a later date is indicated in the
				  bracketed history note at the end of a section.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The purpose of 20.5.111 NMAC is to ensure that releases from
				  above ground storage tanks are detected early to minimize potential harmful
				  resulting effects, and to regulate storage tank systems in order to protect the
				  public health, safety and welfare and the environment of the
				  state.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.7 - DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
The definitions in 20.5.101 NMAC apply to this
				  part.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1100 - REQUIREMENTS AND DEADLINES FOR RELEASE DETECTION FOR AST SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and
				operators of new and existing AST systems shall monitor monthly for releases
				using a method, or combination of methods, of release detection that can detect
				a release from any portion of the tank, connected piping and ancillary
				equipment that routinely contains a regulated substance and meets the
				following:
(1) the method:
(a) meets the performance requirements in
				20.5.111 NMAC;
(b) is installed and
				calibrated in accordance with the manufacturer's instructions;
(c) is operated and maintained in accordance
				with one of the following, beginning on the effective date of these
				regulations:
(i) manufacturer's
				instructions;
(ii) the current
				edition of an industry standard or code of practice developed by a nationally
				recognized association or independent testing laboratory approved in advance by
				the department; or
(iii) an
				approved method that has been determined by the implementing agency to be no
				less protective of human health and the environment than Subparagraph (a) and
				(b) of Subsection (1) above; and
(d) has electronic and mechanical components
				that are tested to ensure proper operation; or
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1101 - REQUIREMENTS FOR INTEGRITY TESTING OR TANK TIGHTNESS TESTING OF ASTS

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and
				operators shall perform a tightness test or internal inspection of ASTs 10
				years after installation, unless the AST is in secondary containment that
				complies with the requirements of 20.5.109 NMAC. Owners or operators shall use
				one or more of the standards and codes listed in Subsection A of this section,
				as applicable, to comply with this requirement.
B. Owners and operators of ASTs shall ensure
				that integrity testing and tank tightness testing:
(1) detect a two-tenth gallon per hour leak
				rate from any portion of the AST that routinely contains a regulated substance
				while accounting for the effects of thermal expansion or contraction of the
				regulated substance, vapor pockets, tank deformation, and evaporation or
				condensation;
(2) comply with
				manufacturer's published testing procedures; and
(3) comply with a current edition of an
				industry standard or code of practice developed by a nationally recognized
				association or independent testing laboratory, and shall be approved in advance
				by the department. Owners and operators shall use one or more of following to
				comply with the requirements of this section:
(a)
American Petroleum Institute
				Specification 12F: "Specification for Shop Welded Tanks for Storage of
				Production Liquids"
.
(b)
American Petroleum Institute Standard 650, "Welded Tanks for Oil
				Storage"
, with applicable addenda;
(c)
American Petroleum Institute
				Standard 653, "Tank Inspection, Repair, Alteration, and
				Reconstruction"
;
(d)
Petroleum Equipment Institute RP200, "Recommended Practices for
				Installation of Aboveground Storage Systems for Motor Vehicle
				Fueling"
;
(e)
Underwriter's Laboratories Standards: UL 142, "Standard for Steel
				Aboveground Tanks for Flammable and Combustible Liquids";
(f)
Steel Tank Institute Standard
				SP001, "Standard for the Inspection of Aboveground Storage Tanks"
;
				or
(g)
National Fire
				Protection Association Standard 30, "Flammable and Combustible Liquids
				Code"
.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1102 - VISUAL INSPECTION REQUIREMENTS FOR ASTS

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and operators of ASTs may use
				visual inspection as a method of release detection if:
(1) all portions of the ASTs, including the
				AST bottoms, are completely visible, readily accessible and are inspected
				monthly;
(2) owners and operators
				maintain a written log of the visual inspections for each AST conducted monthly
				to include the following:
(a) the date and
				time the inspection was conducted;
(b) name and signature of the person who
				conducted the inspection;
(c)
				comments on the condition of each AST;
(d) the results of each inspection;
				and
(e) the volume of water found
				in the AST and if the water has been removed from the tank; and
(3) owners and operators keep
				visual inspection logs available at the facility.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1103 - INTERSTITIAL MONITORING REQUIREMENTS FOR ASTS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of ASTs may use interstitial monitoring
				  to continuously monitor between the AST and a secondary barrier immediately
				  around and underneath the tank, but only if the AST system meets all of the
				  following requirements:
A. the ASTs
				are manufactured or upgraded to include a double-walled bottom in accordance
				with the current edition of an industry standard or code of practice developed
				by a nationally recognized association or independent testing laboratory which
				can be remotely monitored, or the ASTs are installed inside secondary
				containment with an impervious barrier beneath the ASTs meeting the
				requirements of 20.5.109.904 NMAC and the interstice between them can be
				remotely monitored;
B. the
				monitoring system between the AST and the secondary barrier shall meet all of
				the following requirements;
(1) for
				cathodically protected ASTs, the secondary barrier shall be installed so that
				it does not interfere with the proper operation of the cathodic protection
				system;
(2) the groundwater, soil
				moisture, or rainfall will not render the testing or sampling method used
				inoperative so that a release could go undetected for more than 30
				days;
(3) the site is assessed to
				ensure that the secondary barrier is always above the groundwater and not in a
				25-year flood plain, unless the barrier and monitoring designs are for use
				under such conditions;
(4) the
				locations and ports of monitoring wells are clearly marked and secured to avoid
				unauthorized access and tampering;
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1104 - AUTOMATIC TANK GAUGING REQUIREMENTS FOR ASTS

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and operators shall use automatic
				tank gauging systems that are third party certified for the size and capacity
				of the AST. Only third-party certifications that have been reviewed and
				approved by the national work group on leak detection evaluations (NWGLDE) for
				AST use, as evidenced by their posting on the NWGLDE website, nwgle.org, will
				be accepted.
B. Owners and
				operators of ASTs may use automatic tank gauging as a method of release
				detection, every 30 days, if the automatic tank gauging system:
(1) tests for the loss of product and can
				detect a two-tenth gallon per hour leak rate from any portion of the tank that
				routinely contains regulated substances; and
(2) can conduct inventory control or another
				test of equivalent performance in accordance with all of the following:
(a) inventory volume measurements for
				regulated substance inputs, withdrawals, and the amount still remaining in the
				AST are recorded each operating day;
(b) the equipment used is capable of
				measuring the level of regulated substance over the full range of the AST's
				height to the nearest one-eighth of an inch;
(c) the regulated substance inputs are
				reconciled with delivery receipts by measurement of the AST inventory volume
				before and after delivery;
(d)
				deliveries are made through a drop tube that extends to within one foot of the
				AST bottom, unless the AST is bottom loaded;
(e) regulated substance dispensing is metered
				and recorded within the state standards for meter calibration or an accuracy of
				six cubic inches for every five gallons of regulated substance
				withdrawn;
(f) the measurement of
				any water level in the bottom of the AST is made to the nearest one-eighth of
				an inch at least once a month; and
(g) practices described in the
American Petroleum Institute Publication RP1621, "Bulk Liquid Stock
				Control at Retail Outlets"
may be used, where applicable, as guidance
				in meeting the requirements of this section.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1105 - REQUIREMENTS FOR AST UNDERGROUND PRESSURIZED PIPING INSTALLED PRIOR TO JULY 24, 2018

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of above ground storage tank systems
				  with underground pressurized piping installed prior to the effective date of
				  these regulations must have implemented a method, or a combination of methods,
				  of release detection for the piping. The monitoring method, or combination of
				  methods, shall follow the current edition of an industry standard or code of
				  practice developed by a nationally recognized association or independent
				  testing laboratory approved in advance by the department.
A. Owners and operators of AST systems shall:
(1) use automatic line leak detectors
				(including mechanical or electronic detectors) that alert the operator to the
				presence of a leak by restricting or shutting off the flow of regulated
				substances through piping when a leak is detected at three gallons per hour at
				10 pounds per square inch line pressure within one hour;
(2) perform an annual test of the operation
				of the leak detector which includes a simulated leak, is conducted in
				accordance with the manufacturer's testing protocol, and confirms the automatic
				line leak detector detects a leak at three gallons per hour at 10 pounds per
				square inch line pressure within one hour; and and
(3) use a method, or combination of methods,
				for monitoring the piping for releases that complies with one of the following:
(a) a precision line tightness test is
				conducted every 12 months that is capable of detecting a leak of one-tenth
				gallons per hour at one and one-half times the operating pressure; or
(b) use interstitial monitoring that complies
				with all of the requirements in 20.5.111.1103 NMAC, 20.5.111.1106 NMAC, and all
				of the following:
(i) shall automatically
				shut off the submersible turbine pump for the AST if the sensors used for
				interstitial monitoring detect regulated substances or water within the
				interstice or in the containment sumps associated with the piping;
				and
(ii) all sensors shall be
				tested annually in accordance with Subsection C of 20.5.11.1104 NMAC;
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1106 - REQUIREMENTS FOR AST UNDERGROUND PRESSURIZED PIPING INSTALLED OR MODIFIED ON, OR AFTER JULY 24, 2018

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of above ground storage tank systems
				  with underground pressurized piping installed or modified on, or after the
				  effective date of these regulations shall use interstitial monitoring as the
				  method of release detection for the piping. The interstitial monitoring method
				  shall follow the current edition of an industry standard or code of practice
				  developed by a nationally recognized association or independent testing
				  laboratory approved in advance by the department.
A. Owners and operators of AST systems shall:
(1) use automatic line leak detectors
				(including mechanical or electronic detectors) that alert the operator to the
				presence of a leak by restricting or shutting off the flow of regulated
				substances through piping when a leak is detected at three gallons per hour at
				10 pounds per square inch line pressure within one hour;
(2) perform an annual test of the operation
				of the leak detector which includes a simulated leak, is conducted in
				accordance with the manufacturer's testing protocol, and confirms the automatic
				line leak detector detects a leak at three gallons per hour at 10 pounds per
				square inch line pressure within one hour;
(3) use interstitial monitoring that complies
				with all of the requirements in 20.5.111.1103 NMAC and all of the following:
(a) Sensors shall be installed in all
				containment sumps associated with the piping, including under-dispenser
				containment, transition sumps, and submersible turbine pump containment sumps
				used to monitor the interstice;
(b)
				Sensors shall:
(i) monitor the
				interstice;
(ii) monitor all
				containment sumps associated with the piping;
(iii) sound an alarm and automatically shut
				off the submersible turbine pump when a regulated substance or water is
				detected;
(iv) be positioned in the
				lowest point of the containment sump; and
(v) be tested annually in accordance with
				Subsection C of 20.5.111.1104 NMAC;
(c) Containment sumps used for interstitial
				monitoring shall be tested every three years starting three years after the
				effective date of these regulations. The testing of the containment sumps shall
				comply with one of the following:
(i) the
				testing procedures as described in
Petroleum Equipment Institute
				Publication RP 1200, "Recommended Practices for the Testing and Verification of
				Spill, Overfill, Leak Detection and Secondary Containment Equipment at UST
				Facilities"
; or
(ii) the
				equipment manufacturer's published testing procedures.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1107 - REQUIREMENTS FOR AST UNDERGROUND SUCTION PIPING INSTALLED PRIOR TO JULY 24, 2018

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and
				operators of above ground storage tank systems where piping conveys regulated
				substances under suction and was installed prior to the effective date of these
				regulations shall use one of the following methods. These methods shall be
				designed to detect a release from any portion of underground piping:
(1) An annual line tightness test shall be
				conducted and the tightness testing shall be capable of detecting a one-tenth
				gallon per hour leak at one and one-half times the operating pressure;
				or
(2) Interstitial monitoring
				shall be used in accordance with all of the requirements in 20.5.11.1103 NMAC
				and 20.5.11.1105 NMAC;
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1108 - REQUIREMENTS FOR AST UNDERGROUND SUCTION PIPING INSTALLED ON OR AFTER JULY 24, 2018

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and
				operators of above ground storage tank systems where piping conveys regulated
				substances under suction and was installed after the effective date of these
				regulations shall meet the requirements for interstitial monitoring in
				20.5.111.1103 NMAC and the following:
(1)
				Sensors shall be installed in all containment sumps associated with the piping,
				including under-dispenser containment, transition sumps, and secondary
				containment sumps used to monitor the interstice.
(2) Sensors shall:
(a) monitor the interstice;
(b) monitor all containment sumps associated
				with the piping;
(c) sound an alarm
				and automatically shut off the pump when a regulated substance or water is
				detected;
(d) be positioned in the
				lowest point of the containment sump; and
(e) be tested annually in accordance with
				Subsection C of 20.5.111.1104 NMAC.
(3) Containment sumps used for interstitial
				monitoring shall be tested every three years beginning three years after the
				effective date of the regulations. The testing of the containment sumps shall
				comply with one of the following:
(a) the
				testing procedures as described in
Petroleum Equipment Institute
				Publication RP 1200, "Recommended Practices for the Testing and Verification of
				Spill, Overfill, Leak Detection and Secondary Containment Equipment at UST
				Facilities"
; or
(b) the
				equipment manufacturer's published testing procedures.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1109 - REQUIREMENTS FOR AST ABOVE GROUND PIPING

Current through Register Vol. 35, No. 13, July 16, 2024
A. Owners and operators of above ground
				storage tanks with above ground piping that conveys regulated substances either
				by suction or pressure shall monitor for releases every 30 days and may use
				visual inspection if all portions of the piping are completely visible, readily
				accessible, and not in contact with the ground or soil. Owners and operators
				shall keep a log of visual inspection of piping that meets the requirements of
				20.5.111.1102 NMAC.
B. Owners and
				operators of above ground storage tank systems with above ground piping that
				conveys a regulated substance under pressure shall not be required to install
				automatic line leak detectors as long as the entire piping run is above ground
				and a solenoid valve has been installed on the piping at the submersible
				turbine pump. Also, a manually activated control shall be installed that will
				permit the submersible turbine pump to operate only when a dispensing nozzle is
				removed from its bracket or normal position with respect to the dispensing
				device and shall stop the submersible turbine pump when the dispensing nozzle
				is returned to the bracket.
C. For
				piping that does not meet these requirements, owners and operators shall use a
				method, or combination of methods, that meet the requirements in 20.5.111.1105
				NMAC through 20.5.111.1108 NMAC depending on the piping type and when the
				piping was installed or modified.
D. Owners and operators shall use one or more
				of the following to comply with the requirements of this section:
(1)
Petroleum Equipment Institute
				Publication RP 100, "Recommended Practices for Installation of Underground
				Liquid Storage Systems"
;
(2)
Petroleum Equipment Institute RP
				200, "Recommended Practices for Installation of Aboveground Storage Systems for
				Motor Vehicle Fueling"
;
(3)
American Petroleum Institute
				Publication RP 1615, "Installation of Underground Hazardous Substances or
				Petroleum Storage Systems"
;
(4)
American Petroleum Institute 570,
				"Piping Inspection Code: In-Service Inspection, Repair, and Alteration of
				Piping Systems"
;
(5)
American Society of Mechanical Engineering Standard B31.3, "Process
				Piping"
;
(6)
National Fire Protection Association Standard NFPA 110, "Standard for
				Emergency and Standby Power Systems"
; and
(7)
Petroleum Equipment Institute
				Publication RP1400, "Recommended Practices for the Design and Installation of
				Fueling Systems for Emergency Generators, Stationary Diesel Engines, and Oil
				Burner Systems".
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1110 - ALTERNATE METHODS

Current through Register Vol. 35, No. 13, July 16, 2024
A. If owners
				and operators want to install materials or methods of release detection
				equipment for tanks or piping required in 20.5.111 NMAC that are not in
				accordance with the current edition of an industry standard or code of practice
				developed by a nationally recognized association or independent testing
				laboratory, owners and operators shall apply in writing to the department,
				shall provide supporting documentation, and shall not begin the installation
				unless and until the department approves the request in writing. At a minimum,
				the request for an alternate method shall contain the following:
(1) date the form is completed;
(2) facility name, facility ID number,
				address (with county) and telephone number;
(3) owner name, owner ID number, address and
				telephone number;
(4) citation to
				regulation for which alternate method or material (such as type of piping) is
				requested;
(5) brief description of
				the proposed alternate method or material;
(6) justification of proposed alternate
				method or material, including citation to a standard or code supporting its
				use, if available; and
(7)
				demonstration of its equivalent protection of public health, safety and welfare
				and the environment.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 111 - RELEASE DETECTION FOR ABOVE GROUND STORAGE TANK SYSTEMS › Section 20.5.111.1111 - RELEASE DETECTION RECORDKEEPING

Current through Register Vol. 35, No. 13, July 16, 2024
A. All storage tank system owners and
				operators shall maintain records in accordance with 20.5.110 NMAC demonstrating
				compliance with all applicable requirements of 20.5.111 NMAC. If the owner and
				operator of a storage tank are separate persons, only one person is required to
				maintain the records required by this section; however, both parties are liable
				in the event of noncompliance.
B.
				Records to be maintained shall include, but not be limited to:
(1) all written performance claims pertaining
				to any release detection system used, and the manner in which these claims have
				been justified or tested by the equipment manufacturer or installer;
(2) the results of any sampling, testing, or
				monitoring;
(3) written
				documentation of all calibration, maintenance, and repair of release detection
				equipment permanently located on-site and any schedules of calibration and
				maintenance required by the release detection equipment manufacturer;
(4) the results of annual operational tests
				of release detection equipment. At a minimum, the results must list each
				component tested, indicate whether each component tested meets criteria for the
				specified equipment or needs to have action taken, and describe any action
				taken to correct an issue.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
This part applies to owners and operators of above ground
				  storage tank emergency generator systems as provided in 20.5.101 NMAC. If the
				  owner and operator of an above ground storage tank emergency generator system
				  are separate persons, only one person is required to comply with the
				  requirements of this part, including any notice and reporting requirements;
				  however, both parties are liable in the event of
				  noncompliance.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
This part is promulgated pursuant to the provisions of the
				  Hazardous Waste Act, Sections
				  74-4-1
				  through
				  74-4-14
				  NMSA 1978; and the general provisions of the Environmental Improvement Act,
				  Sections
				  74-1-1
				  through
				  74-1-17
				  NMSA 1978.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.5 - EFFECTIVE DATE

Current through Register Vol. 35, No. 13, July 16, 2024
July 24, 2018, unless a later date is indicated in the
				  bracketed history note at the end of a section.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The purpose of 20.5.112 NMAC is to ensure that above ground
				  storage tank emergency generator systems are designed, constructed, installed,
				  modified, repaired, operated, and maintained to minimize releases, to ensure
				  that releases from storage tanks are detected early to minimize potential
				  harmful resulting effects, and to regulate storage tank systems in order to
				  protect the public health, safety and welfare and the environment of the
				  state.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.7 - DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
The definitions in 20.5.101 NMAC apply to this
				  part.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1200 - GENERAL REQUIREMENTS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of above ground storage tank emergency
				  generator systems shall meet the requirements in this part in addition to all
				  of the applicable requirements in the rest of 20.5 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1201 - DEADLINES FOR CLOSING OR UPGRADING ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Not later than July 1, 2013 owners and operators of AST
				  emergency generator systems must have:
A. upgraded AST emergency generator systems
				to meet all performance standards for AST systems in 20.5.109 NMAC, with the
				exception that existing systems need not submit project drawings; or
B. permanently closed any AST emergency
				generator system that does not meet the performance standards in 20.5.109 NMAC
				in accordance with 20.5.115.1502 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1202 - DESIGN, CONSTRUCTION, AND INSTALLATION OF NEW AND UPGRADED ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of above ground storage tank emergency
				  generator systems shall meet all of the requirements in this section in
				  addition to all of the applicable requirements in 20.5.109 NMAC.
A. Owners and operators of ASTs used for
				emergency power generation where the loss of electrical power will not result
				in the loss of human life or serious injury may install motor fuel dispensers
				only if the dispensers are connected to the AST by a separate pump and piping
				system other than that which supplies a regulated substance to the emergency
				generator.
B. Owners and operator
				who install a normally closed solenoid valve in accordance with Subsection D of
				20.5.109.902 NMAC on the supply piping so that a leak will not drain the system
				by siphon shall meet one of the following:
(1)
				solenoid valve shall operate from battery voltage and have manual (nonelectric)
				operation; or
(2) install a manual
				bypass valve.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1203 - DESIGN, CONSTRUCTION, AND INSTALLATION OF NEW AND UPGRADED ABOVE GROUND SUB-BASE TANK EMERGENCY GENERATOR SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of above ground storage tanks that are
				  installed underneath emergency generators, and are also known as belly tanks or
				  sub-base generator tanks, shall meet all of the requirements in this section in
				  addition to all of the applicable requirements in 20.5.109 NMAC.
A. Owners and operators shall be required to
				meet the certified installer requirements in 20.5.105 NMAC for new sub-base
				ASTs.
B. Owners and operators shall
				not be required to meet installation requirements for above ground piping for
				any above ground piping that connects the sub-base AST to the emergency
				generator.
C. Owners and operators
				of sub-base AST systems shall comply with release detection requirements for
				tanks and piping in 20.5.111 NMAC no later than three years after the effective
				date of these regulations.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1204 - OPERATION AND MAINTENANCE REQUIREMENTS FOR ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of above ground storage tank emergency
				  generator systems shall meet all of the requirements for operation and
				  maintenance in 20.5.110 NMAC in addition to all of the applicable requirements
				  in the rest of 20.5 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1205 - RELEASE DETECTION REQUIREMENTS FOR ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS INSTALLED PRIOR TO JULY 24, 2018

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of AST emergency generator systems
				  installed prior to the effective date of these regulations shall meet all of
				  the requirements in this section in addition to all of the applicable
				  requirements in 20.5.111 NMAC.
A.
				Owners and operators of AST emergency generator systems shall implement a
				method, or combination of methods, no later than three years after the
				effective date of these regulations that monitors above ground storage tanks
				every 30 days for releases.
B.
				Owners and operators of AST emergency generator systems shall provide a method,
				or combination of methods, of release detection for underground piping no later
				than three years after the effective date of these regulations. The method, or
				combination of methods, shall follow the current edition of an industry
				standard or code of practice developed by a nationally recognized association
				or independent testing laboratory approved in advance by the department. Owners
				and operators shall comply with the requirements for release detection for
				underground piping as follows:
(1) Owners and
				operators of AST emergency generator systems with piping that conveys a
				regulated substance under pressure shall use automatic line leak detectors for
				emergency generators that alert the operator to the presence of a leak by
				activating a visual and audible alarm when a leak is detected and that comply
				with the requirements of 20.5.111.1105 NMAC, except:
(a) Automatic line leak detectors for
				emergency generators shall not be required to restrict or shut off the flow of
				regulated substances.
(b) Sensors
				used for interstitial monitoring shall not be required to automatically shut
				off the submersible turbine pump when a leak is detected in the interstice of
				the piping or in containment sumps. Sensors used for interstitial monitoring
				shall activate an external audible and visual alarm when liquid is
				detected.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1206 - RELEASE DETECTION REQUIREMENTS FOR ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS INSTALLED OR MODIFIED ON, OR AFTER, JULY 24, 2018

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of AST emergency generator systems
				  installed on, or after, the effective date of these regulations shall meet all
				  of the requirements in this section in addition to all of the applicable
				  requirements in 20.5.111 NMAC upon installation.
A. Owners and operators of AST emergency
				generator systems installed or modified on or after the effective date of these
				regulations must implement a method, or combination of methods, that monitors
				above ground storage tanks every 30 days for releases using an applicable
				method in 20.5.111 NMAC.
B. Owners
				and operators of AST emergency generator systems where the piping is installed
				or replaced on, or after, the effective date of these regulations, and the
				piping conveys a regulated substance under pressure shall use interstitial
				monitoring and automatic line leak detectors that alert the operator to the
				presence of a leak by activating an external audible and visual alarm when
				liquid is detected. Owners and operators of AST emergency generator systems
				shall comply with the requirements of 20.5.111.1106 NMAC, except:
(1) automatic line leak detectors for AST
				emergency generator systems shall not be required to shut off the flow of
				regulated substances; and
(2)
				sensors used to meet the interstitial monitoring requirements for AST emergency
				generator systems shall not be required to automatically shut off the flow of
				product when liquid is detected in the interstice of the piping or in
				containment sumps. Sensors used for interstitial monitoring shall activate a
				secondary audible or visual alarm when liquid is detected.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1207 - CERTIFIED INSTALLERS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of above ground storage tank emergency
				  generator systems shall meet the requirements for certified installers in
				  20.5.105 NMAC in addition to all of the applicable requirements in the rest of
				  20.5 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1208 - ALTERNATE METHODS

Current through Register Vol. 35, No. 13, July 16, 2024
A. If owners
				and operators want to install AST emergency generator systems to meet the
				requirements in this part or want to install release detection equipment for
				tanks or piping installed prior to the effective date of these regulations with
				materials and methods that are not in accordance with the current edition of an
				industry standard or code of practice developed by a nationally recognized
				association or independent testing laboratory, owners and operators shall apply
				in writing to the department, shall provide supporting documentation, and shall
				not begin the installation unless and until the department approves the request
				in writing. At a minimum, the request for an alternate method shall contain the
				following:
(1) date the form is
				completed;
(2) facility name,
				facility ID number, address (with county) and telephone number;
(3) owner name, owner ID number, address and
				telephone number;
(4) citation to
				regulation for which alternate method or material (such as type of piping) is
				requested;
(5) brief description of
				the proposed alternate method or material;
(6) justification of proposed alternate
				method or material, including citation to a standard or code supporting its
				use, if available; and
(7)
				demonstration of its equivalent protection of public health, safety and welfare
				and the environment.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1209 - RECORDKEEPING

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of AST emergency generator systems
				  shall meet the requirements for recordkeeping in this part in addition to all
				  of the applicable requirements in 20.5.110 NMAC and 20.5.111 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 112 - ABOVE GROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.112.1210 - REPORTING

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of AST emergency generator systems
				  shall meet the requirements for reporting in this part in addition to all of
				  the applicable requirements in 20.5.110 NMAC and 20.5.111
				  NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
This part applies to owners and operators of underground
				  storage tank emergency generator systems as provided in 20.5.101 NMAC. If the
				  owner and operator of an underground storage tank emergency generator system
				  are separate persons, only one person is required to comply with the
				  requirements of this part, including any notice and reporting requirements;
				  however, both parties are liable in the event of
				  noncompliance.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
This part is promulgated pursuant to the provisions of the
				  Hazardous Waste Act, Sections
				  74-4-1
				  through
				  74-4-14
				  NMSA 1978; and the general provisions of the Environmental Improvement Act,
				  Sections
				  74-1-1
				  through
				  74-1-17
				  NMSA 1978.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.5 - EFFECTIVE DATE

Current through Register Vol. 35, No. 13, July 16, 2024
July 24, 2018, unless a later date is indicated in the
				  bracketed history note at the end of a section.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The purpose of 20.5.113 NMAC is to ensure that underground
				  storage tank emergency generator systems are designed, constructed, installed,
				  modified, repaired, operated, and maintained to minimize releases, to ensure
				  that releases from storage tanks are detected early to minimize potential
				  harmful resulting effects, and to regulate storage tank systems in order to
				  protect the public health, safety and welfare and the environment of the
				  state.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.7 - DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
The definitions in 20.5.101 NMAC apply to this
				  part.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.1300 - GENERAL REQUIREMENTS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of underground storage tank emergency
				  generator systems shall meet the requirements in this part in addition to all
				  of the applicable requirements in the rest of 20.5 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.1301 - DEADLINES FOR CLOSING OR UPGRADING EXISTING UST EMERGENCY GENERATOR SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Not later than July 1, 2013, owners and operators of UST
				  emergency generator systems installed prior to April 4, 2008, must have:
A. upgraded UST emergency generator systems
				to meet all performance standards for UST systems in this part and 20.5.106
				NMAC; or
B. permanently closed any
				UST emergency generator system that does not meet the performance standards in
				this part and 20.5.106 NMAC in accordance with 20.5.115.1502 NMAC.
New Mexico Administrative Code › Title 20 - ENVIRONMENTAL PROTECTION › Chapter 5 - PETROLEUM STORAGE TANKS › Part 113 - UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS › Section 20.5.113.1302 - DESIGN, CONSTRUCTION, AND INSTALLATION OF NEW AND UPGRADED UNDERGROUND STORAGE TANK EMERGENCY GENERATOR SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Owners and operators of underground storage tank emergency
				  generator systems shall meet all of the requirements in this section in
				  addition to all of the applicable requirements in 20.5.106 NMAC.
A. Owners and operators of USTs used for
				emergency power generation where the loss of electrical power will not result
				in the loss of human life or serious injury may install motor fuel dispensers
				only if the dispensers are connected to the UST by a separate pump and piping
				system other than that which supplies a regulated substance to the emergency
				generator;
B. Owners and operators
				who install a normally closed solenoid valve on the supply piping so that a
				leak will not drain the system by siphon shall meet one of the following:
(1) the solenoid valve shall operate from
				battery voltage and have manual (nonelectric) operation; or
(2) owners and operators shall install a
				manual bypass valve.