reglab/statecodes huggingface dataset:
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-136 - Assessing the site at closure or change in service

Current through Vol. 41, No. 20, July 1, 2024
(a) When a change in service, tank or line
				  repair, and/or replacement is completed, the owner/operator must measure for
				  the presence of a release where contamination is most likely to be present at
				  the underground storage tank system site.
(b) Please refer to the PSTD
				  removal/closure/change of service sampling document on PSTD's website.
(c) If contaminated soils,
				  contaminated groundwater, or free product as a liquid or vapor is discovered,
				  the owner must immediately begin corrective action in accordance with Chapter
				  29 of Commission rules.
(d) All
				  sampling at closures must be under the supervision of a Licensed Environmental
				  Consultant.
Added at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-137 - Applicability to previously closed underground storage tank systems

Current through Vol. 41, No. 20, July 1, 2024
(a) When directed
				  by PSTD, the owner/operator of an underground storage tank system closed before
				  April 21, 1989 must assess the excavation zone and close the underground
				  storage tank system in accordance with this Chapter. PSTD may direct the
				  owner/operator to assess the site or may assess the site itself if a potential
				  for a suspicion of release from the underground storage tank system may, in the
				  judgment of PSTD, pose a current or potential threat to human health, safety or
				  the environment.
(b) Petroleum
				  storage tank systems closed after April 21, 1989 and not upgraded to meet
				  December 23, 1998 upgrade deadline must be removed and the site assessed in
				  accordance with
				  165:25-2-136
				  of Commission rules.
Added at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 2 - General Requirements for Underground Storage Tank Systems › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS › Section 165:25-2-138 - Closure records

Current through Vol. 41, No. 20, July 1, 2024
Owners/Operators must maintain records that demonstrate
					 compliance with all tank closure requirements. Records of the results of the
					 required site assessments must be maintained for at least three (3) years after
					 completion of permanent closure or change in service in one of the following
					 ways:
(1) By the owner or operator who
				  took the UST system out of service.
(2) By the current owner or operator of the
				  UST system site.
(3) Mailing these
				  records to PSTD if they cannot be maintained at the closed facility.
Added at 23 Ok Reg
					 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-1 - Release prohibition

Current through Vol. 41, No. 20, July 1, 2024
The intentional release of regulated substances from an
					 underground storage tank or system is strictly prohibited. No person shall
					 knowingly allow a confirmed or suspected release of regulated substances from
					 an underground storage tank or system to continue without investigation and
					 reporting as required by this Chapter. Owners, operators, their employees or
					 agents of underground storage tank systems, as well as persons who transport
					 regulated substances must ensure that spills and overfills do not
					 occur.
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 22 Ok Reg 1730, eff
					 7-1-05
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-2 - Release reporting [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 10 Ok Reg 2617, eff 6-25-93; Amended at 11 Ok Reg
					 3705, eff 7-11-94; Amended at 12 Ok Reg 2047, eff 7-1-95; Amended at 15 Ok Reg
					 3003, eff 7-15-98; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-3 - Release investigation and confirmation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 11 Ok Reg 769, eff 12-13-93 (emergency); Amended
					 at 11 Ok Reg 3705, eff 7-11-94; Amended at 12 Ok Reg 2047, eff 7-1-95; Amended
					 at 13 Ok Reg 3237, eff 9-1-96; Amended at 15 Ok Reg 3003, eff 7-15-98; Revoked
					 at 18 Ok Reg 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-4 - Activation of a case [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 11 Ok Reg 769, eff 12-13-93 (emergency); Amended
					 at 11 Ok Reg 3705, eff 7-11-94; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5 - General monitoring requirements [AMENDED AND RENUMBERED TO 165:25-3-6.20]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 19 Ok Reg 1609, eff 6-13-02; Amended and
					 renumbered to 165:25-3-6.20 at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5.1 - General release detection methods and devices [AMENDED AND RENUMBERED TO 165:25-3-6.21]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended and renumbered to 165:25-3-6.21 at 23 Ok Reg 2261,
					 eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5.2 - Tank system tightness testing with inventory control [AMENDED AND RENUMBERED TO 165:25-3-6.22]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Amended and renumbered
					 to 165:25-3-6.22 at 23 Ok Reg 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5.3 - Testing or monitoring for vapors [AMENDED AND RENUMBERED TO 165:25-3-6.23]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 19 Ok Reg 1609, eff 6-13-02; Amended at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended and renumbered
					 to 165:25-3-6.23 at 23 Ok Reg 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5.4 - Testing or monitoring for liquids on the groundwater [AMENDED AND RENUMBERED TO 165:25-3-6.24]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 19 Ok Reg 1609, eff 6-13-02; Amended at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended and renumbered
					 to 165:25-3-6.24 at 23 Ok Reg 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5.5 - Interstitial monitoring [AMENDED AND RENUMBERED TO 165:25-3-6.25]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 19 Ok Reg 1609, eff 6-13-02; Amended and
					 renumbered to 165:25-3-6.25 at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5.6 - Automatic tank gauging systems [AMENDED AND RENUMBERED TO 165:25-3-6.26]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Amended and renumbered
					 to 165:25-3-6.26 at 23 Ok Reg 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-5.7 - Manual tank gauging [AMENDED AND RENUMBERED TO 165:25-3-6.27]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended and renumbered to 165:25-3-6.27 at 23 Ok Reg 2261,
					 eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-6 - Monitoring requirements for piping [AMENDED AND RENUMBERED TO 165:25-3-6.29]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 19 Ok Reg 1609, eff 6-13-02; Amended at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended at 23 Ok Reg
					 137, eff 10-6-5 (emergency); Amended and renumbered to 165:25-3-6.29 at 23 Ok
					 Reg 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION REQUIREMENTS › Section 165:25-3-6.1 - Commission-approved alternative methods [RENUMBERED TO 165:25-3-6.30]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Renumbered to
					 165:25-3-6.30 at 23 Ok Reg 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.20 - General monitoring requirements

Current through Vol. 41, No. 20, July 1, 2024
Tanks, including any compartments within a
					 compartmentalized tank that are not in use, must be monitored at least every 30
					 days for releases using one of the methods or combinations of methods listed in
					 this Chapter.
Amended and renumbered
					 from 165:25-3-5 at 23 Ok Reg 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.21 - General release detection methods and devices

Current through Vol. 41, No. 20, July 1, 2024
(a) Owners/operators of new and existing
				  underground storage tank systems must use a release detection method, or a
				  combination of release detection methods, that is:
(1) Capable of detecting a release of
				  regulated substances from any portion of the underground storage tank system
				  that routinely contains product.
(2) Designed, installed, calibrated,
				  operated, and maintained in accordance with the manufacturer's instructions,
				  including routine maintenance and service checks for operability or running
				  conditions.
(3) Capable of meeting
				  the performance requirements of this Chapter, with any performance claims and
				  their manner of determination described in writing by the equipment
				  manufacturer or installer.
(4)
				  Sampled, tested, or checked for a release at least once every 30 days.
(5) If more than one (1) release
				  detection method is present on a petroleum storage tank system, the owner
				  and/or operator must notify PSTD in writing which method is designated as the
				  primary method of release detection. In the event the owner and/or operator
				  switches or utilizes another method of release detection as the primary method,
				  the owner and/or operator must notify PSTD in writing within thirty (30) days
				  of selecting a new primary release detection method.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.22

Current through Vol. 41, No. 20, July 1, 2024
Amended and renumbered
					 from 165:25-3-5.2 at 23 Ok Reg 2261, eff 7-1-06; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.23 - Testing or monitoring for vapors

Current through Vol. 41, No. 20, July 1, 2024
(a) Before installing a new vapor monitoring
				  system or continuing to use an existing vapor monitoring system for thirty (30)
				  day release detection a site-specific site assessment must be conducted to
				  determine the following:
(1) The exact
				  location and total depth of the tank(s) and piping to avoid damage to the UST
				  system during well installation and to determine the number and placement of
				  wells.
(2) That the backfill is
				  sufficiently porous to allow diffusion of vapors from a release to migrate
				  readily to the observation wells (i.e., sand, pea gravel or crushed rock).
(3) That background levels of
				  contamination or naturally occurring organic hydrocarbons are low enough to
				  allow a release from the tank(s) or piping to be detected. To determine
				  background concentrations, a temporary vapor well can be installed in the UST
				  excavation area and the device that will be used for monitoring can be used to
				  get an initial reading.
(4) The
				  location and historical levels of groundwater at the site. If the backfill is
				  saturated with water, because of a perched water table, fluctuating water
				  table, rainfall, etc. above the tank burial depth, a vapor monitoring system
				  should not be used because dispersion of vapors would be restricted and a
				  release could go undetected. Approval for the use of vapor monitor wells for
				  thirty (30) day release detection at a location where there has previously been
				  a confirmed release will be at PSTD's discretion.
(5) Volatility of the stored product and its
				  compatibility with the monitoring device that will be used.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.24 - Testing or monitoring for liquids on the groundwater

Current through Vol. 41, No. 20, July 1, 2024
(a) Before installing a new groundwater
				  monitoring system, or continuing to use an existing groundwater monitoring
				  system for thirty (30) day release detection a site-specific site assessment
				  must be conducted to determine the following:
(1) The exact location and total depth of the
				  tank(s) and piping to avoid damage to the UST system during well installation
				  and to determine the number and placement of wells.
(2) That the backfill is sufficiently porous
				  to allow migration of product from a release to the observation wells (i.e.,
				  sand, pea gravel or crushed rock).
(3) That background levels of contamination
				  or naturally occurring organic hydrocarbons are low enough to allow a release
				  from the tank(s) or piping to be detected. Groundwater monitoring may not be
				  effective if the site has had prior spills or releases.
(4) The location and historical levels of
				  groundwater at the site. Groundwater monitoring cannot be used if the water
				  table is less than three feet (3') below ground surface or more than twenty
				  feet (20') below ground surface.
(5) Fluctuation of groundwater. The well
				  screen must intercept the water table at both high and low elevations. Free
				  product floating on top of the water surface cannot enter a well if the water
				  level is higher than the well screen, nor can free product enter a well if the
				  water level is below the bottom of the well screen. It must be determined that
				  groundwater conditions are such that a release would not go undetected.
(6) The stored product's
				  compatibility with the monitoring device that will be used. The detection
				  device must be able to detect the presence of at least one-eighth of an inch
				  (1/8") of free product on top of the groundwater in the monitoring wells.
				  Groundwater monitoring is only effective if the stored product is lighter than
				  water (i.e., has a specific gravity less than 1.0), which allows the product to
				  float on the water surface. The stored product must not be soluble in water.
				  Products that are highly soluble in water would not be detected as a separate
				  liquid phase.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.26 - Automatic tank gauging systems

Current through Vol. 41, No. 20, July 1, 2024
(a) Automatic tank gauging systems (ATG's)
				  that test for the loss of product must conduct an automatic product level
				  monitor test at a minimum frequency of once every 30 days, and be capable of
				  detecting at least a 0.2 gallon per hour (gph) leak rate for any portion of the
				  tank that routinely contains product.
(b) The test must be performed with the
				  system operating in one of the following modes:
(1) Passing 0.1 gph test at least every
				  thirty (30) days; or
(2) Passing
				  0.2 gph test at least every thirty (30) days along with inventory reconciled at
				  thirty (30) days; or
(3) Passing
				  continuous statistical leak detection ("CSLD") test at least every thirty (30)
				  days along with inventory reconciled at thirty (30) days.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.27 - Manual tank gauging

Current through Vol. 41, No. 20, July 1, 2024
(a)
Restrictions.
Manual tank gauging may be used as an approved
				  method of release detection if the tank has a nominal capacity of 1,000 gallons
				  or less.
(b)
Requirements.
(1) Tank liquid
				  level measurements are taken at the beginning and ending of the period
				  appearing in Appendix Q, during which no liquid is added to or removed from the
				  tank.
(2) Level measurements are
				  based on an average of two (2) consecutive stick readings at both the beginning
				  and ending of the period.
(3) The
				  equipment used is capable of measuring the product over the full range of the
				  tank's height to the nearest one-eighth inch (1/8").
(4) A leak is suspected and subject to the
				  release reporting requirements of Subchapter 3, Part 3 of this Chapter if the
				  variation between beginning and ending measurements exceeds the weekly or
				  thirty (30) day standards in the table in Appendix Q.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.28 - Statistical Inventory Reconciliation (SIR)

Current through Vol. 41, No. 20, July 1, 2024
(a) Deliveries, withdrawals and balance
				  remaining must be recorded each operating day and data must be reconciled every
				  thirty (30) days. Product deliveries must be reconciled with an appropriate
				  device and data must be reconciled every thirty (30) days.
(b) SIR records must demonstrate the
				  following:
(1) Report a quantitative result
				  with a calculated leak rate;
(2) Be
				  capable of detecting a leak rate of 0.2 gallon per hour or a release of one
				  hundred fifty (150) gallons within thirty (30) days, with a probability of
				  detection of 0.95 and a probability of false alarm of 0.05; and
(3) Use a threshold that does not exceed
				  one-half (1/2) the minimum detectible leak rate.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.29 - Monitoring requirements for piping

Current through Vol. 41, No. 20, July 1, 2024
Underground piping that routinely contains regulated
					 substances must be monitored for releases in a manner that meets the following
					 requirements:
(1)
Pressurized
				  piping.
(A) All underground piping
				  that conveys regulated substances under pressure must be equipped with a
				  mechanical or electronic line leak detector installed and operated in
				  accordance with this Chapter.
(B)
				  New installations and facilities replacing a piping system must have a sump
				  sensor, float or similar mechanical device at each tank, transition, and
				  dispenser sump. Sensors should be mounted near the bottom of the sump(s) and
				  accessible for annual testing.
(C)
				  New installations and facilities replacing a piping system must have
				  double-walled piping. The interstitial area of the piping must be open inside
				  the sumps to allow fuel to drain into the sumps in the event that a leak
				  occurs.
(D) The underground
				  pressure piping from the master dispenser to the satellite must be designed and
				  installed so that the satellite piping is tested by the automatic line leak
				  detector. An annual line tightness test is required on the satellite
				  underground piping.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-6.30 - Commission -approved alternative methods [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Renumbered from
					 165:25-3-6.1 at 23 Ok Reg 2261, eff 7-1-06; Revoked at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 2 - RELEASE DETECTION REQUIREMENTS AND METHODS › Section 165:25-3-7 - RENUMBERED

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 22 Ok Reg 1730, eff 7-1-05; Amended at 25 Ok Reg
					 1867, eff 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-8 - Release investigation and confirmation

Current through Vol. 41, No. 20, July 1, 2024
(a) This
				  Section applies to the investigation of all reportable releases unless PSTD
				  specifically waives any part of this Section in writing.
(b) Owners/operators must immediately
				  investigate and confirm all suspected releases of regulated substances
				  requiring reporting under this Chapter within seven (7) days of receipt of
				  notice from PSTD using the following steps or another procedure approved by
				  PSTD:
(1)
System test.
Owners/operators must conduct tightness tests and if applicable, secondary
				  containment testing, that will determine whether a leak exists in the storage
				  tank system or a breach of either wall of the secondary containment has
				  occurred.
(A) Owners/operators must repair,
				  replace or permanently close as defined in OAC
				  165:25-2-135,
				  the underground storage tank system and begin investigation in accordance with
				  (b)(2) of this Section if the test results for the system, tank, delivery
				  piping or the interstice indicates that a release exists.
(B) Further investigation is not required if
				  the test results for the system, tank, delivery piping and interstice do not
				  indicate that a release exists and chemical concentrations of regulated
				  substances detected in soil or water are not the basis for a suspicion of a
				  release.
(C) Owners/operators must
				  conduct a site check as described in (b)(2) of this Section if the test results
				  for the system, tank, delivery piping and interstice do not indicate that a
				  release exists but indicate concentrations of regulated substances detected in
				  soil or water are above action levels cited in (c).
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-9 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-10 - RESERVED

Current through Vol. 41, No. 20, July 1, 2024
Reserved at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-11 - Availability and confidentiality of records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 10 Ok Reg
					 2617, eff 6-25-93; Amended at 14 Ok Reg 2500, eff 7-1-97; Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-12 - Cathodic protection system records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-13 - Release detection records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-14 - Repair records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-15 - Tank removal and closure records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 11 Ok Reg 3705, eff 7-11-94; Amended at 14 Ok Reg
					 2500, eff 7-1-97; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-16 - Inventory records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 11 Ok Reg
					 3705, eff 7-11-94; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-17 - Spill and overfill records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-18 - Corrective action records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-19 - Installation records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RELEASE INVESTIGATION REQUIREMENTS › Section 165:25-3-20 - Financial responsibility records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 5 - SPILL AND OVERFILL PREVENTION REQUIREMENTS [Revoked] › Section 165:25-3-25 - General spill and overfill prevention requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 5 - SPILL AND OVERFILL PREVENTION REQUIREMENTS [Revoked] › Section 165:25-3-26 - Spill and overfill prevention equipment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 18 Ok Reg 2378, eff 7-1-01; Revoked at 21 Ok Reg
					 2036, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 7 - COMPATIBILITY [Revoked] › Section 165:25-3-31 - Compatibility [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-41 - Compliance with nationally recognized code of practice and manufacturer's instructions [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-42 - Pre-installation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-43 - Tank system installation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-44 - Tank system testing [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-45 - Associated equipment [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-46 - Installation drawing [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-47 - Certification of installation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 13 Ok Reg
					 2945, eff 7-11-96; Amended at 18 Ok Reg 2378, eff 7-1-01; Revoked at 21 Ok Reg
					 2036, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-48 - Licensing of Underground Storage Tank Installers [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 10 Ok Reg
					 2617, eff 6-25-93; Amended at 13 Ok Reg 2945, eff 7-11-96; Amended at 15 Ok Reg
					 3003, eff 7-15-98; Amended at 18 Ok Reg 2378, eff 7-1-01; Revoked at 21 Ok Reg
					 2036, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-49 - Underground storage tank installation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 21 Ok Reg 2036, eff
					 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-50 - Licensing procedure for UST Installers [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Amended at 22 Ok Reg
					 1730, eff 7-1-05; Revoked at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-51 - Licensing procedure for UST Removers [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Revoked at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 9 - LICENSING OF UNDERGROUND STORAGE TANK INSTALLERS [Revoked] › Section 165:25-3-52 - Licensing procedure for Monitoring Well Technician [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Revoked at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 11 - REPAIRS TO UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-55 - Repairs to underground storage tank systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Revoked at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-60 - Tank removal and closure [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Revoked at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-61 - Compliance with removal and closure requirements [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-62 - Temporary removal from service [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Revoked at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-63 - Temporary closure; requirements for returning to service [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 18 Ok Reg 2378, eff 7-1-01; Revoked at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-64 - Permanent closure [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Amended at 22 Ok Reg
					 1730, eff 7-1-05; Revoked at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-64.1 - Underground storage tank removal [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 21 Ok Reg 2036, eff 7-1-04; Amended at 22 Ok Reg
					 1730, eff 7-1-05; Revoked at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-65 - Assessing the site at closure or change in service [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 11 Ok Reg 3705, eff 7-11-94; Amended at 14 Ok Reg
					 2500, eff 7-1-97; Amended at 18 Ok Reg 2378, eff 7-1-01; Amended at 21 Ok Reg
					 2036, eff 7-1-04; Amended at 22 Ok Reg 1730, eff 7-1-05; Revoked at 23 Ok Reg
					 2261, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-66 - Applicability to previously closed underground storage tank systems [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 11 Ok Reg
					 3705, eff 7-11-94; Amended at 18 Ok Reg 2378, eff 7-1-01; Amended at 21 Ok Reg
					 2036, eff 7-1-04; Revoked at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 13 - REMOVAL AND CLOSURE OF UNDERGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:25-3-67 - Closure records [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 18 Ok Reg
					 2378, eff 7-1-01; Revoked at 23 Ok Reg 2261, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-70 - Corrective action

Current through Vol. 41, No. 20, July 1, 2024
Corrective action must be conducted in accordance with
					 Chapter 29 of Commission rules.
Added at 18 Ok Reg
					 2378, eff 7-1-01; Amended at 25 Ok Reg 1867, eff
					 7-1-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-71 - General applicability; exception [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 10 Ok Reg
					 2617, eff 6-25-93; Amended at 11 Ok Reg 3705, eff 7-11-94; Amended at 12 Ok Reg
					 2047, eff 7-1-95; Amended at 13 Ok Reg 3237, eff 9-1-96; Amended at 15 Ok Reg
					 3003, eff 7-15-98; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-71.1 - Prescribed forms [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 12 Ok Reg
					 2047, eff 7-1-95; Amended at 13 Ok Reg 3237, eff 9-1-96; Amended at 15 Ok Reg
					 3003, eff 7-15-98; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-72 - Initial response [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 13 Ok Reg
					 3237, eff 9-1-96; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-73 - Initial abatement measures and site check [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 9 Ok Reg
					 2305, eff 6-25-92; Amended at 10 Ok Reg 2617, eff 6-25-93; Amended at 12 Ok Reg
					 2047, eff 7-1-95; Amended at 13 Ok Reg 3237, eff 9-1-96; Amended at 15 Ok Reg
					 3003, eff 7-15-98; Revoked at 18 Ok Reg 2378, eff
					 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-73.1 - Initial site characterization and corrective action plan [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 14 Ok Reg
					 2500, eff 7-1-97; Amended at 15 Ok Reg 3003, eff 7-15-98; Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-74 - Tier 1 and Tier 1A ORBCA [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 10 Ok Reg
					 2617, eff 6-25-93; Amended at 11 Ok Reg 769, eff 12-13-93 (emergency); Amended
					 at 11 Ok Reg 3705, eff 7-11-94; Amended at 12 Ok Reg 2047, eff 7-1-95; Amended
					 at 13 Ok Reg 3237, eff 9-1-96; Amended at 14 Ok Reg 2500, eff 7-1-97; Revoked
					 at 18 Ok Reg 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-74.1 - Classification and prioritization [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg 849,
					 eff 1-6-92 (emergency); Added at 9 Ok Reg 2731, eff 7-13-92; Amended at 11 Ok
					 Reg 3705, eff 7-11-94; Amended at 13 Ok Reg 3237, eff 9-1-96; Revoked at 18 Ok
					 Reg 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-75 - Free product removal [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 10 Ok Reg
					 2617, eff 6-25-93; Amended at 11 Ok Reg 3705, eff 7-11-94; Amended at 12 Ok Reg
					 2047, eff 7-1-95; Amended at 13 Ok Reg 3237, eff 9-1-96; Amended at 14 Ok Reg
					 2500, eff 7-1-97; Amended at 15 Ok Reg 3003, eff 7-15-98; Revoked at 18 Ok Reg
					 2378, eff 7-1-01
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 25 - Underground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 15 - CORRECTIVE ACTION REQUIREMENTS › Section 165:25-3-76 - Tier 2 and Tier 3 ORBCA [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Amended at 10 Ok Reg
					 2617, eff 6-25-93; Amended at 11 Ok Reg 3705, eff 7-11-94; Amended at 12 Ok Reg
					 2047, eff 7-1-95; Amended at 13 Ok Reg 3237, eff 9-1-96; Amended at 14 Ok Reg
					 2500, eff 7-1-97; Revoked at 18 Ok Reg 2378, eff
					 7-1-01