reglab/statecodes huggingface dataset:
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-6 - Duct systems › Section 4101:2-6-01 - Duct systems

Current through all regulations passed and filed through July 1, 2024
Chapter 6 of the International
				Mechanical Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 602.2.1.1 to add exception to read as follows:
Exception:
Wiring methods installed in accordance with Section
				Article 645 of NFPA 70 are permitted for electrical installations in plenums of
				information technology equipment areas and information technology equipment
				rooms that comply with the construction requirements of NFPA 75 and Article 645
				of NFPA 70. The information technology equipment area is required to be
				separated from other areas of the building by a minimum of a one-hour fire
				barrier construction in accordance with the building code. The information
				technology equipment room is required to be separated from other areas of the
				building and the information technology equipment area by a minimum of one-hour
				fire barrier constructed in accordance with the building code.
(B)
Modify section 603.8.2 as follows:
The last sentence is to read "Ducts are
				to be leak tested as required by the applicable energy conservation code
				referenced in Chapter 13 of the building code".
(C)
Modify
			 section 606.2.1 as follows:
Change "International Fire Code" to
				"building code".
(D)
Modify section 606.4.1 as follows:
Change "International Fire Code" to
				building code".
(E)
Modify section 607.5.2 exceptions 3.1 and 3.2 as
			 follows:
Delete the word "Nonmetallic" from the
				beginning of each exception.
(F)
Modify
			 section 607.5.3 by adding a sentence at the end and adding 2 exceptions to read
			 as follows:
Flexible air connectors are not to be
				prohibited in fully ducted sheet steel duct systems where the installation
				meets either of the following:
1.
									Flexible air
			 connectors are installed to connect ducts to air handling equipment and such
			 connectors are located entirely within the mechanical room that contains the
			 air handling equipment.
2.
									Flexible air connectors are installed to connect an
			 overhead metal duct to a ceiling diffuser and such connector is located
			 entirely within the same room as the ceiling diffuser. The flexible air
			 connectors are not to pass through any walls, floors or
			 ceilings.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-7 - Combustion air › Section 4101:2-7-01 - Combustion air

Current through all regulations passed and filed through July 1, 2024
Chapter 7 of the International
				Mechanical Code, 2021 edition, is incorporated by reference and modified in
				Section 101.1.1 of this code.
Replaces: 4101:2-7-01
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-8 - Chimneys and vents › Section 4101:2-8-01 - Chimneys and vents

Current through all regulations passed and filed through July 1, 2024
Chapter 8 of the International
				Mechanical Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
Modify Section
				801.1 to add an exception that
				reads as follows:
Exception:
Section
				501.8 of the "International Fuel
				Gas Code" permits certain gas fired appliances to be installed without venting.
				This section should not be construed as permitting the installation of portable
				unvented heaters in locations otherwise prohibited by section
				3701.82 of the Revised Code or
				rules adopted by the state fire marshal pursuant to 3701.82 of the Revised
				Code.
Replaces: 4101:2-8-01
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-9 - Fire Protection Systems › Section 4101:2-9-01 - Specific appliances, fireplaces and solid fuel-burning equipment

Current through all regulations passed and filed through July 1, 2024
Chapter 9 of the International
				Mechanical Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 901.1 to add exception to read
			 as follows:
Exception:
Section
				501.8 of the "International Fuel
				Gas Code" permits certain gas fired appliances to be installed without venting.
				This section should not be construed as permitting the installation of portable
				unvented heaters in locations otherwise prohibited by section
				3701.82 of the Revised Code or
				rules adopted by the state fire marshal pursuant to 3701.82 of the Revised
				Code.
(B)
Replace section
			 908.3 with the
			 following:
908.3
Location.
Cooling
			 towers, evaporative condensers and fluid coolers are to be located to prevent
			 the discharge of vapor plumes from entering occupied spaces or outdoor public
			 areas. Plume discharges are to be not less than 5 feet (1524 mm) above or 25
			 feet (7620 mm) away from any ventilation inlet to a building including operable
			 windows.
Note:
See ASHRAE Guideline 12 Minimizing the Risk of Legionellosis
				Associated with Building Water Systems.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-10 - Boilers, water heaters and pressure vessels › Section 4101:2-10-01 - Boilers, water heaters and pressure vessels

Current through all regulations passed and filed through July 1, 2024
Chapter 10 of the International
				Mechanical Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Modify the
			 first paragraph of section
			 1001.1 to read as
			 follows:
1001.1
Scope.
This chapter is
			 to govern the installation,
alteration
and
repair
of boilers in Group R occupancy buildings with 4 or 5
			 dwelling units, water heaters and pressure vessels.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-11 - Refrigeration › Section 4101:2-11-01 - Refrigeration

Current through all regulations passed and filed through July 1, 2024
Chapter 11 of the International
				Mechanical Code, 2021 edition, is incorporated by reference and modified in
				Section 101.1.1 of this code.
Replaces: 4101:2-11-01
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-12 - Hydronic piping › Section 4101:2-12-01 - Hydronic piping

Current through all regulations passed and filed through July 1, 2024
Chapter 12 of the International
				Mechanical Code, 2021 edition, is incorporated by reference and modified in
				Section 101.1.1 of this code.
Replaces: 4101:2-12-01
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-13 - Fuel oil piping and storage › Section 4101:2-13-01 - Fuel oil piping and storage

Current through all regulations passed and filed through July 1, 2024
Chapter 13 of the International
				Mechanical Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Replace
			 section 1301.1 with the
			 following:
1301.1
Scope.
This chapter is
			 to govern the design, installation, construction and repair of fuel oil and
			 diesel oil storage and piping systems supplying and piped to building services
			 equipment. The storage of fuel oil and flammable and combustible liquids not
			 associated with building service equipment is to be in accordance with Chapters
			 6 and 57 of the International Fire Code as enforced by the fire
			 official.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-14 - Solar systems › Section 4101:2-14-01 - Solar thermal systems

Current through all regulations passed and filed through July 1, 2024
Chapter 14 of the International
				Mechanical Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
Replace section
				1401.1 with the
				following:
1401.1
Scope.
This
			 chapter governs the design, construction, installation,
alteration
and repair
			 of solar thermal systems,
equipment
and
appliances
intended to utilize solar energy for space heating or
			 cooling or domestic hot water heating.
Replaces: 4101:2-14-01
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-15 - Referenced standards › Section 4101:2-15-01 - Referenced standards

Current through all regulations passed and filed through July 1, 2024
Chapter 15 of the International
				Mechanical Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Add new
			 section 1501.1 to read as
			 follows:
1501.1
General.
This chapter
			 lists the standards that are referenced in various sections of the mechanical
			 code. The standards are listed herein by the promulgating agency of the
			 standard, the standard identification, the effective date and title. The
			 application of the referenced standards is to be as specified in Section
			 102.5.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-72 - Certification of Building Departments › Section 4101:2-72-38 - Certification of the building department of the village of Harrison, Ohio

Current through all regulations passed and filed through July 1, 2024
Rescinded and replaced by 4101:2-72-64, eff 11-1-04
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-73 - Certification of Building Departments › Section 4101:2-73-26 - Certification of the building department of the city of Streetsboro, Ohio

Current through all regulations passed and filed through July 1, 2024
The board of building standards, department of commerce,
				pursuant to division (E) of section
				 3781.10  of the Revised Code,
				orders the certification of the building department of the city of Streetsboro,
				Ohio on the condition that the Portage county building department exercise
				enforcement authority and accept and approve plans and specifications, and make
				inspections in accordance with the provisions of the "Ohio Basic Building Code"
				pursuant to rule 4101:2-1-03 of  the Administrative Code, except"Plumbing"
				provisions.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-75 - Certification of Building Departments › Section 4101:2-75-19 - Certification of the building department of the city of Belpre, Ohio

Current through all regulations passed and filed through July 1, 2024
The board of building standards, department of commerce,
				pursuant to division (E) of section
				 3781.10  of the Revised Code,
				orders the certification of the building department of the city of Belpre, Ohio
				on the condition that the Washington county building department exercise
				enforcement authority and accept and approve plans and specifications, and make
				inspections in accordance with the provisions of the "Ohio Building Code,"
				except "Plumbing" provisions.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-75 - Certification of Building Departments › Section 4101:2-75-20 - Certification of the building department of the village of Middleport, Ohio

Current through all regulations passed and filed through July 1, 2024
The board of building standards, department of commerce,
				pursuant to division (E) of section
				 3781.10  of the Revised Code,
				orders the certification of the building department of the village of
				Middleport, Meigs county, Ohio on the condition that the Washington county
				building department exercise enforcement authority and accept and approve plans
				and specifications, and make inspections in accordance with the provisions of
				the "Ohio Building Code," except "Plumbing" provisions.
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-94 - Certification of Building Departments › Section 4101:2-94-80 - Certification of the Toledo, Ohio building department to enforce Chapters 4101:8-1 to 4101:8-19 of the Administrative Code. [Rescinded]

Current through all regulations passed and filed through July 1, 2024
Rescinded eff 11-1-07
Ohio Administrative Code › Title 4101:2 - Board of Building Standards: Ohio Mechanical Code › Chapter 4101:2-95 - Certification of Building Departments › Section 4101:2-95-32 - Revocation of the certification of the city of Eastlake, Ohio building department

Current through all regulations passed and filed through July 1, 2024
The board of building standards, Ohio department of industrial
				relations, pursuant to division (E) of section
				 3781.10  of the Revised Code,
				orders the revocation of the certification of the city of Eastlake, Ohio
				building department to exercise enforcement authority, to accept and approve
				plans and specifications, and make inspections pursuant to sections
				 3781.03  and
				 3791.04  of the Revised Code, for
				Chapters 4101:2-51, 4101:2-53, 4101:2-55, 4101:2-57, 4101:2-59, 4101:2-61,
				4101:2-63, 4101:2-65, 4101:2-67, 4101:2-69, 4101:2-71, 4101:2-73, and 4101:2-75
				of the Administrative Code.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-1 - General Provisions › Section 4101:3-1-01 - Administration

Current through all regulations passed and filed through July 1, 2024
Section 101
General
101.1
Incorporation by Reference, Title and Rules of
			 Construction.
Except as provided in
			 Chapters 4101:3-1 to 4101:3-15 of the Administrative Code, the International
			 Plumbing Code, 2021 edition, Chapters 2 through 15, as published by the
			 "International Code Council, Inc." including all subsequently published errata
			 and printings, and readily available at
https://www.iccsafe.org
, are hereby incorporated by reference in accordance with
			 sections 121.71 to
			 121.74 of the Revised Code as if
			 set out at length herein.
101.1.1
Rules of Construction.
The following rules of construction are to be applied
			 to the Administrative Code:
1.
											All references to the International Building Code,
			 International Mechanical Code, International Plumbing Code, and International
			 Residential Code mean the Ohio Building Code, Ohio Mechanical Code, Ohio
			 Plumbing Code, and Residential Code of Ohio, respectively, unless otherwise
			 noted. References to "this code" in Sections
			 4101:3-1 to
			 4101:3-15 of the
			 Administrative Code mean the "Ohio Plumbing Code." References to "plumbing
			 code" in divisions 4101:1, 4101:2, 4101:3 and 4101:8 of the Administrative Code
			 mean "Ohio Plumbing Code."
2.
											The phrase "applicable energy conservation code
			 referenced in Chapter 13 of the building code" is substituted for
			 "International Energy Conservation Code."
3.
											Except as
			 otherwise noted, "Chapter 34 of the building code" is substituted for
			 "International Existing Building Code."
4.
											The terms
			 "approval" or "approvals" are substituted for "permit" or "permits,"
			 respectively, when referring to documentation indicating compliance with this
			 code.
5.
											The phrase "owner's representative" is substituted for
			 "owner's authorized agent."
6.
											Except as
			 otherwise noted, "building official" is substituted for "fire code
			 official."
7.
											The phrase "building official" is substituted for "code
			 official."
8.
											The provisions of this code are mandatory whether or
			 not the term "shall" is used.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-3 - General Regulations › Section 4101:3-3-01 - General regulations

Current through all regulations passed and filed through July 1, 2024
Chapter 3 of the International Plumbing
				Code, 2021 edition, as incorporated by reference and modified in Section
				101.1.1 of this code, is further modified as follows:
(A)
Modify the
			 exception to section 301.3 to read as
			 follows:
Exception:
Bathtubs, showers, lavatories, clothes washers and
				laundry trays are not required to discharge to the
sanitary drainage system
where such fixtures discharge to a recycled water
				system approved by the "Ohio Environmental Protection Agency" in accordance
				with Chapter 3745-42 of the Administrative Code or approved by the "Ohio
				Department of Health" in accordance with Chapter 3701-28 of the Administrative
				Code.
(B)
Modify section
			 303.3 as follows:
Replace the phrase "...........third
				party certification..........." with the word
				"...........listed...........".
(C)
Replace
			 section 303.4 to read as
			 follows:
303.4
Approved agency testing and certification.
Plumbing products and materials required by the code to
			 be in compliance with a referenced standard are to be
listed
by an a
pproved agency
as complying with the applicable referenced standards.
			 Products and materials are to be identified in accordance with Section
			 303.1.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-3 - General Regulations › Section 4101:3-3-15.5 - Submission of welding and brazing forms to the division of industrial compliance (DIC). [Rescinded]

Current through all regulations passed and filed through July 1, 2024
Rescinded eff 7-1-07
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-4 - Fittings › Section 4101:3-4-01 - Fixtures, faucets and fixture fittings

Current through all regulations passed and filed through July 1, 2024
Chapter 4 of the International Plumbing
				Code, 2021 edition, as incorporated by reference and modified in Section
				101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 403.1 to add two sentences and
			 an exception at the end of the section to read as follows:
When the actual occupant load will be
				significantly different than that determined by section 1004 of the
building code
, the
building
				official
may establish an alternate
				basis for determining the
occupant
				load
. This alternate basis is to be
				included in the special stipulations and conditions section of the certificate
				of occupancy issued for that structure pursuant to section 111 of the
building code
. For accessibility requirements, see "Chapter 11,
				Accessibility" of the
building
				code
.
Exception:
Facilities are not required in buildings less than 100
				square feet in area if fixtures are available within 500 feet of the
				building.
(B)
Modify table 403.1 as follows:
Relocate the reference to footnote "f"
				to the assembly classification and replace footnote "f" with the
				following:
f.
									The minimum required number, type and location of
			 plumbing fixtures for
public swimming
			 pools
are to be provided in accordance
			 with Section 3109.3.3 of the building code.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-4 - Fittings › Section 4101:3-4-05.3.1 - Water closets, urinals, lavatories and bidets. [Rescinded]

Current through all regulations passed and filed through July 1, 2024
Rescinded eff 7-1-07
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-5 - Water Heaters and Related Safety Devices › Section 4101:3-5-01 - Water heaters

Current through all regulations passed and filed through July 1, 2024
Chapter 5 of the International Plumbing
				Code, 2021 edition, as incorporated by reference and modified in Section
				101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 501.1 to add an exception to
			 read as follows:
Exception:
Water heaters are to comply with the "Ohio Boiler and
				Pressure Vessels rules," Chapters 4101:4-1 to 4101:4-10 of the Administrative
				Code, when any of the following limitations are exceeded:
1.
									Heat input of two
			 hundred thousand BTU per hour;
2.
									Water temperature
			 of two hundred ten degrees Fahrenheit;
3.
									Nominal water
			 containing capacity of one hundred twenty gallons.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-6 - Water Supply systems › Section 4101:3-6-01 - Water supply and distribution

Current through all regulations passed and filed through July 1, 2024
Chapter 6 of the International Plumbing
				Code, 2021 edition, as incorporated by reference and modified in Section
				101.1.1 of this code, is further modified as follows:
(A)
Replace
			 section 601.1 with the
			 following:
601.1
Scope.
This chapter
			 governs the materials, design and installation of
water supply systems
within a building, both hot and cold, for utilization in
			 connection with human occupancy and habitation.
Exceptions:
1.
										This chapter is
			 not applicable to private water systems or recycled water systems as defined in
			 section 3701.344 of the Revised Code and
			 as defined in rule
			 3701-28-01 of the Administrative
			 Code and within the scope of the rules of the "Ohio Department of
			 Health".
2.
										This chapter is not applicable to public water systems
			 as defined in division (A) of section
			 6109.01 of the Revised Code and
			 as defined in rule
			 3745-81-01 of the Administrative
			 Code and within the scope of the rules of the "Ohio Environmental Protection
			 Agency".
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-7 - Sanitary Drainage Systems › Section 4101:3-7-01 - Sanitary drainage

Current through all regulations passed and filed through July 1, 2024
Chapter 7 of the International Plumbing
				Code, 2021 edition, as incorporated by reference and modified in Section
				101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 701.1 as follows:
Add a second sentence and an exception
				to read as follows:
In accordance with section
				3781.03 of the Revised Code, the
				department of the city engineer, in cities having such departments, the boards
				of health districts, or the sewer purveyor, as appropriate, has complete
				supervision and regulation of the entire sewerage and drainage system of the
				jurisdiction, including the
building
				sewer
and all laterals draining into the
				street sewers.
Exception:
Private sewage disposal systems within the scope of the
				"Ohio Department of Health" rules contained within Chapter 3701-29 of the
				Administrative Code, "Household Sewage Disposal Systems".
(B)
Replace section
			 701.2 with the
			 following:
701.2
Connection to sewer required.
Except where permitted by the "Ohio Environmental
			 Protection Agency" or the "Ohio Department of Health", sanitary drainage piping
			 from plumbing fixtures in buildings and sanitary drainage piping systems from
			 premises is to be connected to a public
sewer
.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-8 - Waste › Section 4101:3-8-01 - Indirect/special waste

Current through all regulations passed and filed through July 1, 2024
Chapter 8 of the International Plumbing
				Code, 2021 edition, as incorporated by reference and modified in Section
				101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 802.1 as follows:
Change the reference from "802.1.7" to
				"802.1.8" and add an exception that reads:
Exception:
Approved
health care related fixtures, devices, and equipment may be
				directly connected to the
drainage
				system
if required to be directly
				connected in accordance with the manufacturer's installation
				instructions.
(B)
Add new section 802.1.8 to read as
			 follows:
802.1.8
Dental, drinking or soda fountain, bar sink, floor or shower
			 drain waste.
Wastes from dental or
			 cuspidor fountains, drinking fountains, soda fountains, bar sinks, floor drains
			 or shower drains may be indirectly connected by means of an
air break
to the
sanitary drainage system
. Each indirectly connected item listed above is to
			 discharge, individually, to a directly connected floor drain, waste receptor or
			 standpipe.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-9 - Stacks - Vents › Section 4101:3-9-01 - Vents

Current through all regulations passed and filed through July 1, 2024
Chapter 9 of the International Plumbing
				Code, 2021 edition, as incorporated by reference and modified in Section
				101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 901.3 as follows:
The last sentence is to read: "Air
				admittance valves for chemical waste systems are to comply with Section 918
				including Section 918.8, are to be constructed of
				materials
approved
in accordance with Section
				702.6, and are to be tested for
				chemical resistance in accordance with ASTM F1412."
(B)
Modify
			 section 903.1.1 as follows:
Add the number "12" for the inches
				value and "304.8" for the mm value.
(C)
Modify
			 section 903.1.2 as follows:
Add the phrase "within 10 feet (3048
				mm) of the occupiable area" at the end of the sentence.
(D)
Modify
			 section 906.5.1 as follows:
In the first sentence, add the phrase
				"the building" before "sewer".
(E)
Modify
			 section 913.2 as follows:
The last sentence is to read: "The
				stack is not to receive the discharge of clinical or flushing rim sinks, water
				closets or urinals."
(F)
Modify
			 section 918.8 as follows:
In the first sentence replace the
				reference "702.5" with "702.6" and in the second sentence, add the phrase "or
				where limited by the manufacturer's installation instructions" after
				"plenums".
(G)
Modify section
			 919.1 as follows:
Replace the reference "316" with "106.5
				of the building code".
Replaces: 4101:3-9-01
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-10 - Traps › Section 4101:3-10-01 - Traps, interceptors and separators

Current through all regulations passed and filed through July 1, 2024
Chapter 10 of the International
				Plumbing Building Code, 2021 edition, as incorporated by reference and modified
				in Section 101.1.1 of this code, is further modified as follows:
(A)
Replace
			 section 1001.1 with the
			 following:
1001.1
Scope.
This chapter
			 governs the material and installation of traps, interceptors and separators
			 when installed inside a building and not on the building sewer. The rules of
			 the "Ohio Environmental Protection Agency" may also govern the design and
			 installation of pretreatment devices such as traps, interceptors, and
			 separators.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-11 - Storm sewer drainage › Section 4101:3-11-01 - Storm drainage

Current through all regulations passed and filed through July 1, 2024
Chapter 11 of the International
				Plumbing Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Modify
			 section 1101.2 as follows:
After the word "courtyards", add the
				phrase "in buildings".
(B)
Replace
			 section 1102.4 and table 1102.4 with the
			 following:
1102.4
Building storm sewer pipe.
Deleted.
TABLE 1102.4 BUILDING STORM SEWER
				PIPE.
Deleted.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-12 - Piping and Storage Systems › Section 4101:3-12-01 - Special piping and storage systems

Current through all regulations passed and filed through July 1, 2024
Chapter 12 of the International
				Plumbing Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Replace
			 section 1201.1 to read as
			 follows:
1201.1
Scope.
The provisions
			 of this chapter govern the design and installation of piping and storage
			 systems for nonflammable medical gas systems. All maintenance and operations of
			 such systems are to be in accordance with Chapter 34 of the
building code
and the
			 applicable chapters of the International Fire Code.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-13 - Referenced Standards › Section 4101:3-13-01 - Nonpotable water systems

Current through all regulations passed and filed through July 1, 2024
Chapter 13 of the International
				Plumbing Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Replace
			 section 1301.1 with the
			 following:
1301.1
Scope.
The content of
			 this model code chapter has been deleted. OnSite Nonpotable Water Reuse
			 Systems, Nonpotable Rainwater Collection and Distribution Systems, and
			 Reclaimed Water Systems are considered Private Water Systems as defined in
			 Section 3701.344 of the Revised Code.
			 Private water systems and recycled water systems are regulated by the Ohio
			 Department of Health rules found in Chapter 3701-28 of the Administrative
			 Code.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-14 - Private Water Systems and Recycled Water Systems › Section 4101:3-14-01 - Subsurface graywater soil absorption systems

Current through all regulations passed and filed through July 1, 2024
Chapter 14 of the International
				Plumbing Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Replace
			 Section 1401.1 with the
			 following:
1401.1
Scope.
The content of
			 this model code chapter has been deleted. Subsurface graywater soil absorption
			 systems connected to nonpotable water from on-site water reuse systems are
			 considered process piping systems (not building services piping systems) and,
			 therefore, exempt from approval in accordance with Section
			 102.10 of the building
			 code.
Ohio Administrative Code › Title 4101:3 - Board of Building Standards: Ohio Plumbing Code › Chapter 4101:3-15 - Codes and Standards › Section 4101:3-15-01 - Referenced standards

Current through all regulations passed and filed through July 1, 2024
Chapter 15 of the International
				Plumbing Code, 2021 edition, as incorporated by reference and modified in
				Section 101.1.1 of this code, is further modified as follows:
(A)
Add new
			 section 1501.1 to read as
			 follows:
1501.1
General.
This chapter
			 lists the standards that are referenced in various sections of the plumbing
			 code. The standards are listed herein by the promulgating agency of the
			 standard, the standard identification, the effective date and title. The
			 application of the referenced standards is to be as specified in Section
			 102.5.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-2 - Administration › Section 4101:4-2-01 - Scope, administration, and enforcement

Current through all regulations passed and filed through July 1, 2024
(A) All boilers and
			 pressure vessels proposed for use in the state of Ohio
			 are to
			 be designed, constructed, installed, altered, repaired, maintained, and
			 operated in accordance with the rules adopted by the board as prescribed in
			 Chapters 4101:4-1 to 4101:4-10 of the Administrative Code, except as follows:
(1) Boilers, pressure vessels, and stationary
			 steam engines under federal control or subject to inspection under federal
			 laws;
(2) Air tanks located on
			 vehicles operating under the rules of other state authorities and used for
			 carrying passengers, or freight;
(3) Air tanks installed on the right of way
			 of railroads and used directly in the operation of trains;
(4) Pressure vessels that are under the
			 regulation and control of the state fire marshal under Chapter 3737. of the
			 Revised Code;
(5) Boilers and
			 pressure vessels outside the scope of the applicable section of the "ASME Code
			 for Boilers and Pressure Vessels" as referenced in rule
			 4101:4-3-01 of the
			 Administrative Code;
(6) Historical
			 steam boilers of riveted construction, preserved, restored, or maintained for
			 hobby or demonstration use. In accordance with section
			 4104.33 of the Revised Code,
			 these boilers are to be repaired, altered, inspected and operated in
			 compliance with Chapter 1301:3-4 of the Administrative Code, the rules adopted
			 by the historical boilers licensing board.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-2 - Administration › Section 4101:4-2-02 - Types and qualifications of inspectors

Current through all regulations passed and filed through July 1, 2024
(A) Only an
			 "Authorized Inspector" employed by an "Authorized Inspection Agency"
			 is permitted
			 to conduct inspections of boilers and pressure vessels during
			 construction and fabrication to determine compliance with the rules of the
			 board.
(B) Only a general or
			 special inspector 
								is permitted to conduct inservice periodic
			 inspections for boilers and repair and alteration inspections of boilers and
			 pressure vessels to determine compliance with the rules of the board.
(C) An applicant for examination as an
			 inspector of boilers and pressure vessels is to be
			 qualified as prescribed in the "National Board" publication "NB-263, Rules for
			 National Board Inservice and New Construction Commissioned Inspectors" as
			 referenced in rule
			 4101:4-3-01 of the
			 Administrative Code.
(D) The
			 written examination administered by the superintendent
			 is to be
			 the "National Board Commission Examination."
(E) The superintendent may allow an applicant
			 to sit for the examination at an "On- Demand" location accepted by the
			 "National Board" in accordance with "Part 2" of the "National Board"
			 publication "NB-263, Rules for National Board Inservice and New Construction
			 Commissioned Inspectors" as referenced in rule
			 4101:4-3-01 of the
			 Administrative Code.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-4 - Specifications › Section 4101:4-4-01 - Design of boilers and pressure vessels

Current through all regulations passed and filed through July 1, 2024
(A) All new boilers
			 and pressure vessels proposed for use in the state of Ohio, except those exempt
			 by division (A) of section
			 4104.04 of the Revised Code,
			 are to
			 be designed in accordance with the applicable approved referenced standard(s)
			 adopted in "Table 4101:4-3-01" of rule
			 4101:4-3-01 of the
			 Administrative Code and other requirements as prescribed in rules
			 4101:4-4-01 to
			 4101:4-4-04 of the
			 Administrative Code.
(B) A boiler
			 having the standard stamping of another state that has adopted rules of
			 construction equivalent to those of Ohio may be accepted by the superintendent
			 provided that the person desiring to install the boiler
			 makes application to the superintendent for the
			 installation and includes the manufacturers' data report covering the
			 construction of the boiler.
(C) All
			 electric boilers are to be wired and the shell grounded, in accordance
			 with "NFPA 70, the National Electrical Code" referenced in rule
			 4101:1-35-01 of the
			 Administrative Code.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-4 - Specifications › Section 4101:4-4-02 - Maximum allowable working pressure of new boilers and pressure vessels

Current through all regulations passed and filed through July 1, 2024
(A) The maximum
			 allowable working pressure for boilers and pressure vessels built in accordance
			 with the applicable section of the "ASME Boiler and Pressure Vessel Code" as
			 referenced in rule
			 4101:4-3-01 of the
			 Administrative Code is to be as determined in the applicable approved
			 referenced standard to which it is constructed and stamped. In no case
			 is the
			 maximum allowable pressure permitted to exceed
			 the pressure indicated by the manufacturer's identification stamped or cast
			 upon the boiler or pressure vessel. Upon inspection of a boiler, if conditions
			 are found which justify a reduction of the maximum allowable working pressure,
			 the factor of safety shall be appropriately increased.
(B) The maximum allowable steam working
			 pressure for cast iron boilers, except for hot water boilers,
			 is
			 fifteen psig.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-4 - Specifications › Section 4101:4-4-03 - Safety devices and controls

Current through all regulations passed and filed through July 1, 2024
(A) All boilers and
			 pressure vessels are to be provided with the necessary safety
			 appliances and controls that will prevent pressure and temperature from rising
			 above the design limits. The required safety devices and controls
			 are to
			 be installed and tested as required in the
			 applicable section of the "ASME Boiler and Pressure Vessel Code"
			 and the applicable parts of the "NBIC" as
			 referenced in rule
			 4101:4-3-01 of the
			 Administrative Code. Where differences occur between
			 the "ASME Boiler and Pressure Vessel Code" and the "NBIC," the requirements of
			 the "ASME Boiler and Pressure Vessel Code" will govern.
(B) The operation of a boiler or pressure
			 vessel without the required safety devices or controls is prohibited, except
			 where alternate device(s) are provided for use on a temporary basis.
(C) Any owner or operator who in any manner
			 loads the safety valve or valves to a greater pressure than that allowed by the
			 certificate of operation is subject to the penalty provided in section
			 4104.99 of the Revised
			 Code.
(D) The minimum safety or
			 relief valve relieving capacity for electric boilers 
								is 3.5
			 pounds of steam per hour for each kilowatt input.
(E) The discharge of safety valves and other
			 outlets is to be directed and terminated in such a manner so
			 as not to endanger any person.
(F)
			 Replacement of existing safety devices and controls is to comply
			 with the requirements for new safety devices and controls as prescribed in the
			 applicable section of the "ASME Boiler and Pressure Vessel Code"
			 and the applicable parts of the "NBIC" as
			 referenced in rule
			 4101:4-3-01 of the
			 Administrative Code.
(G) When an
			 owner wishes to install safety devices and controls which will enable a new or
			 an existing boiler to be operated without continuous, manned attendance by a
			 licensed operator, the requirements of paragraph (B)(4) or (B)(5) of rule
			 4101:4-10-01 of the
			 Administrative Code are to be met.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-4 - Specifications › Section 4101:4-4-04 - Steam boiler blowoff systems

Current through all regulations passed and filed through July 1, 2024
(A) The blowoff
			 from boilers may be discharged directly to any place such as a lake, swamp,
			 stream, sump, or open pit provided there is no hazard to life or property.
			 Where a safe place of discharge is not available, a blowoff tank
			 is to be
			 used. The tank is to be designed to separate the flash steam from the
			 water and is
			 to be flashed to a lower pressure system or vented to the atmosphere. The
			 vent is
			 to be large enough to prevent a steam pressure greater than five psig in
			 the blowoff tank. The water from the blowoff tank may be discharged into a
			 building drain or building sewer provided the water temperature does not exceed
			 one hundred forty degrees Fahrenheit.
(B) When a blowoff tank is elevated above the
			 lowest point of a boiler, provisions are to be made
			 for draining water from the boiler.
(C) The shell thickness of a blowoff tank
			 is to be
			 not less than one-fourth inch and is to be constructed for a pressure of not less than
			 twenty five per cent of the allowed pressure of the boilers connected to it for
			 boilers up to and including four hundred psig. For boiler pressure greater than
			 four hundred psig, use "Table 4-4-04(C)" for the blowoff tank allowable
			 pressure. Construction of the blowoff tank is to comply
			 with section VIII, division 1, of the "ASME Boiler and Pressure Vessel Code" as
			 referenced in rule
			 4101:4-3-01 of the
			 Administrative Code and as modified in this rule.
Table 4-4-04(C)
Maximum allowable working pressure of boiler
						  (psig)
Blowoff tank allowable pressure (psig)
3000
400
2250
325
1500
275
1000
200
750
165
500
125
(D)
			 Blowoff piping between the boiler blowoff valve and the blowoff tank or other
			 safe place of discharge, where the pressure is approximately atmospheric and
			 when there are no intervening valves, is to be
			 constructed in accordance with "Table 4-4-04(D)". All boiler blowoff pipe
			 fittings are
			 to be fabricated of steel.
Table 4-4-04(D)
Boiler pressure (psig)
Piping pressure (psig)
1501 to 2000
900
901 to 1500
600
601 to 900
400
250 to 600
250
Below 250
150
(E) In
			 lieu of the design requirements of paragraphs (C) and (D) of this rule, the
			 "National Board" publication entitled "NB-27, A Guide for Blowoff Vessels" as
			 referenced in rule
			 4101:4-3-01 of the
			 Administrative Code may be used for the design, construction, and arrangement
			 of boiler blowoff equipment.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-4 - Specifications › Section 4101:4-4-05 - Clearances

Current through all regulations passed and filed through July 1, 2024
When boilers are replaced or when
				new boilers are installed in either existing or
				new buildings, a minimum clear space of three feet is to be
				provided on the control and service sides of the boiler. All other sides
				are to
				comply with the boiler manufacturer's installation instructions for clearances
				to combustible materials. All boilers are to be so
				located that adequate space will be provided for the proper operation of the
				boiler and its appurtenances, for the inspection of all surfaces, tubes, water
				walls, economizer piping, valves, and other equipment, and for their necessary
				maintenance and repair.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-5 - Special Designs › Section 4101:4-5-01 - Boilers and pressure vessels of special design

Current through all regulations passed and filed through July 1, 2024
(A) When a boiler
			 or pressure vessel proposed for use in Ohio does not conform to all the
			 provisions of the applicable section of the "ASME Boiler and Pressure Vessel
			 Code" referenced in rule
			 4101:4-3-01 of the
			 Administrative Code, application can be made to the board for legal use in Ohio
			 by submitting, prior to fabrication, the following documents, sealed by a
			 registered professional engineer holding a certificate issued under section
			 4733.14 of the Revised Code:
(1) A written analysis detailing how the
			 proposed boiler or pressure vessel does not conform to the requirements of the
			 "ASME Boiler and Pressure Vessel Code";
(2) Detailed construction drawings;
(3) Materials specifications;
(4) Design calculations;
(5) Welding details and procedures, and
			 procedure qualification tests (when applicable); and
(6) Detailed quality control procedures used
			 in all phases of construction.
(Note: All documents submitted are to be in the
				English language, and all dimensions, pressures, temperatures, and material
				properties are
				to be in the same units as used in the applicable section of the "ASME
				Boiler and Pressure Vessel Code" referenced in rule
				4101:4-3-01 of the
				Administrative Code.
Ohio Administrative Code › Title 4101:4 - Boiler Inspection: Ohio Boiler and Pressure Vessel Rules › Chapter 4101:4-6 - Construction and stamping › Section 4101:4-6-01 - Construction and stamping of boilers and pressure vessels

Current through all regulations passed and filed through July 1, 2024
Unless exempt by rule
				4101:4-2-01 of the
				Administrative Code,
(A) All boilers
			 and pressure vessels are to be constructed and tested in accordance with
			 the applicable section(s) of the "ASME Boiler and Pressure Vessel Code" as
			 referenced in rule
			 4101:4-3-01 of the
			 Administrative Code.
(B) All
			 boilers and pressure vessels are to be inspected during construction and after
			 completion by an authorized inspector to determine compliance with the
			 applicable section of the "ASME Boiler and Pressure Vessel Code."
(C) Unless exempt from stamping requirements
			 by the "ASME Boiler and Pressure Vessel Code," after certification of the
			 manufacturer's data report and acceptance by an authorized inspector, the
			 manufacturer is to apply the appropriate "ASME" code stamp symbol
			 and other required markings to the boiler or
			 pressure vessel indicating that the boiler or pressure vessel complies with all
			 of the "ASME" code requirements that are prescribed in the applicable code
			 section referenced in rule
			 4101:4-3-01 of the
			 Administrative Code.
(D) All
			 boilers and pressure vessels are to be registered with the "National Board." In
			 accordance with the "National Board" registration requirements, the original
			 manufacturer's data report, properly executed and signed by both the
			 manufacturer and an authorized inspector, is to be filed
			 with the "National Board" for permanent retention.
(E) The manufacturer, in accordance with the
			 "National Board" registration requirements, is also
			 to apply the "National Board" registration number
			 to the boiler or pressure vessel.