reglab/statecodes huggingface dataset:
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.13 - CHAPTER 5 - GENERAL BUILDING HEIGHTS AND AREAS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
Section 504 - Building Height and Number of Stories.
See this
				  section of the IBC except as provided below.
A.
Section 504.1 - General.
See
				this section of the IBC except as provided below. Add the following section:
504.1.3 - Stair enclosure pressurization increase.
For Group R-1
				and R-2 located in buildings of type VA construction equipped throughout with
				an approved automatic sprinkler system in accordance with section 903.3.1.1,
				the maximum number of stories permitted in section 504.4 may be increased by
				one provided the interior exits stairways and ramps are pressurized in
				accordance with section 903.6.3 and 909.20. Legally required standby power
				shall be provided in accordance with section 909.11 and 2702.2.17 for buildings
				constructed in compliance with this section and shall be connected to stairway
				shaft pressurization equipment, elevators and lifts used for accessible means
				of egress (if provided), elevator hoistway pressurization equipment (if
				provided) and other life safety equipment as determined by the authority having
				jurisdiction. For the purposes of this section, legally required standby power
				shall comply with 2020 NEC section 701.12, options A, B, C, D, F, or
				G.
B.
Section 504.4 - Number
				of stories.
Delete this section and substitute with the following: The
				maximum numbers of stories of a building shall not exceed the limits specified
				in Table 504.4.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.14 - CHAPTER 6 - TYPES OF CONSTRUCTION

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
Section 603 - Combustible Material in Types I and II Construction.
See this section of the IBC except as provided below.
Section 603.1 -
				  Allowable materials.
Add the following exceptions to subsection
				  2:
Exception 28.
Stairways within individual dwelling units and
				  stairways serving a single tenant space are permitted to be of fire-retardant
				  wood or heavy-timber construction. In other than Group R occupancies, such
				  stairways shall not serve as a required means of egress.
Exception
				  29.
Stairways complying with section 510.2, item 4 permitted to be
				  constructed of wood above the horizontal assembly are also permitted to be
				  constructed of wood below the horizontal assembly.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.15 - CHAPTER 7 - FIRE AND SMOKE PROTECTION FEATURES

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
Section 708.4.2 - Fireblocks and draftstops in combustible
				  construction.
See this section of the IBC except delete Exception
				  2.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.17 - CHAPTER 9 - FIRE PROTECTION SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
A.
Section 903 - Automatic Sprinkler
				Systems.
See this section of the IBC except as provided below.
Section 903.2 - Where required.
See this section of the IBC except
				delete the exception.
B.
Section 909 - Smoke Control Systems.
See this section of the IBC
				except as provided below.
(1)
Section
				909.8 - Exhaust method.
See this section of the IBC except as provided
				below.
Section 909.8.1 - Smoke layer.
Delete this section of the
				IBC and substitute with the following: The height of the lowest horizontal
				surface of the accumulating smoke layer shall be maintained at least six feet
				(1829 mm) above any walking surface which forms a portion of a required egress
				system within the smoke zone. The required exhaust rate for the zone shall be
				the largest of the calculated plume mass flow rates for the possible plume
				configurations. Provisions shall be made for a natural or mechanical supply of
				air from outside or adjacent smoke zones to make up for the air exhausted.
				Makeup airflow rates, when measured at the potential fire locations shall not
				increase the smoke production rate beyond the capabilities of the smoke control
				system. The temperature of the makeup air shall be such that it does not expose
				temperature-sensitive fire protection systems beyond their limits.
(2)
Section 909.9 - Design fire.
Delete this section of the IBC and substitute with the following. The design
				fire shall be based on a rational analysis performed by a registered design
				professional and approved by the building official. The design fire shall be
				based on the analysis in accordance with Section 909.4 and this
				section.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.18 - CHAPTER 10 - MEANS OF EGRESS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
A.
Section 1004 - Occupant Load.
See this section of the IBC except as provided below.
Table 1004.5 -
				Maximum floor area allowances per occupant.
See this table of the IBC
				and amend as follows: under the
function of space
column, in
				the
institutional areas
block, below sleeping areas add:
				"correctional facilities and detention centers: 60 square feet gross floor area
				per occupant".
B.
Section
				1010 - Doors, Gates, and Turnstiles.
See this section of the IBC except
				as provided below.
(1)
Section 1010.1.2
				- Egress door types.
See this section of the IBC except delete exception
				#9.
(2)
Section 1010.1.2.1 -
				Direction of swing.
See this section of the IBC and add the following to
				the end: a double-acting door shall be provided with a view panel of not less
				than 200 square inches (0.129 m2): double-acting doors shall not be used as
				exits where any of the following conditions exist:
(a) 1. the occupant load served by the door
				is 100 or more,
(b) 2. the door is
				part of a fire assembly,
(c) 3. the
				door is part of a smoke- and draft-control assembly,
(d) 4. panic hardware is required or provided
				on the door.
(3)
Section 1010.2.14 - Controlled egress doors in Groups I-1 and I-2.
See this section of the IBC and add the words "when approved by the building
				official" at the beginning of the section.
(4)
Section 1010.2.13 - Delayed
				egress.
See this section of the IBC and add the words "when approved by
				the building official" at the beginning of the section.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.19 - CHAPTER 11 - ACCESSIBILITY

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
A.
Section 1102 - Compliance.
See this section of the IBC except as provided below.
Section 1102.1
				Design.
Delete this section of the IBC except and substitute with the
				following: Building and facilities shall be designed and constructed to be
				accessible in accordance with this chapter, Appendix E - Supplementary
				Accessibility Requirements, and the current adopted ICC A117.1.
B.
Section 1104 - Accessible
				Route.
See this section of the IBC except as provided below.
Section 1104.4 - Multistory buildings and facilities.
See this
				section of the IBC except as provided below.
Exception: 1.
Delete
				the exception of this section and substitute with the following: An accessible
				route is not required to stories, mezzanines and occupied roofs that have an
				area of not more than 3,000 square feet (278.7 m2) per story and are located
				either above and or below the accessible levels in buildings or facilities that
				are less than three (3) stories. This exception shall not apply to:
(1)
Subsection 1.1 -
See this
				section of the IBC.
(2)
Subsection 1.2
- See this section of the IBC.
(3)
Subsection 1.3
- See this
				section of the IBC.
(4)
Subsection 1.4
- See this section of the IBC.
(5)
Subsection 1.5
- See this
				section of the IBC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.21 - CHAPTER 13 - ENERGY EFFICIENCY

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the IBC and see NMAC 14.7.9, New
				  Mexico Commercial Energy Conservation Code.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.23 - CHAPTER 15 - ROOF ASSEMBLIES AND ROOFTOP STRUCTURES

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter except as provided below:
A.
Section 1503 - Weather
				Protection.
See this section of the IBC except as provided below.
(1)
Section 1503.3 - Parapet
				walls.
Delete this section and replace with the following: Parapet walls
				shall be coped or covered in accordance with Sections 1503.3.1. 1503.3.2, and
				1503.3.3. The top surface of the parapet wall shall provide positive
				drainage.
(2) Add the following new
				section:
1503.3.3 -
P
lastered Parapets.
Plastered
				parapets shall require a seamless but permeable waterproof cover or weather
				barrier, capping the entire parapet and wrapping over each side. The cover
				shall extend past any break from the vertical a minimum of four inches on the
				wall side. On the roof side, the cover shall properly lap any rising roof felts
				or membranes and be properly sealed. A layer of expanded metal lath shall be
				installed over the cover before plaster or stucco is applied. The lath shall
				extend past any break from the vertical on the wall side a minimum of five
				inches and on the roof side, the same distance as the cover below, allowing for
				plaster stops or seals. No penetrating fasteners are allowed on the horizontal
				surface of parapets.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.25 - CHAPTER 17 - SPECIAL INSPECTIONS AND TESTS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
A.
Section 1705.3 - Concrete
				Construction.
See this section of the IBC except as provided below.
(1)
Subsection 2
- Delete this
				section of the IBC and substitute: continuous concrete footings supporting
				walls of buildings three stories or less in height that are fully supported on
				earth or rock;
(2)
Subsection
				3
- Delete this section of the IBC and substitute: nonstructural
				concrete slabs supported directly on the ground, except pre-stressed
				slabs-on-grade;
(3)
Subsection 4
- Delete this section of the IBC with no
				substitution.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.26 - CHAPTER 18 - SOILS AND FOUNDATIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
Section 1809 - Shallow Foundations.
See this section of the IBC
				  except as provided below.
A.
Section 1809.7 - Prescriptive footings for light-frame
				construction.
Delete this section of the IBC and substitute with the
				following: Where a specific design is not provided, concrete footings
				supporting walls of light-frame construction shall be permitted to be designed
				in accordance with Table 1809.7. A turndown footing cast monolithically with
				the slab-on-grade may be used to support walls of light-frame construction for
				the number of floors outlined in Table 1809.7, provided the minimum width of
				the turndown footing is 12 inches and the depth meets the requirements of
				Sections 1809.4 and 1809.5.
B.
Table 1809.7
- Delete this table and substitute with the following
				table:
TABLE 1809.7
PRESCRIPTIVE FOOTINGS SUPPORTING WALLS OF
								LIGHT-FRAME CONSTRUCTION 
								a, b, c, d, e
NUMBER OF FLOORS SUPPORTED BY THE
								FOOTING
WIDTH OF FOOTING (inches)
THICKNESS OF FOOTING (inches)
1
16
8
C.
Table 1809.7 Footnotes.
See this section of the IBC except delete
				footnote "g" with no substitution.
D.
Section 1809.8 Plain concrete
				footings.
Delete this section of the IBC and substitute with the
				following: The edge thickness of plain concrete footings supporting walls other
				than light-frame construction shall be not less than 8 inches (203MM) where
				placed on soil or rock.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.27 - CHAPTER 19 - CONCRETE

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
A.
Section 1906 Footings for
				Light-Frame Construction.
Delete this section of the IBC with no
				substitution.
B.
Section 1907
				Minimum Slab Provisions.
See this section of the IBC except as provided
				below.
Section 1907.1 General.
Delete this section and the
				exception and substitute with the following: The thickness of concrete floor
				slabs supported directly on the ground shall be not less than 3½ inches
				(89mm). When required by a geotechnical investigation, design professional,
				building official or where moisture sensitive flooring is present, a minimum A
				6-mil (0.006 inch; 0.15mm) polyethylene vapor retarder with joints lapped not
				less than 6 inches (152mm) shall be placed between the base course or subgrade
				and the concrete floor slab, or other approved equivalent methods or materials
				shall be used to retard vapor transmission through the floor slab.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.29 - CHAPTER 21 - MASONRY

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
A.
Section 2111 - Masonry
				Fireplaces.
See this section of the IBC except as provided below.
Section 2111.5 - Seismic Anchorage.
Delete this section of the IBC
				and substitute with the following: Two three-sixteenth-inch by one-inch (4.8 mm
				by 25.4mm) straps shall be embedded a minimum of 12 inches (305 mm) into the
				chimney with a 180-degree bend with a six-inch (152 mm) extension around the
				vertical reinforcing bars in the outer face of the chimney. Each strap shall be
				fastened to the structural framework of the building with two one-half-inch
				(12.7 mm) diameter bolts per strap. Where the joists do not head into the
				chimney, the anchor strap shall be connected to two-inch by four-inch (51 mm by
				102 mm) ties crossing a minimum of four joists. The ties shall be connected to
				each joist with two 16d nails. As an alternative to the two-inch by four-inch
				(51 mm by 102 mm) ties, each anchor strap shall be connected to the structural
				framework by two one-half-inch (12.7 mm) diameter bolts in an approved
				manner.
B.
Section 2113 -
				Masonry Chimneys.
See this section of the IBC except as provided below.
Section 2113.4 - Anchorage.
Delete this section of the IBC and
				substitute with the following: Two three-sixteenth-inch by one-inch (4.8 mm by
				25.4mm) straps shall be embedded a minimum of 12 inches (305 mm) into the
				chimney with a 180 degree bend with a six-inch (152 mm) extension around the
				vertical reinforcing bars in the outer face of the chimney. Each strap shall be
				fastened to the structural framework of the building with two one-half-inch
				(12.7 mm) diameter bolts per strap. Where the joists do not head into the
				chimney, the anchor strap shall be connected to two-inch by four-inch (51 mm by
				102 mm) ties crossing a minimum of four joists. The ties shall be connected to
				each joist with two 16d nails. As an alternative to the two-inch by four-inch
				(51 mm by 102 mm) ties, each anchor strap shall be connected to the structural
				framework by two one-half-inch (12.7 mm) diameter bolts in an approved
				manner.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.31 - CHAPTER 23 - WOOD

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
Section 2308 - Conventional Light-Frame Construction.
See this
				  section of the IBC except as provided below.
A.
Section 2308.4.5 - Joists supporting
				bearing partitions.
See this section of the IBC except delete the first
				sentence and substitute: bearing partitions parallel to joists shall be
				supported on beams, girders, built-up joists of sufficient size to carry the
				load, walls, or other bearing partitions.
B.
Section 2308.7.6 - Framing around
				openings.
See this section of the IBC except delete the first sentence
				and substitute: Trimmer and header joists shall be of sufficient size to
				support the load.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.32 - CHAPTER 24 - GLASS AND GLAZING

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
Section 2403 - General Requirements for Glass.
See this section of
				  the IBC except as provided below.
A.
Section 2403.1 - Identification.
Delete the first paragraph of
				this section of the IBC and substitute: Each pane shall bear the manufacturer's
				label designating the type and thickness of the glass or glazing material. The
				identification shall not be omitted unless approved by the building official.
				The building official is authorized to require an affidavit from the glazing
				contractor certifying that each light is glazed in accordance with approved
				construction documents that comply with the provisions of this chapter. Safety
				glazing shall be identified in accordance with Section 2406.3.
B.
Section 2403.2 - Glass
				supports.
Delete this section of the IBC and substitute: Where one or
				more sides of any pane of glass is not firmly supported, or is subject to
				unusual load conditions, detailed construction documents, detailed shop
				drawings and analysis or test data assuring safe performance for the specific
				installation shall be submitted when required by the building
				official.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.33 - CHAPTER 25 - GYPSUM BOARD, GYPSUM PANEL PRODUCTS AND PLASTER

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC except as provided below.
A.
Section 2510 - Lathing and Furring
				for Cement Plaster (Stucco).
See this section of the IBC except as
				provided below.
Section 2510.6 - Weather - Resistant Barrier.
Delete this section and substitute with the following: Water-resistive barriers
				shall be installed as required in sections, 1403.2, 1405.3, and 1503.2 and,
				where applied over wood-based sheathing, shall comply with section 2510.6.1 or
				2510.6.2.
B.
Section 2512 -
				Exterior Plaster.
See this section of the IBC except as provided below.
(1)
Section 2512.1.1 - On Grade Floor
				Slab.
Delete this section of the IBC and substitute with the following:
				On wood framed or steel stud construction with an on-grade concrete floor slab
				system, approved acrylic based exterior plaster systems and acrylic based color
				coats shall be applied in such a manner as to cover but not to extend below,
				the lath, paper, and screed. When a cement plaster stucco and cement plaster
				color coat is installed, and no perimeter insulation is on the exterior of a
				concrete or masonry foundation, the color coat shall terminate not further than
				six inches (153 mm) below finished grade. All excess plaster shall be removed
				from the site and no drip screeds shall comply with ASTM C 1063.
(2)
Section 2512.1.2 - Weep
				Screeds.
See this section of the IBC.
(3) Add the following section to the IBC.
Section 2512.1.3 - Plaster to Roof Separation.
A reglet and weep
				screed or equivalent metal flashing shall be applied where all stucco wall
				surfaces terminate at a roof.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.35 - CHAPTER 27 - ELECTRICAL

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the IBC and see the NMEC except as
				  provided below.
A.
Section 2701
				- General.
See this section of the IBC except as provided below.
2701.1 - Scope.
Delete this section of the IBC and substitute:
				Electrical systems, including emergency and standby power systems, and
				electrical equipment, appliances, fixtures, fittings, and appurtenances
				thereto, shall be installed, altered, repaired, replaced, maintained, tested,
				and designed pursuant to the provisions of the NMEC.
B.
Section 2702 - Emergency and Standby
				Power Systems.
See this section of the IBC except as provided below.
(1)
Section 2702.1 - General.
See this section of the IBC except as provided below.
(a)
Section 2702.1.1 - Stationary
				generators.
Delete this section of the IBC.
(b)
Section 2702.1.3 -
				Installation.
Delete this section of the IBC.
(c)
Section 2702.1.4 - Load
				transfer.
Delete this section of the IBC.
(d)
Section 2702.1.5 - Load
				duration.
Delete this section of the IBC.
(e)
Section 2702.1.6 - Uninterruptable
				power source.
Delete this section of the IBC.
(f)
Section 2702.1.7 -
				Interchangeability.
Delete this section of the IBC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.36 - CHAPTER 28 - MECHANICAL SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the IBC and see the
				  NMMC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.37 - CHAPTER 29 - PLUMBING SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the IBC and see the NMPC except as
				  provided below.
A.
Section 2901
				- General.
See this section of the IBC except as provided below.
(1)
Section 2901.1 Scope.
Delete
				this section of the IBC and substitute with the following: Plumbing systems,
				including piping systems, equipment, appliances, fixtures, fittings and
				appurtenances, and when connected to a water or sewage system, and all aspects
				of a medical gas system, shall be installed, altered, repaired, replaced,
				maintained, tested and designed pursuant to the provisions of the
				NMPC.
(2)
Section
				2901.2.
All references in Chapter 29 of the IBC to the International
				Plumbing Code are deemed references to the NMPC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.38 - CHAPTER 30 - ELEVATORS AND CONVEYING SYSTEMS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.40 - CHAPTER 32 - ENCROACHMENTS INTO THE PUBLIC RIGHT-OF-WAY

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.41 - CHAPTER 33 - SAFEGUARDS DURING CONSTRUCTION

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IBC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.42 - CHAPTER 34 - EXISTING STRUCTURES

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the IBC and see 14.7.7
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 2 - 2021 NEW MEXICO COMMERCIAL BUILDING CODE › Section 14.7.2.45 - BABY CHANGING FACILITIES

Current through Register Vol. 35, No. 13, July 16, 2024
A.
				Construction of a new restroom, intended for use in a place of public
				accommodation, as defined in 14.5.2 NMAC, shall provide for at least one baby
				changing facility on each floor that has a public toilet facility and shall
				accommodate any person needing to utilize a baby changing facility, pursuant to
				Section 60-13-10.3 NMSA 1978.
B. Baby changing facilities shall be included
				in all required documentation including plans submitted under submittal
				documents pursuant to Subparagraph (b) of Paragraph (1) of Subsection A of
				14.5.2 10 NMAC and shall be subject to plan review pursuant to Subsection A of
				14.5.2.11 NMAC - Permits, and
				inspections pursuant to Subsection A of
				14.5.3.8 NMAC.
C. All requirements for baby changing
				facilities must be complied with in order for a certificate of occupancy to be
				issued or a final inspection approved, whichever is appropriate.
D. Baby changing facilities shall comply with
				the American national standards institute (ANSI) A117.1-2017 Section 603.5
				diaper changing tables; Section 305 floor space; Section 308.2.1 unobstructed
				access; Chapter 7 Communication Elements and Features; Chapter 9 built in
				furnishings and equipment; and Subsection K of
				14.7.2.19 NMAC, Section 1111,
				signage.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.1 - ISSUING AGENCY

Current through Register Vol. 35, No. 13, July 16, 2024
Construction Industries Division (CID) of the Regulation and
				  Licensing Department.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.2 - SCOPE

Current through Register Vol. 35, No. 13, July 16, 2024
This rule applies to all construction, alteration,
				  relocation, enlargement, replacement, repair, equipment
,
use
				  and occupancy, location, removal and demolition of all detached one- and
				  two-family dwellings and multiple single-family dwellings (townhouses) not more
				  than three stories high with separate means of egress, and their accessory
				  structures that is performed in New Mexico on or after December 14, 2023, and
				  that is subject to the jurisdiction of CID, unless performed pursuant to a
				  permit for which an application was received by CID before that date. Any
				  repair, alteration or addition to such building that is associated with a
				  change of occupancy, and any construction not addressed in the NMRBC, shall be
				  subject to and shall comply with the NMCBC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.3 - STATUTORY AUTHORITY

Current through Register Vol. 35, No. 13, July 16, 2024
Section
				  60-13-9 and
				  60-13-44 NMSA 1978.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.5 - EFFECTIVE DATE

Current through Register Vol. 35, No. 13, July 16, 2024
July 14, 2023, unless a later date is cited at the end of a
				  section. From the date of publication of this rule in the New Mexico register,
				  until December 14, 2023, permits may be issued under either the previously
				  adopted rule, or this rule. After December 14, 2023, permits may be issued only
				  under this rule.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.6 - OBJECTIVE

Current through Register Vol. 35, No. 13, July 16, 2024
The purpose of this rule is to establish minimum standards
				  for the general construction of residential buildings in New
				  Mexico.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.7 - DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See 14.5.1 NMAC, General Provisions and Chapter 2 of the 2021
				  International Residential Code (IRC) as amended in
				  14.7.3.10 NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.8 - ADOPTION OF THE 2021 INTERNATIONAL RESIDENTIAL CODE

Current through Register Vol. 35, No. 13, July 16, 2024
A. This rule adopts by reference the 2021
				International Residential Code, as amended by this rule.
B. In this rule, each provision is numbered
				to correspond with the numbering of the 2021 International Residential
				Code.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.9 - CHAPTER 1 SCOPE AND ADMINISTRATION

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IRC except as provided below.
A.
Section R101 Scope and General
				Requirements.
(1)
Section R101.1
				Title.
Delete this section of the IRC and substitute: This code shall be
				known as the 2021 New Mexico residential building code (NMRBC).
(2)
Section R101.2 Scope.
Delete
				this section of the IRC and see
				14.7.3.2 NMAC, Scope and add the
				following:
Exception.
Live/work units complying with the
				requirements of Section 508.5 of the
International Building
				Code
shall be permitted to be built as one- and two-family
dwellings
or townhouses. Automatic fire sprinkler systems
				required by Section 903.2.8 of the
International Building Code
when constructed under the
International Residential Code for One- and
				Two-family Dwellings
shall conform to Section P2904 of the
Residential Building Code
. A home office or business not
				utilizing hazardous materials as defined in the international building code
				with a work area less than 300 sq. ft. is not a live/work unit subject to the
				requirements of the
International Building Code
. A home office
				in dwelling units exceeding 3000 sq. ft. may occupy up to ten percent of the
				floor area.
(3)
Section
				R101.3 Purpose.
See
				14.7.3.6 NMAC,
				Objective.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.10 - CHAPTER 2 DEFINITIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IRC except as provided below.
A.
Section R201 General.
See
				this section in the IRC except as provided below.
Section - R201.3 Terms
				defined in other codes.
Delete this section of the IRC and substitute
				the following: Defined terms not listed in this rule shall have the meanings
				given in 14.5.1.7 NMAC, General Provisions,
				and in the other New Mexico codes.
B.
Section R202 Definitions.
(1)
Building official.
Delete
				this definition and see 14.5.1 NMAC, General Provisions.
(2)
Decorative coating.
A single
				coat of plaster, cementitious or other approved material applied to a concrete
				or masonry surface for cosmetic purposes only.
(3)
Design professional and registered
				design professional.
Delete these definitions and see 14.5.1 NMAC,
				General Provisions.
(4)
Earthen building materials
has the meaning given in 14.7.4 NMAC,
				New Mexico Earthen Building Materials Code.
(5)
Exterior finish coating
means a single coat of plaster, cementitious or other approved material applied
				to a concrete or masonry surface for cosmetic purposes only.
(6)
ICC
means the international
				code council.
(7)
Manufactured home.
Delete this definition from the IRC.
(8)
Unbalanced backfill height
is the difference in height between the exterior finish ground level and the
				lower of the top of the concrete footing that supports the foundation wall,
				retaining wall or the interior finished ground level. Where an interior
				concrete slab on grade is provided and is in contact with the interior surface
				of the foundation wall, the unbalanced backfill height is permitted to be
				measured from the exterior finished ground level to the top of the interior
				concrete slab.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.11 - CHAPTER 3 BUILDING PLANNING

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IRC except as provided below.
A.
Section R301 Design criteria.
See this section of the IRC except as provided below:
(1)
Section R301.2 Climatic and
				geographic design criteria.
Amend footnote "f" as follows: The authority
				having jurisdiction shall fill in this part of the table with the seismic
				design category determined from Section R301.2.2.1 or information from the
				U.S.G.S. software "Design Values for Buildings" found online.
(2)
Section 301.2.2 Seismic
				provisions.
Add the following sentence to the end:
Exception
: Buildings in which earthen building materials form the
				bearing wall system located in seismic design categories A, B, C, Do and
				D1 are exempt from the seismic requirements of this
				code.
(3)
Section R301.2.2.1
				Determination of seismic design category.
Add the following text at the
				end of the section: or information from the U.S.G.S. software "Design Values
				for Buildings" found online.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.12 - CHAPTER 4 FOUNDATIONS

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IRC except as provided below.
Section R403 Footings.
See this section of the IRC except as
				  provided below.
A.
Section
				R403.1.3.2 Masonry stem walls with concrete footings.
See this section
				of the IRC and add the following sentence to the end of the section. Where the
				slabs-on-ground are cast monolithically and rigid insulation is used as a
				forming material, a minimum of one and one-half inch rigid insulation shall be
				used. Where sandy, silty sand or sandy gravel soils are present, rigid
				insulation shall not be used as a forming material. Forms must be constructed
				to prevent the possibility of failure or collapse. Forms shall be constructed
				and maintained so that the finished concrete complies with Section
				R401.2.
B.
Section R403.1.4
				Minimum depth.
Delete the text of this section and substitute with the
				following: All exterior footings shall be placed at least 12 inches (305 mm)
				below grade. Where applicable, the depth of footings shall also conform to
				Sections R403.1.4.1 and R403.1.4.2.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.14 - CHAPTER 6 WALL CONSTRUCTION

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IRC except as provided below.
Section R602 Wood Wall Framing.
See this section of the IRC except
				  as provided below.
A.
Section
				R602.3 Design and construction.
Add the following to this section:
				Structural wall sheathing shall be fastened directly to structural framing
				members and plywood, or oriented strand board shall have a one-eighth inch
				space at panel edge and end joints.
(1)
Section R602.3.1 Stud size, height and spacing.
See this section
				of the IRC except delete exception number two.
(2)
Section R602.3.4 Bottom (sole)
				plate.
Delete this section and replace with the following: Studs shall
				have full bearing on a nominal two-by (51 mm) or larger plate or sill having a
				width at least equal to the width of the studs. Two-inch (51 mm) by six-inch
				(152 mm) or wider exterior wall bottom or sill plates may be cantilevered a
				maximum of one and one-half (38 mm) inches from concrete slab-on-grade to
				accommodate slab-on-grade perimeter insulation if the remaining bearing is
				sufficient to carry the structural load. Anchor bolts shall be placed a minimum
				of two inches from the exterior edge of the concrete. Two inch by four inch or
				wider exterior wall bottom or sill plates may be cantilevered a maximum of half
				inches from concrete slab-on-grade to accommodate slab-on-grade perimeter
				insulation if the remaining bearing is sufficient to carry the structural load.
				Anchor bolts shall be placed a minimum of two inches from the exterior edge of
				the concrete.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.16 - CHAPTER 8 ROOF-CEILING CONSTRUCTION

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IRC except as provided below.
Section R802.1.3 Structural log members.
See this section of the
				  IRC and add the following section:
Section R802.1.3.1 Vigas.
Vigas
				  shall be installed in accordance with Table R802.1.3.1.
Click to
				  view image
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.17 - CHAPTER 9 ROOF ASSEMBLIES

Current through Register Vol. 35, No. 13, July 16, 2024
See this chapter of the IRC except as provided below.
A.
Section R903 Weather
				Protection.
See this section of the IRC except as provided below.
(1)
Section R903.2.1 Locations.
See this section of the IRC and the following to the end of the section:
				Approved reglets or an approved flashing shall be installed at wall and roof
				intersections, wherever there is a change in roof slope or direction and around
				roof openings. Where flashing is of metal, the metal shall be corrosion
				resistant with a thickness of not less than 0.019 inch (0.5 mm) (No. 26
				galvanized sheet).
(2)
Section R903.3 Coping.
Delete the text of this section and
				substitute with the following: Plastered parapets shall require a seamless but
				permeable waterproof cover or weather barrier, capping the entire parapet and
				wrapping over each side. The cover shall extend past any break from the
				vertical a minimum of four inches on the wall side. On the roof side, the cover
				shall properly lap any rising roof felts or membranes and be properly sealed. A
				layer of furred expanded metal lath shall be installed over the cover before
				plaster or stucco is applied. The lath shall extend past any break from the
				vertical on the wall side a minimum of five inches and on the roof side, the
				same distance as the cover below, allowing for plaster stops or seals. No
				penetrating fasteners are allowed on the horizontal surface of
				parapets.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.19 - CHAPTER 11 ENERGY EFFICIENCY

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the IRC and see 14.7.6
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.20 - CHAPTERS 12 THROUGH 23 MECHANICAL

Current through Register Vol. 35, No. 13, July 16, 2024
Delete these chapters of the IRC and see 14.9.2
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.21 - CHAPTER 24 FUEL GAS

Current through Register Vol. 35, No. 13, July 16, 2024
Delete this chapter of the IRC and see 14.9.2
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.22 - CHAPTERS 25 THROUGH 33 PLUMBING

Current through Register Vol. 35, No. 13, July 16, 2024
Delete these chapters of the IRC and see the 14.8.2
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.23 - CHAPTERS 34 THROUGH 43 ELECTRICAL

Current through Register Vol. 35, No. 13, July 16, 2024
Delete these chapters of the IRC and see the 14.10.4
				  NMAC.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.25 - Add the following Chapter to the IRC

Current through Register Vol. 35, No. 13, July 16, 2024
CHAPTER 45 SWIMMING POOLS:
A.
Section R4501.1 General.
The
				provisions of this chapter shall control the design and construction of
				swimming pools, spas and hot tubs installed in or on the lot of a one- or
				two-family dwellings.
B.
Section R4501.2 Pools in flood hazard areas.
Pools that are
				located in flood hazard areas established by Table R301.2(1) of the IRC,
				including above-ground pools, on-ground pools and in-ground pools that involve
				placement of fill, shall comply with Sections R4201.2.1 or R4201.2.2. of the
				IRC.
Exception:
Pools located in riverine flood hazard areas which
				are outside of designated floodways.
C.
Section R4501.2.1 Pools located in
				designated floodways.
Where pools are located in designated floodways,
				documentation shall be submitted to the building official, which demonstrates
				that the construction of the pool will not increase the design flood elevation
				at any point within the jurisdiction.
D.
Section R4501.2.2 Pools located
				where floodways have not been designated.
Where pools are located where
				design flood elevations are specified but floodways have not been designated,
				the applicant shall provide a floodway analysis that demonstrates that the
				proposed pool will not increase the design flood elevation more than one foot
				(305 mm) at any point within the jurisdiction.
E.
Section R4502.1 Definitions.
For the purposes of these requirements, the terms used shall be defined as
				follows.
(1)
Above ground/on-ground
				pool.
See "Swimming pool.".
(2)
Barrier.
A fence, wall,
				building wall or combination thereof, which completely surrounds the swimming
				pool and obstructs access to the swimming pool.
(3)
Hot tub.
See "Swimming
				pool.".
(4)
In-ground
				pool.
See "Swimming pool.".
(5)
Residential.
That which is
				situated on the premises of a detached one- or two-family dwelling or a
				one-family townhouse not more than three stories in height.
(6)
Spa, non-potable.
See
				"Swimming pool.".
(7)
Spa,
				portable.
A non-permanent structure intended for recreational bathing,
				in which all controls, water-heating and water-circulating equipment are an
				integral part of the product.
(8)
Swimming pool.
Any structure intended for swimming or recreational
				bathing that contains water over 24 inches (610 mm) deep. This includes
				in-ground, above-ground and on-ground swimming pools, hot tubs, and
				spas.
(9)
Swimming pool,
				indoor.
A swimming pool which is totally contained within a structure
				and surrounded on all four sides by the walls of the enclosing
				structure.
(10)
Swimming
				pool, outdoor.
Any swimming pool which is not an indoor
				pool.
New Mexico Administrative Code › Title 14 - HOUSING AND CONSTRUCTION › Chapter 7 - BUILDING CODES GENERAL › Part 3 - 2021 NEW MEXICO RESIDENTIAL BUILDING CODE › Section 14.7.3.26 - APPENDIX AJ EXISTING BUILDINGS AND STRUCTURES

Current through Register Vol. 35, No. 13, July 16, 2024
See this section of the IRC except as provided below:
Section AJ102 Compliance.
See this section of the IRC except add
				  the following new section:
Section AJ102.4.5 Compliance.
When
				  alterations are made to the exterior stud framed walls of existing bedrooms and
				  exterior wall framing adjoining the window is exposed, then the replacement
				  window shall be made to comply with section R310 of the IRC. When repairs are
				  made to the exterior stud framed walls of existing bedrooms and exterior wall
				  framing adjoining the window is exposed, then the replacement window shall be
				  made to comply with section R310 of the IRC.