reglab/statecodes huggingface dataset:
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 1 - DESIGN AND INSTALLATION › Section 165:26-2-7 - Collision barriers

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Aboveground storage tanks exposed to traffic must be resistant to damage from
				  the impact of a motor vehicle by suitable collision barriers. The secondary
				  containment dike may serve as a collision barrier provided that it cannot be
				  penetrated by a motor vehicle.
(b)
				  When guard posts or collision barriers are installed, the following design
				  shall be acceptable:
(1) They shall be
				  constructed of steel not less than 4 in. (100 millimeters) in diameter and
				  shall be filled with concrete.
(2)
				  They shall be spaced not more than 4 ft. (1.2 meters) on center.
(3) They shall be set not less than 3 ft (0.9
				  meters) deep in a concrete footing of not less than 15-in. (380 millimeters)
				  diameter.
(4) They shall not be
				  less than three feet (3') above grade and concrete barriers not less than
				  thirty-two inches (32") above grade.
(5) They shall not be less than five feet
				  (5') from the tank shell.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 3 - SECONDARY CONTAINMENT › Section 165:26-2-31 - Double-walled tanks

Current through Vol. 41, No. 20, July 1, 2024
Double-walled tanks do not require additional containment
					 if all the following conditions are met:
(1) The capacity of the tank does not exceed
				  50,000 gallons (189,000 liters).
(2) All piping connections to the tanks are
				  made above the normal maximum liquid level.
(3) A mechanism is provided to prevent the
				  release of liquid from the tank by siphon flow.
(4) A mechanism is provided for determining
				  the level of liquid in the tank, which is accessible to the delivery operator.
(5) A mechanism is provided to
				  prevent overfilling by sounding an alarm when the liquid level in the tank
				  reaches 90 percent of capacity and by automatically stopping the delivery of
				  liquid to the tank when the level in the tank reaches 95 percent of capacity.
				  In no case will these provisions restrict or interfere with the proper
				  functioning of the normal vent or the emergency vent.
(6) Spacing between adjacent tanks is not
				  less than 3 ft (0.9 meters).
(7)
				  The tank is capable of resisting damage from the impact of a motor vehicle or
				  suitable collision barriers are provided in locations where the tank is exposed
				  to traffic.
(8) Where the
				  interstitial space is enclosed, it is provided with emergency venting.
(9) A means is provided to
				  establish the integrity of the interstitial space of the double wall tank.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff
					 7-1-05
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 3 - SECONDARY CONTAINMENT › Section 165:26-2-32 - Secondary containment

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Aboveground storage tanks, other than those with double walls as set out in
				  165:26-2-31,
				  must have secondary containment for the fuels stored in them.
(b) Multiple products stored within the same
				  containment area must be compatible with each other.
(c) If the secondary containment area is open
				  to precipitation, it must be able to contain 110 percent of the capacity of the
				  largest tank plus the volume displaced by other tanks within the containment
				  area.
(d) The secondary containment
				  area must be constructed with materials that are compatible with the product
				  being stored.
(e) The secondary
				  containment area cannot have any uncapped drain that extends outside of the
				  containment.
(f) The secondary
				  containment must be kept intact and free of vegetation, trash, water, and all
				  other items not necessary for fuel storage.
(g) Secondary containment can be made from
				  native soil if the soil meets or exceeds the permeability rates listed in
				  Appendix J, or it can be made of concrete or steel. Generally, soil containment
				  may be preferred in open rural areas and concrete in more congested urban
				  areas. In either case the secondary containment must be impermeable for the
				  products stored in the tanks:
(1) When
				  concrete is used for secondary containment the concrete must be suitable to
				  contain the released product for as long as it would take to recover the
				  release.
(2) Soil containment not
				  meeting the permeability rates listed in Appendix J must be made impermeable by
				  use of a synthetic membrane liner made of rubber, plastic, or a geosynthetic
				  clay liner.
(3) A double-walled
				  tank would meet the criteria of secondary containment.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 3 - SECONDARY CONTAINMENT › Section 165:26-2-32.1 - Spill Prevention, Control and Countermeasure Plan

Current through Vol. 41, No. 20, July 1, 2024
(a) Owners of aboveground storage tanks must
				  comply with the Spill Prevention Control and Countermeasure (SPCC) rule found
				  in Title 40 of the Code of Federal Regulations (CFR), Part 112 (Oil Pollution
				  Prevention). If a Spill Prevention Control and Countermeasure (SPCC) plan is
				  required, it must be kept on site.
(b) The registered Professional Engineer or
				  person responsible for preparation of plan must certify that plan has been
				  prepared in accordance with good engineering practice, including consideration
				  of applicable industry standards and the requirements of 40 CFR 112; procedures
				  for required inspections and testing must be established; and the plan must be
				  adequate for the facility.
Renumbered from
					 165:26-3-22 at 23 Ok Reg 2297, eff 7-1-06; Amended at 26 Ok Reg 1831, eff
					 7-1-09
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 4 - REQUIREMENTS FOR CORROSION PROTECTION SYSTEMS › Section 165:26-2-40 - Corrosion protection

Current through Vol. 41, No. 20, July 1, 2024
(a) Any
				  portion of a tank or its piping system that is in contact with the soil must be
				  protected from corrosion by a properly engineered, installed and maintained
				  cathodic protection system in accordance with recognized standards of design,
				  such as:
(1) American Petroleum Institute
				  Publication 1632 -2002, Cathodic Protection of Underground Petroleum Storage
				  Tanks and Piping Systems;
(2)
				  National Association of Corrosion Engineers Standard RP0193 -2001, Recommended
				  Practice of External Cathodic Protection of On-Grade Metallic Storage Tank
				  Bottoms;
(3) National Association
				  of Corrosion Engineers Standard SP0169-2013, Control of External Corrosion of
				  Underground or Submerged Metallic Piping Systems;
(4) National Association of Corrosion
				  Engineers Standard SP0285-2011, Control of External Corrosion on Metallic
				  Buried, Partially Buried, or Submerged Liquid Storage Systems; and
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 4 - REQUIREMENTS FOR CORROSION PROTECTION SYSTEMS › Section 165:26-2-41 - Compliance with corrosion protection requirements and manufacturer's specifications

Current through Vol. 41, No. 20, July 1, 2024
Corrosion protection systems must be operated and
					 maintained in accordance with the manufacturer's instructions and
					 specifications to provide continuous corrosion protection to the metal
					 components of the storage tank system that are routinely in contact with the
					 ground. If any portion of an AST or metallic piping comes in contact with an
					 electrolyte (dirt, sand, gravel, etc.), cathodic protection should be applied
					 to assist in the control of corrosion. The amount of metal in contact with the
					 electrolyte will determine the appropriate selection of cathodic protection;
					 either galvanic anodes or an impressed current system. The selected cathodic
					 protection system will be designed by a corrosion expert or a qualified
					 engineer trained in the field of cathodic protection.
Renumbered from
					 165:26-3-81 at 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 4 - REQUIREMENTS FOR CORROSION PROTECTION SYSTEMS › Section 165:26-2-42 - Frequency and criteria of inspections and tests

Current through Vol. 41, No. 20, July 1, 2024
Cathodic protection systems must be inspected for proper
					 operation by a qualified corrosion technician in accordance with the following
					 requirements:
(1) Cathodic protection
				  systems must be tested within six(6) months of installation and/or repair, and
				  at least once every three(3) years thereafter by a qualified cathodic
				  protection tester, who can demonstrate education and experience in the
				  measurement of cathodic protection of buried or submerged metal piping systems
				  and metal tanks.
(2) Every
				  sixty(60) days impressed current cathodic protection systems must be inspected
				  by the owner or operator (or owner's designated representative) to ensure that
				  the equipment is working properly.
(3) The criteria used to determine that
				  cathodic protection is adequate must be consistent with a code of practice
				  developed by a nationally recognized organization, such as the National
				  Association of Corrosion Engineers (NACE).
(4) All personnel performing cathodic
				  protection system testing must have the required education, current corrosion
				  certification experience, knowledge and competence to correctly perform testing
				  services in accordance with a certified course and applicable industry
				  standards or codes.
Renumbered from
					 165:26-3-82 at 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 5 - PIPING › Section 165:26-2-51 - Piping protection

Current through Vol. 41, No. 20, July 1, 2024
Piping must be located for maximum practical protection
					 from physical damage.
Added at 21 Ok Reg
					 2079, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 5 - PIPING › Section 165:26-2-52 - Piping and gravity flow

Current through Vol. 41, No. 20, July 1, 2024
Where tanks are at an elevation that produces a gravity
					 head on the dispensing device, the tank outlet must be equipped with an
					 anti-siphon device such as a solenoid valve, positioned adjacent to and
					 downstream from the emergency valve, installed and adjusted so that liquid
					 cannot flow by gravity from the tank in case of piping or hose failure when the
					 dispenser is not in use.
Added at 21 Ok Reg
					 2079, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 5 - PIPING › Section 165:26-2-53 - Valves on piping

Current through Vol. 41, No. 20, July 1, 2024
(a) If a
				  submersible pump system is used, a UL listed emergency shutoff/shear valve must
				  be installed at each dispensing device. Both the emergency shutoff/shear valve
				  and dispensing device shall be rigidly anchored in place.
(b) If a suction pump-type dispensing device
				  with an air eliminator is used, and where the height of liquid in the tank may
				  exceed the height of the suction pump, a UL listed, vacuum-actuated
				  shutoff/shear valve or equivalent-type valve must be installed directly under
				  each dispensing device. Both the shut off/shear valve and dispensing device
				  shall be rigidly anchored in place. Tanks installed in below-grade vaults are
				  not required to comply with this requirement.
(c) Manual shutoff and check valves must be
				  equipped with a pressure-relieving device that will relieve the pressure
				  generated by thermal expansion back to the tank. Manual shutoff valves that are
				  normally open and only closed for maintenance do not require a pressure
				  relieving device.
(d) Each
				  connection to an aboveground tank through which liquid normally flows must be
				  provided with an internal or an external emergency fire valve located as close
				  as practical to the shell of the tank or submerged pump. The fill line may be
				  equipped with a check valve made of steel or nodular iron rather than a fire
				  valve. The steel check valve must be installed downstream of the block valve on
				  fill lines if a fire valve is not installed.
(e) An anti-siphon or solenoid valve must be
				  installed on each supply line according to manufacturer guidance and recognized
				  industry standards.
(f) A manual
				  shut off or ball valve must be installed on each supply line according to
				  manufacturer guidance and recognized industry standards.
(g) All valves must meet the construction
				  criteria of
				  165:26-2-54.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 23 Ok Reg
					 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 5 - PIPING › Section 165:26-2-54 - Aboveground storage tank piping materials

Current through Vol. 41, No. 20, July 1, 2024
(a) The design, fabrication, assembly, test
				  and inspection of the piping system from the fuel tank to the fuel dispensers
				  must be in accordance with the piping manufacturers installation
				  recommendations and instructions.
(b) Pipes, valves, couplings, flexible
				  connectors, fittings and other pressure containing parts must be installed in
				  accordance with Petroleum Equipment Institute RP200,
Recommended
				  Practices for Installation of Aboveground Storage Systems for Motor Vehicle
				  Fueling
.
(c) Refer to
				  Subchapter 8 for guidelines regarding over-water piping used at
				  marinas.
(d) Valves at storage
				  tanks and their connections to the tank must be of steel or nodular iron. Low
				  melting point materials such as aluminum, copper, brass or non-ductile material
				  such as cast iron may be used in aboveground piping provided that they are
				  located downstream of an approved steel or nodular iron emergency valve that
				  has been installed and located as close as practical to the shell of the tank
				  or submerged pump.
(e) Valves at
				  storage tanks may be other than steel or nodular iron if the valves are
				  installed internal to the tank.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Amended at 23 Ok Reg 2297, eff 7-1-06; Amended at
					 25 Ok Reg 2187, eff 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 5 - PIPING › Section 165:26-2-55 - Underground piping materials

Current through Vol. 41, No. 20, July 1, 2024
(a) All new underground product piping and
				  ancillary equipment installed at a new facility or existing facility must have
				  the following characteristics:
(1)
				  Non-metallic;
(2) Double-walled;
(3) A tracer locator wire must be
				  installed in all piping trenches; and
(4) Dispenser sumps must be installed and
				  monitored with sensors as per
				  165:26-3-20.2.
(5) Piping transition sumps must be installed
				  and monitored with sensors if the interstice area of connecting piping cannot
				  be connected in an approved manner.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 5 - PIPING › Section 165:26-2-56 - Installation and monitoring requirements for piping [AMENDED AND RENUMBERED TO 165:26-3-20.2]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Amended and renumbered to 165:26-3-20.2 at 23 Ok
					 Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 5 - PIPING › Section 165:26-2-57 - Commission-approved alternative methods [RENUMBERED TO 165:26-3-20.3]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Renumbered to 165:23-3-20.3 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 7 - VAULT REQUIREMENTS › Section 165:26-2-71 - Vaults

Current through Vol. 41, No. 20, July 1, 2024
A vault is allowed above or below grade and must meet NFPA
					 30 and NFPA 30A requirements.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 25 Ok Reg
					 2187, eff 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 9 - DISPENSER REQUIREMENTS › Section 165:26-2-91.1 - Display on dispenser

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Every dispenser or delivery device regulated by the Commission used for sale of
				  motor fuel to the public must legibly display the type of motor fuel offered
				  for sale.
(b) Any motor fuel must
				  be displayed in accordance with
				  16
				  CFR Part 306.0 through
				  306.12, including
				  Appendices; and sold as provided for by Commission rules and National Institute
				  of Standards and Technology (NIST) Handbook 44, "Specifications, Tolerances,
				  and Other Technical Requirements for Weighing and Measuring Devices".
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 9 - DISPENSER REQUIREMENTS › Section 165:26-2-91 - Dispensers

Current through Vol. 41, No. 20, July 1, 2024
(a) Liquids must be
				  transferred from storage tanks by means of fixed pumps designed and equipped to
				  allow control of the flow and prevent leakage or accidental discharge.
(b) Dispensing devices for Class I
				  and Class II liquids must be listed.
(1)
				  Existing listed or labeled dispensing devices may be modified provided the
				  modifications made are "Listed by Report" by an approved testing laboratory or
				  as otherwise approved by PSTD.
(2)
				  Modification proposals must contain a description of the component parts used
				  in the modification and the recommended methods of installation on specific
				  dispensing devices, and they must be made available to PSTD for approval prior
				  to installation.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 9 - DISPENSER REQUIREMENTS › Section 165:26-2-92 - Dispenser hose

Current through Vol. 41, No. 20, July 1, 2024
(a) Listed hose
				  assemblies must be used to dispense fuel.
(1)
				  Hose length at facilities will not exceed eighteen feet (18') (5.5
				  m).
(2) Hose at retail and marina
				  facilities must be checked daily for evidence of blistering, carcass saturation
				  or separation, cuts, nicks or abrasions that expose reinforcement material and
				  for slippage, misalignment or leaks at couplings.
(3) Hoses on dispensers that are connected to
				  above-ground tanks within a fenced area may not exceed fifty feet (50') in
				  length and must be secured, such as with a hose reel, to protect it from
				  damage.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 9 - DISPENSER REQUIREMENTS › Section 165:26-2-93 - Nozzles

Current through Vol. 41, No. 20, July 1, 2024
At any installation where the normal flow of product may be
					 stopped other than by the hose nozzle valve such as at pre-pay stations, the
					 system must include listed equipment with a feature that causes or requires the
					 closing of the hose nozzle valve before product flow can be resumed or before
					 the hose nozzle valve can be replaced in its normal position in the dispenser;
					 or the hose nozzle valve must not be equipped with a latch-open
					 device.
Added at 21 Ok Reg
					 2079, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 11 - TANK FILLING PROCEDURES › Section 165:26-2-111 - Tank filling operation

Current through Vol. 41, No. 20, July 1, 2024
A delivery vehicle must be separated from any aboveground
					 tank by at least 25 ft. (7.6 m) if possible.
(1) No minimum separation distance is
				  required for tanks that are filled by gravity.
(2) The required minimum separation distance
				  will be reduced to 15 ft. (4.6 m) where the fuel being delivered is not a Class
				  I liquid.
Added at 21 Ok Reg
					 2079, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 13 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-2-131 - Fencing

Current through Vol. 41, No. 20, July 1, 2024
(a) Tanks not
				  enclosed in vaults must be enclosed with a chain link fence at least 6 ft. (2m)
				  high. The fence must be separated from the tanks by at least 10 ft (3 m) and
				  must have a gate that is secured against unauthorized entry.
(b) The area within the fence must be kept
				  free of vegetation, debris and any other material that is not necessary to the
				  proper operation of the tank and piping system.
(c) Tanks are not required to be enclosed
				  within a fence if the property on which the tanks are located already has a
				  perimeter security fence.
(d) A
				  fence may not be required if another method effectively restricts access to the
				  tanks.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 23 Ok Reg 144, eff 10-6-05 (emergency); Amended at
					 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 13 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-2-132 - Required signs

Current through Vol. 41, No. 20, July 1, 2024
(a) Warning
				  signs must be conspicuously posted in the dispensing area incorporating the
				  following or equivalent wording:
(1)
				  WARNING.
(2) It is unlawful and
				  dangerous to dispense gasoline into unapproved containers.
(3) No smoking.
(4) Stop motor.
(5) No filling of portable containers in or
				  on a motor vehicle.
(6) Place
				  container on ground before filling.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 13 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-2-133 - Sources of ignition

Current through Vol. 41, No. 20, July 1, 2024
(a)
				  Smoking materials, including but not limited to matches and lighters, must not
				  be used within 20 ft. (6 m) of areas used for fueling, servicing fuel systems
				  for internal combustion engines, or receiving or dispensing of Class I
				  liquids.
(b) Conspicuous and
				  legible signs prohibiting smoking must be posted within sight of the customer
				  being served.
(c) The motors of all
				  equipment being fueled must be shut off during the fueling operation, except
				  for emergency generators, pumps, etc., where continuing operation is
				  essential.
Added at 21 Ok Reg
					 2079, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 13 - MISCELLANEOUS SAFETY PROVISIONS › Section 165:26-2-134 - Monitoring requirements [AMENDED AND RENUMBERED TO 165:26-3-20.1]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 23 Ok Reg 144, eff 10-6-05 (emergency); Amended
					 and renumbered to 165:26-2-20.1 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 15 - ELECTRICAL › Section 165:26-2-151 - Electrical requirements

Current through Vol. 41, No. 20, July 1, 2024
(a) All
				  electrical work must be performed by a licensed electrician.
(b) All electrical wiring and electrical
				  utilization equipment must be of a type specified by and must be installed in
				  accordance with NFPA 30A and NFPA 70, National Electrical Code.
(c) Clearly identified and easily accessible
				  switch(es) or circuit breaker(s) must be provided at a location remote from
				  dispensing devices, including remote pumping systems, to shut off the power to
				  all dispensing devices in the event of an emergency. The switch or circuit
				  breaker must be a minimum of twenty feet (20') and not more than one hundred
				  feet (100') away from dispensing devices.
(d) Electrical equipment that was installed
				  in compliance with an earlier state or national code will not require
				  modification unless the equipment is hazardous to people or property.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 23 Ok Reg
					 2297, eff 7-1-06; Amended at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 17 - INSTALLATION OF ABOVEGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:26-2-171 - Aboveground storage tank system installation [AMENDED AND RENUMBERED TO 165:26-2-8]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Amended and renumbered to 165:26-2-8 at 23 Ok Reg
					 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 17 - INSTALLATION OF ABOVEGROUND STORAGE TANK SYSTEMS [Revoked] › Section 165:26-2-172 - Compatibility [RENUMBERED TO 165:26-2-1.2]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Renumbered to 165:26-2-1.2 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 19 - REPAIRS TO ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-191 - Repairs to aboveground tank systems

Current through Vol. 41, No. 20, July 1, 2024
Repairs to an aboveground storage tank system, excluding
					 electrical work, must be performed by an AST Installer. Routine maintenance
					 such as painting and repairs to a product dispensing unit will not be
					 considered repairs to the storage tank system.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 25 Ok Reg
					 2187, eff 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 21 - REMOVAL AND CLOSURE OF ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-210 - Tank removal and closure

Current through Vol. 41, No. 20, July 1, 2024
(a) Owners and
				  Operators of all aboveground storage tank systems must notify the Petroleum
				  Storage Tank Division at least fourteen (14) days prior to the removal or
				  permanent closure of aboveground storage tanks and/or lines by submitting the
				  PSTD scheduling form and receiving confirmation of the scheduled removal from
				  PSTD. When scheduling a removal, a site map of where samples are to be taken
				  should be attached to the scheduling form. If events require a change in the
				  date of removal, the Division shall be given forty-eight (48) hours' notice
				  prior to the new date.
(b) An
				  authorized agent of PSTD may be present to observe the removal and to inspect
				  the closed tank system and the surrounding environment prior to
				  backfilling.
(c) Tanks, lines and
				  ancillary equipment must be removed upon closure unless a Commission order
				  grants a variance.
(d) An AST
				  Remover must remove aboveground storage tank systems.
(e) Photos must be taken of tank(s), line(s),
				  and soil at removal. In the event there is a hole in a tank or line, further
				  photographic evidence is required. If tank(s), line(s) or excavated soil show
				  evidence of a release, photos of the apparent release must be taken that
				  indicate the release source.
Added at 23 Ok Reg
					 2297, eff 7-1-06; Amended at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 21 - REMOVAL AND CLOSURE OF ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-211 - Compliance with removal and closure requirements

Current through Vol. 41, No. 20, July 1, 2024
Owners and/or operators of aboveground storage tank systems
					 that are temporarily taken out of service or permanently removed, must comply
					 with all the requirements of this Part.
Added at 21 Ok Reg
					 2079, eff 7-1-04
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 21 - REMOVAL AND CLOSURE OF ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-212 - Temporary removal from service

Current through Vol. 41, No. 20, July 1, 2024
When an aboveground storage tank system is taken
					 temporarily out of service, the owner or operator must:
(1) Drain all fluid to less than one inch
				  (1") of residue remaining in the tank.
(2) Leave all vent lines open and
				  functioning.
(3) Cap and secure
				  all other lines, pumps, manways and ancillary equipment.
(4) Lock all fill caps.
(5) Notify PSTD of a change in service on the
				  prescribed form within thirty (30) days.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 21 - REMOVAL AND CLOSURE OF ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-212.1 - Requirements for returning to service

Current through Vol. 41, No. 20, July 1, 2024
(a) All tanks
				  out of service for more than twelve (12) months are required to be tightness
				  tested and test results submitted to PSTD before returning to
				  service.
(b) A tightness test must
				  be performed by a certified tester and must be completed on the underground
				  portion of out of service systems if more than twelve (12) months have elapsed
				  since the last tightness test. Any system failure will require either closure
				  or upgrade of the failed portion.
(c) All systems out of service for more than
				  twelve (12) months are required to meet all the requirements of this
				  Chapter.
(d) All underground
				  storage tanks being used as aboveground storage tanks that have been out of
				  service for more than twelve (12) months may not be returned to
				  service.
Renumbered from
					 165:26-2-215 at 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 21 - REMOVAL AND CLOSURE OF ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-213 - Permanent closure

Current through Vol. 41, No. 20, July 1, 2024
Owners and/or operators of aboveground storage tank
					 systems who do not intend to use the tanks for fuel storage in the future must
					 close the tank systems after they have been out of service for more than twelve
					 (12) months by performing the following:
(1) Empty, clean, purge and devaporize the
				  tank of all flammable products.
(2)
				  Separate the piping from the tank. All underground piping and ancillary
				  equipment must be removed unless a Commission order grants a
				  variance.
(3) Perform a site
				  assessment pursuant to
				  165:26-2-214, "Assessing the site
				  at tank closure or change in service".
(4) An AST Remover must be on site at all
				  times during the removal of an aboveground storage tank and/or lines.
(5) All UST's currently being used as AST's
				  must be destroyed upon closure. A certificate of destruction must be included
				  with the AST Closure Report and submitted to PSTD within forty-five (45) days
				  of closure.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff
					 7-1-05
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 21 - REMOVAL AND CLOSURE OF ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-214 - Assessing the site at tank closure or change in service

Current through Vol. 41, No. 20, July 1, 2024
(a) Before permanent closure or a change in
				  service is completed, the owner or operator must measure for the presence of a
				  release where contamination is most likely to be present at the aboveground
				  storage tank system site. Please refer to the PSTD sampling document when
				  choosing sample locations.
(b) For
				  tank systems containing petroleum product, analyses must be done for both TPH
				  and BTEX.
(c) If contaminated
				  soils, contaminated groundwater, or free product as a liquid or vapor is
				  discovered, the owner must immediately begin corrective action in accordance
				  with Chapter 29 of Commission rules.
(d) Any sampling at closures must be
				  conducted under the supervision of a Licensed Environmental
				  Consultant.
(e) The requirements of
				  this Section do not apply to aboveground storage tanks which are located in or
				  on buildings.
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 25 Ok Reg
					 2187, eff 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 2 - General Requirements for Aboveground Storage Tank Systems › Part 21 - REMOVAL AND CLOSURE OF ABOVEGROUND STORAGE TANK SYSTEMS › Section 165:26-2-215 - Requirements for returning to service [RENUMBERED TO 165:26-2-212.1]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Renumbered to
					 165:26-2-212.1 at 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION, REPORTING, AND INVESTIGATION [Revoked] › Section 165:26-3-1 - Release prohibition [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 12 Ok Reg 2057, eff 7-1-95; Revoked at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION, REPORTING, AND INVESTIGATION [Revoked] › Section 165:26-3-2 - Release reporting [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 12 Ok Reg 2057, eff 7-1-95; Revoked at 17 Ok Reg
					 2875, eff 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 1 - RELEASE PROHIBITION, REPORTING, AND INVESTIGATION [Revoked] › Section 165:26-3-3 - Release, investigation, and confirmation [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 12 Ok Reg 2057, eff 7-1-95; Amended at 15 Ok Reg
					 3020, eff 7-15-98; Revoked at 17 Ok Reg 2875, eff
					 7-15-00
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-11 - Availability of records [RENUMBERED TO 165:26-1-55]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 14 Ok Reg 2515, eff 7-1-97; Amended at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Renumbered to 165:26-1-55 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-12 - Repair records [RENUMBERED TO 165:26-1-56]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 14 Ok Reg 2515, eff 7-1-97; Amended at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 22 Ok Reg 1752, eff 7-1-05; Renumbered to
					 165:26-1-56 at 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-13 - Tank installation, closure and removal records [RENUMBERED TO 165:26-1-57]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 14 Ok Reg 2515, eff 7-1-97; Amended at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Renumbered to 165:26-1-57 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-14 - Release detection and corrosion protection records [RENUMBERED TO 165:26-1-58]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 12 Ok Reg 2057, eff 7-1-95; Amended at 17 Ok Reg
					 2875, eff 7-15-00; Amended at 21 Ok Reg 2079, eff 7-1-04; Amended at 22 Ok Reg
					 1752, eff 7-1-05; Renumbered to 165:26-1-58 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-15 - Spill and overfill records [RENUMBERED TO 165:26-1-59]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 17 Ok Reg 2875, eff 7-15-00; Renumbered to
					 165:26-1-59 at 23 Ok Reg 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-16 - Piping records [RENUMBERED TO 165:26-1-60]

Current through Vol. 41, No. 20, July 1, 2024
Added at 17 Ok Reg
					 2875, eff 7-15-00; Renumbered to 165:26-1-60 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-17 - Underground line tightness testing [RENUMBERED TO 165:26-1-48]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Renumbered to 165:26-1-48 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 3 - RECORDKEEPING [Revoked] › Section 165:26-3-18 - Inventory records [RENUMBERED TO 165:26-1-61]

Current through Vol. 41, No. 20, July 1, 2024
Added at 21 Ok Reg
					 2079, eff 7-1-04; Renumbered to 165:26-1-61 at 23 Ok Reg 2297, eff
					 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 4 - RELEASE DETECTION › Section 165:26-3-19 - General monitoring requirements

Current through Vol. 41, No. 20, July 1, 2024
Tanks must be monitored at least every 30 days for releases
					 using one of the methods or combinations of methods listed in this
					 Chapter.
Added at 23 Ok Reg
					 2297, eff 7-1-06
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 4 - RELEASE DETECTION › Section 165:26-3-20 - General release detection methods and devices

Current through Vol. 41, No. 20, July 1, 2024
(a) Owners and operators of new and existing
				  aboveground storage tank systems must use a release detection method, or a
				  combination of release detection methods, that is:
(1) Capable of detecting a release of
				  regulated substances from any portion of the aboveground storage tank system
				  that routinely contains product.
(2) Designed, installed, calibrated,
				  operated, and maintained in accordance with the manufacturer's instructions,
				  including routine maintenance and service checks for operability or running
				  conditions.
(3) Capable of meeting
				  the performance requirements of this Chapter, with any performance claims and
				  their manner of determination described in writing by the equipment
				  manufacturer or installer.
(4)
				  Sampled, tested, or checked for a release at least once every 30
				  days.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 4 - RELEASE DETECTION › Section 165:26-3-20.1 - Monitoring requirements for aboveground tanks and aboveground piping

Current through Vol. 41, No. 20, July 1, 2024
One of the following methods must be used:
(1)
Visual Monitoring.
(A) Visual inspection of the aboveground
				  storage tank systems to identify cracks or other defects in the secondary
				  containment area and product transfer area.
(B) Visual inspection of the exterior surface
				  of the tanks, piping, valves, pumps and other equipment for cracks, corrosion,
				  releases and maintenance deficiencies; and identify poor maintenance, operating
				  practices or malfunctioning equipment.
(C) Visual inspection of elevated tanks or
				  tanks on concrete slabs.
(D) Visual
				  inspection of the area between the tank's outer shell or the tank's floor and
				  containment area or a vapor monitoring of the soil directly under the tank
				  bottom or perimeter and the water table, unless the tank containment has a
				  sound concrete floor.
(E) Visual
				  inspections are not adequate where due to the nature of the aboveground storage
				  tank and/or its secondary containment it cannot be determined whether a leak
				  has occurred. A good example would be a vertical tank that is not raised off
				  the ground, making it impossible to visually inspect its bottom, and is not
				  sitting on a sound concrete slab within sound secondary containment.
(F) An annual line tightness test performed
				  by a certified tester may be used in lieu of thirty (30) day visual monitoring
				  for aboveground product piping.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 4 - RELEASE DETECTION › Section 165:26-3-20.2 - Installation and monitoring requirements for underground piping

Current through Vol. 41, No. 20, July 1, 2024
Underground piping that routinely contains regulated
					 substances must be installed and monitored for releases in a manner that meets
					 the following requirements:
(1)
Pressurized piping.
(A) Piping
				  that conveys regulated substances under pressure must be equipped with an
				  automatic line leak detector installed and operated in accordance with this
				  Chapter.
(B) New installations and
				  facilities replacing a piping system must have at least one (1) sump sensor,
				  float or similar mechanical device for each tank system, located at the bottom
				  of the lowest piping gradient sump. The interstitial area of the piping must be
				  open inside the sumps to allow fuel to drain into the sumps in the event that a
				  leak occurs. Sensors must be mounted at the bottom of the sump(s) and
				  accessible for testing.
(C)
				  Underground pressure piping from a master dispenser to a satellite dispenser
				  must be designed and installed so that the satellite piping is tested by the
				  automatic line leak detector. An annual line tightness test is required on the
				  satellite underground piping.
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 4 - RELEASE DETECTION › Section 165:26-3-20.3 - Commission-approved alternative methods [REVOKED]

Current through Vol. 41, No. 20, July 1, 2024
Renumbered from
					 165:26-2-57 at 23 Ok Reg 2297, eff 7-1-06; Revoked at 25 Ok Reg 2187, eff
					 7-11-08
Oklahoma Administrative Code › Title 165 - Corporation Commission › Chapter 26 - Aboveground Storage Tanks › Subchapter 3 - Release Prevention and Detection Requirements › Part 5 - SPILL AND OVERFILL PREVENTION REQUIREMENTS [Revoked] › Section 165:26-3-21 - General spill and overfill prevention requirements [AMENDED AND RENUMBERED TO 165:26-2-5.1]

Current through Vol. 41, No. 20, July 1, 2024
Added at 9 Ok Reg
					 2719, eff 7-13-92; Amended at 17 Ok Reg 2875, eff 7-15-00; Amended at 21 Ok Reg
					 2079, eff 7-1-04; Amended at 22 Ok Reg 1752, eff 7-1-05; Amended at 23 Ok Reg
					 144, eff 10-6-05 (emergency); Amended and renumbered to 165:26-2-5.1 at 23 Ok
					 Reg 2297, eff 7-1-06