reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-5 - Electrical, mechanical, and illumination requirements

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 5.
(a)
				Mechanical equipment shall be installed in accordance with 675 IAC 18, the
				Indiana Mechanical Code.
(b)
				Electrical equipment, system wiring, and grounding of all spa equipment and
				appurtenances shall be in accordance with 675 IAC 17, the Indiana Electrical
				Code.
(c) An emergency shutdown
				device shall be installed that will immediately cut power to the pump serving
				the main outlets. This emergency shutdown device shall be:
(1) readily accessible in the event of an
				emergency;
(2) distinctly labeled
				as EMERGENCY SPA SHUTDOWN DEVICE; and
(3) installed in the same room as the spa and
				within site of the spa.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-6 - Inlets

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 6.
(a) Spa
				inlets and outlets shall be arranged to produce a uniform circulation of water
				throughout the spa.
(b) Water
				velocity in the spa piping shall not exceed ten (10) feet per second with the
				following exceptions:
(1) Suction velocity
				shall not exceed six (6) feet per second.
(2) Water velocity in existing asbestos
				cement pipe shall not exceed six (6) feet per second.
(3) Water velocity in copper pipe shall not
				exceed eight (8) feet per second.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-6.1 - Outlets

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 6.1.
(a) Spa
				inlets and outlets shall be arranged to:
(1)
				produce a uniform circulation of water; and
(2) facilitate the maintenance of a uniform
				disinfectant residual throughout the spa.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-7 - Circulation systems

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 7.
(a) Every
				spa shall be provided with an approved type circulation system capable of
				turning over the entire spa water capacity in not less than thirty (30)
				minutes.
(b) All circulation shall:
(1) go through the spa filtration system;
				and
(2) be chemically treated prior
				to injection into the spa.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-8 - Waste water disposal

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 8.
Waste water shall be discharged to a point in accordance with
				  327 IAC, the rules of the water pollution control board, through an approved
				  airgap or other means in accordance with 675 IAC 16, the Indiana Plumbing
				  Code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-9 - Enclosure

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 9.
All public spas shall be enclosed by a fence, wall, building,
				  or other enclosure that is not less than six (6) feet high to aid in the
				  control of the movement of bathers and to discourage the entrance of unwanted
				  persons.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-10 - Disinfectant equipment and chemical feeders

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 10.
Disinfectant equipment and chemical feeders shall be as
				  follows:
(1) Capable of automatically
				providing a continuous residual chemical effect in accordance with 410 IAC, the
				rules of the Indiana state department of health.
(2) Of an approved type.
(3) Installed downstream from the
				pump.
(4) Wired so they will not
				operate unless the filter pump is operating.
An exception is erosion-type chlorinators may feed their
				  solution to the suction side of the pump.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 3 - Public Spas › Section 3-11 - Water supply

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 11.
(a) The
				water supply serving the spa shall meet 327 IAC, the rules of the water
				pollution control board, before any bather uses the spa.
(b) No direct mechanical connection shall be
				made between the potable water supply and the pool, disinfectant equipment,
				chemical feeders, or system piping for the pool unless it is protected against
				backflow and siphonage in a manner acceptable under 675 IAC 16, the Indiana
				Plumbing Code, or through an approved airgap meeting that same code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-1 - Water attractions, water attraction complexes; general

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 1.
(a) Any new
				construction or alteration of a water attraction or water attraction complex
				shall be designed and installed as specified under this rule.
(b) Wading pools are not water attractions
				and shall conform to 675 IAC 20-2.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-2 - Content of plans; filing requirements

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 2.
(a) Plans
				and specifications for all water attractions shall be submitted under 675 IAC
				12, the general administrative rules, for design release prior to the
				construction, rehabilitation, or alteration of:
(1) any public water attraction or semipublic
				water attraction;
(2) their
				appurtenant equipment;
(3)
				decks;
(4) bathhouses;
				and
(5) appliances;
necessary to maintain the facility in a safe and sanitary
				  condition. Plans and specifications for a public water attraction or a
				  semipublic water attraction shall be prepared under the supervision of and be
				  certified by a design professional, as defined in
				  675 IAC
				  12-6-2.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-3 - Materials of construction

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 3.
Water attractions and all appurtenances thereto shall be
				  constructed of materials that:
(1) are
				nontoxic to humans and the environment;
(2) are impervious and enduring;
(3) can withstand the design
				stresses;
(4) will provide a
				watertight structure with an easily cleaned surface without cracks or joints,
				excluding structural joints; or
(5)
				an easily cleaned surface finish is applied or attached.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-4 - Structural design

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 4.
(a) All
				water attractions shall be designed and constructed to withstand all
				anticipated loading for both empty and full conditions, and a hydrostatic
				relief valve shall be provided for all in-ground water attractions. The design
				professional as described in 675 IAC 12-6 shall be responsible for ensuring
				that the design and construction comply with the requirements for the
				structural stability as described above.
(b) Sand or earth shall not be permitted as
				an interior finish in a public water attraction.
(c) In all water attractions not completely
				enclosed in a heated building, the shell and appurtenances, piping, filter
				system, pump, motor, and other components shall be so designed and constructed
				to facilitate protection from damage due to freezing.
(d) The surfaces within a water attraction
				intended to provide footing for bathers shall be designed to provide a
				slip-resisting surface. The roughness or irregularity of the surfaces shall not
				provide an abrasion hazard to the feet during normal use.
(e) The color, pattern, or finish of the
				basin interior shall not obscure the existence or presence of objects or
				surfaces within the structure. The floor of all water attractions shall be
				white, light colored, or light colored patterns in order to facilitate the
				identification of any objects. "Light colored" means having a light reflectance
				value (LRV) of fifty percent (50%) or more.
(f) The splash zone shall be sloped to drain
				to the surge tank or pool within the same basin.
(g) The maximum floor slope to drain of the
				splash zone shall be 1:12.
(h) All
				exterior walking surfaces shall be sloped to drain away from the splash zone.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-5 - Dimensional design

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 5.
(a) No
				limits are specified for the shape of water attractions except that
				consideration shall be given to shape from the standpoint of safety and
				circulation of the water.
(b) There
				shall be no protrusions, extensions, means of entanglement, or other
				obstructions in the bathing area that can cause the entrapment or injury of the
				bather.
(1) At no time shall interior basin
				divider walls be submerged during operation.
(2) Interior basin divider walls shall not
				exceed eighteen (18) inches in width.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-6 - Floor

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 6.
(a) All
				slopes shall be uniform and shall slope to the drain or the water evacuation
				area.
(1) Where water depths are less than
				five (5) feet, floor slopes shall not exceed 1:12.
(2) Where the water depth is five (5) feet or
				more, floor slopes shall not exceed 1:3.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-7 - Walls

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 7.
Basin walls shall be vertical or within eleven (11) degrees
				  of vertical for a minimum distance of two (2) feet nine (9) inches from the
				  waterline in deep areas or two (2) feet three (3) inches in shallow areas and
				  curved to join the floor.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-8 - Depths

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 8.
(a) The
				transition point between the wading area and deeper areas of a water attraction
				shall be visually set apart with depth numbers, a four (4) inch width row of
				floor tile, painted line, or similar means of a color contrasting with the
				bottom. In all basins with diving equipment, the shallow area shall be visually
				set apart from the deep area with a transition line, depth numbers, and a four
				(4) inch color contrasting with the bottom.
(b) The water depth of all water attractions
				shall be as established by the manufacturer.
(c) Activity pools having a patron accessible
				depth greater than five (5) feet shall have a transition line as specified.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-9 - Diving equipment

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 9.
When diving equipment is installed in a water attraction, it
				  shall conform to 675 IAC 20-2.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-10 - Offset ledges

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 10.
(a) Offset
				ledges, when provided, shall:
(1) fall within
				eleven (11) degrees from vertical starting at the junction of the basin wall
				and waterline; and
(2) have a
				slip-resisting surface.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-11 - Separation distance

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 11.
Separate wading pools and interactive play attractions shall
				  be physically set apart by at least twenty (20) feet from water attraction
				  basins deeper than twenty-four (24) inches or by a barrier, not less than four
				  (4) feet high, that creates a minimum travel distance of twenty (20) feet.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-12 - Deck requirements

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 12.
(a) Deck
				work shall be designed and installed so as to include the quality of subbase,
				concrete mix design, reinforcing, joints, and finishes. Work performed in
				accordance with the American Concrete Institute (ACI) Standard 302.1R-04,
				"Guide for Concrete Floor and Slab Construction" may be deemed to comply with
				this requirement.
(b) Decks, ramps,
				and similar surfaces, including step treads and coping, shall be slip-resistant
				and easily cleanable. The roughness or irregularity of the surfaces shall not
				cause injury or provide an abrasion during normal use. Depth markers, pool
				brand insignias, or similar special features located in or on the deck shall
				conform to this section.
(c) Deck
				surfaces shall be provided at all perimeter areas of water attractions
				specified as entry or exit points.
(d) Deck surfaces shall be of nontoxic,
				natural or man-made, impervious materials.
(e) Steps for the deck outside the perimeter
				shall be in accordance with 675 IAC 13, the Indiana Building Code.
(f) The unobstructed deck width provided
				around deck equipment, including:
(1)
				handrails;
(2) structural support
				columns;
(3) lifeguard chairs;
				and
(4) play equipment;
shall be a minimum of four (4) feet.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-13 - Means of entry and exit

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 13.
(a) All
				public water attractions shall have not less than two (2) means of entry and
				exit located so as to serve opposite sides of the basin. Basins or water areas
				over thirty (30) feet in width shall have not less than one (1) means of entry
				and exit on each side. Not less than one (1) means of entry and exit shall be
				provided for each seventy-five (75) linear feet, or fraction thereof, of basin
				perimeter, unless covered in Table 13-1 of this rule. An exception is leisure
				rivers with one (1) means of entry and exit every three hundred (300) feet of
				basin perimeter.
(b) Where water
				depths are twenty-four (24) inches or less at the basin wall, the basins shall
				be considered as providing their own natural means of entry and exit.
(c) The design and construction of protruding
				and recessed stairs and ramps within a basin shall conform to the following:
(1) Stair treads shall have a minimum
				unobstructed horizontal tread depth of ten (10) inches and a minimum
				unobstructed surface area of two hundred forty (240) square inches. The nose of
				the stair tread shall:
(A) have a
				slip-resistant surface finish; and
(B) be visually set apart with a minimum two
				(2) inch width row of floor tile, painted line, or similar means of a color
				contrasting with the bottom.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-14 - Circulation systems

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 14.
(a) A
				circulation system consisting of:
(1)
				pumps;
(2) piping;
(3) overflows;
(4) skimmers;
(5) filters; and
(6) other necessary equipment;
shall be provided for complete and continuous circulation of
				  water through all parts of the water attraction.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-15 - Filters

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 15.
(a) Filters
				shall be designed and constructed so that, after cleaning per manufacturer's
				instructions, the system can provide the water clarity such that a six (6) inch
				black disc, placed upon a white background, is clearly visible at the deepest
				point of the water attraction when viewed from the edge of the water
				attraction.
(b) Filters shall be
				designed so that filtration surfaces can be inspected and serviced.
(c) On pressure-type filters, a means shall
				be provided to permit the release of air that enters the filter tank. Any
				filter incorporating an automatic internal air release as its principal means
				of air release must have lids that provide a slow and safe release of pressure
				as a part of its design. Any separation tank used in conjunction with any
				filter tank must have a manual means of air release or lid that provides a slow
				and safe release of pressure as they are opened as a part of its
				design.
(d) Pressure filters and
				separation tanks shall have operation and maintenance instructions permanently
				installed on the filter or separation tank and shall include a precautionary
				statement warning not to start up the system after maintenance without first
				opening the air release and proper reassembly of the filter and separation
				tank. The statement must be visible and noticeable within the area of the air
				release.
(e) Piping furnished with
				the filter shall be of suitable material capable of withstanding one and
				one-half (1 1/2) times the working pressure.
(f) Filter components that require servicing
				shall be accessible for inspection and repair when installed according to the
				manufacturer's instructions.
(g)
				The rate of filtration shall not exceed three (3) gallons per minute per square
				foot of filter surface unless the filtration system is specifically listed and
				labeled for use above said rate.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-16 - Pumps

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 16.
(a) A pump
				and motor shall be provided for circulation of the water attraction water.
				Performance of all pumps shall meet or exceed the conditions of flow required
				for filtering and cleaning (if applicable) the filters against the total
				dynamic head developed by the complete system.
(b) Water entering the pump or pumps shall
				pass through the removable strainer. Strainers are permitted before the filter
				when used with submersible pumps.
(c) Pumps shall be selected to perform the
				functions for which they were intended. Pumps and motors must be accessible for
				inspection and service.
(d) All
				motors shall have as a minimum an open, drip-proof enclosure and be constructed
				electrically and mechanically so they will perform satisfactorily under the
				conditions of load and environment normally encountered in water attraction
				installations.
(e) Motors shall be
				capable of operating the pump under full load with a voltage variation of at
				least five percent (5%) from nameplate rating. If the maximum service factor of
				the motor is exceeded (at full voltage), the manufacturer shall indicate this
				on the pump curve.
(f) All motors
				shall have thermal or current overload protection, either built-in or in the
				line starter, to provide locked rotor and running protection.
(g) The motor frame shall contain adequate
				provisions for proper grounding. When a pump is installed below the waterline
				of a water attraction, valves shall be installed on permanently connected
				suction and discharge lines, located in a place outside the walls of the basin,
				where they will be readily accessible for maintenance and removal of the
				pump.
(h) Pressure and vacuum
				gauges shall be installed on all water attractions and the:
(1) vacuum gauge shall be installed as close
				to the pump suction inlet as possible and still maintain an accurate reading;
				and
(2) pressure gauge shall be
				installed on the face piping ahead of the filter or on the top of the filter in
				the area of greatest filter pressure.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-17 - Inlets

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 17.
(a) Water
				attraction inlets for circulated water shall be located to:
(1) produce uniform circulation of water;
				and
(2) facilitate the maintenance
				of a uniform disinfectant residual throughout the entire water attraction.
Where skimmers are used, the inlets shall be located so as to
				  help bring floating particles within range of the skimmers.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-18 - Outlets

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 18.
(a) Water
				attraction inlets and outlets for circulated water shall be located to:
(1) produce uniform circulation of water;
				and
(2) facilitate the maintenance
				of a uniform disinfectant residual throughout the entire pool.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-19 - Perimeter overflow systems

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 19.
(a) A
				surface skimming system shall be:
(1) provided
				on all public water attractions, except leisure rivers, action rivers, or wave
				pools; and
(2) designed and
				constructed to skim the water attraction surface when the water level is
				maintained within the operational parameters of the system's rim or weir
				device.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-20 - Electrical, mechanical, and illumination requirements

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 20.
(a) The
				requirements of 675 IAC 17, the Indiana Electrical Code, shall be followed for
				the wiring, grounding, bonding, and installation of electrical equipment and
				metallic appurtenances to the water attraction.
(b) Artificial lighting shall be provided for
				all water attractions to be used indoors or water attractions used during
				periods of darkness. The lighting shall be sufficient to make a six (6) inch
				black disc, placed on a white background clearly visible from the side of the
				water attraction when that disc is placed on the floor of the water
				attraction.
(c) Mechanical
				equipment shall be designed and installed in accordance with the requirements
				of 675 IAC 18, the Indiana Mechanical Code. Corrosion-resistant fan and
				ductwork shall be installed in the enclosed disinfectant chemical feed room or
				rooms.
(d) Heaters shall be
				installed and tested to comply with the requirements under the 675 IAC 25,
				Indiana Fuel Gas Code for gas applications or 675 IAC 17, the Indiana
				Electrical Code for electrical applications.
(e) Overhead clearance shall be the same as
				for swimming pools as found in the Indiana Electrical Code (675 IAC 17).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-21 - Wastewater disposal

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 21.
Wastewater shall be discharged to a point in accordance with
				  327 IAC, the rules of the water pollution control board, through an approved
				  airgap or other means in accordance with 675 IAC 16, the Indiana Plumbing Code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-22 - Water supply

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 22.
(a) The
				water supply serving the water attraction shall meet 327 IAC, the rules of the
				water pollution control board, before any bather uses the water
				attraction.
(b) No direct
				mechanical connection shall be made between the potable water supply and the
				water attraction, disinfectant equipment, chemical feeders, or system piping
				for the water attraction unless it is protected against backflow and siphonage
				in a manner acceptable under 675 IAC 16, the Indiana Plumbing Code, or through
				an approved airgap meeting that same code.
(c) An over-the-rim spout, if used, shall be
				under a diving or jump board, diving platform, balance tank, adjacent to a
				ladder, or otherwise shielded so as not to create a hazard. Its open end shall:
(1) have no sharp edges; and
(2) not protrude more than two (2) inches
				beyond the interior wall.
The spout shall be separated from the pool water by an air
				  gap of at least six (6) inches or two (2) pipe diameters from the pipe outlet
				  to the rim, whichever is greater.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-23 - Disinfectant equipment and chemical feeders

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 23.
(a)
				Disinfectant equipment and chemical feeders serving only spray/splash pads on
				decks with no standing water shall be capable of automatically providing a
				continuous chemical disinfectant residual of a minimum of two (2) ppm chlorine
				or four (4) ppm bromine.
(b) All
				such equipment shall:
(1) be of an approved
				type; and
(2) be installed
				downstream from the pump and wired so they will not operate unless the filter
				pump is operating. An exception is erosion-type chlorinators may feed their
				solution to the suction side of the pump.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-24 - Safety requirements

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 24.
(a) Water
				attractions shall be provided with one (1) or more suitable handholds around
				their perimeter in areas where depths exceed three (3) feet six (6) inches.
				Handholds shall be provided no farther apart than four (4) feet and may consist
				of any one (1) or a combination of the following:
(1) Coping, ledge, or deck along the
				immediate top edge of a water attraction that provides a slip-resistant surface
				of at least a four (4) inch minimum horizontal width located not over twelve
				(12) inches above the waterline.
(2) Ladders, stairs, or seat
				ledges.
(3) A railing fastened to
				the wall placed not over twelve (12) inches above the waterline.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-26 - Water attraction slides

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 26.
All slides installed as an appurtenance to a public swimming
				  pool or water attraction shall be installed in accordance with the
				  manufacturer's specifications and instructions.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-27 - Design and installation

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 27.
(a) Pool
				slides, drop slides, and waterslides over six (6) feet (one and eight-tenths
				(1.8) m) in height from the slide entrance to the deck of the pool or water
				attraction and incorporating towers to support riders shall be submitted for
				plan review in accordance with 675 IAC 12-6.
(b) Pool slides, drop slides, and waterslides
				shall be designed and assembled such that external surfaces that may come in
				contact with a person using the slide:
(1)
				are smooth and continuous; and
(2)
				will not:
(A) cut;
(B) bruise;
(C) pinch;
(D) puncture; or
(E) cause an abrasion to; any
				person.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 5 - Water Attractions › Section 5-28 - Slide flume water

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 28.
(a) Water
				for flume lubrication shall be a maximum of ten percent (10%) of the
				circulation flow.
(b) The balance
				tank volume for runout slide flume lubrication systems shall be at a minimum of
				two (2) times the absolute value of combined flow rate of the water attraction
				pump (gpm) and of a sufficient volume so as to allow operation through all
				cycles of filtration operation.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 1 - Administration › Section 1-1 - Installation and alteration permit; registration; application; expiration

Current through July 10, 2024
Authority: IC
				  22-13-2-13;
				  IC
				  22-15-5-2
Affected: IC 22-13; IC 22-14; IC
				  22-15-5-3
Sec. 1.
(a) An
				installation permit is required prior to commencement of work for an
				installation of a new regulated lifting device. An alteration permit is
				required prior to commencement of work for an alteration to an existing
				regulated lifting device.
(b) An
				application for an installation or alteration permit shall be made to the
				office of the state building commissioner on forms provided by the office. Each
				application shall contain the following:
(1)
				The name, address, e-mail address, and fax number of the elevator contractor
				that will be installing or altering the regulated lifting device, and if
				applicable, the license number of the elevator contractor.
(2) The name, address, and e-mail address of
				the owner of the building in which the new regulated lifting device is being
				installed or the existing regulated lifting device is being altered.
(3) The name, address, and e-mail address of
				the user of the regulated lifting device.
(4) All information required under IC
				22-15-5-3(c)
				 for registration of the regulated lifting
				device. This includes the following for the regulated lifting device:
(A) The type.
(B) The rated load and speed.
(C)The name of the manufacturer.
(D) The location.
(E) The nature of use.
(5) Complete plans, including:
(A) copies of specifications and accurately
				scaled and fully dimensioned plans showing the location of the installation in
				relation to the plans and elevation of the building;
(B) plans showing the location of the machine
				room and the equipment to be installed, relocated, or altered;
(C) plans showing the structural supporting
				members, including foundations; and
(D) a specification of all materials employed
				and loads to be supported or conveyed.
These plans must be sufficient to show that the installation
				  or alteration will comply with all applicable equipment laws and must be
				  sufficiently complete to illustrate all details of construction and
				  design.
(6) The
				required fee.
(7) The affirmations
				by the appropriate signatories as required under section 1.5 of this
				rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 1 - Administration › Section 1-1.5 - Signatories; affirmation

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-13; IC 22-14; IC
				  22-15-5-3
Sec. 1.5.
(a) All
				signatories to an application shall be determined as follows:
(1) For a corporation, the signatory shall be
				a responsible corporate officer. For the purpose of this section, a responsible
				corporate officer means a president, secretary, treasurer, or vice president of
				the corporation in charge of a principal business function, or any other person
				who performs similar policymaking or decision-making functions for the
				corporation.
(2) For a partnership
				or sole proprietorship, the signatory shall be a general partner or the
				proprietor, respectively.
(3) For a
				municipality, state, or other public agency, the signatory shall be a principal
				executive officer or ranking elected official.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 1 - Administration › Section 1-3.1 - Operating certificate; display; location

Current through July 10, 2024
Authority: IC
				  22-13-2-13;
				  IC
				  22-15-5-4;
				  IC
				  22-15-5-5
Affected: IC 22-13; IC 22-14; IC 22-15
Sec. 3.1.
(a) A
				regulated lifting device may not be operated without an operating certificate
				that covers the operation of the regulated lifting device. However, an
				individual who is performing maintenance on, repairing, installing, or altering
				the regulated lifting device may use the regulating lifting device without an
				operating certificate to the extent necessary to complete the work and required
				testing.
(b) The office shall issue
				an initial operating certificate for a regulated lifting device if:
(1) the applicant for the operating
				certificate has:
(A) demonstrated through an
				acceptance inspection and tests that the regulated lifting device complies with
				the laws governing its construction, repair, maintenance, and operation. This
				acceptance inspection must be conducted by a licensed inspector;
(B) submitted a notice of
				compliance/completion to the office that has been completed and signed and
				affirmed by the appropriate signatory as required under section 1.5 of this
				rule;
(C) paid the required fee;
				and
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 1 - Administration › Section 1-5 - Existing installations; maintenance

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 5.
All existing installations for which an operating permit is
				  in effect shall be maintained in a safe operating condition or shall be taken
				  out of service. All parts of existing installations upon which safe operation
				  is dependent, shall be maintained in proper working order. Broken, worn or
				  otherwise defective components shall be promptly replaced. All electrical
				  equipment and communication systems shall be maintained in a serviceable
				  condition.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 1 - Administration › Section 1-7 - Accident reports and investigations

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 7.
(a) An
				accident involving a regulated lifting device shall be reported by the owner of
				the regulated lifting device within twenty-four (24) hours after the accident
				has occurred. This initial report shall contain, to the extent available, the
				information specified in subsection (b)(1) through (b)(8).
(b) The owner shall submit a final written
				accident report to the office as soon as possible after the accident has
				occurred, but in any event no later than two (2) weeks after the date of the
				accident. The following information shall be included in the final written
				accident report:
(1) Registration number of
				the regulated lifting device.
(2)
				Owner and operator of the regulated lifting device.
(3) The names, address, and phone numbers of
				all persons responsible for the maintenance or repair of the regulated lifting
				device.
(4) Location of the
				regulated lifting device.
(5)
				Names, addresses, and phone numbers of any persons injured.
(6) Date and time of the accident.
(7) Operating condition of the installation
				as known.
(8) Brief details of the
				accident.
(9) Police report, if it
				exists.
(10) Fire department
				report, if it exists.
(11)
				Emergency medical report, if it exists.
(12) Any other emergency response
				reports.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 1 - Administration › Section 1-9 - Title

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 9.
All codes and standards adopted or established in this
				  article shall collectively be known as the Indiana Elevator Safety Code, 2011
				  edition.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 1 - Administration › Section 1-10 - Definitions

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15-5-11
Sec. 10.
(a) The
				definitions in this section apply throughout this article.
(b) "Elevator work" means the:
(1) installation;
(2) alteration;
(3) maintenance;
(4) repair;
(5) replacement; or
(6) placement out of service as described in
				Section 8.11.1.4 of
				675 IAC
				21-3-2; of any regulated lifting device. The term does
				not include demolition, hole drilling, or monthly fire service testing as
				described in Section 8.6.10.1 of
				675 IAC
				21-3-2.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 3 - Elevator Safety Code › Section 3-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 1.
That certain document, being titled as ANSI/ASME A17.1, 2007,
				  Safety Code for Elevators and Escalators, published by the American Society of
				  Mechanical Engineers, Three Park Avenue, New York, New York 10016 is hereby
				  adopted by reference and made a part of this rule as if fully set out herein,
				  save and except those additions, deletions, and amendments as are made in
				  section 2 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 3 - Elevator Safety Code › Section 3-2 - Amendments to adopted code

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 10-19; IC
				  22-12-1-22;
				  IC 22-12-2-10; IC 22-14; IC 22-15; IC
				  36-7-2-9;
				  IC
				  36-8-17-8
Sec. 2.
(a)
				Explanatory material, in the form of notes, that is not part of a table,
				figure, or graph, is not:
(1) a part of this
				standard; and
(2) enforceable as
				part of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 4 - Personnel Hoists › Section 4-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 1.
That certain document being titled as ANSI A10.4, 2004,
				  American National Standard Safety Requirements for Personnel Hoists and
				  Employee Elevators for Construction and Demolition Operations, published by the
				  National Safety Council, 444 North Michigan Avenue, Chicago, Illinois 60611, is
				  hereby adopted by reference and made a part of this section as if fully set out
				  herein, save and except those additions, deletions, and amendments as are made
				  in section 2 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 4 - Personnel Hoists › Section 4-2 - Amendments to adopted standard

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 10-19; IC 22-12; IC
				  22-13-2-10;
				  IC 22-14; IC 22-15-5; IC 25-4; IC 25-31
Sec. 2.
(a)
				Explanatory material, in the form of notes, that is not part of a table,
				figure, or graph, is not:
(1) a part of this
				standard; and
(2) enforceable as
				part of this Indiana Elevator Safety Code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 5 - Manlifts › Section 5-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 1.
That certain document, being titled as ANSI ASME A90.1, 2003,
				  Safety Standard for Belt Manlifts, published by the American Society of
				  Mechanical Engineers, Three Park Avenue, New York, New York 10016, is hereby
				  adopted by reference and made a part of this section as if fully set out
				  herein, save and except those additions, deletions, and amendments as are made
				  in section 3 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 5 - Manlifts › Section 5-3 - Amendments to adopted standard

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC
				  22-13-2-10;
				  IC 22-14; IC 22-15
Sec. 3.
(a)
				Explanatory material, in the form of notes, that is not part of a table,
				figure, or graph, is not:
(1) a part of this
				standard; and
(2) enforceable as
				part of the Indiana Elevator Safety Code (675 IAC 21).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 8 - Platform and Stairway Chair Lifts › Section 8-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 1.
That certain document, being titled as ASME A18.1 2005,
				  Safety Standard for Platform Lifts and Stairway Chairlifts, published by the
				  American Society of Mechanical Engineers, Three Park Avenue, New York, New York
				  10016, is hereby adopted by reference and made a part of this rule as if fully
				  set out herein, save and except those additions, deletions, and amendments as
				  are made in section 2 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 8 - Platform and Stairway Chair Lifts › Section 8-2 - Amendments to adopted code

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 10-19; IC 22-12; IC 22-14; IC 22-15; IC
				  36-7-2-9;
				  IC
				  36-8-17-8
Sec. 2.
(a) Amend
				Section 1.1.3 to read as follows: Except as provided in Section 10.1.1 and
				Section 10.1.2.1, this standard applies to new installations and
				alterations.
(b) Delete Section
				1.1.4, Effective Date, in its entirety without substitution.
(c) In Section 1.2, Purpose and Exceptions,
				delete the third paragraph in its entirety without substitution.
(d) In Section 1.3, Definitions, change the
				definitions to read as follows:
APPROVED means, as to materials, equipment, products, and
				  construction, acceptance by authority having jurisdiction by one (1) of the
				  following methods:
(A) Investigation
				or tests conducted by recognized authorities.
(B) Investigation or tests conducted by
				technical or scientific organizations.
(C) Accepted principles.
The investigation, tests, or principles shall establish that
				  the materials, equipment, products, and construction are safe for their
				  intended purposes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 21 - SAFETY CODES FOR ELEVATORS, ESCALATORS, MANLIFTS AND HOISTS › Rule 9 - Safety Code for Existing Elevators and Escalators › Section 9-1 - Safety Code for Existing Elevators and Escalators

Current through July 10, 2024
Authority: IC 22-3-3; IC
				  22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 1.
That certain document, being titled A17.3 Safety Code for
				  Existing Elevators and Escalators, 2005 Edition, published by the American
				  Society of Mechanical Engineers, Three Park Avenue, New York, New York
				  10016-5990 is hereby adopted by reference and made a part of this rule as if
				  fully set out herein, save and except those additions, deletions, and
				  amendments as are made in section 2 of this rule.