reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 1 - Adoption by Reference; Title; Scope; Applicability; Violations; Exemptions from Inspection › Section 1-1 - Adoption by reference; approval of revisions

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-7; IC 22-13-2; IC 22-15-5; IC
				  22-15-6
Sec. 1.
(a) The
				following documents are hereby adopted by reference as if fully set out in this
				article:
(1) American Society of Mechanical
				Engineers Boiler and Pressure Vessel Code (ASME B&PVC), 2019 edition,
				published by the American Society of Mechanical Engineers, Two Park Avenue, New
				York, New York 10016-5990, limited to the following sections:
(A) Section I - Rules for Construction of
				Power Boilers.
(B) Section II -
				Material Specifications and Properties; Parts A, B, C, and D.
(C) Section III - Nuclear Power Plant
				Components.
(D) Section IV - Rules
				for Construction of Heating Boilers.
(E) Section V - Nondestructive
				Examination.
(F) Section VIII -
				Rules for Construction of Pressure Vessels; Division 1, 2, and 3.
(G) Section IX - Welding, Brazing, and Fusing
				Qualifications.
(H) Section X -
				Fiber-Reinforced Plastic Pressure Vessels.
(I) Section XI - Rules for In-service
				Inspection of Nuclear Power Plant Components.
(J) Section PVO - Pressure Vessels for Human
				Occupancy.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 1 - Adoption by Reference; Title; Scope; Applicability; Violations; Exemptions from Inspection › Section 1-2 - Title; scope; applicability; definition

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-1-5; IC 22-12-7; IC 22-13-2; IC 22-15-2-7;
				  IC 22-15-6
Sec. 2.
(a) This
				article shall be known as the Indiana Boiler and Pressure Vessel
				Rules.
(b) The purpose of this
				article shall be to specify minimum standards that govern the design,
				construction, installation, examination, inspection, repair, and alteration of
				regulated boilers and unfired pressure vessels in Indiana.
(c) This article does not limit in any way
				the builder's right to choose any method of design or form of construction that
				conforms to the standards prescribed, or provided for in this article, as such
				standards cover certain fundamental features of construction and leave a number
				of details to the judgment of designers and acceptance of inspectors.
(d) Any condition not specifically covered by
				the provisions in this section through
				675 IAC
				30-11-6 shall comply with the applicable provisions of
				the ASME B&PVC and the NBIC, as adopted in section 1 of this rule.
(e) Any boiler or unfired pressure
				vessel not described in subsection (f) is regulated by this article, regardless
				of whether it is stationary, portable, leased, rented, or owned and qualifies
				as a regulated boiler or pressure vessel as mentioned in IC 22-156-0.5. The
				vessels listed in subsection (f) are exempted from the ASME B&PVC
				construction standards, inspection requirements, and operating permit
				requirements.
(f) The following
				vessels are not regulated by this article:
(1) Boilers meeting the requirements of
				clauses (A), (B), and (C) as follows:
(A)
				Located in:
(i) a Class 2 structure as
				defined in IC 22-12-1-5;
(ii) a
				residential structure with fewer than seven (7) apartments; or
(iii) a place other than a place of public
				assembly, if not used for residential occupancy.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 1 - Adoption by Reference; Title; Scope; Applicability; Violations; Exemptions from Inspection › Section 1-3

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-1-3 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-1-3 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 1 - Adoption by Reference; Title; Scope; Applicability; Violations; Exemptions from Inspection › Section 1-4 - Violations

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 4-21.5-3; IC 22-12-7; IC 22-13-2-11; IC
				  22-15-6-3
Sec. 4.
Any person violating any of the provisions of this article
				  is subject to sanctions under the provisions of IC 22-12-7.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-1-4 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-1-4 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 1 - Adoption by Reference; Title; Scope; Applicability; Violations; Exemptions from Inspection › Section 1-5 - Exemptions from inspection

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-7; IC 22-13-2-11; IC 22-15-6
Sec. 5.
(a) Each of
				the following vessels must comply with the applicable requirements of the
				edition of the ASME B&PVC in effect at the time of construction, but are
				exempt from inspection and operating permit requirements:
(1) Vessels located on a farm and used solely
				for agricultural purposes.
(2)
				Boilers meeting the requirements of clauses (A), (B), (C), and (D) as follows:
(A) Contain a volume less than one and one
				half (1 1/2) cubic feet.
(B)
				Operate entirely full of a liquid heat transfer fluid that will not vaporize at
				the operating temperature and atmospheric pressure.
(C) Have a gross output rating not exceeding
				three hundred thousand (300,000) Btus per hour.
(D) Are not located in a place of public
				assembly.
(3) Unfired
				pressure vessels that:
(A) contain only water
				under pressure for domestic supply purposes, including those containing air, if
				the compressed air serves only as a cushion or as part of an airlift pumping
				system; and
(B) are located in a
				Class 2 structure as defined in IC 22-12-1-5or a residential structure with
				less than seven (7) apartments.
(4) Steam cleaner as defined in
				675 IAC
				30-4-49.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 2 › Section 2-1

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC 2-2-1 ) to the
					 Fire Prevention and Building Safety Commission ( 675 IAC 30-2-1 ) by P.L.
					 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 2 › Section 2-2

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC 2-2-2
					 ) to the Fire Prevention and Building Safety Commission ( 675 IAC 30-2-2 ) by
					 P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 2 › Section 2-3

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC 2-2-3
					 ) to the Fire Prevention and Building Safety Commission ( 675 IAC 30-2-3 ) by
					 P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 2 › Section 2-4

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC 2-2-4 ) to
					 the Fire Prevention and Building Safety Commission ( 675 IAC 30-2-4 ) by P.L.
					 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-1

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-3-1 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-1 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-2

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-3-2 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-2 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-3 - Application for inspector's license

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 3.
To qualify for an inspector's license, an applicant must do
				  the following:
(1) Apply for an
				inspector's license on a form and in a manner approved by the division, which
				shall include:
(A) the applicant's
				name;
(B) the applicant's
				address;
(C) the education and
				experience of the applicant;
(D) a
				list of the applicant's current and previous employers, including the
				applicant's period of employment and positions held with each employer;
				and
(E) a statement swearing that
				the information provided is true, accurate, and complete.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-4

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-3-4 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-4 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-4.1 - Examination for inspector's license

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 4.1.
(a) An
				examination for an inspector's license, approved by the commission under IC
				22-15-6-5(b)(2), shall be administered by the division or its
				designee.
(b) The division shall
				offer to administer the examination quarterly.
(c) To become eligible to sit for the
				examination, an applicant must:
(1) apply to
				the division at least ten (10) days prior to the examination date;
(2) pay the examination fee in
				675
				IAC 12-3-13; and
(3) demonstrate the applicant meets the
				minimum requirements for education and experience as set forth in section 3(3)
				of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-5 - Issuance of license; record of qualifications; identification card; suspension or revocation

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-7; IC 22-15-6-5
Sec. 5.
(a) The
				division shall issue a boiler and pressure vessel inspector license to an
				applicant who qualifies as set forth in IC 22-15-6-5 section 3 of this
				rule.
(b) A boiler and pressure
				vessel inspector license expires on December 31 of the year of
				issuance.
(c) To renew a boiler and
				pressure vessel inspector license, an applicant must do the following:
(1) File an application on a form approved by
				the division containing any information the division requires to determine
				compliance with this article.
(2)
				Complete a program of continuing education for all renewals subsequent to the
				first year of licensure:
(A) in accordance
				with the requirements of the National Board to maintain a NBBI commission;
				or
(B) that is equivalent to the
				National Board requirements and approved by the division.
(3) Pay the fee in
				675
				IAC 12-3-13.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-6

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-3-6 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-6 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-7 - Inspectors' conflict of interest

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 7.
Inspectors licensed by the state of Indiana shall not engage
				  in any activity which constitutes a conflict of interest with their inspection
				  function.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-3-7 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-7 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-8

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-3-8 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-8 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-9 - Operating permits and inspection schedules

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-7; IC 22-15-6
Sec. 9.
(a) Unless
				exempted by
				675 IAC
				30-1-2(b)  or
				675 IAC 30-1-5, no
				boiler or unfired pressure vessel may be operated until an operating permit is
				issued.
(b) Unless stated
				otherwise, a boiler or unfired pressure vessel shall be inspected annually, and
				its operating permit expires one (1) year after issuance. The following is a
				list of specific boiler and unfired pressure vessel operating permit expiration
				periods and inspection schedules:
(1)
				Operating permits for power boilers expire one (1) year after issuance. Power
				boilers shall be inspected as follows:
(A)
				Externally every twelve (12) months while under pressure, which shall occur
				approximately six (6) months from the issuance of the operating
				permit.
(B) Within every twelve
				(12) months of issuance of an operating permit or renewal, while not under
				pressure, both:
(i) internally, where
				construction permits; and
(ii)
				externally.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-10 - Preparation for inspection; notice

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 10.
The owner or user shall prepare each boiler or unfired
				  pressure vessel for internal inspection and shall prepare for and apply a
				  hydrostatic leak test whenever necessary, on the date specified by the
				  inspector responsible for inspection of the equipment in question, which date
				  shall be no less than fourteen (14) days after the date of notification.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-10 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-10 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-11 - Inspection reports

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 11.
(a) The
				first operating permit inspection of a boiler shall be reported on a form
				patterned after Form NB-5 set forth in Part 2 of the NBIC. Subsequent operating
				permit inspections of these objects shall be reported on a form patterned after
				Form NB-6 set forth in Part 2 of the NBIC.
(b) The first operating permit inspection of
				an unfired pressure vessel shall be reported on a form patterned after Form
				NB-5 in Part 2 of the NBIC. Subsequent operating permit inspections of these
				objects shall be reported on a form patterned after Form NB-7 in Part 2 of the
				NBIC.
(c) The inspection reports
				mentioned in subsections (a) and (b) shall be submitted to the division within
				thirty (30) days of the date of the inspection. The results of inspections
				shall be reported immediately to the division whenever a hazardous condition
				concerning a boiler or unfired pressure vessel is found to exist.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-11 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-11 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-12 - Notice of unsafe boilers and pressure vessels; corrective measures; suspension of inspection certificate

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 4-21.5-4; IC 22-12-7-6
Sec. 12.
If, upon inspection, a boiler or unfired pressure vessel is
				  found to be unsafe for further operation, the inspector shall immediately
				  notify the division and the owner or user shall immediately suspend operation
				  of the boiler or unfired pressure vessel. The division shall issue an order to
				  suspend the operating permit and to stop operation as set forth in IC 22-12-7-6
				  and IC 4-21.5-4 to the owner or user stating what repairs or other corrective
				  measures are required. Until such repairs and other corrective measures have
				  been made or adopted, no further operation of the boiler or pressure vessel
				  involved shall be permitted.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-12 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-12 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-13 - Notice of new, canceled, or suspended insurance risks

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-7; IC 22-15-6
Sec. 13.
(a)
				Insurance inspection agencies shall notify the division within thirty (30) days
				of all boiler or unfired pressure vessel policies written, canceled, or not
				renewed.
(b) If coverage on a
				boiler or unfired pressure vessel is rejected or suspended because of unsafe
				conditions, the inspector shall notify the division as required in section 12
				of this rule.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-13 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-13 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-14

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-3-14 ) to the Fire Prevention and Building
					 Safety Commission ( 675 IAC 30-3-14 ) by P.L. 249-2019, SECTION 15, effective
					 July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-15 - Availability of operating permits

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 15.
An operating permit for a boiler or unfired pressure vessel
				  shall be readily available for review in a place convenient to the
				  equipment.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-15 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-15 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-16

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-3-16 ) to the Fire Prevention and Building
					 Safety Commission ( 675 IAC 30-3-16 ) by P.L. 249-2019, SECTION 15, effective
					 July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-17 - Notice of violations; issuance of orders

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 4-21.5-3-6; IC 22-12-7; IC 22-15-6
Sec. 17.
If, upon the inspection of any boiler or unfired pressure
				  vessel in service, it is found that the same does not fully conform to the
				  standards prescribed in this article but the same is still deemed safe to
				  continue operation the inspector or the employing inspection agency shall
				  submit an inspection report documenting the violations to the division. Upon
				  confirming the violations, the division shall issue an order as set forth at IC
				  22-12-7 and IC 4-21.5-3-6 granting a reasonable time in which to correct the
				  violations.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-17 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-17 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-18 - Assignment of state serial numbers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 18.
Where a state registration number is assigned to a boiler or
				  unfired pressure vessel as hereinafter provided in this article, the division
				  will assign blocks of such state registration numbers to inspectors upon
				  request.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-18 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-18 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-19 - Restamping

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 19.
When the ASME stamping on a boiler or unfired pressure
				  vessel becomes indistinct, the inspector shall instruct the owner or user to
				  have it restamped in accordance with the requirements in Part 2 of the NBIC.
				  Notice of the completion of such stamping together with a facsimile of the
				  stamping applied shall be filed with the division within thirty (30) days after
				  the restamping is completed.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-19 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-19 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-20 - Condemned boilers and pressure vessels; stamp; penalties for use or sale

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-7; IC 22-15-6
Sec. 20.
(a) Any
				boiler or unfired pressure vessel that fails an inspection and is determined by
				the inspector to be irreparable shall be promptly reported by the inspector to
				the division who shall declare it prohibited from further use or operation by
				issuing an order as set forth at IC 22-12-7.
(b) Any boiler or unfired pressure vessel
				declared prohibited from further use by the division shall be stamped by an
				inspector with the letters "XXX" and the letters "IND", as shown by the
				following facsimile, which will designate a condemned boiler or unfired
				pressure vessel:
XXX IND XXX
(c) Any person using or offering for sale
				(other than for salvage) a boiler or unfired pressure vessel declared
				prohibited from further use for operation within the purview of this article
				shall be subject to the penalties provided in IC 22-12-7.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-20 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-20 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-21 - Incident reports

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 21.
When an incident occurs that serves to render a boiler or
				  pressure vessel inoperative and results in personal injury or major property
				  damage, the owner or user or their designee shall, within forty-eight (48)
				  hours of the incident, notify the division and submit an initial report of the
				  incident. In case of a serious incident such as an explosion or loss of life,
				  notice shall be given within twenty-four (24) hours of the incident by
				  telephone or email and neither the boiler nor the unfired pressure vessel nor
				  any of the parts thereof shall be removed or disturbed before an inspection has
				  been made unless for the purpose of protecting health and safety. The owner or
				  user shall cause a detailed report of the incident to be completed by an
				  inspector and submitted to the division. Such report shall include the cause
				  and the origin of the incident, where determinable, and recommendations to
				  prevent a recurrence of the incident.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-21 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-21 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-22

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC 2-3-22
					 ) to the Fire Prevention and Building Safety Commission ( 675 IAC 30-3-22 ) by
					 P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-23 - Reinstallations

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 23.
In any case when a boiler or unfired pressure vessel is
				  reinstalled in the state, the state registration number must remain with the
				  boiler or unfired pressure vessel and the owner or user must notify the
				  division of the location change. The operating permit of the boiler or unfired
				  pressure vessel becomes invalid when it is moved, and a new inspection and
				  operating permit is required to ensure the fittings and appliances comply with
				  the rules for new installations.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-3-23 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-3-23 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-24

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-3-24 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-24 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-25

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-3-25 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-3-25 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 3 - Administration › Section 3-26 - Factor of safety for regulated equipment

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 26.
When performing strength calculations (e.g. minimum required
				  thickness, design pressure or design temperature, remaining useful life) for
				  components of boilers or unfired pressure vessels, a factor of safety lower
				  than that allowed by the edition of the original code of construction (in order
				  to provide allowable stress values exceeding those values specified by the
				  edition of the original code of construction) may not be used.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-1 - Examination for inspector's license

Current through July 10, 2024
Sec. 4.1.
(a) An
				examination for an inspector's license, approved by the commission under IC
				22-15-6-5(b)(2), shall be administered by the division or its
				designee.
(b) The division shall
				offer to administer the examination quarterly.
(c) To become eligible to sit for the examination, an applicant
				must:
(1) apply to the division at least ten
				(10) days prior to the examination date;
(2) pay the examination fee in
				675
				IAC 12-3-13; and
(3) demonstrate the applicant meets the
				minimum requirements for education and experience as set forth in section 3(3)
				of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-1.1 - "Alteration" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 1.1.
"Alteration" means a change in a pressure-retaining part
				  that meets the requirements of Part 3 of the NBIC but is not a repair, as that
				  term is defined in section 42.1 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-2 - "API-ASME" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 2.
"API-ASME" means the code for unfired pressure vessels for
				  petroleum liquids and gases, as set forth in
				  675 IAC
				  30-1-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-2 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-2 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-3 - "API 510" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 3.
"API 510" means the American Petroleum Institute Standard
				  510 - Pressure Vessel Inspection Code as set forth in 680 IAC
				  2-1-1(a)(4)675 IAC
				  30-1-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-3 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-3 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-4 - "ASME code" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 4.
"ASME B&PVC" means the American Society of Mechanical
				  Engineers Boiler and Pressure Vessel Code as set forth in
				  675 IAC
				  30-1-1 unless context indicates that an earlier
				  edition of the code is intended.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-4 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-4 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-5 - "Boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 5 .
(a)
				"Boiler" means a closed vessel in which water or other liquid is heated, steam
				or vapor is generated, steam is superheated, or any combination thereof, under
				pressure for use external to itself by the direct application of any source of
				energy. This definition does not include unfired pressure vessels as defined in
				section 50 of this rule. The term shall include the apparatus used to generate
				heat and all controls and safety devices associated with such apparatus or
				closed vessel.
(b) The term shall
				include, but is not limited to, the following:
(1) Exhibition traction engine boilers as
				defined in section 16 of this rule.
(2) Heaters as defined in section 18.2 of
				this rule.
(3) Heat recovery steam
				generators (HRSG boilers) as defined in section 18.3 of this rule.
(4) Historical boilers as defined in section
				18.4 of this rule.
(5) Hot water
				heating boilers as defined in section 19 of this rule.
(6) Hot water supply boilers as defined in
				section 20 of this rule.
(7) Low
				pressure heating boilers as defined in section 27 of this rule.
(8) Miniature boilers as defined in section
				29 of this rule.
(9) Model boilers
				as defined in section 30 of this rule.
(10) Modular boilers as defined in section
				30.1 of this rule.
(11) Nonstandard
				boilers as defined in section 34 of this rule.
(12) Portable boilers as defined in section
				38.2 of this rule.
(13) Power
				boilers as defined in section 39 of this rule.
(14) Steam cleaners as defined in section 49
				of this rule.
(15) Waste heat
				boilers as defined in section 51 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-6 - "Btu" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 6.
"Btu" means British thermal units.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-6 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-6 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-7

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-7 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-7 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-8

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-8 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-8 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-9

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-9 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-9 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-10 - "Commission" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-2-1; IC 22-15-6
Sec. 10.
"Commission" means the fire prevention and building safety
				  commission established in IC 22-12-2-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-10 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-10 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-11 - "Commissioner" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 11.
"Commissioner" means the state building commissioner.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-11 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-11 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-12

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-4-12 ) to the Fire Prevention and Building
					 Safety Commission ( 675 IAC 30-4-12 ) by P.L. 249-2019, SECTION 15, effective
					 July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-13

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-13 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-13 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-14 - "Division" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 14.
"Division" means the division of fire and building safety
				  established in IC 22-15-2-3 IC 10-19-7-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-14 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-14 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-15 - "Domestic water heater" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 15.
"Domestic water heater" means a water heater that consists
				  of a coil or a closed tank, heated either by direct flame or electrical heating
				  elements, for supplying potable water used external to itself and not exceeding
				  any of the following limits:
(1)
				Eighty (80) gallons nominal water containing capacity.
(2) One hundred thousand (100,000) Btu per
				hour heat input.
(3) One hundred
				fifty (150) psig MAWP.
(4) Two
				hundred ten (210) degrees Fahrenheit outlet water temperature.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-15 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-15 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-16 - "Exhibition traction engine boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 16.
"Exhibition traction engine boiler" means a boiler that is an
				  integral part of a traction engine, threshing machine, or similar piece of
				  equipment used exclusively for exhibition purposes.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-4-16 ) to the Fire Prevention and Building
					 Safety Commission ( 675 IAC 30-4-16 ) by P.L. 249-2019, SECTION 15, effective
					 July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-17 - "Existing installation" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 17.
"Existing installation" means any boiler or unfired pressure
				  vessel installed and placed in operation before July 1, 1953, which was the
				  effective date of the Indiana Boiler and Pressure Vessel Law, which accepted
				  already installed boilers and unfired pressure vessels not constructed or
				  installed to any standard. See
				  675 IAC
				  30-8,
				  675 IAC
				  30-10, and
				  675 IAC
				  30-11.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-17 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-17 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-18 - "External inspection" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 18.
"External inspection" means an inspection in accordance with
				  Part 2 of the NBIC or API 510 that does not involve examination of the interior
				  surfaces of pressure parts of a boiler or unfired pressure vessel.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-18 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-18 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-18.1 - "Fired process heater" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 18.1.
"Fired process heater" means a direct fired heat exchanger
				  that uses hot gases of combustion to raise the temperature of a process liquid
				  or gas flowing directly through coils or tubes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-18.2 - "Heater" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 18.2.
(a)
				"Heater" means a boiler in which water or other liquid is heated under pressure
				for use external to itself by the direct application of any source of
				energy.
(b) The term includes, but
				is not limited to, the following types of units:
(1) Domestic water heaters as defined in
				section 15 of this rule.
(2) Fired
				process heaters as defined in section 18.1 of this rule.
(3) Instant-on water heaters as defined in
				section 25.1 of this rule.
(4)
				Pool/spa heaters as defined in section 38.1 of this rule.
(5) Service water heaters as defined in
				section 45 of this rule.
(6)
				Thermal fluid heaters as defined in section 49.2 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-18.3 - "Heat recovery steam generator (HRSG boiler)" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 18.3.
"Heat recovery steam generator (HRSG boiler)" means an
				  energy recovery heat exchanger that recovers heat from a hot gas stream. It
				  produces steam that can be used in process operations or used to drive a
				  turbine.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-18.4 - "Historical boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6.
Sec. 18.4.
"Historical boiler" means a steam boiler of riveted or
				  welded construction. Historical boilers include steam tractors, traction
				  engines, hobby steam boilers, portable steam boilers, and other such boilers
				  that are being preserved, restored, and maintained for demonstration, viewing,
				  or educational purposes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-19 - "Hot water heating boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 19.
"Hot water heating boiler" means a boiler in which water or
				  other fluid is heated primarily for space heating purposes and does not exceed
				  any of the following operational limits:
(1) One hundred sixty (160) psig
				MAWP.
(2) Two hundred fifty (250)
				degrees Fahrenheit at the boiler outlet.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-19 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-19 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-20 - "Hot water supply boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 20.
"Hot water supply boiler" means a boiler completely filled
				  with water, used primarily for heating an expendable (normally nonreturnable)
				  supply of hot water for distribution in plumbing systems, for consumption in
				  industrial processes, or for other comparable uses, and that does not exceed
				  any of the following operational limits:
(1) one hundred sixty (160) psig
				MAWP.
(2) Two hundred fifty (250)
				degrees Fahrenheit at the boiler outlet.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-20 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-20 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.