reglab/statecodes huggingface dataset:
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter A - General [49 CFR Part 195 Subpart A] › Section V-30117 - What is a Regulated Rural Gathering Line and What Requirements Apply? [49 CFR 195.11]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Each operator of a regulated rural gathering line, as defined in Paragraph 1 of
					 this section, must comply with the safety requirements described in Paragraph 2
					 of this Section. [49
					 CFR 195.11]
1. Definition. As used in this section, a
regulated rural gathering line
means an onshore gathering line
					 in a rural area that meets all of the following criteria- [49
					 CFR 195.11(a)]
a. has a nominal diameter from
					 65/8 inches (168 mm) to
					 85/8 inches (219.1 mm);
					 [49
					 CFR 195.11(a)(1)]
b. is located in or within one-quarter mile
					 (.40 km) of an unusually sensitive area as defined in §30112; and
					 [49
					 CFR 195.11(a)(2)]
c. operates at a maximum pressure established
					 under §30406 corresponding to: [49
					 CFR 195.11(a)(3)]
i. A stress level greater than 20 percent of
					 the specified minimum yield strength of the line pipe; or [49
					 CFR
					 195.11(a)(3)(i)]
ii. if the stress level is unknown or the
					 pipeline is not constructed with steel pipe, a pressure of more than 125 psi
					 (861 kPa) gage. [49
					 CFR
					 195.11(a)(3)(ii)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter A - General [49 CFR Part 195 Subpart A] › Section V-30118 - What requirements apply to low-stress pipelines in rural areas? [49 CFR 195.12]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 General. This Section sets forth the requirements for each category of
					 lowstress pipeline in a rural area set forth in Subsection B of this Section.
					 This Section does not apply to a rural lowstress pipeline regulated under this
					 Subpart as a low-stress pipeline that crosses a waterway currently used for
					 commercial navigation; these pipelines are regulated pursuant to §30103. A.2 [
					49
					 CFR 195.12(a)]
B. Categories
.
An operator
					 of a rural low-stress pipeline must meet the applicable requirements and
					 compliance deadlines for the category of pipeline set forth in Subsection C of
					 this Section. For purposes of this Section, a rural low-stress pipeline is a
					 Category 1, 2, or 3 pipeline based on the following criteria. [
					49
					 CFR 195.12(b)]
1. A Category 1 rural low-stress pipeline: [
					49
					 CFR 195.12(b)(1)]
a. has a nominal diameter of 85/8 inches
					 (219.1 mm) or more; [
					49
					 CFR 195.12(b)(1)(i)
					 ]
b. is located in or within
					 one-half mile (.80 km) of an unusually sensitive area (USA) as defined in
					 §30112; and [
					49
					 CFR 195.12(b)(1)(ii)
					 ]
c. operates at a maximum pressure
					 established under
					 §30406 corresponding to: [
					49
					 CFR 195.12(b)(1)(iii)]
i. a stress level equal to or less than
					 20-percent of the specified minimum yield strength of the line pipe; or [
					49
					 CFR 195.12(b)(1)(iii)(A)
					 ]
ii. if the stress level is
					 unknown or the pipeline is not constructed with steel pipe, a pressure equal to
					 or less than 125 psi (861 kPa) gage. [
					49
					 CFR 195.12(b)(1)(iii)(B)
					 ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter A - General [49 CFR Part 195 Subpart A] › Section V-30119 - What requirements apply to pipelines transporting hazardous liquids by gravity? [49 CFR 195.13]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Scope. Pipelines transporting hazardous liquids by gravity must comply with the
					 reporting requirements of Subchapter B of this Subpart. [49
					 CFR 195.13(a)]
B. Implementation Period [49
					 CFR 195.13(b)]
1. Annual Reporting. Comply with the annual
					 reporting requirements in Subchapter B of this Subpart by March 31, 2021.
					 [49
					 CFR 195.13(b)(1)]
2. Accident and Safety-Related Reporting.
					 Comply with the accident and safety-related condition reporting requirements in
					 Subchapter B of this Subpart by January 1, 2021. [49
					 CFR 195.13(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter A - General [49 CFR Part 195 Subpart A] › Section V-30121 - What requirements apply to reporting-regulated-only gathering lines? [49 CFR 195.15]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Scope. Gathering lines that do not otherwise meet the definition of a regulated
					 rural gathering line in
					 §30117 and any gathering line not already
					 covered under
					 §30103.A.1 or 4 must
					 comply with the reporting requirements of Subchapter B of this Chapter.
					 [49
					 CFR 195.15(a)]
B. Implementation Period [49
					 CFR 195.15(b)].
1. Annual Reporting. Operators must comply
					 with the annual reporting requirements in subpart B of this part by March 31,
					 2021. [49
					 CFR 195.15(b)(1)]
2. Accident and Safety-Related Reporting.
					 Operators must comply with the accident and safety-related condition reporting
					 requirements in Subchapter B of this Subpart by January 1, 2021. [49
					 CFR 195.15(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30122 - How to Notify PHMSA [49 CFR 195.18]

Current through Register Vol. 50, No. 6, June 20, 2024
A. An operator must provide any notification
					 required by this part by: [49 CFR 195.18(a)]
1. sending the notification by electronic
					 mail to InformationResourcesManager@dot.gov; or [49 CFR
					 195.18(a)(1)]
2. sending the notification by mail to ATTN:
					 Information Resources Manager, DOT/PHMSA/OPS, East Building, 2nd Floor,
					 E22-321, 1200 New Jersey Ave. SE., Washington, DC 20590. [49 CFR
					 195.18(a)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30123 - Scope [49 CFR 195.48]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 This Subchapter prescribes requirements for periodic reporting and for
					 reporting of accidents and safety-related conditions. This Subchapter applies
					 to all pipelines subject to this Subpart. An operator of a Category 3 rural
					 low-stress pipeline meeting the criteria in
					 §30118 is not required to complete those
					 parts of the hazardous liquid annual report form PHMSA F 7000-1.1 associated
					 with IM or high consequence areas . [
					49CFR
					 195.48]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30124 - Annual Report [49 CFR 195.49]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Each operator must annually complete and submit DOT Form PHMSA F 7000-1.1 for
					 each type of hazardous liquid pipeline facility operated at the end of the
					 previous year. An operator must submit the annual report by June 15 each year,
					 except that for the 2010 reporting year the report must be submitted by August
					 15, 2011. A separate report is required for crude oil, HVL (including anhydrous
					 ammonia), petroleum products, carbon dioxide pipelines, and fuel grade ethanol
					 pipelines. For each state a pipeline traverses, an operator must separately
					 complete those sections on the form requiring information to be reported for
					 each state. [
					49
					 CFR 195.49]
B. For intrastate facilities subject to the
					 jurisdiction of the Office of Conservation, a copy of the annual report must be
					 sent to the Commissioner of Conservation, Office of Conservation, Pipeline
					 Safety Section, P.O. Box 94275 Baton Rouge, LA 70804-9275.
1. Annual report information must only
					 include data for intrastate facilities subject to the jurisdiction of the
					 Office of Conservation.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30125 - Reporting Accidents [49 CFR 195.50]

Current through Register Vol. 50, No. 6, June 20, 2024
A. An accident report is required for each
					 failure in a pipeline system subject to this Subpart in which there is a
					 release of the hazardous liquid or carbon dioxide transported resulting in any
					 of the following: [
					49 CFR 195.50
					 ]
1. explosion or fire not intentionally set
					 by the operator; [
					49 CFR
					 195.50(a)]
2. release of 5 gallons (19 liters) or more
					 of hazardous liquid or carbon dioxide, except that no report is required for a
					 release of less than 5 barrels (0.8 cubic meters) resulting from a pipeline
					 maintenance activity if the release is: [
					49 CFR
					 195.50(b)]
a. not otherwise reportable under this
					 Section; [
					49 CFR
					 195.50(b)(1)]
b. not one described in §30127(A)(4); [
					49 CFR
					 195.50(b)(2)]
c. confined to company property or pipeline
					 right-of-way; and [
					49 CFR
					 195.50(b)(3)]
d. cleaned up promptly; [
					49 CFR
					 195.50(b)(4)]
3. death of any person; [
					49 CFR
					 195.50(c)]
4. personal injury necessitating
					 hospitalization; [
					49 CFR
					 195.50(d)]
6. in addition to those listed in
					 §30125.A 1-5, any
					 release of carbon dioxide resulting in the following:
a. any potential dangers to human beings
					 and/or animals from the escaped material;
b. bodily harm to any person resulting in one
					 or more of the following:
i. loss of
					 consciousness;
ii. necessity carry a
					 person from the scene;
iii.
					 necessity for medical treatment;
iv. disability which prevents the discharge
					 of normal duties or the pursuit of normal duties beyond the day of the
					 accident
5.
					 estimated property damage, including cost of clean-up and recovery, value of
					 lost product, and damage to the property of the operator or others, or both,
					 exceeding $50,000. [
					49 CFR
					 195.50(e)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30127 - Telephonic Notice of Certain Accidents [49 CFR 195.52]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Notice Requirements. At the earliest
					 practicable moment within one hour following discovery, of a release of the
					 hazardous liquid or carbon dioxide transported resulting in an event described
					 in §30125, but no later than one hour after confirmed discovery, the operator
					 of the system shall give notice, in accordance with §30127.B of any failure
					 that: [
					49 CFR
					 195.52(a)]
1. caused a death or a personal injury
					 requiring hospitalization; [
					49 CFR
					 195.52(a)(1)]
2. resulted in either a fire or explosion not
					 intentionally set by the operator; [
					49 CFR
					 195.52(a)(2)]
3. caused estimated property damage,
					 including cost of clean-up and recovery, value of lost product, and damage to
					 the property of the operator or others, or both, exceeding $50,000; [
					49 CFR
					 195.52(a)(3)]
4. resulted in pollution of any stream,
					 river, lake, reservoir, or other similar body of water that violated applicable
					 water quality standards, caused a discoloration of the surface of the water or
					 adjoining shoreline, or deposited a sludge or emulsion beneath the surface of
					 the water or upon adjoining shorelines; or [
					49 CFR
					 195.52(a)(4)]
5. in the judgment of the operator was
					 significant even though it did not meet the criteria of any other paragraph of
					 this Section. [
					49 CFR
					 195.52(a)(5)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30131 - Accident Reports [49 CFR 195.54]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each operator that experiences an accident
					 that is required to be reported under
					 §30125 must, as soon as practicable, but
					 not later than 30 days after discovery of the accident, file an accident report
					 on DOT Form 7000-1. For intrastate facilities subject to the jurisdiction of
					 the Office of Conservation, a copy of the accident report must be sent
					 concurrently to the Commissioner of Conservation, Office of Conservation,
					 Pipeline Safety Section, P.O. Box 94275 Baton Rouge, LA 70804-9275. [
					49 CFR
					 195.54(a)]
B. Whenever an operator receives any changes
					 in the information reported or additions to the original report on DOT Form
					 7000-1, it shall file a supplemental report within 30 days. For intrastate
					 facilities subject to the jurisdiction of the Office of Conservation, a copy of
					 the supplemental report must be sent concurrently to the Commissioner of
					 Conservation, Office of Conservation, Pipeline Safety Section, P.O. Box 94275
					 Baton Rouge, LA 70804-9275. [
					49 CFR
					 195.54(b)]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30133 - Reporting Safety-Related Conditions [49 CFR 195.55]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Except as provided in §30133 B, each
					 operator shall report in accordance with
					 §30135 the existence of any of the
					 following safety-related conditions involving pipelines in service: [
					49 CFR
					 195.55(a)]
1. general corrosion that has reduced the
					 wall thickness to less than that required for the maximum operating pressure,
					 and localized corrosion pitting to a degree where leakage might result; [
					49 CFR
					 195.55(a)(1)]
2. unintended movement or abnormal loading of
					 a pipeline by environmental causes, such as an earthquake, landslide, or flood
					 that impairs its serviceability; [
					49 CFR
					 195.55(a)(2)]
3. any material defect or physical damage
					 that impairs the serviceability of a pipeline; [
					49 CFR
					 195.55(a)(3)]
4. any malfunction or operating error that
					 causes the pressure of a pipeline to rise above 110 percent of its maximum
					 operating pressure; [
					49 CFR
					 195.55(a)(4)]
5. a leak in a pipeline that constitutes an
					 emergency; [
					49 CFR
					 195.55(a)(5)]
6. any safety-related condition that could
					 lead to an imminent hazard and causes (either directly or indirectly by
					 remedial action of the operator), for purposes other than abandonment, a 20
					 percent or more reduction in operating pressure or shutdown of operation of a
					 pipeline. [
					49 CFR
					 195.55(a)(6)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30135 - Filing Safety-Related Condition Reports [49 CFR 195.56]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each report of a
					 safety-related condition under
					 §30133.A must be filed
					 (received by the commissioner and administrator) in writing within five working
					 days (not including Saturday, Sunday, or federal holidays) after the day a
					 representative of the operator first determines that the condition exists, but
					 not later than 10 working days after the day a representative of the operator
					 discovers the condition. Separate conditions may be described in a single
					 report if they are closely related. Reports may be transmitted by electronic
					 mail to InformationResourcesManager@dot.gov, or by facsimile at (202) 366-7128
					 and to the Commissioner of Conservation by electronic mail to
					 PipelineInspectors@la.gov. [
					49 CFR
					 195.56(a)]
B. The report must be headed "Safety-Related
					 Condition Report" and provide the following information: [
					49 CFR
					 195.56(b)]
1. name and principal address of operator; [
					49 CFR
					 195.56(b)(1)]
2. date of report; [
					49 CFR
					 195.56(b)(2)]
3. name, job title, and business telephone
					 number of person submitting the report; [
					49 CFR
					 195.56(b)(3)]
4. name, job title, and business telephone
					 number of person who determined that the condition exists; [
					49 CFR
					 195.56(b)(4)]
5. date condition was discovered and date
					 condition was first determined to exist; [
					49 CFR
					 195.56(b)(5)]
6. location of condition, with reference to
					 the state (and town, city, or parish) or offshore site, and as appropriate
					 nearest street address, offshore platform, survey station number, milepost,
					 landmark, or name of pipeline; [
					49 CFR
					 195.56(b)(6)]
7. description of the condition, including
					 circumstances leading to its discovery, any significant effects of the
					 condition on safety, and the name of the commodity transported or stored; [
					49 CFR
					 195.56(b)(7)]
8. the corrective action taken (including
					 reduction of pressure or shutdown) before the report is submitted and the
					 planned follow-up or future corrective action, including the anticipated
					 schedule for starting and concluding such action. [
					49 CFR
					 195.56(b)(8)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30139 - [Repealed] Filing Offshore Pipeline Condition Reports [49 CFR 195.57]

Current through Register Vol. 50, No. 6, June 20, 2024
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30140 - Report Submission Requirements [49 CFR 195.58]

Current through Register Vol. 50, No. 6, June 20, 2024
A. General. Except as provided in Subsection
					 B of this Section, an operator must submit each report required by this part
					 electronically to PHMSA at http://opsweb.phmsa.dot.gov unless an alternative
					 reporting method is authorized in accordance with Subsection D of this Section.
					 [
					49 CFR
					 195.58(a)]
1. Each report required by §30140. A, for
					 intrastate facilities subject to the jurisdiction of the Office of
					 Conservation, must also be submitted to Office of Conservation, P.O. Box 94275,
					 Baton Rouge, LA 70804-9275.
a. Annual report
					 information must only include data for intrastate facilities subject to the
					 jurisdiction of the Office of Conservation.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30141 - Abandonment or Deactivation of Facilities. [49 CFR 195.59]

Current through Register Vol. 50, No. 6, June 20, 2024
A. For each abandoned offshore pipeline
					 facility or each abandoned onshore pipeline facility that crosses over, under
					 or through a commercially navigable waterway, the last operator of that
					 facility must file a report upon abandonment of that facility. [
					49 CFR
					 195.59]
1.
					 The preferred method to submit data on pipeline facilities abandoned after
					 October 10, 2000 is to the National Pipeline Mapping System (NPMS) in
					 accordance with NPMS "Standards for Pipeline and Liquefied Natural Gas Operator
					 Submissions"
.
To obtain a copy of the NPMS Standards, please
					 refer to the NPMS homepage at
http://www.npms.PHMSA.dot.gov
or
					 contact the NPMS National Repository at (703) 317-3073. A digital data format
					 is preferred, but hard copy submissions are acceptable if they comply with the
					 NPMS Standards. In addition to the NPMS-required attributes, operators must
					 submit the date of abandonment, diameter, method of abandonment, and
					 certification that, to the best of the operator's knowledge, all of the
					 reasonably available information requested was provided and, to the best of the
					 operator's knowledge, the abandonment was completed in accordance with
					 applicable laws. Refer to the NPMS Standards for details in preparing your data
					 for submission. The NPMS Standards also include details of how to submit data.
					 Alternatively, operators may submit reports by mail, fax, or e-mail to the
					 Office of Pipeline Safety, Pipeline Hazardous Materials Safety Administration,
					 Department of Transportation, Information Resources Manager, PHP-10, 1200 New
					 Jersey Avenue, SE., Washington, DC 20590-0001; fax (202) 366-4566; e-mail,
					 "
InformationResourcesManager@PHMSA .dot.gov
''. The information
					 in the report must contain all reasonably available information related to the
					 facility, including information in the possession of a third party. The report
					 must contain the location, size, date, method of abandonment, and a
					 certification that the facility has been abandoned in accordance with all
					 applicable laws [
					49 CFR
					 195.59(a)].
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30142 - Operator Assistance in Investigation [49 CFR 195.60]

Current through Register Vol. 50, No. 6, June 20, 2024
A. If the Department of Natural Resources
					 investigates an accident, the operator involved shall make available to the
					 representative of the department all records and information that in any way
					 pertain to the accident, and shall afford all reasonable assistance in the
					 investigation of the accident. [
					49 CFR
					 195.60]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30143 - National Pipeline Mapping System [49 CFR 195.61]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each operator of a hazardous liquid
					 pipeline facility must provide the following geospatial data to PHMSA for that
					 facility:
1. geospatial data, attributes,
					 metadata and transmittal letter appropriate for use in the National Pipeline
					 Mapping System. Acceptable formats and additional information are specified in
					 the NPMS Operator Standards manual available at www.npms.phmsa.dot.gov or by
					 contacting the PHMSA Geographic Information Systems Manager at (202) 366-4595;
					 [
					49 CFR
					 195.61(a)(1)]
2. the name of and address for the operator;
					 [
					49 CFR
					 195.61(a)(2)]
3. the name and contact information of a
					 pipeline company employee, to be displayed on a public website, who will serve
					 as a contact for questions from the general public about the operators NPMS
					 data. [
					49 CFR
					 195.61(a)(3)
					 ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30145 - OMB Control Number Assigned to Information Collection [49 CFR 195.63]

Current through Register Vol. 50, No. 6, June 20, 2024
A. The control
					 number assigned by the Office of Management and Budget to the hazardous liquid
					 pipeline information collection pursuant to the Paperwork Reduction Act are
					 2137-0047, 2137-0601, 2137-0604, 2137-0605, 2137-0618, and 2137-0622. [
					49 CFR
					 195.63]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter B - Reporting Accidents and Safety Related Conditions [Subpart B] › Section V-30147 - Safety Data Sheets [49 CFR 195.65]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each owner or operator of a hazardous
					 liquid pipeline facility, following an accident involving a pipeline facility
					 that results in a hazardous liquid spill, must provide safety data sheets on
					 any spilled hazardous liquid to the designated Federal On-Scene Coordinator and
					 appropriate State and local emergency responders within 6 hours of a telephonic
					 or electronic notice of the accident to the National Response Center.
					 [49 CFR
					 195.65(a)].
B. Definitions. In this section:
					 [49 CFR
					 195.65(b)].
1. Federal On-Scene Coordinator. The term
federal on-scene coordinator
has the meaning given such term
					 in section 311(a) of the Federal
					 Water Pollution Control Act (33 U.S.C.
					 1321(a)). [49 CFR
					 195.65(b)(1)]
2. National Response Center. The term
national response center
means the center described under
					 40 CFR
					 300.125(a). [49 CFR
					 195.65(b)(2)]
3. Safety Data Sheet. The term
safety
					 data sheet
means a safety data sheet required under
					 29 CFR
					 1910.1200. [49 CFR
					 195.65(b)(3)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30153 - Scope [49 CFR 195.100]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 This Subchapter prescribes minimum design requirements for new pipeline systems
					 constructed with steel pipe and for relocating, replacing, or otherwise
					 changing existing systems constructed with steel pipe. However, it does not
					 apply to the movement of line pipe covered by §30424 [
					49 CFR
					 195.100]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30155 - Qualifying Metallic Components Other than Pipe [49 CFR 195.101]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Notwithstanding
					 any requirement of the Subchapter which incorporates by reference an edition of
					 a document listed in §30107, a metallic component other than pipe manufactured
					 in accordance with any other edition of that document is qualified for use if:
					 [
					49 CFR
					 195.101]
1. it can be shown through visual inspection
					 of the cleaned component that no defect exists which might impair the strength
					 or tightness of the component; and [
					49 CFR
					 195.101(a)]
2. the edition of the document under which
					 the component was manufactured has equal or more stringent requirements for the
					 following as an edition of that document currently or previously listed in
					 §30107: [
					49 CFR
					 195.101(b)]
a. pressure testing; [
					49 CFR
					 195.101(b)(1)]
b. materials; and [
					49 CFR
					 195.101(b)(2)]
c. pressure and temperature rating. [
					49 CFR
					 195.101(b)(3)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30157 - Design Temperature [49 CFR 195.102]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Material for components of the system must
					 be chosen for the temperature environment in which the components will be used
					 so that the pipeline will maintain its structural integrity. [
					49 CFR
					 195.102(a)]
B. Components of carbon dioxide pipelines
					 that are subject to low temperatures during normal operation because of rapid
					 pressure reduction or during the initial fill of the line must be made of
					 materials that are suitable for those low temperatures. [
					49 CFR
					 195.102(b)]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30159 - Variations in Pressure [49 CFR 195.104]

Current through Register Vol. 50, No. 6, June 20, 2024
A. If, within a pipeline system, two or more
					 components are to be connected at a place where one will operate at a higher
					 pressure than another, the system must be designed so that any component
					 operating at the lower pressure will not be over-stressed. [
					49 CFR
					 195.104]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30161 - Internal Design Pressure [49 CFR 195.106]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Internal design pressure for the pipe in a
					 pipeline is determined in accordance with the following formula:
P = (2 St/D) x E x F
P = internal design pressure in p.s.i. (kPa)
						gauge.
S = yield strength in pounds per square inch (kPa)
						determined in accordance with §30161. B
t = nominal wall thickness of the pipe in inches
						(millimeters). If this is unknown, it is determined in accordance with §30161.
						C
D = nominal outside diameter of the pipe in inches
						(millimeters).
E = seam joint factor determined in accordance with
						§30161. E
F = a design factor of 0.72, except that a design factor
						of 0.60 is used for pipe, including risers, on a platform located off-shore or
						on a platform in inland navigable waters, and 0.54 is used for pipe that has
						been subjected to cold expansion to meet the specified minimum yield strength
						and is subsequently heated, other than by welding or stress relieving as a part
						of welding, to temperature higher than 900 ° F (482 ° C) for any period of time
						or over 600 ° F (316 ° C) for more than one hour. [
						49 CFR
						195.106(a)
						]
B. The yield strength to
					 be used in determining the internal design pressure under §30161. A is the
					 specified minimum yield strength. If the specified minimum yield strength is
					 not known, the yield strength to be used in the design formula is one of the
					 following: [
					49 CFR
					 195.106(b)]
1. the yield strength determined by
					 performing all of the tensile tests of API Specification 5L on randomly
					 selected specimens with the following number of tests: [
					49 CFR
					 195.106(b)(1)(i)]
Pipeline Size
Number of Tests
Less than
6-5/8 in. (168.3 mm) nominal outside diameter
One test for each 200 lengths
6-5/8 through 12-3/4 in. (168 through 323 mm.)
								  nominal outside diameter
One test for each 100 lengths
Larger than
12-3/4 in. (324 mm.) nominal outside diameter
One test for each 50 lengths
2. if the average yield-tensile ratio exceeds
					 0.85, the yield strength shall be taken as 24,000 psi (165,474 kPa). If the
					 average yield tensile ratio is 0.85 or less, the yield strength of the pipe is
					 taken as the lower of the following: [
					49 CFR
					 195.106(b)(1)(ii)]
a. eighty percent of the average yield
					 strength determined by the tensile tests; [
					49 CFR
					 195.106(b)(1)(ii)(A)
					 ]
b. the lowest yield strength
					 determined by the tensile tests; [
					49 CFR
					 195.106(b)(1)(ii)(B)
					 ]
3. if the pipe is not
					 tensile tested as provided in Subsection B, the yield strength shall be taken
					 as 24,000 psi (165,474 kPa). [
					49 CFR
					 195.106(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30163 - External Pressure [49 CFR 195.108]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Any external pressure that will be exerted
					 on the pipe must be provided for in designing a pipeline system. [
					49 CFR 195.108
					 ]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30165 - External Loads [49 CFR 195.110]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Anticipated external loads (e.g., earthquakes, vibration, thermal expansion,
					 and contraction) must be provided for in designing a pipeline system. In
					 providing for expansion and flexibility, Section 419 of ASME/ANSI B31.4 must be
					 followed. [
					49 CFR
					 195.110(a)]
B. The pipe and other components must be
					 supported in such a way that the support does not cause excess localized
					 stresses. In designing attachments to pipe, the added stress to the wall of the
					 pipe must be computed and compensated for. [
					49 CFR
					 195.110(b)]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30167 - Fracture Propagation [49 CFR 195.111]

Current through Register Vol. 50, No. 6, June 20, 2024
A. A carbon dioxide pipeline system must be
					 designed to mitigate the effects of fracture propagation. Piping systems must
					 be analyzed for potential propagating fractures. Methods of limiting the extent
					 of such fractures shall be applied where warranted [49 CFR
					 195.111]
AUTHORITY
						NOTE: Promulgated in accordance with
						R.S.
						30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30169 - New Pipe [49 CFR 195.112]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Any
					 new pipe installed in a pipeline system must comply with the following. [
					49 CFR
					 195.112]
1. The pipe must be made of steel of the
					 carbon, low alloy-high strength, or alloy type that is able to withstand the
					 internal pressures and external loads and pressures anticipated for the
					 pipeline system. [
					49 CFR
					 195.112(a)]
2. The pipe must be made in accordance with a
					 written pipe specification that sets forth the chemical requirements for the
					 pipe steel and mechanical tests for the pipe to provide pipe suitable for the
					 use intended. [
					49 CFR
					 195.112(b)]
3. Each length of pipe with a nominal outside
					 diameter of 4 1/2 in. (114.3 mm) or more must be marked on the pipe or pipe
					 coating with the specification to which it was made, the specified minimum
					 yield strength or grade, and the pipe size. The marking must be applied in a
					 manner that does not damage the pipe or pipe coating and must remain visible
					 until the pipe is installed. [
					49 CFR
					 195.112(c)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30171 - Used Pipe [49 CFR 195.114]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Any
					 used pipe installed in a pipeline system must comply with §
												30169. A 1-2 and
					 the following. [
					49 CFR
					 195.114]
1. The pipe must be of a known specification
					 and the seam joint factor must be determined in accordance with § 30161. E. If
					 the specified minimum yield strength or the wall thickness is not known, it is
					 determined in accordance with §
													30161. B or §
													30161. C as appropriate. [
					49 CFR
					 195.114(a)]
2. There may not be any: [
					49 CFR
					 195.114(b)]
a. buckles; [
					49 CFR
					 195.114(b)(1)]
b. cracks, grooves, gouges, dents, or other
					 surface defects that exceed the maximum depth of such a defect permitted by the
					 specification to which the pipe was manufactured; or [
					49 CFR
					 195.114(b)(2)]
c. corroded areas where the remaining wall
					 thickness is less than the minimum thickness required by the tolerances in the
					 specification to which the pipe was manufactured. However, pipe that does not
					 meet the requirements of §30171. A.2.c may be used if the operating pressure is
					 reduced to be commensurate with the remaining wall thickness. [
					49 CFR
					 195.114(b)(3)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30173 - Valves [49 CFR 195.116]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Each valve installed in a pipeline system must comply with the following. [
					49 CFR
					 195.116]
1. The valve must be of a sound engineering
					 design.  [49 CFR
					 195.116(a)]
2. Materials subject to the internal pressure
					 of the pipeline system, including welded and flanged ends, must be compatible
					 with the pipe or fittings to which the valve is attached. [
					49 CFR
					 195.116(b)]
3. Each part of the valve that will be in
					 contact with the carbon dioxide or hazardous liquid stream must be made of
					 materials that are compatible with carbon dioxide or each hazardous liquid that
					 it is anticipated will flow through the pipeline system. [
					49 CFR
					 195.116(c)]
4. Each valve must be both hydrostatically
					 shell tested and hydrostatically seat tested without leakage to at least the
					 requirements set forth in Section 11 of ANSI/API 6D (incorporated by reference,
					 see §30107). [
					49 CFR
					 195.116(d)]
5. Each valve other than a check valve must
					 be equipped with a means for clearly indicating the position of the valve
					 (open, closed, etc.). [
					49 CFR
					 195.116(e)]
6. Each valve must be marked on the body or
					 the nameplate, with at least the following: [
					49 CFR
					 195.116(f)]
a. manufacturer's name or trademark; [
					49 CFR
					 195.116(f)(1)]
b. class designation or the maximum working
					 pressure to which the valve may be subjected; [
					49 CFR
					 195.116(f)(2)]
c. body material designation (the end
					 connection material, if more than one type is used); and [
					49 CFR
					 195.116(f)(3)]
d. nominal valve size. [
					49 CFR
					 195.116(f)(4)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30175 - Fittings [49 CFR 195.118]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Butt-welding type fittings must meet the marking, end preparation, and the
					 bursting strength requirements of ASME/ANSI B16.9 or MSS SP-75 (incorporated by
					 reference, see §30107). [
					49 CFR
					 195.118(a)]
B. There may not be any buckles, dents,
					 cracks, gouges, or other defects in the fitting that might reduce the strength
					 of the fitting. [
					49 CFR
					 195.118(b)]
C. The fitting must be suitable for the
					 intended service and be at least as strong as the pipe and other fittings in
					 the pipeline system to which it is attached. [
					49 CFR
					 195.118(c)]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30177 - Passage of Internal Inspection Devices [49 CFR 195.120]

Current through Register Vol. 50, No. 6, June 20, 2024
A. General. Except as provided in Subsection
					 B and C of this Section, each new pipeline and each main line section of a
					 pipeline where the line pipe, valve, fitting or other line component is
					 replaced must be designed and constructed to accommodate the passage of
					 instrumented internal inspection devices in accordance with NACE SP0102
					 (incorporated by reference, see
					 §30107 [49
					 CFR 195.120(a)]
B. Exceptions. This Section does not apply
					 to: [49 CFR
					 195.120(b)]
1. manifolds; [
					49 CFR
					 195.120(b)(1)]
2. station piping such as at pump stations,
					 meter stations, or pressure reducing stations; [
					49 CFR
					 195.120(b)(2)]
3. piping associated with tank farms and
					 other storage facilities; [
					49 CFR
					 195.120(b)(3)]
4. cross-overs; [
					49 CFR
					 195.120(b)(4)]
5. pipe for which an instrumented internal
					 inspection device is not commercially available; and [49 CFR
					 195.120(b)(5)]
6. offshore pipelines, other than main lines
					 10 inches (254 mm) or greater in nominal diameter, that transport liquids to
					 onshore facilities. [49 CFR
					 195.120(b)(6)]
7. other piping that the administrator under
					 CFR Part 190.9 and the commissioner under Chapter 313 of this Subpart, finds in
					 a particular case would be impracticable to design and construct to accommodate
					 the passage of instrumented internal inspection devices. [
					49 CFR
					 195.120(b)(7)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30179 - Fabricated Branch Connections [49 CFR 195.122]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each pipeline system must be designed so
					 that the addition of any fabricated branch connections will not reduce the
					 strength of the pipeline system. [
					49 CFR
					 195.122]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30181 - Closures [49 CFR 195.124]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Each closure to be installed in a pipeline system must comply with the 2007
					 ASME Boiler and Pressure Vessel Code (BPVC) (Section VIII, Division 1)
					 (incorporated by reference, see §30107) and must have pressure and temperature
					 ratings at least equal to those of the pipe to which the closure is attached. [
					49 CFR
					 195.124]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30183 - Flange Connection [49 CFR 195.126]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each component of a flange connection must
					 be compatible with each other component and the connection as a unit must be
					 suitable for the service in which it is to be used. [
					49 CFR 195.126
					 ]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.