reglab/statecodes huggingface dataset:
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30185 - Station Piping [49 CFR 195.128

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Any pipe to be installed in a station that is subject to system pressure must
					 meet the applicable requirements of this Subchapter. [
					49 CFR 195.128
					 ]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30187 - Fabricated Assemblies [49 CFR 195.130]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each fabricated assembly to be installed
					 in a pipeline system must meet the applicable requirements of this Subchapter.
					 [
					49 CFR
					 195.130]
AUTHORITY NOTE:
						Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30189 - Design and Construction of Above Ground Breakout Tanks [49 CFR 195.132]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each above
					 ground breakout tank must be designed and constructed to withstand the internal
					 pressure produced by the hazardous liquid to be stored therein and any
					 anticipated external loads. [
					49 CFR
					 195.132(a)]
B. For aboveground breakout tanks first
					 placed in service after October 2, 2000, compliance with Subsection A. of this
					 Section requires one of the following. [
					49 CFR
					 195.132(b)]
1. Shop-fabricated, vertical, cylindrical,
					 closed top, welded steel tanks with nominal capacities of 90 to 750 barrels
					 (14.3 to 119.2 m3) and with internal vapor space
					 pressures that are approximately atmospheric must be designed and constructed
					 in accordance with API Spec 12F (incorporated by reference, see §30107). [
					49 CFR
					 195.132(b)(1)]
2. Welded, low-pressure [i.e., internal vapor
					 space pressure not greater than 15 psig (103.4 kPa)], carbon steel tanks that
					 have wall shapes that can be generated by a single vertical axis of revolution
					 must be designed and constructed in accordance with API Std 620(incorporated by
					 reference, see §30107). [
					49 CFR
					 195.132(b)(2)]
3. Vertical, cylindrical, welded steel tanks
					 with internal pressures at the tank top approximately atmospheric pressures
					 [i.e., internal vapor space pressures not greater than 2.5 psig (17.2 kPa), or
					 not greater than the pressure developed by the weight of the tank roof] must be
					 designed and constructed in accordance with API Std 650 (incorporated by
					 reference, see §30107). [
					49 CFR
					 195.132(b)(3)]
4. High pressure steel tanks [i.e., internal
					 gas or vapor space pressures greater than 15 psig (103.4 kPa)] with a nominal
					 capacity of 2000 gallons (7571 liters) or more of liquefied petroleum gas (LPG)
					 must be designed and constructed in accordance with API Std 2510(incorporated
					 by reference, see §30107). [
					49 CFR
					 195.132(b)(4)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30191 - Leak Detection [49 CFR 195.134]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
					 Scope. This section applies to each hazardous liquid pipeline transporting
					 liquid in single phase (without gas in the liquid). [49 CFR
					 195.134(a)]
B. General [49 CFR
					 195.134(b)]
1. For each pipeline constructed prior to
					 October 1, 2019. Each pipeline must have a system for detecting leaks that
					 complies with the requirements in
					 §30444 by October 1, 2024. [49 CFR
					 195.134(b)(1)] 2. For each
					 pipeline constructed on or after October 1, 2019. Each pipeline must have a
					 system for detecting leaks that complies with the requirements in
					 §30444 by October 1, 2020.[49 CFR
					 195.134(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 301 - Transportation of Hazardous Liquids by Pipeline [49 CFR Part 195] › Subchapter C - Design Requirements [49 CFR Part 195 Subpart C] › Section V-30193 - Additional Requirements for Carbon Dioxide Pipelines

Current through Register Vol. 50, No. 6, June 20, 2024
A. Vents 1. Carbon dioxide may not be
					 relieved into the atmosphere of a building or other confined space where
					 hazardous levels of carbon dioxide might accumulate above the human exposure
					 level set by the United States Department of Labor, Occupational Safety and
					 Health Administration as depicted in the following table, unless the
					 appropriate respiratory protection is provided.
Condition
Minimum Respiratory
								  Protection Required above 5000 vppm
Gas concentration 50,000 vppm or less
Any supplied air respirator or self-contained
								  respirator.
Greater than 50,000 vppm or entry and escape from
								  unknown concentrations
Self-contained breathing apparatus with a full
								  face-piece operated in pressure demand or other positive pressure mode. A
								  combination respirator which includes a Type C supplied-air respirator with a
								  full face-piece operated in pressure-demand or positive pressure or continuous
								  flow mode and an auxiliary self-contained breathing apparatus operated in
								  pressure-demand or other positive pressure mode.
Fire Fighting
Self-contained breathing apparatus with a full
								  face-piece operated in pressure-demand or other positive pressure mode.
Escape
Any escape self-contained breathing
								  apparatus
2. except
					 for the reporting requirements of Subchapter B of this Subpart see §30199,
					 transportation of a hazardous liquid through a pipeline by gravity;
					 [49 CFR
					 195.1(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30200 - Scope [49 CFR 195.200]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				  This Chapter prescribes minimum requirements for constructing new pipeline
				  systems with steel pipe, and for relocating, replacing, or otherwise changing
				  existing pipeline systems that are constructed with steel pipe. However, this
				  Chapter does not apply to the movement of pipe covered by §30424 [
				  49 CFR
				  195.200]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30202 - Compliance with Specifications or Standards [49 CFR 195.202]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each pipeline
				  system must be constructed in accordance with comprehensive written
				  specifications or standards that are consistent with the requirements of this
				  Subpart. [
				  49 CFR
				  195.202]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30204 - Inspection-General [49 CFR 195.204]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				  Inspection must be provided to ensure the installation of pipe or pipeline
				  systems in accordance with the requirements of this Chapter. Any operator
				  personnel used to perform the inspection must be trained and is qualified in
				  the phase of construction to be inspected. An operator must not use operator
				  personnel to perform a required inspection if the operator personnel performed
				  the construction task requiring inspection. Nothing in this section prohibits
				  the operator from inspecting construction tasks with operating personnel who
				  are involved in other construction tasks. [
				  49 CFR 195.204
				  ]
B. Each operator shall notify the
				  Pipeline Safety Section of the Office of Conservation, Louisiana Department of
				  Natural Resources, by electronic mail at PipelineInspectors@la.gov of proposed
				  pipeline construction at least seven days prior to commencement of said
				  construction.
AUTHORITY NOTE:
					 Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30205 - Repair, Alteration and Reconstruction of Aboveground Breakout Tanks That Have Been in Service [49 CFR 195.205]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Aboveground breakout tanks that have been
				  repaired, altered, or reconstructed and returned to service must be capable of
				  withstanding the internal pressure produced by the hazardous liquid to be
				  stored therein and any anticipated external loads. [
				  49
				  CFR 195.205(a)]
B. After October 2, 2000, compliance with
				  Subsection A of this Section requires the following: [
				  49
				  CFR 195.205(b)]
1. For tanks designed for approximate
				  atmospheric pressure, constructed of carbon and low alloy steel, welded or
				  riveted, and non-refrigerated; and for tanks built to API Std 650 (incorporated
				  by reference, see §30107) or its predecessor Standard 12C; repair, alteration
				  and reconstruction must be in accordance with API Standard Std 653 (except
				  section 6.4.3) (incorporated by reference, see §30107). [
				  49
				  CFR 195.205(b)(1)
				  ]
2. For tanks built to API Spec
				  12F (incorporated by reference, see §30107) or API Std 620 (incorporated by
				  reference, see §30107), the repair, alteration, and reconstruction must be in
				  accordance with the design, welding, examination, and material requirements of
				  those respective standards. [
				  49
				  CFR 195.205(b)(2)
				  ]
3. For high pressure tanks built
				  to API Std 2510 (incorporated by reference, see §30107), repairs, alterations,
				  and reconstruction must be in accordance with API Std 510 (incorporated by
				  reference, see §30107). [
				  49
				  CFR 195.205(b)(3)
				  ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30206 - Material Inspection [49 CFR 195.206]

Current through Register Vol. 50, No. 6, June 20, 2024
A. No pipe or other component may be
				  installed in a pipeline system unless it has been visually inspected at the
				  site of installation to ensure that it is not damaged in a manner that could
				  impair its strength or reduce its serviceability. [
				  49 CFR
				  195.206]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30207 - Transportation of Pipe [49 CFR 195.207]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Railroad. In a pipeline operated at a hoop
				  stress of 20 percent or more of SMYS, an operator may not use pipe having an
				  outer diameter to wall thickness ratio of 70 to 1, or more, that is transported
				  by railroad unless the transportation is performed in accordance with API RP
				  5L1 (incorporated by reference, see §30107). [
				  49 CFR
				  195.207(a)]
B. Ship or Barge. In a pipeline operated at a
				  hoop stress of 20 percent or more of SMYS, an operator may not use pipe having
				  an outer diameter to wall thickness ratio of 70 to 1, or more, that is
				  transported by ship or barge on both inland and marine waterways, unless the
				  transportation is performed in accordance with API RP 5LW (incorporated by
				  reference, see §30107). [
				  49 CFR
				  195.207(b)]
C. Truck. In a pipeline to be operated at a
				  hoop stress of 20 percent or more of SMYS, an operator may not use pipe having
				  an outer diameter to wall thickness ratio of 70 to 1, or more, that is
				  transported by truck unless the transportation is performed in accordance with
				  API RP 5LT (incorporated by reference, see §30107).
AUTHORITY NOTE:
					 Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30208 - Welding of Supports and Braces [49 CFR 195.208]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Supports or braces may not be welded
				  directly to pipe that will be operated at a pressure of more than 100 p.s.i.
				  (689 Kpa) gage. [
				  49 CFR
				  195.208]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30210 - Pipeline Location [49 CFR 195.210]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Pipeline right-of-way must be selected to
				  avoid, as far as practicable, areas containing private dwellings, industrial
				  buildings, and places of public assembly. [
				  49 CFR
				  195.210(a)]
B. No pipeline may be located within 50 feet
				  (15 meters) of any private dwelling, or any industrial building or place of
				  public assembly in which persons work, congregate, or assemble, unless it is
				  provided with at least 12 inches (305 millimeters) of cover in addition to that
				  prescribed in §30248 [
				  49 CFR
				  195.210(b)]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30212 - Bending of Pipe [49 CFR 195.212]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Pipe must not have a wrinkle bend. [
				  49 CFR
				  195.212(a)]
B. Each field bend must comply with the
				  following: [
				  49 CFR
				  195.212(b)]
1. a bend must not impair the serviceability
				  of the pipe; [
				  49 CFR
				  195.212(b)(1)]
2. each bend must have a smooth contour and
				  be free from buckling, cracks, or any other mechanical damage; [
				  49 CFR
				  195.212(b)(2)]
3. on pipe containing a longitudinal weld,
				  the longitudinal weld must be as near as practicable to the neutral axis of the
				  bend unless: [
				  49 CFR
				  195.212(b)(3)]
a. the bend is made with an internal bending
				  mandrel; or [
				  49 CFR
				  195.212(b)(3)(i)]
b. the pipe is 12-3/4 in. (324 mm.) or less
				  nominal outside diameter or has a diameter to wall thickness ratio less than
				  70. [
				  49 CFR
				  195.212(b)(3)(ii)
				  ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30214 - Welding Procedures [49 CFR 195.214]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Welding must be performed by a qualified
				  welder or welding operator in accordance with welding procedures qualified
				  under section 5, section 12, Appendix A or Appendix B of API Std 1104
				  (incorporated by reference, see §30107), or Section IX of the ASME Boiler and
				  Pressure Vessel Code (ASME BPVC) (incorporated by reference, see §30107). The
				  quality of the test welds used to qualify the welding procedures must be
				  determined by destructive testing. [49 CFR
				  195.214(a)].
B. Each welding procedure must be recorded in
				  detail, including the results of the qualifying tests. This record must be
				  retained and followed whenever the procedure is used. [
				  49 CFR
				  195.214(b)]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30216 - Welders: Miter Joints [49 CFR 195.216]

Current through Register Vol. 50, No. 6, June 20, 2024
A. A miter joint is not permitted (not
				  including deflections up to three degrees that are caused by misalignment). [
				  49 CFR
				  195.216]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30222 - Welders-Qualification of Welders [49 CFR 195.222]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each welder or welding operator must be
				  qualified in accordance with section 6, section 12, Appendix A or Appendix B of
				  API Std 1104 (incorporated by reference, see §30107), or section IX of the ASME
				  Boiler and Pressure Vessel Code (ASME BPVC), (incorporated by reference, see
				  §30107) except that a welder or welding operator qualified under an earlier
				  edition than listed in §30107, may weld but may not requalify under that
				  earlier edition. [49
				  CFR 195.222(a)].
B. No welder or welding operator may weld
				  with a particular welding process unless, within the preceding six calendar
				  months, the welder or welding operator has: [
				  49
				  CFR 195.222(b)]
1. engaged in welding with that process; and
				  [
				  49
				  CFR 195.222(b)(1)
				  ]
2. had one weld tested and found
				  acceptable under section 9 or appendix A of API Std 1104 (incorporated by
				  reference, see §30107). [
				  49
				  CFR 195.222(b)(2)
				  ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30224 - Welding: Weather [49 CFR 195.224]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Welding must be protected from weather
				  conditions that would impair the quality of the completed weld. [
				  49 CFR 195.224
				  ]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30226 - Welding: Arc Burns [49 CFR 195.226]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each arc burn must be repaired. [
				  49 CFR
				  195.226(a)]
B. An arc burn may be repaired by completely
				  removing the notch by grinding, if the grinding does not reduce the remaining
				  wall thickness to less than the minimum thickness required by the tolerances in
				  the specification to which the pipe is manufactured. If a notch is not
				  repairable by grinding, a cylinder of the pipe containing the entire notch must
				  be removed. [
				  49 CFR
				  195.226(b)]
C. A ground may not be welded to the pipe or
				  fitting that is being welded. [
				  49 CFR
				  195.226(c)]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30228 - Welds and Welding Inspection: Standards of Acceptability [49 CFR 195.228]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each weld and
				  welding must be inspected to insure compliance with the requirements of this
				  Chapter. Visual inspection must be supplemented by nondestructive testing. [
				  49 CFR
				  195.228(a)]
B. The acceptability of a weld is determined
				  according to the standards in Section 9 or Appendix A of API Std 1104. Appendix
				  A of API Std 1104 may not be used to accept cracks. [
				  49 CFR
				  195.228(b)
				  ]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S. 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30230 - Welds: Repair or Removal of Defects [49 CFR 195.230]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each weld that is unacceptable under
				  §30228 must be removed or repaired.
				  Except for welds on an off-shore pipeline being installed from a pipelay
				  vessel, a weld must be removed if it has a crack that is more than 8 percent of
				  the weld length. [
				  49 CFR
				  195.230(a)]
B. Each weld that is repaired must have the
				  defect removed down to sound metal and the segment to be repaired must be
				  preheated if conditions exist which would adversely affect the quality of the
				  weld repair. After repair, the segment of the weld that was repaired must be
				  inspected to ensure its acceptability. [
				  49 CFR
				  195.230(b)]
C. Repair of a crack, or of any defect in a
				  previously repaired area must be in accordance with written weld repair
				  procedures that have been qualified under §30214 Repair procedures must
				  provide that the minimum mechanical properties specified for the welding
				  procedure used to make the original weld are met upon completion of the final
				  weld repair. [
				  49 CFR
				  195.230(c)]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30234 - Welds: Nondestructive Testing [49 CFR 195.234]

Current through Register Vol. 50, No. 6, June 20, 2024
A. A weld may be nondestructively tested by
				  any process that will clearly indicate any defects that may affect the
				  integrity of the weld. [
				  49 CFR
				  195.234(a)]
B. Any nondestructive testing of welds must
				  be performed: [
				  49 CFR
				  195.234(b)]
1. in accordance with a written set of
				  procedures for nondestructive testing; and [
				  49 CFR
				  195.234(b)(1)]
2. with personnel that have been trained in
				  the established procedures and in the use of the equipment employed in the
				  testing. [
				  49 CFR
				  195.234(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30246 - Installation of Pipe in a Ditch [49 CFR 195.246]

Current through Register Vol. 50, No. 6, June 20, 2024
A. All pipe installed in a ditch must be
				  installed in a manner that minimizes the introduction of secondary stresses and
				  the possibility of damage to the pipe. [
				  49 CFR
				  195.246(a)]
B. Except for pipe in the Gulf of Mexico and
				  its inlets in waters less than 15 feet deep, all offshore pipe in water at
				  least 12 feet deep (3.7 meters) but not more than 200 feet deep (61 meters)
				  deep as measured from the mean low water must be installed so that the top of
				  the pipe is below the underwater natural bottom (as determined by recognized
				  and generally accepted practices) unless the pipe is supported by stanchions
				  held in place by anchors or heavy concrete coating or protected by an
				  equivalent means. [
				  49 CFR
				  195.246(b)]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30248 - Cover over Buried Pipeline [49 CFR 195.248]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Unless specifically exempted in this
				  Chapter, all pipe must be buried so that it is below the level of cultivation.
				  Except as provided in §30248. B of this Section, the pipe must be installed so
				  that the cover between the top of the pipe and the ground level, road bed,
				  river bottom, or underwater natural bottom (as determined by recognized and
				  generally accepted practices), as applicable, complies with the following table
				  [
				  49 CFR
				  195.248(a)].
Cover (Inches)(Millimeters)
Location
For Normal Excavation
For Rock
								Excavation1
Industrial, commercial and residential area
36 (914)
30 (762)
Crossings of inland bodies of water with a width
								of at least 100 ft. (30 meters) from high water mark to high water mark
48 (1219)
18 (457)
Drainage ditches at public roads and railroads
36 (914)
36 (914)
Deepwater port safety zone
48 (1219)
24 (610)
Gulf of Mexico and its inlets in waters less than
								15 feet (4.6 meters) deep as measured from mean low water
36 (914)
18 (457)
Other offshore areas under water less than 12 ft
								(3.7 meters) deep as measured from mean low water
36 (914)
18 (457)
Any other area
30 (762)
18 (457)
1 Rock excavation is any
					 excavation that requires blasting or removal by equivalent means.
B. Except for the Gulf of Mexico
				  and its inlets in waters less than 15 feet (4.6 meters) deep, less cover than
				  the minimum required by Subsection A of this Section and
				  §30210 may be used if [
				  49 CFR
				  195.248(b)] :
1. it is impracticable to comply with the
				  minimum cover requirements; and [
				  49 CFR
				  195.248(b)(1)]
2. additional protection is provided that is
				  equivalent to the minimum required cover. [
				  49 CFR
				  195.248(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30250 - Clearance between Pipe and Underground Structures [49 CFR 195.250]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Any pipe
				  installed underground must have at least 12 inches (305 millimeters) of
				  clearance between the outside of the pipe and the extremity of any other
				  underground structure, except that for drainage tile the minimum clearance may
				  be less than 12 inches (305 millimeters) but not less than 2 inches (51
				  millimeters). However, where 12 inches (305 millimeters) of clearance is
				  impracticable, the clearance may be reduced if adequate provisions are made for
				  corrosion control. [
				  49 CFR
				  195.250]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30252 - Backfilling [49 CFR 195.252]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				  When a ditch for a pipeline is backfilled, it must be backfilled in a manner
				  that: [
				  49
				  CFR 195.252(a)]
1. provides firm support under the pipe; and
				   [49
				  CFR 195.252(a)(1)
				  ]
2. prevents damage to the pipe
				  and pipe coating from equipment or from the backfill material. [
				  49
				  CFR 195.252(a)(2)
				  ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30254 - Above Ground Components [49 CFR 195.254]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Any component may be installed above
				  ground in the following situations, if the other applicable requirements of
				  this Subpart are complied with: [
				  49 CFR
				  195.254(a)]
1. overhead crossing of highways, railroads,
				  or body of water; [
				  49 CFR
				  195.254(a)(1)]
2. spans over ditches and gullies; [
				  49 CFR
				  195.254(a)(2)]
3. scraper traps or block valves; [
				  49 CFR
				  195.254(a)(3)]
4. area under the direct control of the
				  operator; [
				  49 CFR
				  195.254(a)(4)]
5. in any area inaccessible to the public. [
				  49 CFR
				  195.254(a)(5)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30256 - Crossing of Railroads and Highways [49 CFR 195.256]

Current through Register Vol. 50, No. 6, June 20, 2024
A. The pipe at each railroad or highway
				  crossing must be installed so as to adequately withstand the dynamic forces
				  exerted by anticipated traffic loads. [
				  49 CFR
				  195.256]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30262 - Pumping Equipment [49 CFR 195.262]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Adequate ventilation must be provided in
				  pump station buildings to prevent the accumulation of hazardous vapors. Warning
				  devices must be installed to warn of the presence of hazardous vapors in the
				  pumping station building. [
				  49 CFR
				  195.262(a)]
B. The following must be provided in each
				  pump station: [
				  49 CFR
				  195.262(b)]
1. safety devices that prevent overpressuring
				  of pumping equipment, including the auxiliary pumping equipment within the
				  pumping station; [
				  49 CFR
				  195.262(b)(1)]
2. a device for the emergency shutdown of
				  each pumping station; [
				  49 CFR
				  195.262(b)(2)]
3. if power is necessary to actuate the
				  safety devices, an auxiliary power supply. [
				  49 CFR
				  195.262(b)(3)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30264 - Impoundment, Protection against Entry, Normal/Emergency Venting or Pressure/Vacuum Relief for Aboveground Breakout Tanks [49 CFR 195.264]

Current through Register Vol. 50, No. 6, June 20, 2024
A. A means must be
				  provided for containing hazardous liquids in the event of spillage or failure
				  of an aboveground breakout tank. [
				  49
				  CFR 195.264(a)]
B. After October 2, 2000, compliance with
				  Subsection A of this Section requires the following for the aboveground
				  breakout tank specified. [
				  49
				  CFR 195.264(b)]
1. For tanks built to API Spec 12F, API Std
				  620, and others (such as API Standard 650(or its predecessor Standard 12C)),
				  the installation of impoundment must be in accordance with the following
				  sections of NFPA-30 (incorporated by reference, see §30107): [
				  49
				  CFR 195.264(b)(1)]
a. impoundment around a breakout tank must be
				  installed in accordance with Section 22.11 2; and [
				  49
				  CFR 195.264(b)(1)(i)
				  ]
b. impoundment by drainage to a
				  remote impounding area must be installed in accordance with Section 221.1 [
				  49
				  CFR 195.264(b)(1)(ii)
				  ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 302 - Transportation of Hazardous Liquids by Pipeline-Construction [49 CFR Part 195 Subpart D] › Section V-30266 - Construction Records [49 CFR 195.266]

Current through Register Vol. 50, No. 6, June 20, 2024
A. A complete record that shows the following
				  must be maintained by the operator involved for the life of each pipeline
				  facility: [
				  49 CFR
				  195.266]
1. the total number of girth welds and the
				  number nondestructively tested, including the number rejected and the
				  disposition of each rejected weld; [
				  49 CFR
				  195.266(a)]
2. the amount, location, and cover of each
				  size of pipe installed; [
				  49 CFR
				  195.266(b)]
3. the location of each crossing of another
				  pipeline; [
				  49 CFR
				  195.266(c)]
4. the location of each buried utility
				  crossing; [
				  49 CFR
				  195.266(d)]
5. the location of each overhead crossing; [
				  49 CFR
				  195.266(e)]
6. the location of each valve and corrosion
				  test station. [
				  49 CFR
				  195.266(f)]
7. for pipelines transporting carbon dioxide,
				  the location of each weighted pipe or other item connected to the
				  pipe.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30300 - Scope [49 CFR 195.300]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				  This Chapter prescribes minimum requirements for the pressure testing of steel
				  pipelines. However, this Chapter does not apply to movement of pipe under
				  §30424 [49 CFR 195.300]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30302 - General Requirements [49 CFR 195.302]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Except as otherwise provided in this
				  Section and in
				  §30305 B, no operator may operate a
				  pipeline unless it has been pressure tested under this Chapter without leakage.
				  In addition, no operator may return to service a segment of pipeline that has
				  been replaced, relocated, or otherwise changed until it has been pressure
				  tested under this Chapter without leakage. Pipelines transporting carbon
				  dioxide must be hydrostatically tested without leakage. [49 CFR
				  195.302(a)]
B. Except for pipelines converted under
				  §30111, the following pipelines may be operated without pressure testing under
				  this Chapter. [
				  49 CFR
				  195.302(b)]
1. Any hazardous liquid pipeline whose
				  maximum operating pressure is established under §30406. A.5 that is: [
				  49 CFR
				  195.302(b)(1)]
a. an interstate pipeline constructed before
				  January 8, 1971; [
				  49 CFR
				  195.302(b)(1)(i)]
b. an interstate offshore gathering line
				  constructed before August 1, 1977; [
				  49 CFR
				  195.302(b)(1)(ii)
				  ]
c. an intrastate pipeline
				  constructed before October 21, 1985; or [
				  49 CFR
				  195.302(b)(1)(iii)
				  ]
d. a low-stress pipeline
				  constructed before August 11, 1994 that transports HVL. [
				  49 CFR
				  195.302(b)(1)(iv)
				  ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30304 - Test Pressure [49 CFR 195.304]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				  The test pressure for each pressure test conducted under this Chapter must be
				  maintained throughout the part of the system being tested for at least four
				  continuous hours at a pressure equal to 125 percent, or more, of the maximum
				  operating pressure and, in the case of a pipeline that is not visually
				  inspected for leakage during the test, for at least an additional four
				  continuous hours at a pressure equal to 110 percent, or more, of the maximum
				  operating pressure. [
				  49
				  CFR 195.304]
AUTHORITY NOTE:
					 Promulgated in accordance with
					 R.S.30:703
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30305 - Testing of Components [49 CFR 195.305]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each pressure test under
				  §30302 must test all pipe and attached
				  fittings, including components, unless otherwise permitted by §30305. B [
				  49 CFR
				  195.305(a)]
B. A component, other than pipe, that is the
				  only item being replaced or added to the pipeline system need not be
				  hydrostatically tested under §30305. A if the manufacturer certifies that
				  either: [
				  49 CFR
				  195.305(b)]
1. the component was hydrostatically tested
				  at the factory; or [
				  49 CFR
				  195.305(b)(1)]
2. the component was manufactured under a
				  quality control system that ensures each component is at least equal in
				  strength to a prototype that was hydrostatically tested at the factory. [
				  49 CFR
				  195.305(b)(2)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30306 - Test Medium [49 CFR 195.306]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				  Except as provided in §30306 B, C, and D, water must be used as the test
				  medium. [
				  49
				  CFR 195.306(a)]
B. Except for offshore pipelines, liquid
				  petroleum that does not vaporize rapidly may be used as the test medium if: [
				  49
				  CFR 195.306(b)]
1. the entire pipeline section under test is
				  outside of cities and other populated areas; [
				  49
				  CFR 195.306(b)(1)
				  ]
2. each building within 300 feet
				  (91 meters) of the test section is unoccupied while the test pressure is equal
				  to or greater than a pressure which produces a hoop stress of 50 percent of
				  specified minimum yield strength; [
				  49
				  CFR 195.306(b)(2)
				  ]
3. the test section is kept under
				  surveillance by regular patrols during the test; and [
				  49
				  CFR 195.306(b)(3)
				  ]
4. continuous communication is
				  maintained along entire test section. [
				  49
				  CFR 195.306(b)(4)
				  ]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30307 - Pressure Testing Aboveground Breakout Tanks [49 CFR 195.307]

Current through Register Vol. 50, No. 6, June 20, 2024
A. For aboveground
				  breakout tanks built to API Spec 12F (incorporated by reference, see §30107)
				  and first placed in service after October 2, 2000, pneumatic testing must be in
				  accordance with section 5.3 of API Spec 12 F. [
				  49 CFR
				  195.307(a)]
B. For aboveground breakout tanks built to
				  API Std 620 (incorporated by reference, see §30107) and first placed in service
				  after October 2, 2000, hydrostatic and pneumatic testing must be in accordance
				  with section 7.18 of API Std 620. [
				  49 CFR
				  195.307(b)]
C. For aboveground breakout tanks built to
				  API Std 650 (incorporated by reference, see §30107) and first placed in service
				  after October 2, 2000, testing must be in accordance with sections 7.3.5 of API
				  Standard 650 (incorporated by reference, see §30107). [
				  49 CFR
				  195.307(c)]
D. For aboveground atmospheric pressure
				  breakout tanks constructed of carbon and low alloy steel, welded or riveted,
				  and non-refrigerated; and tanks that are returned to service after October 2,
				  2000, and are built to API Std 650 or its predecessor Standard 12C; the
				  necessity for the hydrostatic testing of repair, alteration, and reconstruction
				  is covered in section 12.3 of API Standard 653. [
				  49 CFR
				  195.307(d)]
E. For aboveground breakout tanks built to
				  API Std 2510 (incorporated by reference, see §30107) and first placed in
				  service after October 2, 2000, pressure testing must be in accordance with 2007
				  ASME Boiler and Pressure Vessel Code (BPVC), (Section VIII, Division 1 or 2). [
				  49 CFR
				  195.307(e)]
AUTHORITY NOTE:
					 Promulgated in accordance with
					 R.S.
					 30:703.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30308 - Testing of Tie-Ins [49 CFR 195.308]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Pipe associated with tie-ins must be
				  pressure tested, either with the section to be tied in or separately. [
				  49 CFR 195.308
				  ]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 303 - Transportation of Hazardous Liquids by Pipeline-Pressure Testing [49 CFR Part 195 Subpart E] › Section V-30310 - Records [49 CFR 195.310]

Current through Register Vol. 50, No. 6, June 20, 2024
A. A
				  record must be made of each pressure test required by this Chapter, and the
				  record of the latest test must be retained as long as the facility tested is in
				  use.  [49 CFR
				  195.310(a)]
B. The record required by §30310. A must
				  include: [
				  49 CFR
				  195.310(b)]
1. the pressure recording charts; [
				  49 CFR
				  195.310(b)(1)]
2. test instrument calibration data; [
				  49 CFR
				  195.310(b)(2)]
3. the name of the operator, the name of the
				  person responsible for making the test, and the name of the test company used,
				  if any; [
				  49 CFR
				  195.310(b)(3)]
4. the date and time of the test; [
				  49 CFR
				  195.310(b)(4)]
5. the minimum test pressure; [
				  49 CFR
				  195.310(b)(5)]
6. the test medium; [
				  49 CFR
				  195.310(b)(6)]
7. a description of the facility tested and
				  the test apparatus; [
				  49 CFR
				  195.310(b)(7)]
8. an explanation of any pressure
				  discontinuities, including test failures, that appear on the pressure recording
				  charts; [
				  49 CFR
				  195.310(b)(8)]
9. where elevation differences in the section
				  under test exceed 100 feet (30 meters), a profile of the pipeline that shows
				  the elevation and test sites over the entire length of the test section; and [
				  49 CFR
				  195.310(b)(9)]
10. temperature of the test medium or pipe
				  during the test period. [
				  49 CFR
				  195.310(b)(10)]
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 304 - Transportation of Hazardous Liquids by Pipeline-Operation and Maintenance [49 CFR Part 195 Subpart F] › Section V-30400 - Scope [49 CFR 195.400]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				  This Chapter prescribes minimum requirements for operating and maintaining
				  pipeline systems constructed with steel pipe. [
				  49 CFR
				  195.400]
AUTHORITY NOTE:
					 Promulgated in accordance with R.S.
					 30:753.
Louisiana Administrative Code › Title 33 - ENVIRONMENTAL QUALITY › Part V - Hazardous Wastes and Hazardous Materials › Subpart 3 - Natural Resources › Chapter 304 - Transportation of Hazardous Liquids by Pipeline-Operation and Maintenance [49 CFR Part 195 Subpart F] › Section V-30401 - General Requirements [49 CFR 195.401]

Current through Register Vol. 50, No. 6, June 20, 2024
A. No operator may operate or maintain its
				  pipeline systems at a level of safety lower than that required by this Chapter
				  and the procedures it is required to establish under §30402. A [
				  49 CFR
				  195.401(a)]
B. An operator must make repairs on its
				  pipeline system according to the following requirements. [
				  49 CFR
				  195.401(b)]
1. Non Integrity Management Repairs. Whenever
				  an operator discovers any condition that could adversely affect the safe
				  operation of its pipeline system, it must correct the condition within a
				  reasonable time. However, if the condition is of such a nature that it presents
				  an immediate hazard to persons or property, the operator may not operate the
				  affected part of the system until it has corrected the unsafe condition. [
				  49 CFR
				  195.401(b)(1)]
2. Integrity Management Repairs. When an
				  operator discovers a condition on a pipeline covered under §30452, the operator
				  must correct the condition as prescribed in §30452. H [
				  49 CFR
				  195.401(b)(2)]
3. Prioritizing Repairs. An operator must
				  consider the risk to people, property, and the environment in prioritizing the
				  correction of any conditions referenced in Paragraphs B.1 and 2 of this
				  Section. [49 CFR
				  195.401(b)(3)]