reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-24 - Campground sewage disposal

Current through July 10, 2024
Authority: IC 16-19-3-4
Affected: IC 13-18-12; IC 16-19-3
Sec. 24.
(a) All
				sewage generated by a campground, including gray water, shall be disposed of
				via a connection to a public sewer if available within a reasonable distance
				from the campground. If a public sewer is not available within a reasonable
				distance, sewage disposal must comply with
				410
				IAC 6-12,
				410 IAC
				6-10, Bulletin S.E. 11, Bulletin S.E. 13, or
				applicable rules of the Indiana department of environmental
				management.
(b) If individual sewer
				connections are provided for recreational vehicles, these connections shall
				meet the following minimum requirements:
(1)
				Each individual sewer riser shall be at least four (4) inches in
				diameter.
(2) Each individual sewer
				connection shall be tightly capped when a recreational vehicle is not
				connected.
(3) The rim of the riser
				pipe shall extend four (4) inches above the ground, and surface drainage shall
				be diverted away from the riser.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-25 - Sanitary dumping station

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 25.
(a) All
				campgrounds, except those having only independent campsites, shall have at
				least one (1) sanitary dumping station for each two hundred fifty (250)
				dependent campsites or fraction thereof.
(b) Each sanitary dumping station must be
				equipped with the following:
(1) A four (4)
				inch sewer riser pipe with a self-closing hinged cover or other tight-fitting
				closure.
(2) A concrete apron at
				least three (3) feet in diameter and sloped to drain the area surrounding the
				inlet of the riser pipe.
(3) A
				water outlet for sanitary maintenance of the station.
(4) A sign located at the water outlet which
				states that the water is not for drinking, but for flushing and cleaning
				holding tanks and the dump station area.
(5) A vacuum breaker installed downstream of
				the last shut-off valve that meets the requirements of 675 IAC 16.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-26 - Campground sanitary facilities

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 26.
(a) A
				campground with dependent campsites shall have flush toilets, sanitary vault
				privies, or portable toilets, in the following ratios:
Number of Dependent Campsites
Toilet Facilities
Urinals*
Men
Women
Men
1-15
1
1
0
16-30
1
2
1
31-45
2
3
1
46-60
2
4
2
61-100
3
5
2
*Toilets may be substituted for the required number of
				  urinals on a one-for-one basis.
(b) Campgrounds with more than one hundred
				(100) dependent campsites shall be provided with one (1) flush toilet, sanitary
				vault privy, or portable toilet for each sex in the ratio of one (1) per thirty
				(30) dependent campsites and one (1) urinal for each one hundred (100)
				additional campsites.
(c) The
				entrance to a sanitary facility shall have a sign to designate which sex may
				use the facility. Solid walls extending from floor to ceiling shall separate
				facilities for each sex located in the same building.
(d) For all common use rooms that contain
				sanitary or laundry facilities, excluding sanitary vault privies and portable
				toilets, the following minimum requirements shall apply:
(1) Floors, walls, and partitions around
				showers, lavatories, and other plumbing fixtures shall be smooth, nonabsorbent,
				and easily cleanable.
(2) Bathing
				and hand washing facilities shall have hot and cold water under pressure.
				Bathing facilities shall have an approved, properly operating automatic
				temperature control valve. The valve must control the water temperature at the
				point of use so it will not exceed one hundred twenty (120) degrees
				Fahrenheit.
(3) An operating
				mechanical exhaust device is required and must replace the air in the facility
				at least six (6) times per hour.
(4) Exterior openings shall be screened
				utilizing screening of not less than sixteen (16) mesh.
(5) Entrances to toilet and bathing
				facilities shall have self-closing doors.
(6) Toilet and bathing facilities shall be
				configured to prevent viewing of the interior through the entrance
				door.
(7) Light fixtures shall have
				guards or shields to prevent shattering.
(8) At least twenty (20) foot-candles of
				light measured thirty (30) inches above the floor must be provided throughout
				the interior of any permanent facility within a campground.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-28 - Refuse collection and disposal

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 26.
(a) Refuse,
				including garbage, shall be collected, stored, and disposed of properly so the
				campground is clean and litter free. Refuse shall not accumulate in a manner
				that could:
(1) result in rodent harborage or
				promote insect breeding; or
(2)
				cause a fire, safety, or health hazard.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-29 - Electrical distribution system

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 29.
(a) After
				the effective date of this rule, all new wiring, lighting, and electrical
				hook-ups shall be installed in compliance with 675 IAC 17. Existing wiring,
				lighting, and electrical hook-ups shall be installed and maintained in a safe
				condition.
(b) Fifteen (15) and
				twenty (20) ampere, one hundred twenty-five (125) volt receptacles at sanitary
				facilities shall have approved ground fault circuit interrupter
				protection.
(c) Electrical
				receptacles shall have wiring and circuit breakers or fuses sized to conform to
				the amperage of the receptacle they supply.
(d) Switches, circuit breakers, receptacles,
				control equipment, and metering devices located in wet places or outside a
				building shall be weatherproof.
(e)
				Splices in electrical wires in accessible locations shall be made in approved
				junction boxes.
(f) When
				underground conductors enter or leave a building or a trench, they shall have
				mechanical protection from physical damage. The protection must be rigid
				conduit, intermediate metal conduit, rigid nonmetallic conduit, schedule 80
				electrical plastic tubing, or other mechanical means. Underground conductors in
				conduit shall be a minimum of eighteen (18) inches below finished grade.
				Underground conductors not in conduit shall be a minimum of twenty-four (24)
				inches below finished grade.
(g)
				Electrical equipment and conductors shall not be attached to trees.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-30 - Emergency equipment and services

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 30.
Telephone service shall be made available to all campers,
				  and access shall be provided at all times to such service for emergency use.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-31 - Registration

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 31.
A register containing the name and home address of the
				  campsite occupant and the dates of arrival and departure must be maintained and
				  available for inspection by the department or the local health
				  officer.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-32 - Right of entry

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 32.
The department or the local health officer may enter public
				  or private property at reasonable times and, upon presentation of credentials,
				  to do any of the following:
(1)
				Inspect facilities, equipment, or records.
(2) Investigate allegations, conduct tests,
				or collect samples.
(3) Obtain
				information necessary to the issuance of a permit pursuant to this
				rule.
(4) Determine whether any
				person is subject to, or in violation of, this rule or a permit issued pursuant
				to this rule.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-33 - Local authorities

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 33.
Local health officers may enforce the rules of the
				  department. County and municipal authorities within their respective
				  jurisdictions have jurisdiction over zoning, building codes, and ordinances
				  pertaining to campgrounds.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-34 - Incorporation by reference

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 34.
Bulletin S.E. 11 and Bulletin S.E. 13 are incorporated by
				  reference as part of this rule. Copies of these bulletins may be obtained by
				  request to the department.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.1 - Campgrounds › Section 7.1-35 - Enforcement

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 4-21.5-3-6; IC 4-21.5-3-8; IC 16-19-3
Sec. 35.
The department may commence an action under IC
				  16-19-3-4,
				  IC
				  16-19-3-5,
				  and IC 4-21.5-3-6, or IC 4-21.5-3-8 against a campground operator who:
(1) fails to comply with this rule;
				or
(2) interferes with or obstructs
				the department or its designated agent in the performance of duties pursuant to
				this rule.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-1 - Definitions

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 1.
The definitions in this rule apply throughout this
				  rule.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-2 - "Bathing beach" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 2.
"Bathing beach" means a body of water not contained within a
				  structure, chamber, or tank and used for swimming, diving, or recreational
				  bathing.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-3 - "Camp" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 3.
"Camp" means a youth camp.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-4 - "Department" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 4.
"Department" means the Indiana department of health.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-5 - "Designated adult" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 5.
"Designated adult" means the individual with the primary
				  responsibility for health matters, food, staff supervision, the administration
				  of program operations, and business and transportation services.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-6 - "Gray water" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 6.
"Gray water" means wastewater originating from dish washing,
				  hand washing, laundering, showers, or sinks.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-7 - "Local health officer" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 7.
"Local health officer" means the health officer of any local
				  health department or their authorized representative.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-8 - "Person" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 8.
"Person" means any individual, firm, partnership, company,
				  corporation, trustee, association, municipality, county, authority, estate, or
				  public or private entity owning, conducting, controlling, managing, or
				  operating a camp.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-9 - "Primitive camp" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 9.
"Primitive camp" means a youth camp that operates at a site
				  having only tents.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-10 - "Public sewer" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 10.
"Public sewer" means a sewage disposal facility provided by
				  a utility, municipality, conservancy district, or regional sewer
				  district.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-11 - "Public water supply" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 11.
"Public water supply" means water supplied by a utility,
				  municipality, conservancy district, regional water district, rural water
				  corporation, or not-for-profit water corporation.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-12 - "Tent" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 12.
"Tent" means a shelter having twenty-five percent (25%) or
				  more of its walls or roof, or both, covered by fabric material.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-13 - "Water station" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 13.
"Water station" means a facility for filling water storage
				  containers with potable water from an approved water system.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-14 - "Youth camp" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 14.
"Youth camp" means any area or tract of land established,
				  operated, or maintained to provide more that seventy-two (72) continuous hours
				  of outdoor group living experiences away from established residences for
				  educational, recreational, sectarian, or health purposes to ten (10) or more
				  children who are under eighteen (18) years of age and not accompanied by a
				  parent or guardian.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-15 - Construction permit requirement

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 15.
Any person planning the construction, addition to, or
				  significant change in the construction of any youth camp shall, at least ninety
				  (90) days prior to the initiation of any such construction, submit plans, drawn
				  to scale, for review and approval by the department. These plans must be
				  certified by a registered engineer or architect licensed to practice in
				  Indiana.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-16 - General supervision

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 16.
When a youth camp is in session, there shall be a designated
				  adult on the premises who is responsible for compliance with this rule.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-17 - General health

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 17.
(a) When a
				youth camp is in session, there shall be an individual present who is
				designated as the health supervisor and who has completed at least the Red
				Cross Standard First Aid Course or its equivalent.
(b) A member of the camp health staff shall
				conduct a health screening of each camper to identify any illness or
				communicable disease. The screening shall:
(1)
				occur not more than twelve (12) hours after arrival at camp; and
(2) include a check of medications in use by
				each camper.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-18 - Infirmary

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 18.
(a) Youth
				camps constructed after the effective date of this rule shall include a
				separate room with toilet and lavatory facilities to be used as an infirmary
				and isolation area.
(b) The
				separate room described in subsection (a) shall have the following:
(1) Ventilation to keep it free of excessive
				heat, condensation, vapors, noxious odors, and fumes.
(2) Heating equipment capable of maintaining
				a temperature of at least sixty-eight (68) degrees Fahrenheit.
(3) At least one (1) cot per one hundred
				(100) campers and staff, with a minimum of two (2) cots.
(4) At least one (1) adult shall be present
				when campers are in the infirmary.
(5) At least seventy (70) foot-candles of
				light measured thirty (30) inches from the floor.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-19 - First aid kits

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 19.
(a) First
				aid kits shall be available to camp staff at food service operations, beaches,
				the infirmary, the camp office, primitive camps, and readily available in a
				timely manner to all program areas. First aid may be administered only by
				properly trained staff.
(b) As a
				minimum, each first aid kit must include the following:
(1) One (1) watertight medication
				canister.
(2) Thirty (30) adhesive
				bandages, each measuring one (1) inch by three (3) inches.
(3) One (1) roll of adhesive tape measuring
				one-half (½) inch by ten (10) yards.
(4) Nine (9) antiseptic towelettes.
(5) Two (2) disposable gloves, such as
				surgical or examination type.
(6)
				One (1) triangular bandage.
(7) Six
				(6) sponge dressing pads, each measuring two (2) inches by two (2)
				inches.
(8) Four (4) sponge
				dressing pads, each measuring three (3) inches by three (3) inches.
(9) Two (2) sponge dressing pads, each
				measuring four (4) inches by four (4) inches.
(10) One (1) instant ice compress measuring
				at least six (6) inches by four (4) inches.
(11) Two (2) large fabric fingertip
				bandages.
(12) Two (2) large fabric
				knuckle bandages.
(13) Two (2)
				island bandages each measuring two (2) inches by three (3) inches.
(14) Two (2) adhesive Telfa bandages each
				measuring two (2) inches by two (2) inches.
(15) One (1) eye pad.
(16) Three (3) providone-iodine
				pads.
(17) Six (6) alcohol
				cleansing pads.
(18) Three (3)
				tubes of triple-antibacterial cream.
(19) One (1) conform bandage roll measuring
				two (2) inches by five (5) yards.
(20) One (1) pair of scissors.
(21) One (1) pair of tweezers.
(22) One (1) emergency blanket.
(23) One (1) refillable plastic
				case.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-20 - Records

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 20.
(a) A
				record for each camper must be maintained by the designated adult operating a
				camp and shall contain the following:
(1) The
				camper's name and address.
(2) The
				name, address, and telephone number of the camper's parent, legal guardian, or
				designated adult emergency contact.
(3) Authorization from the parent or guardian
				for emergency medical care.
(4) A
				list of relevant health conditions that camp personnel may encounter.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-21 - Campsites and safety

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 21.
(a) No
				condition, situation, or installation shall be created, installed, or
				maintained that:
(1) may cause or result in a
				health or safety hazard; or
(2)
				cause or transmit disease or harbor rodents or other vermin.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-22 - Emergency equipment and procedures

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 22.
(a)
				Telephone service shall be provided to each youth camp as follows:
(1) Telephone service shall always be
				accessible at youth camps.
(2) The
				telephone number of the nearest fire department, police department, poison
				control center, and emergency medical service shall be posted next to each
				telephone. Where 911 service is available, only the poison control center
				telephone number must be posted.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-23 - Fire and building safety

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 23.
(a) Each
				youth camp shall be equipped with a minimum of a 4-A, 60-B:C, ten (10) pound,
				multipurpose, dry chemical, pressure fire extinguisher within one hundred (100)
				feet of each kitchen, furnace room, and sleeping facilities.
(b) Fire extinguishers must be readily
				accessible and maintained in an operable condition.
(c) Exits from structures must be maintained
				free of obstructions and have exit signs clearly posted.
(d) Buildings with occupancy of more than ten
				(10) persons shall have at least two (2) separate and independent exits. Exits
				shall not be closer to each other than fifty percent (50%) of the longest
				exterior dimension of the building.
(e) Buildings with occupancy above the first
				floor shall have two (2) separate and independent exits. At least one (1) exit
				shall lead directly to the outside.
(f) A one-room building used for sleeping
				shall be equipped with a smoke detector.
(g) Buildings with two (2) or more
				compartmentalized sleeping rooms shall have hard-wired interconnected smoke
				detectors. (h) All required smoke detectors shall be UL listed.
(i) All required smoke detectors shall be
				kept clean and tested monthly.
(j)
				Fire drills shall be held within twenty-four (24) hours of the beginning of
				each camping session and weekly thereafter.
(k) Gasoline and other flammable fluids shall
				be marked and stored in locked containers or in locked buildings not occupied
				by campers.
(l) Gasoline and other
				flammable fluids shall be stored at least fifty (50) feet from sleeping
				quarters.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-24 - Electrical safety

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 24.
(a) Wiring,
				lighting, and electrical receptacles shall be installed and maintained in a
				safe condition.
(b) Fifteen (15)
				and twenty (20) ampere, one hundred twenty-five (125) volt receptacles in
				sanitary facilities, bathrooms, garages, or maintenance buildings or located
				outside of buildings shall be equipped with ground-fault circuit interrupter
				protection.
(c) Electrical
				receptacles shall have wiring and circuit breakers or fuses sized to conform to
				the amperage of the receptacles they supply.
(d) Electrical switches, circuit breakers,
				receptacles, control equipment, and metering devices located in wet places or
				outside of a building shall be weatherproof.
(e) Splices to electrical wires at accessible
				locations shall be made utilizing approved junction boxes.
(f) In areas subject to vehicle movement,
				service drop conductors of not over six hundred (600) volts nominal, shall be
				at least eighteen (18) feet above the ground surface. In other areas, the
				minimum clearance shall be ten (10) feet above the ground surface.
(g) Electrical equipment and conductors shall
				not be attached to trees.
(h)
				Electrical receptacles shall be grounded and shall not have an open neutral,
				open hot conductor, or reverse polarity.
(i) Loose electrical equipment shall be
				secured. Face plates and panel fronts shall be in place to prevent accidental
				contact.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-25 - Water supplies

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 25.
(a) Camps
				shall be provided with an adequate and convenient supply of potable water that
				meets the Indiana department of environmental management public water supply
				drinking water quality standard found in 327 IAC 8. Potable water shall always
				be available for culinary, drinking, laundry, and bathing purposes.
(b) Wells shall be constructed, installed,
				and located in accordance with 327 IAC 8 and 312 IAC 13.
(c) A camp shall exclusively use a public
				water supply if public water is available within a reasonable distance. If a
				public water supply is not available, a camp shall have water supplied from a
				well that complies with 327 IAC 8.
(d) The construction and location of all camp
				wells with less than fifteen (15) service connections or serving less than
				twenty-five (25) people shall comply with all the requirements of this
				rule.
(e) Camp water supply and
				distribution systems shall have the capacity to deliver a minimum water
				pressure of twenty (20) pounds per square inch to all water stations and
				connections during periods of peak water usage. The water supply shall have
				capacity to meet total daily water demands. If a well or pump cannot meet peak
				or daily water demand, camps shall be provided with sufficient usable storage
				capacity to meet the demand.
(f)
				The casing pipe of a well shall project not less than:
(1) twenty-four (24) inches above floor level
				or finished grade; or
(2)
				thirty-six (36) inches above the regulatory flood elevation if located in a
				designated flood hazard area identified by the Federal Emergency Management
				Agency.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-26 - Sewage disposal

Current through July 10, 2024
Authority: IC 16-19-3-4
Affected: IC 13-18-12; IC 16-19-3
Sec. 26.
(a) Sewage
				shall be disposed of by a connection to a public sewer, if available within a
				reasonable distance from the camp. If a public sewer is not available within a
				reasonable distance from the camp, sewage disposal must comply with
				410
				IAC 6-12,
				410 IAC
				6-10, Bulletin S.E. 11, Bulletin S.E. 13, or
				applicable rules of the Indiana department of environmental management for
				sewage disposal facilities other than sanitary vault privies or septic tank
				soil-absorption systems.
(b) Only
				wastewater management businesses licensed pursuant to IC 13-18-12 shall clean
				camp privies and portable toilets of waste. Privies must be pumped when the
				accumulated waste is within eighteen (18) inches of the privy floor.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-28 - Cooking and eating facilities

Current through July 10, 2024
Authority: IC 16-19-3-4
Affected: IC 16-19-3
Sec. 28.
(a) Central
				kitchen and dining halls shall comply with
				410
				IAC 7-24.
(b) Kitchens separate from the central dining
				hall and used for individual campers to prepare meals shall meet the following
				requirements:
(1) Provide a refrigerator and a
				range with a ventilation hood.
(2)
				Provide a three (3) compartment sink or a two (2) compartment sink and a
				dishwasher or use only single service dishes and utensils.
(3) Provide a numerically scaled indicating
				thermometer in each refrigerator accurate to plus or minus three (3) degrees
				Fahrenheit, located as to be easily readable.
(4) Provide shielded or guarded light
				fixtures providing at least seventy (70) foot-candles of light on all food
				preparation surfaces and at equipment or utensil washing areas.
(5) Provide a hand washing lavatory having
				hot and cold water and a combination faucet.
(6) Provide the hand washing lavatory with a
				supply of hand cleansing soap and a supply of sanitary towels or a hand drying
				device. Sinks used for food preparation or food washing equipment shall not be
				used for hand washing.
(7) Common
				towels are prohibited.
(8) Provide
				a mop sink for use and disposal of mop water. Food preparation sinks shall not
				be used for this purpose.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-29 - Buildings and sleeping shelters

Current through July 10, 2024
Authority: IC 16-19-3-4
Affected: IC 16-19-3
Sec. 29.
(a)
				Buildings, structures, tents, and cabins shall be kept in good repair and
				maintained in a safe and sanitary condition.
(b) Floors and floor coverings in buildings
				used for sleeping or camp activities shall be in good repair and easily
				cleanable.
(c) Buildings used for
				sleeping shall have screened openable windows or mechanical ventilation as
				required by 675 IAC 14-4.3-1.
(d)
				Outside openings shall be screened with at least sixteen (16) mesh screen to
				prevent the entrance of insects.
(e) Screened doors shall be tight-fitting, in
				good repair, and self-closing.
(f)
				At least thirty (30) square feet of floor space per camper must be provided in
				rooms used for sleeping.
(g) Beds
				shall be arranged so the heads of the sleepers are at least six (6) feet apart
				and there is at least thirty (30) inches between the sides of the beds. Beds
				are not required to be permanently affixed to the floor.
(h) Sleeping rooms shall have a minimum
				ceiling height of seven (7) feet.
(i) Bedding provided by the camp operator
				shall be clean and washed before use by a new camper.
(j) Foam bed mattresses shall be provided
				with easily cleanable mattress covers.
(k) Vertical separation between the top of
				the lower mattress of a double deck bunk and the upper bunk shall be a minimum
				of twenty-seven (27) inches. The vertical separation from the top of the upper
				mattress to the ceiling shall be a minimum of thirty-six (36) inches.
(l) Bunk beds used by campers shall be
				equipped with guardrails on the upper bunk. Guardrails are required on any side
				of a bunk not placed tightly against a wall.
(m) At least twenty (20) foot-candles of
				light shall be provided throughout buildings used for sleeping.
(n) Tent material shall be flame-retardant.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-31 - Refuse collection

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 31.
(a) Refuse,
				including garbage, shall be collected, stored, and disposed of properly so the
				camp is clean and litter free. Refuse shall not accumulate in a manner that
				could:
(1) result in rodent harborage or
				promote insect breeding; or
(2)
				cause a fire, safety, or health hazard.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-32 - Animal and pest control

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 32.
(a) Animal
				shelters, corrals, tie rails, or hitching posts shall not be located within two
				hundred (200) feet of a dining hall, kitchen, or other place where food is
				prepared, cooked, or served.
(b)
				Buildings, grounds, and storage areas shall be kept free of insect and rodent
				infestations and free of refuse that could harbor rodents, mosquitoes, flies,
				and other pests.
(c) Lumber, pipe,
				and other building materials shall be stored at least four (4) inches above the
				ground.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-33 - Right of entry

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 33.
The department or the local health officer may enter public
				  or private property at reasonable times and, upon presentation of credentials,
				  to do any of the following:
(1) Inspect
				facilities, equipment, or records.
(2) Investigate allegations, conduct tests,
				or collect samples.
(3) Obtain
				information necessary to the issuance of a permit pursuant to this
				rule.
(4) Determine whether any
				person is subject to, or in violation of, this rule or a permit issued pursuant
				to this rule.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-34 - Incorporation by reference

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 34.
Bulletin S.E. 11 and Bulletin S.E. 13 are incorporated by
				  reference as part of this rule. Copies of these bulletins may be obtained free
				  of charge by mailing a request to the department.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-35 - Local authorities

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 16-19-3
Sec. 35.
Local health officers may enforce the rules of the
				  department. County and municipal authorities within their respective
				  jurisdictions have jurisdiction over zoning, building codes, and ordinances
				  pertaining to camps.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 7.2 - Youth Camps › Section 7.2-36 - Enforcement

Current through July 10, 2024
Authority: IC
				  16-19-3-4
Affected: IC 4-21.5-3-6; IC 4-21.5-3-8; IC
				  16-19-3-5
Sec. 36.
The department may commence an action under IC
				  16-19-3-4,
				  IC
				  16-19-3-5,
				  and IC 4-21.5-3-6, or IC 4-21.5-3-8 against a camp operator who:
(1) fails to comply with this rule;
				or
(2) interferes with or obstructs
				the department or its designated agent in the performance of duties pursuant to
				this rule.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-1 - Definitions

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 1.
The definitions in this rule apply throughout this rule.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-2 - "AASHTO" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 2.
"AASHTO" means the American Association of State Highway and
				  Transportation Officials.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-3 - "ABS" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 3.
"ABS" means acrylonitrile-butadiene-styrene.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-4 - "ANSI" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 4.
"ANSI" means the American National Standards Institute.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-5 - "ASTM" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 5.
"ASTM" means the American Society for Testing and Materials.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-6 - "Bedroom" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 6.
"Bedroom" means either any room:
(1) in a residence that the local health
				department and the owner agree could be occupied for the purpose of sleeping
				and contains:
(A) an area of seventy (70)
				square feet or more;
(B) at least
				one (1) operable window or exterior door for emergency egress or rescue;
				and
(C) for new construction, a
				closet; or
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-7 - "Bedroom equivalent" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 7.
"Bedroom equivalent" means any jetted bathtub with a capacity
				  of greater than one hundred twenty-five (125) gallons.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-8 - "Commissioner" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 8.
"Commissioner" means the commissioner of the department or
				  his or her legally authorized representative.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-9 - "Construction permit" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 9.
"Construction permit" means written approval by a local
				  health department for the installation, repair, or replacement of a residential
				  on-site sewage system.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-10 - "Densic material" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 10.
"Densic material" means relatively unaltered materials (do
				  not meet requirements for any other named diagnostic horizons or any other
				  diagnostic soil characteristic) that have a noncemented rupture resistance
				  class. The bulk density or the organization is such that roots cannot enter,
				  except in cracks. These are mostly earthy materials, such as till, volcanic
				  mudflows, and some mechanically compacted materials. Some noncemented rock can
				  be densic materials if they are dense or resistant enough to keep roots from
				  entering, except in cracks. Densic materials are noncemented and thus differ
				  from paralithic materials and the material below a lithic contact, both of
				  which are cemented. Densic materials have, at their upper boundary, a densic
				  contact if they have no cracks or if the spacing of cracks that roots can enter
				  is ten (10) centimeters (cm) or more. These materials can be used to
				  differentiate soil series if the materials are within the series control
				  section.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-11 - "Department" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 11.
"Department" means the Indiana department of health.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-12 - "Design daily flow" or "DDF" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 12.
"Design daily flow" or "DDF" means the calculated peak daily
				  sewage flow from a residence used to design a residential on-site sewage
				  system. It is one hundred fifty (150) gallons per day times the number of
				  bedrooms and bedroom equivalents.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-13 - "Distribution box" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 13.
"Distribution box" means a structure designed to distribute
				  effluent by gravity from a septic tank equally into the trenches of the soil
				  absorption system connected thereto.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-14 - "Drainageway" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 14.
"Drainageway" means the channel portion of the landscape in
				  which surface water or rainwater runoff gathers intermittently to flow to a
				  lower elevation.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-15 - "Dwelling" or "residence" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 15.
"Dwelling" or "residence" means any house or place used or
				  intended to be used as a place of seasonal or permanent human habitation or for
				  sleeping for one (1) or two (2) families, and any associated outbuildings that
				  are for the private use of the owner.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-16 - "Fill" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 16.
"Fill" means soil transported and deposited by man, as well
				  as soil recently transported and deposited by natural erosion forces. Fill is
				  evidenced by one (1) or more of the following:
(1) No soil horizons or indistinct soil
				horizons.
(2) Depositional
				stratification.
(3) Presence of a
				soil horizon that has been covered.
(4) Materials in a horizon such as cinders or
				construction debris.
(5) Position
				in the landscape.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-17 - "Foundation drain" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 17.
"Foundation drain" means that portion of a residential
				  drainage system provided to drain only ground water from outside of the
				  foundation of the house or from under the basement floor.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-18 - "Health officer" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 18.
"Health officer" means the health officer of a local board of
				  health.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-19 - "INDOT" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 19.
"INDOT" means the Indiana department of transportation.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-20 - "Interceptor drain" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 20.
"Interceptor drain" means a subsurface drainage system
				  constructed only on the upslope side or sides of a soil absorption system for
				  the purpose of diverting subsurface water around the soil absorption system
				  site.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-21 - "Local health department" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC 16-20
Sec. 21.
"Local health department" means a local health department
				  created pursuant to IC 16-20, or its duly authorized representative.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-22 - "NEMA" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 22.
"NEMA" means the National Electrical Manufacturers
				  Association.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-23 - "NRCS" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 23.
"NRCS" means the United States Department of Agriculture,
				  Natural Resources Conservation Service.
Indiana Administrative Code › Title 410 - INDIANA DEPARTMENT OF HEALTH › Article 6 - SANITARY ENGINEERING › Rule 8.3 - Residential On-Site Sewage Systems › Section 8.3-24 - "NSF" defined

Current through July 10, 2024
Authority: IC
				  16-19-3-4;
				  IC
				  16-19-3-5
Affected: IC
				  16-19-3-4
Sec. 24.
"NSF" means the National Sanitation Foundation
				  International.