reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-12 - Visitable bathrooms

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 12.
(a) Either
				all bathrooms in the dwelling unit shall comply with subsection (b) or at least
				one (1) bathroom in the dwelling unit shall comply with subsection (b) and all
				other bathrooms and powder rooms within the dwelling unit shall be on an
				accessible route with usable entry doors in accordance with TABLE V6.1 in
				section 6(a) of this rule or TABLE V6.2 in section 6(b) of this rule.
(b) Bathrooms that have reinforced walls for
				grab bars (see section 10 of this rule) shall conform to section 3(2)(B)(iii)
[sic.]
of this rule as follows:
(1) Sufficient maneuvering space shall be
				provided within the bathroom for a person using a wheelchair or other mobility
				aid to:
(A) enter and close the
				door;
(B) use the
				fixtures;
(C) reopen the door;
				and
(D) exit.
Doors may swing into the clear floor space provided at any
				  fixture if the maneuvering space is provided. Maneuvering spaces may include
				  any knee space or toe space available below bathroom
				  fixtures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-13 - Floor or ground surfaces

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-23-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 13.
(a) Floor or
				ground surfaces shall:
(1) be stable, firm,
				and slip-resistant; and
(2) comply
				with this section.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-14 - Exterior accessible routes

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 14.
(a) Exterior
				accessible routes shall consist of one (1) or more of the following components:
(1) Walking surfaces with a slope not greater
				than 1:20.
(2) Doorways.
(3) Ramps.
(4) Curb ramps.
(5) Elevators.
(6) Wheelchair (platform) lifts.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-1 - Purpose

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 1.
The purpose of this rule is to locate editions of NFPA
				  Standards adopted by the commission in one (1) article.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-2 - NFPA 10; standard for portable fire extinguishers

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 25-4; IC 25-31; IC 36-7
Sec. 2.
(a) That
				certain standard, being titled NFPA 10, Standard for Portable Fire
				Extinguishers, 2010 edition, published by the National Fire Protection
				Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts 02169-7471, be
				and the same is hereby adopted by reference as if fully set out in this section
				except as revised hereafter.
(b)
				This rule is available for review and reference at the:
Legal and Code Services Section
Indiana Department of Homeland Security
Indiana Government Center South
302 West Washington Street, Room W246
Indianapolis, Indiana 46204
(c) Delete the text of Section 1.1 and insert
				the following: Scope. The provisions of this standard apply to the selection,
				installation, inspection, maintenance, and testing of portable extinguishing
				systems.
(d) Delete Section 1.2 in
				its entirety without substitution.
(e) Amend Section 2.2 as follows:
(1) In the reference to NFPA 14, delete "2010
				edition" and insert "as adopted at
				675 IAC 13-1-9
				".
(2) In the reference to NFPA 58,
				delete "2008 edition" and insert "as adopted at
				675 IAC
				28-1-22 ".
(3) In the reference to NFPA 72, delete "2010
				edition" and insert "as adopted at
				675 IAC
				28-1-28 ".
(4) In the reference to NFPA 86, delete "2007
				edition" and insert "as adopted at
				675 IAC
				28-1-31 ".
(5) In the reference to NFPA 385, delete
				"2007 edition" and insert "as adopted at
				675
				IAC 28-1-34 ".
(6) In the reference to NFPA 407, delete
				"2007 edition" and insert "as adopted at
				675 IAC
				28-1-36 ".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-3 - NFPA 11; standard for low-, medium-, and high-expansion foam

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 3.
(a) Standard
				for Low-, Medium-, and High-Expansion Foam, NFPA 11, 2005 edition, published by
				National Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy,
				Massachusetts 02269-9101 is adopted by reference except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 11 are not adopted, are not enforceable, and are
				for information purposes only:
(1) NFPA 16,
				NFPA 24, NFPA 30, NFPA 1150, NFPA 1901, and NFPA 1961.
(2) ANSI B1.20.1, B16.1, B16.3, B16.4, B16.5,
				B16.9, B16.11, and B16.25.
(3) ASTM
				A 53, A 105, A 106, A 135, A 182, A 216, A 234, A 312, A 395, A 795, and SI
				10.
(4) AWS D10.9.
(5) API 650.
(6) IEEE 45.
(7) IMO Safety of life at Sea SOLAS
				Regulations II-2/4.3 and 4.3.5.
(8)
				UL 162.
(9) Notes: (2) and (3) in
				Table 5.2.5.2.2.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-4 - NFPA 12; standard on carbon dioxide extinguishing systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 4.
(a) Standard
				on Carbon Dioxide Extinguishing Systems, NFPA 12, 2005 Edition, published by
				National Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy,
				Massachusetts 02269-9101 is adopted by reference except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 12 are not adopted, are not enforceable, and are
				for information purposes only:
(1) ASME B
				31.1.
(2) ANSI/IEEE C 2.
(3) MNBV/ANSI Z535.
(4) API/ASME, Code for Unfired Pressure
				Vessels for Petroleum Liquids and Gases.
(5) ASTM A 53.
(6) ASTM A 106.
(7) ASTM A 120.
(8) ASTM A 182.
(9) CGA G6.2.
(10) CSA C22.1.
(11) Title 46, Code of Federal Regulations,
				Part 58.20.
(12) Title 46, Code of
				Federal Regulations, Part 72.
(13)
				Title 49, Code of Federal Regulations, Parts 171-190 (DOT).
(14) Bureau of Mines Bulletins 503 and 627
				(DOT).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-6 - NFPA 13R; Standard for the installation of sprinkler systems in residential occupancies up to and including four stories in height

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 10-19-7; IC 22-11-8; IC 22-12; IC
				  22-13; IC 22-14; IC 22-15; IC 25-4; IC 25-31; IC 36-7
Sec. 6.
(a) That
				certain standard, being titled NFPA 13R, Standard for the Installation of
				Sprinkler Systems in Residential Occupancies up to and Including Four Stories
				in Height, 2010 edition, published by the National Fire Protection Association
				(NFPA), 1 Batterymarch Park, Quincy, Massachusetts 02169-7471, be and the same
				is hereby adopted by reference as if fully set out in this section except as
				revised hereafter. This rule is available for review and reference at the:
Legal and Code Services Section
Indiana Department of Homeland Security
Indiana Government Center South
302 West Washington Street, Room W246
Indianapolis, Indiana 46204
(b) Amend Section 1.2 as follows:
(1) Delete the text of Section 1.2.1 and
				insert to read as follows: The purpose of this standard shall be to provide a
				sprinkler system that aids in the detection and control of residential
				fires.
(2) Delete the text of
				Section 1.2.2 and insert to read as follows: A sprinkler system designed and
				installed in accordance with this standard shall be expected to prevent
				flashover (total involvement) in the room of fire origin, where
				sprinklered.
(3) Amend Section
				1.2.3 by deleting "trained" and inserting "qualified".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-8 - NFPA 15; standard for water spray fixed systems for fire protection

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 8.
(a) That
				certain document, being titled NFPA 15-Standard for Water Spray Fixed Systems
				for Fire Protection, 2001 Edition, published by the National Fire Protection
				Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts 02269-9101, be
				and the same is hereby adopted by reference, as if fully set out in this
				section except as revised hereafter.
(b) The following documents referenced in
				NFPA 15 are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 16.
(2) NFPA 18.
(3) NFPA 22.
(4) NFPA 24.
(5) NFPA 214.
(6) ANSI/ASME B1.20.1.
(7) ANSI B16.1.
(8) ANSI B16.3.
(9) ANSI B16.4.
(10) ANSI B16.5.
(11) ANSI B16.9.
(12) ANSI B16.11.
(13) ANSI B16.18.
(14) ANSI B16.22.
(15) ANSI B16.25.
(16) ANSI B36.10M.
(17) ANSI B36.19M.
(18) ANSI C2.
(19) ASTM A 53.
(20) ASTM A 135.
(21) ASTM A 182.
(22) ASTM A 234.
(23) ASTM A 312.
(24) ASTM A 536.
(25) ASTM A 795.
(26) ASTM B 75.
(27) ASTM B 88.
(28) ASTM B 251.
(29) ASTM D 2996.
(30) ASTM E 380.
(31) ASTM F 1173.
(32) AWS A5.8.
(33) AWS B2.1.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-9 - NFPA 17; standard for dry chemical extinguishing systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 9.
(a) Standard
				for Dry Chemical Extinguishing Systems, NFPA 17, 2002, published by National
				Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts
				02269-9101 is adopted by reference except as revised hereafter.
(b) The following documents referenced in
				NFPA 17 are not adopted, are not enforceable, and are for information purposes
				only:
(1) ASTM A 53.
(2) ANSI C-2.
(3) ANSI/ASME B31.1.
(4) UL 300.
(5) UL 1254
(6) Title 29, Code of Federal
				Regulations.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-10 - NFPA 17A; standard for wet chemical extinguishing systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 10.
(a)
				Standard for Wet Chemical Extinguishing Systems, NFPA 17A, 2002 Edition,
				published by National Fire Protection Association (NFPA), 1 Batterymarch Park,
				Quincy, Massachusetts 02269-9101 is adopted by reference except as revised
				hereafter.
(b) The document, UL
				300, referenced in NFPA 17A is not adopted, is not enforceable, and is for
				information purposes only:
(c) The
				following documents have been adopted and are enforceable:
(1) NFPA 70 as adopted in 675 IAC
				17.
(2) NFPA 72 as adopted in
				section 28 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-12 - NFPA 25; standard for the inspection, testing, and maintenance of water-based fire protection systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 25-4; IC 25-31; IC 36-7
Sec. 12.
(a) That
				certain document, being titled NFPA 25-Standard for the Inspection, Testing,
				and Maintenance of Water-Based Fire Protection Systems, 2011 Edition, published
				by the National Fire Protection Association (NFPA), 1 Batterymarch Park,
				Quincy, Massachusetts 02169-7471, be and the same is hereby adopted by
				reference, as if fully set out in this section except as revised
				hereafter.
(b) This rule is
				available for review and reference at:
Legal and Code Services Section
Indiana Department of Homeland Security
Indiana Government Center South
302 West Washington Street, Room W246
Indianapolis, Indiana 46204
(c) Delete Section 1.1.1 without
				substitution.
(d) Amend Section
				1.1.3 to delete "generally accepted practices" and insert "the applicable rules
				of the commission".
(e) Delete
				Section 1.2.2 without substitution.
(f) Delete the title and text of Section 1.3
				and
[sic]
and insert: Alternative materials, methods, and
				design. See
				675 IAC
				12-6-11, alternative materials, methods, and
				design.
(g) Amend Section 2.2 as
				follows:
(1) In the reference to NFPA 11,
				delete "2010 edition" and insert "as adopted at
				675
				IAC 28-1-3 ".
(2) In the reference to NFPA 13, delete "2010
				edition" and insert "as adopted at
				675
				IAC 13-1-8 ".
(3) In the reference to NFPA 14, delete "2010
				edition" and insert "as adopted at
				675 IAC 13-1-9
				".
(4) In the reference to NFPA 15,
				delete "2007 edition" and insert "as adopted at
				675
				IAC 28-1-8 ".
(5) In the reference to NFPA 20, delete "2010
				edition" and insert "as adopted at
				675
				IAC 13-1-10 ".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-13 - NFPA 33; standard for spray application using flammable and combustible materials

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 13.
(a) That
				certain document, being titled NFPA 33-Standard for Spray Application Using
				Flammable and Combustible Materials, 2003 Edition, published by the National
				Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts
				02269-9101, be and the same is hereby adopted by reference as if fully set out
				in this section, except as revised.
(b) The following documents referenced in
				NFPA 33 are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 16.
(2) NFPA 30.
(3) NFPA 69.
(4) NFPA 91.
(5) NFPA 101.
(6) NFPA 220.
(7) NFPA 432.
(8) NFPA 496.
(9) NFPA 701.
(10) UL 340.
(11) UL 900.
(12) UL 2208.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-14 - NFPA 34; dipping and coating processes using flammable or combustible liquids (Repealed)

Current through July 10, 2024
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-15 - NFPA 37; standard for the installation and use of stationary combustion engines and gas turbines

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 15.
(a) That
				certain standard, being titled NFPA 37, Standard for the Installation and Use
				of Stationary Combustion Engines and Gas Turbines, 2002 Edition, published by
				National Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy,
				Massachusetts 02269-9101, be and the same is hereby adopted by reference as if
				fully set out in this section except as revised hereafter.
(b) The following documents referenced in
				NFPA 37, are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 11A.
(2) NFPA 12A.
(3) NFPA 30.
(4) NFPA 54.
(5) NFPA 211.
(6) NFPA 750.
(7) API 620.
(8) API 650.
(9) ANSI/ASME B31.3.
(10) MSS SP-69.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-16 - NFPA 50; standard for bulk oxygen systems at consumer sites

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 16.
(a) That
				certain standard, being titled NFPA 50, Standard for Bulk Oxygen Systems at
				Consumer Sites, 2001 Edition, published by the National Fire Protection
				Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts 02269-9101, be
				and the same is hereby adopted by reference, as if fully set out in this
				section except as revised hereafter.
(b) The following documents referenced in
				NFPA 50 are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 99.
(2) NFPA 220.
(3) ANSI/ASME B31.3.
(4) CGA S-1.3.
(5) ASTM E 136.
(6) Title 49, Code of Federal
				Regulations.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-17 - NFPA 50B; standard for liquefied hydrogen systems at consumer sites

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 17.
(a) That
				certain document, being titled NFPA 50B, Standard for Liquefied Hydrogen
				Systems at Consumer Sites, 1999 Edition, published by the National Fire
				Protection Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts
				02269-9101, be and same is hereby adopted by reference, as if fully set out in
				this section except as revised hereafter.
(b) The following documents referenced in
				NFPA 50B are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 220.
(2) NFPA 496.
(3) ASME B31.3.
(4) CGA S-1.1.
(5) CGA S-1.2.
(6) CGA S-1.3.
(7) ASTM E136-96a.
(8) Title 49, Code of Federal
				Regulations.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-18 - NFPA 51; standard for the design and installation of oxygen-fuel gas system for welding, cutting, and allied processes

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 18.
(a) That
				certain document, being titled as NFPA 51, Standard for the Design and
				Installation of Oxygen-Fuel Gas System for Welding, Cutting and Allied
				Processes, 2002 Edition, published by the National Fire Protection Association,
				1 Batterymarch Park, Quincy, Massachusetts 02269-9101, be and the same is
				hereby adopted by reference, as if fully set out in this section, except as
				revised hereafter.
(b) The
				following documents referenced in NFPA 51 are not adopted, are not enforceable,
				and are for information purposes only:
(1)
				NFPA 54.
(2) NFPA 101.
(3) NFPA 255.
(4) NFPA 259.
(5) ANSI B31.3.
(6) ANSI Z49.1.
(7) ASTM B 88.
(8) ASTM E 136.
(9) ANSI/CGA C4.
(10) ANSI/CGA V1.
(11) CGA G1.6.
(12) CGA E-1.
(13) CGA E-3.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-20 - NFPA 51B; standard for fire prevention during welding, cutting and other hot work (Repealed)

Current through July 10, 2024
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-21 - NFPA 52; compressed natural gas (CNG) vehicular fuel systems code

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 21.
(a) That
				certain document, being titled NFPA 52-Compressed Natural Gas (CNG) Vehicular
				Fuel Systems Code, 2002 Edition, published by the National Fire Protection
				Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts 02269-9101, be
				and the same is hereby adopted by reference, as if fully set out in this
				section except as revised hereafter.
(b) The following documents referenced in
				NFPA 52 are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 30.
(2) NFPA 30A.
(3) NFPA 54.
(4) NFPA 101.
(5) NFPA 259.
(6) NFPA 302.
(7) NFPA 303.
(8) NFPA 496.
(9) ANSI SI 10.
(10) ANSI Z 87.1.
(11) ANSI Z 89.1.
(12) API RP 2003.
(13) ANSI/ASME B31.3.
(14) ASTM A 47.
(15) ASTM A 395.
(16) ASTM A 536.
(17) ASTM E 136.
(18) CGA S-1.1.
(19) CSA B 51.
(20) ANSI/IAS NGV1.
(21) ANSI/IAS NGV2.
(22) IAS US 5-96.
(23) SAE J 1616.
(24) Title 49, Code of Federal
				Regulations.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-23 - NFPA 59; utility lp-gas plant code

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 23.
(a) That
				certain document, being titled NFPA 59-Utility LP-Gas Plant Code, 2004 Edition,
				published by the National Fire Protection Association (NFPA), 1 Batterymarch
				Park, Quincy, Massachusetts 02269-9109, be and the same is hereby adopted by
				reference, as if fully set out in this section except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 59 are not adopted, are not enforceable, and are
				for information purposes only:
(1) NFPA
				11A.
(2) NFPA 12A.
(3) NFPA 16.
(4) NFPA 22.
(5) NFPA 24.
(6) NFPA 30.
(7) NFPA 54.
(8) NFPA 101.
(9) NFPA 290.
(10) NFPA 780.
(11) NFPA 1961.
(12) NFPA 1962.
(13) NFPA 1963.
(14) NFPA 1971.
(15) NFPA 1981.
(16) API 607-1998.
(17) API 620-2001.
(18) ASCE 7.
(19) ASME B31.3.
(20) ASTM A47.
(21) ASTM A395.
(22) ASTM A536.
(23) UL 132.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-24 - NFPA 59A; standard for the production, storage, and handling of liquefied natural gas (LNG)

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 24.
(a) That
				certain document, being titled NFPA 59A-Standard for the Production, Storage
				and Handling of Liquefied Natural Gas (LNG), 2001 Edition, published by the
				National Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy,
				Massachusetts 02269-9101, be and same is hereby adopted by reference, as if
				fully set out in this section, except as revised hereafter.
(b) The following documents referenced in
				NFPA 59A are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 11A.
(2) NFPA 12A.
(3) NFPA 16.
(4) NFPA 22.
(5) NFPA 24.
(6) NFPA 30.
(7) NFPA 54.
(8) NFPA 101.
(9) NFPA 255.
(10) NFPA 600.
(11) NFPA 701.
(12) NFPA 1221.
(13) NFPA 1901.
(14) ACI 301.
(15) ACI 304.6R.
(16) ACI 311.4R.
(17) ACI 318.
(18) ACI 318R.
(19) ACI 344R-W.
(20) ACI 372R.
(21) ACI 373R.
(22) ACI 506.2.
(23) API 6D.
(24) API 620.
(25) API 2510.
(26) ASCE 7.
(27) ASME B31.3.
(28) ASME B31.5.
(29) ASME B31.8.
(30) ASTM A366.
(31) ASTM A416.
(32) ASTM A421.
(33) ASTM A615.
(34) ASTM A722.
(35) ASTM A821.
(36) ASTM A966.
(37) ASTM C33.
(38) ASTM E380.
(39) CGA 341.
(40) CGA S-1.3.
(41) CSA B51.
(42) CAN 4-S102.
(43) CAN 3-A23.3.
(44) CAN 3-A23.4.
(45) CAN A23.1.
(46) CSA G279.
(47) CSA C22.1.
(48) CSA G30.3.
(49) CSA G30.5.
(50) CSA G30.18.
(51) NEHRP Recommended Provisions for Seismic
				Regulation for New Buildings and Other Structures-1997.
(52) GRI Report 96/0396.5.
(53) GRI Report 0176.
(54) GRI Report 0242.
(55) Uniform Building Code 1994.
(56) NACE RP 0169.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-28 - NFPA 72; national fire alarm and signaling code

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-11-8; IC 22-12; IC 22-13; IC
				  22-14; IC 22-15; IC 36-7
Sec. 28.
(a) That
				certain standard, being titled NFPA 72, National Fire Alarm and Signaling Code,
				2010 edition, published by the National Fire Protection Association (NFPA), 1
				Batterymarch Park, Quincy, Massachusetts 02269-9101, be and the same is hereby
				adopted by reference as if fully set out in this section except as revised
				hereafter.
(b) This rule is
				available for review and reference at the:
Legal and Code Services Section
Indiana Department of Homeland Security
Indiana Government Center South
302 West Washington Street, Room W246
Indianapolis, Indiana 46204
(c) Delete Section 1.4 in its entirety
				without substitution.
(d) Amend
				Section 1.5 by deleting the text and substituting "See
				675 IAC
				12-6-11.".
(e) Delete Section 1.7 in its entirety
				without substitution.
(f) Amend
				Section 2.2 as follows:
(1) In the reference
				to NFPA 10, delete "2010 edition" and insert "as adopted at
				675 IAC
				28-1-2 ".
(2) In the reference to NFPA 11, delete "2010
				edition" and insert "as adopted at
				675
				IAC 28-1-3 ".
(3) In the reference to NFPA 13, delete "2010
				edition" and insert "as adopted at
				675 IAC 13-1-5
				".
(4) In the reference to NFPA 25,
				delete "2008 edition" and insert "as adopted at
				675
				IAC 28-1-12 ".
(5) In the reference to NFPA 70, delete "2008
				edition" and insert "as adopted at 675 IAC 17-1-8 ".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-30 - NFPA 82; standard on incinerators, waste and linen handling systems and equipment

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 30.
(a) That
				certain document, being titled NFPA 82-Standard on Incinerators, Waste and
				Linen Handling Systems and Equipment, 2004 Edition, published by National Fire
				Protection Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts
				02269-9101 be and the same is adopted by reference, as if fully set out in this
				section except as revised hereafter.
(b) The following documents referenced in
				NFPA 82 are not adopted, are not enforceable, and are for information purposes
				only:
(1) NFPA 31.
(2) NFPA 54.
(3) NFPA 90A.
(4) NFPA 211.
(5) NFPA 259.
(6) NFPA 5000.
(7) ASTM C 27.
(8) ASTM C 199.
(9) ASHRAE handbook HVAC Systems and
				Equipment, 2000.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-31 - NFPA 86; standard for ovens and furnaces

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 31.
(a) That
				certain standard, being titled as NFPA 86, Standard for Ovens and Furnaces,
				2003 Edition, published by the National Fire Protection Association (NFPA), 1
				Batterymarch Park, Quincy, Massachusetts 02269-9101, be and the same is hereby
				adopted by reference, as if fully set out in this section except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 86 are not adopted, are not enforceable, and are
				for information purposes only:
(1) NFPA
				30.
(2) NFPA 31.
(3) NFPA 50A.
(4) NFPA 54.
(5) NFPA 79.
(6) NFPA 91.
(7) NFPA 750.
(8) ANSI Z50.1.
(9) ASME B31.1.
(10) ASME B31.3.
(11) ASTM D396.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-34 - NFPA 385; standard for tank vehicles for flammable and combustible liquids

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 34.
(a) That
				certain document, being titled NFPA 385-Standard for Tank Vehicles for
				Flammable and Combustible Liquids, 2000 Edition, published by the National Fire
				Protection Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts
				02269-9101, be and the same is hereby adopted by reference except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 385 are not adopted, are not enforceable, and are
				for information purposes only:
(1) NFPA
				30.
(2) ANSI Z 535.1.
(3) ASTM B 209.
(4) ASTM D 5.
(5) ASTM D 323.
(6) Title 49, Code of Federal
				Regulations.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-36 - NFPA 407; standard for aircraft fuel servicing

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 36.
(a) That
				certain standard, being titled as NFPA 407, 2001 Edition, Standard for Aircraft
				Fuel Servicing, published by the National Fire Protection Association (NFPA), 1
				Batterymarch Park, Quincy, Massachusetts 02269-9101, be and the same is hereby
				adopted by reference, as if fully set out in this section except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 407 are not adopted, are not enforceable, and are
				for information purposes only:
(1) NFPA
				30.
(2) NFPA 410.
(3) NFPA 415.
(4) NFPA 418.
(5) ANSI B 31.3.
(6) API Bulletin 1529.
(7) ASTM D 380.
(8) AWS A 5.10.
(9) UL 913.
(10) Title 49, Code of Federal
				Regulations.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-38 - NFPA 704; standard system for the identification of the fire hazards of materials for emergency response

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 38.
(a) That
				certain standard, being titled as NFPA 704, Standard System for the
				Identification of the Fire Hazards of Materials for Emergency Response, 2001
				Edition, published by the National Fire Protection Association, 1 Batterymarch
				Park, Quincy, Massachusetts 02269-9101, be and the same is hereby adopted by
				reference, as if fully set out in this section except as revised
				herein.
(b) The following documents
				referenced in NFPA 704 are not adopted, are not enforceable, and are for
				information purposes only:
(1) NFPA
				495.
(2) ASTM D 86.
(3) ASTM D 92.
(4) Process Safety Progress, Vol. 18, No. 4,
				1999.
(5) UN Manual of Tests
				Criteria.
(6) UN Recommendations on
				the Transport of Dangerous Goods, Model Regulations.
(7) Title 49.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-39 - NFPA 1123; code for fireworks display

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-11-14-2; IC 22-12; IC 22-13; IC
				  22-14; IC 22-15; IC 36-7
Sec. 39.
(a) That
				certain standard, being titled as NFPA 1123, Code for Fireworks Display, 2006
				Edition, published by the National Fire Protection Association, 1 Batterymarch
				Park, Quincy, Massachusetts 02269, be and the same is hereby adopted by
				reference, as if fully set out in this section except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 1123 are not adopted, are not enforceable, and are
				for information purposes only:
(1) NFPA
				160.
(2) NFPA 306.
(3) NFPA 1122.
(4) NFPA 1124.
(5) NFPA 1127.
(6) Title 16, Code of Federal
				Regulations.
(7) Title 27, Code of
				Federal Regulations.
(8) Title 49,
				Code of Federal Regulations.
(9)
				API Standard 87-1.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 28 - NATIONAL FIRE PROTECTION ASSOCIATION (NFPA) STANDARDS › Rule 1 - National Fire Protection Association (NFPA) Standards › Section 1-40 - NFPA 2001; standard on clean agent fire extinguishing systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 36-7
Sec. 40.
(a)
				Standard on Clean Agent Fire Extinguishing Systems, NFPA 2001, 2004 Edition,
				published by National Fire Protection Association (NFPA), 1 Batterymarch Park,
				Quincy, Massachusetts 02269-9101 is adopted by reference except as revised
				hereafter.
(b) The following
				documents referenced in NFPA 2001 are not adopted, are not enforceable, and are
				for information purposes only:
(1) ANSI
				B1.20.1.
(2) ANSI C2.
(3) ASME B31.1.
(4) ASTM A 120.
(5) ASTM SI 10.
(6) CGA C-6.
(7) CAN/CSA-Z234.1.
(8) IMO MSC/Circular 848.
(9) ISO/IEC Guide 7.
(10) UL 2127.
(11) UL 2166.
(12) ULC S524-M91.
(13) ULC S529-M87.
(14) OSHA, Title 29 CFR.
(15) Title 46 CFR, Part 72.
(16) Title 46 CFR, Subchapter J.
(17) Title 49 CFR, Parts 170-190.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 1 - General Provisions › Section 1-1 - Scope

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC
				  22-12-1-4; IC
				  22-12-1-17.7; IC 22-13; IC 22-14;
				  IC 22-15; IC 36-7
Sec. 1.
(a) This
				article contains building and fire safety rules applicable to outdoor event
				equipment, as defined in IC
				22-12-1-17.7.
(b) For purposes of the definition of
				"outdoor event equipment", as defined in IC
				22-12-1-17.7, the phrase "not
				otherwise attached or anchored to, or otherwise a part of, another Class 1
				structure" means that the outdoor event equipment is designed, constructed, and
				installed separately from any other Class 1 structure, such as a stage or
				platform, and is, or is intended to be, an independent, standalone Class 1
				structure.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 1 - General Provisions › Section 1-2 - Applicability

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-8.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 2.
(a)
				Notwithstanding
				675 IAC
				12-6-2(f), for purposes of this
				article, "temporary outdoor event equipment" means outdoor event equipment that
				is installed at any single location in Indiana for not more than forty-five
				(45) calendar days in any one (1) calendar year.
(b) A construction design release, as
				described in
				675 IAC 12-6, is not required for
				temporary outdoor event equipment.
(c) Notwithstanding
				675 IAC
				12-6-2(f), for purposes of this
				article, "permanent outdoor event equipment" means outdoor event equipment that
				is installed at any single location in Indiana for more than forty-five (45)
				calendar days in any calendar year.
(d) A construction design release, as
				described in
				675 IAC 12-6, is required for
				permanent outdoor event equipment.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 1 - General Provisions › Section 1-3 - Definitions

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-8.5; IC 22-13-2-13
Affected: IC 10-19-2; IC 22-12-2; IC 22-13; IC 22-14; IC
				  22-15; IC 36-7-2-9; IC 36-8-17-8
Sec. 3.
The following definitions apply throughout this
				  article:
(1) "Building code" means the
				Indiana Building Code (675 IAC 13) in effect on the date that the outdoor event
				equipment is first installed at any location in Indiana.
(2) "Chapters 26, 29, 30, and 31 and Section
				1.2.1 of ASCE 7" means the documents incorporated by reference in
				675 IAC 29-2-2.
(3) "Commission" means the fire prevention
				and building safety commission created pursuant to IC 22-12-2.
(4) "Competent person" means an individual
				who, through education, training, and experience, is capable of performing the
				periodic inspections of outdoor event equipment required under this
				article.
(5) "Division" means the
				division of fire and building safety of the Indiana department of homeland
				security created pursuant to IC
				10-19-2.
(6) "Inspection authority" means the
				division, the local building official authorized under IC
				36-7-2-9 and local ordinance, and
				the local fire department authorized under IC
				36-8-17-8.
(7) "Owner" means the person that holds title
				to the real estate on which the outdoor event equipment is located.
(8) "Scenic components" means decorative
				components of outdoor event equipment that are not directly connected to the
				audio, lighting, or video systems in the outdoor event equipment.
(9) "Severe weather" means thunderstorms,
				tornadoes, flooding, high winds, hailstorms, or other similar, natural weather
				events.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 1 - General Provisions › Section 1-4 - Exemptions

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 4.
(a) Temporary
				outdoor event equipment that does not exceed twenty (20) feet above the surface
				of the stage or platform and that meets both of the following conditions is not
				subject to regulation under this article:
(1)
				For each foot of height from the ground to the highest point of the outdoor
				event equipment, all members of the public shall be placed an equal distance
				from the outdoor event equipment, plus an additional eight (8) feet.
(2) Except for installation and dismantling
				of the outdoor event equipment, no person is located within any portion or part
				of the outdoor event equipment.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-1 - Plans and specifications for outdoor event equipment

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC 25-4; IC
				  25-31; IC 36-7
Sec. 1.
(a) The owner
				shall have plans and specifications for each configuration of outdoor event
				equipment, including, without limitation, each configuration of structural
				design, and audio, lighting, video, and scenic components, prepared by an
				individual who is:
(1) competent to design
				the outdoor event equipment; and
(2) registered as an architect under IC 25-4
				or as a professional engineer under IC 25-31.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-2 - ASCE/SEI 7-10; minimum design loads for buildings and other structures

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-8.5; IC 22-13-2-13
Affected: IC 22-12-1-17.7; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 2.
(a) Section
				1.2.1 of Chapter 1, as contained at pages 1-2; Chapter 26, as contained at
				pages 187-201; Chapter 29, as contained at pages 249-255; Chapter 30, as
				contained at pages 257-297; and Chapter 31, as contained at page 299 of that
				certain document being titled ASCE/SEI 7-10 Minimum Design Loads for Buildings
				and Other Structures, Third Printing Errata Incorporated Includes Supplement 1,
				as published by the American Society of Civil Engineers, 1801 Alexander Bell
				Dr., Reston, VA 20191, are hereby adopted by reference as if fully set out in
				this article save and except those revisions made in this section.
(b) Section 1.2.1 of Chapter 1 is hereby
				amended as follows:
(1) The definition of
				"Authority Having Jurisdiction" is amended to read as follows: "Authority
				Having Jurisdiction" means the inspection authority.
(2) The definition of "Other Structures" is
				amended to read as follows: "Other Structures" means outdoor event equipment as
				defined in IC 22-12-1-17.7.
(3) The
				definition of "Temporary Facilities" is amended to read as follows: "Temporary
				Facilities" means temporary outdoor event equipment, as defined in
				675 IAC
				29-1-2(a).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-3 - Submission of plans and specifications

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 3.
The owner shall submit the plans and specifications required
				  in section 1 of this rule, under an affidavit that such plans and
				  specifications comply with the requirements of this article, to the inspection
				  authority at each location in Indiana at which the outdoor event equipment is
				  used not less than fourteen (14) calendar days prior to the first use of the
				  outdoor event equipment at each such location in each calendar
				  year.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-4 - Maintenance of outdoor event equipment

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 4.
The owner shall maintain the outdoor event equipment at all
				  times in a condition at least as safe as it was when it was first constructed
				  and installed in accordance with this article.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-5 - Inspections of outdoor event equipment

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 5.
The owner shall have the outdoor event equipment inspected
				  by a competent person to determine continuing compliance with the requirements
				  of this article each time the outdoor event equipment is installed and each
				  time it is dismantled.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-6 - Responsibility of titleholder for outdoor equipment

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 6.
The person that holds title to the outdoor event equipment
				  shall ensure that the outdoor event equipment is manufactured and installed in
				  accordance with the requirements of this article.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-7 - Installation of outdoor event equipment

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 7.
The person that installs the outdoor event equipment shall
				  ensure that the installation complies with the requirements of section 1(c)(9)
				  of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 29 - OUTDOOR EVENT EQUIPMENT › Rule 2 - Installation and Use Requirements › Section 2-8 - Emergency response plan

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-8.5; IC
				  22-13-2-13
Affected: IC
				  10-19-3-7; IC 22-12; IC 22-13; IC
				  22-14; IC 22-15; IC 36-7
Sec. 8.
The owner shall create and implement an emergency response
				  plan to provide for the safe dismantling of the outdoor event equipment and
				  evacuation of all persons from the area in which the outdoor event equipment is
				  located in the event of severe weather or other natural disaster.