Missouri Code of State Regulations › Title 2 - DEPARTMENT OF AGRICULTURE › Division 90 - Weights, Measures and Consumer Protection › Chapter 10 - Liquefied Petroleum Gases › Section 2 CSR 90-10.013 - Installation Requirements

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This amendment updates the forms in sections
				  (1), (2), (3), (6), and (7).
PUBLISHER'S NOTE: The secretary of state has
				  determined that the publication of the entire text of the material which is
				  incorporated by reference as a portion of this rule would be unduly cumbersome
				  or expensive. This material as incorporated by reference in this rule shall be
				  maintained by the agency at its headquarters and shall be made available to the
				  public for inspection and copying at no more than the actual cost of
				  reproduction. This note applies only to the reference material. The entire text
				  of the rule is printed here.
(1) Prior to any installations at buildings
				of public assembly or use such as schools, churches, recreational halls,
				tourist courts, hotels, hospitals, sanitariums, convalescent homes, nursing
				homes, rest homes, four- (4-) unit apartments, and larger or similar types of
				public buildings having institutional occupancies, for new construction, major
				renovations, or additions to these installations and mobile home parks,
				shopping center areas, service stations, bulk plants, industrial plants, and
				other similar locations of public gathering, form MPSC-0910 must be completed
				and submitted to the inspection authority. Form MPSC-0910, January 1, 2016, is
				published by the Missouri Propane Safety Commission, 4110 Country Club Dr.,
				Ste. 200, Jefferson City, MO 65109-0302 and is incorporated by reference. This
				rule does not incorporate any subsequent amendments or additions to the
				referenced material.
(2) The owner
				of a retail cylinder exchange cabinet shall submit a completed form MPSC-0955
				to the commission within fifteen (15) days following the installation of a
				cylinder exchange cabinet.
(3) Form
				MPSC-0910 including detailed plans shall be furnished to the inspection
				authority for approval before installation of LP gas containers having a water
				capacity of over two thousand (2,000) gallons, or two (2) or more containers
				that are to be connected and have a combined capacity exceeding four thousand
				(4,000) gallons, or when LP gas in the liquid phase is to be withdrawn or of a
				container charging plant where portable containers are to be recharged and
				filled regardless of the capacity of the storage containers used as the supply
				for filling containers and cylinders. Form MPSC-0910, January 1, 2016, is
				published by the Missouri Propane Safety Commission, 4110 Country Club Dr.,
				Ste. 200, Jefferson City, MO 65109-0302 and incorporated by reference. This
				rule does not incorporate any subsequent amendments or additions to the
				referenced material. When approval is granted, one (1) copy of the plans will
				be returned to the party submitting the original proposal. Final inspection and
				approval is required before placing the installation into service. If
				installation of the proposed LP gas system has not begun within one hundred
				eighty (180) days from the date of approval by the state LP gas inspection
				authority, new plans shall be resubmitted prior to the time installation does
				begin.
(4) The following
				requirements shall be met on plans that shall be submitted to the inspection
				authority of Missouri for approval before starting construction:
(A) A complete copy of the plans shall be
				submitted to the inspection authority together with detailed
				specifications;
(B) Plans shall be
				on good quality paper, legible, and contain the information required by this
				section; and
(C) Plans and
				specifications are to be accompanied by a written application on a form
				prescribed by the inspection authority and shall include the following:
1. The address of the proposed location and
				the name and mailing address of the owner or builder;
2. An outline of the boundary lines of the
				property owned or leased;
3. A
				diagram showing adjoining property on all sides and the distance to all
				adjacent buildings and roadways;
4.
				A diagram showing the location and sizes of each container or containers on the
				plot of ground to be used;
5. A
				diagram pinpointing each location where liquid transfer will be made, such as
				loading, unloading, and bottling;
6. A general layout of piping, pipe supports,
				and pipe protection; the location, size, and type of each important piece of
				equipment, gate valve, excess flow valve, pressure relief valve, hose,
				regulator, and all other important parts of the system planned;
7. The location of each building or shed to
				be built on the property and each sewer or drain opening;
8. The location of electrical lines and poles
				and telephone poles if located twenty-five feet (25') or less from storage
				tanks or liquid transfer areas;
9.
				The location of the electrical service pole;
10. The location of fences;
11. The dimensions of tank foundations,
				footings, reinforcements, and tank clearance above ground level;
12. Storage container dimensions, whether new
				or used, and the name of the manufacturer; and
13. All used containers of two thousand
				(2,000) gallons water capacity or more to be reinstalled shall have all valves,
				including relief valves, removed and inspected.