reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 22 - FIRE PREVENTION CODES › Rule 2.5 - 2014 Indiana Fire Code › Section 2.5-47 - Chapter 67; water-reactive solids and liquids

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 47.
Chapter 67 is amended as follows: Delete Section 6701.2
				  without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 22 - FIRE PREVENTION CODES › Rule 2.5 - 2014 Indiana Fire Code › Section 2.5-48 - Appendix A; board of appeals

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 48.
Appendix A is amended as follows: Delete Appendix A Board of
				  Appeals in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 22 - FIRE PREVENTION CODES › Rule 2.5 - 2014 Indiana Fire Code › Section 2.5-49 - Appendix A-1 and A-2; emergency escape plan and emergency information

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 49.
Add Appendix A-1 and A-2 as follows:
(1) Appendix A-1 Emergency Escape Plan
				Sign.
(2) Appendix A-2 Emergency
				Information Sign.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 22 - FIRE PREVENTION CODES › Rule 2.5 - 2014 Indiana Fire Code › Section 2.5-50 - Appendices B through G

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 50.
The following appendices are not adopted and may be used for
				  information purposes only:
(1)
				Appendix B; Fire-flow Requirements for Buildings.
(2) Appendix C; Fire Hydrant Locations and
				Distribution.
(3) Appendix D; Fire
				Apparatus Access Roads.
(4)
				Appendix E; Hazard Categories.
(5)
				Appendix F; Hazard Ranking.
(6)
				Appendix G; Cryogenic Fluids-Weight and Volume Equivalents.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 23 - RECREATIONAL FACILITIES › Rule 1 - Amusement Device Code › Section 1-62 - Fee schedule, Part III; scope

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 62.
The provisions of Fee Schedule, Part III ( 675 IAC 23-1-62
				  through
				  675 IAC
				  23-1-64 ) of this code shall apply to the fees charged
				  for inspection of amusement devices.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 23 - RECREATIONAL FACILITIES › Rule 1 - Amusement Device Code › Section 1-63 - Annual inspection fees

Current through July 10, 2024
Authority: IC
				  22-12-6-6;
				  IC
				  22-13-2-9;
				  IC
				  22-15-2-6; IC
				  22-15-7
Affected: IC
				  22-13-2-3;
				  IC
				  22-15-2-7; IC
				  36-7-2-9
Sec. 63.
(a) The fee
				for an annual inspection of permanent and portable amusement devices except for
				those covered in subsection (b) shall be based on the size and complexity of
				the device as follows:
FEE
TYPE OF DEVICE
DESCRIPTION
$144
Kiddie
An amusement device designed for seventy-five pounds
							 (75#) or less per passenger unit intended for use by children age twelve (12)
							 and under.
$144
Major
An amusement device designed for seventy-five pounds
							 (75#) or more intended for use by children above age twelve (12) and not listed
							 as a spectacular amusement device.
$144
Spectacular
Includes the following list of amusement devices and
							 any similar amusement device:
Himalayas-Flying Bobs
Sky Wheels
Sky Divers
Falling Stars
High Rise, Roller Coaster
Enterprise
Log Flume
Hang 10
(b)
				The fee for an annual inspection of passenger tramways, aerial tramways and
				lifts, surface lifts and tows shall be based on mode of transportation of
				passengers uphill, on the surface or above the surface.
MODE OF TRANSPORTATION
FEE-PER DRIVING MECHANISM
On Surface
$144
Above Surface
$288
(c)
				Reinspection fees shall be one-half (½) of the annual inspection
				fee.
(d) Subsequent inspection fee
				shall be one hundred dollars ($100) per device.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-1 - Title, purpose, availability

Current through July 10, 2024
Authority: IC 12-17.2-2-9
Affected: IC 16-19-3-4; IC 22-13-2-2
Sec. 1.
(a) Title.
				This rule ( 675 IAC 24-1 ) shall be known as the Migrant Day Care Nursery Fire
				Safety Code, and shall be published by the fire and building services
				department for general use and distribution under that title. Whenever the term
				"this code" is used throughout this rule ( 675 IAC 24-1 ) it shall mean the
				Migrant Day Care Nursery Fire Safety Code.
(b) Purpose. The purpose of this code is to
				establish minimum fire safety requirements for migrant day care nurseries. This
				code, combined with the rules of the department of public welfare (470 IAC),
				and the rules of the state board of health (410 IAC) forms the complete package
				of regulations for migrant day care nurseries.
(c) Availability. This rule ( 675 IAC 24-1 )
				is available for purchase from the Fire and Building Services Department, 1099
				North Meridian Street, Suite 900, Indianapolis, Indiana 46204
[Current
				address is the Department of Fire and Building Services, Indiana Government
				Center-South, 302 West Washington Street, Indianapolis, Indiana
				46204.]
.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-2 - Scope, enforcement

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 2.
(a) Scope.
				This code applies to migrant day care nurseries and is adopted under IC
				12-3-2-3.5
[IC 12-3 was repealed by P.L. 2-1992, SECTION 897, effective
				February 14, 1992.]
, taking into consideration that exempted centers
				operate in donated space, provide care for less than one hundred twenty (120)
				days during the calendar year and provide care only to children from migrant
				families.
(b) Enforcement. This
				code shall be enforced by the state fire marshal through his deputies.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-3 - Definitions

Current through July 10, 2024
Authority: IC 12-17.2-2-9
Affected: IC 16-19-3-4; IC 22-13-2-2
Sec. 3.
For the purpose of this code ( 675 IAC 24-1 ), the following
				  terms shall have the meaning indicated.
"Building systems" means the group of interacting,
				  interrelated or interdependent elements forming the collective building.
"Commission" means the Indiana fire prevention and building
				  safety commission.
"Egress" means a way out or exit.
"Exempted center" means a day nursery that:
(1) is operated under the federally funded Head Start Program
				  (
				  42 U.S.C.
				  9831 et seq.) and the Texas Migrant
				  Council;
(2) provides services for children from migrant worker
				  families;
(3) is operated during a single period of less than one
				  hundred twenty (120) consecutive days during a calendar year.
"Exit" means a continuous and unobstructed means of egress to
				  a public way and shall incude intervening aisles, doors, doorways, corridors,
				  exterior exit balconies, ramps, stairways, smokeproof enclosures, horizontal
				  exits, exit passageways, exit courts and yards.
"Grade" (adjacent ground elevation) means the lowest point of
				  elevation of the finished surface of the ground, paving or sidewalk between the
				  building and a line five (5) feet from the building.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-4 - Inspections

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 4.
The state fire marshal shall cause exempted centers to be
				  inspected a minimum of once each year.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-5 - Additional regulations

Current through July 10, 2024
Authority: IC 12-17.2-2-9
Affected: IC 16-19-3-4; IC 22-13-2-2
Sec. 5.
All exempted centers shall comply with the requirements of
				  this code, as well as the Indiana fire prevention code ( 675 IAC 22-2 ), the
				  Indiana flammable and combustible liquids and gases code ( 675 IAC 22-1 ), the
				  Indiana building code ( 675 IAC 13-2
[ 675 IAC 13-2 was repealed filed
				  Feb 15, 1989, 5:00 p.m.: 12 IR 1552, eff Apr 3, 1989.]
), and any other
				  applicable rules of the commission.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-6 - Location of exempted center

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 6.
The exempted center shall be located, within the building, on
				  the floor or portion of the building closest to grade level.
EXCEPTIONS: The exempted center may be located one (1) floor
				  above or below the level closest to grade level:
(1) if the building is equipped throughout
				with an automatic fire suppression system; or
(2) if the building is equipped throughout
				with a smoke detection system located in the corridors and interconnected to a
				manual fire alarm system; or
(3) if
				the staff ratio (of staff members to children in particular age groups) is
				double the ratio required by the department of public welfare.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-7 - Egress requirements

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 7.
(a) A
				minimum of two (2) exits, other than elevators, are required when the number of
				occupants in any exempted center or portion thereof, used by children ages 0-2,
				is at least seven (7), and for children ages 3-6 is at least sixteen (16).
				Exits shall be located a distance apart, equal to but not less than one-half
				(1/2) of the length of the maximum overall diagonal dimension of the area to be
				served, measured in a straight line between exits. This distance may be
				decreased to one-third (1/3) if the building is equipped throughout with a
				supervised sprinkler system. See Table 8-A
[sic., Table
				7-A]
.
(b) Exit doors shall
				meet the following requirements:
(1) Exit
				doors shall swing in the direction of exit travel when serving an occupancy of
				fifty (50) or more.
(2) Exit doors
				shall be openable from the inside without the use of a key or any special
				knowledge or effort.
(3) There
				shall be a floor or landing on each side of the exit door of a sufficient width
				to allow uninterrupted egress.
(4)
				Exit doors shall be so marked that they are readily distinguishable from the
				adjacent construction.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-8 - Cooking equipment

Current through July 10, 2024
Authority: IC 12-17.2-2-9
Affected: IC 16-19-3-4; IC 22-13-2-2
Sec. 8.
All cooking equipment employing flammable liquids of an
				  appreciable depth (greater than one-fourth inch (1/4") (0.64 cm.)) shall be
				  protected with a hood and an automatic extinguishing system in accordance with
				  NFPA standard 96 as adopted by the commission (
				  675 IAC
				  13-1-17
[
				  675 IAC
				  13-1-17 was repealed filed Aug 26, 1992, 5:00 p.m.: 16
				  IR 62, eff Nov 1, 1992.]
). Portable fire extinguishers shall be
				  provided in accordance with NFPA standard 10 as adopted by the commission (
				  675 IAC
				  22-2-13
[
				  675 IAC
				  22-2-13 was repealed filed Nov 15, 1990, 2:00 p.m.: 14
				  IR 739.]
).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-9 - Flammable and combustible liquids

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 9.
(a) Storage
				and use of flammable or combustible liquids shall be limited to that required
				for maintenance and cooking.
(b)
				Not more than ten (10) gallons of flammable or Class II combustible liquids
				shall be stored in the exempted center unless in a secured, approved storage
				cabinet or inside a secured, approved storage area.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-10 - Fire extinguishers

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 10.
(a) The
				child caring area of the exempted center shall be protected with a minimum of
				two (2) 2-A rated portable fire extinguishers.
(b) The cooking area of the exempted center
				shall be protected with a minimum of one (1) 5-B:C rated portable fire
				extinguisher.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-11 - General fire safety

Current through July 10, 2024
Authority: IC 12-17.2-2-9
Affected: IC 16-19-3-4; IC 22-13-2-2
Sec. 11.
(a) The
				building, building systems and appliances used therein shall be maintained in a
				manner which does not constitute a distinct hazard to life or
				property.
(b) Combustible and
				flammable waste materials shall not be allowed to accumulate in or around the
				center.
(c) Storage, handling and
				disposal of combustible or flammable material shall be handled in accordance
				with the Indiana fire prevention code ( 675 IAC 22-2 ).
(d) Appliances which are designed to produce
				heat (stoves, furnaces, etc.) and their associated apparatus shall be subjected
				to regular cleaning and maintenance so as not to create a fire hazard.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-12 - Fire drills

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 12.
(a) Fire
				drills shall be held in the exempted center, at least once during each month of
				operation.
(b) The first fire drill
				shall be held within the first five (5) days of operation of the center and,
				when possible, in conjunction with the local fire chief.
(c) The evacuation shall be triggered by the
				sounding of a fire alarm or, when there is no fire alarm in the building, by
				another audible alarm (such as the ringing of a hand held bell).
(d) Fire drills shall include complete
				evacuation of all persons in the exempted center and the assembling of said
				persons at a designated area outside of the building.
(e) All staff members shall be familiar with
				the fire drill procedure and the method by which the fire department will be
				contacted in case of fire.
(f) A
				record of all fire drills shall be kept on the premises and the person in
				charge of the exempted center shall keep written reports containing the
				following information:
(1) Time of
				drill.
(2) Date of drill.
(3) Weather conditions when occupants are
				evacuated.
(4) Number of occupants
				evacuated.
(5) Total time for
				evacuation.
(6) Any other
				information relevant to the drill.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 24 - SUPPLEMENTARY FIRE SAFETY RULES › Rule 1 - Migrant Day Care Nursery Fire Safety Code › Section 1-13 - Notification of fire department

Current through July 10, 2024
Authority: IC
				  12-17.2-2-9
Affected: IC
				  16-19-3-4;
				  IC
				  22-13-2-2
Sec. 13.
Prior to the first day of operation, the person in charge of
				  the exempted center shall, in writing, notify the local fire chief of all the
				  following:
(1) Address of the exempted
				center.
(2) Area of building being
				used by the center.
(3) Dates of
				operation including days of week.
(4) Time of operation.
(5) Method by which the fire department will
				be contacted in case of fire.
(6)
				Number of children.
(7) Date and
				time of first fire drill.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 25 - FUEL GAS CODE › Rule 3 - 2014 Indiana Fuel Gas Code › Section 3-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 1.
(a) That
				certain document being titled the International Fuel Gas Code, 2012 Edition,
				second printing dated February 2012, as published by the International Code
				Council, Inc., 4051 West Flossmoor Road, Country Club Hills, Illinois
				60478-5795, is hereby adopted by reference as if fully set out in this rule
				save and except those revisions made in this rule.
(b) This rule is available for review and
				reference at the:
Legal and Code Service Section
Indiana Department of Homeland Security
Indiana Government Center South 302 West Washington Street,
				  Room W246
Indianapolis, Indiana 46204
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 25 - FUEL GAS CODE › Rule 3 - 2014 Indiana Fuel Gas Code › Section 3-3 - Chapter 2; definitions

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14-2-10; IC 22-15-2-7; IC
				  25-4; IC 25-31; IC 36-7-2-9; IC 36-8-17-9
Sec. 3.
Chapter 2 is amended as follows:
(a) Delete the title and the text of Section
				201.3 in its entirety and insert to read as follows: Section 201.3. Terms
				defined in other codes. Where terms are not defined in this code and are
				defined in the Indiana Building Code (675 IAC 13), Indiana Electrical Code (675
				IAC 17), Indiana Fire Code (675 IAC 22), Indiana Energy Conservation Code (675
				IAC 19), Indiana Mechanical Code (675 IAC 18) or Indiana Plumbing Code (675 IAC
				16), such terms shall have the meanings ascribed to them as in those
				codes.
(b) Amend Section 202,
				Definitions as follows:
(1) Amend the
				definition for APPROVED to read as follows: APPROVED means acceptance by the
				authority having jurisdiction by one (1) of the following methods:
(1) Investigation or tests conducted by
				recognized authorities; or
(2)
				Investigation or tests conducted by nationally recognized technical or
				scientific organizations; or
(3)
				Nationally accepted principles.
The investigation, tests, or principles shall establish that
				  the method, materials, equipment, design, or type of construction is safe for
				  its intended purpose.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 25 - FUEL GAS CODE › Rule 3 - 2014 Indiana Fuel Gas Code › Section 3-4 - Chapter 3; general regulations

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 4.
(a) Amend
				Section 301.3, Listed and labeled, to delete the text and insert to read as
				follows: Appliances regulated by this code shall be listed and labeled unless
				otherwise approved.
(b) Delete
				Section 301.4, in its entirety without substitution.
(c) Amend Section 305.1 by deleting, from the
				last line, "and the requirements determined by the code official" and inserting
				"or other approved methods".
(d)
				Amend Section 310.1.1 by adding an exception to read as follows: Exception:
				CSST with an arc-resistant jacket listed by an approved agency for installation
				without the direct bonding as, prescribed in this section shall be installed in
				accordance with its listing and the manufacturer's installation instructions.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 25 - FUEL GAS CODE › Rule 3 - 2014 Indiana Fuel Gas Code › Section 3-5 - Chapter 4; gas piping installations

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 5.
(a) Add an
				exception to Section 401.9, to read as follows: Exception: The manufacturer's
				identification for fittings and pipe nipples shall be on each piece or shall be
				printed on the fitting or nipple packaging or provided in
				documentation.
(b) Amend Section
				401.10, in the second sentence, to delete "an approved" in both places and
				insert "a".
(c) Amend Section
				406.7.1.3(3) by deleting "with a combustible gas indicator that complies with
				section 406.7.1.4".
(d) Amend
				Section 406.7.2.1(4) by deleting "with a listed combustible gas detector in
				accordance with Section 406.7.2.2".
(e) Amend Section 412, Liquefied petroleum
				gas motor vehicle fuel-dispensing station, to delete the text and insert to
				read as follows: See Indiana Fire Code.
(f) Amend Section 413, Compressed natural gas
				motor vehicle fuel-dispensing stations to delete the text and insert to read as
				follows: See Indiana Fire Code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 25 - FUEL GAS CODE › Rule 3 - 2014 Indiana Fuel Gas Code › Section 3-6 - Chapter 8; referenced standards

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 6.
Amend the last sentence of the first paragraph to read as
				  follows: The application of the referenced standards shall be as specified in
				  Section 101.3.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 1 - Definitions › Section 1-1 - Definitions

Current through July 10, 2024
Authority: IC 22-11-14.5-3; IC 22-13; IC 35-47.5-4-4.5
Affected: IC 35-47.5-2-13; IC 35-47.5-5-11
Sec. 1.
The following definitions apply throughout this
				  article:
(1) "Airblast" means the
				noise and concussion originating from a blast, usually produced by the
				detonation gases venting to the atmosphere.
(2) "Approved testing agency" means a person
				who administers the required examination for licensed regulated explosive
				use-blaster in accordance with
				675
				IAC 26-2-4.
(3) "Blast" means the controlled detonation
				of explosives or explosive materials to break or move, or both, rock or other
				materials.
(4) "Blast design" means
				the process of calculating blasthole diameter and layout, detonator timing,
				regulated explosives and blasting agent selection and consideration of geology
				and topography to create a blast, within accepted safety guidelines, that
				delivers the desired quantity and quality of broken material.
(5) "Blast initiation system" means the
				combination of detonators, detonation systems, and regulated explosives used to
				initiate a blast.
(6) "Boosting"
				means the use of a unit of explosives or blasting agent to perpetuate or
				intensify an explosive reaction.
(7) "Borehole" means a drilled hole, usually
				in rock, into which regulated explosives are loaded for blasting.
(8) "Flyrock" means dirt, mud, stone,
				fragmented rock, and other solid material propelled through the air from a
				blast.
(9) "Ground vibration" means
				a shaking of the ground in a specific wave form originating from a
				blast.
(10) "Licensed regulated
				explosive use-blaster" means an individual who:
(A) supervises or directs and performs the
				loading and firing of explosives materials;
(B) is an employee of a licensed regulated
				explosive use-operator; and
(C) is
				licensed by the office of the state fire marshal under this rule.
A licensed regulated explosive use-blaster may supervise or
				  direct and perform any type of blasting.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 2 - Licensure Requirements › Section 2-1 - Purpose

Current through July 10, 2024
Authority: IC
				  22-11-14.5-3; IC
				  22-13; IC
				  35-47.5-4-4.5
Affected: IC
				  35-47.5-5-11
Sec. 1.
This rule establishes the licensure requirements for the use
				  of regulated explosives as follows:
(1) Requirements for licensed regulated
				explosive use-blaster as provided in sections 2 through 4 of this
				rule.
(2) Requirements for licensed
				regulated explosive use-operator as provided in sections 7 through 9 of this
				rule.
(3) Procedures for the office
				of the state fire marshal to administer a program to issue licenses to
				individuals who comply with the requirements for licensed regulated explosive
				use-blaster and licensed use permits to persons who comply with the
				requirements for obtaining licensed use permits.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 2 - Licensure Requirements › Section 2-2 - Application for licensure as a licensed regulated explosive use-blaster

Current through July 10, 2024
Authority: IC
				  22-11-14.5-3; IC
				  22-13; IC
				  35-47.5-4-4.5
Affected: IC
				  35-47.5-5-11
Sec. 2.
An applicant for licensure as a licensed regulated explosive
				  use-blaster shall submit evidence to the office of the state fire marshal on a
				  form approved by the fire prevention and building safety commission and under
				  penalty of perjury that the individual:
(1) has successfully completed:
(A) the examination approved by the office of
				the state fire marshal and administered by an approved testing agency;
				and
(B) one (1) year of experience
				in the proper use of regulated explosives;
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 2 - Licensure Requirements › Section 2-3 - Licensure examination

Current through July 10, 2024
Authority: IC
				  22-11-14.5-3; IC
				  22-13; IC
				  35-47.5-4-4.5
Affected: IC
				  35-47.5-5-11
Sec. 3.
(a) The
				subjects for the licensed regulated explosive use-blaster examination are as
				follows:
(1) Explosives and related products,
				including the following:
(A) High
				explosives.
(B) Blasting
				agents.
(C) Chemical and physical
				properties of explosive products and appropriate product selection.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 2 - Licensure Requirements › Section 2-4 - Issuance of licensed regulated explosive use-blaster license; reciprocity; renewal of license; maintenance and sanctions

Current through July 10, 2024
Authority: IC 22-11-14.5-3; IC 22-13; IC 35-47.5-4-4.5
Affected: IC 22-12-7-7; IC 35-47.5-5-11
Sec. 4.
(a) The
				office of the state fire marshal shall issue a license to an individual who:
(1) complies with the requirements of section
				2 of this rule or is certified under 312 IAC 25-9; and
(2) pays the licensure fee of one hundred
				seventy-five dollars ($175), payable to the fire and building services
				fund.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 2 - Licensure Requirements › Section 2-5 - Application for licensure as a licensed regulated explosive use-operator

Current through July 10, 2024
Authority: IC
				  22-11-14.5-3; IC
				  22-13; IC
				  35-47.5-4-4.5
Affected: IC
				  35-47.5-5-11
Sec. 5.
A person who takes possession of a regulated explosive in the
				  state of Indiana for the purpose of detonation under the person's direction or
				  control shall submit an application to become a licensed regulated explosive
				  use-operator to the office of the state fire marshal on a form approved by the
				  fire prevention and building safety commission and under penalty of perjury.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 2 - Licensure Requirements › Section 2-6 - Issuance of licensed regulated explosive use-operator license; maintenance; renewal

Current through July 10, 2024
Authority: IC
				  22-11-14.5-3; IC
				  22-13; IC
				  35-47.5-4-4.5
Affected: IC
				  35-47.5-5-11
Sec. 6.
(a) The
				office of the state fire marshal shall issue a licensed regulated explosive
				use-operator license to a person who has:
(1)
				applied under section 5 of this rule; and
(2) paid a fee in the amount of three hundred
				fifty dollars ($350).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 26 - REGULATED EXPLOSIVES; USE AND LICENSURE › Rule 2 - Licensure Requirements › Section 2-7 - Orders, sanctions, and appeals

Current through July 10, 2024
Authority: IC
				  22-11-14.5-3; IC
				  22-13; IC
				  35-47.5-4-4.5
Affected: IC 4-21.5-3; IC
				  22-12-7-7;
				  IC
				  35-47-1-5; IC
				  35-47.5-2-13;
				  IC
				  35-47.5-5-11
Sec. 7.
(a) The
				office of the state fire marshal may enforce the provisions of this rule
				through the issuance of administrative orders under IC 22-12-7.
(b) Orders issued under subsection (a) may
				include corrective actions or sanctions in accordance with IC
				22-12-7-7.
(c) Any person aggrieved by an order issued
				by the office of the state fire marshal may petition for administrative review
				under IC 22-12-7 and IC 4-21.5-3.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-1 - Scope and enforcement

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 1.
This rule applies only to the design and construction of one
				  (1) or more visitability features in one (1) and two (2) family dwellings and
				  Class 1 townhouses. In accordance with IC
				  22-13-4-7(g), the
				  provisions of this rule are not mandatory unless a person contracts with a
				  designer or a builder for construction of a visitability feature adopted in
				  this rule in the new construction of a dwelling, in which case the designer and
				  builder shall comply with the standards adopted in this rule for the design and
				  construction of the visitability feature. The standards adopted under this
				  rule:
(1) shall be enforced by a
				political subdivision that enforces the commission's standards with respect to
				Class 2 structures; and
(2) may not
				be enforced by the department of fire and building services.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-2 - Definitions

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 2.
The following definitions apply throughout this rule:
(1) "Accessible" means that a dwelling or
				portion of a dwelling can be approached, entered, and used by persons with a
				disability.
(2) "Accessible route"
				means a continuous unobstructed path connecting accessible elements and spaces
				in a building or within a site that can be negotiated by a person with a
				disability using a wheelchair. Interior accessible routes may include
				corridors, floors, and ramps. Exterior accessible routes may include parking
				access aisles, curb ramps, walks, and ramps.
(3) "Adaptable dwelling units" means dwelling
				units that include one (1) or more of any features of adaptable design
				specified in section 3 of this rule.
(4) "Bathroom" means a bathroom, which
				includes a water closet (toilet), lavatory (sink), and bathtub or shower. The
				term does not include single-fixture facilities or those with only a water
				closet and lavatory. The term includes a compartmented bathroom, which is:
(A) one in which the fixtures are distributed
				among interconnected rooms;
(B)
				considered a single unit; and
(C)
				subject to the requirements for bathrooms.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-3 - Design and construction requirements

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 3.
When a person contracts with a designer or builder, or both,
				  for the construction of a dwelling with a visitability feature:
(1) the feature shall be designed and
				constructed in such a manner that complies with the standard put forth in the
				section of this rule for that feature; and
(2) the accessible route shall be designed
				and constructed in such a manner that:
(A) at
				least one (1) building entrance is on an accessible route;
(B) all doors on the accessible route shall
				be thirty-six (36) inches (ninety-one and forty-four hundredths (91.44)
				centimeters) in width; and
(C) all
				dwelling units shall contain the features of adaptable design, such as:
(i) an accessible route into and through the
				dwelling unit;
(ii) light switches,
				electrical receptacle outlets, thermostats, and other environmental controls in
				accessible locations;
(iii)
				reinforcements in bathroom walls to allow installation of grab bars around the
				toilet, tub, shower stall, and shower seat, where such facilities are
				provided;
(iv) kitchens and
				bathrooms such that an individual in a wheelchair can maneuver about the space;
				and
(v) all habitable rooms shall
				have a minimum size of seven (7) feet by ten (10)
				feet.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-4 - Entrances

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 4.
(a) Each
				building shall have at least one (1) building entrance on an exterior
				accessible route.
(b) Only one (1)
				entrance is required to be accessible to any one (1) ground floor of a
				building, except in cases where an individual dwelling unit has a separate
				exterior entrance. In every case, the accessible entrance shall be on an
				accessible route to the dwelling unit.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-5 - Usable doors

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 5.
(a) Within
				the dwelling unit, a door intended for user passage through the unit having a
				clear opening of at least thirty-four (34) inches (eighty-six and thirty-six
				hundredths (86.36) centimeters) nominal width when the door is open ninety (90)
				degrees (one and fifty-seven hundredths (1.57) radians), measured between the
				face of the door and the stop, shall conform to section 3(2)(A) of this rule
				(see Figure 1(a), 1(b), and 1(c)). Openings more than twenty-four (24) inches
				(sixty and ninety-six hundredths (60.96) centimeters) in depth are not
				considered doorways (see Figure 1(d)). Figure 1(a) through 1(d) is as follows:
Click here to view
				  Image
NOTE: A thirty-six (36) inch (ninety-one and forty-four
				  hundredths (91.44) centimeters) door hung in the standard manner shall provide
				  an acceptable, nominal thirty-four (34) inch (eighty-six and thirty-six
				  hundredths (86.36) centimeters) clear opening. This door may be adapted to
				  provide a wider opening by using offset hinges or by removing lower portions of
				  the door stop, or both. Pocket or sliding doors are acceptable doors in
				  dwelling units and have the added advantage of not impinging on clear floor
				  space in small rooms.
(b)
				Handles, pulls, latches, locks, and other operable parts on accessible doors
				shall have a shape that is easy to grasp with one (1) hand and does not require
				tight grasping, pinching, or twisting of the wrist to operate. Such hardware
				shall be thirty-four (34) inches (eighty-six and thirty-six hundredths (86.36)
				centimeters) minimum and forty-eight (48) inches (one hundred twenty-one and
				ninety-two hundredths (121.92) centimeters) maximum above the floor or ground.
				Where sliding doors are in the fully open position, operating hardware shall be
				exposed and usable from both sides. An exception is that locks used only for
				security purposes and not used for normal operation are permitted in any
				location.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-6 - Maneuvering clearances at doors

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 6.
(a) Swinging
				doors shall have maneuvering clearances complying with TABLE V6.1 as follows:
				TABLE V6.1 MANEUVERING CLEARANCES FOR MANUAL SWINGING DOORS
TYPE OF USE
MINIMUM CLEARANCES
APPROACH DIRECTION
DOOR SIDE
PERPENDICULAR TO DOOR1
BEYOND LATCH PARALLEL TO DOOR
From front
Pull
60 inches (1,524 mm)
18 inches (457 mm)
From front
Push
48 inches (1,219 mm)
0 inches (0 mm)2
From hinge
Pull
60 inches (1,524 mm) 54 inches (1,372
							 mm)5
36 inches (914 mm) 42 inches (1,067
							 mm)5
From hinge
Push
42 inches (1,067 mm)3
54 inches (1,372 mm)
From latch
Pull
48 inches (1,219 mm)4
24 inches (610 mm)
From latch
Push
42 inches (1,067 mm)4
24 inches (610 mm)
1Maneuvering space shall include
				  full width of doorway.
2Add 12 inches (305 mm) if closer and
				  latch provided.
3Add 6 inches (152 mm) if closer and
				  latch provided.
4 Add 6 inches (152 mm) if closer
				  provided.
5Alternative design.
(b) Sliding doors and folding doors shall
				have maneuvering clearances complying with Table V6.2 as follows: TABLE V6.2
				MANEUVERING CLEARANCES FOR SLIDING AND FOLDING DOORS
APPROACH DIRECTION
MINIMUM CLEARANCES
PERPENDICULAR TO DOOR1
PARALLEL TO DOOR
From front
48 inches (1,219 mm)
0 inches (0 mm)
From hinge side
42 inches (1,067 mm)
54 inches (1,372 mm)2
From latch side
42 inches (1,067 mm)
24 inches (610 mm)2
1Maneuvering space shall include
				  full width of doorway.
2From the latch side toward the
				  approach direction.
(c)
				Floor or ground surface within the maneuvering clearances shall have a slope
				not greater than 1:48 and shall comply with section 13 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-7 - Maneuvering clearances at doorways without doors

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 7.
(a) Doorways
				without doors that are less than thirty-six (36) inches (nine hundred fourteen
				(914) millimeters) wide shall have maneuvering clearances complying with TABLE
				V7.1 as follows:
TABLE V7.1 MANEUVERING CLEARANCES FOR DOORWAYS WITHOUT DOORS
APPROACH DIRECTION
MINIMUM CLEARANCES
PERPENDICULAR TO DOORWAY1
From front
48 inches (1,219 mm)
From side
42 inches (1,067 mm)
1Maneuvering space shall include
				  full width of doorway.
(b)
				Where the plane of the doorway is recessed more than eight (8) inches (twenty
				and three-tenths (20.3) centimeters) from the plane of the wall, clearances for
				front approach shall be provided.
(c) Floor or ground surface within the
				maneuvering clearances shall have a slope not greater than 1:48 and shall
				comply with section 13 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-8 - Accessible route into and through the dwelling unit

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 8.
(a) A minimum
				clear width of thirty-six (36) inches (ninety-one and forty-four hundredths
				(91.44) centimeters) shall be provided.
(b) In single-story dwelling units, changes
				in levels within the dwelling unit with heights greater than one-fourth
				(¼) inch through one-half (½) inch (greater than six and
				thirty-five hundredths (6.35) millimeters through twelve and seven-tenths
				(12.7) millimeters) shall be beveled with a slope no greater than 1:2. Except
				for design features, such as a loft or an area on a different level within a
				room, for example, a sunken living room, changes in levels greater than
				one-half (½) inch shall be ramped or have other means of access. Where a
				single-story dwelling unit has special design features, all portions of the
				single-story unit, except the loft or the sunken or raised area, shall be on an
				accessible route. Additional requirements are as follows:
(1) In single-story dwelling units with
				lofts, all spaces other than the loft shall be on an accessible
				route.
(2) Design features, such as
				sunken or raised functional areas, shall not interrupt the accessible route
				through the remainder of the dwelling unit.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-9 - Light switches, electrical receptacle outlets, thermostats, and other environmental controls in accessible locations

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 9.
Light switches, electrical receptacle outlets, thermostats,
				  and other environmental controls shall be located no higher than forty-eight
				  (48) inches (one hundred twenty-one and nine-tenths (121.9) centimeters) and no
				  lower than eighteen (18) inches (forty-five and seventy-two hundredths (45.72)
				  centimeters) above the floor. If the reach is over an obstruction, for example,
				  an overhanging shelf twenty-four (24) inches (sixty and ninety-six hundredths
				  (60.96) centimeters) in depth, the maximum height is reduced to forty-four (44)
				  inches (one hundred eleven and seventy-six hundredths (111.76) centimeters) for
				  forward approach, or forty-six (46) inches (one hundred sixteen and eighty-four
				  hundredths (116.84) centimeters) for side approach, provided the obstruction,
				  for example, a kitchen base cabinet, is no more than twenty-four (24) inches
				  (sixty and ninety-six hundredths (60.96) centimeters) in depth. The depth of
				  obstructions shall not exceed twenty-five (25) inches (sixty-three and
				  five-tenths (63.5) centimeters) from the wall beneath a control (see Figure 2).
				  Figure 2 is as follows:
Click here to view
				  Image
Click here to view
				  Image
Figure 2 Reach Ranges
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-10 - Reinforced walls for grab bars

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-13-4-7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 10.
(a)
				Reinforced bathroom walls to allow later installation of grab bars around the
				toilet, tub, shower stall, and shower seat, where such facilities are provided,
				shall conform to section 3(2)(C)(iii) of this rule (see Figures 3, 4, and 5).
				Where the toilet is not placed adjacent to a side wall, the bathroom shall
				comply if provision is made for installation of floor mounted foldaway or
				similar alternative grab bars. Where the powder room is the only toilet
				facility located on an accessible level of a multistory dwelling unit, it shall
				comply with this requirement for reinforced walls for grab bars. Figures 3, 4,
				and 5 are as follows:
Click here to view
				  Image
Click here to view
				  Image
Click here to view
				  Image
Figure 5 showers in Adaptable Bathrooms
NOTE: Installation of reinforcement for grab bars for
				  bathtubs or showers is not limited by the illustrative figures. Reinforced
				  areas for floor-mounted grab bars is
[sic, are]
acceptable.
(b)
				Reinforcement for grab bars may be provided in a variety of ways, for example,
				by plywood or wood blocking, so long as the necessary reinforcement is placed
				to permit later installation of grab bars in appropriate locations.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 27 - INDIANA VISITABILITY RULE FOR ONE AND TWO FAMILY DWELLINGS AND TOWNHOUSES › Rule 1 - Indiana Visitability Rule › Section 1-11 - Visitable kitchens

Current through July 10, 2024
Authority: IC
				  22-13-2-2; IC
				  22-13-2-13; IC
				  22-2-13-4 -7
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 11.
(a) A clear
				floor space at least thirty (30) inches by forty-eight (48) inches (seventy-six
				and two-tenths (76.2) centimeters by one hundred twenty-one and nine-tenths
				(121.9) centimeters) that allows a parallel approach by a person in a
				wheelchair shall be provided at the range or cooktop and sink, and either a
				parallel or forward approach shall be provided at the oven, dishwasher,
				refrigerator/freezer, or trash compactor (see Figure 6). Figure 6 is as
				follows:
Click here to view
				  Image
Figure 6 Minimum Clear Floor Space for
				  Wheelchairs
(b) Clearance
				between counters and all opposing base cabinets, countertops, appliances, or
				walls shall be at least forty (40) inches (one hundred one and six-tenths
				(101.6) centimeters).
(c) In
				U-shaped kitchens with a sink, range, or cooktop at the base of the "U", a
				sixty (60) inch (one hundred fifty-two and four-tenths (152.4) centimeters)
				diameter turning space shall be provided to allow parallel approach, or base
				cabinets shall be removable at that location to allow knee space for a forward
				approach.