reglab/statecodes huggingface dataset:
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 27 - RULES AND REGULATIONS GOVERNING THE TENTS AND EQUIPMENT OF CIRCUSES AND TRAVELING AMUSEMENT SHOWS (REPEALED) › Section 219-27-01 - Location

Current through 2024-29, July 17, 2024
A. No tent or tents shall be erected to cover
				more than seventy-five (75) per cent of the premises; nor shall any tent be
				erected closer than ten (10) feet to other structures except as hereinafter
				provided in paragraphs (B) and (C). Stake lines of adjacent tents shall be
				sufficiently distant from each other to provide an area to be used as a means
				of emergency egress.
B. Concession
				or other tents not occupied by the public need not be separated from each other
				and may be erected less than ten (10) feet from other structures only if the
				administrative official deems such closer spacing safe from hazard to the
				public.
C. Tents, each not
				exceeding 1,200 square feet in area, located on fair grounds or similar open
				spaces need not be separated ten (10) feet from each other, provided safety
				precautions meeting the approval of the administrative official are
				taken.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 27 - RULES AND REGULATIONS GOVERNING THE TENTS AND EQUIPMENT OF CIRCUSES AND TRAVELING AMUSEMENT SHOWS (REPEALED) › Section 219-27-03 - Flame Resistance

Current through 2024-29, July 17, 2024
A. All tents
				occupied for assembly, or in which animals are stabled, or those located within
				that portion of the premises used by the public; and all tents in places of
				outdoor assembly in or about which any devices using fuels are operated, and
				all tarpaulins and decorative materials in connection with any of these, shall
				meet the requirements for resistance to fire prescribed in the Federal
				Specification for Fire, Water and Weather Resistant Cotton Duck,
				CCC-D-746.
B. With the application
				for any circus, carnival or traveling amusement show license, the Commissioner
				of Public Safety shall require a affidavit attesting to the date the tent
				fabric was last treated with flame retardant solution and the date the wood was
				last surface treated or impregnated, the trade name and kind of chemical used
				in such treatments, the name of person or firm treating the test fabric and
				wood and the name and address of the owner of same. An additional copy of this
				affidavit shall be kept in the office of the circus, carnival, or traveling
				amusement show and shall be produced for inspection upon request of
				inspectional authorities.
C. Where
				tents are used as places of assembly with a capacity of two hundred (200) or
				more persons, the seats, chairs, jacks and other appurtenances of wood, must be
				suitably treated to reduce the fire hazard by a suitable application of a
				surface treatment or by impregnation.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 27 - RULES AND REGULATIONS GOVERNING THE TENTS AND EQUIPMENT OF CIRCUSES AND TRAVELING AMUSEMENT SHOWS (REPEALED) › Section 219-27-04 - Fire Hazards

Current through 2024-29, July 17, 2024
A. The ground
				enclosed by any tent used in connection with a place of outdoor assembly, and
				for a reasonable distance but not less than ten (10) feet outside of such
				structure or structures, shall be cleared of all flammable material or
				vegetation which will carry fire. This work shall be accomplished to the
				satisfaction of the administrative official prior to the erection of such
				structure or structures. The premises shall be kept free from such flammable
				materials during the period for which the premises are used by the
				public.
B. No hay, straw, shavings
				or similar combustible materials other than that necessary for the current
				feeding and care of animals shall be permitted within any tent used for public
				assembly.
C. No smoking, fireworks,
				or unapproved open flame of any kind shall be permitted in any tent while
				occupied by the public. "No smoking" signs shall be conspicuously posted in any
				tent open to the public.
D. Signs
				prohibiting smoking shall be prominently displayed at all entrances and at
				other locations within any tent used as a place of assembly, so that they may
				be clearly visible to all occupants. Frequent announcement regarding such
				prohibition shall be made, preferably over a public address system if
				available. Suitable noncombustible containers shall be provided at all
				entrances for the proper disposition of cigar or cigarette butts and pipe
				dottle and a uniformed attendant shall be stationed at such locations to advise
				patrons of the no smoking regulations.
E. Tents shall not be used for the display of
				motion pictures unless safety film is used, and then only if tent is licensed
				by the Commissioner of Public Safety for such projection.
F. No tier of seats shall rise to a height
				exceeding twelve (12) feet.
G. All
				lighting shall be by electricity, with lamps properly guarded to prevent
				ignition by radiation. In tents utilized by the public emergency lighting
				facilities must be provided.
1. All wiring
				must conform to the requirements of the National Electrical Code and conductors
				shall be trenched and covered.
2.
				Liquefied Petroleum gas shall not be utilized by any circus or carnival unless
				the storage containers, fittings, appliances and equipment are in accordance
				with rules and regulations governing transportation and storage of liquefied
				petroleum gas promulgated by the Commissioner of Public Safety.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-1

Current through 2024-29, July 17, 2024
This rule incorporates by reference the following American
				  Standard for Testing and Materials (ASTM) standards. All rights reserved by the
				  ASTM. Individual reprints (single or multiple) copies of these standards may be
				  obtained by contacting ASTM at 00 Barr Harbor Drive, PO Box C700, West
				  Conshohocken, PA 9428-2959 or by phone at (60) 832-9585 or service@astm.org
				  e-mail; or through the ASTM website,
www.astm.org
.
ASTM # F 698-94
,
Standard Specification
				  for Physical Information to be Provided for Amusement Rides and Devices,
2000 edition
ASTM # F 770-93
,
Standard Practice for
				  Operation Procedures for Amusement Rides and Devices,
2000
				  edition
ASTM # F 747-97
,
Standard Terminology
				  Relating to Amusement Rides and Devices,
1997
				  edition
ASTM # F 846-92,
Standard Guide for
				  Testing Performance of Amusement Rides and Devices,
2003
				  edition
ASTM # F 853-05
,
Standard Practice for
				  Maintenance Procedures for Amusement Rides and Devices,
2005
				  edition
ASTM # 1159-03a
,
Standard Practice for
				  Design and Manufacture of Patron Directed, Artificial Climbing Walls, Dry
				  Slide, Coin Operated and Purposeful Water Immersion Amusement Rides and Devices
				  and Air Supported Structures,
2003 edition
ASTM # 1193-04b
,
Standard Practice for
				  Amusement Ride and Device Manufacturer Quality Assurance Program and
				  Manufacturing Requirements,
2004 edition
ASTM # 1305-94
,
Standard Guide for
				  Classification of Amusement Ride and Device Related to Injuries and Illnesses,
2002 edition
ASTM # 1950-99
,
Standard Specification
				  for Physical Information to be Transferred With Used Amusement Rides and
				  Devices,
2002 edition
ASTM # 2007-00
,
Standard Practice for
				  the Classification, Design, Manufacture, and Operation of Concession Go-Karts
				  and Facilities,
2000 edition
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-2 - CERTIFICATE OF LIABILITY

Current through 2024-29, July 17, 2024
1. A person,
				persons, firm or corporation owning or controlling midways and amusement
				devices shall furnish a certificate of public liability insurance, in an amount
				of $1,000,000.00, as a minimum.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-3 - ELECTRICAL REQUIREMENTS

Current through 2024-29, July 17, 2024
1. All electrical
				equipment and installations shall comply with NFPA # 70 (National Electrical
				Code) as adopted by the Electricians Examining Board, Department of Business
				Regulation, State of Maine.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-4 - MEANS OF EGRESS AND ACCESS NOT PROVIDED BY THE MANUFACTURER

Current through 2024-29, July 17, 2024
1. Platforms required for use in loading and
				unloading passengers of amusement rides, when raised four (4) feet or more
				above the ground or floor shall be provided with standard guard rails on all
				open sides. The loading or unloading side of the platform will not be required
				to be railed if passengers are not permitted on the loading platform until the
				conveyance is stopped for loading or unloading. Platforms may have sectional
				rails separating loading and waiting areas.
2. Inclined walkways or ramps for access to
				loading platforms, if used, shall be inclined so that the slope shall not
				exceed one (1) foot in eight (8) feet, and shall be securely fastened. Such
				ramps shall not be less than eighteen (18) inches wide. Wherever the gradient
				so warrants, cleats shall be secured across the walkway at uniform intervals
				not to exceed twelve (12) inches, or some other effective anti-slip surface
				shall be provided. Standard railings shall be provided on open sides of ramps
				in accordance with the requirements for stairways included in these
				rules.
3. Safe means shall be
				provided for reaching all elevated runways and platforms. Whenever in general
				use, they shall be equipped with a permanent stairway, or stationary ladder
				where it is impracticable to provide a stairway. The side rails of such
				stationary ladders shall extend at least forty-two (42) inches above the level
				served or handholds shall be provided to at least forty-two (42) inches above
				such level.
4. Standard railings
				shall be placed on all open sides of stairs or ramps and for such use may be
				from thirty (30) to thirty-six (36) inches high and serve as required
				handrails.
5. Stairs having more
				than four (4) risers and ramps more than thirty (30) inches high shall be
				equipped with permanent and substantial handrails for the full length of such
				stairs or ramps.
6. Handrails shall
				be placed:
A. On all open sides of stairs and
				ramps;
B. On one side of an
				enclosed stair four (4) feet or less in width,
C. On both sides of any stair more than four
				(4) feet in width;
D. On both sides
				and in the center of stairs more than eight (8) feet in width. The width of
				stairs shall be taken as the length of tread between stringers.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-5 - ACCIDENTS

Current through 2024-29, July 17, 2024
1. Evacuation procedures shall be established
				for each ride for use in case of emergency. Any necessary equipment needed for
				such evacuation shall be readily available for use.
2. It will be the responsibility of the ride
				owner or his representative to report to the State Fire Marshal's Office via
				Regional State Police Barracks any personal injury accident as follows:
A. Immediately if injury requires emergency
				room treatment or hospitalization;
B. Within twenty-four (24) hours if personal
				injury requires emergency first aid.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-6 - MIDWAYS

Current through 2024-29, July 17, 2024
1. Grounds
A. Rides and concessions shall not be set in
				natural drainage areas.
B. Rides
				and concessions shall be kept a minimum of ten (10) feet away from overhead
				electrical lines.
C. Roadways and
				walks shall be of sufficient width to allow access for public safety emergency
				vehicles.
D. Roadways and walks
				shall be free of debris, holes, and other hazards.
E. Except for an emergency response vehicle,
				no motor vehicle shall be permitted on the midway from the time the midway
				opens until closing including those operated by owners and operators, vendors
				and service vehicles.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-7 - FIRE PROTECTION

Current through 2024-29, July 17, 2024
1. The person,
				persons, firm or corporation owning the midway shall provide an adequate, as
				defined in subsection 2 below, and sufficient amount of fire fighting equipment
				for the entire midway.
2. An
				adequate and sufficient amount of fire fighting equipment includes a hose
				attached to a charged standpipe or portable fire extinguishing device located
				every 75 feet within the midway area.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-8 - CONCESSION STANDS

Current through 2024-29, July 17, 2024
1. All electrical
				equipment and installations shall comply with NFPA #70, National Electrical
				Code, as adopted by the State Electricians Examining Board.
2. Hinges, awnings, and braces must be safety
				keyed, nails shall not be used for hinge or support pins.
3. Every effort shall be made to keep stakes
				and ropes from traffic areas. Where this is not possible, highly visible covers
				shall be provided.
4. Seats and
				counter areas must be free of nails, other similar protrusions, and
				splinters.
5. Shooting galleries,
				dart games, and ball pitch games shall have adequate ricochet protection to
				prevent projectiles from leaving the concession stand area and striking a
				passerby.
6. A 10 BC rated dry
				chemical fire extinguisher shall be provided where deep fat fryers are in
				use.
7. All tents and air-supported
				structures for public assembly, if used when natural light is not available,
				shall have emergency lighting in accordance with provisions in the Life Safety
				Code NFPA #101.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 28 - RULES GOVERNING OPERATIONS OF AMUSEMENT DEVICES AND MIDWAYS › Section 219-28-9 - UNLICENSED AMUSEMENT DEVICES

Current through 2024-29, July 17, 2024
1. All electrically
				powered, fixed, child amusement rides located in an established play area of a
				shopping center or restaurant do not require a license. All children rides in
				established play areas shall comply with the following safety requirements:
A. All rides limited to 4 or fewer seats or
				riders;
B. Every ride shall be
				controlled by an electrical switch located at least 6 feet above the
				floor.
C. The control switch shall
				be the type which must be manually engaged to operate the ride and shall, when
				released, return to the "off' position;
D. No ride shall operate at a rate exceeding
				100 feet per minute.
E. No
				admission shall be charged;
F. The
				electrical installation shall comply with the National Electrical
				Code.
G. Operating safety
				instructions shall be posted by operator's switch.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-01 - DEFINITIONS

Current through 2024-29, July 17, 2024
When used in these Regulations the following terms and
				  definitions shall prevail:
A.
				Commissioner shall mean whatever individual is duly appointed and qualified as
				Commissioner of Public Safety under the provisions of Section 2 of Chapter 56
				of the Revised Statutes of 1944.
B.
				State Fire Inspector shall mean and include whatever individual is duly
				appointed by the Commissioner of Public Safety in accordance with Section 29 of
				Chapter 85 of the Revised Statutes of 1944.
C. Inspector shall mean and include
				individuals in cities and towns designated as such under the provisions of
				Section 21 of Chapter 85 of the Revised Statutes of 1944.
D. Architect or Engineer shall mean whatever
				individual is duly registered under the provisions of Section 1 of Chapter 74
				of the Revised Statutes of 1944.
E.
				Grandstand: A permanent structure having a solid floor and individual
				seats.
F. Bleacher: A structure
				with open risers with or without individual seats.
G. Stadium: A structure with its
				enclosures.
H. Arena: The area in
				the central part of the stadium.
I.
				Portable Grandstand or Bleacher: An assembly of prefabricated units, readily
				erected for a specific period of motor vehicle racing.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-02 - Scope of Rules

Current through 2024-29, July 17, 2024
These regulations shall apply to grandstands, bleachers,
				  stadiums, or arenas as the use of the structure warrants. If in the opinion of
				  the Commissioner of Public Safety an existing structure may be dangerous to
				  life or limb, he shall order the owner thereof to furnish a certificate from a
				  licensed architect or engineer showing the calculations for anchorage and
				  footing including soil test data, and live, dead, sway, and wind loads of
				  structural members. Such certificate to be submitted with plans of changes
				  which he deems necessary to make the structure safe.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-03 - Plans and Specifications

Current through 2024-29, July 17, 2024
A. Plans and
				Specifications: No structure which is designed to be used, or in which
				alternations shall be made for the purpose of using it or continuing its use as
				a grandstand, permanent bleacher, stadium or arena, shall be erected, and no
				alternations shall be made therein until plans and specifications in
				triplicate, have been deposited with the Commissioner of Public Safety. The
				Commissioner of Public Safety may require plans showing all details of
				construction, including the size of materials of all members with methods of
				anchorage and footings, including soil test data, and calculations and live,
				dead, sway and wind loads for all structural members, and then further require
				an affidavit from a licensed architect or engineer certifying as to such
				calculations for structural members. The Commissioner of Public Safety may
				require that space under a grandstand or permanent bleachers used for
				commercial purposes shall be enclosed in one-hour fire resistive materials, and
				also make such further requirements as may be necessary to prevent the spread
				of fire.
B. Plans and
				specifications of portable bleachers, shall be approved by the Commissioner of
				Public Safety before the bleacher is erected or relocated. The Commissioner
				shall require that all grass or vegetation shall be cut and removed, and no
				combustible material shall be allowed to accumulate under the
				bleacher.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-04 - General Construction Requirements

Current through 2024-29, July 17, 2024
A.
				Permanent grandstands shall be erected upon and attached to concrete or masonry
				foundations extending below the maximum depth of frost and at least six (6" )
				inches above natural grade.
B.
				Grandstands shall be designed to support, in addition to their own weight, a
				uniformly distributed live load of not less than one hundred (100) pounds per
				square foot of gross horizontal projection of the grandstand. All seats and
				foot-board members shall be designed for live loads of not less than one
				hundred twenty (120) pounds per linear foot. Grandstands shall be designed to
				resist, without live load, a horizontal wind load of thirty (30) pounds per
				square foot of all vertical projections of the stand, and with full live load,
				one half of such wind load. Grandstands shall be designed to resist a
				horizontal swaying force applied to the seats in a direction parallel to the
				length of the seats, of twenty-four (24) pounds per linear foot of seats, and
				in a direction perpendicular to the length of the seats of ten (10) pounds per
				linear foot of seats.
C. Portable
				grandstands and bleachers shall be provided with wood sleepers or mud sills of
				at least two inch (2") plank, or shall be supported on masonry footings. If so
				directed, sills shall be placed both parallel and at right angles to seating
				platforms. All bearing surfaces shall make contact as the Commissioner shall
				direct.
D. Mud sills or sleepers
				shall be of adequate area to support superimposed loads without settlement, and
				shall be secured against lateral movement. The toe of each stringer shall be
				secured to the mud sill or sleeper, all horses or posts shall be provided as
				directed. No more than one cantilever seat shall be permitted.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-05 - Aisles

Current through 2024-29, July 17, 2024
A. A grandstand having a railing along the
				front shall be provided with aisles so located that no portion of any seat
				shall be more than thirty (30') feet from the nearest aisle. A grandstand
				having seats with backs shall be provided with aisles so located that no
				portion of any seat shall be more than thirty (30') feet from the nearest
				aisle.
B. Aisles shall not be less
				than three feet six inches (3' 6") in width, provided, that where an aisle is
				divided into two parts, each part shall be two (2') feet in width. Where an
				aisle is elevated above ground level, each aisle shall be provided with a
				stairway or ramp not less than the width of the aisle.
C. Grandstands or bleachers having more than
				thirty (30) row of seats shall have transverse aisles not less than forty-five
				(45') feet apart leading to stairs or ramps. The Commissioner Of Public Safety
				may require that a transverse aisle end on a stairway. Transverse aisles shall
				not be less than five (5') feet in width.
D. Aisles shall be located as directed by the
				Commissioner of Public Safety. Bleachers without aisles shall have not more
				than fifteen (15) rows of seats.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-06 - Seats and Seating Platforms

Current through 2024-29, July 17, 2024
A. Seats and
				Seating Platforms: The horizontal distance back-to-back of bleacher seat
				platforms used without individual chairs shall not be less than twenty-two
				(22") inches. Where the same level is used for seats with backs these levels
				shall not be less than twenty-four (24") inches in width. Where chairs are
				used, the horizontal distance back-to-back shall be thirty (30")
				inches.
B. Seats shall be securely
				fastened to their supports in such a manner that they cannot accidentally be
				displaced. Foot rests shall be supported in such a manner that they cannot
				accidentally be displaced. Foot rests which are lapped shall be provided with
				some positive means to prevent displacement of one piece on the other. All
				chairs shall be securely fastened in place.
C. Where seats are not provided or marked
				off, a width of eighteen (18") inches shall be considered one seat.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-07 - Exits

Current through 2024-29, July 17, 2024
A. Outdoor grandstands, bleachers, stadiums
				or arenas shall be provided with exits calculated on the basis of one (1') foot
				in width for each three hundred (300) persons, or fraction thereof served.
				Exits shall not be less than three feet six inches (3' 6") in width, nor less
				than seven (7') feet clear height, and shall be located as directed by the
				Commissioner of Public Safety.
B.
				Each exit shall be designated by a sign bearing the word "EXIT" in letters not
				less than five (5") inches in height and one half (1/2") inch in width, having
				red letters on a white background, or white letters on a red background,
				located as directed. Each change in direction of a way of egress shall be
				designated by a directional sign, located as directed by the Commissioner of
				Public Safety.
C. Exits, aisles,
				and ways of egress shall be properly illuminated at all times when the
				structure is in use. Where artificial illumination is required, a secondary
				source of illumination shall be provided as directed by the Commissioner of
				Public Safety under Section 29.12.
D. Egress doors or gates shall be determined
				by the Commissioner-of Public-Safety. Turnstiles shall not be permitted in any
				required egress unless adjacent thereto a suitable exit is provided.
E. Railings eighteen (18") inches in height
				shall be provided: (a) along back of all grandstands if the rear seat is more
				than four (4') feet above the ground; (b) along those portions of the ends
				where the seats are more than four (4') feet above the ground; (c) along the
				front if the foot rest is more than two (2') feet above the ground.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-08 - Sanitation

Current through 2024-29, July 17, 2024
Grandstands and permanent bleachers shall be provided with
				  reasonably accessible toilet rooms for either sex having not less than one
				  urinal and one water closet for men and not less than two water closets for
				  women for each three hundred (300) persons, or fraction thereof, served. Toilet
				  rooms shall be vented to atmosphere as directed by the Commissioner of Public
				  Safety Through urinals are prohibited.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-09 - Crash Barrier Construction - Indoor and Outdoor Tracks

Current through 2024-29, July 17, 2024
Crash Barrier Construction - Indoor and Outdoor Race Tracks:
				  Automobile or motorcycle race tracks hereafter erected shall have a bumper
				  rail, a primary type A or B crash barrier and a secondary crash barrier at the
				  outer circumference of the track and shall conform to either of the following
				  types of construction: Type A for tracks without earth traps Type B for tracks
				  with earth traps
A. Type "A" Barriers
				Defined: There shall be a bumper rail secured to 6" x 6" posts set at least
				three feet six inches (3' 6") below grade. Posts shall be spaced not more than
				eight (8') feet apart. The top of the rail shall not be more than two (2') feet
				above the surface of the track and shall be placed at right angles to the
				surface of the track.
1. There shall be a
				primary crash barrier outside and consisting of a chain link fence or
				equivalent barrier. Poles shall be of 2 1/2" pipe, set at least below grade or
				below frost line, spaced not more than ten (10') feet on center. The fence
				shall be not less than four (4') feet in height.
2. The first or lowest seat or chair or
				platform of the grandstand shall be not less than ten (10') feet above track
				level.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-10 - Fire Safety

Current through 2024-29, July 17, 2024
A. Extinguishers of
				an approved type, in a number to be determined by the Commissioner of Public
				Safety shall be made available at all times. In addition such other fire
				extinguishing equipment may be required by the head of the fire department in
				the city or town where motor vehicle racing is held shall be
				provided.
B. The individual firm or
				corporation holding the period of motor vehicle racing shall arrange for the
				detailing of at least one member of the local fire department or a larger
				number as deemed necessary by the head of the fire department. They shall be on
				duty from the beginning to the end of the racing daily.
C. Any unforeseen condition that presents a
				fire hazard, or would contribute to the rapid spread of fire, or would delay or
				interfere with the rapid exit of persons from the grandstand, bleachers,
				stadium or arena, or would interfere with or delay the extinguishment of a
				fire, and which is not otherwise covered by these rules and regulations, shall
				be immediately abated, eliminated or corrected as ordered by the inspection
				authority.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-11 - Insurance

Current through 2024-29, July 17, 2024
No motor vehicle racing shall be conducted until a
				  certificate of Public Liability Insurance has been filed with the Insurance
				  Commissioner. Such certificate shall indicate that a policy providing Bodily
				  Injury Liability Insurance with minimum limits of $50,000 each person,
				  $1,000,000 each accident and Property Damage Liability Insurance of $25,000
				  each accident has been issued by an Insurance Company acceptable to the
				  Insurance Commissioner. Ten (10) days notice of cancellation of Liability
				  Insurance shall be given in writing to the Commissioner of Public
				  Safety.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-12 - Auxiliary Lighting

Current through 2024-29, July 17, 2024
A. The use of
				electricity supplied by a 110-115 V generator or approved storage battery
				system for secondary means of illumination is permitted and shall be connected
				to the emergency lighting panels through an automatic throw-over switch which
				will operate immediately in the event of failure in the general lighting
				supply. At no time shall the connected secondary lighting load be greater than
				the rated capacity of the generator or storage battery system. The generator or
				storage battery system shall have sufficient capacity to supply the lighting
				circuits so connected for not less than one and one-half (1 1/2) hours. The
				automatic throw-over switch shall be connected so that when the principal
				lighting supply is restored it will throw back to normal operating position.
				Provision shall be made for automatic charging of all wet batteries of such
				lighting systems. Batteries and generators shall be inspected and tested at
				intervals of not less than once a week. The automatic throw-over switch shall
				be tested each day.
B. No open
				flame shall be used for illumination or decorative effect.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 29 - RULES AND REGULATIONS RELATING TO STRUCTURES USED BY THE PUBLIC AS SPECTATORS DURING MOTOR VEHICLE RACING › Section 219-29-13 - Wiring Construction

Current through 2024-29, July 17, 2024
All wiring for electricity shall be done in accordance with
				  the best practice. In case any question arises as to what is the best practice,
				  work done according to the requirements of the National Board of Fire
				  Underwriters shall be considered as so done.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 31 - RULES FOR THE MANUFACTURE, TRANSPORTATION, STORAGE AND USE OF EXPLOSIVE MATERIALS › Section 219-31-1

Current through 2024-29, July 17, 2024
This rule is an agency incorporation by reference to the
				  National Fire Protection Association Standard #495,
Explosive Materials
				  Code
, 2006 edition. All rights reserved by the National Fire
				  Protection Association. Copies of this standard are available through the
				  National Fire Protection Association, 1 Batterymarch Park, Quincy, MA
				  02269.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 31 - RULES FOR THE MANUFACTURE, TRANSPORTATION, STORAGE AND USE OF EXPLOSIVE MATERIALS › Section 219-31-3 - CERTIFICATE OF PUBIC [PUBLIC] LIABILITY

Current through 2024-29, July 17, 2024
A certificate of public liability insurance in the amount of
				  $500,000.00 to cover losses, damages or injuries that may ensue to persons or
				  property must be furnished to the Office of State Fire Marshal prior to
				  issuance of a permit to use, store or transport explosives. This certificate
				  must also have a ten day notice of cancellation or change of policy.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 31 - RULES FOR THE MANUFACTURE, TRANSPORTATION, STORAGE AND USE OF EXPLOSIVE MATERIALS › Section 219-31-4 - VIOLATIONS - CIVIL VIOLATIONS

Current through 2024-29, July 17, 2024
Forfeiture of not less than $100.00 nor more than $500.00 may
				  be adjudicated for each offense. All such substances may be seized by a peace
				  officer and forfeited and, within 20 days after such seizures, may be libeled
				  according to law. Cities or towns may make and enforce reasonable ordinances or
				  bylaws not inconsistent with these rules.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 31 - RULES FOR THE MANUFACTURE, TRANSPORTATION, STORAGE AND USE OF EXPLOSIVE MATERIALS › Section 219-31-5 - RECORD KEEPING AND REPORTING

Current through 2024-29, July 17, 2024
Any person who sells or markets explosive materials as
				  defined by Title
				   25 M.R.S.A.
				  §2471, within the State of Maine, shall
				  submit a report upon request to the Office of State Fire Marshal of the sale or
				  transfer of ownership of all explosive materials sold or transferred to a new
				  owner by said person listing the date of delivery, the name, address and
				  explosive use, purchase and transport license, number of persons to whom the
				  explosives were sold or delivered; along with the type, size, identification
				  number and amount of explosives sold. This report shall be submitted monthly,
				  on such forms as the State Fire Marshal may designate, not later than the
				  fifteenth day of each month.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 31 - RULES FOR THE MANUFACTURE, TRANSPORTATION, STORAGE AND USE OF EXPLOSIVE MATERIALS › Section 219-31-6 - NOTIFICATION OF LOSS, THEFT OR UNLAWFUL REMOVAL

Current through 2024-29, July 17, 2024
The loss, theft, or unlawful removal of explosive materials
				  shall be reported within 24 hours to the Office of State Fire Marshal and the
				  Bureau of Alcohol, Tobacco and Firearms.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Section 219-34-1

Current through 2024-29, July 17, 2024
This rule incorporates by reference NFPA #30, 2008 Edition,
Standards for Flammable and Combustible Liquids
, not including
				  standards relating to storage in underground tanks of materials currently
				  regulated by the Maine Department of Environmental Protection under Title 38 or
				  to storage of flammable substances that are regulated by the Department of
				  Professional and Financial Regulation under Title 32. Copies of this standard
				  are available through the National Fire Protection Association, 1 Batterymarch
				  Park, Quincy, MA 02269.
1. The
				following table and sections in NFPA #30,
Standards for Flammable and
				Combustible Liquids
, shall be excluded from this rule:
A. Table 22.4.1.1 (b) of NFPA 30
Reference Table for Use in Tables 22.4.1.1 (a) , 22.4.1.3, and
				22.4.1.5.
All references to table 22.4.1.1
				(b
)
of NFPA 30, shall be interpreted as a reference to
				"
Table
4.3.2.1.1(b)
State of Maine
Reference
				Table for Use in Tables 22.4.1.1 (a), 22.4.1.3, and 22.4.1.5" (see table in
				appendix A to be incorporated in this rule).
B. All references to underground storage
				tanks:
C. Sections of NFPA 30
				referring to underground storage tanks, which are regulated by the Maine
				Department of Environmental Protection under Title 38 MRSA §561 are
				excluded from this rule.
D.
				Sections of NFPA 30 referring to the underground storage of flammable substance
				are:
23.6.2
23.5.3
23.6
A.23.3.3
21.7.4.3.9
23.3.4
C.6.
23.13
23.13.3
23.14
23.5
21.7.5
A.21.7.5
28.10.2
23.4
21.7.1.5
21.7.4.3
A.21.7.4.3.3(2)
C.5
21.7.4.3.8
C.2
21.5
23.6
A.23.6.1
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Section 219-34-2

Current through 2024-29, July 17, 2024
This rule incorporates by reference NFPA # 30A, 2008 Edition,
Code for Motor Fuel Dispensing Facilities and Repair Garages.
Copies of this standard are available through the National Fire
				  Protection Association, 1 Batterymarch Park, Quincy, MA 02269.
1. The following table and section(s) in NFPA
				#30A,
Code for Motor Fuel Dispensing Facilities and Repair Garages
				Standards for Flammable and Combustible Liquids
, 2008 edition shall
				not be included in this rule:
A. Table 4.3.2.4
Tanks shall be located in accordance with Table 4.3.2.4.
All
				references to it shall be replaced with a reference to "Table 4.3.2.4
State
of Maine
Minimum Separation
				Requirements for Aboveground Tanks" (see table in Appendix B).
B. Section 6.3.8
At unattended
				self-serve motor fuel dispensing facilities, coin- and currency-type devices
				shall only be permitted with the approval of the authority having
				jurisdiction
.
C. Section
				6.7.2
At unattended motor fuel dispensing facilities, the devices or
				disconnects shall be readily accessible to patrons and at least one device or
				disconnect shall be readily accessible to each group of dispensing devices on
				an individual island.
D.
				Section 7.3.5
Fixed Fire Protection
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Section 219-34-3

Current through 2024-29, July 17, 2024
This rule incorporates by reference NFPA #30B,
Code
				  for the Manufacture and Storage of Aerosol Products,
2007 Edition.
				  Copies of this standard are available through the National Fire Protection
				  Association, 1 Batterymarch Park, Quincy, MA 02269.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Section 219-34-4

Current through 2024-29, July 17, 2024
This rule incorporates NFPA #385, 2007 Edition,
Standard for Tank Vehicles for Flammable and Combustible
				  Liquids
. Copies of this standard are available through the National
				  Fire Protection Association, 1 Batterymarch Park, Quincy, MA 02269.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Section 219-34-5

Current through 2024-29, July 17, 2024
Applications, Construction Plans, Technical Specifications,
				  Permits and Fees of Aboveground Flammable Liquid Storage Facilities. (Note: see
				  Title
				  25 M.R.S.A
				  §2481 through §
									2484
				  ).
1. The construction plans and
				technical specifications for storage facilities exceeding 1,320 gallons, in one
				or multiple tanks, shall be certified by a professional engineer.
2. A permit is non-transferable pursuant to
				Title 25 M.R.S.A §2481,(5). A person acquiring an existing facility must
				notify the Office of the State Fire Marshal within 180 days of assuming
				ownership of that facility.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Section 219-34-6 - PERMITS FOR TEMPORARY TANKS

Current through 2024-29, July 17, 2024
1. The
				owner/operator of an aboveground flammable liquid storage tank that is located
				at a temporary work site and will be on the site for 180 days or less shall not
				be required to obtain a permit but must otherwise comply with this
				chapter.
2. Operation of a
				temporary tank in excess of 180 days shall require a permit pursuant to this
				chapter under Title 25 M.R.S.A. §2483.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Section 219-34-7 - SPECIAL REGULATIONS FOR REPORTING OIL DISCHARGES AT ABOVEGROUND FLAMMABLE LIQUID STORAGE FACILITIES

Current through 2024-29, July 17, 2024
1. An owner or
				operator of an aboveground flammable liquid storage facility containing oil, or
				any person who causes or is responsible for a discharge of oil or who has
				custody or control of the oil at the time of the discharge at such a facility,
				must report a discharge prohibited by 38 M.R.S.A. §543 within two hours to
				the Department of Environmental Protection.
2. For the purposes of this chapter
				"Aboveground flammable liquid storage facility" means any aboveground storage
				tank or tanks containing flammable liquids, together with associated piping,
				transfer and dispensing facilities.
3. For the purposes of this chapter
				"Flammable liquid" means either a combustible liquid having a flash point at or
				above 100 degrees Fahrenheit or any volatile liquid having a flash point below
				100º Fahrenheit.
4. For the
				purpose of this section, "discharge" means any spilling, leaking, pumping,
				pouring, emitting, escaping, emptying or dumping.
5. For the purpose of this section, "oil"
				means oil, oil additives, petroleum products and their byproducts of any kind
				and in any form including, but not limited to, petroleum, fuel oil, sludge, oil
				refuse, oil mixed with other nonhazardous waste, crude oils and all other
				liquid hydrocarbons regardless of specific gravity.
6. This section does not apply to the storage
				of oil regulated by the Maine Department of Professional and Financial
				Regulation under Title 32.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Appendix 219-34-A

Current through 2024-29, July 17, 2024
Table
4.3.2.1.1(b)
State of Maine
Reference Table for Use in Tables 4.3.2.1.1(a),
							 4.3.2.1.2, and 4.3.2.1.4
Tank Capacity (gal)
Minimum distance from
Minimum Distance from property
nearest side of any public
line that is or can be built upon,
way or from the nearest
including the opposite side of a
important building on the
public way (ft)
same property (ft)
275 or less
25
25
276 to 750
25
25
754 to 12,000
25
25
12,001 to 30,000
25
25
30,001 to 50,000
30
25
50,001 to 100,000
50
25
100,001 to 500,000
80
25
500,001 to 1,000,000
100
35
1,000,001 to 2,000,000
135
45
2,000,001 to 3,000,000
165
55
3,000,001 to more
175
60
For SI units, 1 ft. = 0.3 m; 1 gal = 3.8
							 L.
Code of Maine Rules › 16 - DEPARTMENT OF PUBLIC SAFETY › 219 - OFFICE OF STATE FIRE MARSHAL › Chapter 34 - RULES AND REGULATIONS FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS › Appendix 219-34-B

Current through 2024-29, July 17, 2024
Table 4.3.2.4
State of
						  Maine
Minimum Separation Requirements for Aboveground Tanks
Tank Type
Individual Tank Capacity (gal) (See
						  4.3.2.3 and 4.3.2.5)
Minimum distance from the nearest important
						  building on the same property (ft)
Minimum distance from the nearest
						  fuel dispensing device (ft) (see 4.3.2.6)
Minimum distance from lot
						  line that is or can be built upon, including the opposite side of a public way
						  (ft)
Distance from the nearest side of any public way
						  (ft)
Minimum distance between tanks (ft)
Tanks in Vaults*
0 -
						  12,000
25
25
50
25
Separate
						  compartments required for each tank
Protected aboveground tanks
less than or equal
						  to 6,000
5
0
15
5
3
6,001 - 12,000
15
25
25
15
3
Fire resistant tanks
0 -
						  12,000
25
25
50
25
3
Other tanks meeting the requirements of NFPA 30A
0 - 12,000
50
50
100
50
3