reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State-owned and Leased Buildings Fire Safety › Section R. 29.1504 - Plans and specifications

Current through Vol. 24-12, July 15, 2024
Rule 4.
(1) When
				required by the authority having jurisdiction, the owner or the owner's
				authorized representative shall submit plans and specifications to the office
				of fire safety for projects that involve construction, remodeling, an addition,
				or maintenance functions.
(2) When
				required by the authority having jurisdiction, the owner or the owner's
				authorized representative shall ensure that plans and specifications for work
				that involves the practices of architecture or engineering, as defined by the
				provisions of 1980 PA 299, as amended, being $339.101 et seq.of the Michigan
				Compiled Laws, and known as the occupational code, bear the seal of an
				architect or professional engineer who is licensed pursuant to the provisions
				of 1980 PA 299, as amended.
(3)
				When required by the authority having jurisdiction, the owner or the owner's
				authorized representative shall ensure that plans and specifications contain
				all of the following information, as applicable:
(a) A complete floor plan and layout of the
				building drawn accurately to scale.
(b) The use of each room.
(c) The dimensions of each room.
(d) The size, location, direction of swing,
				and fire rating of each door and frame assembly.
(e) The size and location of
				windows.
(f) The materials of wall
				assembly, including the fire-resistance rating of the wall assembly.
(g) The type of construction as identified by
				the provisions of the national fire protection association standard no. 220,
				1995 edition, entitled "Standard on Types of Building Construction" as adopted
				in these rules.
(h) The number of
				stories, including basement and attic areas.
(i) The interior finish
				classification.
(j) The location of
				fuel-fired equipment.
(k) The type
				of furnace and water heater.
(l)
				Air-handling system specifications.
(m) Fire detection and alarm system plans and
				specifications that are in compliance with the provisions of the act.
(n) Sprinkler or other suppression system
				plans and specifications that are in compliance with the provisions of the
				act.
(o) The type, size, and
				location of fire extinguishers.
(p)
				Other pertinent information that is required to determine compliance with these
				rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State-owned and Leased Buildings Fire Safety › Section R. 29.1506 - Projects affecting outside configuration of building; site plan and specifications; local fire department specifications; fire safety measures during construction

Current through Vol. 24-12, July 15, 2024
Rule 6.
(1) For
				projects that involve construction, addition, or remodeling which affect the
				outside configuration of a building, and as part of the building plans and
				specifications otherwise required by these rules, before construction begins,
				the owner or the owner's authorized representative shall provide the local fire
				department with a site plan and specifications that detail all of the
				following:
(a) The available water
				supply.
(b) Hydrant
				locations.
(c) Vehicle access
				routes.
(d) Fire lanes.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State-owned and Leased Buildings Fire Safety › Section R. 29.1507 - Electrical equipment; inspections; certificate

Current through Vol. 24-12, July 15, 2024
Rule 7.
(1) The
				owner or owner's authorized representative shall ensure that electrical wiring
				and equipment, including an emergency supply if installed, is installed in
				compliance with the applicable provisions of
				R 408.30801 et seq. of the Michigan
				Administrative Code. Copies of the rules are available from the Michigan
				Department of Consumer and Industry Services, Bureau of Construction Codes,
				2501 Woodlake Circle, Second Floor, P.O. Box 30254, Okemos, Michigan 48864, or
				from the internet address www.state.mi.us/orr [File Link Not
				Available].
(2) Electrical
				inspection shall be made by an electrical inspection authority acceptable to
				the office of fire safety. The electrical authority shall issue a final
				certificate of compliance covering the installation. A copy of the certificate
				shall be provided to the office of fire safety by the owner or owner's
				authorized representative.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State-owned and Leased Buildings Fire Safety › Section R. 29.1509 - Fire reporting

Current through Vol. 24-12, July 15, 2024
Rule 9. After the occurrence of a fire that results in a loss
				  of life, personal injury, or loss of property, the administrative authority of
				  the facility shall immediately notify the local fire department of all details
				  of the fire.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Section R. 29.1620 - Rescissions

Current through Vol. 24-12, July 15, 2024
Rule 20.
(1)R
				28.101, R 28.102, and R 28.104 to R 28.106 of the Michigan Administrative Code
				are rescinded.
(2)R 29.2501 to R
				29.2733 of the Michigan Administrative Code are rescinded.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Section R. 29.1651 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 1.
(1) These
				rules apply to both of the following under sections 2 and 2b of 1941 PA 207 MCL
				29.2 and 29.2b:
(a) Fire safety requirements
				for the construction, operation, or maintenance of places of public assemblage.
				Exception: Places of public assemblage constructed in compliance with 1972 PA
				230, MCL 125.1501, are exempt from the construction requirements of the
				code.
(b) Fire safety requirements
				for the operation and maintenance of commercial buildings, industrial
				buildings, and residential buildings, excluding 1-and 2-family dwellings and
				mobile homes.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Section R. 29.1652 - Uniform fire code; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 2.
(1) Except
				as amended by parts 2 to 4 of these rules, the provisions of Chapters 1 to 6,
				10 to 14, 20 to 34, 40 to 41, 43 to 45, 50 to 52, 60, 63, 65 and 70, NFPA
				(national fire protection association) 1, entitled "Uniform Fire Code," 2006
				edition, are adopted by reference as part of these rules. Copies of the adopted
				provisions are available for inspection and distribution either at the office
				of the Bureau of Fire Services, Michigan Department of Energy, Labor &
				Economic Growth, P.O. Box 30700, 525 W. Allegan, 4th Floor, Lansing, Michigan
				48913, or from the National Fire Protection Association, 1 Batterymarch Park,
				P.O. Box 9101, Quincy, Massachusetts 02269-9101, telephone number
				1-800-344-3555. The cost as of the time of adoption of these rules is $75.00
				per copy.
(2) Additional references
				by adoption are identified in
				R
				29.1654, which also indicates where the references can
				be obtained and the cost at the time of the adoption of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Section R. 29.1655 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 5. Sections 3.3.24, 3.3.32, 3.3.38, 3.3.44, 3.3.45,
				  3.3.45.1, 3.3.45.2, 3.3.45.3, 3.3.45.4, 3.3.47, 3.3.145, 3.3.149, 3.4, 3.4.1,
				  3.4.2, 3.4.2.1, 3.4.2.2, 3.4.3, 3.4.4, 3.4.5, 3.4.6, 3.4.7, 3.4.8, 3.4.9,
				  3.4.9.1, 3.4.10, 3.4.11, 3.4.12, 3.4.13, 3.4.14, 3.4.15, 3.4.16, 3.4.17,
				  3.4.18, 3.4.19, 3.4.20, 3.4.21 and 3.4.22 of chapter 3 of the code are deleted,
				  sections 3.2.2, 3.2.3, 3.3.165.1, 3.3.165.10, 3.3.165.11, 3.3.165.12,
				  3.3.165.15, 3.3.165.18 and 3.3.172 of chapter 3 of the code are amended, and
				  sections 3.2.11 and 3.2.12 of chapter 3 of the code are added to read as
				  follows: 3.2.2 "Authority having jurisdiction" (AHJ). The director of the
				  department of energy, labor, and economic growth or an employee of the
				  department of energy, labor, and economic growth appointed by the director to
				  implement the act. 3.2.3 Code. The national fire protection association
				  pamphlet no. 1, 2006 edition, entitled "Uniform Fire Code." as amended by these
				  rules.3.2.11 Maintenance. The service required to keep fire safety materials,
				  equipment, systems, and system components in a condition of good repair or
				  efficiency to assure the fire safety systems, materials, or equipment perform
				  as intended. The service includes the replacement of component parts when for
				  any reason the parts become undependable or inoperable and includes periodic
				  inspections and tests of the fire safety materials, equipment, and systems.
				  3.2.12 Operation. The regular performance of the full range of intended
				  functions of the fire safety features required by these rules.
3.3.24 Deleted.
3.3.32 Deleted.
3.3.38 Deleted.
3.3.44 Deleted.
3.3.45 Deleted.
3.3.45.1 Deleted.
3.3.45.2 Deleted.
3.3.45.3 Deleted.
3.3.45.4 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Section R. 29.1656 - General requirements

Current through Vol. 24-12, July 15, 2024
Rule 6. Sections 4.1.3.1.2.2, 4.1.3.1.2.3, 4.1.3.1.2.4,
				  4.1.3.2.2, 4.1.3.2.2.1, 4.1.3.2.2.2, 4.1.3.2.2.3, 4.1.3.2.2.4, 4.1.3.2.2.5,
				  4.3.2, 4.3.2.1, 4.3.2.2, 4.5.2, 4.5.5, 4.5.5.1 and 4.5.5.2 of chapter 4 of the
				  code are deleted and sections 4.1.3.1.2.1, 4.1.4.2.2, 4.1.4.2.3, 4.1.4.2.4,
				  4.1.5.2 and 4.3 of chapter 4 of the code are amended to read as follows:
4.1.3.1.2.1 Buildings and facilities
				shall be maintained to protect occupants who are not intimate with the initial
				fire development for the amount of time needed to evacuate, relocate, or defend
				in place.
4.1.3.1.2.2
				Deleted.
4.1.3.1.2.3
				Deleted.
4.1.3.1.2.4
				Deleted.
4.1.3.2.2 Deleted.
4.1.3.2.2.1 Deleted.
4.1.3.2.2.2 Deleted.
4.1.3.2.2.3 Deleted.
4.1.3.2.2.4 Deleted.
4.1.3.2.2.5 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Section R. 29.1657 - Performance-based option

Current through Vol. 24-12, July 15, 2024
Rule 7. Sections 5.1, 5.1.1, 5.1.2, 5.1.3, 5.1.4, 5.1.5,
				  5.1.6, 5.1.6.1, 5.1.6.2, 5.1.7, 5.1.8, 5.1.9, 5.1.10, 5.1.10.1, 5.1.10.2,
				  5.1.10.2.1, 5.1.10.2.2, 5.1.11, 5.1.12, 5.1.12.1, 5.1.12.2, 5.1.12.3, 5.1.13,
				  5.2, 5.2.1, 5.2.2, 5.2.2.1, 5.2.2.2, 5.2.2.3, 5.2.2.4, 5.2.2.5, 5.2.2.6,
				  5.2.2.7, 5.2.2.8, 5.3, 5.3.1, 5.3.2, 5.3.3, 5.3.4, 5.3.5, 5.4, 5.4.1, 5.4.1.1,
				  5.4.1.2, 5.4.1.3, 5.4.1.3.1, 5.4.1.3.2, 5.4.1.4, 5.4.1.5, 5.4.1.6, 5.4.2,
				  5.4.2.1, 5.4.2.1.1, 5.4.2.1.2, 5.4.2.2, 5.4.2.3, 5.4.2.4, 5.4.2.5, 5.4.2.6,
				  5.4.2.7, 5.4.2.8, 5.4.3, 5.4.3.1, 5.4.3.1.1, 5.4.3.1.2, 5.4.4, 5.4.4.1,
				  5.4.4.2, 5.4.4.3, 5.4.4.4, 5.4.4.4.1, 5.4.4.4.2, 5.4.5, 5.4.5.1, 5.4.5.2, 5.5,
				  5.5.1, 5.5.1.1, 5.5.1.2, 5.5.2, 5.5.3, 5.5.3.1, 5.5.3.1.1, 5.5.3.1.2, 5.5.3.2,
				  5.5.3.3, 5.5.4, 5.5.5, 5.6, 5.7, 5.7.1, 5.7.1.1, 5.7.1.2, 5.7.2, 5.7.2.1,
				  5.7.2.2, 5.7.3, 5.7.4, 5.7.5, 5.7.6, 5.7.7, 5.7.8, 5.7.9, 5.7.10, 5.7.11,
				  5.7.11.1, 5.7.11.2, 5.7.12, 5.7.13 and 5.7.14 of chapter 5 of the code are
				  deleted to read as follows:
5.1
				Deleted.
5.1.1 Deleted.
5.1.2 Deleted.
5.1.3 Deleted.
5.1.4 Deleted.
5.1.5 Deleted.
5.1.6 Deleted.
5.1.6.1 Deleted.
5.1.6.2 Deleted.
5.1.7 Deleted.
5.1.8 Deleted.
5.1.9 Deleted.
5.1.10 Deleted.
5.1.10.1 Deleted.
5.1.10.2 Deleted.
5.1.10.2.1 Deleted.
5.1.10.2.2 Deleted.
5.1.11 Deleted.
5.1.12 Deleted.
5.1.12.1 Deleted.
5.1.12.2 Deleted.
5.1.12.3 Deleted.
5.1.13 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Section R. 29.1658 - Classification of occupancy

Current through Vol. 24-12, July 15, 2024
Rule 8. Sections
				  6.1.14.4.2,
				  6.1.14.4.3
				  and 6.1.14.4.4 of chapter 6 of the code are deleted and section 6.1.14.4.1 of
				  chapter 6 of the code is amended to read as follows:
6.1.14.4.1 Where separated occupancies are
				provided, each part of the building comprising a distinct occupancy, as
				described in this chapter, shall be completely separated from other occupancies
				by 2-hour fire resistive assemblies, unless separation is provided by approved
				existing separations. 6.1.14.4.1
6.1.14.4.2 Deleted.
6.1.14.4.3 Deleted.
6.1.14.4.4 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1659 - General fire safety

Current through Vol. 24-12, July 15, 2024
Rule 9. Sections 10.1.3, 10.3.4.1, 10.9, 10.9.1, 10.9.2,
					 10.9.2.1, 10.9.2.2, 10.9.3, 10.11.1, 10.11.1.1, 10.11.1.3, 10.11.1.4,
					 10.11.2.2, 10.11.2.3, 10.11.2.4, 10.11.5, 10.12.2, 10.12.2.1, 10.12.2.2,
					 10.12.2.3, 10.12.3, 10.12.3.1, 10.12.3.1.1, 10.12.3.1.2, 10.12.3.1.3,
					 10.12.3.1.4, 10.12.3.1.5, 10.12.3.1.6, 10.12.3.1.7, 10.12.3.1.8, 10.12.3.2,
					 10.12.3.2.1, 10.12.3.2.2, 10.12.3.3, 10.12.3.4, 10.12.3.5, 10.12.3.6,
					 10.12.3.7, 10.12.3.7.1, 10.12.3.7.2, 10.12.3.8, 10.12.3.9, 10.12.3.10, 10.15.1,
					 10.15.3, 10.15.11.1, 10.17, 10.17.1, 10.17.2, 10.17.3 and 10.19.2 of chapter 10
					 of the code are deleted and sections 10.1.1, 10.1.2, 10.3.1, 10.11.3 and
					 10.12.1.1 of chapter 10 of the code are amended to read as follows:
10.1.1 Every existing building or structure
				  shall be arranged, equipped, maintained, and operated in accordance with this
				  code to provide a reasonable level of life safety, property protection, and
				  public welfare from the actual and potential hazards created by fire,
				  explosion, and other hazardous conditions.
10.1.2 Every existing building shall comply
				  with this code.
10.1.3
				  Deleted.
10.3.1 No existing
				  building shall be occupied in whole or in part in violation of the provisions
				  of this code.
10.3.4.1
				  Deleted.
10.9 Deleted.
10.9.1 Deleted.
10.9.2 Deleted.
10.9.2.1 Deleted.
10.9.2.2 Deleted.
10.9.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1660 - Building services

Current through Vol. 24-12, July 15, 2024
Rule 10. Sections 11.1.6.1, 11.1.6.4, 11.3.1.2, 11.3.2,
					 11.3.3, 11.3.4, 11.3.5, 11.5.1.1, 11.5.1.2, 11.5.1.3, 11.5.1.4, 11.5.1.5,
					 11.5.1.6, 11.5.1.7, 11.6.1, 11.6.1.1, 11.6.1.2, 11.6.1.3, 11.6.1.4, 11.6.1.5,
					 11.7.1, 11.7.2.1, 11.7.2.2, 11.7.3, 11.8.1, 11.8.4, 11.9, 11.9.1, 11.9.2,
					 11.9.3, 11.9.4, 11.9.5 and 11.9.6 of chapter 11 of the code are deleted and
					 sections 11.1.2, 11.1.3, 11.3.1.1, 11.4, 11.5.4 and 11.6.2 of chapter 11 of the
					 code are amended to read as follows:
11.1.2 All electrical appliances, fixtures,
				  equipment, or wiring shall be maintained in accordance with the Michigan
				  electrical code.
11.1.3 Permanent
				  wiring shall be installed and maintained in accordance with the Michigan
				  electrical code.
11.1.6.1 Deleted.
11.1.6.4 Deleted.
11.3.1.1 Elevators shall be in compliance
				  with the rules promulgated by the Michigan elevator safety board pursuant to
				  the provisions 1967act 227, MCL 408.8101.
11.3.1.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1661 - Features of fire protection

Current through Vol. 24-12, July 15, 2024
Rule 11. Sections 12.2, 12.2.1, 12.2.2, 12.3.1, 12.4.2,
					 12.4.4, 12.4.5, 12.7.1, 12.7.2.1, 12.7.2.1.1, 12.7.2.1.2, 12.7.2.2, 12.7.2.3,
					 12.7.3.2, 12.7.3.2.1, 12.7.3.2.2, 12.7.3.4, 12.7.3.5, 12.7.3.6, 12.7.3.7,
					 12.7.3.8, 12.7.3.9, 12.7.3.10, 12.7.3.10.1, 12.7.3.10.2, 12.7.4, 12.7.4.1,
					 12.7.4.2, 12.7.4.3, 12.7.4.4, 12.8, 12.8.1, 12.8.2, 12.8.3, 12.8.3.1, 12.8.3.2,
					 12.8.3.3, 12.8.3.4, 12.8.3.5, 12.8.4, 12.8.4.2, 12.9, 12.9.1, 12.9.2, 12.9.2.1,
					 12.9.2.2, 12.9.2.3, 12.9.3, 12.9.4, 12.9.4.1, 12.9.4.2, 12.9.4.3, 12.9.4.4,
					 12.9.4.5, 12.9.5, 12.9.5.1, 12.9.5.2, 12.9.5.3, 12.9.5.4, 12.9.5.4.1,
					 12.9.5.4.2, 12.9.5.5, 12.9.5.6, 12.9.5.7, 12.9.5.7.1, 12.9.5.7.2, 12.9.5.7.3,
					 12.9.6, 12.9.6.1, 12.9.6.2, 12.9.6.3, 12.9.6.4, 12.9.6.5, 12.9.6.6, 12.9.7,
					 12.9.7.1, 12.9.7.2, 12.9.7.3, 12.9.7.4 and 12.9.7.5 of chapter 12 of the code
					 are deleted and sections 12.1 and 12.4.1 of the code are amended, to read as
					 follows:
12.1 General. This chapter
				  shall apply to existing, permanent, or temporary buildings.
12.2 Deleted.
12.2.1 Deleted.
12.2.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1663 - Means of egress

Current through Vol. 24-12, July 15, 2024
Rule 13. Sections 14.2, 14.3.1, 14.5.1.1.1, 14.5.1.1.3,
					 14.5.1.1.4, 14.5.1.1.6, 14.5.1.4, 14.5.1.5.4, 14.5.2.3, 14.5.2.6, 14.5.2.7,
					 14.5.2.7.2, 14.5.4.3, 14.6.1, 14.6.1.1, 14.6.1.2, 14.6.1.3, 14.6.2, 14.6.2.1,
					 14.6.2.2, 14.6.2.3, 14.6.3, 14.6.3.2, 14.6.4, 14.6.4.1, 14.6.4.1.1, 14.6.4.1.2,
					 14.6.4.1.3, 14.6.4.1.4, 14.6.4.1.5, 14.6.4.1.6, 14.6.4.1.7, 14.6.4.1.8,
					 14.6.4.2, 14.6.4.2.1, 14.6.4.2.2, 14.6.4.3, 14.6.4.4, 14.6.4.5, 14.6.4.6,
					 14.6.4.7, 14.6.4.8, 14.7, 14.7.1, 14.7.2, 14.7.3, 14.7.4, 14.8.1.2, 14.8.2.3,
					 14.9.1.5, 14.10.1.1.4, 14.10.1.2, 14.10.1.3.2, 14.10.1.3.3, 14.10.1.3.4,
					 14.10.1.3.5, 14.10.1.3.6, 14.10.1.3.7, 14.10.1.4, 14.10.1.4.1, 14.10.1.4.2,
					 14.10.1.5, 14.10.1.6, 14.10.2.1, 14.10.3, 14.10.3.1, 14.10.3.2, 14.10.3.3,
					 14.10.3.4, 14.10.4, 14.10.4.1, 14.10.4.1.1, 14.10.4.1.2, 14.10.4.1.3,
					 14.10.4.1.4, 14.10.4.2, 14.10.4.2.1, 14.10.4.2.2, 14.10.4.2.3, 14.10.4.3,
					 14.10.4.4, 14.10.4.5, 14.10.4.6, 14.10.4.7, 14.10.4.8, 14.10.4.9, 14.11.1.2,
					 14.11.1.3, 14.11.1.4, 14.11.2, 14.11.2.1, 14.11.2.2, 14.11.2.3, 14.11.2.4,
					 14.11.2.5, 14.11.2.6, 14.11.2.7, 14.12.1.1, 14.13.1.1, 14.13.1.2, 14.14.1.1,
					 14.14.1.5.2, 14.14.1.6, 14.14.1.7 and 14.15.1 of chapter 14 of the code are
					 deleted and sections 14.1, 14.5.1.2, 14.5.3.2, 14.5.3.3.1, 14.5.3.3.3,
					 14.8.3.3.1, 14.10.1.1.3, 14.10.1.2.1, 14.14.4 and 14.14.6.5.1.2 of chapter 14
					 of the code are amended to read as follows:
14.1 Application. Means of egress in existing
				  buildings shall comply with this code and NFPA 101, life safety code.
14.2 Deleted.
14.3.1 Deleted.
14.5.1.1.1 Deleted.
14.5.1.1.3 Deleted.
14.5.1.1.4 Deleted.
14.5.1.1.6 Deleted.
14.5.1.2 Doors required to be of the
				  side-hinged or pivoted-swinging type shall swing in the direction of egress
				  travel where serving a room or area with an occupant load of 50 or
				  more.
14.5.1.4 Deleted.
14.5.1.5.4 Deleted.
14.5.2.3 Deleted.
14.5.2.6 Deleted.
14.5.2.7 Deleted.
14.5.2.7.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1664 - Planned building groups

Current through Vol. 24-12, July 15, 2024
Rule 14 Sections
					 15.1,
					 15.1.1,
					 15.1.2, 15.2 and 15.3 of chapter 15 of the code are deleted to read as
					 follows:
15.1 Deleted.
15.1.1 Deleted.
15.1.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1665 - Safeguards during building construction, alteration, and demolition operations

Current through Vol. 24-12, July 15, 2024
Rule 15. Sections 16.2.2.2, 16.2.3.1.2, 16.3.4.5.4,
					 16.3.4.5.5, 16.4.2, 16.4.2.1, 16.4.2.2, 16.4.2.3, 16.4.2.4, 16.6.1, 16.8,
					 16.8.1, 16.8.2, 16.8.3, 16.8.3.1 and 16.8.3.2 of chapter 16 of the code are
					 deleted to read as follows:
16.2.2.2
				  Deleted.
16.2.3.1.2
				  Deleted.
16.3.4.5.4
				  Deleted.
16.3.4.5.5
				  Deleted.
16.4.2 Deleted.
16.4.2.1 Deleted.
16.4.2.2 Deleted.
16.4.2.3 Deleted.
16.4.2.4 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1666 - Wildland urban interface

Current through Vol. 24-12, July 15, 2024
Rule 16. Sections
					 17.1,
					 17.2,
					 17.3,
					 17.3.1,
					 17.3.2, 17.3.3, 17.3.3.1, 17.3.3.2, 17.3.3.3, 17.3.4, 17.3.4.1, 17.3.4.2,
					 17.3.4.2.1, 17.3.4.2.2, 17.3.4.3, 17.3.4.4, 17.3.4.5, 17.3.4.6, 17.3.4.6.1,
					 17.3.4.6.2, 17.3.4.7, 17.3.4.7.1, 17.3.4.7.2, 17.3.4.8, 17.3.4.8.1, 17.3.4.8.2,
					 17.3.4.8.3, 17.3.4.9,17.3.5, 17.3.5.1, 17.3.5.1.1, 17.3.5.1.2, 17.3.5.1.3,
					 17.3.5.1.3.1, 17.3.5.1.3.2, 17.3.5.1.4, 17.3.5.1.4.1, 17.3.5.1.4.2, 17.3.5.1.5,
					 17.3.5.2, 17.3.5.2.1, 17.3.5.2.2, 17.3.5.3, 17.3.6, 17.3.7, 17.3.7.1, 17.3.7.2,
					 17.3.7.3, 17.3.7.4, 17.3.8 and 17.3.9 of chapter 17 of the code are deleted to
					 read as follows:
17.1
				  Deleted.
17.2 Deleted.
17.3 Deleted.
17.3.1 Deleted.
17.3.2 Deleted.
17.3.3 Deleted.
17.3.3.1 Deleted.
17.3.3.2 Deleted.
17.3.3.3 Deleted.
17.3.4 Deleted.
17.3.4.1 Deleted.
17.3.4.2 Deleted.
17.3.4.2.1 Deleted.
17.3.4.2.2 Deleted.
17.3.4.3 Deleted.
17.3.4.4 Deleted.
17.3.4.5 Deleted.
17.3.4.6 Deleted.
17.3.4.6.1 Deleted.
17.3.4.6.2 Deleted.
17.3.4.7 Deleted.
17.3.4.7.1 Deleted.
17.3.4.7.2 Deleted.
17.3.4.8 Deleted.
17.3.4.8.1 Deleted.
17.3.4.8.2 Deleted.
17.3.4.8.3 Deleted.
17.3.4.9 Deleted.
17.3.5 Deleted.
17.3.5.1 Deleted.
17.3.5.1.1 Deleted.
17.3.5.1.2 Deleted.
17.3.5.1.3 Deleted.
17.3.5.1.3.1 Deleted.
17.3.5.1.3.2 Deleted.
17.3.5.1.4 Deleted.
17.3.5.1.4.1 Deleted.
17.3.5.1.4.2 Deleted.
17.3.5.1.5 Deleted.
17.3.5.2 Deleted.
17.3.5.2.1 Deleted.
17.3.5.2.2 Deleted.
17.3.5.3 Deleted.
17.3.6 Deleted.
17.3.7 Deleted.
17.3.7.1 Deleted.
17.3.7.2 Deleted.
17.3.7.3 Deleted.
17.3.7.4 Deleted.
17.3.8 Deleted.
17.3.9 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1667 - Fire department access and water supply

Current through Vol. 24-12, July 15, 2024
Rule 17. Sections 18.1.1, 18.1.1.1, 18.1.1.2, 18.2.3.1.1,
					 18.2.3.1.3, 18.2.3.1.4, 18.2.3.2, 18.2.3.2.1, 18.2.3.2.1.1, 18.2.3.2.2,
					 18.2.3.2.2.1, 18.2.3.3, 18.2.3.4, 18.2.3.4.1, 18.2.3.4.1.1, 18.2.3.4.1.2,
					 18.2.3.4.1.2.1, 18.2.3.4.1.2.2, 18.2.3.4.4, 18.2.3.4.6.2, 18.2.3.4.6.3,
					 18.2.3.4.7,18.2.4.1.2, 18.3.1, 18.3.2 and 18.3.3 of chapter 18 of the code are
					 deleted to read as follows:
18.1.1
				  Deleted.
18.1.1.1 Deleted.
18.1.1.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1668 - Combustible waste and refuse

Current through Vol. 24-12, July 15, 2024
Rule 18. Section 19.1.1 of chapter 19 of the code is
					 deleted to read as follows: 19.1.1 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1670 - Aircraft hangers

Current through Vol. 24-12, July 15, 2024
Rule 20. Sections 21.1.1, 21.2.2.1, 21.2.3.1,
				  21.2.3.3, 21.2.3.4, 21.2.3.5, 21.2.3.5.1, 21.2.3.5.2, 21.2.3.5.3, 21.2.3.5.3.1,
				  21.2.3.5.3.1.1, 21.2.3.5.3.1.2, 21.2.3.5.3.1.3, 21.2.3.5.3.2, 21.2.4, 21.2.4.1,
				  21.2.4.2, 21.2.4.3, 21.2.4.4, 21.2.5, 21.2.6, 21.2.6.1, 21.2.6.2, 21.2.6.2.1,
				  21.2.6.2.2, 21.2.6.2.3, 21.2.6.2.4, 21.2.6.3, 21.2.6.3.1, 21.2.6.3.2,
				  21.2.6.3.3, 21.2.6.4, 21.2.6.5, 21.2.6.5.1, 21.2.6.5.2, 21.3, 21.3.1, 21.3.1.1,
				  21.3.1.2, 21.3.2, 21.3.2.1, 21.3.3.1, 21.3.3.4, 21.3.3.6, 21.3.3.6.1,
				  21.3.3.6.2, 21.3.4, 21.3.4.1, 21.3.4.2, 21.3.4.3, 21.3.4.4, 21.3.4.4.1,
				  21.3.4.4.2, 21.3.5, 21.3.6, 21.3.6.1, 21.3.6.2, 21.3.6.3, 21.3.6.4, 21.3.6.4.1,
				  21.3.6.4.2, 21.3.6.4.3, 21.3.6.5, 21.3.6.6, 21.3.6.7, 21.3.6.8 and 21.3.6.9 of
				  chapter 21 of the code are deleted and sections 21.1, 21.3.3.2.1 and 21.3.3.2.3
				  of chapter 21 of the code are amended to read as follows:
21.1 Hangars. The protection of aircraft
				  hangars from fire shall comply with this section; NFPA 409, standard on
				  aircraft hangars; NFPA 410, standard on aircraft maintenance; and section 40.6
				  and section
				  42.6
				  of NFPA 101 as they relate to operation and maintenance.
21.1.1 Deleted.
21.2.2.1 Deleted.
21.2.3.1 Deleted.
21.2.3.3 Deleted.
21.2.3.4 Deleted.
21.2.3.5 Deleted.
21.2.3.5.1 Deleted.
21.2.3.5.2 Deleted.
21.2.3.5.3 Deleted.
21.2.3.5.3.1 Deleted.
21.2.3.5.3.1.1 Deleted.
21.2.3.5.3.1.2 Deleted.
21.2.3.5.3.1.3 Deleted.
21.2.3.5.3.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1671 - Motor vehicle fluids; hazardous materials

Current through Vol. 24-12, July 15, 2024
Rule 21. Sections 22.2 and 22.8 of chapter 22 of the code
					 are deleted and sections 22.9.1 and 22.9.2.3 of chapter 22 of the code are
					 amended to read as follows:
22.2
				  Deleted.
22.8 Deleted.
22.9.1 General. The storage, use, and
				  handling of motor vehicle fluids and hazardous materials shall be in accordance
				  with rules promulgated under the act.
22.9.2.3 Flammable and combustible liquids
				  shall be stored and handled in accordance with rules promulgated under the
				  act.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1672 - Semiconductor facilities

Current through Vol. 24-12, July 15, 2024
Rule 22. Section 23.3 of the code is deleted and section
					 23.1 of chapter 23 of the code is amended to read as follows:
23.1 General. All semiconductor facilities
				  containing a clean room or a clean zone, or both, shall comply with NFPA 318,
				  standard for the protection of semiconductor fabrication facilities, and
				  chapter 23 as they relate to operation and maintenance.
23.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1673 - Drycleaning plants

Current through Vol. 24-12, July 15, 2024
Rule 23. Section
					 24.2
					 of chapter 24 of the code is deleted and section
					 24.1.1
					 of chapter 24 of the code is amended to read as follows:
24.1.1 Drycleaning plants shall comply with
				  NFPA 32, standard for drycleaning plants, and this chapter as they relate to
				  operation and maintenance.
24.2
				  Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1674 - Grandstands; bleachers; folding and telescopic seating; tents; membrane structures

Current through Vol. 24-12, July 15, 2024
Rule 24. Sections 25.1.2, 25.1.6.1, 25.1.6.2, 25.1.10.1.4,
					 25.3.1, 25.3.1.1, 25.3.1.2, 25.3.1.3, 25.3.1.4, 25.3.1.5, 25.3.2, 25.3.2.1,
					 25.3.2.2, 25.3.2.3, 25.3.2.4, 25.3.2.5, 25.3.2.6, 25.3.3.3, 25.3.3.4, 25.3.3.5,
					 25.3.5, 25.3.5.1, 25.3.5.2, 25.3.5.3, 25.3.5.4, 25.3.5.5, 25.3.5.6, 25.3.5.7,
					 25.3.5.8, 25.3.6.2, 25.3.6.3, 25.4, 25.4.1, 25.4.1.1, 25.4.1.2, 25.4.1.3,
					 25.4.1.4, 25.4.1.5, 25.4.2, 25.4.2.1, 25.4.2.2, 25.4.2.3, 25.4.2.4, 25.4.2.5,
					 25.4.2.6, 25.4.2.7, 25.4.2.8, 25.5.1.1, 25.5.1.2, 25.5.1.3, 25.5.1.4, 25.5.2,
					 25.5.2.1, 25.5.2.2, 25.5.2.3, 25.5.2.4, 25.6.1.3, 25.6.4, 25.6.4.1, 25.6.4.2,
					 25.6.4.3 and 25.6.4.4 of chapter 25 of the code are deleted and sections
					 25.1.1, 25.1.4.1, 25.3.4 and 25.4.3.2 of chapter 25 of the code are amended to
					 read as follows:
25.1.1 The location,
				  protection, and maintenance of grandstands and bleachers, folding and
				  telescopic seating, tents, and membrane structures shall meet the requirements
				  of this chapter. Seating facilities located in the open air or within enclosed
				  or semi-enclosed structures, such as tents, membrane structures, and stadium
				  complexes, shall comply with NFPA 101, NFPA 102, standard for grandstands,
				  folding and telescopic seating, tents, and membrane structures, and chapter 25
				  as they related to operation and maintenance.
25.1.2 Deleted.
25.1.4.1 Storage and handling of flammable
				  liquids or gases shall be in accordance with the rules promulgated under the
				  act.
25.1.6.1 Deleted.
25.1.6.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1675 - Fire protection for laboratories using chemicals

Current through Vol. 24-12, July 15, 2024
Rule 25. Sections
					 26.2
					 and
					 26.3
					 of chapter 26 of the code are deleted and section
					 26.1.1
					 of chapter 26 of the code is amended to read as follows:
26.1.1 The handling or storage of chemicals
				  in laboratory buildings, laboratory units, and laboratory work areas whether
				  located above or below grade shall comply with chapter 26 and NFPA 45, standard
				  on fire protection for laboratories using chemicals as they relate to operation
				  and maintenance.
26.2
				  Deleted.
26.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1676 - Manufactured homes; recreational vehicle sites

Current through Vol. 24-12, July 15, 2024
Rule 26. Sections 27.1, 27.1.1, 27.1.2, 27.2, 27.2.1 and
					 27.2.2 of chapter 27 of the code are deleted to read as follows:
27.1 Deleted.
27.1.1 Deleted.
27.1.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1677 - Operation of marinas; boatyards; yacht clubs; boat condominiums; docking facilities associated with residential condominiums; multiple-docking facilities at multi-family residences; all associated piers, docks, and floats

Current through Vol. 24-12, July 15, 2024
Rule 27. Sections
					 28.1.6.2.1.1,
					 28.1.6.2.1.2,
					 28.1.6.2.1.3, 28.1.6.2.2, 28.1.6.2.2.1, 28.1.6.2.2.2, 28.1.6.2.3, 28.1.6.2.3.1,
					 28.1.6.2.3.2, 28.1.6.2.3.3, 28.1.6.2.3.4, 28.1.6.2.4, 28.1.6.3, 28.1.6.3.1,
					 28.1.6.3.2, 28.1.6.3.3, 28.1.6.3.4, 28.1.6.3.5, 28.1.6.3.6, 28.1.6.4, 28.1.6.5,
					 28.1.6.5.1, 28.1.6.5.2, 28.1.8.1.8.2, 28.1.8.1.8.3, 28.2.1 and 28.2.3 of
					 chapter 28 of the code are deleted and section 28.1.1 of chapter 28 of the code
					 is amended to read as follows:
28.1.1
				  The operation of marinas, boatyards, yacht clubs, boat condominiums, docking
				  facilities associated with residential condominiums, multiple-docking
				  facilities at multiple-family residences, and all associated piers, docks, and
				  floats shall comply with NFPA 303, fire protection standard for marinas and
				  boatyards, and section
				  28.1as
				  they relate to operation and maintenance.
28.1.6.2.1.1 Deleted.
28.1.6.2.1.2 Deleted.
28.1.6.2.1.3 Deleted.
28.1.6.2.2 Deleted.
28.1.6.2.2.1 Deleted.
28.1.6.2.2.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1678 - Standards for parking garages

Current through Vol. 24-12, July 15, 2024
Rule 28. Section
					 29.1.1 of
					 chapter 29 of the code is amended to read as follows: 29.1.1 The protection of
					 existing parking garages as well as the control of hazards in open parking
					 structures, enclosed parking structures, and basement and underground parking
					 structures shall comply with section
					 42.8
					 of NFPA 101, NFPA 88A, standard for parking structures, and this chapter as
					 they apply to operation and maintenance.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1679 - Motor fuel dispensing facilities; repair garages

Current through Vol. 24-12, July 15, 2024
Rule 29. Sections 30.1.1.3, 30.1.3, 30.1.4, 30.1.6,
					 30.1.6.1, 30.1.6.2, 30.1.6.3, 30.1.6.4, 30.1.6.5, 30.1.6.6, 30.1.6.7, 30.1.6.8,
					 30.1.6.9, 30.2.1.1, 30.2.3, 30.2.4, 30.2.5, 30.2.5.1, 30.2.5.2, 30.2.6,
					 30.2.6.1, 30.2.6.2, 30.2.6.3, 30.2.6.4, 30.2.7, 30.2.8, 30.2.8.1, 30.2.8.2,
					 30.2.8.3, 30.2.8.4, 30.2.9.3, 30.2.9.4, 30.2.9.5, 30.2.9.6, 30.3.1, 30.3.1.1,
					 30.3.1.2, 30.3.2.3, 30.3.2.4 and 30.3.2.4.1 of chapter 30 of the code are
					 deleted and sections 30.1.1.1, 30.2.1 and 30.2.9.2 of chapter 30 of the code
					 are amended to read as follows:
30.1.1.1 Motor fuel dispensing facilities,
				  marine/motor fuel dispensing facilities, motor fuel dispensing facilities
				  located inside buildings, and fleet vehicle motor fuel dispensing facilities
				  shall comply with NFPA 30A, code for motor fuel dispensing facilities and
				  repair garages, section 30.1, and section 30.3as they relate to operation and
				  maintenance.
30.1.1.3
				  Deleted.
30.1.3 Deleted.
30.1.4 Deleted.
30.1.6 Deleted.
30.1.6.1 Deleted.
30.1.6.2 Deleted.
30.1.6.3 Deleted.
30.1.6.4 Deleted.
30.1.6.5 Deleted.
30.1.6.6 Deleted.
30.1.6.7 Deleted.
30.1.6.8 Deleted.
30.1.6.9 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1680 - Forest products

Current through Vol. 24-12, July 15, 2024
Rule 30. Sections
					 31.2,
					 31.3.3.2.2,
					 31.3.4.3.1, 31.3.7.4, 31.3.7.4.1 and 31.3.7.4.2 of chapter 31 of the code are
					 deleted and section
					 31.1
					 of chapter 31 of the code is amended to read as follows:
31.1 General. The storage, manufacturing, and
				  processing of timber, lumber, plywood, veneers, and by-products shall be in
				  accordance with this chapter and NFPA 664, standard for the prevention of fires
				  and explosions in wood processing and woodworking facilities as they relate to
				  operation and maintenance.
31.2
				  Deleted.
31.3.3.2.2
				  Deleted.
31.3.4.3.1
				  Deleted.
31.3.7.4 Deleted.
31.3.7.4.1 Deleted.
31.3.7.4.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1681 - Motion picture and television production studio soundstages and approved production facilities

Current through Vol. 24-12, July 15, 2024
Rule 31. Sections 32.2, 32.4.1, 32.4.1.1, 32.4.1.2,
					 32.4.1.3, 32.4.1.3.1, 32.4.1.3.2, and 32.4.1.4 of chapter 32 of the code are
					 deleted and section 32.1 of chapter 32 of the code is amended to read as
					 follows:
32.1 General. The operation
				  and maintenance of soundstages and approved production facilities used in
				  motion picture and television industry productions shall comply with NFPA 140,
				  standard on picture and television production studio soundstages and approved
				  production facilities, and chapter 32 as they relate to operation and
				  maintenance.
32.2
				  Deleted.
32.4.1 Deleted.
32.4.1.1 Deleted.
32.4.1.2 Deleted.
32.4.1.3 Deleted.
32.4.1.3.1 Deleted.
32.4.1.3.2 Deleted.
32.4.1.4 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1682 - Outside storage of tires

Current through Vol. 24-12, July 15, 2024
Rule 32. Sections
					 33.1.2,
					 33.2.1, 33.2.1.1, 33.2.1.2, 33.2.1.3, 33.3.2 and 33.3.4 of chapter 33 of the
					 code are deleted and section 33.3.1 of chapter 33 of the code is amended to
					 read as follows:
33.1.2
				  Deleted.
33.2.1 Deleted.
33.2.1.1 Deleted.
33.2.1.2 Deleted.
33.2.1.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1683 - General storage

Current through Vol. 24-12, July 15, 2024
Rule 33. Sections 34.1.2, 34.3, 34.3.1, 34.3.2, 34.3.3,
					 34.3.3.1, 34.3.3.2, 34.3.3.3, 34.5.1, 34.5.2, 34.5.2.1, 34.5.2.2, 34.5.2.3,
					 34.5.2.4, 34.5.2.5, 34.5.3.2, 34.5.5, 34.5.5.1, 34.5.5.1.1, 34.5.5.1.2,
					 34.5.5.2, 34.7.2, 34.7.2.1, 34.7.2.2, 34.7.2.3, 34.7.3.4.1, 34.7.3.4.1.1,
					 34.7.3.4.1.2, 34.7.3.4.1.3, 34.7.3.4.2, 34.7.3.4.2.1, 34.7.3.4.2.2, 34.8,
					 34.8.1, 34.8.1.1, 34.8.1.2, 34.8.1.3, 34.8.2, 34.8.2.1, 34.8.2.2, 34.8.2.2.1,
					 34.8.2.2.2, 34.8.2.3, 34.8.3, 34.8.3.1, 34.8.3.1.1, 34.8.3.1.2, 34.8.3.1.3,
					 34.8.3.1.4, 34.8.3.2, 34.8.3.2.1, 34.8.3.2.2, 34.8.3.2.3, 34.9, 34.9.1, 34.9.2
					 and 34.9.3 of chapter 34 of the code are deleted and section 34.4.4.2 of
					 chapter 34 of the code is amended to read as follows:
34.1.2 Deleted.
34.3 Deleted.
34.3.1 Deleted.
34.3.2 Deleted.
34.3.3 Deleted.
34.3.3.1 Deleted.
34.3.3.2 Deleted.
34.3.3.3 Deleted.
34.4.4.2 Protection shall be in accordance
				  with rules promulgated under the act.
34.5.1 Deleted.
34.5.2 Deleted.
34.5.2.1 Deleted.
34.5.2.2 Deleted.
34.5.2.3 Deleted.
34.5.2.4 Deleted.
34.5.2.5 Deleted.
34.5.3.2 Deleted.
34.5.5 Deleted.
34.5.5.1 Deleted.
34.5.5.1.1 Deleted.
34.5.5.1.2 Deleted.
34.5.5.2 Deleted.
34.7.2 Deleted.
34.7.2.1 Deleted.
34.7.2.2 Deleted.
34.7.2.3 Deleted.
34.7.3.4.1 Deleted.
34.7.3.4.1.1 Deleted.
34.7.3.4.1.2 Deleted.
34.7.3.4.1.3 Deleted.
34.7.3.4.2 Deleted.
34.7.3.4.2.1 Deleted.
34.7.3.4.2.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1684 - Dust explosion prevention

Current through Vol. 24-12, July 15, 2024
Rule 34. Section 40.2 of chapter 40 of the code is deleted
					 and section 40.1 of chapter 40 of the code is amended to read as
					 follows:
40.1 General. Equipment,
				  processes, and operations that involve the manufacture, processing, blending,
				  repackaging, or handling of combustible particulate solids or combustible dusts
				  regardless of concentration or particle size shall be maintained in accordance
				  with the following standards as they relate to operation and
				  maintenance:
(1) NFPA 61, standard
				  for the prevention of fires and dust explosions in agricultural and food
				  processing facilities.
(2) NFPA 69,
				  standard on explosion prevention systems.
(3) NFPA 85, boiler and combustion systems
				  hazards code.
(4) NFPA 120,
				  standard for fire prevention and control in coal mines.
(5) NFPA 484, standard for combustible
				  metals.
(6) NFPA 654, standard for
				  the prevention of fire and dust explosions from the manufacturing, processing,
				  and handling of combustible particulate solids.
(7) NFPA 655, Standard for Prevention of
				  Sulfur Fires and Explosions
(8)
				  NFPA 664, standard for the prevention of fires and explosions in wood
				  processing and woodworking facilities.
40.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1685 - Hot work operations

Current through Vol. 24-12, July 15, 2024
Rule 35. Sections
					 41.1.5,
					 41.1.5.1 and
					 41.1.5.2 of chapter 41 of the code are deleted and sections 41.1.1 and 41.6.1
					 of chapter 41 of the code are amended to read as follows:
41.1.1 Hot work shall comply with NFPA 51B,
				  standard for fire prevention during welding, cutting, and other hot work, and
				  this chapter as they relate to operation and maintenance.
41.1.5 Deleted.
41.1.5.1 Deleted.
41.1.5.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1687 - Spraying, dipping, and coating using flammable or combustible materials

Current through Vol. 24-12, July 15, 2024
Rule 37. Sections 43.1.1.4, 43.1.2.2, 43.1.3, 43.1.3.1,
					 43.1.3.1.1, 43.1.3.1.2, 43.1.3.1.3, 43.1.3.1.4, 43.1.3.1.5, 43.1.3.1.6,
					 43.1.3.1.7, 43.1.3.1.8, 43.1.3.2, 43.1.3.3, 43.1.3.3.1, 43.1.3.3.2, 43.1.3.5,
					 43.1.4.1.1, 43.1.4.1.2, 43.1.4.1.3, 43.1.4.1.4, 43.1.4.2, 43.1.4.2.1,
					 43.1.4.2.1.1, 43.1.4.2.1.2, 43.1.4.2.1.3, 43.1.4.2.1.4, 43.1.4.2.1.5,
					 43.1.4.2.2, 43.1.4.2.2.1, 43.1.4.2.2.2, 43.1.4.3, 43.1.4.3.1, 43.1.4.3.2,
					 43.1.4.4, 43.1.4.4.1, 43.1.4.4.2, 43.1.4.4.2.1, 43.1.4.4.2.2, 43.1.4.4.3,
					 43.1.4.4.4, 43.1.4.4.5, 43.1.4.4.5.1, 43.1.4.4.5.2, 43.1.4.5, 43.1.4.5.1,
					 43.1.4.5.2, 43.1.4.5.3, 43.1.5.1, 43.1.5.2, 43.1.5.4, 43.1.5.5, 43.1.5.5.1,
					 43.1.5.5.2, 43.1.5.6, 43.1.5.7, 43.1.5.8, 43.1.5.8.1, 43.1.5.8.2, 43.1.5.8.3,
					 43.1.5.8.4, 43.1.5.9, 43.1.5.10, 43.1.5.10.1, 43.1.5.10.2, 43.1.5.10.3, 43.1.6,
					 43.1.6.1, 43.1.6.2, 43.1.6.2.1, 43.1.6.2.2, 43.1.6.2.3, 43.1.6.3, 43.1.6.3.1,
					 43.1.6.3.2, 43.1.6.3.3, 43.1.6.3.4, 43.1.6.3.5, 43.1.6.3.6, 43.1.6.4,
					 43.1.6.4.1, 43.1.6.4.2, 43.1.6.4.3, 43.1.6.4.4, 43.1.6.4.5, 43.1.6.4.6,
					 43.1.6.5, 43.1.6.5.1, 43.1.6.5.2, 43.1.6.5.3, 43.1.6.5.4, 43.1.6.5.5,
					 43.1.6.5.6, 43.1.7, 43.1.7.1, 43.1.7.1.1, 43.1.7.1.2, 43.1.7.2, 43.1.7.2.1,
					 43.1.7.2.1.1, 43.1.7.2.2, 43.1.7.3, 43.1.7.4, 43.1.7.4.1, 43.1.7.4.2,
					 43.1.7.4.3, 43.1.7.4.4, 43.1.7.4.5, 43.1.7.4.6, 43.1.7.4.7, 43.1.7.4.7.1,
					 43.1.7.4.7.2, 43.1.7.5, 43.1.7.7, 43.1.7.7.1, 43.1.7.7.2, 43.1.7.8, 43.1.7.8.1,
					 43.1.7.8.2, 43.1.8.7.3, 43.1.8.7.4, 43.5.3.1, 43.5.3.5, 43.5.3.5.1, 43.5.3.5.2,
					 43.5.3.9, 43.7.2, 43.8.3, 43.8.5.1, 43.8.5.2, 43.8.5.3, 43.8.6, 43.8.6.1 and
					 43.8.6.2 of chapter 43 of the code are deleted and sections 43.1.1, 43.2, 43.3
					 and 43.9.1 of chapter 43 of the code are amended to read as follows:
43.1.1 Operations involving the spray
				  application of flammable and combustible materials shall comply with NFPA 33,
				  standard for spray application using flammable or combustible materials, and
				  section 43.1as they relate to operation and maintenance.
43.1.1.4 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1688 - Solvent extraction

Current through Vol. 24-12, July 15, 2024
Rule 38. Section 44.3 of chapter 44 of the code is deleted
					 and section 44.1 of chapter 44 of the code is amended to read as
					 follows:
44.1 General. Solvent
				  extraction plants shall comply with NFPA 36, standard for solvent extraction
				  plants, and chapter 44 as they relate to operation and maintenance.
44.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1689 - Combustible fibers

Current through Vol. 24-12, July 15, 2024
Rule 39. Sections
					 45.1.3,
					 45.2, 45.2.1, 45.2.2, 45.5.3, 45.5.3.1, 45.5.3.2, 45.5.4, 45.5.4.1, 45.5.4.2,
					 45.5.4.3, 45.5.4.4, 45.5.4.5, 45.5.5, 45.5.5.1 and 45.5.5.2 of chapter 45 of
					 the code are deleted and section
					 45.1.1 of
					 chapter 45 of the code is amended to read as follows:
45.1.1 The storage, use, and handling of
				  combustible fibers shall comply with the requirements of chapter 45 as they
				  relate to operation and maintenance.
45.1.3 Deleted.
45.2 Deleted.
45.2.1 Deleted.
45.2.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1690 - Commercial cooking equipment

Current through Vol. 24-12, July 15, 2024
Rule 40. Sections 50.1.4, 50.2.1.1.1, 50.2.1.1.2, 50.2.1.6,
					 50.2.2, 50.2.2.1, 50.2.2.2, 50.2.2.3, 50.2.2.3.1, 50.2.2.3.2, 50.2.2.3.3,
					 50.2.3, 50.3.4, 50.4, 50.4.1, 50.4.2, 50.4.3, 50.4.3.1, 50.4.3.2, 50.4.4.4,
					 50.4.4.6, 50.4.4.8, 50.4.4.8.1, 50.4.4.8.2, 50.4.4.8.3, 50.4.4.8.4, 50.4.4.8.5,
					 50.4.4.8.6, 50.4.4.8.7, 50.4.4.9, 50.4.4.10, 50.4.5, 50.4.5.1, 50.4.5.2,
					 50.4.5.3, 50.4.6, 50.4.6.1, 50.4.6.2, 50.4.6.3, 50.4.6.4, 50.4.7, 50.4.7.1,
					 50.4.7.2, 50.4.7.3, 50.4.7.4, 50.4.7.5, 50.4.7.6, 50.4.8, 50.4.8.1, 50.4.8.2,
					 50.4.9, 50.4.9.1, 50.4.9.2, 50.4.9.3, 50.4.9.4, 50.4.10, 50.4.10.1, 50.4.10.2,
					 50.4.11, 50.4.11.1, 50.4.11.2, 50.4.11.2.1, 50.4.11.2.2 and 50.6.2 of chapter
					 50 of the code are deleted and section 50.1.1 of chapter 50 of the code is
					 amended to read as follows:50.1.1 The operation, inspection, and maintenance of
					 all public and private commercial cooking equipment shall comply with this
					 chapter and NFPA 96, standard for ventilation control and fire protection of
					 commercial cooking operations.
50.1.4
				  Deleted.
50.2.1.1.1
				  Deleted.
50.2.1.1.2
				  Deleted.
50.2.1.6
				  Deleted.
50.2.2 Deleted.
50.2.2.1 Deleted.
50.2.2.2 Deleted.
50.2.2.3 Deleted.
50.2.2.3.1 Deleted.
50.2.2.3.2 Deleted.
50.2.2.3.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1691 - Industrial ovens and furnaces

Current through Vol. 24-12, July 15, 2024
Rule 41. Sections 51.1.2, 51.1.2.1, 51.1.2.2 and 51.3 of
					 chapter 51 of the code are deleted and section 51.1.1 of chapter 51 of the code
					 is amended to read as follows:
51.1.1
				  Application. Industrial ovens and furnaces shall comply with this chapter and
				  the applicable provisions of NFPA 86, standard for ovens and furnaces; NFPA
				  86c, standard for industrial furnaces using a special processing atmosphere;
				  and NFPA 86D, standard for industrial furnaces using vacuum as an atmosphere as
				  they relate to operation and maintenance only.
51.1.2 Deleted.
51.1.2.1 Deleted.
51.1.2.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1692 - Ventilation

Current through Vol. 24-12, July 15, 2024
Rule 42. Sections 52.2, 52.2.1, 52.2.2, 52.3.3.3, 52.3.3.4
					 and 52.3.10 of chapter 52 of the code are deleted and section 52.3.6 of chapter
					 52 of the code is amended to read as follows:
52.2 Deleted.
52.2.1 Deleted.
52.2.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1693 - Mechanical refrigeration

Current through Vol. 24-12, July 15, 2024
Rule 43. Sections 53.1, 53.1.1, 53.1.2, 53.2, 53.3, 53.4,
					 53.4.1, 53.4.2, 53.5, 53.5.1, 53.5.2, 53.5.3, 53.6, 53.7, 53.7.1, 53.7.1.1,
					 53.7.1.2, 53.7.1.3, 53.7.2, 53.7.2.1, 53.7.2.1.1, 53.7.2.1.2, 53.7.2.2,
					 53.7.2.2.1, 53.7.2.2.2, 53.8, 53.8.1, 53.8.2, 53.8.2.1, 53.8.2.2, 53.8.2.3,
					 53.8.3, 53.8.3.1, 53.8.3.2, 53.8.3.3, 53.8.4, 53.8.4.1, 53.8.4.2, 53.8.4.3,
					 53.8.5, 53.8.5.1, 53.8.5.2, 53.8.5.3, 53.8.5.4, 53.9, 53.9.1, 53.9.2, 53.9.3,
					 53.9.4, 53.9.5, 53.9.6, 53.9.7, 53.9.8, 53.10, 53.10.1, 53.10.2, 53.10.2.1,
					 53.10.2.2, 53.10.3, 53.10.3.1, 53.10.3.2, 53.10.3.3, 53.10.3.4, 53.10.4,
					 53.10.4.1, 53.10.4.2, 53.10.4.3, 53.10.5, 53.10.5.1, 53.10.5.2, 53.10.5.3,
					 53.10.5.4, 53.10.5.5, 53.10.5.6, 53.10.5.7, 53.10.5.8, 53.10.6, 53.10.6.1,
					 53.10.6.2, 53.10.7, 53.10.7.1, 53.10.7.1.1, 53.10.7.1.2, 53.10.7.2, 53.10.8,
					 53.10.8.1, 53.10.8.2, 53.10.9, 53.10.9.1, 53.10.9.2, 53.11, 53.11.1, 53.11.2,
					 53.11.2.1, 53.11.2.2, 53.11.2.3, 53.11.3, 53.11.4, 53.11.5, 53.12, 53.12.1,
					 53.12.2, 53.13, 53.14, 53.14.1, 53.14.2, 53.15, 53.15.1, 53.15.2, 53.15.3,
					 53.15.4, 53.15.5, 53.16, 53.16.1, 53.16.2, 53.17, 53.18, 53.18.1, and 53.19 of
					 chapter 53 of the code are deleted to read as follows:
53.1 Deleted.
53.1.1 Deleted.
53.1.2 Deleted.