Louisiana Administrative Code › Title 17 - CONSTRUCTION › Part I - Uniform Construction Code › Chapter 1 - Adoption of the Louisiana State Uniform Construction Code (Formerly LAC 55:VI.Chapter 3) › Section I-103 - International Building Code (Formerly LAC 55:VI.301.A.1)

Current through Register Vol. 50, No. 6, June 20, 2024
A.
International Building Code
(IBC), 2021 Edition, not
										including Chapter 1, Administration, Chapter 11, Accessibility, Chapter 27, Electrical. The applicable
										standards referenced in that code are included for regulation of construction within this state. Furthermore,
										IBC shall be amended as follows and shall only apply to the
International Building Code
.
Amend
Chapter 2, Definitions.
Mini-Storage Facility- a self-service storage
																		 facility which rents or leases individual storage space to occupants for the storage and/or removal of
																		 personal property.
Amend
Table 509.1
Adopt
Item (18)
Stationary storage battery systems having an energy
																		 capacity greater than the threshold quantity specified in 2021 IFC Table 1207.1.1, shall have a 2 HR
																		 Separation and/or Protection.
Amend
Section 903.2.1 2, Group A-2.
Amend
Item (2.)
Item (2). The fire area has an occupant load of 300
																		 or more.
Adopt
Item (4.)
Item (4). Open-air pavilions on three sides or more,
																		 not exceeding 12,000 square feet, shall not be required to comply with 903.2.1.2(1) and 903.2.1.2(2) where
																		 each side has unobstructed access to a public way (10'-0" wide by 10'-0") 'high). No fixed elements,
																		 equipment, seating, etc. are permitted within the 10'-0" by 10'-0" access.
Adopt
Exceptions
(a). The requirements of Sections 903.2.1.2(1) shall
																		 not apply to a single multipurpose room less than 12,000 sf when all of the following conditions are
																		 met.
(1.) The single multi-purpose room shall not be used
																		 for display or exhibition, bars or taverns.
(2.) The single multi-purpose room shall not share
																		 exit access with other occupancies. Non-separated accessory uses that are incidental or ancillary to the
																		 single multi-purpose room shall be considered as part of the assembly occupancy. The accessory uses shall not
																		 be limited to 10 percent of the single multi-purpose room floor area and/or building, but shall be included
																		 and considered as part of the limited assembly room floor area.
(3.) The single multi-purpose room shall not be part
																		 of a fire area containing other assembly occupancies.
(4.) A single multi-purpose room with an occupant
																		 load greater than 300 persons shall be provided with a fire alarm system in accordance with Section
																		 907.2 1
(5.) The single multi-purpose room with its accessory
																		 or ancillary uses shall be separated, when part of a multiple occupancy, in accordance with Table 508.4 and
																		 Section 707 from the remainder of the building. The single multi-purpose room fire area containing the single
																		 multi-purpose room and its accessory or ancillary uses shall be less than 12,000 sf.
(6.) Provide system smoke detection in all areas in
																		 accordance with Section 907 throughout the entire building.
Amend
Section 903.2.1 3, Group A-3.
Adopt
Item (4.)
4. Open air pavilions on three sides or more, not
																		 exceeding 12,000 square feet, shall not be required to comply with Section 903.2.1.3(2) where each side has
																		 unobstructed access to a public way (10'-0" wide by 10'-0" high). No fixed elements, equipment, seating, etc.
																		 are permitted within the 10'-0" by 10'-0" access.
Adopt
Exceptions
(a). The requirements of Sections 903.2.1.3(1) shall
																		 not apply to a single multipurpose room less than 12,000 sf when all of the following conditions are
																		 met:
(1.) The single multi-purpose room shall not be used
																		 for display or exhibition.
(2.) The single multi-purpose room shall not share
																		 exit access with other occupancies. Non-separated accessory uses that are incidental or ancillary to the
																		 single multi-purpose room shall be considered as part of the assembly occupancy. The accessory uses shall not
																		 be limited to 10 percent of the single multi-purpose room floor area and/or building, but shall be included
																		 and considered as part of the limited assembly room floor area.
(3.) The single multi-purpose room shall not be part
																		 of a fire area containing other assembly occupancies.
(4.) A single multi-purpose room with an occupant
																		 load greater than 300 persons shall be provided with a fire alarm system in accordance with Section
																		 907.2 1
(5.) The single multi-purpose room with its accessory
																		 or ancillary uses shall be separated, when part of a multiple occupancy, in accordance with Table 508.4 and
																		 Section 707 from the remainder of the building. The single multi- purpose room fire area containing the
																		 single multi-purpose room and its accessory or ancillary uses shall be less than 12,000 sf.
(6.) Provide system smoke detection in all areas in
																		 accordance with Section 907 throughout the entire building.
Amend
Section 903.2.9 4, Group S-1.
Amend
Exception
Adopt
Item (2)
(2.) The requirement of Section 903.2.9.4 shall not
																		 apply to mini-storage facilities less than 12,000 sf. Mini-storage facilities, including mini-storage
																		 facilities which are climate-controlled, shall comply with 903.2.9(1) thru 903.2.9(4).
Amend
Section 903.2 8, Group R.
Adopt
Exceptions
(a). An automatic sprinkler system is not required
																		 when not more than two dwelling or sleeping units are attached to a commercial or non-residential occupancy
																		 where all of the following conditions exist: (1.) The dwelling or sleeping units shall be separated
																		 vertically and/or horizontally from the non-residential occupancy as well as each other by two-hour
																		 construction in accordance with Sections 707
(2.) Provide system smoke detection in all areas in
																		 accordance with Section 907 throughout the entire building.
(3.) Egress from the dwelling or sleeping units shall
																		 not pass through the non-residential occupancy.
(4.) The building shall not exceed two
																		 stories.
Adopt
(b.) An automatic sprinkler system is not required in
																		 Residential Group R-3, boarding houses (transient and nontransient) as defined by Section 310 5, where one of
																		 the following conditions exist:
(1.) Every sleeping room has a door opening directly
																		 to the exterior at the street or finish grade.
(2.) Every sleeping room has a door opening directly
																		 to the exterior which leads to an outside stair protected in accordance with Section 1027
Amend
Section 1010.2 4, Locks and
																		 Latches.
Amend
Item (2.)
Electric locking systems, including electromechanical
																		 locking systems and electromagnetic locking systems, shall be permitted to be locked in the means of egress
																		 in Group I-1 or I-2 occupancies where persons receiving care require their containment. Controlled egress
																		 doors shall be permitted in such occupancies where the building is equipped throughout with an automatic
																		 sprinkler system in accordance with Section 903.3.1.1 or an approved automatic smoke or heat detection system
																		 installed in accordance with Section 907, provided that the doors are installed and operate in accordance
																		 with all of the following:
(a.) The door locks shall unlock on actuation of the
																		 automatic sprinkler system or automatic fire detection system.
(b.) The door locks shall unlock on loss of power
																		 controlling the lock or lock mechanism.
(c.) The door locking system shall be installed to
																		 have the capability of being unlocked by a switch located at the fire command center, a nursing station or
																		 other approved location. The switch shall directly break power to the lock.
(d.) A means of manual mechanical unlocking must be
																		 provided at each door that is not in direct view of the remote release location required by Item c.
(e.) The procedures for unlocking the doors shall be
																		 described and approved as part of the emergency planning and preparedness required by Chapter 4 of the
																		 International Fire Code.
(f.) All clinical staff shall have the keys, codes or
																		 other means necessary to operate the locking systems.
(g.) Emergency lighting shall be provided at the
																		 door.
(h.) The door locking system units shall be listed in
																		 accordance with UL 294.
(i.) "Automatic" Re-Locking, after an emergency
																		 release as described above, shall be prohibited. A specific human action dedicated for re-locking doors must
																		 be provided at the remote control location or at each lock location.
(j.) Document the "staff/patient ratio" for the
																		 occupants of the locked area to the authority having jurisdiction. The ratio shall be within state and
																		 federal licensing/certification guidelines. Please note that only "nurses" and "nurses' aides" assigned to
																		 the locked area shall be considered acceptable responsible staff in regard to this ratio
																		 documentation.
(k.) Provide the reason for installing specialized
																		 security measures to the authority having jurisdiction.
(l.) Documentation addressing each condition itemized
																		 above shall be provided to the authority having jurisdiction and shall include the signature of the building
																		 owner or the facility administrator.
Amend
Item (3.)
3. In buildings in occupancy Group A having an
																		 occupant load of 500 or less, Groups B and M, the main door or doors are permitted to be equipped with
																		 key-operated locking devices from the egress side provided:
3.1. The locking device is readily distinguishable as
																		 locked.
3.2. A readily visible durable sign is posted on the
																		 egress side on or adjacent to the door stating: THIS DOOR TO REMAIN UNLOCKED WHEN THIS SPACE IS OCCUPIED. The
																		 sign shall be in letters 1 inch (25 mm) high on a contrasting background.
3.3. The use of the key-operated locking device is
																		 revocable by the building official for due cause.
Adopt
Item (3.4)
Doors remain unlocked when the building or space is
																		 occupied
Adopt
Item (3.5)
A key is immediately available to any occupant inside
																		 the building or space when it is locked.
Repeal
Item (8)
Repeal
Item (8.1)
Repeal
Item (8.2)
Repeal
Item (8.3)
Repeal
Item (8.4)
Repeal
Item (8.5)
Repeal
Item (8.6)
Repeal
Exception
Where approved, in Group I occupancies, the
																		 installation of a sign is not required where care recipients who because of clinical needs require restraint
																		 or containment as part of the function of the treatment area.
Amend
(7.) Emergency lighting shall be provided on the
																		 egress side of the door.
(8.) The delayed egress locking system units shall be
																		 listed in accordance with UL 294.
Amend
Section 1010.2 11, Door hardware release of
																		 electrically locked egress doors.
(a.) a. Doors in the required means of egress shall
																		 be permitted to be locked with an electromagnetic locking system where equipped with hardware and where
																		 installed and operated in accordance with all of the following:
(1.) The hardware that is affixed to the door leaf
																		 has an obvious method of operation that is readily operated under all lighting conditions.
(2.) The hardware is capable of being operated with
																		 one hand.
(3.) Operation of the hardware directly interrupts
																		 the power to the electromagnetic lock and unlocks the door immediately.
(4.) Loss of power to the locking system
																		 automatically unlocks the door.
(5.) Where panic or fire exit hardware is required by
																		 Section 1010.1 10, operation of the panic or fire exit hardware also releases the electromagnetic
																		 lock.
(6.) The locking system units shall be listed in
																		 accordance with UL 294.
Adopt
Item (5.)
(5.) The activation of manual fire alarm boxes that
																		 activate the fire alarm system shall not be required to unlock the doors.
Amend
Item (6.)
(6.) Activation of the building automatic sprinkler
																		 system or fire detection system, where provided, shall automatically unlock the doors. The doors shall remain
																		 unlocked until the fire alarm system has been reset.
Amend
Item (7.)
(7.) The door locking system units shall be listed in
																		 accordance with UL 294.
Adopt
Item (8.)
(8.) Doors in buildings with an occupancy in Group A
																		 shall not be secured from the egress side during periods that the building is open to the general
																		 public.
Adopt
Item (9.)
(9.) Doors in buildings with an occupancy in Group
																		 R-3 or Group I-3 shall not be equipped with this locking system.
Adopt
Item (10.)
(10.) Doors serving any Group M occupancy shall be
																		 permitted to be equipped with this locking system in buildings equipped throughout with an automatic
																		 sprinkler system in accordance with Section 903.3.1.1 or an approved automatic smoke or heat detection system
																		 installed in accordance with Section 907
Adopt
Item (11.)
(11.) Emergency egress lighting shall be provided at
																		 the door.
Amend
Section 1010.2 12, Sensor Release of Electrically
																		 Locked Egress Doors.
Adopt
Exception
The activation of manual fire alarm boxes that
																		 activate the building fire-protective signaling system shall not be required to unlock the door
																		 leaves.
Amend
Section 1010.2 13, Delayed Egress.
Delayed egress locking systems shall be permitted to
																		 be installed on doors serving the following occupancies in buildings that are equipped throughout with an
																		 automatic sprinkler system in accordance with Section 903.3.1 or an approved automatic smoke or heat
																		 detection system installed in accordance with Section 907
Amend
Item (3)
Group A, other than the main entrance/exit
																		 doors.
Amend
Section 1010.2 13.1, Delayed Egress Locking
																		 System.
Amend
Item (5.)
The egress path from any point shall not pass through
																		 more than one delayed egress locking system.
Repeal
Exception
Repeal
Item (1.)
Repeal
Item (2.)
Amend
Item (6.)
Repeal
Exception
Amend
Section 1020 2, Construction.
Amend
Exception
Adopt
Item (6.)
(6.) A fire-resistance rating is not required for
																		 corridors where the space or area served does not exceed the occupant load and common path of egress travel
																		 values, for each occupancy, listed in Table 1006.2.1. The travel distance to the exit from the space or area
																		 served shall not exceed the common path of travel.
Amend
Section 1020 6, Air Movement in Corridors.
Corridors that require protection under Table
																		 1020.1-Corridor Fire-Resistance Rating, shall not serve as supply, return, exhaust, relief or ventilation air
																		 ducts.
Amend
Section 1027 6
Amend
Exceptions
Adopt
Item (5)
(4.) Exterior stairs or ramps which serve no more
																		 than one story above the level of exit discharge and constructed with non-combustible materials or
																		 constructed with fire retardant treated lumber, shall be allowed when the fire separation distance is between
																		 5 and 10 feet measured from the exterior edge of the stairway or ramp.
Amend
Section 1031 2
Amend
Exception
Amend
Item (6)
(4.) In other than Group R-3 occupancies, buildings
																		 equipped throughout with an approved automatic sprinkler system in accordance with Section 903.3.1 1
Repeal
Section 1207, Enhanced Classroom Acoustics.
Amend
1507.1.2, Ice barriers.
An ice barrier shall be installed for asphalt
																		 shingles,
metal roof shingles
, mineral-surfaced roll roofing, slate and slate-type shingles,
																		 wood shingles, and wood shakes. The ice barrier shall consist of not less than two layers of
underlayment
cemented together, or a self-adhering polymer modified bitumen sheet shall be
																		 used in place of normal
underlayment
and extend from the lowest edges of all roof surfaces
																		 to a point not less than 24 inches (610 mm) inside the
exterior wall
line of the
																		 building.
Amend
1507.2.7, Ice barrier
Ice barriers shall comply with Section 1507.1 2
Amend
1507.5.4, Ice barrier
Ice barriers shall comply with Section 1507.1 2
Amend
1507.6.4, Ice barrier
Ice barriers shall comply with Section 1507.1 2
Amend
1507.7.4, Ice barrier
Ice barriers shall comply with Section 1507.1 2
Amend
1507.8.4, Ice barrier
Ice barriers shall comply with Section 1507.1 2
Amend
1507.9.4, Ice barrier
Ice barriers shall comply with Section 1507.1 2
Amend
1507.16.4, Ice barrier
Ice barriers shall comply with Section 1507.1 2
Amend
1507.17.4.2, Ice barrier
An ice barrier consisting of not fewer than two
																		 layers of
underlayment
cemented together or of a self-adhering polymer modified bitumen
																		 sheet shall be used instead of normal
underlayment
and extend from the lowest edges of all
																		 roof surfaces to a point not less than 24 inches (610 mm) inside the
exterior wall
line of
																		 the building.
Amend
Section 1603.1 5, Earthquake Design Data.
The following information related to seismic loads
																		 shall be shown, regardless of whether seismic loads govern the design of the lateral-force-resisting system
																		 of the building:
a. seismic importance factor, I, and occupancy
																		 category;
b. mapped spectral response accelerations, SS and
																		 S1;
c. site class;
d. spectral response coefficients, SDS and
																		 SD1;
e. seismic design category;
f. basic seismic-force-resisting system(s);
g. design base shear;
h. seismic response coefficient(s), CS;
i. response modification factor(s), R;
j. analysis procedure used;
Adopt
Exceptions
Adopt
Item (1.)
(1.) Construction documents that are not required to
																		 be prepared by a registered design professional;
Adopt
Item (2.)
(2.) Construction documents for structures that are
																		 assigned to Seismic Design Category A.
Amend
Section 1609 2, Protection of Openings.
In wind-borne debris regions, glazing in buildings
																		 shall be impact resistant or protected with an impactresistant covering meeting the requirements of an
																		 approved impact-resistant standard or ASTM E 1996 and ASTM E 1886 referenced herein as follows:
a. Glazed openings located within 30 feet (9144 mm)
																		 of grade shall meet the requirements of the large missile test of ASTM E 1996.
b. Glazed openings located more than 30 feet (9144
																		 mm) above grade shall meet the provisions of the small missile test of ASTM E 1996.
Amend
Exceptions
Amend
Item (1.)
(1.) Wood structural panels with a minimum thickness
																		 of 7/16 inch (11.1 mm) and maximum panel span of 8 feet (2438 mm) shall be permitted for opening protection
																		 in one- and two-story buildings classified as Risk Category 2. Panels shall be precut so that they shall be
																		 attached to the framing surrounding the opening containing the product with the glazed opening. Panels shall
																		 be predrilled as required for the anchorage method and shall be secured with the attachment hardware
																		 provided. Attachments shall be designed to resist the components and cladding loads determined in accordance
																		 with the provisions of ASCE 7, with corrosion-resistant attachment hardware provided and anchors permanently
																		 installed on the building. Attachment in accordance with Table 1609.1.2 with corrosion resistant attachment
																		 hardware provided and anchors permanently installed on the building is permitted for buildings with a mean
																		 roof height of 45 feet (13 716 mm) or less where
Vasd
determined in
																		 accordance with Section 1609.3.1 does not exceed 140 mph (63 m/s).
Amend
Item (2.)
(2.) Glazing in Risk Category I buildings as defined
																		 in Section 1604 5, including greenhouses that are occupied for growing plants on a production or research
																		 basis, without public access shall be permitted to be unprotected.
Amend
Item (3.)
(3.) Glazing in Risk Category II, III or IV buildings
																		 located over 60 feet (18 288 mm) above the ground and over 30 feet (9144 mm) above aggregate surface roofs
																		 located within 1,500 feet (458 m) of the building shall be permitted to be unprotected.
Amend
Section 1612 42, Design and
																		 Construction.
The design and construction of buildings and
																		 structures located in flood hazard areas, including coastal high hazard areas and coastal A zones, shall be
																		 in accordance with Chapter 5 of ASCE 7 and ASCE 24. The local jurisdictions, utilizing flood plain manager,
																		 shall have the authority to adopt higher freeboard amounts as needed (CRS, etc.) but shall not have the
																		 authority to adopt freeboard amounts less than those required in ASCE-24.
Amend
Section 1613 1, Scope.
Every structure, and portion thereof, including
																		 nonstructural components that are permanently attached to structures and their supports and attachments,
																		 shall be designed and constructed to resist the effects of earthquake motions in accordance with ASCE 7,
																		 excluding Chapter 14 and Appendix 11A. The seismic design category for a structure is permitted to be
																		 determined in accordance with Section
																		 1613 or ASCE 7-10. Figure 1613.5(1) shall be replaced with
																		 ASCE 7-10 Figure 22-1. Figure 1613.5(2) shall be replaced with ASCE 7-10 Figure 22-2.
Repeal
Referenced ASCE 24-14, Freeboard.
Delete Referenced ASCE 24-14 Freeboard requirements
																		 and Table 1-1, Flood Design Class of Buildings and Structures.
Amend
Section 1613 1, Scope.
Every structure, and portion thereof, including
																		 nonstructural components that are permanently attached to structures and their supports and attachments,
																		 shall be designed and constructed to resist the effects of earthquake motions in accordance with ASCE 7,
																		 excluding Chapter 14 and Appendix 11A. The seismic design category for a structure is permitted to be
																		 determined in accordance with Section 1613 or ASCE 7-10. Figure 1613.5(1) shall be replaced with ASCE 7-10
																		 Figure 22-1. Figure 1613.5(2) shall be replaced with ASCE 7-10 Figure 22-2.
Amend
Chapter 29
Adopt
Chapter 29
All plumbing provisions located in this Chapter shall
																		 reference 2021 IPC with Louisiana Amendments.
Repeal
Section 3001 2, Emergency Elevator Communication
																		 Systems.
Amend
Section 3113, Relocatable Buildings.
Relocatable Buildings constructed on or after January
																		 1, 2007 Shall conform to the Louisiana Industrialized Building Act. Relocatable Buildings constructed prior
																		 to January 1, 2007 shall meet the requirements of Section 3113 3
Amend
Section 3313 2, Supplemental Information.
Supplemental information specific to a relocatable
																		 building shall be submitted to the authority having jurisdiction. It shall, as a minimum, include the
																		 following:
Adopt
Item (1)
Each relocatable module constructed after January 1,
																		 2007 shall conform with the Louisiana Industrialized Buildings Act and shall have a data plate that is
																		 permanently attached on or adjacent to the electrical panel, and shall include the following
																		 information:
Occupancy group.
Manufacturer's name and address.
Date of manufacture.
Serial number of module.
Design wind speed.
Special limitations if any.
Adopt
Exception:
Buildings without Data Plate shall meet requirements
																		 of Section 3113.3 and remaining requirements of this section.
Adopt
Item (2)
Foundation Design Documents.
Adopt
Item (3)
Site-built structure or appurtenance attached to the
																		 relocatable building.
Amend
3113.3, Buildings Built prior to January 1,
																		 2007.
Relocatable buildings without a data plate shall be
																		 inspected and certified by one of the following methods:
Adopt
Item (1)
Inspection and acceptance by Local Building Official
																		 to meet the code requirements in place at time of construction.
Adopt
Item (2)
Inspection and acceptance by a third party inspector
																		 registered with LSUCCC to meet the code requirements in place at time of construction.
Adopt
Item (3)
Recertification and acceptance to current code and
																		 requirements of the Louisiana Industrialized Building Act.
Repeal
Section 3313, Fire Protection During
																		 Construction
Repeal
Section 3314, Fire Watch During Construction
Adopt
Appendix G
Amend
User Notes
Repeal
Amend
Section G102 Definitions
Repeal
Manufactured Home
Repeal
Manufactured Home Park or Subdivision
Repeal
Recreational Vehicle
Amend
Section G103.1 General
Repeal
Item 1
Repeal
Item 2
Repeal
Item 3
Repeal
Item 4
Repeal
Item 7
Amend
Section G104 Power and Duties
Repeal
Section G104.5.1 Floodway revisions
Repeal
Section G104.6 Watercourse alteration
Repeal
Section G104.6.1 Engineering analysis
Repeal
Section G104.7 Alterations in coastal area
Amend
Section G105 Permits
Repeal
Section G105.2 Application for permit
Repeal
Item 1
Repeal
Item 2
Repeal
Item 3
Repeal
Item 4
Repeal
Item 5
Repeal
Item 6
Repeal
Item 7
Repeal
Item 8
Amend
Section G106 Variances
Amend
Section G106.7 Conditions for issuance
Repeal
Item 5
Repeal
Section G107 Subdivisions
Repeal
Section G107.1 General
Repeal
Item 1
Repeal
Item 2
Repeal
Item 3
Repeal
Section G 107.2 Subdivision requirements
Repeal
Item 1
Repeal
Item 2
Repeal
Item 3
Repeal
Item 4
Amend
Section G108 Site Improvement
Repeal
Section G108.3 Sewer Facilities
Repeal
Section G108.4 Water Facilities
Repeal
Section G108.5 Storm drainage
Repeal
Section G108.6 Streets and sidewalks
Repeal
Section G109 Manufactured Homes
Repeal
Section G109.1 Elevation
Repeal
Section G109.2 Foundations
Repeal
Section G109.3 Anchoring
Repeal
Section G109.4 Protection of mechanical equipment and
																		 outside appliances
Repeal
Exception
Repeal
Section G109.5 Enclosures
Repeal
Section G 110 Recreational Vehicles
Repeal
Section G110.1 Placement prohibited
Repeal
Section G110.2 Temporary placement
Repeal
Section G110.3 Permanent Placement
Repeal
Section G111 Tanks
Repeal
Section G111.1 Tanks
Amend
Section 112 Other Building Work
Repeal
Section G112.2 Fences
Repeal
Section G112.3 Oil derricks
Repeal
Section G112.4 Retaining walls, sidewalks and
																		 driveways
Repeal
Section G112.5 Swimming pools
Repeal
Section G112.6 Decks, porches, and patios
Repeal
Section G112.7 Nonstructural concrete slabs in
																		 coastal high-hazard areas and coastal A zones
Repeal
Section G112.8 Roads and watercourse crossings in
																		 regulated floodways
Amend
Section G114 Utility and Miscellaneous Group U
Amend
Section G114.1 Utility and Miscellaneous Group
																		 U
Utility and miscellaneous Group U includes buildings
																		 that are accessory in character and miscellaneous structures not classified in any specific occupancy in this
																		 code, including, but not limited to, agricultural buildings, aircraft hangars (accessory to a one- or
																		 two-family residence), barns, carports, grain silos (accessory to a residential occupancy), greenhouses,
																		 livestock shelters, private garages, sheds, and stables.
AUTHORITY NOTE: Promulgated
											  in accordance with R.S. 40:1730.22(C) and (D) and 40:1730.26(1).