reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 6 - New Installations of Boilers › Section 6-1 - Compliance with ASME code; special designs

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-13-2-11; IC 22-15-6
Sec. 1.
(a) No
				boiler, except an existing installation of a boiler to be reinstalled or one
				exempted by
				675 IAC
				30-1-2, shall be installed in this state on or after
				July 1, 1953, unless it conforms with the edition of the ASME B&PVC in
				effect when the boiler was designed or constructed. A boiler installed on or
				after January 5, 1996 that requires an ASME B&PVC manufacturer's data
				report shall be registered with the NBBI.
(b) Each reinstalled or secondhand boiler
				shall be installed in accordance with the requirements of Part 1 of the NBIC,
				as referenced in
				675 IAC
				30-1-1.
(c) Where a boiler of special design does not
				comply with the adopted standards in
				675 IAC
				30-1-1, its construction must be approved in
				accordance with the variance procedure established in IC 22-13-2-11.
(d) A boiler shall not be operated until a
				valid operating permit is issued, as required by 675 IAC 30-39.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-6-1 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-6-1 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 6 - New Installations of Boilers › Section 6-2 - Inspection; stamping of serial number

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 2.
(a) Upon
				completion of the installation of a boiler, it shall be inspected by an
				inspector. At the time of the first operating permit inspection, the inspector
				shall assign and attach a state registration number, preceded by the letters
				"IN". The letters and figures shall not be less than one-fourth (1/4) inch in
				height and shall be arranged as follows:
IN 123456
(b) The number assigned shall be one (1) from
				the series provided to the inspector under
				675 IAC
				30-3-18.
(c) The number shall not be concealed by
				lagging or paint and shall be visible at all times.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-6-2 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-6-2 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 6 - New Installations of Boilers › Section 6-3

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-6-3 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-6-3 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 7 - New Installations of Unfired Pressure Vessels › Section 7-1 - Compliance with ASME code; special designs

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-13-2-11; IC 22-15-6
Sec. 1.
(a) No
				unfired pressure vessel, except an existing installation of an unfired pressure
				vessel to be reinstalled or one exempted by the provisions of
				675 IAC
				30-1-2, shall be installed in this state on or after
				July 1, 1953 unless it conforms with the edition of the ASME B&PVC in
				effect at the time of design or construction. An unfired pressure vessel
				installed on or after January 5, 1996, that requires an ASME B&PBV
				manufacturer's data report shall be registered with the National
				Board.
(b) Each reinstalled and
				secondhand unfired pressure vessel shall be installed in accordance with the
				requirements of Part 1 of the NBIC, as adopted in
				675 IAC
				30-1-1.
(c) Where an unfired pressure vessel of
				special design does not comply with the adopted standards in this article, its
				construction must be approved in accordance with the variance procedure
				established in IC 22-13-2-11.
(d)
				An unfired pressure vessel cannot be operated until an operating permit is
				issued, as required by
				675 IAC
				30-3-9.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-7-1 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-7-1 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 7 - New Installations of Unfired Pressure Vessels › Section 7-2 - Inspection; assignment of state registration number

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 2.
(a) Upon
				completion of the installation of the unfired pressure vessel, it shall be
				inspected by an inspector. At the time of the first operating permit
				inspection, the inspector shall assign and attach a state registration number,
				preceded by the letters "IN". The letters and figures shall not be less than
				one-fourth (1/4) inch in height and shall be arranged as follows:
IN 123456
(b) The number assigned shall be one (1) from
				the series provided to the inspector in accordance with
				675 IAC
				30-3-18.
(c) The number shall not be concealed by
				lagging or paint and shall be visible at all times.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-7-2 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-7-2 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-1 - MAWP for standard boilers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 1.
The MAWP for a standard boiler shall be determined in
				  accordance with the applicable provisions of the edition of the ASME B&PVC
				  under which it was constructed and stamped.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-1 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-1 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-3 - Maximum working pressure for all boilers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 3.
In no case shall the maximum working pressure of any boiler
				  be increased to a pressure greater than would be allowed for a new boiler of
				  the same construction.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-3 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-3 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-4 - MAWP for water tube boilers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 4.
The MAWP for a water tube boiler, the tubes of which are
				  secured to cast iron or malleable iron headers, or which have cast iron mud
				  drums, shall not exceed one hundred sixty (160) psig.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-4 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-4 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-5 - Cast iron boilers; use as power boiler prohibited

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 5.
No cast iron boiler shall be used as a power
				  boiler.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-8-5 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-8-5 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-6 - Access for inspection of drum heads

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 6.
Heads of lower drums of boilers shall be thoroughly examined
				  at the operating permit inspection, and either a sufficient amount of brickwork
				  shall be removed or inspection doors provided to enable this examination to be
				  made.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-6 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-6 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-7 - Inspection; assignment of state registration number; alternative standards

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 7.
(a) At the
				time of the first operating permit inspection, the inspector shall assign and
				attach a state registration number preceded by the letters "IND". The letters
				and figures shall not be less than one-fourth (1/4) inch in height and shall be
				arranged as follows:
IND 1234
(b) The number assigned shall be one (1) from
				the series provided to the inspector in accordance with
				675 IAC
				30-3-18.
(c) The number shall not be concealed by
				lagging or paint and shall be visible at all times.
(d) All existing power boiler installations
				shall conform to sections 8 through 16 of this rule or shall conform to the
				edition of the ASME B&PVC under which they were constructed and stamped, or
				to the ASME B&PVC as adopted in
				675 IAC
				30-1-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-7 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-7 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-8 - Feed supply and piping

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 8.
(a) All
				boilers shall have a feed supply which will permit the boiler to be fed at any
				time while the boilers are under pressure.
(b) A boiler having more than five hundred
				(500) square feet of water heating surface shall have at least two (2) means of
				feeding. One (1) of these means shall be an approved feed pump, an injector, or
				an inspirator. A source of feed directly from pressure mains may be considered
				one (1) of the means if sufficient pressure is available at all times to feed
				the boiler against a pressure six percent (6%) greater than the release
				pressure of the safety valve with the highest release setting.
(c) The feed water shall be introduced into
				the boiler in such manner that it will not be discharged close to riveted
				joints of shell or furnace sheets, or directly against surfaces exposed to
				gases at high temperature or direct radiation from the fire.
(d) The feed piping to the boiler shall be
				provided with a check valve near the boiler and a valve or cock between the
				check valve and the boiler. When two (2) or more boilers are fed from a common
				source, there shall also be a valve on the branch to each boiler between the
				check valve and source of supply. Whenever a globe valve is used on feed
				piping, the inlet shall be under the disk of the valve.
(e) In all cases where returns are fed back
				to the boiler by gravity, there shall be a check valve and stop valve on each
				return line, the stop valve to be placed between the boiler and the check
				valve, and both shall be located as close to the boiler as is
				practicable.
(f) When deaerating
				heaters are not employed, temperature of the feed water shall be no less than
				one hundred twenty degrees Fahrenheit (120°F). Where deaerating heaters are
				employed, the minimum feed water temperature shall be not less than two hundred
				fifteen degrees Fahrenheit (215°F).
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-8-8 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-8-8 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-9 - Fire-actuated fusible plugs

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 9.
Fire-actuated fusible plugs, if used, shall conform to the
				  edition of the ASME B&PVC under which the power boiler in which the plugs
				  are installed was constructed and stamped, or to the ASME B&PVC as adopted
				  in
				  675 IAC
				  30-1-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-9 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-9 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-10 - Water columns, gage cocks, and gage glasses

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 10.
(a) No
				outlet connections shall be placed on the piping that connects the water column
				to the boiler. The only exceptions allowed are as follows:
(1) Damper regulator.
(2) Feed water regulator.
(3) Low water fuel cut-out.
(4) Drains.
(5) Gauges.
(6) Such apparatus that does not permit the
				escape of an appreciable amount of steam or water. The water column shall be
				provided with a valved drain of at least three-fourths (3/4) inch pipe
				size.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-11 - Steam gages; shutoff valves; nipple and globe valves

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 11.
(a) Each
				steam boiler shall have a steam gauge, with a dial range not less than one and
				one-half (11/2) times the MAWP, that is connected to the steam space or to the
				steam connection to the water column. The steam gauge shall be connected to a
				siphon or equivalent device of sufficient capacity to keep the gauge tube
				filled with water, and so arranged that the gauge cannot be shut off from the
				boiler except by a cock placed near the gauge and provided with a tee or lever
				handle arranged to be parallel to the pipe in which it is located when the cock
				is open.
(b) When a steam gauge
				connection longer than eight (8) feet becomes necessary, a shut off valve may
				be used near the boiler provided the valve is of the outside screw and yoke
				type and is locked open. The line shall be ample size with provisions for free
				blowing.
(c) Each boiler shall be
				provided with a one-fourth (1/4) inch nipple and globe valve connected to the
				steam space for the exclusive purpose of attaching a test gauge when the boiler
				is in service so that the accuracy of the boiler steam gauge may be
				ascertained.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-11 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-11 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-12 - Stop valves; drainage

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 12.
(a) Each
				steam outlet from a boiler (except safety valve connections) shall be fitted
				with a stop valve located as close as practicable to the boiler.
(b) When a stop valve is so located that
				water can accumulate, ample drains shall be provided. The drainage shall not be
				discharged on the top of the boiler or its setting.
(c) When boilers provided with manholes are
				connected to a common steam main, the steam connection from each boiler shall
				be fitted with two (2) stop valves having an ample free blow drain between
				them. The discharge of this drain shall be visible to the operator while
				manipulating the valves and shall be piped clear of the boiler setting. The
				stop valves shall consist preferably of one (1) automatic nonreturn valve (set
				next to the boiler) and a second valve of the outside-screw-and-yoke
				type.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-12 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-12 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-13 - Blow-off piping; heat protection; fittings

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 13.
(a) The
				construction of the setting openings and their sealing around each blow-off
				pipe shall permit free expansion and contraction.
(b) All blow-off piping, when exposed to
				furnace heat, shall be protected by fire brick or other heat resisting
				material, so constructed that the piping may be readily inspected.
(c) Each boiler shall have a blow-off pipe,
				fitted with a valve or cock, in direct connection with the lowest water space.
				Cocks shall be of the gland or guard type and suitable for the pressure
				allowed. The use of globe valves shall not be permitted. If the maximum
				allowable working pressure exceeds one hundred (100) psig, each blow-off pipe
				shall be provided with two (2) valves or a valve and a cock, such valves and
				cocks to be suitable for the intended pressure and temperature.
(d) When the maximum allowable working
				pressure exceeds one hundred (100) psig, blow-off piping shall be suitable for
				the intended pressure and temperature. The piping shall not be
				galvanized.
(e) All fittings
				between the boiler and blow-off valve shall be constructed of material suitable
				for the intended pressure and temperature. In case of renewal of blow-off pipe
				or fittings, they shall be installed in accordance with the rules governing new
				installations.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-13 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-13 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-15 - Repair or replacement of fittings or appliances

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 15.
Whenever repairs are made to fittings or appliances or it
				  becomes necessary to replace them, the work shall comply with the edition of
				  the ASME B&PVC or the NBIC under which the power boiler was constructed and
				  stamped, the ASME B&PVC, or the NBIC.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-15 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-15 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 8 - Existing Installations of Power Boilers (prior to July 1, 1953) › Section 8-16 - Conditions not covered by this article

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 16.
Any condition not specifically covered by this rule shall be
				  treated as new installations and comply with the applicable provisions of the
				  codes adopted in
				  675 IAC
				  30-1-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-8-16 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-8-16 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-1

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-1 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-1 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-2

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-2 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-2 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-3

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-3 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-3 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-4

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-4 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-4 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-5

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-5 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-5 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-6

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-6 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-6 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-7

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-9-7 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-7 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-8

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-8 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-8 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-9

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-9 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-9 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 9 › Section 9-10

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-9-10 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-9-10 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-1 - MAWP for standard boilers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 1.
The MAWP of a heating boiler built in accordance with the
				  ASME B&PVC shall in no case exceed the pressure indicated by the
				  manufacturer's identification stamped or cast upon the boiler or upon an
				  identification plate secured to it.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-1 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-1 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-2 - MAWP for nonstandard riveted boilers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 2.
The MAWP for the shell of a nonstandard heating riveted
				  boiler shall be determined in accordance with
				  675 IAC
				  30-8 this covering existing installations of power
				  boilers, except that in no case shall the MAWP of such a boiler exceed fifteen
				  (15) psig for steam or one hundred sixty (160) psig for water, at a temperature
				  not exceeding two hundred fifty (250) degrees Fahrenheit.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-2 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-2 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-3 - MAWP for nonstandard welded boilers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 3.
The MAWP of a nonstandard steel or wrought iron low pressure
				  heating boiler of welded construction shall not exceed fifteen (15) psig for
				  steam. For other than steam service, the maximum allowable working pressure
				  shall be calculated in accordance with Section IV of the ASME B&PVC.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-3 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-3 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-4 - MAWP for nonstandard cast iron boilers

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 4.
The MAWP for a nonstandard boiler composed principally of
				  cast iron, or having cast iron shell or head and steel or wrought iron tubes,
				  shall not exceed fifteen (15) psig for steam service or thirty (30) psig for
				  water service.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-4 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-4 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-5 - Feed water connections; stop and check valves

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 5.
Feed water connections shall be independent of any water
				  gauge connections and be made to the condensate return pipe or reservoir of the
				  condensate return pump. There shall be a stop valve and a check valve in the
				  feed water line at the boiler.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-5 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-5 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-6 - Return pumps; water level control

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 6.
Each condensate return tank where practicable shall be
				  provided with an automatic water level control set to maintain the water level
				  within safe limits.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-10-6 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-10-6 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-7 - Water gage glasses; location

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 7.
Each steam heating boiler shall have at least one (1) water
				  gauge glass with the lowest visible part above the heating surfaces in the
				  primary combustion chamber. When the heating surfaces above the low water line
				  may be injured by contact with gases of high temperature, the water gauge shall
				  be raised until the lowest visible part of the gauge glass is above such
				  heating surface.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-7 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-7 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-8 - Steam gages for low pressure steam heating boilers; connections; dial range; stops

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 8.
(a) Each low
				pressure steam heating boiler shall have a steam gauge connected to its steam
				space or to its water column, or its steam connections by means of a siphon or
				equivalent device to keep the gauge tube filled with water and so arranged that
				the gauge cannot be shut off from the boiler except by a cock with a tee or
				lever handle, placed in the pipe near the gauge. The handle of the cock shall
				be parallel to the pipe in which it is located when the cock is open.
(b) The scale on the dial of a low pressure
				steam heating boiler gauge shall be graduated to not less than thirty (30)
				psig. The gauge shall be provided with effective stops for the indicating
				pointer at the zero (0) point and at the maximum pressure point. The travel of
				the pointer from zero (0) to thirty (30) psig pressure shall be at least three
				(3) inches.
(c) Connections to
				steam-gauge siphons shall be of nonferrous metal when either:
(1) smaller than one (1) inch pipe size and
				longer than five (5) feet between siphon and the point of connection of pipe
				and boiler; or
(2) smaller than
				one-half (1/2) inch pipe size and shorter than five (5) feet between the siphon
				and point of connection of pipe to the boiler.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-9 - Pressure or altitude gages for hot water heating boilers; connections; dial range; stops

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 9.
(a) Each hot
				water heating boiler shall have a pressure or altitude gauge connected to it or
				to its flow connection in such a manner that it cannot be shut off from the
				boiler except by a cock with a tee or lever handle, placed on the pipe near the
				gauge. The handle of the cock shall be parallel to the pipe in which it is
				located when the cock is open.
(b)
				The scale on the dial of the pressure or altitude gauge shall be graduated to
				not less than one and one-half (11/2) times the MAWP. The gauge shall be
				provided with effective stops for the indicating pointer at the zero (0) point
				and at the maximum pressure point.
(c) Pressure or altitude gauge connections
				shall be of nonferrous composition when smaller than one (1) inch pipe
				size.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-9 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-9 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-10 - Thermometers for hot water heating boilers; location and connection

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 10.
Each hot water heating boiler shall have a thermometer so
				  located and connected that it shall be easily readable when observing the water
				  pressure or altitude. The thermometer shall be so located that it shall at all
				  times indicate the temperature in degrees Fahrenheit of the water in the
				  boiler, at or near the outlet. The pressure or altitude gauges and thermometer
				  may be separate devices, or a combination device.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-10 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-10 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-11 - Stop valves and check valves

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 11.
(a) If a
				heating boiler may be closed off from the heating system by closing a steam
				stop valve, there shall be a check valve in the condensate return line between
				the boiler and the system.
(b) If
				any part of a heating system may be closed off from the remainder of the system
				by closing a steam stop valve, there shall be a check valve in the condensate
				return pipe from that part of the system.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-11 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-11 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-12 - Safety valves for low pressure steam heating boilers; dimensions and capacity

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 12.
(a) Each
				low pressure steam heating boiler shall have one (1) or more safety valves of
				the spring-pop type adjusted and sealed to discharge at a pressure not to
				exceed fifteen (15) psig.
(b) Each
				safety valve for a low pressure steam heating boiler that has a diameter
				three-fourths (3/4) inch or larger shall have a substantial device that will
				positively lift the disk from its seat at least one-sixteenth (1/16) inch when
				there is no pressure on the boiler. The seats and disks shall be of suitable
				material to resist corrosion.
(c)
				No safety valve for a low pressure steam heating boiler shall be smaller than
				three-fourths (3/4) inch and shall have a substantial device that will
				positively lift the disk from its seat at least one-sixteenth (1/16) inch when
				there is no pressure on the boiler. The seats and disks shall be of suitable
				material to resist corrosion.
(d)
				The minimum capacity of the valve or valves shall be governed by the capacity
				marking on the boiler called for in Section IV of the ASME B&PVC.
(e) The minimum valve capacity in pounds per
				hour shall be determined by dividing the maximum Btu output at the boiler
				nozzle obtained by the firing of any fuel for which the unit is designed by one
				thousand (1,000). In every case the requirements of subsection (f) shall be
				met.
(f) The steam safety valve
				capacity for each low pressure steam heating boiler shall be such that with the
				fuel-burning equipment installed, and fires at a maximum rate, the pressure of
				the low pressure steam heating boiler shall not exceed fifteen (15) psig with
				all safety valves open.
(g) When
				operating conditions are changed or additional boiler heating surface is
				installed, the valve capacity shall be checked and increased if necessary to
				meet the new conditions and be in accord with subsection (f). The additional
				valves required may be installed on the outlet pipe providing there is no
				intervening valve nor any other branching pipes between additional valves and
				the boiler.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-12 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-12 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-14 - Installation of safety and relief valves

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 14.
(a) Safety
				valves shall be connected to a heating boiler with the spindle vertical if
				possible, either directly to a tapped or flanged opening in the boiler, to a
				fitting connected to the boiler by a close nipple, to a Y base, to a valveless
				steam pipe between adjacent boilers, or to a valveless header connecting steam
				outlets on the same boiler.
(b)
				Relief valves shall be connected to the top of a heating boiler, with spindle
				vertical if possible, either directly to a tapped or flanged opening on the
				boiler, to a fitting connected to the boiler by a close nipple, to a Y base, or
				to a valveless header connecting water outlets on the same boiler.
(c) When a Y base is used, the inlet area
				shall not be less than the combined outlet areas. When the size of the boiler
				requires a safety valve or relief valve larger than four and one-half (41/2)
				inches in diameter, two (2) or more valves having the required combined
				capacity shall be used.
(d) No
				shut-off of any description shall be placed between the safety or relief valve
				and the boiler, or on discharge pipes between such valves and the atmosphere.
				Safety and relief valves shall not be connected to an internal pipe in the
				boiler.
(e) When a discharge pipe
				is used, its cross-sectional area shall be not less than the cross-sectional
				area of the valve or aggregate area based on the nominal diameters of the
				valves with which it connects, and the discharge pipe shall be fitted with an
				open drain to prevent water from lodging in the upper part of the valve or in
				the pipe. When an elbow is placed on a safety or relief valve discharge pipe,
				it shall be supported so that no stress is placed on the valve body. The
				discharge from a safety or relief valve shall be directed to a safe
				location.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-14 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-14 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-15 - Repair or replacement of fittings or appliances

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 15.
Whenever repairs are made to fittings or appliances or it
				  becomes necessary to replace them, the work must comply with the ASME B&PVC
				  or the NBIC.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-15 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-15 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 10 - Existing Installations of Heating Boilers › Section 10-16 - Inspection; stamping of serial number

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 16.
(a) At the
				time of the first operating permit inspection, the inspector shall assign and
				attach a state registration number preceded by the letters "IND". The letters
				and figures shall not be less than one-fourth (1/4) inch in height and shall be
				arranged as follows:
IND 1234
(b) All cast iron heating boilers shall have
				securely attached to the front of the boiler a metal tag not less than one (1)
				inch in height that shall have the state registration number stamped
				thereon.
(c) The number assigned
				shall be one (1) from the series provided to the inspector in accordance with
				675 IAC
				30-3-18.
(d) The number shall not be concealed by
				lagging or paint and shall be visible at all times.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-10-16 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-10-16 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 11 - Existing Installations of Unfired Pressure Vessels (prior to July 1, 1953) › Section 11-1 - MAWP for standard unfired pressure vessels

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 1.
The MAWP for a standard unfired pressure vessel shall be
				  determined in accordance with the edition of the ASME B&PVC or API-ASME
				  code under which it was constructed and stamped.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-11-1 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-11-1 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 11 - Existing Installations of Unfired Pressure Vessels (prior to July 1, 1953) › Section 11-3 - Safety factor

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 3.
The minimum factor of safety shall in no case be less than
				  four (4) for carbon steel or low-alloy steel vessels operating with metal
				  temperatures below seven hundred (700) degrees Fahrenheit. For high alloy steel
				  the maximum allowable stress value shall be indicated in the applicable table
				  of maximum allowable stress values provided in the applicable provisions of the
				  ASME B&PVC in effect at the time of fabrication for the material and
				  temperature involved. The factor of safety may be increased (or the maximum
				  allowable stress may be reduced) when deemed necessary by the inspector to
				  ensure the operation of the vessel is within safe limits.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-11-3 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-11-3 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 11 - Existing Installations of Unfired Pressure Vessels (prior to July 1, 1953) › Section 11-4 - Safety appliances

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 4.
Each unfired pressure vessel shall be protected by such
				  safety and relief valves and interlocking, indicating, and controlling safety
				  devices as will ensure its safe operation. These valves and devices shall be so
				  constructed, located, and installed that they cannot readily be rendered
				  inoperative. The relieving capacity of safety valves shall be such as to
				  prevent a rise of pressure in the vessel in excess of that permitted by
				  applicable provisions of the API-ASME code or the ASME B&PVC, taking into
				  account the effect of static head. Safety valve discharges shall be carried to
				  a point where damage to property or injury to personnel is
				  minimized.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-11-4 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-11-4 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.