reglab/statecodes huggingface dataset:
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 1 - SEPTIC TANKS › Rule 15-15-77-1-5.1.4 - Design

Current through June 25, 2024
All septic tanks (prefabricated concrete, steel,
					 fiberglass or polyethylene) must be designed according to minimum standards as
					 follows:
1. General
a. The septic tank shall be watertight,
				  structurally sound and not subject to excessive corrosion or decay. The outlet
				  of the septic tank should be placed so as not to be located below the Seasonal
				  High Water Table.
b. The minimum
				  hydraulic detention time of the septic tank must be two (2) days (48 hours)
				  based on daily sewage flows. In no case shall the septic tank have a minimum
				  effective liquid capacity of less than seven hundred fifty (750)
				  gallons.
c. All tanks manufactured
				  in two (2) sections must have an interlocking type joint. Tanks manufactured in
				  two sections must be sealed and joined with an approved sealant such as butyl
				  rubber or other approved pliable sealant that is waterproof,
				  corrosion-resistant and is warranted by the manufacturer for sealing concrete
				  septic tanks.
d. All septic tanks
				  with a capacity of greater than fifteen hundred (1,500) gallons shall be deemed
				  structurally sound by a licensed Professional Engineer via stamped
				  letter.
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 1 - SEPTIC TANKS › Rule 15-15-77-1-5.1.5 - Effluent Filters

Current through June 25, 2024
Effluent filters shall meet the following criteria:
1. The filter shall retain all partials
				  greater than one-eight (1/8) inch in size.
2. The assembly shall perform as a
				  conventional tank outlet, meeting the requirements of Rule 5.1.4.3, when the
				  filter is removed.
3. The filter
				  must be designed to handle the flow of the system it is to serve and not result
				  in excessive maintenance. For a single family dwelling, maintenance is
				  considered "excessive" when the filter requires service or cleaning more than
				  one (1) time per year. Service shall be performed each time the tank is pumped,
				  and in accordance with manufacturer's specifications.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 1 - SEPTIC TANKS › Rule 15-15-77-1-5.1.6 - Minimum Standards for Septic Tank Construction

Current through June 25, 2024
1. General
a. All septic tanks manufactured for sale in
				  the state of Mississippi shall bear an imprint identifying the manufacturer,
				  the serial number assigned to the manufacturer's plans and specifications
				  approved by the Department, the liquid or working capacity of the tank and be
				  marked with the date of manufacture. These imprints and markings must be
				  visible at the time of inspection by the Department.
b. All openings and lids shall be capable of
				  being sealed in a way that will prevent entrance of surface water and
				  groundwater.
c. Tank openings shall
				  be securely fastened or sealed to prevent unwarranted access to the contents of
				  the tanks vandal, tamper and child resistant. Acceptable protection of openings
				  may include, but is not limited to:
i. A
				  padlock
ii. An "O" ring with twist
				  lock cover requiring special tools for removal
iii. Covers weighing sixty-five (65) pounds
				  or more, net weight iv. Stainless steel or other corrosion resistant fasteners
				  for fiberglass or polyethylene lids.
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 1 - SEPTIC TANKS › Rule 15-15-77-1-5.1.7 - Minimum Standards for Concrete Reinforcement

Current through June 25, 2024
1.
				  Tanks Reinforced with Welded Steel Concrete Wire
a. The reinforcing wire shall be a minimum
				  number ten (10) gauge six (6) inch on centers. The reinforcing wire shall be
				  lapped a minimum of six (6) inches.
b. Lids for prefabricated septic tanks shall
				  have one (1) 3/8 inch steel reinforcing rod per foot of length and
				  width.
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 1 - SEPTIC TANKS › Rule 15-15-77-1-5.1.8 - Maintenance

Current through June 25, 2024
The septic tank should be pumped at a frequency depending
					 on the wastewater flow. The recommended pumping cycle is three (3) to five (5)
					 years, but pumping should not occur until the settleable solids have reached a
					 depth of 1/3 the septic tank liquid depth. This can be determined by "sticking"
					 the tank.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 1 - SEPTIC TANKS › Rule 15-15-77-1-5.1.9 - Septic Tank Sizing

Current through June 25, 2024
The effective liquid capacity of septic tanks for
					 dwellings shall be based on the number of bedrooms proposed or anticipated as
					 shown in the table below:
Number of Bedrooms
Number of Occupants
Minimum Effective Liquid Capacity (gallons)
							 without baffle or effluent filter
Minimum Effective Liquid Capacity (gallons) with
							 baffle or effluent filter
2 or less
4 or less
750
750
3
6
900
900
4
8
1200
1000
5
10
1500
1250
6
12
1800
1500
For each additional bedroom add 260 gallons
For each additional occupant over 2 per bedroom add 130
					 gallons
For a nonresidential application, the septic tank will be
					 sized at twice the estimated daily flow
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.2.1 - General

Current through June 25, 2024
1. All Advanced Treatment Systems installed
				  in the state of Mississippi shall be in compliance with the current revision of
				  the National Sanitation Foundation/American National Standard Institute
				  International Standard 40 or 245 testing protocol, hereby incorporated into
				  regulation by reference and shall be certified by an approved third party
				  certification program. The Division will maintain a current listing of
				  registered and certified manufacturers. The current list will be made available
				  by the Department.
2. The
				  Department shall only approve individual Advanced Treatment Systems that have
				  no discharge of wastewater off the property of the generator.
3. All Advanced Treatment Systems must be
				  installed according to the Certified Manufacturer's specifications by a
				  factory-trained installer that is an authorized representative of the
				  manufacturer.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.2.2 - Definitions

Current through June 25, 2024
1. Aerator - a mechanical device that provides dissolved
					 oxygen to an Advanced Treatment System.
2. Advanced Treatment System - treatment component that
					 utilizes oxygen to degrade or decompose wastewater.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.2.3 - Location

Current through June 25, 2024
1. Advanced Treatment Systems shall be
				  installed level on undisturbed soil. If leveling or elevation change is
				  necessary, the Advanced Treatment System must be placed on a bed of
				  sand.
2. It is recommended the
				  outlet of the Advanced Treatment System should be placed so as not to be below
				  the Seasonal High Water Table.
3.
				  An Advanced Treatment System should not be located in an area that collects
				  surface water. This water may enter the Advanced Treatment System causing a
				  failure by flooding. This flooding will cause the effluent to be discharged
				  before it is properly treated.
4.
				  The Advanced Treatment System must be installed according to the following
				  minimum distances:
a. foundations five (5)
				  feet
b. property lines ten (10)
				  feet
c. potable water supplies and
				  all private wells fifty (50) feet
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.2.4 - Inlet and Outlet

Current through June 25, 2024
1. The inlet and
				  outlet must be schedule forty (40) pipe four (4) inches in diameter. A three
				  (3) inch house sewer stubout, when used, shall be connected to the four (4)
				  inch pipe from the septic tank inlet using manufactured fittings designed for
				  that purpose.
2. The inlet and
				  outlet pipe (schedule 40 four (4) inch) must extend a minimum of three (3) feet
				  onto undisturbed soil before entering and after exiting the Advanced Treatment
				  System.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.2.5 - Maintenance

Current through June 25, 2024
1. All Advanced Treatment Systems should be
				  pumped at a frequency based on the wastewater volume generated by the residence
				  or establishment. The pumping cycle will depend on the level of the sludge in
				  the Advanced Treatment System. The sludge should not be allowed to accumulate
				  more than the recommended depth specified by the manufacturer of the Advanced
				  Treatment System. If the sludge is allowed to discharge, a clogging problem may
				  occur if any additional treatment or disposal system is used in conjunction
				  with the Advanced Treatment System.
2. All Advanced Treatment Systems shall be
				  maintained and inspected as required by the Certified Manufacturer.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.2.6 - Aerators

Current through June 25, 2024
The type of aerator used with the Advanced Treatment
					 System is mandated by the manufacturer. The maintenance of the aerator is
					 outlined in the manual provided by the Certified Manufacturer or his authorized
					 representative.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.2.7 - Sizing

Current through June 25, 2024
SIZING - AGGREGATE REPLACEMENT (Expanded Polystyrene
					 System) "Horizontal" Configuration
Results of the Soil and Site Evaluation
Soil Textural Class
Ribbon Lengths (Inches)
EPA Manual Application Rate GPD/
Ft2
Absorption Area Per Bedroom**
Additional Absorption Over 2 Person Per
								Bedroom**
3-1 0H
1-12
2-12
3-12
1-14
3-10 H
1-12
2-12
3-12
1-14
Ft 
								2
Lf
Lf
Lf
Lf
Lf
Ft 
								2
Lf
Lf
Lf
Lf
Lf
Gravel
-
-
NOT SUITABLE
Coarse
Sand
-
1.2
108
30
75
37
25
36
54
15
38
19
13
18
Medium
Sand
-
1.2
108
30
75
37
25
36
54
15
38
19
13
18
Fine
Sand
-
0.8
163
46
114
57
38
55
81
23
57
29
19
28
Loamy Sand
-
0.8
163
46
114
57
38
55
81
23
57
29
19
28
Sandy Loam
<.5
0.6
217
60
151
75
50
72
108
30
76
38
25
36
Light
Loam
<.5
0.6
217
60
151
75
50
72
108
30
76
38
25
36
Heavy
Loam
.5 - 1
0.45
289
81
201
101
67
97
144
40
101
52
33
49
Silt Loam
<1
0.45
289
81
201
101
67
97
144
40
101
52
33
49
Sandy Clay Loam
1 - 2
0.45
289
81
201
101
67
97
144
40
101
52
33
49
Light
Clay Loam
1 - 1.5
0.30
433
120
299
153
100
144
217
60
100
77
50
72
Heavy
Clay Loam
1.5 - 2.0
0.20
650
178
449
225
150
217
325
89
225
113
75
109
Light
Silty Clay Loam
1 - 1.5
0.30
433
120
299
153
100
144
217
60
100
77
50
72
Heavy
Silty Clay Loam
1.5 - 2.0
0.20
650
178
449
225
150
217
325
89
225
113
75
109
Sandy Clay
>2.0
-
NOT SUITABLE
Silty Clay
>2.0
-
NOT SUITABLE
Clay
>2.0
-
NOT SUITABLE
Minimum and maximum trench widths are 24 and 36 inches,
					 respectively.
** Bedroom is equivalent to 130 gallons per
					 day.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 2 - ADVANCED TREATMENT SYSTEMS Rule › Rule 15-15-77-2-5.6.17 - System Design

Current through June 25, 2024
2. Determine the
				  average daily flow from the residence: Number of bedrooms X 130 gallons per
				  day
3. Determining the size of the
				  absorption area, basal area, side slopes, and maximizing length requirements:
a. a. Sizing the absorption area The
				  absorption area size shall be determined by the
loading
rate of
				  the fill material. The fill material shall be coarse sand, 0.5-1.0 mm (USDA
				  designation), and is the same as concrete sand (Section S-703, MS Standard
				  Specification for State Aid road and bridge construction). The
loading
				  rate
of this material is 1.2 gallons per day per square foot. Note: A
				  fill material as heavy as a light loam may be used, but this will change the
				  size of the absorption area size. Use the appropriate
loading rate
of the fill to calculate the absorption area.
i. Example: Three (3) bedroom home @ 390
				  gallons per day
ii. 390 gallons per
				  day / 1.2 gallons per day per square foot =
325 square feet
iii. Absorption area = 325 square
				  feet
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.1 - General

Current through June 25, 2024
1. The treatment facility and pump/dosing
				  chamber shall be designed, constructed and installed so all joints, seams, and
				  component parts preclude infiltration of surface and groundwater, while
				  preventing the escape of wastewater or other liquids.
2. Electrical equipment shall be protected
				  with safety devices (overload interrupting devices, fuses, etc.). Electrical
				  equipment shall comply with appropriate National Electrical Manufacturer's
				  Association (NEMA). Electrical component parts shall be covered by the
				  manufacturer's limited warranty and must be installed in a manner to eliminate
				  potential contact with sewage or effluent, including connections.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.2 - Soil and Site Evaluation

Current through June 25, 2024
1. A satisfactory
				  soil and site evaluation will comply with the following criteria:
a. Absence of or protection from frequent
				  flooding.
b. Landscape position
				  with positive surface runoff.
c.
				  Slopes of less than sixteen (16)%
d. Depth to high water table of greater than
				  six (6) inches.
e. Depth to
				  bedrock, fragipan, redoximorphic features or plinthite of greater than twelve
				  (12) inches.
f. Soil texture and
				  color defined by the Natural Resource Conservation Service as indicating good
				  drainage and suitable for surface application of wastewater, based on a soil
				  boring of five (5) feet.
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.3 - Location of Spray Irrigation Disposal Systems

Current through June 25, 2024
1. All
				  components of the spray irrigation disposal system shall be located a minimum
				  of:
a. Five (5) feet from any dwelling or
				  permanent structure.
b. Ten (10)
				  feet from any property line.
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.4 - Registration

Current through June 25, 2024
The term "manufacturer" for this section will mean the
					 Certified Manufacturer of the treatment method, unless otherwise specified.
					 Each manufacturer's treatment and disposal components shall be registered with
					 the Department as a system. The treatment method shall be in compliance with
					 the current standards of National Sanitation Foundation/American National
					 Standards Institute International Standard 40 and/or 245 and the applicable
					 sections of the regulations.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.5 - Pump/Dosing Chambers

Current through June 25, 2024
1. The pump/dosing
				  chamber shall have a minimum working capacity of 1.5 times the maximum volume
				  produced for timed-dose and per manufacturer's specifications for demand-dose
				  systems.
2. The dosing chamber
				  shall be equipped with an audible high water alarm.
3. The pump/dosing chamber shall have a grade
				  level access large enough to allow servicing and/or removal of the largest
				  component in the chamber. Access ports shall be protected against unauthorized
				  entrance or removal.
4. The
				  pump/dosing chamber shall be vented through the grade level access or by means
				  of a separate vent. In either case the vent shall be a minimum of one (1) inch
				  in diameter.
5. The pump/dosing
				  chamber shall be made of material resistant to the corrosive effects of
				  wastewater, chemicals used for disinfection and designed to withstand the
				  lateral and bearing loads to which it is expected to be subjected.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.6 - Minimum Pump Specifications

Current through June 25, 2024
1. The pumping
				  system shall be designed to deliver wastewater at the required volume and
				  pressure specified by the spray irrigation head manufacturer.
2. The pumping system shall be equipped with
				  a low water cutoff to prevent damage to the pump during low water conditions in
				  the dosing chamber.
3. The pump
				  shall be constructed of corrosion resistant materials suitable for effluent
				  pumping.
4. The pump shall be sized
				  per manufacturers' specifications to meet or exceed the hydraulic head of the
				  system while delivering the required volume.
5. The pump shall be installed in compliance
				  with manufacturers' specifications so as not to violate pump
				  warranty.
6. The suction and
				  pressure lines shall be PVC schedule 40 and shall be sized to deliver the
				  required volume at the design pressure while not exceeding a velocity of five
				  feet per second.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.7 - Minimum Filter Specifications

Current through June 25, 2024
1. The filter shall
				  filter the effluent to the minimum specifications of the spray irrigation head
				  manufacturer to prevent clogging.
2. The filter shall be made of material
				  resistant to the corrosive effects of wastewater and chemicals used for
				  disinfection.
3. The filters shall
				  be readily accessible for inspection and/or service.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.8 - Minimum Specifications for Irrigation Equipment

Current through June 25, 2024
1. Sprinklers, valves, controllers and all
				  other equipment used in a spray irrigation system shall be designed,
				  manufactured and warranted by their manufacturer for use in effluent disposal
				  systems.
2. Sprinklers must be of
				  low trajectory type designed to reduce aerosols. Low trajectory spray
				  sprinklers have a nozzle trajectory equal to or less than thirty (30)
				  degrees.
3. Sprinklers shall be
				  connected to their supply line by means of polyethylene (PE) pipe or a swing
				  joint manufactured specifically for this purpose.
4. Radius reduction by means of nozzle
				  retaining screw, distance control diffuser pin or other similar devices shall
				  not be allowed.
5. Impact and
				  pop-up sprinklers may be used. Sprinkler risers greater than twenty four (24)
				  inches in height must be braced.
6.
				  Equipment susceptible to freezing must be adequately protected to prevent
				  freezing.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.9 - Minimum Specifications for Disinfection

Current through June 25, 2024
Effluent discharge from spray irrigation systems shall be
					 adequately disinfected prior to surface application. The method of disinfection
					 and the disinfection equipment must be in compliance with Chapter 6
					 Disinfection.
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 15 - Division of On-site Wastewater › Subpart 77 - On-site Wastewater Regulations › Subchapter 7 - SPRAY IRRIGATION DISPOSAL SYSTEM › Rule 15-15-77-7-5.7.10 - Minimum Specifications for the Spray Field

Current through June 25, 2024
1.
				  Spray irrigation systems may not be installed in drain ways, swamps, marshes,
				  floodplain, concave landscape positions or other areas which would be
				  prohibited.
2. Treated effluent
				  shall be sprayed evenly over the entire spray field area with non overlapping
				  patterns. The spray field shall consist of a minimum of three (3) spray
				  heads.
3. The effluent distribution
				  system shall be designed, constructed and maintained to provide for even
				  distribution of effluent throughout the spray field.
4. Surface runoff of sprayed effluent from
				  the spray field area shall not be permitted. Rainwater shall be diverted away
				  from the spray field area.
5. The
				  spray field area shall be designed and operated to prevent surface accumulation
				  of sprayed effluent.
6. In order to
				  prevent entrapped air causing serious problems pipelines shall be routed on
				  contour, downhill or even uphill but not up and downhill along the same section
				  of pipe.
7. The size of the spray
				  field area shall be determined by soil texture and slope of the site to be
				  sprayed (See Table 1).
Table I
SIZING Spray Irrigation
Results of the Soil and Site Evaluation
Soil Textural Class
Ribbon Lengths (Inches)
EPA Manual Application Rate
							 GPD/Ft2
Absorption Area in
							 Ft2/Bedroom
Additional Absorption Area Over 2 Persons
							 Per Bedroom
Slope
Slope
0 to 8 %
9 to 12%
13 to 16%
0 to 8 %
9 to 12%
13 to 16%
Gravel
NOT SUITABLE
Coarse and Medium Sand Fine and Loamy Sand Sandy Loam
< 0.5
1.2
0.8
0.6
694
928
1,040
347
478
520
Loam Silt Loam Sandy Clay Loam
<0.5 - 1.0
< 0.5 - 1.0
1.0 - 2.0
0.45
1387
1734
2323
694
867
1162
Silt Clay Loam Clay Loam Sandy Clay
1.0 - 2.0
1.0 - 2.0
>2.0
0.2 - 0.3
0.2 - 0.3
-
2782
4637
6951
1391
2319
3476
Silty Clay Clay
>2.0
-
6951
8693
11588
3476
4347
5794
Table II
FILL MATERIAL
Seasonal High Water Table Depth (inches)
...with a Restrictive Horizon/Layer (inches)
...without a Restrictive Horizon/Layer (inches)
0
6
12
1
5
11
2
4
10
3
3
9
4
2
8
5
1
7
6
-
6
7
-
5
8
-
4
9
-
3
10
-
2
11
-
1
12
-
-
Click
					 Here To View Image
Click
					 Here To View Image
Miss Code Ann.
					 §
											41-67-3
Miss Code Ann.
					 §
											41-67-3
Miss Code Ann.
					 §
											41-67-3
Miss Code Ann.
					 §
											41-67-3
Miss Code Ann.
					 §
											41-67-3
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 1 - GENERAL › Rule 15-16-1-1.1.1

Current through June 25, 2024
Every Hospice located inside the boundaries of a
						municipality shall comply with all local municipal codes and ordinances
						applicable thereto. In addition, each hospice shall comply with all applicable
						federal laws and state laws inclusive of Mississippi Code Annotated (41-85-1)
						through (41-85-25).
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 2 - LEGAL AUTHORITY › Rule 15-16-1-1.2.1 - Adoption of Rules, Regulations, and Minimum Standards

Current through June 25, 2024
The Mississippi State Department of Health, Bureau of
						Health Facilities, Licensure and Certification adopts the following rule
						governing the licensing and regulation of hospices as authorized by the
						Mississippi Code Annotated Section
						41-85-1
						through
						41-85-25
						and in accordance with House Bill 379 enacted by the Regular 1995 Session of
						the Legislature of the State of Mississippi known as the "Mississippi Hospice
						Law of 1995". The Bureau of Health Facilities, Licensure and Certification
						amends the following regulations which will govern the licensing of hospice
						agencies licensed on or after adoption of this rule.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 2 - LEGAL AUTHORITY › Rule 15-16-1-1.2.2 - Effective date of Rules, Regulations, and Minimum Standards for Hospice

Current through June 25, 2024
The provisions of this rule shall govern all hospice
						agencies, regardless of the date of issuance of license.
Miss. Code
						Ann. §
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 2 - LEGAL AUTHORITY › Rule 15-16-1-1.2.3 - Fire Safety

Current through June 25, 2024
No freestanding hospice may be licensed until it shows
						conformance to the safety regulations providing minimum standards for
						prevention and detection of fire as well as for protection of life and property
						against fire (Refer to NFPA 10 and NFPA 72).
Miss. Code
						Ann. §
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 4 - PROCEDURE GOVERNING ADOPTION AND AMENDEMENT › Rule 15-16-1-1.4.1 - Authority

Current through June 25, 2024
The Mississippi State Department of Health shall have
						the power to adopt, amend, promulgate and enforce such minimum standards of
						operation as it deems appropriate, within the law.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 4 - PROCEDURE GOVERNING ADOPTION AND AMENDEMENT › Rule 15-16-1-1.4.2 - Amendment

Current through June 25, 2024
The Minimum Standards of Operation for Hospice may be
						amended by the Mississippi State Department of Health as necessary to promote
						the health, safety and welfare of persons receiving services.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 5 - CLASSIFICATION OF HOSPICE › Rule 15-16-1-1.5.1

Current through June 25, 2024
For the purpose of these rules, regulations, and minimum
						standards, hospice shall be classified as:
1. Freestanding Hospice
2. Hospital Hospice
3. Nursing Home Hospice
4. Home Health Agency Hospice
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 5 - CLASSIFICATION OF HOSPICE › Rule 15-16-1-1.5.2 - Hospice Core Service

Current through June 25, 2024
To be classified as a Hospice these core services shall
						be provided but need not be limited to the following:
1. Physician Service
2. Nursing Service
3. Medical Social Service
4. Pastoral/Counseling Services
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 5 - CLASSIFICATION OF HOSPICE › Rule 15-16-1-1.5.3 - Inpatient Hospice

Current through June 25, 2024
To be classified as an Inpatient Hospice that provides
						inpatient care, the core services (physician, nursing, medical, social and
						counseling) shall be provided on the premises. Inpatient Hospice must have a
						registered nurse on duty seven days a week, twenty-four hours a day to provide
						direct patient care. Other members and types of personnel sufficient to meet
						the total needs of the patient shall be provided.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 6 - LICENSING › Rule 15-16-1-1.6.1

Current through June 25, 2024
It shall be unlawful to operate or maintain a hospice
						without first obtaining a license from the department. The Mississippi State
						Department of Health is the licensing authority for hospice in the State of
						Mississippi.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 7 - TYPES OF LICENSES › Rule 15-16-1-1.7.1 - Regular License

Current through June 25, 2024
A license shall be issued to each hospice that meets the
						requirements as set forth in these regulations. The license shall show the
						classification Home Health, Nursing Home, Hospital or
						Freestanding.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 7 - TYPES OF LICENSES › Rule 15-16-1-1.7.2 - Provisional License

Current through June 25, 2024
Within its discretion, the Mississippi State Department
						of Health may issue a provisional license when a temporary condition of
						non-compliance with these regulations exists in one or more particulars. A
						provisional license shall be issued only if the Department of Health is
						satisfied that preparations are being made to qualify for a regular license and
						that the health and safety of patients will not be endangered. One condition on
						which a provisional license may be issued is as follows: A new hospice agency
						may be issued a provisional license prior to opening and subsequent to meeting
						the required minimum staffing personnel. The license issued under this
						condition shall be valid until the issuance of a regular license or June 30
						following date of issuance whichever may be sooner. A provisional license may
						be reissued only if it is satisfactorily proven to the Department of Health
						that efforts are being made to fully comply with these regulations by a
						specified time.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 7 - TYPES OF LICENSES › Rule 15-16-1-1.7.3

Current through June 25, 2024
A hospice program against which a revocation or
						suspension proceeding is pending at the time of licensure renewal may be issued
						a conditional license effective until final disposition by the department of
						such proceedings.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.1

Current through June 25, 2024
A Hospice shall not be operated in Mississippi without a
						valid license from Mississippi State Department of Health.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.2

Current through June 25, 2024
Any person or organization desiring to operate a hospice
						shall file with the Department of Health:
1. Application on a form prescribed and
					 furnished by the Department of Health; and
2. Fees as applicable per State law
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.3

Current through June 25, 2024
The application shall include complete information
						concerning the address of the applicant; the ownership of the hospice; if
						organized as a corporation, the names and addresses of each officer and
						director of the corporation; if organized as a partnership, the names and
						addresses of each partner; membership of the governing body; the identities of
						the medical director and administrator; and any other relevant information
						which the Mississippi State Department of Health may require. A written
						amendment to the current application shall be filed when there is a change in
						any of the information reported in the application.
Miss. Code
						Ann. §
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.4

Current through June 25, 2024
Ownership of the hospice shall be fully disclosed in the
						application. This disclosure shall include names and addresses of all corporate
						officers and any person(s) having a five percent (5%) financial
						interest.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.5

Current through June 25, 2024
A license shall be issued to the person(s) named only
						for the premises listed on the application for licensure. Separate applications
						and licenses are required for hospices maintained separately, even if they are
						owned or operated by the same person(s), business or corporation, and may be
						doing business under the same trade name. No hospices shall establish a
						branch/satellite facility outside the geographic service
						area.
Miss. Code
						Ann. §
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.6

Current through June 25, 2024
Licenses are not transferable or assignable by the
						licensee.
Miss. Code
						Ann. §
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.7

Current through June 25, 2024
Each planned change of ownership or lease shall be
						reported to the Department at least thirty (30) days prior to such change along
						with an application from the proposed new owners/lessees for a new
						license.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.8

Current through June 25, 2024
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.9 - Fees

Current through June 25, 2024
Prior to review for an initial license and prior to
						license renewal, the facility shall submit fees as established by the
						Mississippi State Board of Health, made payable to the Mississippi State
						Department of Health, either by business check, money order, or electronic
						means.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.10

Current through June 25, 2024
Operational Requirements/Conditions of Operation - In
						order for a hospice program to be considered operational, the program
						must:
1. Have admitted at least three
					 patients since the last annual survey;
2. Be able to accept referrals at any
					 time;
3. Have adequate staff to
					 meet the needs of their current patients;
4. Have required designated staff on the
					 premises at all times during business hours;
5. Be immediately available by
					 telecommunications 24 hours per day. A registered nurse must answer calls from
					 patients and other medical personnel after hours;
6. Be open for business of providing hospice
					 services to those who need assistance.
Miss. Code
						Ann. §
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 8 - APPLICATION FOR LICENSE › Rule 15-16-1-1.8.11 - License Renewal Process

Current through June 25, 2024
1. A license issued
					 for the operation of a hospice program, unless sooner suspended or revoked,
					 shall expire automatically on June 30 of each calendar year.
2. Renewal packet includes forms required for
					 renewal of license.
3. An agency
					 seeking a renewal of its hospice license shall:
a. Request a renewal packet from the bureau
					 if one is not received at least 45 days prior to license expiration;
b. Complete all forms and return to bureau at
					 least 30 days prior to license expiration;
c. Submit the current annual licensure fees
					 with packet. An application is not considered to have been submitted unless the
					 licensure fees are received.
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.1

Current through June 25, 2024
Mississippi State Department of Health shall be notified,
						in writing, of any of the following within five working days following the
						occurrence:
1. Address/location (An
					 Inpatient Hospice facility must notify and receive approval by Mississippi
					 State Department of Health prior to a change of address/location);
2. Agency name;
3. Phone number;
4. Hours of operation/24 hour contact
					 procedure;
5. Change in address or
					 phone number of any branch office;
6. Administrator;
7. Director of nursing; and
8. Cessation of business.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.2 - Name of Institution

Current through June 25, 2024
Every hospice shall be designated by a permanent and
						distinctive name which shall be used in applying for a license and shall not be
						changed without first notifying the licensing agency in writing and receiving
						written approval of the change from the licensing agency. Such notice shall
						specify the name to be discontinued as well as the new name proposed. Only the
						official name by which the institution is licensed shall be used in telephone
						listing, on stationery, in advertising, etc. Two or more facilities shall not
						be licensed under similar names in the same vicinity.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.3 - Number of Beds

Current through June 25, 2024
Each application for license shall specify the maximum
						number of inpatient beds in the hospice as determined by these regulations. The
						maximum number of inpatient beds for which the facility is licensed shall not
						be exceeded.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.4

Current through June 25, 2024
A license for a hospice program shall not be issued if
						the hospice is to be located in an area in violation of any local zoning
						ordinances or regulations.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.5

Current through June 25, 2024
Following inspection and evidence of compliance with
						these regulations, the Mississippi State Department of Health may issue a
						license. Only licensed hospices shall be authorized to use the name
						"hospice.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.6

Current through June 25, 2024
A license shall be displayed in a prominent place in the
						hospice's administrative offices.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.7 - Inspections

Current through June 25, 2024
1. Observation and examination of the hospice
					 operation shall be available at all reasonable hours to properly identified
					 representatives of the Department.
2. The Department shall conduct inspections
					 of all Parent and Branch units annually.
3. Hospice inspections shall include personal
					 contacts with recipients of the hospice service.
Miss. Code Ann.
						§
												41-85-7
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 1 - MINIMUM STANDARDS OF OPERATION FOR HOSPICE › Subchapter 9 - NOTIFICATION OF CHANGES › Rule 15-16-1-1.9.8 - Change of Ownership

Current through June 25, 2024
Should a hospice program/facility wish to undergo a
						change of ownership, the facility must:
1. Submit a written request to Mississippi
					 State Department of Health to obtain a Change of Ownership (CHOW) Package.
2. Submit the following with the
					 request for CHOW within five (5) working days after the act of sale:
a. A new license application and the current
					 licensing fee. The purchaser of the agency must meet all criteria required for
					 initial licensure for hospice;
b.
					 Any changes in the name and or address of the agency;
c. Any changes in administrative personnel;
d. Copy of the Bill of Sale and/or
					 legal document reflecting change;
e. Copy of Articles of
					 Incorporation.