reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-48 - Water connections and outlets

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 48.
(a) Water
				Connection. Each mobile structure with a water distribution system shall be
				equipped with a three-fourths inch (3/4") threaded inlet connection. This
				connection shall be tagged or marked "fresh water connection". A matching cap
				or plug shall be provided to seal the water inlet when it is not in use, and
				shall be permanently attached to the mobile structure or water supply piping.
When a mobile structure includes expandable rooms or is
				  composed of two (2) or more units, fittings or connectors designed for such
				  purpose shall be provided to connect any water piping. When not connected, the
				  water piping shall be protected by means of matching caps or plugs in
				  accordance with section
				  675 IAC
				  15-2-87(b).
(b) Prohibited connections shall be as
				follows:
(1) The installation of potable
				water supply piping, fixture or appliance connections shall be made in a manner
				to preclude the possibility of backflow.
(2) No part of the water system shall be
				connected to any drainage or vent piping.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-49 - Water heaters; relief valves; prohibited location

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 49.
Relief valves shall be as follows:
(1) All water heaters shall be installed with
				approved and listed fully automatic valve or valves designed to provide
				temperature and pressure relief.
(2) Any temperature relief valve or combined
				pressure and temperature relief valve installed shall have the temperature
				sensing element immersed in the hottest water within the upper six inches (6")
				of the tank. It shall be set to start relieving at a pressure of one hundred
				fifty (150) psi or the rated working pressure of the tank whichever is lower
				and at or below a water temperature of 210°.
(3) Relief valves shall be provided with
				full-sized drains which shall be directed downward and discharge beneath the
				mobile structure. Drain lines shall be of a material listed for hot water
				distribution and shall drain fully by gravity, shall not be trapped, and shall
				not have their outlets threaded.
(4) Prohibited Location. Water heaters
				depending on combustion of fuel, shall not be installed in sleeping rooms,
				bathrooms/restrooms, closets.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-50 - Material standards for water piping and fittings

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 50.
(a) Piping
				Material. Water pipe shall be of standard weight brass, galvanized steel, Type
				K, L, or M copper tubing, approved or listed plastic, or other approved or
				listed material.
Plastic Piping. All plastic water piping and fittings in
				  mobile structures must be approved or listed for use with hot
				  water.
(b) Fittings.
				Appropriate fittings shall be used for all changes in size and where pipes are
				joined. The material and design of fittings shall conform to the type of piping
				used.
(1) Fittings for screw piping shall be
				standard and weight galvanized iron for galvanized iron and steel pipe, and of
				brass for brass piping. They shall be installed where required for change in
				direction, reduction of size, or where pipes are joined together.
(2) Fittings for copper tubing shall be cast
				brass or drawn copper (sweat soldered) or shall be listed or approved fittings
				for the purpose intended.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-51 - Installation of piping

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 51.
(a) Minimum
				Requirement. All piping equipment, appurtenances, and devices shall be
				installed in workmanlike manner and shall conform with the provisions and
				intent of this code.
(b) Screw
				pipe. Iron pipe-size brass or galvanized iron or steel pipe and fittings shall
				be joined with approved or listed standard pipe threads fully engaged in the
				fittings. Pipe ends shall be reamed to the full bore of the pipe. Pipe-joint
				compound shall be insoluble in water, shall be nontoxic and shall be applied to
				male threads only.
(c) Solder
				Fittings. Joints in copper water tube shall be made by the appropriate use of
				approved cast brass or wrought copper fittings, properly soldered together. The
				surface to be soldered shall be thoroughly cleaned bright by mechanical means.
				The joints shall be properly fluxed and made with approved solder.
(d) Flared Fittings. A flaring tool shall be
				used to shape ends of flared tubing to match the flare of fittings.
(e) Plastic Pipe and Fittings. Plastic pipe
				and fittings shall be joined by installation methods recommended by the
				manufacturer or by an approved standard.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-52 - Size of water supply piping

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 52.
(a) Minimum
				Size. The size of water supply piping and branch lines shall not be not less
				than sizes shown in Table 1B, as follows:
TABLE 1B
Minimun [sic.] Size Tubing and Pipe for
							 Water Distribution Systems
Number of Fixtures
Tubing (Nominal)
Pipe Iron Pipe Size (Inches)
Dia. (Inches)
Outer Dia. (Inches)
1
1/4*
3/8
1/2
2
3/8
1/2
1/2
3
1/2
5/8
1/2
4
1/2
5/8
1/2
5 or more
3/4
7/8
3/4
*6 feet maximum length. Exception: Three-eighths inch (3/8")
				  nominal diameter or one-half inch (1/2") optional diameter size for clothes
				  washing or dishwashing machines, unless larger size is recommended by the
				  fixture manufacturer.
One-half inch (1/2") nominal diameter or five-eighths inch
				  (5/8") optional diameter minimum size for flushometer or metering tube valves
				  unless otherwise specified in their listing.
No galvanized screw piping shall be less than one-half inch
				  (1/2") iron pipe size. (b) Sizing Procedure. Both hot and cold water systems
				  shall be computed by the following method:
(1) Size of Branch. Start at the remote
				outlet on any branch of the hot or cold water piping and progressively count
				towards the water service connection, computing the total number of fixtures
				supplied along each section of piping. Where branches are joined together, the
				number of fixtures on each branch shall be totalled so that no fixture is
				counted twice. Following down the left-hand column of Table 1B, in (a) above, a
				corresponding number of fixtures will be found. The required pipe or tubing
				size is indicated in the other columns on the same line.
(2) A water heater, food waste disposal unit,
				evaporative cooler or ice maker shall not be counted as a water-using fixture
				when computing pipe sizes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-53 - Drainage systems; materials

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 53.
(a) Pipe.
				Drainage piping shall be standard weight steel, wrought iron, brass, copper
				tube DWV, listed plastic, cast iron, or other approved or listed materials.
				Drainage piping shall be designed to provide for one-fourth inch (1/4") per
				foot grade in horizontal piping.
EXCEPTION: Horizontal drainage piping may have a uniform
				  slope of not less than one-eighth (1/8) of an inch per foot or one (1) percent
				  toward the point of disposal provided accessible cleanouts are installed per
				  Section 40 of this code.
(b)
				Fittings. Drainage fittings shall be recessed drainage pattern with smooth
				interior waterways of the same diameter as piping and shall be of a material
				conforming to the type of piping used. Fittings for screw pipe shall be cast
				iron, malleable iron, brass, or listed plastic with standard pipe threads.
				Fittings for copper tubing shall be cast brass or wrought copper. Socket-type
				fittings for plastic piping shall comply with listed standards. Brass or bronze
				adapter or wrought copper fittings shall be used to join copper tubing to the
				threaded pipe.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-54 - Drain outlets

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 54.
(a)
				Clearance from Drain Outlet. The drain outlet shall be provided with a minimum
				clearance of three inches (3") in any direction from all parts of the structure
				or appurtenances and with not less than eighteen inches (18") unrestricted
				clearance directly in front of the drain outlet.
(b) Drain Connector. The drain connector
				shall not be smaller than the piping to which it is connected and shall be
				equipped with a watertight cap or plug matching the drain outlet. The cap or
				plug shall be permanently attached to the mobile structure or drain
				outlet.
(c) The drain outlet and
				drain connector shall not be less than three inches (3") inside
				diameter.
(d) Preassembly of Drain
				Lines. Drain lines, provided by the manufacturer located under the mobile
				structure designed to bring the drain system to one distribution point and
				which may be damaged in transit, must be designed for proper site
				assembly.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-55 - Drain connections

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 55.
(a) Fixture
				Connections. Drainage piping shall be provided with approved or listed inlet
				fittings for fixture connections, correctly located according to the size and
				type of fixture to be connected.
(b) Toilet Connection. The drain connection
				for each toilet shall be three inches (3") minimum inside diameter and shall be
				fitted with an iron, brass, or listed plastic floor flange adaptor ring
				securely screwed, soldered or otherwise permanently attached to the drain
				piping, in an approved manner and securely fastened to the floor.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-56 - Size of drainage piping

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 56.
Fixture Load. Except as provided by
				  675 IAC 15-2-52, drain pipe sizes
				  shall be determined by the type of fixture and the total number connected to
				  each drain.
(1) Fixture Unit. A one
				and one-half inch (1 1/2") minimum diameter piping shall be required for one
				(1) and not more than three (3) individually vented fixtures.
(2) Fixture Unit. A two inch (2") minimum
				diameter piping shall be required for four (4) or more fixtures individually
				vented.
(3) A three inch (3")
				minimum diameter piping shall be required for toilets.
(4) When a combination of two (2) or more
				water closets, sinks, showers, urinals, or clothes washing equipment are
				installed, the Indiana plumbing code shall apply for mobile system-commercial
				transitory plumbing systems.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-57 - Wet-vented drainage system

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 57.
(a) A common
				vent may be used for two (2) fixtures set on the same floor level but
				connecting at different levels in the stack, provided the vertical drain is one
				pipe diameter larger than the upper fixture drain but in no case smaller than
				the lower fixture drain, whichever is the larger.
(b) Length of Trap Arm. Fixture traps shall
				be located within the distance given in Table 2B, in
				675 IAC 15-2-62. Not more than
				one (1) trap shall connect to a trap arm.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-58 - Offsets and branch fittings

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 58.
(a) Changes
				in Direction. Changes in direction of drainage piping shall be made by the
				appropriate use of approved or listed fittings, and shall be of the following
				angles: 1/32 bend, 1/16 bend, 1/8 bend, 1/6 bend, or 1/4 bend; or other
				approved or listed fittings or combination of fittings with equivalent radius
				or sweep.
(b) Horizontal to
				Vertical. Horizontal drainage lines, connecting with a vertical pipe shall
				enter through 1/8 bend "Y" branches, 1/6 bend "Y" branches, long-turn "TY"
				branches, sanitary "T" branches, or other approved or listed fittings, or
				combination of fittings having equivalent sweep. Fittings having more than one
				(1) branch at the same level shall not be used, unless the fitting is
				constructed so that the discharge from any one (1) branch cannot readily enter
				any other branch. However, a double sanitary "T" may be used when the drain
				line is increased not less than two (2) pipe sizes.
(c) Horizontal to Horizontal and Vertical to
				Horizontal. Horizontal drainage lines connecting with other horizontal drainage
				lines or vertical drainage lines connected with horizontal drainage lines shall
				enter through 1/8 bend degree "Y" branches, long-turn "TY" branches, or other
				approved or listed fittings or combination of fittings having equivalent sweep.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-59 - Grade of horizontal drainage piping

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 59.
Except for fixture connections on the inlet side of the
				  trap, horizontal drainage piping shall be run in practical alignment and have a
				  uniform grade of not less than one-fourth inch (1/4") per foot toward the
				  mobile structure drain outlet. Where it is impractical, due to the structural
				  features or arrangement of any mobile structure, to obtain a grade of
				  one-fourth inch (1/4") per foot, the pipe or piping may have a grade of not
				  less than one-eighth inch (1/8") per foot, when a full size cleanout is
				  installed at the upper end.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-60 - Vent piping and fittings

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 60.
(a) Each
				plumbing fixture trap shall be protected against siphonage and back pressure,
				and air circulation shall be ensured throughout all parts of the drainage
				system by means of vents installed in accordance with the requirements of this
				section and as otherwise required by this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-61 - Material standards for vent piping and fittings

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 61.
(a) Pipe.
				Vent piping shall be standard weight steel, wrought iron, brass, copper tube
				DWV, listed plastic cast iron or other approved or listed materials.
(b) Fittings. Appropriate fittings shall be
				used for all changes in direction or size and where pipes are joined. The
				material and design of vent fittings shall conform to the type of piping used.
(1) Fittings for screw pipe shall be cast
				iron, malleable iron, plastic, or brass, with standard pipe threads.
(2) Fittings for copper tubing shall be cast
				brass or wrought copper.
(3)
				Fittings for plastic piping shall be of appropriate material and made to
				approved or applicable standards.
(4) Brass adaptor fittings or wrought copper
				shall be used to join copper tubing to threaded pipe.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-62 - Size of vent piping

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 62.
(a) Main
				Vent. The drain piping for each toilet shall be vented by a one and one-half
				inch (1 1/2") minimum diameter vent connected to the main drain by one of the
				following methods:
(1) A one and one-half
				inch (1 1/2") diameter (min.) individual vent pipe or equivalent directly
				connected to the toilet drain and extended undiminished outside through the
				roof.
(2) A one and one-half inch
				(1 1/2") diameter (min.) continuous vent or equivalent indirectly connected to
				the toilet drain piping through a two inch (2") wet-vented drain that carries
				the waste of not more than one (1) fixture.
(3) Two (2) or more vented drains when at
				least one is wet-vented, or two inch (2") diameter (minimum), and each drain is
				separately connected to the main drain.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-63 - Anti-siphon trap vent

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 63.
(a)
				Anti-Siphon Trap Devices. Where an anti-siphon trap vent device is used as a
				secondary vent, it shall be installed in accordance with the conditions of its
				listing and shall be accessible. The lowest point of the valve seal when in the
				normally closed position shall not be less than six inches (6") above the flood
				level of the fixture. The toilet shall be vented in accordance with
				675 IAC 15-2-62. Only anti-siphon
				trap vent devices which have been approved shall be installed.
(b) Not more than two (2) fixtures
				individually protected by anti-siphon trap vent devices shall be drained by a
				common one and one-half inch (1 1/2") drain.
(c) Three (3) or more fixtures individually
				protected by anti-siphon trap vent devices shall be drained by a common two
				inch (2") drain.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-64 - Horizontal vent connections and grade

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 64.
(a)
				Horizontal Vents. Each vent shall extend vertically from its fixture "T" above
				the extreme flood level of the fixture it is venting before offsetting
				horizontally or being connected with any other vent pipe. Vents for horizontal
				drains shall connect above the centerline of the drain piping ahead of the
				trap.
(b) Grade. Vents shall be
				designed to drain back to the drainage system by gravity.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-65 - Vent terminal

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 65.
(a) Roof
				Extension. Each vent pipe shall extend through its flashing and terminate
				vertically, undiminished in size not less than two inches (2") above the roof
				Vent openings shall not be less than three feet, zero inches (3'0") away from
				any motor-driven air intake that opens into habitable areas.
(b) Flashing. The opening around each vent
				pipe shall be made watertight by an adequate flashing or flashing
				materials.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-66 - Vent caps

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 66.
Vent caps, if provided, shall be of the removable type
				  (without removing the flashing from the roof where it is required to perform
				  tests required by
				  675 IAC 15-2-68) or when the vent
				  is used as a clean out.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-67 - Water pressure tests

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 67.
Water System All water piping in the water distribution
				  systems shall be subjected to a pressure test. The test shall be made by
				  subjecting the system to air or water at fifty (50) psi for fifteen (15)
				  minutes without loss of pressure.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-68 - Waste and vent system tests

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 68.
The waste and vent system shall be tested by one (1) of the
				  three (3) following alternate methods for evidence or indication of
				  leakage.
(1) Water Test. Before
				plumbing fixtures are connected, all of the openings into the piping shall be
				plugged and the entire piping system subjected to a static water test for
				fifteen (15) minutes by filling it with water to the top of the highest vent
				opening. There shall be no evidence of leakage.
(2) Air Test. After all fixtures have been
				installed, the traps filled with water and the remaining openings securely
				plugged, the entire system shall be subjected to a two inch (2") (manometer)
				water column air pressure test. If the system loses pressure, leaks may be
				located with smoke pumped into the system, or with soap suds spread on the
				exterior of the piping (Bubble Test).
(3) Flood Level Test. The mobile structure
				shall be in a level position, all fixtures shall be connected, and the entire
				system shall be filled with water to the rim of the toilet bowl. (Tub and
				shower drains shall be plugged.) After all trapped air has been released, the
				test shall be sustained for not less than fifteen (15) minutes without evidence
				of leaks. Then the system shall be unplugged and emptied. The waste piping
				above the level of the toilet bowl shall then be tested and show no indication
				of leakage when the high fixtures are filled with water and emptied
				simultaneously to obtain the maximum possible flow in the drain
				piping.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-69 - Fixture tests

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 69.
The plumbing fixtures and connections shall be subjected to
				  a slow test by filling them with water and checking for leaks and retarded flow
				  while they are being emptied.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-70 - Shower compartment tests

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 70.
Nonmetallic shower compartments and receptors shall be
				  tested for leaks prior to being covered by finish material. Each pan shall be
				  filled with water to the top of the dam for not less than fifteen (15)
				  minutes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-71 - Scope of heating, cooling, and fuel-burning system standards

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 71.
(a) The
				provisions of
				675 IAC 15-2-71-675 IAC 15-2-87
				cover the heating, cooling, and fuel burning systems and equipment installed
				within or on mobile structures except for commercial mobile structures which
				shall conform to the Indiana mechanical code (675 IAC
				18-1
[675 IAC
				18-1 was repealed filed Oct 28, 1988, 3:00 p.m.: 12 IR
				588, eff Jan 2, 1989. See
				675 IAC
				18-1.3.]).
(b) Wherever rules of the commission and the
				provisions of
				675 IAC 15-2-71-675 IAC 15-2-87
				differ, the requirements of the provisions of
				675 IAC 15-2-71-675 IAC
				15-2-87 shall apply.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-73 - LP-gas systems; service line pressure

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 73.
(a) System S
				shall be of the vapor-withdrawal type.
(b) Gas, at a pressure not over fourteen
				inches (14") water (one-half (1/2) psi) shall be delivered from the system into
				the gas supply connection.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-74 - LP-gas containers

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 74.
(a) Maximum
				Capacity. No more than two (2) containers having an individual water capacity
				of not more than one hundred five (105) pounds (approximately forty-five (45)
				pounds LP-gas capacity), shall be installed on or in a compartment of any
				mobile structure.
(b) Construction
				of Containers. Containers shall be constructed and marked in accordance with
				the Indiana Flammable and Combustible Liquids and Gases Code (675 IAC
				22-1).
(c)
				Location of LP-gas containers and systems shall be as follows:
(1) LP-gas containers shall not be installed,
				nor shall provisions be made for installing or storing any LP-gas container,
				event
[sic]
temporarily, inside any mobile structure except of
				listed, completely self-contained hand torches, lanterns, or similar equipment
				with containers having a maximum water capacity of not more than two and
				one-half (2 1/2) pounds (approximately one (1) pound LP-gas
				capacity).
(2) Containers, control
				valves, and regulating equipment, when installed shall be mounted on the hitch
				of the mobile structure, or installed in a compartment that is vaportight to
				the inside of the mobile structure and accessible only from the outside. The
				compartment shall be ventilated at top and bottom to facilitate diffusion of
				vapors. The compartment shall be ventilated with two vents having an aggregate
				area of not less than two percent (2%) of the floor area of the compartment and
				shall open unrestricted to the outside atmosphere. The required vents shall be
				equally distributed between the floor and ceiling of the compartment. If the
				lower vent is located in the access door or wall, the bottom edge of the vent
				shall be flush with the floor level of the compartment. The top vent shall be
				located in the access door or wall with the bottom of the vent not more than
				twelve inches (12") below the ceiling level of the compartment. All vents shall
				have an unrestricted discharge to the outside atmosphere. Access doors or
				panels of compartments shall not be equipped with locks or require special
				tools or knowledge to open.
(3)
				Permanent and removable fuel containers shall be securely mounted to prevent
				jarring loose, slipping or rotating and the fastenings shall be designed and
				construed
[sic]
to withstand static loading in any direction
				equal to twice the weight less than four (4) based on the ultimate strength of
				the material to be used.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-75 - Oil tanks

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 75.
(a)
				Installation. Oil tanks and listed automatic pumps (oil filters) installed for
				gravity flow of oil to heating equipment shall be installed so that the top of
				the tank is no higher than eight feet (8') above the appliance oil control and
				the bottom of the tank is not less than eighteen inches (18") above the
				appliance oil control.
(b)
				Auxiliary Storage Tank. Oil supply tanks affixed to a mobile structure shall be
				so located as to require filling and draining from the outside and shall be in
				a place readily available for inspection. If the fuel supply tank is located in
				a compartment of a mobile structure and the compartment shall be ventilated at
				the bottom to permit diffusion of vapors and shall be insulated from the
				structural members of the body. Tanks so installed shall be provided with an
				outside fill and vent pipe and an approved liquid level gauge.
(c) Shutoff Valve. A readily accessible,
				approved manual shutoff valve shall be installed at the outlet of an oil supply
				tank. The valve shall be installed to close against the supply.
(d) Fuel Oil Filters. All oil tanks, except
				for integrally mounted tanks, shall be equipped with an approved oil filter or
				strainer located downstream from the tank shutoff valve. The fuel oil filter or
				strainer shall contain a sump with a drain for the entrapment of
				water.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-76 - Gas piping systems

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 76.
(a) General.
				The requirements of this section shall govern the installation of all fuel gas
				piping attached to any mobile structure. Gas delivered into the gas supply
				system shall be at a pressure not exceeding fourteen inch (14") water column
				(1/2 psi). None of the requirements listed in this section shall apply to the
				piping as a part of an appliance.
Rodent Resistance. All exterior openings around piping,
				  ducts, plenums or vents shall be sealed to resist the entrance of
				  rodents.
(b) Materials. All
				materials used for the installation, extension, alteration, or repair of any
				gas piping system shall be new and free from defects or internal obstructions.
				It shall not be permissible to repair defects in gas piping or fittings.
				Inferior or defective materials shall be removed and replaced with acceptable
				material. The system shall be made of materials having a melting point of not
				less than 1,450° F, except as provided in (e).
(1) Steel or wrought-iron pipe shall comply
				with the Indiana Mechanical Code (675 IAC 18-1
[675 IAC 18-1 was repealed filed
				Oct 28, 1988, 3:00 p.m.: 12 IR 588, eff Jan 2, 1989. See
				675 IAC 18-1.3.]).
Threaded brass pipe in iron pipe sizes may be used. Threaded brass
				pipe shall comply with the Indiana Mechanical Code (675 IAC 1 8-1
[675 IAC 18-1 was repealed filed
				Oct 28, 1988, 3:00 p.m.: 12 IR 588, eff Jan 2, 1989. See
				675 IAC
				18-1.3.]).
(2) Fittings for gas piping shall be wrought
				iron, malleable iron, steel, or brass (containing not more than seventy-five
				percent (75%) copper).
(3) Copper
				tubing shall be annealed type, Grade K or L, shall conform to the Indiana
				Mechanical Code (675 IAC 18-1
[675 IAC 18-1 was repealed filed
				Oct 28, 1988, 3:00 p.m.: 12 IR 588, eff Jan 2, 1989. See
				675 IAC 18-1.3.]).
When
				used on systems designed for natural gas, such tubing shall be internally
				tinned.
(4) Steel tubing shall
				conform to the Indiana Mechanical Code (675 IAC
				18-1
[675 IAC
				18-1 was repealed filed Oct 28, 1988, 3:00 p.m.: 12 IR
				588, eff Jan 2, 1989. See
				675 IAC
				18-1.3.]).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-77 - Oil piping systems

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 77.
(a) General.
				The requirements of this section shall govern the installation of all liquid
				fuel piping attached to any mobile structure. None of the requirements listed
				in this section shall apply to the piping in the appliance(s).
(b) Materials. All materials used for the
				installation extension, alteration, or repair, of any oil piping system shall
				be new and free from defects or internal obstructions. The system shall be made
				of materials having a melting point of not less than 1450° F., unless
				otherwise specified in this section. They shall consist of one or more of the
				materials described in (b)(1) through (b)(4).
(1) Steel or wrought-iron pipe shall comply
				with the Indiana Mechanical Code (675 IAC 18-1
[675 IAC 18-1 was repealed filed
				Oct 28, 1988, 3:00 p.m.: 12 IR 588, eff Jan 2, 1989. See
				675 IAC 18-1.3.]).
Threaded copper or brass pipe in iron pipe sizes may be
				used.
(2) Fittings for oil piping
				shall be wrought iron, malleable iron, steel, or brass (containing not more
				than seventy-five percent (75%) copper).
(3) Copper tubing shall be annealed type,
				Grade K or L conforming to the Indiana Mechanical Code (675 IAC
				18-1
[675 IAC
				18-1 was repealed filed Oct 28, 1988, 3:00 p.m.: 12 IR
				588, eff Jan 2, 1989. See
				675 IAC
				18-1.3.]).
(4) Steel tubing shall have a minimum wall
				thickness of 0.032 inch diameters up to one-half inch (1/2") and 0.049 inch for
				diameters one-half inch (1/2") and larger. Steel tubing shall be constructed in
				accordance with the Indiana Mechanic (675 IAC
				18-1
[675 IAC
				18-1 was repealed filed Oct 28, 1988, 3:00 p.m.: 12 IR
				588, eff Jan 2, 1989. See
				675 IAC
				18-1.3.]).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-78 - General appliance standards

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 78.
(a)
				Heat-producing appliances and vents, roof jacks and chimneys necessary for
				their installation in mobile structures shall be listed or certified by a
				nationally recognized testing agency for use in manufactured homes. Air
				conditioning units, combination air conditioning and heating units shall be
				listed or certified by a nationally recognized testing agency for the
				application for which the unit is intended.
(b) Fuel-burning heat-producing appliances
				and refrigeration appliances, except ranges and ovens, shall be of the vented
				type and vented to the outside.
(c)
				Fuel-burning appliances shall not be converted from one fuel to another fuel
				unless converted in accordance with the terms of their listing and the
				appliance manufacturer's instructions.
(d) Gas-fired absorption comfort-cooling
				units shall meet all the requirements of American National Standard for
				Gas-Fired Absorption Summer Air Conditions
[sic]
Appliances.
(e) Mechanical
				comfort-cooling units shall meet all the requirements of the Standard for
				Unitary Air Conditioning Equipment.
(f) Direct refrigeration systems serving any
				air conditioning or comfort-cooling system installed in a mobile structure
				shall conform to the Indiana Mechanical Code (675 IAC
				18-1
[675 IAC
				18-1 was repealed filed Oct 28, 1988, 3:00 p.m.: 12 IR
				588, eff Jan 2, 1989. See
				675 IAC 18-1.3.]).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-79 - Gas clothes dryers

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 79.
(a) Gas
				clothes dryers shall be exhausted to the outside by a moisture-lint exhaust
				duct and termination fitting listed or certified as components of the
				dryer.
(b) A clothes dryer
				moisture-lint exhaust duct shall not be connected to any other duct, vent or
				chimney.
(c) The exhaust duct shall
				not terminate beneath the mobile structure.
(d) Moisture-lint exhaust ducts shall not be
				connected with sheet metal screws or other fastening devices which extend into
				the interior of the duct.
(e) Gas
				Clothes Dryer Stub in Requirements. A mobile structure may be provided with
				"stubbed in" equipment at the factory to supply a gas clothes dryer for future
				installation by the owner provided it complies with the following provisions:
(1) The "stubbed in" gas outlet shall be
				provided with a shutoff valve, the outlet of which is closed by threaded pipe
				plug or cap.
(2) The "stubbed in"
				gas outlet shall be permanently labeled to identify it for use only as the
				supply connection for a gas clothes dryer.
(3) A moisture-lint exhaust duct system shall
				be roughed in by the manufacturer at the time of original installation. The
				moisture-lint exhaust system shall comply with the provisions of (a) through
				(d).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-80 - Installation of appliances

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 80.
(a) The
				installation of each appliance shall conform to the terms of its listing and
				the manufacturer's instructions. The installer shall leave the manufacturer's
				instructions attached to the appliance. Every appliance shall be secured in
				place to avoid displacement.
(b)
				All fuel-burning appliances, except ranges, ovens, illumination appliances,
				clothes dryers, solid fuel-burning fireplaces and solid fuel-burning fireplace
				stoves, shall be installed to provide for the complete separation of the
				combustion system from the interior atmosphere of the mobile structure.
				Combustion air inlets and flue gas outlets shall be listed or certified as
				components of the appliance. The required separation may be obtained by:
(1) the installation of direct vent system
				(sealed combustion system) appliances, or
(2) the installation of appliances within
				enclosures so as to separate the appliance combustion system and venting system
				from the interior atmosphere of the mobile structure. There shall not be any
				door, removable access panel, or other opening into the enclosure from the
				inside of the mobile structure. Any opening for ducts, piping, wiring, etc.,
				shall be sealed.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-81 - Venting and combustion air systems

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 81.
(a) The
				venting as required by
				675 IAC 15-2-78(b)
				 shall be accomplished by one or more of the
				methods given in (a)(1) and (a)(2) below:
(1)
				An integral vent system listed or certified as part of the appliance.
(2) A venting system consisting entirely of
				listed components, including roof jack, installed in accordance with the terms
				of the appliance listing and the appliance manufacturer's instructions (see
				675 IAC
				15-2-80(b)).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-82 - Operating instructions

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 82.
Operating instructions shall be provided with appliances.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-83 - Appliance information

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 83.
Information on clearances, input rating, lighting and
				  shutdown shall be attached to the appliances with the same permanence as the
				  nameplate, and so located that it is easily readable when the appliance is
				  properly installed.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-84 - Access to appliances

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 84.
Every appliance shall be accessible for inspection, service,
				  repair, and replacement without removing permanent construction. Sufficient
				  room shall be available to enable the operator to observe the burner, control,
				  and ignition means while starting the appliance.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-85 - Location of appliances

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 85.
Heat-producing appliances shall be so located that no doors,
				  drapes, or other such material can be placed or swung closer to the front of
				  the appliance than the clearances specified on the labeled appliances.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-86 - Clearances

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 86.
Clearances between heat-producing appliances and adjacent
				  surfaces shall not be less than specified in the terms of their listing.
				  Clearance spaces shall be framed in or guarded to prevent creation of storage
				  space within the clearance specified.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-92 - Receptacle outlets

Current through July 10, 2024
Authority: IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 92.
(a) All
				receptacle outlets shall be:
(1) of grounding
				type;
(2) installed according to
				Section 210-7 of the Indiana Electrical Code (675 IAC
				17-1
[675 IAC
				17-1 was repealed filed Feb 17, 1987, 3:15 p.m.: 10 IR
				1389, eff Mar 1, 1987 [IC
				4-22-2-36 suspends the
				effectiveness of a rule document for thirty (30) days after filing with the
				secretary of state. LSA Document #86-153 was filed Feb 17, 1987.].]);
(3) except when supplying specific
				appliances, be parallel-blade, fifteen (15) ampere, one hundred twenty-five
				(125) volt, either single or duplex.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-93 - Fixtures; appliances

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 93.
(a)
				Electrical materials, devices, appliances, fittings, and other equipment
				installed, intended for use in, or attached to the mobile structure shall be
				approved for the application and shall be connected in an approved manner when
				in service. Facilities shall be provided to securely fasten appliances when the
				mobile structure is in transit.
(b)
				Specifically approved pendant-type fixtures or pendant cords shall be permitted
				in mobile structures.
(c) If a
				lighting fixture is provided over a bathtub or in a shower stall, it shall be
				of the enclosed and gasketed type approved for wet locations.
(d) The switch for shower lighting fixtures
				and exhaust fans located over a tub or in a shower stall shall be located
				outside the tub or shower space.
(e) Any combustible wall or ceiling finish
				exposed between the edge of a fixture, canopy, or pan and an oulet box shall be
				covered with noncombustible material.
(f) Every appliance shall be accessible for
				inspection, service, repair, or replacement without removal of permanent
				construction.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-95 - Grounding

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 95.
General. Grounding of both electrical and nonelectrical
				  metal parts in a mobile structure shall be through connection to a grounding
				  bus in the mobile structure distribution panelboard. The grounding bus shall be
				  grounded through the green-colored conductor in the supply cord or the feeder
				  wiring to the service ground in the service-entrance equipment located adjacent
				  to the mobile structure location. Neither the frame of the mobile structure nor
				  the frame of any appliance shall be connected to the neutral conductor in the
				  mobile structure.