reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-135 - Section G2412.1; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 135.
Change the text of SECTION G2412.1 to read as
				  follows:
This section shall govern the design, installation, and
				  modification of piping systems. The applicability of this code to piping
				  systems extends from the point of delivery to the connections with the
				  appliances and includes the design, materials, components, fabrication,
				  assembly, installation, and testing of such piping systems.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-136 - Section G2412.9; identification

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 136.
Change the text of SECTION G2412.9 to read as
				  follows:
Each uncut length of pipe and tubing and each pipe fitting,
				  utilized in a fuel gas system, shall bear the identification of the
				  manufacturer.
Exceptions:
1. Steel
				pipe sections that are cut from longer sections of pipe.
2. Steel pipe fittings 2 inches or less in
				size.
3. Where identification is
				provided on the product packaging or crating.
4. Where other approved documentation is
				provided.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-137 - Section G2414.3; other materials

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 137.
Change the text of SECTION G2414.3 to read as
				  follows:
Material not covered by the standards specifications listed
				  herein shall be investigated and tested to determine that it is safe and
				  suitable for the proposed service, and, in addition, shall be recommended for
				  that service by the manufacturer and shall be approved by the building
				  official.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-138 - Section G2420.2; meter valve

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 138.
Change the text of SECTION G2420.2 to read as
				  follows:
Every nonutility owned meter shall be equipped with a shutoff
				  valve located on the supply side of the meter.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-139 - Section G2422.1; connecting appliances

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 139.
Change the text of ITEM 2 of SECTION G2422.1 to read as
				  follows:
2. Corrugated stainless steel
				tubing (CSST) where installed in accordance with the manufacturer's
				instructions and when protected from damage by a semirigid sleeve or conduit
				where it enters the appliance.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-140 - Section G2425.1; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 140.
Change the text of SECTION G2425.1 to read as
				  follows:
This section shall govern the installation and approval of
				  factory built chimneys, chimney liners, vents, and connectors and the
				  utilization of masonry chimneys serving gas-fired appliances.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-141 - Section G2427.4.1.1; plastic vent joints

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 141.
Delete the last sentence of the text of SECTION G2427.4.1.1
				  without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-142 - Section G2427.6.11; marking

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 142.
Delete SECTION G2427.6.11 in its entirety without
				  substitution, and renumber SECTION G2427.6.12 to read as SECTION G2427.6.11.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-143 - Section G2427.7.13; marking

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 143.
Delete SECTION G2427.7.13 in its entirety without
				  substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-144 - Section G2427.8; venting system termination location

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 144.
Change the text of SECTION G2427.8 to read as
				  follows:
The location of venting system terminations shall comply with
				  the following:
1. A mechanical draft
				venting system shall terminate not less than 3 feet (914 mm) above any
				forced-air inlet located within 10 feet (3,048 mm).
Exceptions:
1. This
				provision shall not apply to the combustion air intake of a direct-vent
				appliance.
2. This provision shall
				not apply to the separation of the integral outdoor air inlet and flue gas
				discharge of listed outdoor appliances.
2. A mechanical draft venting system,
				excluding direct vent appliances, shall terminate not less than four (4) feet
				(1,219 mm) below, four (4) feet (1,219 mm) horizontally from, or one (1) foot
				(305 mm) above any door, operable window or gravity air inlet into any
				building. The bottom of the vent terminal shall be located not less than 12
				inches (305 mm) above finished ground level.
3. If the appliance and manufacturer's
				installation instructions are not available, the clearances for
				through-the-wall, direct-vent terminals shall be in accordance with Table
				G2427.8.
4. Through the wall vents
				for Category II and IV appliances and noncategorized condensing appliances
				shall not terminate over public walkways or over an area where condensate or
				vapor could create a nuisance or hazard or could be detrimental to the
				operation of regulators, relief valves, or other equipment. Drains for
				condensate shall be installed in accordance with the appliance and vent
				manufacturer's instructions.
5.Vent
				systems for Category IV appliances that terminate through an outside wall of a
				building and discharge flue gases perpendicular to the adjacent wall shall be
				located not less than 10 feet (3,048 mm) horizontally from an operable opening
				in an adjacent building. This requirement shall not apply to vent terminals
				that are 2 feet (607 mm) or more above or 25 feet (7,620 mm) or more below
				operable openings.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-145 - Section G2428.1; Definitions

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 145.
Change the definition of APPLIANCE CATEGORIZED VENT
				  DIAMETER/AREA in SECTION G2428.1 to read as follows:
The minimum vent area/diameter permissible for Category I
				  appliances to maintain a nonpositive vent static pressure when tested in
				  accordance with approved nationally recognized standards.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-146 - Section G2431.1; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 146.
Change the text of SECTION G2431.1 to read as
				  follows:
Sections G2432 through G2454 shall govern the approval,
				  design, installation, construction, and alteration of the appliances and
				  equipment specifically identified herein.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-147 - Section G2448.1; water heaters

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 147.
Add an EXCEPTION to the end of SECTION G2448.1 to read as
				  follows:
EXCEPTION: Boilers and pressure vessels regulated pursuant to
				  IC 22-15-6 are not regulated by this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-148 - Section G2452.1; boilers

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 148.
Add an EXCEPTION to the end of SECTION G2452.1 to read as
				  follows:
EXCEPTION: Boilers and pressure vessels regulated pursuant to
				  IC 22-15-6 are not regulated by this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-149 - Section P2501; general

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 149.
Delete SECTION P2501 in its entirety and substitute to read
				  as follows:
The provisions of Chapters 1, 2, and 25 through 32 of this
				  code shall establish the requirements for plumbing and plumbing systems.
				  Compliance with the Indiana Plumbing Code (675 IAC 16) shall be allowed instead
				  of compliance with this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-150 - Section P2502; existing plumbing systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 150.
Change SECTION P2502 as follows:
(1) Delete the text of SECTION P2502.1 and
				substitute to read as follows: See the General Administrative Rules (675 IAC
				12).
(2) Delete SECTION P2502.2 in
				its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-151 - Section P2503.1; reserved

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 151.
Change SECTION P2503.1 as follows:
(1) Change the title of SECTION P2503.1 to
				read as follows: SECTION P2503.1 RESERVED.
(2) Delete the text of SECTION P2503.1
				without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-152 - Section P2503.2; concealment

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 152.
Change the text of SECTION P2503.2 to read as
				  follows:
A plumbing or drainage system, or part thereof, shall not be
				  covered, concealed, or put into use until it has been tested.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-153 - Section P2503.5.2; finished plumbing

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 153.
Change the text of ITEM 2 of SECTION P2503.5.2, without
				  amending ITEM 2.1 or 2.2, to read as follows: 2. Gas tightness. Where required
				  by local ordinance, a final test for gas tightness of the DWV system shall be
				  made by the smoke or peppermint test as follows:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-154 - Section P2503.8; testing of backflow prevention devices

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 154.
Change SECTION P2503.8 as follows:
(1) Change the title and text of SECTION
				P2503.8 to read as follows: SECTION P2503.8 TESTING OF BACKFLOW PREVENTION
				DEVICES. Testing of backflow prevention devices shall comply with Section
				P2503.8.1.
(2) Delete SECTION
				P2503.8.1 in its entirety without substitution.
(3) Change the title and text of SECTION
				P2503.8.2 to read as follows:
SECTION P2503.8.1 TESTING.
Reduced pressure principle, double check, double check
				  detector, and pressure vacuum breaker backflow preventer assemblies shall be
				  tested at the time of installation.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-155 - Section P2603.1; general

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 155.
Change the text of SECTION P2603.1 to read as
				  follows:
In the process of installing any part of a plumbing and
				  drainage installation, the finished floors, walls, ceilings, tile work, or any
				  other part of the building or premises that must be changed or replaced shall
				  be left in a safe structural condition in accordance with the requirements of
				  the building portion of this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-156 - Section P2603.4; pipes through foundation walls

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 156.
Change the text of SECTION P2603.4 to read as
				  follows:
A pipe that passes through a foundation wall shall be
				  provided with a relieving arch, or a pipe sleeve shall be built into the
				  foundation wall. The sleeve shall be larger than the pipe passing through the
				  wall.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-157 - Section P2603.5; freezing

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 157.
Change the text of SECTION P2603.5 to read as
				  follows:
In localities having a winter design temperature of 32°F
				  (0°C) or lower as shown in Table R301.2(1) of this code, a soil or waste
				  pipe shall not be installed outside of a building, in exterior walls, in attics
				  or crawl spaces, or in any other place subjected to freezing temperature unless
				  adequate provision is made to protect it from freezing by insulation or heat,
				  or both. Waterlines shall not be installed outside the thermal envelope of a
				  building, in attics or crawlspaces, or in any other place subjected to freezing
				  temperatures unless adequate provision is made to protect such waterlines from
				  freezing by insulation, ambient heat, or alternate heat source. No waterlines
				  shall be concealed in walls above grade that are part of the thermal envelope.
				  Water service pipe shall be installed not less than 12 inches (305 mm) deep and
				  not less than 6 inches (152 mm) below the frost line.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-158 - Section P2603.5.1; sewer depth

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 158.
Delete SECTION P2603.5.1 in its entirety without
				  substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-159 - Section P2609.1; identification

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 159.
Change the text of SECTION P2609.1 to read as
				  follows:
Each length of pipe, tubing, and each pipe fitting, trap,
				  fixture, material, and device utilized in a plumbing system shall bear the
				  identification of the manufacturer and any markings required by the applicable
				  referenced standards. Nipples and sections created from the cutting and
				  threading of approved pipe shall not be required to be identified.
EXCEPTION: Where the manufacturer identification cannot be
				  marked on pipe fittings and pipe nipples because of the small size of such
				  fittings, the identification shall be printed on the item packaging or on
				  documentation provided with the item.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-160 - Section P2609.2; installation of materials

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 160.
Change the text of SECTION P2609.2 to read as
				  follows:
Materials used shall be installed in strict accordance with
				  the standards under which the materials are approved. In the absence of such
				  installation procedures, the manufacturer's instructions shall be followed.
				  Where the requirements of referenced standards or manufacturer's instructions
				  do not conform to the minimum provisions of this code, the provisions of this
				  code shall apply.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-161 - Section P2706.1.2; standpipes

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 161.
Add an EXCEPTION to the end of SECTION P2706.1.2 to read as
				  follows:
EXCEPTION: A 1 1/2 inch (38 mm) standpipe shall extend a
				  minimum of 30 inches (762 mm) and a maximum of 42 inches (1,067 mm).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-162 - Section P2801.6; required pan

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 162.
Add an EXCEPTION to the end of SECTION P2801.6 to read as
				  follows:
EXCEPTION: When installed on a water-resistant floor sloped
				  to a floor drain in the same room or space.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-163 - Section P2903.5; water hammer

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 163.
Change the text of SECTION P2903.5 to read as
				  follows:
The flow velocity of the water distribution system shall be
				  controlled to reduce the possibility of water hammer. When installed,
				  water-hammer arrestors shall be installed in accordance with the manufacturer's
				  instructions. Water-hammer arrestors shall conform to ASSE 1010.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-164 - Section P2903.9.1; service valve

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 164.
Change the text of SECTION P2903.9.1 to read as
				  follows:
Each dwelling unit shall be provided with an accessible main
				  shutoff valve near the entrance of the water service. The valve shall be of a
				  full-open type having nominal restriction to flow, with provision for drainage
				  such as a bleed orifice or installation of a separate drain valve.
				  Additionally, the water service shall be valved at the curb or lot line in
				  accordance with local ordinance.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-165 - Section P2906.9.1.2; CPVC plastic pipe

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 165.
Change the text of SECTION P2906.9.1.2 to read as
				  follows:
Joint surfaces shall be clean and free from moisture. Joints
				  shall be made in accordance with the pipe, fitting, or solvent cement
				  manufacturer's installation instructions. Where such instructions require a
				  primer to be used, an approved primer shall be applied, and a solvent cement
				  conforming to ASTM F493 shall be applied to joint surfaces. Where such
				  instructions allow for a one-step solvent cement, yellow or red in color and
				  conforming to ASTM F493, to be used, the joint surfaces shall not require
				  application of a primer before the solvent cement is applied. The joint shall
				  be made while the cement is wet, and in accordance with ASTM D2846 or ASTM
				  F493. Solvent cement joints shall be permitted above or below ground.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-166 - Section P2906.9.1.3; CPVC/AL/CPVC pipe

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 166.
Change the text of SECTION P2906.9.1.3 to read as
				  follows:
Joint surfaces shall be clean and free from moisture, and an
				  approved primer shall be applied. Solvent cement conforming to ASTM F493 shall
				  be applied to all joint surfaces. The joint shall be made while the cement is
				  wet and in accordance with ASTM D2846 or ASTM F493. Solvent-cemented joints
				  shall be installed above or below ground.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-167 - Section P2910.4; reserved

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 167.
Change SECTION P2910.4 as follows:
(1) Change the title of SECTION P2910.4 to
				read as follows:
SECTION P2910.4 RESERVED.
(2) Delete the text of SECTION P2910.4
				without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-168 - Section P2912.15; tests

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 168.
Change SECTION P2912.15 as follows:
(1) Change the title and text of SECTION
				P2912.15 to read as follows:
SECTION P2912.15 TESTS. Tests shall be performed in
				  accordance with Sections P2912.15.1 through P2912.15.8.
(2) Change the title and text of SECTION
				P2912.15.1 to read as follows:
SECTION P2912.15.1 ROOF GUTTER TEST.
Roof gutters shall be tested to verify that the installation
				  and slope is in accordance with Section P2912.5.1. Gutters shall be tested by
				  pouring not less than 1 gallon of water (3.8 L) into the end of the gutter
				  opposite the collection point. The gutter being tested shall not leak and shall
				  not retain standing water.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-169 - Section P2913.1; general

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 169.
Change the text of SECTION P2913.1 to read as
				  follows:
The provisions of this section shall govern the construction,
				  installation, and alteration of systems supplying nonpotable reclaimed water.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-170 - Section P2913.4; tests

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 170.
Change SECTION P2913.4 as follows:
(1) Change the title and text of SECTION
				P2913.4 to read as follows: SECTION P2913.4 TESTS.
Tests shall be performed in accordance with Sections
				  P2913.4.1 and P2913.4.2.
(2) Change the title of SECTION P2913.4.2 to
				read as follows:
SECTION P2913.4.2 TESTING OF BACKFLOW PREVENTION ASSEMBLIES.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-171 - Section P3003.9.2; solvent cementing

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 171.
Change the text of SECTION P3003.9.2 to read as
				  follows:
Joint surfaces shall be clean and free from moisture. A
				  primer that conforms to ASTM F656 shall be applied. Solvent cement conforming
				  to ASTM D2564, CSA B137.3, or CSA B181.2 shall be applied to all joint
				  surfaces. The joint shall be made while the cement is wet and shall be in
				  accordance with ASTM D2855. Solvent-cement joints shall be installed above or
				  below ground.
EXCEPTION: A primer shall not be required where all of the
				  following conditions apply:
1. The
				solvent cement used is third party certified as conforming to ASTM
				D2564.
2. The solvent cement is
				used only for joining PVC drain, waste and vent pipe, and fittings in
				nonpressure applications in sizes up to and including 4 inches (102 mm) in
				diameter.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-172 - Section P3005.1.2; heel-inlet or side-inlet quarter bends, drainage

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 172.
Change the text of SECTION P3005.1.2 to read as
				  follows:
Heel-inlet quarter bends shall be an acceptable means of
				  connection, except where the quarter bends serves a water closet. A low-heel
				  inlet shall not be used as a wet-vented connection. Side-inlet quarter bends
				  shall be an acceptable means of connection for both wet venting and stack
				  venting arrangements.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-173 - Section P3005.2.2; reserved

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 173.
Change SECTION P3005.2.2 as follows:
(1) Change the title of SECTION P3005.2.2 to
				read as follows:
SECTION P3005.2.2 RESERVED.
(2) Delete the text of SECTION P3005.2.2
				without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-174 - Section P3005.2.4; changes of direction

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 174.
Change the text of SECTION P3005.2.4 to read as
				  follows:
Where a horizontal drainage pipe or a building drain has a
				  change of horizontal direction greater than 45 degrees (0.79 rad), a cleanout
				  shall be installed at the change of direction. Where more than one change of
				  horizontal direction greater than 45 degrees (0.79 rad) occurs within 40 feet
				  (12,192 mm) of developed length of piping, the cleanout installed for the first
				  change of direction shall serve as the cleanout for all changes in direction
				  within that 40 feet (12,192 mm) of developed length of piping.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-175 - Section P3005.4; drain pipe sizing

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 175.
Change the text of ITEM 5 of SECTION P3005.4 to read as
				  follows:
5. Determine the pipe
				diameter and slope of the building drain based on the accumulated d.f.u.
				values, using Table P3005.4.2.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-176 - Section P3005.4.2; building drain size and slope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 176.
Change the title of SECTION P3005.4.2 to read as
				  follows:
SECTION P3005.4.2 BUILDING DRAIN SIZE AND SLOPE.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-177 - Table P3005.4.2; maximum number of fixture units allowed to be connected to the building drain or building drain branches

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 177.
Change the title of TABLE P3005.4.2 to read as
				  follows:
TABLE 3005.4.2 MAXIMUM NUMBER OF FIXTURE UNITS ALLOWED TO BE
				  CONNECTED TO THE BUILDING DRAIN OR BUILDING DRAIN BRANCHES.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-178 - Section P3007.3.5; ejector connection to the drainage system

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 178.
Change the text of SECTION P3007.3.5 to read as
				  follows:
Pumps connected to the drainage system shall connect to
				  building drain, soil stack, waste stack, or horizontal branch drain.
Where the discharge line connects into horizontal drainage
				  piping, the connection shall be made through a wye fitting into the top of the
				  drainage piping and such wye fitting shall be located not less than 10 pipe
				  diameters from the base of any soil stack, waste stack, or fixture drain.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-179 - Section P3009; subsurface landscape irrigation systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 179.
Delete SECTION P3009 in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-180 - Section P3010; replacement of underground building sewers and building drains by pipe burst methods

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 180.
Delete SECTION P3010 in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-181 - Section P3011; replacement of underground sewers by PVC fold and form methods

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 181.
Delete SECTION P3011 in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-182 - Section P3101.1; general

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 182.
Change the text of SECTION P3101.1 to read as
				  follows:
This chapter shall govern the selection and installation of
				  piping, tubing, and fittings for vent systems. This chapter shall control the
				  minimum diameter of vent pipes, circuit vents, branch vents, and individual
				  vents, and the size and length of vents and various aspects of vent stacks and
				  stack vents. Additionally, this chapter regulates vent grades and connections,
				  height above fixtures and relief vents for stacks and fixture traps, and the
				  venting of sumps.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-183 - Section P3101.2.1; venting required

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 183.
Add an EXCEPTION to the end of SECTION P3101.2.1 to read as
				  follows:
EXCEPTION: Floor drains.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-184 - Section P3101.4; extension outside a structure

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 184.
Delete SECTION P3101.4 in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-185 - Section P3103.1.1; roof extension

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 185.
Change the text of SECTION P3103.1.1 to read as
				  follows:
Open vent pipes that extend through a roof that do not meet
				  the conditions of Section P3103.1.2 or P3103.1.3 shall terminate not less than
				  12 inches (300 mm) above the highest point where the vent passes through the
				  roof.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-186 - Section P3103.2; frost closure

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 186.
Delete SECTION P3103.2 in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-187 - Section P3105.1; distance of trap from vent

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 187.
Change the title "EXCEPTION" in SECTION P3105.1 to read as
				  "EXCEPTIONS", number the first exception as "1.", and add a second exception to
				  SECTION P3105.1 to read as follows: 2. A trap arm serving only a bathtub,
				  tub/shower combination, or shower may be increased to 9 feet with a slope of
				  not less than c inch per foot.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-188 - Section P3114.3; where permitted

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 188.
Change the text of SECTION P3114.3 to read as
				  follows:
Individual vents, branch vents, and circuit vents shall be
				  permitted to terminate with a connection to an air admittance valve.
Individual and branch-type air admittance valves shall vent
				  only fixtures that are on the same floor level and connect to a horizontal
				  branch drain.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-189 - Section P3201.2.1.1; potable water trap seal protection

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 189.
Change the title and text of SECTION P3201.2.1.1 to read as
				  follows: SECTION P3201.2.1.1 POTABLE WATER TRAP SEAL PROTECTION.
Traps shall be of a deep seal design or a potable
				  water-supplied trap seal primer valve shall supply water to the trap.
				  Water-supplied trap seal primer valves shall conform to ASSE 1018. The
				  discharge pipe from the trap seal primer valve shall connect to the trap above
				  the trap seal on the inlet side of the trap.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-190 - Table P3201.7; size of traps for plumbing fixtures

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 190.
Change TABLE P3201.7 to read as follows:
TABLE P3201.7
SIZE OF TRAPS FOR PLUMBING FIXTURES
PLUMBING FIXTURE
TRAP SIZE MINIMUM (inches)
Bathtub (with or without shower head or whirlpool
							 attachments)
1 1/2
Bidet
1 1/4
Clothes washer standpipe
1 1/2a or 2
Dishwasher (on separate trap)
1 1/2
Floor drain
2
Kitchen sink (one or two traps, with or without
							 dishwasher and food waste disposer)
1 1/2
Laundry tub (one or more compartments)
1 1/2
Lavatory
1 1/4
Shower (based on the total flow rate through
							 showerheads and bodysprays)
Flow rate:
5.7 gpm and less
1 1/2
More than 5.7 gpm up to 12.3 gpm
2
More than 12.3 gpm up to 25.8 gpm
3
More than 25.8 gpm up to 55.6 gpm
4
For SI: 1 inch = 25.4 mm, 1 gallon per minute = 3.785
				  L/m.
a. Standpipe shall extend a
				minimum 30 inches (762 mm) above the trap weir for 1 1/2 inch (38 mm)
				standpipes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-191 - Section E3401.2; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 191.
Delete the text of SECTION E3401.2 and substitute to read as
				  follows:
Chapters 1 and 34 through 43 of this code shall cover the
				  installation of electrical systems, equipment, and electrical components for
				  the permanent heating, ventilating, air conditioning, plumbing, sanitary,
				  emergency detection, emergency communication, or fire or explosion suppression
				  systems that are part of a Class 1 structure, Class 2 structure townhouse, one
				  and two family dwellings and their accessory structures. Services within the
				  scope of this code shall be limited to 120/240-volt, 0 to 400 ampere,
				  single-phase systems. The omission from these chapters of any material or
				  method of construction provided for in the Indiana Electrical Code (675 IAC 17)
				  shall not be construed as prohibiting the use of such material or method of
				  construction. Electrical systems, equipment, or components not specifically
				  addressed in these chapters shall comply with the applicable provisions of the
				  Indiana Electrical Code (675 IAC 17). Compliance with the Indiana Electrical
				  Code (675 IAC 17) is allowed instead of compliance with this code. This section
				  does not require the installation of an electrical system in Class 2
				  structures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-192 - Section E3401.3; not covered

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 192.
Add ITEM 3 to SECTION E3401.3 to read as follows:
3. Installations not part of a Class 1
				structure or Class 2 structure townhouse or one and two family dwelling and
				their accessory structures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-193 - Section E3403.2; compliance

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 193.
Change the title and text of SECTION E3403.2 to read as
				  follows:
SECTION E3403.2 COMPLIANCE.
New electrical work and parts of existing systems affected by
				  new work or alterations shall be installed in compliance with the requirements
				  of Chapters 34 through 43 of this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-194 - Section E3405.2; working clearances for energized equipment and panelboards

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 194.
Add a sentence to the end of the first paragraph of the text
				  of SECTION E3405.2 to read as follows: A panelboard installed behind the swing
				  of a door shall not be considered in violation of these
				  provisions.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-195 - Section E3501; general

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 195.
Change SECTION E3501 as follows:
(1) Change the definition of APPROVED to read
				as follows:
APPROVED means, as to materials, equipment, appliances,
				  methods of design, and types of construction, acceptance by the building
				  official by one (1) of the following methods:
(1) investigation or tests conducted by
				recognized authorities;
(2)
				investigation or tests conducted by technical or scientific organizations;
				or
(3) accepted principles.
The investigation, tests, or principles shall establish that
				  the materials, equipment, appliances, methods of design, and types of
				  construction are safe for their intended purpose.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-196 - Section E3601.2; number of services

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 196.
Add an EXCEPTION to the end of SECTION E3601.2 to read as
				  follows:
EXCEPTION: A building with more than one occupancy shall be
				  permitted to have one set of service-entrance conductors for each service, run
				  to each occupancy.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-197 - Section E3601.6.2; service disconnect location

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 197.
Add a sentence to the end of SECTION E3601.6.2 to read as
				  follows:
Conductors shall be considered outside of a building or
				  structure under any of the following conditions:
1. where installed under not less than 2
				inches (51 mm) of concrete beneath a building or other structure;
2. where installed within a building or other
				structure in a raceway that is encased in concrete or brick not less than 2
				inches thick; or
3. where
				installed in conduit and under not less than 18 inches (457 mm) of earth
				beneath a building or other structure.