reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 1 - GENERAL PROVISIONS › Section R. 325.17103 - Adoption by reference; purchase

Current through Vol. 24-12, July 15, 2024
Rule 103. The following standards are incorporated by
					 reference in these rules:
(a) The
				  national fire protection association standard, NFPA No.32 entitled,
				  "Drycleaning Plants 2000." The standard is available for inspection at the
				  Lansing office of the Department of Environmental Quality, Air Quality
				  Division, Constitution Hall, 525 West Allegan Street, P.O. Box 30260, Lansing,
				  Michigan 48909-7760, and may be purchased at a cost of $22.25, as of the time
				  these rules were promulgated, from the National Fire Protection Association, 1
				  Battery March Park, P. O. Box 9101, Quincy, Massachusetts 02269-9101.
(b) "National Perchloroethylene Air Emission
				  Standards for Dry Cleaning Facilities," 40 C.F.R., part 63, subpart M (2002). A
				  copy of these regulations may be inspected at the Lansing office of the air
				  quality division of the department of environmental quality. Copies of 40
				  C.F.R., part 63, may be obtained from the Department of Environmental Quality,
				  Air Quality Division, 525 West Allegan Street, P.O. Box 30260, Lansing,
				  Michigan 48909-7760, at a cost as of the time of adoption of these rules of
				  $56.00; from the Superintendent of Documents, P.O. Box 371954, Pittsburgh,
				  Pennsylvania 15250-7954, at a cost as of the time of adoption of these rules of
				  $56.00; or on the United States government printing office internet web site at
http://www.gpo.gov
.
(c) "Standards of Performance for Petroleum
				  Dry Cleaners," 40 C.F.R., part 60, subpart JJJ. A copy of these regulations may
				  be inspected at the Lansing office of the air quality division of the
				  department of environmental quality. Copies of 40 C.F.R., part 60, may be
				  obtained from the Department of Environmental Quality, Air Quality Division,
				  525 West Allegan Street, P.O. Box 30260, Lansing, Michigan, 48909-7760, at a
				  cost as of the time of the adoption of these rules of $56.00; from the
				  Superintendent of Documents, P.O. Box 371954, Pittsburgh, Pennsylvania
				  15250-7954, at a cost as of the time of adoption of these rules of $56.00; or
				  on the United States government printing office internet web site at
http://www.gpo.gov
.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 1 - GENERAL PROVISIONS › Section R. 325.17104 - Daily inspections; recordkeeping of dry cleaning machines and related equipment

Current through Vol. 24-12, July 15, 2024
Rule 104. The owner or operator shall conduct daily
					 surveillance checks of each dry cleaning machine and related equipment and
					 perform necessary maintenance in order to prevent unnecessary loss of dry
					 cleaning solvent or solvent vapors. Owners or operators of type IV dry cleaning
					 establishments shall maintain records according to the requirements defined
					 under the "National Perchloroethylene Air Emission Standards for Dry Cleaning
					 Facilities," 40 C.F.R., Part 63, subpart M, adopted by reference in R
					 325.17103. Owners or operators of type I, II or III dry cleaning establishments
					 shall maintain records according to the requirements defined under the "
					 Standards of Performance for Petroleum Dry Cleaners," 40 C.F.R., Part 60,
					 subpart JJJ, adopted by reference in R 325.17103.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 1 - GENERAL PROVISIONS › Section R. 325.17106 - Dry cleaning solvent

Current through Vol. 24-12, July 15, 2024
Rule 106. The use of dry cleaning solvents, other than
					 those specifically designated for a machine are prohibited, unless prior
					 approval is obtained from the department.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 1 - GENERAL PROVISIONS › Section R. 325.17107 - Establishment requirements generally

Current through Vol. 24-12, July 15, 2024
Rule 107. A dry cleaning establishment shall comply with
					 all of the following provisions:
(a)
				  Filter cartridges, filter residues, and other residues containing dry cleaning
				  solvent shall be stored in a suitable covered container and properly disposed
				  of so as to not create a hazard to the health or safety of a person or persons
				  at a type IV dry cleaning establishment or by preventing the risk of a fire or
				  explosion from occurring at a type I, II, or III dry cleaning
				  establishment.
(b) Dry cleaning,
				  dry dyeing, waterproofing, and related processes by immersion and agitation in
				  vessels without covers are not permitted.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 1 - GENERAL PROVISIONS › Section R. 325.17109 - Operations vigilance; notification to department of threat or hazard to public health or safety; report

Current through Vol. 24-12, July 15, 2024
Rule 109.
(1) An
				  owner, operator, or employee of a type IV dry cleaning establishment shall
				  maintain all dry cleaning operations and equipment to prevent threats or
				  hazards to the public health and safety. An owner, operator, or employee of a
				  type I, II or III dry cleaning establishment shall maintain all dry cleaning
				  operations and equipment to prevent threats to the health or safety of a person
				  or persons by preventing the risk of a fire or explosion from
				  occurring.
(2) If a condition or
				  incident presents a threat or hazard as defined in R 325.17109(1), then the
				  owner or operator of a dry cleaning establishment shall immediately initiate
				  corrective actions and notify the department by not later than the next
				  business day upon learning of the condition or incident. Within 30 days after
				  the condition or incident, the owner or operator shall file a written report
				  with the department outlining, in detail, discovery of the condition or
				  incident, the cause, and the corrective actions taken.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17202 - Submission of plans and specifications for construction or modification of dry cleaning establishment

Current through Vol. 24-12, July 15, 2024
Rule 202. Before construction or modification of any dry
					 cleaning establishment, or portion thereof, plans and specifications shall be
					 submitted to the department by the owner, operator, or a designated agent for
					 review and approval and shall meet all of the following requirements:
(a) Be accompanied with a transmittal letter
				  and a completed license application form as prescribed and provided by the
				  department. The transmittal letter shall identify and summarize the plans and
				  specifications for the project and indicate the authorization of any designated
				  agent for the owner or operator.
(b) Be accompanied with the appropriate fee
				  prescribed by the public health code for type IV dry cleaning establishments or
				  the fire prevention code for type I, II or III dry cleaning establishments and
				  made payable to "state of Michigan."
(c) Be accompanied with proof of approval
				  from the local governmental authority either by a form provided by the
				  department or a building permit.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17203 - Construction details for plans and specifications; modifications

Current through Vol. 24-12, July 15, 2024
Rule 203.
(1)
				  Plans and specifications for a new dry cleaning establishment or modification
				  of an existing dry cleaning establishment that are submitted to the department
				  for approval shall include, at a minimum, the items specified in section 13303
				  of the public health code and all of the following, where applicable:
(a) Site plan.
(b) Structural design.
(c) Construction materials.
(d) Construction and installation schedules
				  and methods.
(e) Water supply,
				  waste water disposal, and floor drains.
(f) Garbage and rubbish disposal
				  facilities.
(g) Ventilation and
				  make-up air equipment, location, and airflow direction.
(h) High-pressure steam boilers.
(i) Water and space heating
				  equipment.
(j) Btu/hr. input
				  ratings.
(k) Type and model of
				  proposed equipment.
(l) Location,
				  size, and type of combustion air openings.
(m) Fire protection systems.
(n) Permanently installed storage
				  tanks.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17203a - Compliance with state or local code requirements

Current through Vol. 24-12, July 15, 2024
Rule 203a. Compliance with these rules does not relieve an
					 owner from complying with a state or local code or requirement that is not in
					 conflict with these rules.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17204 - Review of plans and specifications by department

Current through Vol. 24-12, July 15, 2024
Rule 204.
(1) Upon
				  receipt of the transmittal letter, plans, and specifications, license or
				  certificate application, appropriate fee, and proof of local approval, the
				  department shall review the documents as soon as practical to determine their
				  completeness with regard to the minimum requirements specified by these rules
				  and to determine their adequacy. In making its review, the department shall not
				  approve the plans and specifications for a type IV establishment unless it
				  determines the dry cleaning establishment, or a portion thereof, is designed to
				  protect the health or safety of a person or persons. The department shall not
				  approve the plans and specifications for a type I, II or III establishment
				  unless it determines the dry cleaning establishment, or a portion thereof, is
				  designed to protect the health or safety of a person or persons by preventing
				  the risk of a fire or explosion from occurring.
(2) If the department determines that plans
				  and specifications or other pertinent information are incomplete, inaccurate,
				  or do not comply with these rules, it shall notify the applicant and may
				  request the submission of revised plans and specifications with appropriate
				  corrections or additions. The department shall not initiate the approval
				  process under this part until the completed license or certificate application
				  form and appropriate fee are received as well as the plans, specifications, and
				  proof of local approval that comply with the public health code for type IV
				  establishments or the fire prevention code for type I, II or III establishments
				  and these rules.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17205 - Approval of plans and specifications; authorization for construction, installation, or modification of establishment

Current through Vol. 24-12, July 15, 2024
Rule 205.
(1) Upon
				  a determination that provisions of R 325.17204(1) are met and the plans and
				  specifications for the construction, installation, or modification of a dry
				  cleaning establishment, or portion thereof, are complete and in compliance with
				  the public health code for type IV establishments or the fire prevention code
				  for type I, II or III establishments, and these rules, the department shall
				  mark the plans or drawings showing approval and the date of approval, shall
				  notify the owner, operator, or designated agent thereof of the approval, and
				  shall authorize construction, installation, or modification of the dry cleaning
				  establishment.
(2) The approval of
				  plans and specifications and authorization for construction, installation, or
				  modification of a dry cleaning establishment by the department pursuant to the
				  public health code, for a type IV establishment, or the fire prevention code,
				  for a type I, II or III establishment, and these rules shall expire within 1
				  year from the date of approval, unless the owner, operator, or designated agent
				  of the dry cleaning establishment applies in writing to the department for an
				  extension of the approval and construction authorization before its expiration.
				  The request for extension shall identify the project for which the approval was
				  issued and the reason for the delay in construction or initiation of the
				  project. If an extension is granted, the department may require modification of
				  the plans and specifications to incorporate updated dry cleaning practices
				  where applicable.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17207 - Approvals and authorizations; terms and conditions

Current through Vol. 24-12, July 15, 2024
Rule 207. An approval and authorization issued under R
					 325.17205 shall require that the project be constructed in accordance with the
					 approved plans and specifications. The department may attach additional
					 conditions to an approval and authorization if it determines the conditions are
					 necessary to assure proper construction, installation, modification, or
					 operation of the establishment, or portion thereof.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17208 - Deviations from approved plans and specifications; minor changes not affecting installation or operation; as-built plans

Current through Vol. 24-12, July 15, 2024
Rule 208.
(1)
				  Deviations from approved plans and specifications in the installation or
				  operation of a dry cleaning establishment, or portion thereof, shall be
				  submitted in writing to the department, before construction, installation, or
				  modification is initiated.
(2)
				  Changes in the construction, installation or modification of the dry cleaning
				  establishment that do not affect the health or safety of a person or persons at
				  a type IV establishment or that do not affect the health or safety of a person
				  or persons at a type I, II or III establishment from fire or explosion shall be
				  allowed without first obtaining approval from the department.
(3) As-built plans that clearly show the work
				  as constructed or installed shall be submitted to the department upon
				  request.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17209 - Approval and authorization; rescission; orders to stop construction

Current through Vol. 24-12, July 15, 2024
Rule 209.
(1) The
				  department may rescind its approval of plans and specifications and
				  authorization for construction, installation, or modification of a dry cleaning
				  establishment, if it determines that the owner, operator, or designated agent
				  is not undertaking the work substantially in accordance with approved plans and
				  specifications. The department shall notify the owner, operator, or designated
				  agent before the rescission of authorization, shall afford him or her the
				  opportunity to take any corrective action as may be required, and may pursue
				  further remedies as authorized by the public health code or the fire prevention
				  code and these rules.
(2) If an
				  owner, operator, or designated agent of a dry cleaning establishment fails to
				  submit plans and specifications for the construction, installation, or
				  modification of the establishment; fails to construct, install, or modify a dry
				  cleaning establishment in accordance with approved plans and specifications; or
				  fails to take corrective actions as required under subrule (1) of this rule,
				  then the department may issue a written stop work order to the owner, operator,
				  or designated agent to halt any construction, installation, or modification
				  activities and may pursue other remedies as provided by the public health code
				  or the fire prevention code.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17210 - Inspection of dry cleaning establishment

Current through Vol. 24-12, July 15, 2024
Rule 210.
(1) When
				  the construction of a new dry cleaning establishment is completed, the owner,
				  operator, or designated agent shall notify the department and arrange for an
				  inspection of the establishment. The owner, operator, or designated agent shall
				  not operate the dry cleaning establishment until an approved inspection is
				  completed and is in compliance with part 3 of these rules.
(2) When a modification of an existing dry
				  cleaning establishment is completed, the owner, operator, or designated agent
				  shall notify the department for approval. The department shall determine if an
				  on-site inspection is necessary.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 2 - PLANS AND SPECIFICATIONS › Section R. 325.17211 - Storage tank installation, operation, and closure plan review and approval

Current through Vol. 24-12, July 15, 2024
Rule 211. The owner of a dry cleaning establishment shall
					 obtain department approval for the installation, operation and closure of dry
					 cleaning liquid storage tanks as follows:
(a) A copy of the plans and specifications
				  shall be submitted to the storage tank unit of the waste and hazardous
				  materials division of the department for inside and outside above-ground
				  storage tanks that exceed 1,100 gallons in capacity for class I, II and IIIA
				  solvents. These plans and specifications shall be reviewed for compliance with
				  the fire prevention code and R 29.5209 et seq.
(b) A copy of the plans and specifications
				  shall be submitted to the storage tank unit of the waste and hazardous
				  materials division for underground tanks that meet the requirements of part 211
				  of 1994 PA 451, MCL 324.21101. These plans and specifications shall be reviewed
				  for compliance with part 211 of 1994 PA 451, MCL 324.21101, and R 29.2113 et
				  seq.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17301 - Applications for initial licenses; required information; fees; local approval

Current through Vol. 24-12, July 15, 2024
Rule 301. A completed license application form for an
					 initial type I, II, III, or IV license and the applicable fee prescribed by R
					 325.17302 shall be submitted to the department. At the time an initial license
					 application is submitted to the department, the owner or operator of a
					 drycleaning establishment shall provide satisfactory evidence of local approval
					 of the establishment. Evidence of local approval shall accompany the license
					 application form. The initial license application and local approval forms
					 shall be obtained from the department.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17302 - License applications; fees

Current through Vol. 24-12, July 15, 2024
Rule 302.
(1) The
				  owner or operator of a type I, II and/or III dry cleaning establishment shall
				  submit the fee prescribed in section 5i of the fire prevention code together
				  with the application.
(2) The owner
				  or operator of a type IV dry cleaning establishment shall submit the fee
				  prescribed in section 13306 of the public health code together with the
				  application.
(3) Payment of the
				  license application fee shall be by check or money order made payable to:
				  "state of Michigan."
(4) A dry
				  cleaning establishment shall not be operated without a license issued pursuant
				  to the public health code for type IV establishments or a certificate issued
				  pursuant to the fire prevention code for type I, II or III
				  establishments.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17303 - Application for annual license renewal; expiration

Current through Vol. 24-12, July 15, 2024
Rule 303.
(1) An
				  application for an annual renewal license for a dry cleaning establishment
				  shall be made by the owner or operator of the establishment on forms provided
				  by the department. The renewal application shall include all of the information
				  required on the form, the signature of the owner or operator, and any other
				  information which may be required by the department. Renewal license
				  application forms shall be obtained from the department.
(2) A dry cleaning establishment license
				  shall expire on December 31 of each year.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17304 - Review of initial license application; pre-licensing inspection; issuance of license

Current through Vol. 24-12, July 15, 2024
Rule 304.
(1) The
				  department shall promptly review an application for initial licensure of a dry
				  cleaning establishment to determine if the application is complete and
				  accurate. The department may return an incomplete or inaccurate application to
				  an owner or operator or may request any additional information determined
				  necessary to assure completeness or accuracy of the application.
(2) After the department determines that an
				  application for licensure is complete and accurate, it shall inspect the dry
				  cleaning establishment to determine compliance with the public health code for
				  type IV establishments or the fire prevention code for type I, II or III
				  establishments and these rules. The inspection shall be conducted by the
				  department before issuance or denial of the initial license.
(3) The department may attach any condition
				  or restriction to an initial license, under subrule (1) of this rule, when
				  determined necessary for compliance with the public health code for type IV
				  establishments or the fire protection code for type I, II or III
				  establishments.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17305 - Renewal of license; denial or revocation; conditions or restrictions

Current through Vol. 24-12, July 15, 2024
Rule 305.
(1)
				  After review of a renewal license application for a dry cleaning establishment
				  and the latest annual inspection by the department under R 325.17304(2), the
				  department shall issue or deny the license renewal. The license, if issued,
				  shall be sent directly to the owner or operator of the dry cleaning
				  establishment.
(2) The department
				  may attach any condition or restriction to a renewal license, issued or renewed
				  pursuant to subrule (1) of this rule when determined necessary for compliance
				  with the public health code for type IV establishments or the fire prevention
				  code for type I, II or III establishments.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17306 - Suspension and revocation of license

Current through Vol. 24-12, July 15, 2024
Rule 306.
(1) If
				  the department determines that a type IV dry cleaning establishment is not
				  being operated in accordance with the requirements of the public health code
				  and these rules or that a type I, II or III dry cleaning establishment is not
				  being operated in accordance with the requirements of the fire prevention code
				  and these rules, then the department shall notify the licensee and shall
				  provide an opportunity for the licensee to take corrective action. If the
				  licensee does not effect the corrections within the time prescribed by the
				  department, the department may suspend, revoke, or deny the license of the
				  establishment. Procedures for the suspension or revocation of a license shall
				  be in accordance with, and subject to, part 10 of these rules.
(2) If a license is suspended, revoked, or
				  denied by the department, then the owner or operator of the dry cleaning
				  establishment shall cease all dry cleaning operations until the expiration of
				  the period of suspension or reinstatement of the license, whichever is
				  applicable.
(3) This rule does not
				  apply to emergency procedures as prescribed by subsection (3) of section 13321
				  of the public health code.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17307 - Removal of suspension and reinstatement of license

Current through Vol. 24-12, July 15, 2024
Rule 307. A person whose license has been suspended by the
					 department may, at any time, request the department to inspect the dry cleaning
					 establishment for the purpose of reinstatement of the license. Based upon its
					 inspection, if the department determines that the owner or operator of the
					 establishment has taken steps to correct the violations or conditions prompting
					 the suspension of the license and determines that a type IV establishment will
					 be operated in compliance with the public health code and these rules, or that
					 a type I, II or III establishment will be operated in compliance with the fire
					 prevention code, these rules, and other applicable state laws, then the
					 department shall reinstate the license. An owner or operator whose license has
					 been suspended may apply for a new license in the same manner as an initial
					 applicant.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 3 - LICENSURE › Section R. 325.17308 - Transfer of ownership or operation; application for license after construction, installation, or modification of establishment

Current through Vol. 24-12, July 15, 2024
Rule 308.
(1)
				  Before the transfer of ownership or operation of a dry cleaning establishment,
				  the proposed licensee shall notify the department in writing, submit a
				  completed application for a new license accompanied with the appropriate fee,
				  and arrange for the department to conduct an inspection of the dry cleaning
				  establishment. The department shall conduct an inspection of the dry cleaning
				  establishment and shall notify the owner or operator in writing of its
				  findings, and the prospective licensee shall be apprised of any deficiencies
				  which shall be corrected as a condition of issuance of a license. The
				  prospective licensee shall not operate the dry cleaning establishment until a
				  final license approval is issued by the department.
(2) If a license application is submitted to
				  the department for operation after construction, installation, or modification
				  of a dry cleaning system, then the application shall be accompanied by evidence
				  of compliance with part 2 of these rules.
(3) A license is not transferable upon change
				  of ownership.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 4 - DRY CLEANING MACHINE REQUIREMENTS › Section R. 325.17401 - Dry cleaning machine exhaust systems

Current through Vol. 24-12, July 15, 2024
Rule 401.
(1) A
				  dry cleaning machine which uses a solvent and is designed to be installed and
				  operated without a loading door exhaust system as specified in subrule (2) of
				  this rule shall be approved for operation only if the machine is constructed
				  and operated in a manner to limit the peak work area concentration of the
				  solvent vapors.
(2) Except as
				  provided in subrule (1) of this rule, dry cleaning machines and recovery units
				  or dryers shall be equipped with an exhaust system capable of providing an
				  indraft velocity across the entire loading door opening which averages 100 feet
				  per minute. The exhaust from the blower shall be tightly piped to a point not
				  less than 5 feet above the roof of the building, any adjacent parapet wall, or
				  adjacent building, whichever is applicable, and a minimum of 25 feet away from
				  any return air opening. The stack shall be soldered or taped to prevent vapors
				  from entering the work area and shall be equipped with a vertical discharge
				  cap. Exhaust ducts from dry cleaning machines and recovery units or dryers
				  shall be sized and joined in a manner to maintain the required air flow from
				  each unit.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 4 - DRY CLEANING MACHINE REQUIREMENTS › Section R. 325.17402 - Prevention of liquid solvent and solvent vapor loss; piping of recovered dry cleaning solvent

Current through Vol. 24-12, July 15, 2024
Rule 402.
(1) A
				  dry cleaning system shall be designed, installed, operated, and maintained in a
				  manner to prevent the loss of liquid solvent or solvent vapor.
(2) Recovered dry cleaning solvent from all
				  types of recovery equipment shall be piped directly into an enclosed
				  tank.
(3) Pipe joint compounds and
				  dry cleaning machine gasketing shall be made of a material which resists
				  penetration and deterioration by solvents or solvent vapors.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 4 - DRY CLEANING MACHINE REQUIREMENTS › Section R. 325.17403 - Button and lint traps

Current through Vol. 24-12, July 15, 2024
Rule 403.
(1)
				  Button or lint traps on dry cleaning machines shall be designed so as to
				  prevent loss of solvent or solvent vapor.
(2) A solvent bypass arrangement shall be
				  provided for the button or lint trap if overflow might occur due to partial or
				  total blocking of the trap.
(3) A
				  button or lint trap cover shall be kept closed during normal operations of the
				  dry cleaning machine.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 4 - DRY CLEANING MACHINE REQUIREMENTS › Section R. 325.17404 - Electrical components

Current through Vol. 24-12, July 15, 2024
Rule 404. The electrical wiring and electrical components
					 associated with a type I, II, III, and IV dry cleaning machine shall be
					 approved by a nationally- recognized electrical testing
					 laboratory.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 4 - DRY CLEANING MACHINE REQUIREMENTS › Section R. 325.17405 - Exterior venting of solvent filters, stills, water separators, and sludge cookers

Current through Vol. 24-12, July 15, 2024
Rule 405. Solvent filters, solvent stills, solvent-water
					 separators, sludge cookers, and any required pressure relief vents that are not
					 designed and operated to limit the peak work area concentration of solvent
					 vapors shall be vented to the exterior of the building.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 4 - DRY CLEANING MACHINE REQUIREMENTS › Section R. 325.17406 - Manuals for installation, operation, and maintenance

Current through Vol. 24-12, July 15, 2024
Rule 406. An applicant submitting plans and specifications
					 pursuant to part 2 of these rules shall provide the installation, operation,
					 and maintenance manuals, upon request of the department, which indicate the use
					 of new or revised models of dry cleaning machines. The manuals shall include
					 all of the following:
(a) A complete
				  description of the dry cleaning machine cycle, solvent loss and exposure
				  safeguards, and machine performance.
(b) The location and identification of all
				  controls.
(c) Routine maintenance
				  procedures.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 5 - BUILDING REQUIREMENTS › Section R. 325.17501 - Location of establishments; approval by department

Current through Vol. 24-12, July 15, 2024
Rule 501.
(1) The
				  location and the type of building used for the dry cleaning establishment shall
				  be approved by the department.
(2)
				  The department shall conduct an on-site evaluation of a new dry cleaning
				  building location before the plans and specifications are submitted to the
				  department for review and approval. The owner, operator, or designated agent
				  shall be responsible for contacting the department to arrange an inspection to
				  comply with this part.
(3) The
				  department shall not approve the location of a dry cleaning building or dry
				  cleaning establishment if the building or establishment does not comply with
				  the public health code for type IV installations or the fire prevention code
				  for type I, II or III installations.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 5 - BUILDING REQUIREMENTS › Section R. 325.17503 - Approval of new dry cleaning establishment in building occupied in part as dwelling prohibited; exception

Current through Vol. 24-12, July 15, 2024
Rule 503. The department shall not grant approval of plans
					 for the installation of a new dry cleaning establishment in a building which is
					 occupied in part as a dwelling, except upon demonstration by the prospective
					 owner and concurrence by the department that the dry cleaning establishment is
					 specifically located or constructed, or both, in a manner that will not create
					 a potential hazard to the occupants of the building or to the
					 public.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 5 - BUILDING REQUIREMENTS › Section R. 325.17504 - Building requirements generally

Current through Vol. 24-12, July 15, 2024
Rule 504.
(1)
				  Buildings in which type I, II, III, and IV dry cleaning systems are installed
				  shall be structures with concrete floors in good condition.
(2) A dry cleaning establishment shall not be
				  located in a basement or other location which is difficult to ventilate. An
				  exception may be granted when, due to special construction, location, or use,
				  the installation will not create a potential hazard to the occupants or the
				  public, as determined by the department.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 5 - BUILDING REQUIREMENTS › Section R. 325.17505 - Compliance with building requirements of local governmental authorities

Current through Vol. 24-12, July 15, 2024
Rule 505. All new dry cleaning establishments shall comply
					 with applicable requirements of local governmental authorities. The owner or
					 operator of a dry cleaning establishment shall provide written evidence of this
					 compliance on forms provided by the department. The written evidence shall
					 accompany the plans and specifications submitted to the department for approval
					 under part 2 of these rules.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 5 - BUILDING REQUIREMENTS › Section R. 325.17506 - Dry cleaning establishments with adjacent occupancies in same or adjoining building; vapor seal requirements

Current through Vol. 24-12, July 15, 2024
Rule 506. Any dry cleaning establishment with adjacent
					 occupancies within the same building or in other adjoining buildings shall be
					 provided with an effective vapor seal to prevent infiltration of dry cleaning
					 solvent vapors into the adjacent occupancies or buildings. Porous walls,
					 partitions, and roof-to-partition wall areas shall be effectively sealed in a
					 manner approved by the department.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 5 - BUILDING REQUIREMENTS › Section R. 325.17509 - Boiler room construction and boiler location

Current through Vol. 24-12, July 15, 2024
Rule 509. Boiler room construction and the location of a
					 boiler in a dry cleaning establishment shall comply with all applicable
					 requirements of state and local governmental authorities, including the bureau
					 of safety and regulation of the Michigan department of consumer and industry
					 services.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 5 - BUILDING REQUIREMENTS › Section R. 325.17510 - Combustion air openings

Current through Vol. 24-12, July 15, 2024
Rule 510.
(1)
				  Nonpowered combustion air openings for fuel-fired unit space heaters, steam
				  boilers, and water heaters shall be sized at &frac12 square inch of net
				  free area per 1,000 Btu per hour input and 1 square inch net free area per
				  1,000 Btu per hour input for dryers.
(2) If powered combustion air supply
				  equipment is used as an alternate to subrule (1) of this rule for water heaters
				  and boilers, then the powered combustion air supply equipment shall be selected
				  to provide not less than 0.33 cubic feet per minute per 1,000 Btu per hour
				  input and shall be electrically interlocked to the combustion controls of each
				  unit.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 7 - INSTALLATION, OPERATION, AND VENTILATION › Section R. 325.17701 - Control of solvent and solvent vapors; exhaust ventilation generally

Current through Vol. 24-12, July 15, 2024
Rule 701.
(1) Dry
				  cleaning systems in type I, II, III, and IV dry cleaning establishments shall
				  be installed and maintained to prevent the unnecessary escape of solvents or
				  solvent vapors into the dry cleaning machine room and public area atmospheres
				  and so that the vapor concentration shall not exceed the allowable
				  concentration in these areas for those compounds as specified in R 325.51101 et
				  seq.
(2) General mechanical exhaust
				  ventilation shall be provided in a dry cleaning machine room to effectively
				  control the buildup of dry cleaning solvent vapors. The exhaust ventilation
				  system shall be designed and installed to have a minimum capacity of 1 complete
				  change of air in the dry cleaning machine room each 5 minutes in order to
				  control emergency spills or leaks.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 7 - INSTALLATION, OPERATION, AND VENTILATION › Section R. 325.17705 - Dry cleaning equipment in public laundry establishments; ventilation of dry cleaning machine rooms and flow of air from user operator area

Current through Vol. 24-12, July 15, 2024
Rule 705.
(1) If
				  dry cleaning machines are located in public laundry facilities, then there
				  shall be an operator on the premises when the dry cleaning machine is in
				  operation.
(2) Dry cleaning
				  equipment in type I, II, III, or IV establishments also having a public
				  laundry, shall have general mechanical exhaust ventilation in the dry cleaning
				  machine room to create a continuous flow of air from the operator's area and
				  the public laundry portion of the establishment to the outside of the building
				  to prevent dry cleaning solvent vapor buildup.
(3) General exhaust ventilation required by
				  this rule shall be provided on a continuous basis while the dry cleaning
				  establishment is open for business or while the dry cleaning equipment is being
				  operated or serviced.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 7 - INSTALLATION, OPERATION, AND VENTILATION › Section R. 325.17706 - Make-up air requirements generally

Current through Vol. 24-12, July 15, 2024
Rule 706.
(1) In
				  addition to the exhaust ventilation systems required by these rules, a supply
				  of make-up air which is equal to or greater than the total air being exhausted
				  from the building shall be provided to all type I, II, III, and IV
				  establishments.
(2) Regardless of
				  the type of make-up air system selected, sufficient replacement air shall be
				  provided to prevent a negative pressure condition within the
				  building.
(3) Make-up air intakes
				  shall be remotely located from the general exhaust location so as to provide
				  maximum personnel protection from exposure to solvent vapors.
(4) The location of all make-up air systems
				  and the flow direction of powered make-up air systems shall be approved by the
				  department before installation.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 7 - INSTALLATION, OPERATION, AND VENTILATION › Section R. 325.17709 - Ventilation exhaust ducts and deodorizing vents; size; sealing; discharge height

Current through Vol. 24-12, July 15, 2024
Rule 709.
(1)
				  Ventilation exhaust ducts and deodorizing vents in dry cleaning establishments
				  shall be sized to maintain the required air flow. The joints of the ducts shall
				  be effectively sealed, soldered, or taped. The ducts shall extend to a minimum
				  height of 5 feet above the roofline and a minimum of 25 feet from any air
				  intake unit or opening and shall extend above any adjacent parapet wall or
				  above adjacent buildings, whichever is higher. The ducts shall be equipped with
				  a vertical discharge cap.
(2) Where
				  deodorizing vents are connected to a common duct, the main duct shall be sized
				  to maintain rated airflow from all the dry cleaning machines and shall be
				  extended as required by subrule (1) of this rule. Backdraft dampers in
				  individual deodorizing stacks may be required by the department.
(3) The exit location of ventilation ducts
				  and deodorizing system vents shall be installed so as to prevent the entry of
				  solvent-contaminated air into the make-up air supply or other air intakes or
				  combustion air systems in the dry cleaning establishment.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 7 - INSTALLATION, OPERATION, AND VENTILATION › Section R. 325.17713 - Portable fire extinguisher requirement

Current through Vol. 24-12, July 15, 2024
Rule 713. Two portable fire extinguishers with at least a
					 2a, 10bc rating are required and 1 shall be mounted near the dry cleaning
					 machine in each dry cleaning establishment.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 7 - INSTALLATION, OPERATION, AND VENTILATION › Section R. 325.17714 - Organic vapor respirator requirement; selection

Current through Vol. 24-12, July 15, 2024
Rule 714.
(1) An
				  approved organic vapor respirator is required for each type IV dry cleaning
				  establishment. The respirator shall be kept near the dry cleaning machine in a
				  sealed container, shall be properly identified, shall be in good repair, and
				  shall be available for immediate use. Chemical specific cartridges for the
				  respirators shall be approved and used according to the manufacturer's
				  specifications only. The wearer shall replace the cartridge immediately upon
				  noticing an odor.
(2) The
				  respirator shall meet the requirements described in R 325.60051 et
				  seq.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 9 - INSPECTIONS OF DRY CLEANING ESTABLISHMENTS › Section R. 325.17901 - Evaluation of establishments generally

Current through Vol. 24-12, July 15, 2024
Rule 901. In accordance with the provisions of sections
					 13304 and 13307 of the code, the department shall make surveys, on-site
					 inspections, surveillance observations, or special purpose investigations for
					 the purpose of evaluating the construction, operation, adequacy, or condition
					 of dry cleaning establishments.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 9 - INSPECTIONS OF DRY CLEANING ESTABLISHMENTS › Section R. 325.17902 - On-site inspections and surveillance observations

Current through Vol. 24-12, July 15, 2024
Rule 902. On-site inspections and surveillance observations
					 of dry cleaning establishments may include, but are not limited to, a review of
					 all of the following:
(a) Dry cleaning
				  establishment physical facilities and equipment.
(b) The maintenance program for the dry
				  cleaning establishment.
(c) Storage
				  of chemicals and materials used in the dry cleaning establishment.
(d) The design and operation of the dry
				  cleaning establishment.
(e) A cross
				  connection control program to prevent contaminants from entering a public water
				  supply system due to a reversal of flow.
(f) Security measures provided to protect the
				  public health and the operation of the dry cleaning establishment.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 9 - INSPECTIONS OF DRY CLEANING ESTABLISHMENTS › Section R. 325.17903 - Access for inspections

Current through Vol. 24-12, July 15, 2024
Rule 903. An authorized representative of the department,
					 after proper identification, may enter any dry cleaning establishment at any
					 reasonable time for the purpose of making inspections and reviewing records of
					 the establishment to determine compliance with the public health code for type
					 IV installations or the fire prevention code for type I, II or III
					 installations and these rules.
Michigan Administrative Code › Department - Environmental Quality › Air Quality Division › Dry Cleaning Establishments › Part 9 - INSPECTIONS OF DRY CLEANING ESTABLISHMENTS › Section R. 325.17905 - Correction of violations

Current through Vol. 24-12, July 15, 2024
Rule 905. If the violations identified from the inspection
					 report are not corrected as required within the specified time period, then the
					 department may issue an order to cease or modify operations at the dry cleaning
					 establishment or the department may initiate license suspension, revocation, or
					 denial proceedings in accordance with parts 3 and 10 of these
					 rules.