reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 2 - Design of liquefied hydrogen systems › Section R. 29.7094 - Liquefied H2 to gaseous H2 systems

Current through Vol. 24-12, July 15, 2024
Rule 94. Sections 2-16 to 2-16.4 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
2-16Liquefied H2 to gaseous
						H2 systems.
2-16.1 Section 2-16 shall apply to the design,
						construction, installation, and operation of equipment used to produce gaseous
						H2 from liquefied H2.
2-16.2 Gaseous H2 storage
						containers and equipment located downstream of liquefied
						H2 containers are not regulated by section 2-16. Gaseous
						H2 storage containers and equipment shall comply with
						part 2 of these rules.
2-16.3 In addition to the emergency shutdown systems
						described in section 7-6, the emergency shutdown system shall also shut off the
						liquid supply and power to the liquefied H2 transfer
						equipment necessary for producing gaseous H2 from
						liquefied H2.
2-16.4 Transfer piping, pumps, and compressors shall be
						protected from vehicle collision damage and shall comply with section
						2-1.5.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 2 - Design of liquefied hydrogen systems › Section R. 29.7095 - Temporary installations

Current through Vol. 24-12, July 15, 2024
Rule 95. Sections 2-17 and 2-17.1 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
2-17 Temporary installations.
2-17.1 ASME or U.S. DOT containers that are used as
						portable storage containers, see definition of portable container in section
						1-5, for temporary, less than 6 months at any given location, stationary
						service shall comply with the following:
(a) If mounted on legs or supports, then such
					 supports shall be of steel and either shall be welded to the container by the
					 manufacturer at the time of fabrication or shall be attached to lugs that have
					 been so welded to the container. The legs or supports or the lugs for the
					 attachment of these legs or supports shall be secured to the container in
					 accordance with the code or rule under which the container was designed and
					 built, to withstand loading in any direction equal to twice the weight of the
					 empty container and attachments.
(b) If the container is mounted on a trailer
					 or semitrailer running gear so that the unit can be moved by a conventional
					 over-the-road tractor, then attachment to the vehicle, or attachments to the
					 container to make it a vehicle, shall comply with the appropriate U.S. DOT
					 requirements for cargo tank service. The unit also shall comply with applicable
					 state and U.S. DOT motor carrier regulations and shall be approved by the
					 department.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 2 - Design of liquefied hydrogen systems › Section R. 29.7096 - Indoor fueling

Current through Vol. 24-12, July 15, 2024
Rule 96. Section 2-18 of the storage and handling of
						gaseous and Liquefied H2 code is added as
						follows:
2-18 Indoor fueling. Indoor fueling of liquefied
						H2 is not permitted unless department approved.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 3 - Location of liquefied hydrogen systems › Section R. 29.7097 - General requirements

Current through Vol. 24-12, July 15, 2024
Rule 97. Sections 3-1.1 and 3-1.3 to 3-1.5 are reproduced
						from NFPA 50B, and sections 3-1.2, 3-1.6 to 3-1.13 of the storage and handling
						of gaseous and Liquefied H2 code is added as
						follows:
3-1 General requirements.
3-1.1 The storage containers shall be located so that
						they are readily accessible to mobile supply equipment at ground level and to
						authorized personnel. Roadways or other means of access for emergency
						equipment, such as fire department apparatus, shall be provided.
3-1.2 Systems shall not be located beneath or where
						exposed by failure of the following:
(a) Electric power lines as follows:
(i) Not less than 50 feet (15.2 meters)
					 horizontally from the vertical plane below the nearest overhead wire of an
					 electric trolley, train, or bus line.
(ii) Not less than 5 feet (1.5 meters)
					 horizontally from the vertical plane below the nearest overhead electrical
					 wire.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 3 - Location of liquefied hydrogen systems › Section R. 29.7099 - Handling of liquefied H2 inside buildings other than separate buildings and special rooms

Current through Vol. 24-12, July 15, 2024
Rule 99. Sections 3-3 and 3-3.1 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
3-3 Handling of liquefied H2
						inside buildings other than separate buildings and special rooms.
3-3.1 Portable liquefied H2
						containers of 50-gallons (189-Liters) or less capacity as permitted in Table
						3-2.1 and in compliance with section 3-1.5 where housed inside buildings not
						located in a special room and exposed to other occupancies shall comply with
						the following minimum requirements.
(a) Containers shall be located 20 feet (6.1
					 meters) from all classes of flammable and combustible liquids and readily
					 combustible materials such as excelsior or paper.
(b) Containers shall be located 15 feet (4.6
					 meters) from ordinary electrical equipment, and 25 feet (7.6 meters) from open
					 flames, welding or other sources on ignition.
(c) Containers shall be located 50 feet (15
					 meters) from storage of oxidizing gases.
(d) Containers shall be protected against
					 damage or injury due to falling objects or work activity in the area.
(e) Containers shall be firmly secured and
					 stored in an upright position and protected against damage in accordance with
					 the provisions of section 2-1.7.
(f) Pressure relief devices on the containers
					 shall be vented directly outdoors or to a hood that is suitable for flammable
					 and combustible vapors.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 3 - Location of liquefied hydrogen systems › Section R. 29.7100 - Location of dispensing operations and equipment

Current through Vol. 24-12, July 15, 2024
Rule 100. Sections 3-4 to 3-4.4 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows: 3-4 Location of dispensing operations and equipment.
3-4.1 Dispensing equipment located outdoors shall be in
						accordance with the following:
(a)
					 Dispensing equipment shall be allowed under weather protection in accordance
					 with the requirements of section 4-5 and constructed in a manner that prevents
					 the accumulation of H2 gas.
3-4.2 Dispensing equipment shall not be beneath electric
						power lines or where exposed by their failure, and shall be a minimum of 10
						feet (3.1 meters) from the nearest important building or property line or 20
						feet (6.2 meters) from any activity that involves a fixed source of
						ignition.
3-4.3 Dispensing equipment shall be located so that all
						parts of the vehicle being served are on the premises of the motor fuel
						dispensing facility.
3-4.4 Dispensing equipment shall be protected against
						collision damage by means acceptable to the department. Dispensing devices
						shall be securely bolted in place. Dispensing devices shall be installed in
						accordance with manufacturer's instructions.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 3 - Location of liquefied hydrogen systems › Section R. 29.7101 - Installation of emergency shutdown equipment

Current through Vol. 24-12, July 15, 2024
Rule 101. Sections 3-5 to 3-5.2 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
3-5 Installation of emergency shutdown equipment.
3-5.1 Breakaway protection shall be provided in a manner
						such that, if a pullaway event occurs, liquefied H2 will
						cease to flow at any separation.
3-5.2 A breakaway device shall be installed at every
						dispensing point. Such a device shall be arranged to separate by a force not
						greater than 150 pounds (75 kilograms), when applied in any direction that the
						vehicle would move. Breakaway devices shall be compatible with a standard
						acceptable to the department.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 4 - Design considerations at specific locations › Section R. 29.7102 - Outdoor locations

Current through Vol. 24-12, July 15, 2024
Rule 102. Sections 4-1 to 4-1.4 are reproduced from NFPA
						50B as follows:
4-1 Outdoor locations.
4-1.1 Roadways and yard surfaces located below liquefied
						hydrogen piping as well as areas under the fill connections and delivery
						vehicle's uninsulated hydrogen piping from which liquid air can drip shall be
						constructed of noncombustible materials. For the purposes of this standard,
						asphaltic and bitumastic paving shall be considered combustible. If expansion
						joints are used, fillers also shall be of noncombustible materials.
4-1.2 If walls, roofs, weather shelters, or canopies are
						provided, they shall be constructed of noncombustible or limited-combustible
						materials.
4-1.3 Electrical wiring and equipment shall comply with
						section 2-7.
4-1.4 Lighting shall be provided for nighttime transfer
						operation.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 4 - Design considerations at specific locations › Section R. 29.7103 - Specific requirements

Current through Vol. 24-12, July 15, 2024
Rule 103. Sections 4-2 to 4-2.2.3 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
4-2 Specific requirements.
4-2.1 The location of liquefied H2
						storage, as determined by the maximum total quantity of liquefied
						H2, shall be in accordance with table 3-2.1.
4-2.2 Installation of liquefied H2
						inside buildings other than detached buildings and gas rooms.
4-2.2.1 More than 1 system of 50 gallons (189.5 liters)
						or less capacity may be installed in the same room or area outside of special
						rooms located as allowed in table 3-2.1 and in compliance with section 4-2.1,
						provided the systems are separated by at least 50 feet (50.2 meters) or by a
						full height fire-resistive partition having a minimum fire resistance rating of
						2 hours is located between the systems.
4-2.2.2 The separation distance between multiple systems
						of 50 gallons (189.5 liters) or less may bereduced to 25 feet (7.6 meters) in
						buildings where the space between storage areas is free of combustible
						materials and protected with a sprinkler system.
4-2.2.3 When sprinkler protection is provided, the area
						in which the H2 is stored or used shall be protected
						with a sprinkler system designed to be not less than that required by NFPA 13
						for extra hazard group 1 with a minimum design area of 2,500 square feet (762
						square meters).
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 4 - Design considerations at specific locations › Section R. 29.7104 - Separate buildings

Current through Vol. 24-12, July 15, 2024
Rule 104. Sections 4-3 to 4-3.5 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
4-3 Separate buildings.
4-3.1 Separate buildings containing more than 300 gallons
						(1137 liters) of liquefied H2 shall be constructed of
						noncombustible or limited-combustible materials on a substantial frame. Walls
						and roofs shall be lightly fastened. All venting elements shall be designed to
						relieve at a maximum pressure of 25 pounds/square foot. Doors shall be located
						in such a manner that they are readily accessible to personnel in an emergency.
						Exception: Window glazing may be of plastic.
Exception: Explosion venting shall be in accordance with
						section 4-4.3.
4-3.2 Ventilation to the outdoors shall be provided.
						Inlet openings shall be located within 18 inches (45.72 centimeters) of the
						floor in exterior walls only. Outlet openings shall be located at the high
						point of the room in exterior walls or roof. Both the inlet and outlet vent
						openings shall have a minimum total area of 1 square foot/1000 cubic foot (0.3
						square meters/305 cubic meters) of room volume. Discharge from outlet openings
						shall be directed or conducted to a location that allows for dissipation of the
						exhaust air in the ambient surroundings away from air intakes and occupied
						spaces.
4-3.3 There shall be no sources of ignition within the
						room or area where the H2 system is installed.
4-3.4 Electrical wiring and equipment shall comply with
						section 2-7.
Exception: All electrical wiring and equipment in the
						separate building shall be class I, division 2, group B.
4-3.5 Heating, if provided, shall be by indirect means
						such as steam or hot water.
Exception: Electrical heating shall be in accordance with
						section 4-3.4.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 4 - Design considerations at specific locations › Section R. 29.7106 - Canopies

Current through Vol. 24-12, July 15, 2024
Rule 106. Sections 4-5 to 4-5.2 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
4-5 Canopies.
4-5.1 A container installation that has a canopy or roof
						shall have prior approval by the department based on the best interests of
						public health, safety, and welfare and the environment. This canopy or roof
						shall not limit the dissipation of heat or dispersion of flammable vapors and
						cannot restrict firefighting access and control.
4-5.2 A roof or canopy shall meet all of the following
						conditions:
(a) The lowest elevation
					 of the roof or canopy shall not be less than 4 feet (1.8 meters) from the top
					 of the container.
(b) All container
					 vent(s) are extended through the roof or canopy.
(c) The roof or canopy is constructed in such
					 a way that it will not allow for vapors to accumulate under the canopy or
					 roof.
(d) Constructed of
					 non-combustible materials.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 4 - Design considerations at specific locations › Section R. 29.7107 - Outdoor fill station

Current through Vol. 24-12, July 15, 2024
Rule 107. Sections 4-6 to 4-6.2 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
4-6 Outdoor fill station.
4-6.1 Each line between a liquid storage facility and a
						dispenser at a fill station shall have a valve that closes when 1 of the
						following occurs:
(4) The power supply
					 to the dispenser is cut off.
(5)
					 Any emergency shutdown device at the refueling station is activated.
4-6.2 A manual shutoff valve shall be provided at a fill
						station upstream of the breakaway device specified in section 3-5, where it is
						readily accessible to the person dispensing H2, unless 1
						of the following occurs:
(a) The
					 self-closing valve referred to in section 4-6.1 is located immediately upstream
					 of the dispenser.
(b) The dispenser
					 is equipped with a self-closing valve that closes each time the dispenser is
					 turned to the off position or when an emergency device is activated.
4-6.3 The liquid hydrogen dispenser shall provide a means
						to safely vent all hydrogen that may become trapped in sections of the
						dispenser between closed valves in all shut down modes including loss of
						power.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7108 - Operation

Current through Vol. 24-12, July 15, 2024
Rule 108. Section 5-1is reproduced from NFPA 50B, and
						sections 5-1.1 to 5-1.9 of the storage and handling of gaseous and Liquefied
						H2 code are added as follows:
5-1 Operation. For installations that require any
						operation of equipment by the user, instructions shall be maintained at
						operating locations.
5-1.1 Where an overpressure incident that results in
						operation of the overpressure protection system of the dispenser occurs, the
						dispenser pressure control system shall be examined and certified by a
						qualified operator prior to being returned to service.
5-1.2 Liquefied H2 fueling
						facilities shall be designed so that, in the event of a power failure, the
						system shall go into fail-safe condition.
5-1.3 The maximum delivery pressure at the vehicle tank
						inlet shall not exceed the maximum allowable pressure of the vehicle fuel
						tanks.
5-1.4 Hose and arms shall be equipped with a shutoff
						valve at the fuel end and a breakaway device that meets the requirements of
						section 3-5 to minimize release of liquid and vapor in the event that a vehicle
						pulls away while the hose remains connected. Such a device shall be installed
						and maintained in accordance with the manufacturer's instructions.
5-1.5 When not in use, hose shall be secured to protect
						it from damage.
5-1.6 Where a hose or arm of nominal 3 inches (7.62
						centimeters) diameter or larger is used for liquid transfer or where 1 of
						nominal 4 inches (10.16 centimeters) diameter or larger is used for vapor
						transfer, an emergency shutoff valve shall be installed in the piping of the
						transfer system within 10 feet (3.1 meters) from the nearest end of the hose or
						arm.
5-1.6.1 Where either a liquid or vapor line has 2 or more
						legs, an emergency shutoff valve shall be installed either in each leg or in
						the line before the legs.
5-1.7 Bleed or vent connections shall be provided so that
						loading arms and hose can be drained and depressurized prior to disconnection,
						if necessary. These bleed or vent connections shall lead to a safe point of
						discharge.
5-1.8 A fueling connector and mating vehicle receptacle
						shall be used for reliable, safe, and secure transfer of liquefied or gaseous
						H2 to or from the vehicle with minimal leakage.
5-1.8.1 The fueling connector either shall be equipped
						with an interlock device that prevents release while the line is open or shall
						have self-closing ends that automatically close upon disconnection.
5-1.9 The transfer of liquefied H2
						into vehicular onboard fuel supply containers shall be performed in accordance
						with the manufacturer's instructions. The dispenser manufacturer's instructions
						shall be posted at the dispensing device.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7109 - Maintenance

Current through Vol. 24-12, July 15, 2024
Rule 109. Sections 5-2 to 5-2.11 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
5-2 Maintenance.
5-2.1 Hoses, nozzles, and breakaways shall be examined
						visually to ensure that they are safe for use and shall be maintained in
						accordance with manufacturer's instructions on at least a quarterly basis, or
						if required by the manufacturer.
5-2.2 Hose shall be tested for leaks per manufacturer's
						requirements, and any leakage shall be a reason for rejection and
						replacement.
5-2.3 Testing shall be carried out with helium or with
						helium/ H2 blend as the test gas or if this is not
						possible, with H2 using suitable precautions.
5-2.4 The facility operator shall maintain a maintenance
						log in good condition and accessible to department inspection. Records shall be
						maintained for a minimum of 2 years.
5-2.5 Controllers on fuel stations shall be designed to
						verify the integrity of the fuel hose, breakaway, nozzle, and receptacle by
						pressurizing these components to at least the vehicle back pressure and
						checking pressure drop prior to the start of fueling.
5-2.6 Containers and their appurtenances, piping systems,
						compression equipment, controls, and detection devices shall be maintained in
						operating condition and according to manufacturer's instructions.
5-2.7 Pressure relief valves shall be maintained in
						operating condition.
5-2.8 Maintenance personnel shall be trained in leak
						detection procedures.
5-2.9 Area within 10 feet (3.1 meters) of dispenser shall
						be free from debris, weeds and other material that present a fire
						hazard.
5-2.10 Safety, gas detection, and fire protection
						equipment shall be tested or inspected at intervals not to exceed 6
						months.
5-2.11 Maintenance activities on fire control equipment
						shall be scheduled so that a minimum of equipment is taken out of service at
						any 1 time and fire prevention safety is not compromised.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7110 - Cathodic protection maintenance

Current through Vol. 24-12, July 15, 2024
Rule 110. Sections 5-3 and 5-3.1 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
5-3 Cathodic protection maintenance.
5-3.1
(a) Owners
					 and operators shall ensure that all metallic container systems that are
					 underground, mounded, or partially underground are protected and maintained to
					 minimize corrosion as cited in the NACE standard RP0169 entitled "Recommended
					 Practice, Control of External Corrosion of Underground or Submerged Metallic
					 Piping Systems" and NACE recommended practice RP02 85 entitled "Corrosion
					 Control of Underground Storage Tank Systems by Cathodic Protection," adopted by
					 reference in section 8.
(b) All
					 corrosion protection systems shall be operated and maintained to continuously
					 provide corrosion protection to the metal components of the portion of the ASME
					 approved container system that routinely contains liquid
					 H2 and that is in contact with the ground.
(c) All container systems equipped with
					 cathodic protection systems shall be inspected for proper operation by a NACE
					 certified cathodic protection tester as defined in section 1-3. The
					 H2 system shall be tested within 6 months of
					 installation and at least once each calendar year at intervals not to exceed 15
					 months.
(d) Container systems
					 equipped with impressed current cathodic protection systems shall be inspected
					 by the owner every 60 days to ensure that the equipment is operating within
					 design specifications. The design limits shall be readily available.
(e) If container systems are equipped with
					 cathodic protection, then the owner or operator shall maintain records to
					 demonstrate that the cathodic protection is in compliance with the performance
					 standards of this section.
The records shall provide both of the following:
(i) The results of the last 3 inspections
					 required in subsection (d) of this section.
(ii) The results of testing from the last 2
					 inspections required in subsection (c) of this section.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7111 - Stray or impressed currents and bonding

Current through Vol. 24-12, July 15, 2024
Rule 111. Sections 5-4 to 5-4.3 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
5-4 Stray or impressed currents and bonding.
5-4.1 Where stray or impressed currents are used or can
						be present on dispensing systems, such as cathodic protection, protective
						measures to prevent ignition shall be taken.
5-4.2 Static protection between the fuel dispenser and
						the vehicle shall not be required where H2 is
						transferred by conductive hose, flexible metallic tubing, or pipe connections
						where both halves of the metallic couplings are in continuous contact.
5-4.3 The transfer surface shall be concrete or shall
						have a resistivity not exceeding API RP 2003, "Protection Against Ignitions
						Arising Out of Static, Lightning, and Stray Currents," adopted by reference in
						section 8, performance criteria of 1 megohm as measured using a method
						acceptable to the department, such as EN 10 81:1998 "Resilient Floor Coverings
						- Determination of the Electrical Resistance," adopted by reference in section
						8.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7112 - Emergency plan

Current through Vol. 24-12, July 15, 2024
Rule 112. Sections 5-5 to 5-5.1.2 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
5-5 Emergency plan.
5-5.1 Emergency plan requirements.
5-5.1.1 An emergency plan shall be prepared and updated
						wherever gaseous or liquefied H2 are produced, handled,
						stored, or used.
5-5.1.2 The plan shall be available to the department for
						inspection upon reasonable notice and shall include all of the following
						information:
(a) The type of emergency
					 equipment available and its location.
(b) A brief description of any testing or
					 maintenance programs for the available emergency equipment.
(c) An indication that hazard identification
					 labeling is provided for each storage area.
(d) Location of posted emergency
					 procedures.
(e) A material safety
					 data sheet (MSDS or equivalent) that is available for the gaseous or liquefied
					 H2 stored or used on the site.
(f) A list of personnel or a site operating
					 authority who are designated and trained to be liaison personnel for the fire
					 department and who are responsible for but shall not be limited to the
					 following:
(i) Aiding the emergency
					 responders in pre-emergency planning.
(ii) Identifying the location of the gaseous
					 and liquefied H2 stored or used.
(iii) Accessing material safety data
					 sheets.
(iv) Knowledge of the site
					 emergency procedures.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7113 - Release of H2

Current through Vol. 24-12, July 15, 2024
Rule 113. Sections 5-6 to 5-6.2 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
5-6 Release of H2.
5-6.1 Records of unexpected discharges. Accurate records
						of the unexpected discharge of gaseous or liquefied H2
						shall be kept by the facility and made readily available upon request. Records
						shall be kept for a minimum of 2 years.
5-6.2 Container failure. When an unexpected discharge due
						to primary container failure is discovered the department and the local fire
						department, shall be immediately notified, and the container shall be repaired
						or be removed from service.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7114 - Security

Current through Vol. 24-12, July 15, 2024
Rule 114. Sections 5-7 and 5-7.1 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows: 5-7 Security.
5-7.1 Liquid H2 and compressed gas
						cylinders, containers, and systems shall be secured against accidental
						dislodgement and against access by unauthorized personnel.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 5 - Operation › Section R. 29.7115 - Leaks, damage, or corrosion

Current through Vol. 24-12, July 15, 2024
Rule 115. Sections 5-8 and 5-8.1 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
5-8 Leaks, damage, or corrosion.
5-8.1 Leaking, damaged, or corroded, liquid or gaseous
						H2 systems shall be removed from service, replaced or
						repaired.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 6 - Fire protection › Section R. 29.7116 - Cautionary information

Current through Vol. 24-12, July 15, 2024
Rule 116. Sections 6-1 to 6-1.2 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
6-1 Cautionary information.
6-1.1 Hazard identification signs shall be conspicuously
						placed at all locations where H2 is produced, stored,
						used, or handled.
6-1.2 Ratings shall be assigned in accordance with NFPA
						704, "Standard System for the Identification of the Hazards of Materials for
						Emergency Response," adopted by reference in section 8.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 6 - Fire protection › Section R. 29.7117 - Signs

Current through Vol. 24-12, July 15, 2024
Rule 117. Sections 6-2 to 6-2.3 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
6-2.1 Signs prohibiting smoking or open flames within 25
						feet (7.6 meters) shall be provided where H2 is
						produced, stored, or used.
6-2.2 A sign with the following legends printed in red
						capital letters on a white background shall be conspicuously posted as follows:
						"NON-ODORIZED FLAMMABLE GAS - CRYOGENIC LIQUID or COLD GAS - NO SMOKING - NO
						OPEN FLAMES" All lettering on signage shall be 3 inches (7.62 centimeters) or
						more.
Exception: This does not apply to motor vehicle
						dispensing per sections 7.2.13 and 4-4.
						8.1.
6-2.3 Identification signs. Visible hazard identification
						signs shall be provided in accordance with NFPA 704, "Standard System for the
						Identification of the Hazards of Materials for Emergency Response", adopted by
						reference in section 8.1.1, at entrances to buildings or areas in which
						liquefied H2 is stored, handled or
						used.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 6 - Fire protection › Section R. 29.7118 - Fire extinguisher

Current through Vol. 24-12, July 15, 2024
Rule 118. Section 6-3 of the storage and handling of
						gaseous and Liquefied H2 code is added as follows: 6-3 A
						portable fire extinguisher(s) having a rating of not less than 40-B:C or
						2-20-B:C shall be located within 75 feet (22.9 meters) from the pumps,
						dispensers, and container fill openings. Fire extinguishers shall be inspected
						and maintained according to NFPA 10, "Standard for Portable Fire
						Extinguishers," adopted by reference in section 8-1.1.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 6 - Fire protection › Section R. 29.7119 - Sprinkler protection

Current through Vol. 24-12, July 15, 2024
Rule 119. Section 6-4 of the storage and handling of
						gaseous and Liquefied H2 code is added as
						follows:
6-4 When sprinkler protection is provided, the area in
						which H2 is stored or used shall be protected with an
						automatic sprinkler system designed to be not less than that required by NFPA
						13, "Standard for the Installation of Sprinkler Systems," adopted by reference
						in section 8.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 7 - Liquefied hydrogen dispensing systems › Section R. 29.7120 - System component qualification

Current through Vol. 24-12, July 15, 2024
Rule 120. Section 7-1 of the storage and handling of
						gaseous and Liquefied H2 code is added as
						follows:
7-1 System component qualification. System components
						shall comply with applicable provisions of Chapters 2 and 3 of this
						part.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 7 - Liquefied hydrogen dispensing systems › Section R. 29.7122 - Operational requirements for full-service liquefied H2 motor fuel dispensing facilities

Current through Vol. 24-12, July 15, 2024
Rule 122. Sections 7-3 to 7-3.2 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
7-3 Operational requirements for full-service liquefied
						H2 motor fuel dispensing facilities.
7-3.1 Each motor fuel dispensing facility shall have an
						attendant or supervisor on duty whenever the facility is open for business. The
						attendant or supervisor shall dispense liquefied H2 into
						fuel tanks of motor vehicles or into portable containers.
7-3.2 The provisions of section 2-1 of this part shall
						not prohibit the temporary use of a portable storage container in conjunction
						with the dispensing of liquefied H2 into a container of
						a motor vehicle or other motorized equipment which is on the premises and which
						is not accessible to the public. A portable storage container installation
						shall only be made with the approval of the department and comply with all the
						requirements of section 2-13.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 7 - Liquefied hydrogen dispensing systems › Section R. 29.7123 - Operational requirements for attended self-service motor fuel dispensing facilities

Current through Vol. 24-12, July 15, 2024
Rule 123. Sections 7-4 to 7-4.5 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
7-4 Operating requirements for attended self-service
						motor fuel dispensing facilities.
7-4.1 Self-service motor fuel dispensing facility shall
						mean that portion of a property where liquefied H2 used
						as motor fuel is stored and dispensed from fixed, approved dispensing equipment
						into the fuel containers of motor vehicles by persons other than the facility
						attendant and shall also include, where provided, facilities for sale of other
						retail products.
7-4.2 There shall be not less than 1 attendant on duty
						while the self-service facility is open for business. The attendant's primary
						function shall be to supervise, observe, and control the dispensing of
						liquefied H2 while the liquefied
						H2 is actually being dispensed.
7-4.3 The responsibility of the attendant shall be as
						follows:
(a) Prevent the dispensing of
					 liquefied H2 into portable containers in or on a motor
					 vehicle.
(b) Control sources of
					 ignition.
(c) Immediately activate
					 emergency controls and notify the fire department of any fire. The attendant or
					 supervisor on duty shall be mentally and physically capable of performing the
					 functions and assuming the responsibility prescribed in section 7-4.
7-4.4 Operating instructions shall be conspicuously
						posted in the dispensing area.
7-4.5 The dispensing area shall at all times be in clear
						view of the attendant, and the placing or allowing of any obstacle to come
						between the dispensing area and the attendant control area is prohibited. This
						may be achieved by cameras or mirrors, or both. The attendant shall at all
						times be able to communicate with persons in the dispensing
						area.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 7 - Liquefied hydrogen dispensing systems › Section R. 29.7124 - Operational requirements for unattended self-service motor fuel dispensing facilities

Current through Vol. 24-12, July 15, 2024
Rule 124. Sections 7-5 to 7-5.5 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
7-5 Operating requirements for unattended self-service
						motor fuel dispensing facilities.
7-5.1 Unattended self-service shall be permitted subject
						to the approval of the department based on the best interests of public health,
						safety, and welfare and the environment. Users shall use a key, card, or other
						method which is unique to each user, and which is provided by the facility
						operator, and shall be properly trained in dispensing operations. The owner
						shall verify such training to the department upon request.
7-5.2 At least 1 emergency shutoff device specified in
						section 7-6shall be provided, and shall be reset only by the owner or an
						owner's authorized agent.
7-5.3 Operating instructions shall be conspicuously
						posted in the dispensing area. The instructions shall include the location of
						emergency controls.
7-5.4 In addition to the warning signs specified in
						section 6-2, emergency instructions shall be conspicuously posted in the
						dispenser area. The instructions shall incorporate the following or equivalent
						wording: "Emergency Instructions In Case of Fire:
(1) Use emergency stop button.
(2) Report accident by calling the local fire
					 number. Report location." 7-5.5 A telephone or other approved, clearly
					 identified means to notify the fire department shall be provided on the site in
					 a location approved by the department.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 7 - Liquefied hydrogen dispensing systems › Section R. 29.7125 - Emergency shutoff devices

Current through Vol. 24-12, July 15, 2024
Rule 125. Sections 7-6 and 7-6.1 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
7-6 Emergency shutoff devices.
7-6.1 Liquefied H2 dispensing
						systems shall be provided with 1 or more clearly identified emergency shutoff
						devices or electrical disconnects at the dispensing area. Such devices or
						disconnects shall be installed in approved locations but not less than 10 feet
						(3.1 meters) and not more than 100 feet (30.5 meters) away from the dispensing
						area and which is along the means of egress. Emergency shutoff devices or
						electrical disconnects shall disconnect power and fuel supply to all dispensing
						devices, to all remote pumps serving the dispensing devices, and to all
						associated power. When more than 1 emergency shutoff device or electrical
						disconnect is provided, all devices shall be interconnected. Resetting an
						emergency shutoff shall require manual intervention and the manner of resetting
						shall be approved by the department.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Gaseous and Liquefied Hydrogen Systems › Part 3 - STORAGE AND HANDLING OF LIQUEFIED HYDROGEN NFPA 50B › Chapter 7 - Liquefied hydrogen dispensing systems › Section R. 29.7126 - Refueling from transport vehicles

Current through Vol. 24-12, July 15, 2024
Rule 126. Sections 7-7 to 7-7.11 of the storage and
						handling of gaseous and Liquefied H2 code are added as
						follows:
7-7 Refueling from transport vehicles. The dispensing of
						liquefied H2 in the open from a transport vehicle to a
						motor vehicle located at commercial, industrial, governmental, or manufacturing
						establishments and intended for fueling vehicles used in connection with their
						businesses shall be permitted if all of the requirements of sections 7-7.1 to
						7-7.11 have been met.
7-7.1 The department shall be notified before commencing
						operations under section 7-7.
7-7.2 The transport vehicle shall comply with U.S. DOT
						requirements for the transportation of liquefied
						H2.
7-7.3 Nighttime deliveries shall only be made in an area
						considered to be adequately lighted.
7-7.4 The transport vehicle flasher lights shall be in
						operation while dispensing operations are in progress.
7-7.5 Smoking materials, including matches, lighters, and
						other sources of ignition, including torches, shall not be used within 20 feet
						(6.1 meters) of the dispensing of liquefied H2 in the
						open from a transport vehicle to a motor vehicle.
7-7.6 Each area where dispensing of liquefied
						H2 in the open from a transport vehicle to a motor
						vehicle shall be provided with 1 or more listed fire extinguishers that have a
						minimum capability of 40-B:C. The fire extinguishers shall be readily
						accessible to the dispensing operation. Fire extinguishers shall be inspected
						and maintained under NFPA 10, "Standard for Portable Fire Extinguishers,"
						adopted by reference in section 8.
7-7.7 Mobile fueling shall take place aboveground, shall
						not be beneath electric power lines or where exposed by their failure, and
						shall be 10 feet (3.1 meters) from the nearest important building, property
						lines or combustible storage.
7-7.8 Transport vehicle brakes shall be set and chock
						blocks shall be in place.
7-7.9 Persons performing dispensing operations shall be
						qualified to deliver and dispense H2 fuels. Operations
						of transport vehicles used for mobile fueling operations shall have access
						on-site or be in possession of an emergency communications device to notify the
						proper authorities if there is an emergency.
7-7.10 The transport vehicles shall be positioned with
						respect to vehicles being fueled to prevent traffic from driving over the
						delivery hose and between the transport vehicle and motor vehicle being fueled.
						The dispensing hose shall be properly placed on an approved reel or in an
						approved compartment before moving the transport vehicle.
7-7.11 The transfer area shall meet the requirements of
						section 5-4.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Adult Foster Care Facilities › Part 1 - GENERAL PROVISIONS › Section R. 400.18101 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 101.
(1)
				  These rules apply to all adult foster care facilities licensed for 7 or more
				  adults pursuant to the provisions of 1979 PA 218, MCL 400.701 to
				  400.737
(2) These rules supersede
				  all local regulations applicable specifically to adult foster care facilities.
				  Local ordinances, regulations, or construction codes regulating institutions
				  shall not be applied to adult foster care facilities licensed for 7 or more
				  adults including existing adult foster care congregate facilities. This subrule
				  shall not be construed to exempt adult foster care facilities from local
				  construction codes that are applicable to private residences. This provision is
				  in compliance with section 33 of the adult foster care facility licensing act,
				  1979 PA 218, MCL 400.733.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Adult Foster Care Facilities › Part 1 - GENERAL PROVISIONS › Section R. 400.18103 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 103. As used in these rules for new and existing adult
					 foster care facilities and congregate facilities licensed for 7 or more
					 adults:
(a) "Act" means 1979 PA 218,
				  MCL 400.701 to 400.737
(b) "Adult
				  foster care facility" has the same meaning as defined in the act.
(c) "Approved" means acceptable to the bureau
				  of fire services, unless specifically indicated otherwise in these
				  rules.
(d) "Authority having
				  jurisdiction" means the bureau of fire services, an employee of the bureau of
				  fire services, or an employee of a city, village, or township delegated to
				  enforce the code under section 2b of the act.
(e) "Code" means national fire protection
				  association standard no. 101, 2006 edition, entitled "life safety
				  code."
(f) "Congregate facility"
				  means an adult foster care facility with the approved capacity to receive more
				  than 20 adults for foster care.
(g)
				  "Conversion" means either of the following:
(i) To change the license category for an
				  existing facility.
(ii) To change
				  the purpose for which a building, a room, or an area is designed.