reglab/statecodes huggingface dataset:
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 33 - SANITATION AND SEWERAGE: SANITATION IN THE ICF-IID AND/OR THE ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.33.1 - Water Supply

Current through June 25, 2024
1. If at all
					 possible, all water shall be obtained from a community public water supply
					 (CWS). If not possible to obtain water from a community public water supply
					 (CWS) source, the private water supply shall meet the approval of the local
					 county health department and/or the Mississippi State Department of
					 Health.
2. Water under pressure
					 sufficient to operate fixtures at the highest point during maximum demand
					 periods shall be provided. Water under pressure of at least twenty (20) pounds
					 per square inch shall be piped to all sinks, toilets, lavatories, tubs,
					 showers, and other fixtures requiring water.
3. It is recommended that the water supply
					 into the ICF-IID can be obtained from two (2) separate water lines if
					 possible.
4. A dual hot water
					 supply shall be provided. The temperature of hot water to lavatories and
					 bathing facilities shall not exceed one hundred fifteen (115) degrees
					 Fahrenheit, nor shall hot water be less than one hundred (100) degrees
					 Fahrenheit.
5. Each ICF-IID shall
					 have a written agreement for an alternate source of potable water in the event
					 of a disruption of the normal water supply.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 33 - SANITATION AND SEWERAGE: SANITATION IN THE ICF-IID AND/OR THE ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.33.2 - Disposal of Liquid and Human Wastes

Current through June 25, 2024
1. There shall be
					 installed within the ICF-IID a properly designed waste disposal system
					 connecting to all fixtures to which water under pressure is piped.
2. All liquid and human waste, including
					 floor-wash water and liquid waste from refrigerators, shall be disposed of
					 through trapped drains into a public sewer system where such system is
					 available.
3. In localities where a
					 public sanitary sewer is not available, liquid and human waste shall be
					 disposed of through trapped drains into sewerage disposal system approved by
					 the local county health department and/or the Mississippi State Department of
					 Health. The sewerage disposal system shall be of a size and capacity based on
					 the number of clients and personnel housed and employed in the ICF-IID. Where
					 the sewerage disposal system is installed prior to the opening of the ICF-IID,
					 it shall be assumed, unless proven otherwise, that the system was designed for
					 ten (10) or fewer persons.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 33 - SANITATION AND SEWERAGE: SANITATION IN THE ICF-IID AND/OR THE ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.33.3 - Premises

Current through June 25, 2024
The premises shall be kept neat, clean, and free of an
						accumulation of rubbish, weeds, ponded water, or other conditions which would
						have a tendency to create a health hazard.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 33 - SANITATION AND SEWERAGE: SANITATION IN THE ICF-IID AND/OR THE ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.33.4 - Control of insects, rodents, etc

Current through June 25, 2024
The ICF-IID shall be kept free of ants, flies, roaches,
						rodents, and other insects and vermin. Proper methods for their eradication and
						control shall be utilized.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 33 - SANITATION AND SEWERAGE: SANITATION IN THE ICF-IID AND/OR THE ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.33.5 - Toilet Room Cleanliness

Current through June 25, 2024
Floors, walls, ceilings, and fixtures of all toilet
						rooms shall be kept clean and free of objectionable odors. These rooms shall be
						kept free of an accumulation of rubbish, cleaning supplies, toilet articles,
						etc.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 33 - SANITATION AND SEWERAGE: SANITATION IN THE ICF-IID AND/OR THE ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.33.6 - Garbage Disposal

Current through June 25, 2024
1. Garbage must be
					 kept in water-tight suitable containers with tight fitting covers. Garbage
					 containers must be emptied at frequent intervals and cleaned before using
					 again.
2. Proper disposition of
					 infectious materials shall be observed.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 34 - REGULATED MEDICAL WASTE IN AN ICF-IID AND/OR A ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.34.1 - Standards and Requirements

Current through June 25, 2024
All the requirements of the standards set forth in this
						section shall apply, without regard to the quantity of medical waste generated
						per month, to any generator of medical waste.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 34 - REGULATED MEDICAL WASTE IN AN ICF-IID AND/OR A ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.34.2 - Medical Waste

Current through June 25, 2024
1. Medical waste
					 must be kept in water-tight suitable containers with tight fitting covers.
					 Medical waste containers must be emptied at frequent intervals and cleaned
					 before using again.
2. Proper
					 disposition of medical waste materials shall be observed.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 35 - HOUSEKEEPING AND PHYSICAL PLANT IN AN ICF-IID AND/OR AN ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.35.1 - Housekeeping Facilities and Services

Current through June 25, 2024
1. The physical
					 plant shall be kept in good repair, neat, and attractive. The safety and
					 comfort of the client shall be the first consideration.
2. Janitor closets shall be provided with a
					 mop-cleaning sink and be large enough in area to store house cleaning supplies
					 and equipment. A separate janitor closet area and equipment should be provided
					 for the food service area.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 35 - HOUSEKEEPING AND PHYSICAL PLANT IN AN ICF-IID AND/OR AN ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.35.2 - Bathtubs, Showers, and Lavatories

Current through June 25, 2024
Bathtubs, showers, and lavatories shall be kept clean
						and in proper working order. They shall not be used for laundering or for
						storage of soiled materials. Neither shall these facilities be used for
						cleaning mops, brooms, etc.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 35 - HOUSEKEEPING AND PHYSICAL PLANT IN AN ICF-IID AND/OR AN ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.35.3 - Client Bedrooms

Current through June 25, 2024
Client bedrooms shall be cleaned and dusted as often as
						necessary to maintain a clean, attractive appearance. All sweeping should be
						damp sweeping; all dusting should be damp dusting with a good detergent or
						germicide.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 35 - HOUSEKEEPING AND PHYSICAL PLANT IN AN ICF-IID AND/OR AN ICF-IID RESIDENTIAL COMMUNITY HOME › Rule 15-16-1-49.35.4 - Storage

Current through June 25, 2024
1. Such items as beds, mattresses, mops, mop
					 buckets, dust rags, etc. shall not be kept in hallways, corners, toilet or
					 bathrooms, clothes closets, or client bedrooms.
2. The use of attics for storage of
					 combustible materials is prohibited.
3. If basements are used for storage, they
					 shall meet acceptable standards for storage and for fire safety.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 36 - LAUNDRY: GENERAL › Rule 15-16-1-49.36.1 - Commercial Laundry

Current through June 25, 2024
Facilities may use commercial laundries or they may
						provide a laundry within the institution.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 37 - PHYSICAL FACILITIES › Rule 15-16-1-49.37.1 - Location and Space Requirements

Current through June 25, 2024
Each ICF-IID shall have laundry facilities unless
						commercial laundries are used. The laundry shall be located in a specifically
						designated area, and there shall be adequate room and space for sorting,
						processing, and storage of soiled material. Laundry rooms or soiled linen
						storage areas shall not open directly into a client bedroom or food service
						area. Soiled materials shall not be transported through the food service area.
						If commercial laundry is used, separate satisfactory storage areas shall be
						provided for clean and soiled linens. There shall be provided a clean linen
						storage area separate from the laundry area.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 37 - PHYSICAL FACILITIES › Rule 15-16-1-49.37.2 - Ventilation

Current through June 25, 2024
Provisions shall be made for proper mechanical
						ventilation of the laundry. Provisions shall be made to prevent the
						recirculation of air through the heating and air condition
						systems.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 37 - PHYSICAL FACILITIES › Rule 15-16-1-49.37.3 - Lint Traps

Current through June 25, 2024
Adequate and effective lint traps shall be provided for
						driers.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 37 - PHYSICAL FACILITIES › Rule 15-16-1-49.37.4 - Laundry Chutes

Current through June 25, 2024
When laundry chutes are provided they shall have a
						minimum diameter of two (2) feet; and they shall be installed with flushing
						ring, vent, and drain.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 37 - PHYSICAL FACILITIES › Rule 15-16-1-49.37.5 - Laundry Equipment

Current through June 25, 2024
Laundry equipment shall be of the type to adequately
						perform the laundry needs of the institution. The equipment shall be installed
						to comply with all local and state codes.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.1 - Building Classification

Current through June 25, 2024
1. To qualify for a
					 license, the ICF-IID shall be planned to serve the type of patients to be
					 admitted and shall comply with the following:
a. All facilities constructed after the
					 effective date of these regulations shall comply with the building requirements
					 set forth in the regulations.
b.
					 After the effective date of these regulations, all additions to facilities
					 shall comply with the building requirements for a license. Approval shall not
					 be granted for an addition to an existing building which will increase the bed
					 capacity unless the existing structure is basically sound and is to be brought
					 into a condition of acceptable conformity with the current
					 regulations.
c. Authority to
					 Waiver. The licensing agency may waive certain requirements in these
					 regulations at its discretion for facilities requesting licensure as an ICF-IID
					 and/or an ICF-IID Residential Community Home provided the health and safety of
					 clients will not be endangered.
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.2 - Location

Current through June 25, 2024
All facilities established or constructed after the
						adoption of these regulations shall be located so that they are free from undue
						noise, smoke, dust, or foul odors and shall not be located adjacent to disposal
						plants, cemeteries, main line railroads, funeral home, airport,
						etc.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.3 - Site

Current through June 25, 2024
The proposed site for an ICF-IID must be approved by the
						licensing agency. Factors to be considered in approving a site in addition to
						the above may be convenience to medical and hospital services, approved water
						supply and sewerage disposal, public transportation, community services,
						services of an organized fire department, an availability to labor supply. Not
						more than one-third (1/3) of a site shall be covered by a building(s) except by
						special approval of the licensing agency. One example whereby approval may be
						granted is where the structure is to be placed in a very desirable location
						where the grounds are limited and very expensive. Where such approval is
						granted, the structure will be required to have a living room, day room, sun
						room, and recreational areas adequate to compensate for lack of required
						outside area.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.4 - Local Restrictions

Current through June 25, 2024
The site and structure of all facilities shall comply
						with local building, fire and zoning ordinances. Evidence to this effect signed
						by local building, fire, and zoning officials shall be
						presented.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.5 - Transportation

Current through June 25, 2024
Facilities shall be located on streets or roads which
						have all weather surfaces. They should be located convenient to public
						transportation facilities (if available).
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.6 - Communication

Current through June 25, 2024
There shall be not less than one telephone in the home
						and such additional telephones as are necessary to summon help in event of fire
						or other emergency. The telephone shall be listed under the official licensed
						name or title of the home.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.7 - Occupancy

Current through June 25, 2024
No part of the ICF-IID may be rented, leased, or used
						for any commercial purpose not related to the operation of the
						home.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 38 - PHYSICAL PLANT: GENERAL › Rule 15-16-1-49.38.8 - Basement

Current through June 25, 2024
1. The basement shall be considered as a
					 story if one-half (1/2) or more of its clear height is above the average
					 elevation of the ground adjoining the building on all sides.
2. No client shall be housed on any floor
					 that is below ground level.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.1 - New Construction, Additions, and Renovations

Current through June 25, 2024
When construction is contemplated either for new
						buildings, conversions, additions, or alterations to existing buildings, one
						set of plans and specifications shall be submitted to the licensing agency for
						review and approval. The submission shall be made in not less than two stages
						preliminary and final. Floor plans shall be drawn to scale of one-eight (1/8)
						inch to equal one (1) foot or one-fourth (1/4) inch to equal one (1)
						foot.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.2 - Minor Alterations and Remodeling

Current through June 25, 2024
Minor alterations and remodeling which do not affect the
						structural integrity of the building, change functional operation, affect fire
						safety, or add beds or facilities or those for which the ICF-IID is licensed do
						not need to have plans submitted for review provided that a detailed
						explanation of the proposed alteration or remodeling is submitted to and
						approved by the licensing agency.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.3 - First Stage Submission-Preliminary Plans

Current through June 25, 2024
First stage or preliminary plans shall include:
1. Plot plan showing size and shape of entire
					 site; location of proposed building and any existing structure(s); adjacent
					 streets, highways, sidewalks, railroads, etc., all properly designated; and
					 size, characteristics, and location of all existing public utilities.
2. Floor plan showing over-all dimensions of
					 building(s); location, size, and purpose of all rooms; location and size of all
					 doors, windows, and other openings with swing of doors properly indicated;
					 dimensions of all corridors and hallways; and location of stairs, elevators,
					 dumbwaiters, vertical shafts, and chimneys.
a. Outline specifications giving kinds and
					 types of materials.
b. A scaled
					 drawing of one-fourth (1/4) inch to one (1) foot shall be submitted for the
					 following areas: Kitchen, dishwashing area, nurses' station and utility
					 room(s).
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.4 - Final Stage Submission-Working Drawings and Specifications

Current through June 25, 2024
: Final stage or working drawings and specifications
						shall include:
1. Architectural
					 drawings
2. Structural
					 drawings
3. Mechanical drawings to
					 include plumbing, heat, and air-conditioning
4. Electrical drawings
5. Detailed specifications
6. Approval of working drawings and
					 specifications shall be obtained from the licensing agency in writing prior to
					 the beginning of actual construction.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.5 - Preparation of Plans and Specifications

Current through June 25, 2024
The preparation of drawings and specifications shall be
						executed by or under the immediate supervision of an architect who shall
						supervise construction and furnish a signed statement that construction was
						performed according to plans and specifications approved by the licensing
						agency.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.6 - Contract Modifications

Current through June 25, 2024
Any contract modification which affects or changes the
						function, design, or purpose of an ICF-IID shall be submitted to and approved
						by the licensing agency prior to the beginning of work set forth in any
						contract modification.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.7 - Notification of Start of Construction

Current through June 25, 2024
The licensing agency shall be informed in writing at the
						time construction is begun.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.8 - Inspections

Current through June 25, 2024
The licensing agency or its authorized representatives
						shall have access at all times to the work for inspection whenever it is in
						preparation or progress, and the owner shall ascertain that proper facilities
						are made available for such access and inspection.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.9 - Limit of Approval

Current through June 25, 2024
In construction delayed for a period of exceeding six
						(6) months from the time of approval of final working plans and specifications,
						a new evaluation and/or approval shall be obtained from the licensing
						agency.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.10 - Water Supply, Plumbing, Sewerage Disposal

Current through June 25, 2024
The water supply and sewerage disposal shall be approved
						by the local county health department and/or the Division of Sanitary
						Engineering, Mississippi State Department of Health. No system of water supply,
						plumbing, sewerage, garbage, or refuse disposal shall be installed nor any such
						existing system materially altered or extended until complete plans and
						specifications for the installation, alteration, or extension have been so
						approved and submitted to the licensing agency for review and final
						determination.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 39 - SUBMISSION OF PLANS AND SPECIFICATIONS FOR ICF-IIDS OR ICF-IID RESIDENTIAL COMMUNITY HOMES › Rule 15-16-1-49.39.11 - Availability of Approved Plans

Current through June 25, 2024
Every licensed ICF-IID shall maintain, on the premises
						and available for inspection, a copy of current approved architectural plans
						and specifications.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.1 - Scope

Current through June 25, 2024
The provision of this section shall apply to all
						facilities except for those sections or paragraphs where a specific exception
						is granted for existing facilities.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.2 - Structural Soundness and Repair; Fire Resistive Rating

Current through June 25, 2024
The building shall be structurally sound, free from
						leaks and excessive moisture, in good repair, and painted at sufficient
						intervals to be reasonably attractive inside and out.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.3 - Temperature

Current through June 25, 2024
Adequate heating and cooling shall be provided in all
						rooms used by clients so that a minimum temperature of seventy-five (75) to
						eighty (80) degrees Fahrenheit may be maintained.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.4 - Lighting

Current through June 25, 2024
Each client's room shall have artificial light adequate
						for reading and other uses as needed. There should be a minimum of ten (10)
						foot-candles of lighting for general use in client's room and a minimum of
						thirty (30) foot-candles of lighting for reading purposes. All entrances,
						corridors, stairways, ramps, cellars, attics, storerooms, kitchens, laundries,
						and service units shall have sufficient artificial lighting to prevent
						accidents and promote efficiency of service. Night lights shall be provided in
						all corridors, stairways, toilets, and bathing rooms.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.5 - Screens

Current through June 25, 2024
All screen doors and non-stationary windows shall be
						equipped with tight fitting full length, sixteen (16) mesh screens. Screen
						doors shall swing out and shall be equipped with self-closing
						devices.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.6 - Floors

Current through June 25, 2024
All floors shall be smooth and free from defects such as
						cracks and be finished so that they can be easily cleaned.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.7 - Walls and Ceilings

Current through June 25, 2024
All walls and ceilings shall be of sound construction
						with an acceptable surface and shall be maintained in good repair. Generally
						the walls and ceilings should be painted a light color.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.8 - Ceiling Height

Current through June 25, 2024
All ceilings shall have a height of at least eight (8)
						feet except that a height of seven (7) feet and six (6) inches may be approved
						for corridors or toilets and bathing rooms where the lighting fixtures are
						recessed. Exception may be made for existing facilities.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.9 - Handrails

Current through June 25, 2024
In an ICF-IID, handrails shall be installed on both
						sides of all corridors and hallways used by clients. The handrails should be
						installed from thirty-two (32) inches to thirty-six (36) inches above the
						floors. The handrails should have a return to the wall at each rail ending. An
						exception may be made for existing facilities. In addition, grab bars shall be
						installed in at least one bathroom beside the toilet and beside the lavatory in
						an ICF-IID Residential Community Home.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.10 - Ramps and Inclines

Current through June 25, 2024
Ramps and inclines, where installed for the use of
						clients, shall not exceed one (1) foot of rise in twelve (12) feet of run,
						shall be furnished with a non-slip floor, and shall be provided with handrails
						on both sides. Exception may be granted for existing ramps and inclines on
						existing facilities.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.11 - Call System

Current through June 25, 2024
A call system shall be in place in an ICF-IID at the
						nurses' station to receive client calls through a communication system to
						include audible and visual signals from bedrooms, toilets, and bathing
						facilities. In the residential community home setting, there shall be a
						communication system in place throughout the residence to address the immediate
						needs of the clients.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 40 - GENERAL BUILDING REQUIREMENTS › Rule 15-16-1-49.40.12 - Trash Chutes

Current through June 25, 2024
The installation and/or use of trash chutes is
						prohibited.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 41 - FIRE SAFETY AND CONSTRUCTION › Rule 15-16-1-49.41.1 - Date of Construction and Life Safety Code Compliance

Current through June 25, 2024
1. New buildings and/or building not
					 previously approved for use as a Residential Community Home (6 [Six] clients or
					 less), Small ICF/IID (16 clients or less), or Large ICF/IID (More than 16
					 clients) on the effective date of these regulations shall comply with Chapter
					 32 "New Residential Board and Care" edition of the
Life Safety
					 Code
(NFPA 101) effective on the date of application.
2. Existing buildings and/or building not
					 previously approved for use as a Small ICF/IID (16 clients or less) or Large
					 ICF/IID (More than 16 clients) on the effective date of these regulations shall
					 comply with Chapter 33 "Existing Residential Board and Care" edition of the
Life Safety Code
(NFPA 101).
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 41 - FIRE SAFETY AND CONSTRUCTION › Rule 15-16-1-49.41.2 - ICF-IID Required Rooms and Areas

Current through June 25, 2024
1. Client bedroom.
					 (See Rule 49.19.3 )
2. Special care
					 room. (See Rule 49.19.4 )
3.
					 Nurses' Station. (See Rule 49.19.5 )
4. Utility room. (See Rule 49.19.6
					 )
5. Toilet and bathing facilities.
					 (See Rule 49.19.7 )
6. Clean linen
					 storage. Adequate areas shall be provided for storing clean linens which shall
					 be separate from dirty linen storage.
7. Wheelchair area. Adequate area shall be
					 provided for storage of wheelchairs.
8. Kitchen. (See Rule 49.32.2
					 49.32.4)
9. Dining room. The dining
					 area shall be large enough to seat three-fourth (3/4) of the maximum capacity
					 of an ICF-IID. The dining area can also be used for social, recreational, or
					 religious activities. It is recommended that a separate dining area be provided
					 for personnel.
10. Food storage. A
					 food storage room shall be provided convenient to the kitchen in all future
					 licensed homes. It should have cross ventilation. All foods must be stored a
					 minimum of twelve (12) inches above the floor.
11. Day room or living room. Adequate day or
					 living room area shall be provided for clients or clients and guests. These
					 areas shall be designated exclusively for this purpose and shall not be used as
					 sleeping area or otherwise. It is recommended that at least two (2) such areas
					 be provided and more in larger homes.
12. Janitor closet. At least one (1)
					 janitor's closet shall be provided for each floor. The closet shall be equipped
					 with a mop sink and be adequate in area to store cleaning supplies and
					 equipment. A separate janitor's closet shall be provided for the food service
					 area.
13. Garbage can cleaning and
					 storage area.
14. General storage.
					 A minimum area equal to at least five (5) square feet per bed shall be provided
					 for general storage.
15. Laundry.
					 If laundry is done in the institution, a laundry room shall be provided.
					 Adequate equipment for the laundry load of the home shall be installed. The
					 sorting, washing, and extracting process should be separated from the folding
					 and ironing area-preferably in separate rooms. In addition refer to Subchapter
					 36, Laundry, General; and Subchapter 37, Physical Facilities.
16. Separate toilet room (lavatory and water
					 closet) shall be provided for male and female employees.
17. A separate toilet room with a door that
					 can be locked shall be provided for the public.
18. Food Service Supervisors
					 Office.
19. Social Services
					 Office.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 41 - FIRE SAFETY AND CONSTRUCTION › Rule 15-16-1-49.41.3 - Immediate Jeopardy

Current through June 25, 2024
(Serious and Immediate to Health and Safety). A
						situation in which the ICF-IID's failure to meet one or more licensure
						requirements has caused, or is likely to cause, serious injury, harm,
						impairment, or death to a client.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 41 - FIRE SAFETY AND CONSTRUCTION › Rule 15-16-1-49.41.4 - Ban on all Admissions

Current through June 25, 2024
A ban on all admissions to an ICF-IID and/or the ICF-IID
						residential community home shall be imposed by the licensing agency when it has
						been determined by the licensing agency that the ICF-IID and/or the ICF-IID
						residential community home is not in compliance with program requirements or an
						immediate jeopardy is determined to exist based upon survey findings. These
						deficiencies must be determined as Immediate Jeopardy as defined under Rule
						49.41.3.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 42 - STATE MONITORING › Rule 15-16-1-49.42.1 - State Monitoring

Current through June 25, 2024
A State Monitor may oversee the correction of cited
						deficiencies in an ICF-IID or an ICF-IID residential community home as a
						safeguard against further harm to clients when a finding of noncompliance has
						resulted in harm to a client or when there is a situation that is likely to
						cause serious injury, harm, impairment or death to a resident
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 49 - MINIMUM STANDARDS FOR OPERATION FOR INTERMEDIATE CARE FACILITIES FOR INDIVIDUALS WITH INTELLECTUAL DISABILITIES › Subchapter 43 - DIRECTED PLAN OF CORRECTION › Rule 15-16-1-49.43.1

Current through June 25, 2024
A Directed Plan of Correction is a plan which the
						licensing agency, or the temporary manager, develops to require an ICF-IID or
						an ICF-IID residential community home to take action within specified time
						frames.
Miss. Code Ann.
						§
												43-11-13