reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Compressed Natural Gas (CNG) Vehicular Fuel Systems › Part 2 - AMENDMENTS TO VEHICULAR GASEOUS FUEL SYSTEMS CODE › Section R. 29.4755 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 755. NFPA official definitions. Sections 3.2.1, and
					 3.2.2 of the vehicular gaseous fuel systems code are adopted with the following
					 changes and section 3.2.2.1 is added to the vehicular gaseous fuel systems code
					 as follows:
3.2.1 "Approved" means
				  acceptable to the department.
3.2.2
				  "Authority having jurisdiction (AHJ)" means the department of licensing and
				  regulatory affairs.
3.2.2.1 "Department"
				  means department of licensing and regulatory affairs.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5601 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 601. These rules apply to the storage and handling of
				  flammable and combustible liquids (FL/CL) as specified in parts 2 to 5 of these
				  rules. Compliance with these rules does not excuse compliance with other
				  applicable state and federal statutes and rules and
				  regulations.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5602 - Flammable and combustible liquids (FL/CL) code; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 602. The provisions of the National Fire Protection
				  Association (NFPA) pamphlet number 30, 2012 edition, entitled "Flammable and
				  Combustible Liquids (FL/CL) Code," referred to in part 2 of these rules, are
				  adopted by reference. Copies of the adopted NFPA 30 are available for
				  inspection and distribution either at the office of the Bureau of Fire
				  Services, Storage Tank Division, 3101 Technology Boulevard, Lansing, Michigan
				  48910, or from the National Fire Protection Association (NFPA), 1 Batterymarch
				  Park, Quincy, Massachusetts, 02269-9101. The cost of NFPA 30, as of the time of
				  adoption of these rules, is $52.50 per copy.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5603 - Code for motor fuel dispensing facilities and repair garages; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 603. The provisions of the National Fire Protection
				  Association (NFPA) pamphlet number 30A, 2012 edition, entitled, "Code for Motor
				  Fuel Dispensing Facilities and Repair Garages," referred to in part 3 of these
				  rules, is adopted by reference. Copies of the adopted NFPA 30A are available
				  for inspection and distribution either at the office of the Bureau of Fire
				  Services, Storage Tank Division, 3101 Technology Boulevard, Lansing, Michigan
				  48910, or from the National Fire Protection Association (NFPA), 1 Batterymarch
				  Park, Quincy, Massachusetts, 02269-9101. The cost of NFPA 30A, as of the time
				  of adoption of these rules, is $40.50 per copy.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5604 - Standard for installation of oil-burning equipment; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 604. The provisions of the National Fire Protection
				  Association (NFPA) pamphlet number 31, 2011 edition, entitled "Standard for the
				  Installation of Oil-Burning Equipment," referred to in part 4 of these rules,
				  are adopted by reference. Copies of the adopted NFPA 31 are available for
				  inspection and distribution either at the office of the Bureau of Fire
				  Services, Storage Tank Division, 3101 Technology Boulevard, Lansing, Michigan
				  48910, or from the National Fire Protection Association (NFPA), 1 Batterymarch
				  Park, Quincy, Massachusetts, 02269-9101. The cost of NFPA 31, as of the time of
				  adoption of these rules, is $44.50 per copy.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5605 - Standard for installation and use of stationary combustion engines and gas turbines; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 605. The provisions of the National Fire Protection
				  Association (NFPA) pamphlet number 37, 2010 edition, entitled "Standard for the
				  Installation and Use of Stationary Combustion Engines and Gas Turbines,"
				  referred to in part 5 of these rules, are adopted by reference. Copies of the
				  adopted NFPA 37 are available for inspection and distribution either at the
				  office of the Bureau of Fire Services, Storage Tank Division, 3101 Technology
				  Boulevard, Lansing, Michigan 48910, or from the National Fire Protection
				  Association (NFPA), 1 Batterymarch Park, Quincy, Massachusetts, 02269-9101. The
				  cost of NFPA 37, as of the time of adoption of these rules, is $40.50 per
				  copy.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5651 - Scope

Current through Vol. 24-12, July 15, 2024
Rule 651. Sections 1.1.2(10), 1.1.2(11), 1.1.2(12), and
				  1.1.2(13) are added to the FL/CL code as follows:
1.1.2 (10) Any portion of a new or existing
				stationary fire pump system where the requirements of part 2 conflict with the
				requirements of NFPA 20.
1.1.2 (11)
				Storage and handling of Class IIIb liquids.
1.1.2 (12) Flow-through process
				tanks.
1.1.2 (13) Oil and gas
				operations utilized for the purpose of exploration, development, operation, and
				abandonment of hydrocarbon resources regulated under part 615, supervisor of
				wells, of the natural resources and environmental protection act, 1994 PA 451,
				MCL 324.61501 to 324.61527. Part 615 does not regulate crude petroleum
				collection tanks that do not receive crude petroleum directly from a wellhead
				through a pipeline system.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5652 - Equivalency

Current through Vol. 24-12, July 15, 2024
Rule 652. Sections 1.5.2(a) and 1.5.2(b)are added to the
				  FL/CL code, and section 1.5.3 of the FL/CL code is adopted with changes as
				  follows:
1.5.2(a) An owner or operator
				may apply for a variance to the rules by applying to the bureau with a
				satisfactory explanation as to why compliance is not possible. The bureau may
				approve a variance upon finding that the variance is based on the best
				interests of public health, safety, welfare, and property and the
				environment.
1.5.2(b) A person
				aggrieved by a final decision of the bureau on a request for variance may
				appeal to the circuit court within 21 days of the decision.
1.5.3(3) Part 3 of these rules.
1.5.3(4) Part 4 of these rules.
1.5.3(10) Part 5 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5653 - Prohibitions

Current through Vol. 24-12, July 15, 2024
Rule 653. Section 1.7 of the FL/CL code is adopted with the
				  following changes and sections 1.7.1, 1.7.2, 1.7.3, 1.7.4, 1.7.4.1, 1.7.4.1.1,
				  1.7.4.1.2, 1.7.4.1.3, and 1.7.5 are added to the FL/CL code as follows:
1.7 Prohibitions.
1.7.1 Upon notification by the bureau a
				person shall not deliver any liquid into a storage tank system under any
				circumstances that are prohibited by these rules or if a tank is not in
				compliance with these rules. The notification may include verbal or written
				communication or an affixed written notification on the storage tank
				system.
1.7.2 A person shall not
				tamper with, remove, or disregard written notification affixed to the storage
				tank system.
1.7.3 A storage tank
				system or practice that is not in compliance with these rules is in violation
				of these rules.
1.7.4 An owner or
				operator shall not continue to use a storage tank system that is causing a
				release and shall expeditiously empty the system or the component that is
				causing the release until the system is repaired or replaced, pursuant to these
				rules.
1.7.4.1 A leak from the primary tank
				into the interstice of a new or existing secondary containment tank is not
				considered a release requiring that the secondary containment tank be emptied,
				provided all of the following are met:
1.7.4.1.1 The secondary containment tank is
				repaired, replaced, or permanently closed within 6 months of discovery of the
				release.
1.7.4.1.2 Temporary or
				permanent liquid tight spill control is provided for the secondary containment
				tank within 7 days of discovery of the release to the secondary containment
				tank interstice.
1.7.4.1.3 There is
				no release from the outer shell of the secondary containment
				tank.
1.7.5
				The bureau may order, at the expense of the owner, a tightness test of the
				storage tank system when there is reason to believe that the integrity of the
				storage tank system is compromised.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5654 - Permits

Current through Vol. 24-12, July 15, 2024
Rule 654. Section 1.8 of the FL/CL code is adopted with the
				  following changes and sections 1.8.1, 1.8.2, 1.8.3, 1.8.4, and 1.8.5 are added
				  to the FL/CL code as follows: 1.8 Permits.
1.8.1 For installations, where individual
				storage capacity is more than 1,100 gallons (4,180 liters), an owner or owners
				designee shall submit an application for plan review to the bureau not less
				than 30 days before the installation of an aboveground storage tank system.
				Tanks with storage capacity of 1,100 gallons or less shall comply with these
				rules but are not required to submit an application for plan review and are not
				required to be certified.
1.8.2 The
				installation application shall include a plot map that shows all of the
				following information:
(a) The locations of
				buildings, public roadways, railroad mainlines, and power lines.
(b) Storm sewers, sanitary sewers, manholes,
				and catch basins.
(c) The proposed
				locations of tanks and buildings.
(d) The location of property lines.
(e) The location of existing tanks,
				aboveground and underground, within 50 feet (15 meters) of the
				installation.
(f) The material of
				construction, the dimension, and the capacity of each tank.
(g) The class of liquid stored.
(h) The type of venting and pressure
				relief.
(i) The method of spill
				control provided.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5655 - Referenced publications

Current through Vol. 24-12, July 15, 2024
Rule 655. NFPA publications. Section
				  2.2is
				  adopted with the following addition: NFPA 20, Standard for the Installation of
				  Stationary Pumps for Fire Protection, 2013 edition.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5656 - STI publications

Current through Vol. 24-12, July 15, 2024
Rule 656. Section 2.3.8 of the FL/CL code is adopted with the
				  following changes: 2.3.8 STI Publications. Steel Tank Institute, Division of
				  STI/SPFA, 944 Donata Court, Lake Zurich, IL 60047. STI SP001, Standard for the
				  Inspection of Aboveground Storage Tanks, 2011.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5657 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 657. General. Sections 3.2.1 and 3.2.2 of the FL/CL code
				  are adopted with the following changes and sections 3.1.1, 3.2.2(a), 3.3.21.1,
				  3.3.64, 3.3.65, and 3.3.66 are added to the FL/CL code:
3.1.1 Definitions in chapter 3 apply to
				existing and new storage tank installations.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5658 - NFPA official definitions

Current through Vol. 24-12, July 15, 2024
Rule 658. Sections 3.2.1 and 3.2.2 of the FL/CL code are
				  adopted with the following changes and section 3.2.2(a) is added to the FL/CL
				  code:
3.2.1 "Approved" means
				acceptable to the bureau.
3.2.2
				"Authority having jurisdiction (AHJ)" means the bureau of fire services.
3.2.2(a) "Bureau" means bureau of fire
				services.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5659 - General definitions

Current through Vol. 24-12, July 15, 2024
Rule 659. Sections 3.3.21.1, 3.3.64, 3.3.65, and 3.3.66 are
				  added to the FL/CL code:
3.3.21 "Flash
				point" means the minimum temperature of a liquid at which sufficient vapor is
				given off to form an ignitable mixture with the air, near the surface of the
				liquid or within the vessel used, as determined by the appropriate test
				procedure and apparatus specified in section 4.4.
3.3.21.1 "Flow-through process tank" means a
				tank that forms an integral part of a production process through which there is
				a steady, variable, recurring, or intermittent flow of materials during the
				operation of the process and the tank is utilized to carry out or control the
				heating, cooling, mixing, blending, separating, metering, or chemical action of
				materials. The processing is done on a regular basis and it is the primary
				function of the tank. A flow-through process tank does not include a tank that
				is used for the storage of materials before its introduction into the
				production process or for the storage of finished products or byproducts from
				the production process or a tank that is only used to recirculate
				materials.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5660 - Testing requirements for tanks

Current through Vol. 24-12, July 15, 2024
Rule 660. Section 21.5.1.5 is added to the FL/CL code as
				  follows: 21.5.1.5 Testing of existing tanks may be performed pursuant to
				  section 21.5, instead of R 29.5224 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5661 - Closure of aboveground storage tanks

Current through Vol. 24-12, July 15, 2024
Rule 661. Section 21.7.4.1 of the FL/CL code is adopted with
				  the following changes: 21.7.4.1 Closure of aboveground storage tanks. An owner
				  or operator shall close tanks that have not been used for more than 12 months.
				  To permanently close an aboveground storage tank that is no longer needed to
				  store regulated substance, the owner or operator shall notify the department,
				  not less than 30 days before the intended closure, on form BFS 3858 provided by
				  the bureau. To permanently close an aboveground storage tank, the owner or
				  operator shall empty and clean the tank of all liquid and sludge, render it
				  vapor-free, and safeguard it against trespassing. Piping that is permanently
				  removed from service shall be emptied of all liquids and sludge, be purged and
				  capped, or be removed from the ground.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5662 - Inspection and maintenance of storage tanks and storage tank appurtenances

Current through Vol. 24-12, July 15, 2024
Rule 662. Section 21.8.1.1 is added to the FL/CL code as
				  follows: 21.8.1.1 Inspection of existing tanks may be performed pursuant to
				  section 21.8.1, instead of R 29.5221 and R 29.5231 of these
				  rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5663 - Inspection and maintenance of aboveground storage tanks

Current through Vol. 24-12, July 15, 2024
Rule 663. Section 22.17.2.1 is added to the FL/CL code as
				  follows:
22.17.2.1 Inspection of
				existing tanks may be performed pursuant to section 22.17.2, instead of R
				29.5221 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5664 - Location of loading and unloading facilities

Current through Vol. 24-12, July 15, 2024
Rule 664. Sections
				  28.4.2.1
				  and 28.4.2.2 are added to the FL/CL code as follows:
28.4.2.1 A fire protected tank or a tank in a
				vault is exempt from compliance with the separation distance requirements for
				the loading and unloading risers.
28.4.2.2 A tank which has a capacity of 3,000
				gallons (11,340 liters) or less which is located 10 feet (3 meters) from any
				building, and which is provided with spill and audible overfill protection or
				other means acceptable to the bureau based on the best interests of public
				health, safety, and welfare and the environment, is exempt from compliance with
				the separation distance requirements for loading and unloading
				risers.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5701 - Scope

Current through Vol. 24-12, July 15, 2024
Rule 701. Sections 1.1.1.1 and 1.1.3 are added to the FL/CL
				  code as follows: 1.1.1.1 This part does not apply to new or existing motor fuel
				  dispensing facilities that are part of an automotive assembly process and
				  dispense fuel exclusively during the assembly process. 1.1.3 All of the
				  provisions of part 2 of these rules apply to this part.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5702 - Equivalency

Current through Vol. 24-12, July 15, 2024
Rule 702. Sections 1.5.3 and 1.5.4 are added to the FL/CL
				  code as follows:
1.5.3 An owner or
				operator may apply for a variance to the rules by applying to the bureau with a
				satisfactory explanation as to why compliance is not possible. The bureau may
				approve a variance upon finding that the variance is based on the best
				interests of public health, safety, welfare, and property and the
				environment.
1.5.4 A person
				aggrieved by a final decision of the bureau on a request for variance may
				appeal to the circuit court within 21 days of the decision.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5703 - Prohibitions

Current through Vol. 24-12, July 15, 2024
Rule 703. Sections 1.8, 1.8.1, 1.8.2, 1.8.3, 1.8.4, 1.8.4.1,
				  1.8.4.1.1, 1.8.4.1.2, 1.8.5 are added to the FL/CL code as follows:
1.8 Prohibitions.
1.8.1 Upon notification by the bureau a
				person shall not deliver any liquid into a storage tank system under any
				circumstances that are prohibited by these rules or if a tank is not in
				compliance with these rules. The notification may include verbal or written
				communication or an affixed written notification on the storage tank
				system.
1.8.2 A person shall not
				tamper with, remove, or disregard written notification affixed to the storage
				tank system.
1.8.3 Any storage tank
				system or practice that is not in compliance with these rules is in violation
				of these rules.
1.8.4 An owner or
				operator shall not continue to use a storage tank system that is causing a
				release and shall expeditiously empty the system or the component that is
				causing the release until the system is repaired or replaced, pursuant to these
				rules.
1.8.4.1 A leak from the primary tank
				into the interstice of a new or existing secondary containment tank is not
				considered a release requiring that the tank be emptied, provided all of the
				following are met:
1.8.4.1.1 The secondary
				containment tank is repaired, replaced, or permanently closed within 6 months
				of discovery of the release.
1.8.4.1.2 Temporary or permanent liquid tight
				spill control is provided for the secondary containment tank within 7 days of
				discovery of the release to the secondary containment tank
				interstice.
1.8.4.1.3 There is no
				release from the outer shell of the secondary containment
				tank.
1.8.5
				The bureau may order, at the expense of the owner, a tightness test of the
				storage tank system when there is reason to believe that the integrity of the
				storage tank system is compromised.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5704 - Application

Current through Vol. 24-12, July 15, 2024
Rule 704. Sections 1.9 and 1.9.1 are added to the FL/CL code
				  as follows:
1.9 Installation
				Application Submittal Requirements.
1.9.1 An
				aboveground storage tank system installation application shall meet the
				requirements of section 1.8 of part 2 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5705 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 705. General. Section 3.1.1 of the FL/CL code is adopted
				  with the following changes:
3.1.1
				Definitions in chapter 3 apply to existing and new storage tank
				installations.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5706 - NFPA official definitions

Current through Vol. 24-12, July 15, 2024
Rule 706. Sections 3.2.1 and 3.2.2 of the FL/CL code are
				  adopted with the following changes:
3.2.1 "Approved" means acceptable to the
				bureau.
3.2.2 "Authority having
				jurisdiction (AHJ)" means the bureau of fire services.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5707 - General definitions

Current through Vol. 24-12, July 15, 2024
Rule 707. Sections 3.3.11.6, and 3.3.15.1 of the FL/CL code
				  are adopted with the following changes, and sections 3.3.15.4, 3.3.15.5,
				  3.3.19, 3.3.20, 3.3.20.1, and 3.3.20.2 are added to the FL/CL code as
				  follows:
3.3.11.6 "Unattended
				self-service motor fuel dispensing facility" means a motor fuel dispensing
				facility that does not have an attendant or employee on duty. The customer or
				vehicle operator conducts the dispensing operation. This includes coin,
				currency, membership card, and credit card dispensing operations. Unattended
				self-service motor fuel dispensing facilities shall include those, new or
				existing, where access is limited by locked dispensers, security fencing, or
				other means to effectively prevent unauthorized access or dispensing.
3.3.15.1 "Aboveground storage tank (AST)
				system" means a tank or combination of tanks, including the pipes that are
				connected to the tank, tanks, or ancillary equipment containment systems, if
				any, which is, was, or may have been, used to contain an accumulation of
				liquids and which has less than 10% of its volume, including the volume of the
				underground pipes that are connected to the tank, or tanks, beneath the surface
				of the ground.
3.3.15.4 "Tank
				system" means an AST system or an UST system.
3.3.15.5 "Underground storage tank (UST)
				system" means a tank or combination of tanks including the underground pipes
				that are connected to the tank or tanks or underground ancillary equipment
				containment system, if any, which is, was, or may have been, used to contain an
				accumulation of liquids and which has 10% or more of its volume, including the
				volume of the underground pipes that are connected to the tank or tanks,
				beneath the surface of the ground.
3.3.19 "Bureau" means bureau of fire
				services.
3.3.20 "Building" means
				any structure used or intended for supporting or sheltering any use or
				occupancy.
3.3.20.1 "Important building"
				means a building that is considered not expendable in an exposure
				fire.
3.3.20.2 "Storage tank
				building" means a 3-dimensional space that is enclosed by a roof and walls that
				cover more than 1/2 of the possible area of the sides of the space, is of
				sufficient size to allow entry by personnel, will likely limit the dissipation
				of heat or dispersion of vapors, and restricts access for fire
				fighting.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5708 - Aboveground storage tanks

Current through Vol. 24-12, July 15, 2024
Rule 708. Section 4.3.2.6.1 is added to the FL/CL code as
				  follows:
4.3.2.6.1 A minimum
				separation is not required for a listed secondary containment tank which is
				4,000 gallons (15,120 liters) or less and which has a 64 inch (162.6
				centimeters) nominal diameter or smaller.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5709 - General construction requirements

Current through Vol. 24-12, July 15, 2024
Rule 709. Section 7.4.2 of the FL/CL code is adopted with the
				  following changes:
7.4.2 General
				construction requirements. In major repair garages, where CNG, LNG, hydrogen or
				LPG fueled vehicles are repaired, all applicable requirements of R 29.4601 to R
				29.4652,
				R
				29.7001 to
				R
				29.7127, or R 29.6001 to R 29.6097 shall be
				met.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5801 - Scope

Current through Vol. 24-12, July 15, 2024
Rule 801. Section 1.1.6 is added to the FL/CL code as
				  follows:
1.1.6 All of the provisions
				of part 2 of these rules apply to this part.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5802 - Equivalency

Current through Vol. 24-12, July 15, 2024
Rule 802. Sections 1.5.3 and 1.5.4 are added to the FL/CL
				  code as follows:
1.5.3 An owner or
				operator may apply for a variance to the rules by applying to the bureau with a
				satisfactory explanation as to why compliance is not possible. The bureau may
				approve a variance upon finding that the variance is based on the best
				interests of public health, safety, welfare, and property and the
				environment.
1.5.4 A person
				aggrieved by a final decision of the bureau on a request for variance may
				appeal to the circuit court within 21 days of the decision.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5803 - Application

Current through Vol. 24-12, July 15, 2024
Rule 803. Section 1.7 of the FL/CL code is adopted with the
				  following changes and section 1.7.1 is added to the FL/CL code as
				  follows:
1.7 Installation application
				submittal requirements.
1.7.1 An aboveground
				storage tank system installation application shall meet the requirements of
				section 1.8 of part 2 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5804 - Prohibitions

Current through Vol. 24-12, July 15, 2024
Rule 804. Sections 1.8, 1.8.1, 1.8.2, 1.8.3, 1.8.4, 1.8.4.1,
				  1.8.4.1.1, 1.8.4.1.2, 1.8.4.1.3, 1.8.5 are added to the FL/CL code as
				  follows:
1.8 Prohibitions.
1.8.1 Upon notification by the bureau a
				person shall not deliver any liquid into a storage tank system under any
				circumstances that are prohibited by these rules or if a tank is not in
				compliance with these rules. The notification may include verbal or written
				communication or an affixed written notification on the storage tank
				system.
1.8.2 A person shall not
				tamper with, remove, or disregard written notification affixed to the storage
				tank system.
1.8.3 Any storage tank
				system or practice that is not in compliance with these rules is in violation
				of these rules.
1.8.4 An owner or
				operator shall not continue to use a storage tank system that is causing a
				release and shall expeditiously empty the system or the component that is
				causing the release until the system is repaired or replaced, pursuant to these
				rules.
1.8.4.1 A leak from the primary tank
				into the interstice of a new or existing secondary containment tank is not
				considered a release requiring that the tank be emptied, provided all of the
				following are met:
1.8.4.1.1 The secondary
				containment tank is repaired, replaced, or permanently closed within 6 months
				of discovery of the release.
1.8.4.1.2 Temporary or permanent liquid tight
				spill control is provided for the tank within 7 days of discovery of the
				release to the secondary containment tank interstice.
1.8.4.1.3 There is no release from the outer
				shell of the secondary containment tank.
1.8.5 The bureau may order, at the expense of
				the owner, a tightness test of the storage tank system when there is reason to
				believe that the integrity of the storage tank system is
				compromised.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5805 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 805. Scope. Section 3.1.1 is added to the FL/CL code as
				  follows:
3.1.1 Definitions in chapter
				3 apply to existing and new storage tank installations.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5806 - NFPA official definitions

Current through Vol. 24-12, July 15, 2024
Rule 806. Sections 3.2.1 and 3.2.2 of the FL/CL code are
				  adopted with the following changes:
3.2.1 "Approved" means acceptable to the
				bureau.
3.2.2 "Authority having
				jurisdiction (AHJ)" means the bureau of fire services.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5807 - General definitions

Current through Vol. 24-12, July 15, 2024
Rule 807. Sections 3.3.57.6, 3.3.57.7, 3.3.57.8, 3.3.68,
				  3.3.69, 3.3.69(a), 3.3.69(b) are added to the FL/CL code as follows:
3.3.57.6 "Aboveground storage tank (AST)
				system" means a tank or combination of tanks, including the pipes that are
				connected to the tank, tanks, or ancillary equipment containment systems, if
				any, which is, was, or may have been, used to contain an accumulation of
				liquids and which has less than 10% of its volume, including the volume of the
				underground pipes that are connected to the tank, or tanks, beneath the surface
				of the ground.
3.3.57.7 "Tank
				system" means an AST system or UST system.
3.3.57.8 "Underground storage tank (UST)
				system" means a tank or combination of tanks including the underground pipes
				that are connected to the tank or tanks or underground ancillary equipment
				containment system, if any, which is, was, or may have been, used to contain an
				accumulation of liquids and which has 10% or more of its volume, including the
				volume of the underground pipes that are connected to the tank or tanks,
				beneath the surface of the ground.
3.3.68 "Bureau" means bureau of fire
				services.
3.3.69 "Building" means
				any structure used or intended for supporting or sheltering any use or
				occupancy.
3.3.69(a) "Important building"
				means a building that is considered not expendable in an exposure
				fire.
3.3.69(b) "Storage tank
				building" means a 3-dimensional space that is enclosed by a roof and walls that
				cover more than 1/2 of the possible area of the sides of the space, is of
				sufficient size to allow entry by personnel, will likely limit the dissipation
				of heat or dispersion of vapors, and restricts access for fire
				fighting.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5808 - Acceptable liquid fuels

Current through Vol. 24-12, July 15, 2024
Rule 808. Sections 4.5.1(6) and 4.5.1(7) of the FL/CL code
				  are adopted with the following changes:
4.5.1
				(6) ASTM D7467, Standard specification for Diesel Fuel Oil,
				Biodiesel Blend (B6-B20)
4.5.1 (7)
				ASTM D975, Standard Specification for Diesel Fuel Oils.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5809 - Basic design and construction of tanks

Current through Vol. 24-12, July 15, 2024
Rule 809. Section 7.2.3 of the FL/CL code is adopted with the
				  following changes: 7.2.3 Tanks meeting the requirements of part 2 of these
				  rules meet the requirements of this section.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5810 - Areas subject to flooding or earthquake

Current through Vol. 24-12, July 15, 2024
Rule 810. Section 7.2.8.1 of the FL/CL code is adopted with
				  the following changes: 7.2.8.1 When in a designated flood zone, the applicable
				  requirements of part 2 of these rules shall be met.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5811 - Installation of underground tanks

Current through Vol. 24-12, July 15, 2024
Rule 811. Sections 7.4.5 and 7.4.7 of the FL/CL code are
				  adopted with the following changes:
7.4.5 Underground tanks shall be installed
				pursuant to manufacturers instructions and pursuant to the applicable
				requirements of part 2 of these rules.
7.4.7 Underground tanks that are taken out of
				service shall be removed or permanently closed pursuant to part 2 of these
				rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5812 - Installation of outside aboveground tanks

Current through Vol. 24-12, July 15, 2024
Rule 812. Section 7.8.3 of the FL/CL code is adopted with the
				  following changes:
7.8.3 A tank or
				tanks whose capacity exceeds 660 gallons (2500L) shall be installed pursuant to
				part 2 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5813 - Tank leakage testing and periodic inspection

Current through Vol. 24-12, July 15, 2024
Rule 813. Section 7.11.1(2) of the FL/CL code is adopted with
				  the following changes:
7.11.1(2) For
				field-erected tanks, the applicable requirements of part 2 of these rules
				apply.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5814 - Permanent abandonment of underground tanks

Current through Vol. 24-12, July 15, 2024
Rule 814. Section 7.14 of the FL/CL code is adopted with the
				  following changes:
7.14 Permanent
				abandonment of underground tanks. If an underground fuel storage tank is
				permanently removed from service, the applicable requirements of part 2 of
				these rules apply.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5815 - Centralized oil distribution systems

Current through Vol. 24-12, July 15, 2024
Rule 815. Section 9.2.9 of the FL/CL code is adopted with the
				  following changes: 9.2.9 Aboveground tanks shall be provided with spill control
				  by meeting the applicable requirements of part 2 of these
				  rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5816 - Installation clearances

Current through Vol. 24-12, July 15, 2024
Rule 816. Section 12.6.2 of the FL/CL code is adopted with
				  the following changes:
12.6.2 Used oil
				burning appliances shall be separated from flammable or combustible liquids
				pursuant to part 3 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5901 - Scope

Current through Vol. 24-12, July 15, 2024
Rule 901. Section 1.1.1 is added to the FL/CL code as
				  follows:
1.1.1 All of the provisions
				of part 2 of these rules apply to this part.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5902 - Application

Current through Vol. 24-12, July 15, 2024
Rule 902. Section 1.3.4 added to the FL/CL code as
				  follows:
1.3.4 This part does not
				apply to any portion of a new or existing stationary fire pump system where the
				requirements of part 5 conflict with the requirements of NFPA 20.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5903 - Equivalency

Current through Vol. 24-12, July 15, 2024
Rule 903. Sections 1.5.3 and 1.5.4 are added to the FL/CL
				  code as follows:
1.5.3 An owner or
				operator may apply for a variance to the rules by applying to the bureau with a
				satisfactory explanation as to why compliance is not possible. The bureau may
				approve a variance upon finding that the variance is based on the best
				interests of public health, safety, welfare, and property and the
				environment.
1.5.4 A person
				aggrieved by a final decision of the bureau on a request for variance may
				appeal to the circuit court within 21 days of the decision.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5904 - Installation application

Current through Vol. 24-12, July 15, 2024
Rule 904. Sections 1.7 and 1.7.1 are added to the FL/CL code
				  as follows:
1.7 Installation
				application submittal requirements.
1.7.1 An
				aboveground storage tank system installation application shall meet the
				requirements of section 1.8 of part 2 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5905 - Prohibitions

Current through Vol. 24-12, July 15, 2024
Rule 905. Sections 1.8, 1.8.1, 1.8.2, 1.8.3, 1.8.4, 1.8.4.1,
				  1.8.4.1.1, 1.8.4.1.2, 1.8.4.1.3, and 1.8.5 are added to the FL/CL code as
				  follows:
1.8 Prohibitions.
1.8.1 Upon notification by the bureau a
				person shall not deliver any liquid into a storage tank system under any
				circumstances that are prohibited by these rules or if a tank is not in
				compliance with these rules. The notification may include verbal or written
				communication or an affixed written notification on the storage tank
				system.
1.8.2 A person shall not
				tamper with, remove, or disregard written notification affixed to the storage
				tank system.
1.8.3 Any storage tank
				system or practice that is not in compliance with these rules is in violation
				of these rules.
1.8.4 An owner or
				operator shall not continue to use a storage tank system that is causing a
				release and shall expeditiously empty the system or the component that is
				causing the release until the system is repaired or replaced, pursuant to these
				rules.
1.8.4.1 A leak from the primary tank
				into the interstice of a new or existing secondary containment tank is not
				considered a release requiring that the tank be emptied, provided all of the
				following are met:
1.8.4.1.1 The secondary
				containment tank is repaired, replaced, or permanently closed within 6 months
				of discovery of the release.
1.8.4.1.2 Temporary or permanent liquid tight
				spill control is provided for the secondary containment tank within 7 days of
				discovery of the release to the secondary containment tank
				interstice.
1.8.4.1.3 There is no
				release from the outer shell of the secondary containment
				tank.
1.8.5
				The bureau may order, at the expense of the owner, a tightness test of the
				storage tank system when there is reason to believe that the integrity of the
				storage tank system is compromised.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5906 - NFPA publications

Current through Vol. 24-12, July 15, 2024
Rule 906. Section
				  2.2
				  of the FL/CL code is amended to add reference to NFPA 20 as follows:
NFPA 20, Standard for the Installation of Stationary Pumps
				  for Fire Protection, 2013 edition.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5907 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 907. General. Section 3.1.1 is added to the FL/CL code
				  as follows:
3.1.1 Definitions in
				chapter 3 apply to existing and new storage tank installations.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5908 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 908. NFPA official definitions. Sections 3.2.1 and 3.2.2
				  of the FL/CL code are adopted with the following changes:
3.2.1 "Approved" means acceptable to the
				bureau.
3.2.2 "Authority having
				jurisdiction (AHJ)" means the bureau of fire services.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5909 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 909. General definitions. Sections 3.3(a), 3.3(a)(1),
				  3.3(a)(2), 3.3(b), 3.3.11.4, 3.3.11.5, and 3.3.11.6 are added to the FL/CL code
				  as follows:
3.3(a) "Building" means
				any structure used or intended for supporting or sheltering any use or
				occupancy.
3.3(a)(1) "Important building"
				means a building that is considered not expendable in an exposure
				fire.
3.3(a)(2) "Storage tank
				building" means a 3-dimensional space that is enclosed by a roof and walls that
				cover more than 1/2 of the possible area of the sides of the space, is of
				sufficient size to allow entry by personnel, will likely limit the dissipation
				of heat or dispersion of vapors, and restricts access for fire
				fighting.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5910 - Gas piping

Current through Vol. 24-12, July 15, 2024
Rule 910. Section 5.1.1(3) of the FL/CL code is adopted with
				  the following changes:
5.1.1(3) LP-gas
				systems shall be installed pursuant to the provisions of R 29.6001 to R
				29.6097.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5911 - Design and construction of liquid fuel tanks

Current through Vol. 24-12, July 15, 2024
Rule 911. Section
				  6.1
				  of the FL/CL code is adopted with the following changes and section
				  6.1.3
				  is added to the FL/CL code as follows:
6.1 Design and construction of liquid fueled
				tanks. Fuel tanks shall be constructed pursuant to the applicable tank
				specifications in part 2 of these rules.
6.1.3 Tanks not used to store liquids for 12
				months shall be permanently closed by complying with the requirements of part 2
				of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5912 - Installation criteria for fuel tanks containing class I fuels

Current through Vol. 24-12, July 15, 2024
Rule 912. Section
				  6.2.2
				  of the FL/CL code is adopted with the following changes:
6.2.2 Fuel tanks shall be installed pursuant
				to the applicable installation provisions of part 2 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5913 - Fuel tanks outdoors (aboveground or underground) or beneath a structure

Current through Vol. 24-12, July 15, 2024
Rule 913. Section
				  6.3.3
				  of the FL/CL code is adopted with the following changes:
6.3.3 Fuel tanks outdoors (aboveground or
				underground) or beneath a structure. Fuel tanks located outside, either
				aboveground or underground, or beneath a structure shall comply with the
				applicable provisions of part 2 of these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5914 - Installation criteria for fuel tanks containing liquefied petroleum gases

Current through Vol. 24-12, July 15, 2024
Rule 914. Section
				  6.4
				  of the FL/CL code is adopted with the following changes:
6.4 Installation criteria for fuel tanks
				containing liquefied petroleum gases. LP-Gas systems in the liquid phase shall
				be installed pursuant to the provisions of R 29.6001 to
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Storage and Handling of Flammable and Combustible Liquids › Section R. 29.5915 - Filling

Current through Vol. 24-12, July 15, 2024
Rule 915. Section
				  6.6.3
				  of the FL/CL code is adopted with the following changes: 6.6.3 Piping for fuel
				  tanks shall be pursuant to part 2 of these rules.