reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30715 - Permits

Current through Vol. 24-12, July 15, 2024
Rule 715.
Sections 106.5.3 and 106.5.4 of the code are amended to
						  read as follows:
106.5.3. Expiration. Each permit issued by the code
						  official under the provisions of the code shall expire by limitation and become
						  null and void if the work authorized by this permit is not commenced within 180
						  days from the date of such permit, or if the work authorized by this permit is
						  suspended or abandoned at any time after the work is commenced for a period of
						  180 days. Before this work may be recommenced, the permit shall be reinstated
						  if the code has not changed. If the code has changed and the work was not
						  started, a new permit shall be first obtained for such work, provided no
						  changes have been made or will be made in the original construction document
						  for this work and provided further that the suspension or abandonment has not
						  exceeded 1 year.
106.5.4. Application and extensions. The authority
						  having jurisdiction may grant a 180-day extension of the original permit time
						  period of 180 days, upon presentation by the permittee of a satisfactory reason
						  for failure to start or complete the work or activity authorized by the
						  permit.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30716 - Fees

Current through Vol. 24-12, July 15, 2024
Rule 716. Section
						  109.1 of the code is amended to
						  read as follows:
109.1. Fees. The fees
						prescribed by the act shall be paid to the enforcing agency of the jurisdiction
						before a permit to begin work for new construction, alteration, removal,
						demolition, or other building operation may be issued. In addition, an
						amendment to a permit necessitating an additional fee shall not be approved
						until the additional fee is paid. The authority having jurisdiction may
						withhold issuance of any newly requested permits to an individual who has
						outstanding permit fees owed to that authority having jurisdiction.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30717 - Right of entry

Current through Vol. 24-12, July 15, 2024
Rule 717.
Section 104.4 of the code is amended to read as
						  follows: 104.4 Right of entry. If a building or premises is occupied, the code
						  official shall present his or her credentials to the occupant and request
						  entry. If a building or premises is unoccupied, the code official shall first
						  make a reasonable effort to locate either the owner, the owner's authorized
						  agent or other person having care or control of the building or premises and
						  request entry. If entry is refused, the code official has recourse to every
						  remedy provided by law to secure entry.
When a code official has first obtained a proper
						  inspection warrant or other remedy provided by law to secure entry, the owner,
						  owner's authorized agent or occupant or person having charge, care or control
						  of the building or premises shall not fail or neglect, after a proper request
						  is made as provided in this rule, to permit the code official prompt entry into
						  the building or premises to inspect or examine the building or premises
						  pursuant to this code.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30718 - Violation penalties

Current through Vol. 24-12, July 15, 2024
Rule 718. Section 108.4 of the code is amended to read
						  as follows:
108.4. Violation penalties. A person who violates a
						  provision of the code, who fails to conform with any of the requirements
						  thereof, or who erects, installs, alters, or repairs plumbing work in violation
						  of the approved construction documents or directive of the enforcing agency, or
						  a permit or certificateissued under the provisions of the code shall be subject
						  to review and may result in licensing action pursuant to the skilled trades
						  regulation act, 2016 PA 407, MCL 339.5101 to 339.5517.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30721 - Required tests

Current through Vol. 24-12, July 15, 2024
Rule 721.
Sections 309.3 and 312.1 of the code are amended and
						  section 312.3 is added to read as
						  follows:
309.3. Flood hazard areas
						subject to high-velocity wave action. Structures located in flood hazard areas
						subject to high-velocity wave action shall meet the requirements of section
						309.2. The plumbing systems,
						pipes, and fixtures shall not be mounted on or penetrate through walls intended
						to break away under flood loads. 312.1. Required tests. The permit holder shall
						make the applicable tests prescribed in sections
						312.2 to
						312.10.2 to determine compliance
						with the code. The permit holder shall give reasonable advance notice to the
						code official when the plumbing work is ready for testing. The equipment,
						material, power, and labor necessary for the inspection and test shall be
						furnished by the permit holder and the permit holder shall be responsible for
						determining that the work will withstand the test pressure prescribed in this
						rule. All plumbing system piping shall be tested with either water or, for
						piping systems other than plastic, by air. After the plumbing fixtures have
						been set and their traps filled with water, the entire drainage system shall be
						submitted to final tests. The code official shall require the removal of any
						cleanouts if necessary to ascertain if the pressure has reached all parts of
						the system.
Exception: Drainage and vent low pressure air tests for
						  plastic piping systems shall be acceptable as prescribed in section
						  312.3 of the code.
312.3 Drainage and vent air test.
						An air test shall be made by forcing air into the system until there is a
						uniform gauge pressure of 5 psi (34.5 kPa) or sufficient to balance a 10-inch
						(254 mm) column of mercury. This pressure shall be held for a test period of
						not less than 15 minutes. Any adjustments to the test pressure required because
						of changes in ambient temperatures or the seating of gaskets shall be made
						before the beginning of the test period.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30722 - Separate facilities

Current through Vol. 24-12, July 15, 2024
Rule 722. Section 403.2 of the code is amended to read
						  as follows:
403.2. Separate
						facilities. Where plumbing fixtures are required, separate facilities shall be
						provided for each sex.
Exceptions:
1. Separate facilities shall not be required
						for private facilities.
2. Separate
						facilities shall not be required in structures or tenant spaces with a total
						occupant load, including both employees and customers, of 15 or
						fewer.
3. Separate facilities shall
						not be required in mercantile occupancies in which the maximum occupant load is
						50 or fewer.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30723 - Distance of trap from vent

Current through Vol. 24-12, July 15, 2024
Rule 723. Section 909.1 of the code is amended to read
						  as follows:
909.1 Distance of trap
						from vent. Each fixture trap shall have a protecting vent located so that the
						slope and the developed length in the fixture drain from the trap weir to the
						vent fitting are within the requirements in table 909.1.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725 - Industrial or commercial wastes

Current through Vol. 24-12, July 15, 2024
Rule 725.Section
						  302.2 of the code is amended to
						  read as follows:
302.2. Industrial or
						commercial wastes. Industrial or commercial wastes shall not be introduced into
						the public sewer or private disposal system without receiving prior approval in
						the following manner:
(1) Industrial or
						commercial wastes discharged to a public sewer system are subject to review,
						approval, and regulation by the owner of the sewage treatment system under the
						authority of the federal water pollution control act of 1972, as amended,
						33
						U.S.C.1251 et seq., and sections 3101 to 3119
						of Act No. 451 of the Public Acts of 1994, as amended, being 324. 3101 to 324.
						3119 of the Michigan Compiled Laws.
(2) Industrial or commercial wastes
						discharged to an on-site disposal system are subject to review, approval, and
						regulation by the Michigan department of environmental quality under the
						authority of sections 3101 to 3119 of Act No. 451 of the Public Acts of 1994,
						as amended, being 324.3101 to 324.3119 of the Michigan Compiled Laws.
(3) Industrial or commercial wastes
						discharged to an on-site holding tank are subject to review, approval, and
						regulation under sections 3101 to 3119, 11101 to 11152, and 12101 to 12118 of
						Act No. 451 of the Public Acts of 1994, as amended, being 324.3101 to 324.3119,
						324.11101 to 324.11152 and 324.12101 to 324.12118 of the Michigan Compiled
						Laws, and the federal resource conservation and recovery act of 1976, as
						amended,
						42
						U.S.C.6901 et seq.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725a - Radioactive material

Current through Vol. 24-12, July 15, 2024
Rule 725a.Section 302.2.1 is added to the code to read
						  as follows:
302.2.1. Radioactive
						material. Possession of radioactive material is regulated by state or federal
						license. The disposal of radioactive material shall not create a hazard to
						operational or maintenance personnel of the institution or to the public.
						Radioactive waste disposal is controlled by the Michigan department of
						environmental quality by conditions for disposal in a radioactive material
						license issued under the authority of part 135 of Act No.368 of the Public Acts
						of 1978, as amended, being 333.13501 et seq.of the Michigan Compiled Laws, and
						the ionizing radiation rules, being
						R
						325.5001 et seq. of the Michigan Administrative Code,
						or is controlled by the United States nuclear regulatory commission by
						conditions for disposal in a license issued under the authority of the atomic
						energy act of 1954,
						42
						U.S.C.2011 et seq.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725c - Venting of fixture drains

Current through Vol. 24-12, July 15, 2024
Rule 725c. Section 909.2 of the code is amended to read
						  as follows:
909.2. Venting of fixture
						drains. The vent for a fixture drain, except where serving a fixture with
						integral traps, such as water closets, shall connect above the weir of the
						fixture trap being vented. The total slope shall not exceed the diameter of the
						fixture drain.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725d - Type of fixtures

Current through Vol. 24-12, July 15, 2024
Rule 725d. Section
						  915.1 is added to the code to
						  read as follows:
915.1. Type of
						fixtures. A combination waste and vent system shall not serve fixtures other
						than floor drains, sinks, lavatories and drinking fountains. Combination waste
						and vent systems shall not receive the discharge from a food waste disposer or
						clinical sink.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725e - Fixture traps

Current through Vol. 24-12, July 15, 2024
Rule 725e. Section
						  1002.1 is added to the code to
						  read as follows:
1002.1. Fixtures
						traps. Each plumbing fixture shall be separately trapped by a liquid-seal trap,
						except as otherwise allowed by this code. The vertical distance from the
						fixture outlet to the trap weir shall not exceed 24 inches, 609.6 mm, and the
						horizontal distance shall not exceed 30 inches, 762 mm, measured from the
						centerline of the fixture outlet to the centerline of the inlet of the trap.
						The height of a clothes washer standpipe above a trap shall conform to section
						802.4.3. A fixture shall not be
						double trapped.
Exceptions:
1.
						This section shall not apply to fixtures with integral traps.
2. A combination plumbing fixture is allowed
						to be installed on 1 trap, provided that 1 compartment is not more than 6
						inches, 152 mm, deeper than the other compartment and the waste outlets are not
						more than 30 inches, 762 mm, apart.
3. A grease interceptor intended to serve as
						a fixture trap in accordance with the manufacturer's installation instructions
						shall be allowed to serve as the trap for a single fixture or a combination
						sink of not more than 3 compartments where the vertical distance from the
						fixture outlet to the inlet of the interceptor does not exceed 30 inches, 762
						mm, and the developed length of the waste pipe from the most upstream fixture
						outlet to the inlet of the interceptor does not exceed 60 inches, 1524
						mm.
4. Floor drains in multilevel
						parking structures that discharge to a building storm sewer shall not be
						required to be individually trapped. Where floor drains in multilevel parking
						structures are required to discharge to a combined building sewer system, the
						floor drains shall not be required to be individually trapped provided that
						they are connected to a main trap in accordance with section
						1103.1.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725f - Inspection and testing of backflow prevention assemblies

Current through Vol. 24-12, July 15, 2024
Rule 725f. Section
						  312.10 is added to the code to
						  read as follows:
312.10. Inspection
						and testing of backflow prevention assemblies. Inspection and testing shall
						comply with section
						312.10.1 and
						312.10.2
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725g - Inspections

Current through Vol. 24-12, July 15, 2024
Rule 725g. Section
						  312.10.1 is added to the code to
						  read as follows:
312.10.1.
						Inspections. Inspections shall be made of all backflow prevention assemblies
						and air gaps after installation or relocation to determine whether the
						assemblies are operable and air gaps exist.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30725h - Testing

Current through Vol. 24-12, July 15, 2024
Rule 725h. Section
						  312.10.2 is added to the code to
						  read as follows:
312.10.2. Testing.
						Reduced pressure principle, double check, pressure vacuum breaker, reduced
						pressure detector fire protection, double check detector fire protection, and
						spill-resistant vacuum breaker backflow preventer assemblies and hose
						connection backflow preventers shall be tested at the time of installation,
						immediately after repairs or at the time of relocation. Test gauges shall
						comply with ASSE 1064. The testing procedure shall be performed in accordance
						with 1 of the following standards:
(a) ASSE
						5013.
(b) ASSE 5015.
(c) ASSE 5020.
(d) ASSE 5047.
(e) ASSE 5048.
(f) ASSE 5052.
(g) ASSE 5056.
(h) CSA B64.10.
(i) CSA
						B64.10.1.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30726 - Building sewer

Current through Vol. 24-12, July 15, 2024
Rule 726.
Table 702.3 and section 703.1 of the code are amended
						  to read as follows:
MATERIAL
STANDARD
Acrylonitrile butadiene styrene (ABS) plastic
								  pipe in IPS diameters, including Schedule 40, DR 22 (PS 200) and DR 24 (PS
								  140); with a solid, cellular core or composite wall
ASTM D2661; ASTM
								  F628; ASTM F1488; CSA B181.1
Acrylonitrile butadiene styrene (ABS) plastic
								  pipe in sewer and drain diameters, including SDR 42 (PS 20), PS 35, SDR 35 (PS
								  45), PS 50, PS 100, PS 140, SDR 23.5 (PS 150) and PS 200; with a solid,
								  cellular core or composite wall.
ASTM F1488; ASTM D2751
Cast-iron pipe
ASTM A74; ASTM A888; CISPI
								  301
Concrete pipe
ASTM C14; ASTM C76; CSA
								  A257.1M; CSA A257.2M
Copper or copper-alloy tubing (Type K or
								  L)
ASTM B75; ASTM B88; ASTM B251
Polyethylene (PE) plastic pipe
								  (SDR-PR)
ASTM F714
Polypropylene (PP) plastic pipe
ASTM
								  F2736; ASTM F2764; CSA B182.13
Polyvinyl chloride (PVC) plastic pipe in IPS
								  diameters, including Schedule 40, DR 22 (PS 200) and DR 24 (PS 140); with a
								  solid, cellular core or composite wall
ASTM D2665; ASTM F891; ASTM
								  F1488
Polyvinyl chloride (PVC) plastic pipe in sewer
								  and drain diameters, including PS 25, SDR 41 (PS 28), PS 35, SDR 35 (PS 46), PS
								  50, PS 100, SDR 26 (PS 115), PS 140 and PS 200; with a solid, cellular core or
								  composite wall. ASTM F891; ASTM F1488; ASTM D3034; CSA B182.2; CSA B182.4
								  Polyvinyl
ASTM F891; ASTM F1488; ASTM D3034; CSA B182.2; CSA
								  B182.4
Polyvinyl chloride (PVC) plastic pipe with a
								  3.25-inch O.D. and a solid, cellular core or composite wall
ASTM D2949;
								  ASTM F1488
Polyvinylidene fluoride (PVDF) plastic
								  pipe
ASTM F1673; CSA B181.3
Stainless steel drainage systems, Types 304 and
								  316L
ASME A112.3.1
Vitrified clay pipeVitrified clay
								  pipe
ASTM C4; ASTM C700
For SI: 1 inch = 25.4 mm.
703.2 Drainage pipe in filled ground. Where a building
						  sewer or building drain is installed on filled or unstable ground, the drainage
						  pipe shall conform to one of the standards for ABS plastic pipe, cast-iron
						  pipe, copper or copper-alloy tubing, or PVC plastic pipe indicated in Table
						  702.3
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30726a - Pipe fittings

Current through Vol. 24-12, July 15, 2024
Rule 726a. Section
						  702.4 is added to the code to
						  read as follows:
Table 702.4
PIPE FITTINGS
MATERIAL
STANDARD
Acrylonitrile butadiene styrene (ABS) plastic
										pipe in IPS diameters
ASME A112.4.4; ASTM D2661; ASTM F628; CSA
										B181.1
Acrylonitrile butadiene styrene (ABS) plastic
										pipe in sewer and drain diameters
ASTM D2751
Cast iron
ASME B16.4; ASME B16.12; ASTM A74; ASTM A888;
										CISPI 301
Copper or Copper alloy
ASME B16.15; ASME B16.18; ASME B16.22; ASME
										B16.23; ASME B16.26; ASME B16.29
Galvanized steel pipe
ASTM A53
Glass
ASTM C1053
Gray iron and ductile iron
AWWA C110/A21.10
Polyethylene
ASTM D2683
Polyolefin
ASTM F1412; CSA B181.3
Polyvinyl chloride (PVC) plastic in IPS
										diameters
ASME A112.4.4; ASTM D2665; ASTM F1866
Polyvinyl chloride (PVC) plastic pipe in
										sewer and drain diameters
ASTM D3034
Polyvinyl chloride (PVC) plastic pipe with a
										3.25-inch O.D.
ASTM D2949
Polyvinylidene fluoride (PVDF) plastic
										pipe
ASTM F1673; CSA B181.3
Stainless steel drainage system, Types 304
										and 316L
ASME A112.3.1
Steel
ASME B16.9; ASME B16.11; ASME B16.28
Vitrified clay
ASTM C700
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30727 - Water distribution pipe

Current through Vol. 24-12, July 15, 2024
Rule 727. Table 605.4 of the code is amended to read as
						  follows:
Table 605.4
WATER DISTRIBUTION PIPE
MATERIAL
STANDARD
Chlorinated polyvinyl chloride (CPVC) plastic
										pipe and tubing
ASTM D2846; ASTM F441; ASTM F442; CSA
										B137.6
Chlorinated polyvinyl
										chloride/aluminum/chlorinated polyvinyl chloride (CPVC/AL/CPVC)
ASTM F2855
Copper or copper-alloy pipe
ASTM B42; ASTM B302; ASTM B43
Copper or copper-alloy tubing (Type K, WK, L,
										WL, M or WM)
ASTM B75; ASTM B88; ASTM B251; ASTM
										B447
Cross-linked polyethylene (PEX) plastic
										tubing
ASTM F876; CSA B137.5
Cross-linked
										polyethylene/aluminum/cross-linked polyethylene (PEX-AL-PEX) pipe
ASTM F1281; ASTM F2262; CSA B137.10
Cross-linked
										polyethylene/aluminum/high-density polyethylene (PEX-AL-HDPE)
ASTM F1986
Ductile iron pipe
AWWA C151/A21.51; AWWA C115/A21.15
Galvanized steel pipe
ASTM A53
Polyethylene/aluminum/polyethylene (PE-AL-PE)
										composite pipe
ASTM F1282
Polyethylene of raised temperature (PE-RT)
										plastic tubing
ASTM F2769; CSA B137.18
Polypropylene (PP) plastic pipe or
										tubing
ASTM F2389; CSA B137.11
Stainless steel pipe (Type 304/304L)
ASTM A312; ASTM A778
Stainless steel pipe (Type 316/316L)
ASTEM A312; ASTEM A778
(REFERENCE
						  R 408.30732, SECTION
						  605.2.1)
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30727a - Location of full-open valve

Current through Vol. 24-12, July 15, 2024
Rule 727a. Section
						  606.1 is added to the code to
						  read as follows:
606.1. Location of
						full-open valve. Full-open valves shall be installed in the following
						locations:
1. On the building water service
						pipe from the public water supply near the curb.
2. On the water distribution supply pipe at
						the entrance into the structure.
2.1. In
						multiple tenant buildings, where a common water supply piping system is
						installed to supply spaces other than 1 and 2 family dwellings, a main shutoff
						valve shall be provided for each tenant or space.
3. On the discharge side of every water
						meter.
4. On the base of every
						water riser pipe in occupancies other than multiple-family residential
						occupancies that are 2 stories or less in height and in 1 and 2 family
						residential occupancies.
5. On the
						top of every water down-feed pipe in occupancies other than 1 and 2 family
						residential occupancies.
6. On the
						entrance to every water supply pipe to a dwelling unit, except where supplying
						a single fixture equipped with individual stops.
7. On the water supply pipe to a gravity or
						pressurized water tank.
8. On the
						water supply pipe to every water heater.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30727b - Labeling of water distribution pipes in bundles

Current through Vol. 24-12, July 15, 2024
Rule 727b. Section
						  606.7 is added to the code to
						  read as follows:
606.7. Labeling of
						water distribution pipes in bundles. Where water distribution piping is bundled
						at installation, each pipe in the bundle shall be identified using stenciling,
						commercially available pipe labels, or approved color-coded piping materials.
						The identification shall indicate the pipe contents and the direction of flow
						in the pipe. The interval of the identification markings on the pipe shall not
						exceed 25 feet, 7620mm. There shall be at least 1 identification label on each
						pipe in each room, space, or story.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30727c - Tempered water temperature control

Current through Vol. 24-12, July 15, 2024
Rule 727c. Section
						  607.1.2 is added to the code to
						  read as follows:
607.1.2. Tempered
						water temperature control. Tempered water shall be controlled by 1 of the
						following:
1. A limiting device conforming to
						ASSE 1070/ASME A112.1070/CSA B125.70 and set to not greater than 110 degrees
						Fahrenheit or 43 degrees Celsius.
2. A thermostatic mixing valve conforming to
						ASSE 1017.
3. A water heater
						conforming to ASSE 1082.
4. A water
						heater conforming to ASSE 1084.
5.
						Emergency eye wash tepid water limits shall not be less than 60 degrees
						Fahrenheit or 15.6 degrees Celsius and not greater than 100 degrees Fahrenheit
						or 37.8 degrees Celsius and conform to ASSE
						1071.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30729a - Pipe fitting

Current through Vol. 24-12, July 15, 2024
Rule 729a. Table 605.5 is added to the code to read as
						  follows:
Table 605.5
PIPE FITTINGS
MATERIAL
STANDARD
Acrylonitrile butadiene styrene (ABS)
										plastic
ASTM D2468
Cast iron
ASME B16.4
Chlorinated polyvinyl chloride (CPVC)
										Plastic
ASSE 1061; ASTM D2846; ASTM F437; ASTM F438;
										ASTM F439; CSA B137.6
Copper or copper alloy
ASME B16.15; ASME B16.18; ASME B16.22; ASME
										B16.26; ASME B16.51; ASSE 1061; ASTM F1476; ASTM F1548; ASTM F3226
Cross-linked
										polyethylene/aluminum/high-density polyethylene (PEX-AL-HDPE)
ASTM F1986
Fittings for cross-linked polyethylene (PEX)
										plastic tubing
ASSE 1061; ASTM F877; ASTM F1807; ASTM F
										1960; ASTM F2080; ASTM F2098, ASTM F2159; ASTM 2434; ASTM F2735; CSA
										B137.5
Fittings for polyethylene of raised
										temperature (PE-RT) plastic tubing
ASSE 1061; ASTM D3261; ASTM F1807; ASTM 2098;
										ASTM F2159; ASTM 2735; ASTM F2769; CSA B137.18
Galvanized steel pipe
ASTM A53
Gray iron and ductile iron
ASTM F1476; ASTM F1548; AWWA C110/A21.10;
										AWWA C153/A21.53
Insert fittings for
										polyethylene/aluminum/polyethylene (PE-AL-PE) and cross-linked
										polyethylene/aluminum/cross-linked polyethylene (PEX-AL-PEX)
ASTM F1281; ASTM F1282; ASTM F1974; CSA
										B137.9; CSA B137.10
Malleable iron
ASME B16.3
Metal (brass) insert fittings for
										polyethylene/aluminum/polyethylene (PE-AL-PE) and cross-linked
										polyethylene/aluminum/cross-linked polyethylene (PEX-AL-PEX)
ASTM F1974
Polyethylene (PE) plastic pipe
ASTM D2609; ASTM D2683; ASTM D3261; ASTM
										F1055; CSA B137.1
Polypropylene (PP) plastic pipe or
										tubing
ASTM F2389; CSA B137.11
Polyvinyl chloride (PVC) plastic
ASTM D2464; ASTM D2466; ASTM D2467; CSA
										B137.2; CSA B137.3
Stainless steel (Type 304/304L)
ASTM A312; ASTM A778; ASTM F1476; ASTM F1548;
										ASTM F3226
Stainless steel (Type 316/316L)
ASTM A312; ASTM A778; ASTM F1476; ASTM F1548;
										ASTM F3226
Steel
ASME B16.9, ASME B16.11; ASME B16.28; ASTM
										F1476; ASTM F1548
(REFERENCE
						  R 408.30732, SECTION
						  605.2.1)
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30729b - Manufactured pipe nipples

Current through Vol. 24-12, July 15, 2024
Rule 729b. Table 605.8 is added to the code to read as
						  follows:
Table 605.8
MANUFACTURED PIPE NIPPLES
MATERIAL
STANDARD
Copper, copper alloy, and
										chromium-plated
ASTM B687
Galvanized steel pipe
ASTM A53
Steel
ASTM A773
(REFERENCE
						  R 408.30732, SECTION
						  605.2.1)
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30728 - Sewer depth

Current through Vol. 24-12, July 15, 2024
Rule 728. Section 305.4.1 of the code is amended to
						  read as follows:
305.4.1. Sewer depth.
						A building sewer that connects to a private disposal system shall be a minimum
						of 8 inches (203 mm) to the top of the pipe below finished grade at the point
						of septic tank connection. Building sewers shall be installed a minimum of 42
						inches (1067 mm) below grade.
Exception: When permitted by the code
						  official.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30730 - Sewer required

Current through Vol. 24-12, July 15, 2024
Rule 730.
Section 701.2 of the code is amended and section 701.9
						  is added to read as follows:
701.2.
						Sewer required. Every building in which plumbing fixtures are installed and all
						premises having drainage piping shall be connected to a public sewer, where
						available, or an approved private sewage disposal system.
701.9. Connections. Direct connection of a
						steam exhaust, blowoff, or drip pipe shall not be made with the building
						drainage system. Waste water where discharged into the building drainage system
						shall be at a temperature not greater than 140°F (60°C). Where higher
						temperatures exist, approved cooling methods shall be provided.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30731 - Laundries

Current through Vol. 24-12, July 15, 2024
Rule 731.
Sections 1002.6 and 1003.6 of the code are amended to
						  read as follows:
1002.6. Building
						traps. Building (house) traps shall be prohibited, except where local
						conditions necessitate these traps. Building traps shall be provided with a
						cleanout and a relief vent or fresh air intake on the inlet side of the trap.
						The size of the relief vent or fresh air intake shall not be less than
						&frac12 the diameter of the drain to which the relief vent or air intake
						connects. The relief vent or fresh air intake shall be carried above grade and
						shall be terminated in a screened outlet located outside the
						building.
1003.6. Laundries.
						Commercial laundries shall be equipped with an interceptor with a wire basket
						or similar device, removable for cleaning, that prevents passage into the
						drainage system of solids 0.5 inch (12.7 mm) or larger in size, string, rags,
						buttons, or other materials detrimental to the public sewage system.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30732 - Lead content of drinking water pipe and fittings

Current through Vol. 24-12, July 15, 2024
Rule 732. Section
						  605.2.1 is added to the code to
						  read as follows:
605.2.1. Lead content
						of drinking water pipe and fittings. Pipe, pipe fittings, joints, valves,
						faucets, and fixture fittings utilized to supply water for drinking or cooking
						purposes shall comply with NSF 372 and shall have a weighted average lead
						content of 0.25% or less.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30735 - Hot water supply required

Current through Vol. 24-12, July 15, 2024
Rule 735.
Section 607.1 of the code is amended to read as
						  follows:
607.1. Where required.
(1) In residential occupancies, hot water
						shall be supplied to all plumbing fixtures and equipment utilized for bathing,
						washing, culinary purposes, cleansing, laundry, or building maintenance. In
						nonresidential occupancies, hot water shall be supplied for culinary purposes,
						cleansing, laundry, or building maintenance purposes. In nonresidential
						occupancies, hot water or tempered water shall be supplied for bathing and
						washing purposes. Tempered water shall be supplied through a water temperature
						limiting device that conforms to ASSE 1070, and shall limit the tempered water
						to a maximum of 110 degrees Fahrenheit (43 degrees Celsius). This provision
						does not supersede the requirement for protective shower valves in accordance
						with section 424.3 of the code.
(2)
						Tempered water shall be supplied to bathing and hand washing facilities in the
						occupancies identified in the following by individual water temperature
						limiting devices to individual fixtures:
(a)
						Elementary schools.
(b) Child care
						centers.
(c) Day care
						centers.
(d) Nurseries.
(e) Adult group homes.
(f) Adult congregate homes.
(g) Childrens camps.
(h) At accessible plumbing
						fixtures.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30736 - Water supply

Current through Vol. 24-12, July 15, 2024
Rule 736. Section
						  411.3 is added to the code to
						  read as follows:
411.3. Water supply.
						Where hot and cold water is supplied to an emergency shower or eyewash station,
						the temperature of the water supply shall only be controlled by a
						temperature-actuated mixing value complying with ASSE 1071. Where water is
						supplied directly to an emergency shower or eyewash station from a water
						heater, the water heater shall comply with ASSE 1085.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30741c - Connections to automatic fire sprinkler systems and standpipe systems

Current through Vol. 24-12, July 15, 2024
Rule 741c.
Section 608.17.4 of the code is amended to read as
						  follows:
608.17.4. Connections to automatic fire sprinkler
						  systems and standpipe systems. The potable water supply to automatic fire
						  sprinkler and standpipe systems shall be protected against backflow by a double
						  check backflow prevention assembly, a double check fire protection backflow
						  prevention assembly, or a reduced pressure principle fire protection backflow
						  prevention assembly.
Exception: Isolation of the water distribution system
						  is not required for deluge, preaction, or dry pipe systems.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30749 - Special equipment; water supply protection

Current through Vol. 24-12, July 15, 2024
Rule 749. Section 608.3.1 of the code is amended to
						  read as follows:
608.3.1. Special
						equipment; water supply protection. The water supply for hospital fixtures
						shall be protected against backflow with a reduced pressure principle backflow
						prevention assembly, an atmospheric or spill-resistant vacuum breaker assembly,
						or an air gap. Vacuum breakers for bedpan washer hoses, autopsy tables, and
						hose connections in health care or laboratory areas shall not be located less
						than 6 feet (1829 mm) above the floor.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30753a - Roof extensions

Current through Vol. 24-12, July 15, 2024
Rule 753a. Section 903.1 of the code is amended to read
						  as follows:
903.1. Roof extension. All
						open vent pipes that extend through a roof shall be terminated at least 1 foot
						(305 mm) above the roof, except that if a roof is to be used for any purpose
						other than weather protection, then the vent extensions shall be run not less
						than 7 feet (2134 mm) above the roof.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30753b - Roof extension unprotected

Current through Vol. 24-12, July 15, 2024
Rule 753b. Section
						  903.1.1 is added to the code to
						  read as follows:
903.1.1. Roof
						extension unprotected. Open vent pipes that extend through a roof shall be
						terminated not less than 12 inches, 304.8 mm, above the
						roof.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30754a - Frost Closure

Current through Vol. 24-12, July 15, 2024
Rule 754a. Section 903.2 of the code is amended to read
						  as follows:
Section 903.2. Frost Closure. To prevent frost closure,
						  every vent extension through a roof shall be a minimum of 3 inches (76 mm) in
						  diameter. Any increase in the size of the vent shall be made inside the
						  building a minimum of 1 foot (305 mm) below the roof or inside the wall.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30754b - Extensions outside a structure

Current through Vol. 24-12, July 15, 2024
Rule 754b. Section 903.7 of the code is amended to read
						  as follows: 903.7. Extensions outside a structure. Vent pipes installed on the
						  exterior of the structure shall be protected against freezing by insulation or
						  heat, or both.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30755 - Storm drainage

Current through Vol. 24-12, July 15, 2024
Rule 755. Table 1102.4 of the code is amended to read
						  as follows:
TABLE 1102.4
BUILDING STORM SEWER PIPE
MATERIAL
STANDARD
Acrylonitrile butadiene styrene (ABS) plastic
										pipe in IPS diameters, including Schedule 40, DR 22 (PS 200) and DR 24 (PS
										140); with a solid, cellular core or composite wall.
ASTM D2661; ASTM F628; ASTM F1488; CSA
										B181.1; CSA B182.1
Cast-iron pipe
ASTM A74; ASTM A888; CISPI 301
Concrete pipe
ASTM C14; ASTM C76; CSA A257.1M; CSA
										A257.2M
Copper or copper-alloy tubing (Type K, L, M
										or DWV)
ASTM B75; ASTM B88; ASTM B251; ASTM
										B306
Polyethylene (PE) plastic pipe
ASTM F667; ASTM F2306/F2306; ASTM
										F2648/F2648M
Polypropylene (PP) plastic pipe
ASTM F2736; ASTM F2764; CSA B182.13
Polyvinyl chloride (PVC) plastic pipe (Type
										DWV, SDR26, SDR35, SDR41, PS50 or PS100) in IPS diameters, including Schedule
										40, DR 22 (PS 200) and DR 24 (PS 140); with a solid, cellular core or composite
										wall
ASTM D2665; ASTM D3034; ASTM F891; ASTM
										F1488; CSA B181.2; CSA B182.2; CSA B182.4
Vitrified clay pipe
ASTM C4; ASTM C700
Stainless steel drainage systems, Type
ASME A112.3.1
316L
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30755a - Rainfall rate conversion method

Current through Vol. 24-12, July 15, 2024
Rule 755a. Section
						  1106.2.1 is added to the code to
						  read as follows:
1106.2.1. Rainfall
						rate conversion method. The rainfall rate falling on a roof surface shall be
						converted to a gallon per minute (L/m) flow rate in accordance with equation
						11-1.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30757 - Horizontal drains within building and building sewers

Current through Vol. 24-12, July 15, 2024
Rule 757.
Sections 708.3, 708.3.4, and 708.3.5 of the code are
						  being added to read as follows:
708.3 Where required. Cleanouts shall be located in
						  accordance with sections 708.3.1, 708.3.3 to 708.3.5.
708.3.1. Horizontal drains within building and building
						  sewers. All horizontal drains within buildings and building sewers shall be
						  provided with cleanouts located not more than 100 feet (30 480 mm)
						  apart.
For underground piping that is more than 10 inches in
						  diameter, manholes shall be provided and located at every major change of
						  direction, grade, elevation, or size of pipe or at intervals of not more than
						  400 feet (12 1920 mm). Metal covers shall be provided for the manholes and
						  shall be of sufficient weight to meet local traffic and loading
						  conditions.
Within buildings, manhole covers shall be gastight and
						  the manhole shall be vented with not less than a 4- inch (102 mm) pipe.
708.3.3. Changes of direction. Cleanouts shall be
						  installed at each change of direction greater than 45 degrees (0.79 rad) in the
						  building sewer, building drain and horizontal waste or soil lines. Where more
						  than one change of direction occurs in a run of piping, only one cleanout shall
						  be required for each 40 feet (12 192 mm) of developed length of the drainage
						  piping.
708.3.4. Base of stack. A cleanout shall be provided
						  at the base of each waste or soil stack.
708.3.5. Building drain and building sewer junction.
						  There shall be a cleanout near the junction of the building drain and the
						  building sewer. The cleanout shall be either inside or outside the building
						  wall and shall be brought up to the finished ground level or to the basement
						  floor level. An approved two-way cleanout is allowed to be used at this
						  location to serve as a required cleanout for both the building drain and
						  building sewer. The cleanout at the junction of the building drain and building
						  sewer shall not be required if the cleanout on a 3 - inch (76mm) or larger
						  diameter soil stack is located within a developed length of 10 feet (3048 mm)
						  of the building drain and building sewer connection. The minimum size of the
						  cleanout at the junction of the building drain and building sewer shall comply
						  with Section 708.7.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30757a - Discharge pipe and fittings

Current through Vol. 24-12, July 15, 2024
Rule 757a. Section 712.3.3 of the code is added to read
						  as follows:
712.3.3. Discharge pipe
						and fittings. Discharge piping and fittings shall be constructed of approved
						materials.