reglab/statecodes huggingface dataset:
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 80 - PHYSICAL PLANT CONSTRUCTION › Rule 15-16-1-51.80.2 - Codes

Current through June 25, 2024
The term "safe" as used in Subchapter 80 hereof shall be
						interpreted in the light of compliance with the requirements of the latest
						codes presently in effect, which are incorporated by reference as a part of
						these Minimum Standards; National Fire which includes the Life Safety Code,
						National Fire Protection Association or Standard Building Code, Southern
						Building Code Congress and Standard Plumbing Code, Southern Building Code
						Congress or American Standard National Plumbing Code, American Standards
						Association No. 17.3; and Sanitary Code of the Mississippi Department of
						Health.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 80 - PHYSICAL PLANT CONSTRUCTION › Rule 15-16-1-51.80.3

Current through June 25, 2024
New buildings must conform to the codes listed in the
						paragraph above. Where a choice of codes is provided above, an applicant may
						choose which of the codes he will follow, and the provisions of the code chosen
						shall apply throughout except to the extent that these Minimum Standards
						specifically permit deviation therefrom.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.1 - Construction

Current through June 25, 2024
Construction
shall not be started for any
						institution subject to these standards (whether new or remodeling or additions
						to an existing facility) until the plans and specifications for such
						construction or remodeling have been submitted to the Licensing Agency in
						writing and its approval of the changes given in writing.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.2 - Exception

Current through June 25, 2024
Foundation changes made necessary by unanticipated
						conditions, or any conditions which present a hazard to life or property if not
						immediately corrected.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.3

Current through June 25, 2024
Plans and specifications for any substantial
						construction or remodeling should be prepared by competent architects and
						engineers licensed to practice in the state and who assume responsibility for
						supervising the construction. The following plans shall be submitted to the
						Licensing Agency for review:
1.
					 Preliminary Plans - To include schematics of building, plot plans showing size
					 and shape of entire site, existing structures, if any, streets and location and
					 characteristics of all needed utilities, floor plans of every floor diminished
					 and with proposed use of each room or area shown. If for additions or
					 remodeling, plan of existing building showing all proposed alterations, outline
					 specifications to include a general description of the construction, type of
					 finishes, and type of heating, ventilating, plumbing and electrical systems
					 proposed.
2. Final Working Drawings
					 and Specifications - Complete and in sufficient detail to be the basis for the
					 award of construction contracts.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.4

Current through June 25, 2024
All plans submitted for review must be accompanied in
						their first submission by an order of the governing board indicating the type
						and scope of license to be applied for.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.5

Current through June 25, 2024
Plans receiving approval by the Licensing Agency upon
						which construction has not begun within six (6) months following such approval
						must be resubmitted for approval.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.6

Current through June 25, 2024
In all new facilities, plans must be submitted to all
						regulatory agencies, such as the County Health Department, etc., for approval
						prior to starting construction.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.7

Current through June 25, 2024
Upon completion of construction an inspection shall be
						made by the Licensing Agency and approval given prior to occupying the building
						or any part thereof.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.8 - Environment

Current through June 25, 2024
All facilities shall be so located that they are
						reasonably free from undue noises, smoke, dust or foul odors, and should not be
						located adjacent to railroads, freight yards, schools, children's playgrounds,
						airports, industrial plants or disposal plants.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.9 - Zoning Restrictions

Current through June 25, 2024
The locations of an institution shall comply with all
						local zoning ordinances.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.10 - Access

Current through June 25, 2024
Institutions located in rural areas must be served by
						good roads which can be kept passable at all times.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.11 - Elements of Construction

Current through June 25, 2024
Corridors-shall be 6'0" wide and 7'6" high (clear). The
						surface of all floors and walls shall be washable. All corridors longer than
						150' shall be subdivided by a smoke barrier and must be maintained free of
						obstruction.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.12 - Doors

Current through June 25, 2024
All doors in corridors shall be 20-minutes fire rated
						floors (1-3/4" solid core wood door as a minimum). All doors to patient
						bedrooms, diagnostic and treatment areas, and other doors used by residents
						shall be at least 36" wide. No door shall swing into the corridor except closet
						doors. to hazardous areas defined in the Life Safety Code shall be 1-1/2 hours
						"B" labeled fire doors. Exit doors shall conform to the requirements set forth
						in the Life Safety Code.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.13 - Stairs

Current through June 25, 2024
Shall be 44" wide, minimum; be in a 2-hour fire
						enclosure; and have a "B" (1-1/2 hour) level door at all
						landings.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.14 - Elevators

Current through June 25, 2024
One power driven elevator is required in all facilities
						having patient rooms above the first floor. Two or more elevators are required
						if 60 or more patients are housed above the ground floor.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.15 - One-Story Building

Current through June 25, 2024
Wall, ceiling and roof construction shall be of a type
						approved as being of 1-hour fire resistive construction as defined by National
						Bureau of Fire Underwriters or the Bureau of Standards. Floor systems shall be
						of non-combustible construction.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.16 - Multi-Story Building

Current through June 25, 2024
Must be of two-hour fire resistive constructions as
						defined in Standard Building Code or comply with the Life Safety Code of
						National Fire Protection Association as applied to hospitals.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.17 - Fire Reporting and Protection

Current through June 25, 2024
A manually operated electrically supervised fire alarm
						system shall be installed in each facility. There must be a telephone in the
						building to summon help in case of fire.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.18 - Sprinkler systems

Current through June 25, 2024
Sprinkler systems
tied into the fire alarm
						system shall be provided at least for hazardous areas. Adequate water supply
						shall be provided for the sprinkler system. Hazardous areas are: Laundries,
						Storage Areas, Repair and Maintenance Shops, Soiled Linen Collection Rooms,
						Trash Collection Rooms, Laundry Chutes, and Trash Chutes.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.19 - Flame Spread Rate (ASTM Standard E84-61)

Current through June 25, 2024
Flame Spread Rate (ASTM Standard E84-61)
on
						all wall and ceiling surfaces in required exists and hazardous areas shall be
						25 or less. All other areas shall have a flame spread rating of not more than
						75, except that up to 10% of the aggregate wall and ceiling area may have a
						finish with a rating up to 200.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.20 - Heating and Ventilating

Current through June 25, 2024
Suitable artificial heat shall be furnished to maintain
						75 degrees F, inside temperature with 10 degrees F, outside temperature.
						Circulating hot water from a remote boiler or vapor-steam with circulating
						pumps and controls on emergency electrical service to provide heating in case
						of power failures are the preferred methods of heating. Electrical heating will
						be approved provided a standby electric generator is provided of capacity to
						furnish 80% of the maximum heating load in addition to other power and lighting
						loads that may be connected to it, or the facility is supplied by two electric
						service lines connected to separate transformers at the sub-station so arranged
						that electric services can be maintained in case of failure of one line or
						transformer. Direct fired units are forbidden except in areas such as
						laundries, storerooms, kitchens, and similar occupancies and then only if in
						ductwork or more than 8 feet above the floor. Open flame heaters are
						prohibited. Gas fired ranges and other appliances (except Bunsen burners) may
						be used where no hazard is created, but must be services with rigid pipe
						connections. Gas fired sterilizer, water heater, and other like appliances
						shall have provided adequate air intake for combustion and full venting for
						combustion products. No hall will be used as a plenum. Mechanical ventilation
						shall be installed in all toilets and janitors closets.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.21 - Toilets, janitors' closets, soiled linen, dishwashing and similar areas

Current through June 25, 2024
Toilets, janitors' closets, soiled linen,
						dishwashing and similar areas
shall have six (6) air changes per hour.
						Areas occupied by patients shall have two (2) air changes per
						hour.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.22 - Plumbing

Current through June 25, 2024
All institutions subject to these standards shall be
						connected to an approved municipal water system or to a private supply whose
						purity has been certified by the laboratory of the Mississippi Department of
						Health. Private supplies must be sampled, tested, and its purity certified at
						least twice annually and immediately following any repair or modification to
						the underground lines, the elevated tank, or to the well or pump. Supply must
						be adequate, both as to volume and pressure, for fire fighting purposes.
						Deficiencies in either must be remedied by the provision of auxiliary pumps,
						pressure tanks or elevated tanks as may be required.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.23

Current through June 25, 2024
An approved circulating method of supplying hot water
						for all uses must be provided. Water to lavatories and bathing areas must be
						100 degrees-110 degrees F. Water to mechanical dishwashers must be delivered at
						180 degrees F. for rinsing.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.24

Current through June 25, 2024
Supply piping within the building shall be in accordance
						with plumbing code incorporated by reference in Rule 51.81.22 hereof. Special
						care must be taken to avoid use of any device or installation which might cause
						contamination of the supply through back-siphonage or cross
						connections.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.25 - Sewage Disposal

Current through June 25, 2024
All institutions subject to these standards shall
						dispose of all sanitary wastes through connection to a suitable municipal
						sewerage system or through a private sewerage system that has been approved in
						writing by the Sanitary Engineering Department of the Mississippi Department of
						Health and the Air and Water Pollution Board.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 81 - SUBMISSION OF PLANS AND SPECIFICATIONS › Rule 15-16-1-51.81.26

Current through June 25, 2024
All fixtures located in the kitchen, including the
						dishwasher, shall be installed so as to empty into a drain which is not
						directly connected to the sanitary house drain. Kitchen drain may empty into a
						manhole or catch basin having a perforated cover with an elevation of at least
						24" below the kitchen floor elevation, and thence to the sewer. Exceptions:
						existing licensed institutions which have no plumbing fixtures installed on
						floors which are above the floor on which the kitchen is
						located.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.1 - General

Current through June 25, 2024
To provide electricity during an interruption of the
						normal electric supply that could affect the medical care, treatment, or safety
						of the occupants, an emergency source of electricity shall be provided and
						connected to certain circuits for lighting and power. The source of this
						emergency electric service shall be an emergency generator, with a stand-by
						supply of fuel of 24 hours. Emergency electrical systems shall be provided in
						accordance with the applicable section of the Life Safety
						Code.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.2 - Patient Rooms

Current through June 25, 2024
Each patient room shall meet the following
						requirements:
1. Shall contain 100 sq.
					 ft. of floor area for a single bedroom and 80 sq. ft. per bed in
					 multi-bedrooms;
2. Ceiling Height.
					 Shall be 8'0" minimum;
3. All rooms
					 housing patients shall be outside rooms and shall have window area equal to 1/8
					 of the floor area. The sill shall not be higher than 36 inches above the floor
					 and shall be above grade. Windows shall not have any obstruction to vision
					 (wall, cooling tower, etc.) within 50 feet as measured perpendicular to the
					 plane of the window;
4. Each
					 patient shall be provided with a hanging storage space of not less than 16" X
					 24" X 52" for his personal belongings;
5. Each patient room shall be equipped with a
					 quality bed acceptable for his environment;
6. A bedside cabinet or table shall be
					 provided;
7. Rooms shall be
					 equipped with curtains or blinds at windows. All curtains shall have a flame
					 spread of 25 or less;
8. All walls
					 shall be suitable for washing;
9.
					 All walls and ceilings shall have a 1-hour fire rating;
10. A lavatory shall be located in the
					 bedroom or in a private toilet room; and
11. Patient bed light shall be provided which
					 shall be capable of control by the patient.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.3 - Service Areas

Current through June 25, 2024
The size of each service area will depend on the number
						beds within the unit and shall include the following:
1. Nurses Station. For charting,
					 communication and storage for supplies and nurses personal effects;
2. Nurses Toilet with Lavatory. Convenient to
					 nurses' station;
3. Clean Work
					 Room. For storage and assembly of supplies. Shall contain storage cabinets or
					 storage carts, work counter and sink;
4. Soiled Utility. Shall contain deep sink
					 work counter, waste receptacle, soiled linen receptacle;
5. Medicine Station. Adjacent to nurses'
					 station, with sink, small refrigerator, locked storage and work counter. (May
					 be in clean work room in self-contained cabinet.);
6. Clean Linen Storage. A closet large enough
					 to hold an adequate supply of clean linen;
7. Provision for between-meal
					 nourishments;
8. Patient Bath. At
					 least one tub or shower stall for each 18 patients not served by private
					 bath;
9. Fire Extinguisher. One
					 approved Class 2A unit for each 3000 sq/ ft.; and
10. Janitor's Closet. Closet large enough to
					 contain floor receptor with plumbing and space for some supplies and mop
					 buckets.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.4 - Special Care Room for Isolation

Current through June 25, 2024
It shall contain:
1. One patient bed per room; and
2. Private lavatory and toilet.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.5 - Seclusion Room

Current through June 25, 2024
If a seclusion room is provided, it shall be provided
						with a key-only lock or an electronic lock on the door tied into the fire alarm
						system, and a security screen on the window.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.6 - Dietary

Current through June 25, 2024
Construction and equipment shall comply with Mississippi
						Department of Health regulations, and shall include:
1. Food preparation center. Provide lavatory
					 (without mirror) with wrist action blades, soap dispenser and disposable towel
					 dispenser. All cooking appliances to have ventilating hood;
2. Food serving facilities. If dining space
					 is provided, it shall contain a minimum of 15 sq. ft. per person
					 seated;
3. Dishwashing room.
					 Provide commercial type dishwashing equipment;
4. Pot washing facilities;
5. Refrigerated storage (three day
					 supply);
6. Day storage (three day
					 supply);
7. Cart cleaning
					 facilities (can be in dishwashing room);
8. Can wash and storage (must be
					 fly-tight);
9. Cart
					 storage;
10. Dietitian's
					 office;
11. Janitors
					 closet;
12. Personnel toilets and
					 lockers convenient to, but not in, the kitchen proper; and
13. Approved automatic fire extinguisher
					 system in range hood. In addition, Class 1B extinguisher to be installed in the
					 kitchen.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.7 - Administrative Area

Current through June 25, 2024
To include:
1.
					 Business office with information desk, and personnel toilets;
2. Administrator's office;
3. Admitting area;
4. Lobby or foyer, with public
					 toilets;
5. Medical Library (This
					 area should be as close to medical records as possible);
6. Space for conferences and in-service
					 training;
7. Medical
					 records--office and storage;
8.
					 Director of Nurses' office; and
9.
					 Fire Extinguisher. An approved Class 2A unit shall be provided.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.8 - Housekeeping Area

Current through June 25, 2024
To include:
1.
					 Housekeeper's office or suitable area designated for record keeping;
					 and
2. Storage space for the maid's
					 carts, if used.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.9 - Laundry

Current through June 25, 2024
To include:
1.
					 Soiled linen room with lavatory with wrist action blades;
2. Clean linen and mending area. (To include
					 space for storage of clean linen carts);
3. Laundry process room. Commercial type
					 equipment sufficient for the needs of the facility. (If laundry is processed
					 outside facility, this area not needed);
4. Janitors closet; and
5. Facilities shall be provided for personal
					 laundry for use by patients. This area shall be separated from areas by a one
					 hour fire rated wall.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.10 - General Storage

Current through June 25, 2024
There shall be a two hour fire rated lockable room large
						enough to provide five square feet of general storage for each bed provided. If
						storage is provided in a separate building it must be fifty feet
						away.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.11 - Boiler Room

Current through June 25, 2024
Space shall be adequate for the installation and
						maintenance of the required machinery.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.12 - Maintenance Area

Current through June 25, 2024
Sufficient area for performing routine maintenance
						activities shall be provided and shall include an office or suitable area
						designated for recordkeeping.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.13 - Day Room

Current through June 25, 2024
At least two general areas for use as living room, day
						room or recreation shall be provided. A minimum of 18 square feet per patient
						bed shall be available for this purpose.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.14 - Dining Room

Current through June 25, 2024
A minimum of 15 square feet per patient bed shall be
						provided for use as a . Adequate tables and chairs shall be provided to seat
						all patients, staff and guests.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.15 - Counseling Rooms

Current through June 25, 2024
At least one small room shall be provided for each 20
						patients for the purpose of individual private treatment or
						counseling.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.16 - Examination and Treatment Room

Current through June 25, 2024
At least one room shall be provided for the purpose of
						examination and treatment. The room shall be equipped with a lavatory and towel
						dispenser, examination table and storage space, with adequate
						lighting.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 82 - EMERGENCY ELECTRIC SERVICE › Rule 15-16-1-51.82.17 - Group Counseling Rooms

Current through June 25, 2024
At least two rooms shall be provided large enough to
						accommodate 8-10 patients for the purpose of group counseling
						sessions.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.1 - Administrative

Current through June 25, 2024
Relates to the fiscal and general management of a
						facility rather than to the direct provision of services to
						patients.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.2 - Aftercare

Current through June 25, 2024
Services that are provided to a patient after discharge
						and that support and increase the gains made during
						treatment.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.3 - Applicant

Current through June 25, 2024
An individual who has applied for admission to a program
						but who has not completed the intake process.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.4 - Approved

Current through June 25, 2024
Acceptable to the authority having
						jurisdiction.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.5 - Assessment

Current through June 25, 2024
Those procedures by which a program evaluates an
						individual's strengths, weakness, problems and needs.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.6 - Audiological Assessment

Current through June 25, 2024
The audiological tests for delineating the site of
						auditory dysfunction, including such tests as pure tone air-conduction and
						bone-conduction threshold, speech reception thresholds, speech discrimination
						measurements, impedance measurements, and others.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.7 - Audiologists, Qualified

Current through June 25, 2024
An individual who is certified by the American
						Speech-Language-Hearing Association as clinically competent in the area of
						audiology and is licensed by the State.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.8 - Audiometric Screening

Current through June 25, 2024
A process that may include such tests as pure tone aid
						conduction thresholds, pure tone air-conduction thresholds, pure tone
						air-conduction suprathreshold screenings, impedance measurements, or
						observations of reactions to auditory stimuli.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.9 - Audit, Financial

Current through June 25, 2024
An independent review by a public accountant certifying
						that a facility's financial reports reflect its financial
						status.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.10 - Authentication

Current through June 25, 2024
Proof of authority and responsibility by written
						signature, identifiable initials, computer key, or other method. The use of a
						rubber stamp signature is acceptable only under the following conditions: the
						person whose signature the rubber stamp represents is the only one who has
						possession of the stamp and is the only one who uses it, and this person gives
						the chief executive officer a signed statement that he or she is the only one
						who has the stamp and is the only one who will use it.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.11 - Authority Having Jurisdiction

Current through June 25, 2024
The organization, office, or individual responsible for
						approving a piece of equipment, an installation, or a
						procedure.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.12 - Bylaws

Current through June 25, 2024
The laws, rules, or regulations adopted for the
						government of the facility. Also used for the laws, rules, or regulations of
						the professional staff.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.13 - Chief Executive Officer

Current through June 25, 2024
A job-descriptive term used to identify the individual
						appointed by the governing body to act on its behalf in the overall management
						of the facility. Other job titles may include administrator, superintendent,
						director, president, vice-president, and executive
						vice-president.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.14 - Child Psychiatrist, Qualified

Current through June 25, 2024
A doctor of medicine who specializes in the assessment
						and treatment of children and/or adolescents having psychiatric disorders and
						who is fully licensed to practice medicine in the state in which he or she
						practices. The individual shall have successfully completed training in a child
						psychiatry fellowship program approved by the Liaison Committee on Graduate
						Medical Education of the American Medical Association or have been certified in
						child psychiatry by the American Board of Psychiatry and
						Neurology.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.15 - Child Psychologist, Qualified

Current through June 25, 2024
An individual licensed by the State Board of
						Psychological Examiners with a specialty area in either developmental
						psychology or in clinical or counseling psychology with demonstrated
						educational background and experience in the evaluation and treatment of
						children and/or adolescents.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.16 - Department

Current through June 25, 2024
A staff entity organized on administrative, functional,
						or disciplinary lines.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.17 - Dietetic Services

Current through June 25, 2024
The provision of services to meet the nutritional needs
						of patients, with specific emphasis on patients who have special dietary needs,
						for example, patients who are allergic to certain foods or who cannot accept a
						regular diet.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.18 - Diet Manual

Current through June 25, 2024
An up-to-date, organized system for standardizing the
						ordering of diets.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.19 - Discharge

Current through June 25, 2024
The point at which the patient's active involvement with
						a facility is terminated and the facility no longer maintains active
						responsibility for the patient.
Miss. Code Ann.
						§
												43-11-13
Mississippi Administrative Code › Title 15 - Mississippi Department of Health › Part 16 - Health Facilities › Subpart 1 - Health Facilities Licensure and Certification › Chapter 51 - MINIMUM STANDARDS OF OPERATION FOR PSYCHIATRIC RESIDENTIAL TREATMENT FACILITIES › Subchapter 83 - GLOSSARY › Rule 15-16-1-51.83.20 - Drug History

Current through June 25, 2024
A delineation of the drugs used by a patient, including
						prescribed and unprescribed drugs and alcohol. A drug history includes, but is
						not necessarily limited to, the following: drugs used in the past; drugs used
						recently, especially within the preceding 48 hours; drugs of preference;
						frequency with which each drug is used; route of administration of each drug;
						drugs used in combination; dosages used; year of first use of each drug;
						previous occurrences of overdose, withdrawal, or adverse drug reactions; and
						history or previous treatment received for alcohol or drug
						abuse.
Miss. Code Ann.
						§
												43-11-13