reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-96 - Insulated neutral

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 96.
(a) The
				grounded circuit conductor (neutral) shall be insulated from the grounding
				conductors and from equipment enclosures and other grounded parts. The grounded
				(neutral) circuit terminals in the distribution panelboard and in ranges,
				clothes dryers, counter-mounted cooking units, and wall-mounted ovens shall be
				insulated from the equipment enclosure. Bonding screws, straps, or buses in the
				distribution panelboard or in appliances shall be removed and
				discarded.
(b) Connection of ranges
				and clothes dryers with one hundred fifteen/two hundred thirty (115/230) volt,
				three (3) wire ratings shall be made with four (4) conductor cord and three (3)
				pole, four (4) wire grounding type plugs, or by Type AC metal-clad cable or
				conductors enclosed in flexible metal conduit. For one hundred fifteen (115)
				volt rated devices, a three (3) conductor cord and a two (2) pole, three (3)
				wire grounding type plug shall be permitted.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-97 - Equipment grounding

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 97.
(a) The
				green-colored insulated grounding wire in the supply cord or permanent feeder
				wiring shall be connected to the grounding bus in the distribution panelboard
				or disconnecting means.
(b) In the
				electrical system, all exposed metal parts, enclosures, frames, lamp fixture
				canopies, etc., shall be effectively bonded to the grounding terminal or
				enclosure of the distribution panelboard.
(c) Cord-connected appliances, such as
				washing machines, clothes dryers, refrigerators, and the electrical system of
				gas ranges, etc., shall be grounded by means of an approved cord with grounding
				conductor and grounding-type attachment plug.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-98 - Bonding of noncurrent-carrying metal parts

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 98.
(a) All
				exposed noncurrent-carrying metal parts that may become energized shall be
				effectively bonded to the grounding terminal or enclosure of the distribution
				panelboard. A bonding conductor shall be connected between each distribution
				and an accessible terminal on the chassis.
(b) Grounding terminals shall be of the
				solderless type and approved as pressure terminal connectors recognized for the
				wire size used. The bonding conductor shall be solid or stranded, insulated or
				bare, and shall be No. 8 copper minimum, or equal. The bonding conductor shall
				be routed so as not to be exposed to physical damage.
NOTE: Protection can be afforded by the configuration of the
				  chassis.
(c) Metallic gas,
				water and waste pipes and metallic air-circulating ducts shall be considered
				bonded if they are connected to the terminal on the chassis ((a) of this
				section) by clamps, solderless connectors, or by suitable ground-type
				straps.
(d) Any metallic roof and
				exterior covering shall be considered bonded if (1) the metal panels overlap
				one another and are securely attached to the wood or metal frame parts by
				metallic fasteners, and (2) if the lower panel of the metallic exterior
				covering is secured by metallic fasteners at a cross member of the chassis by
				two (2) metal straps per mobile structure of section at opposite ends. The
				bonding strap material shall be a minimum of four inches (4") in width of
				material equivalent to the skin or a material of equal or better electrical
				conductivity. The straps shall be fastened with paint-penetrating fittings such
				as screws, and starwashers or equivalent.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-99 - Electrical tests

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 99.
(a)
				Dielectric Strength Test. The wiring of each mobile structure shall be
				subjected to a one (1) minute, nine hundred (900) volt dielectric strength test
				(with all switches closed) between live parts (including neutral and the mobile
				structure ground). Alternatively, the test may be performed at one thousand
				eighty (1080) volts for one (1) second. This test shall be performed after
				branch circuits are complete and after fixtures or appliances are installed.
EXCEPTION: Fixtures or appliances which are listed shall not
				  be required to withstand the dielectric strength test.
(b) Continuity and Operational Tests and
				Polarity Checks. Each mobile structure shall be subjected to:
(1) an electrical continuity test to assure
				that all exposed electrically conductive parts are properly bonded;
(2) an electrical operational test to
				demonstrate that all equipment, except water heaters and electric furnaces, is
				connected and in working order; and
(3) electrical polarity checks of permanently
				wired equipment and receptacle outlets to determine that connections have been
				properly made.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-101 - Interconnection of multiple section mobile residential structures

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 101.
(a)
				Fixed-type Wiring. Approved and listed fixed-type wiring methods shall be used
				to join portions of a circuit which must be electrically joined which are
				located in adjacent sections of mobile structures after the structure is
				installed on its support foundation. The circuits junction shall be accessible
				for disassembly when the structure is prepared for relocation.
(b) Disconnecting Means. Multiple section
				mobile structures not having permanently installed feeders, and which are to be
				moved from one (1) location to another shall be permitted to have disconnecting
				means with branch-circuit protective equipment in each unit when so located
				that after assembly or joining together of units, they shall not be
				interconnected on either the live side or the load side, except that the
				grounding means shall be electrically interconnected.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-102 - Outdoor fixtures, outlets, and appliances

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 102.
(a) Outdoor
				fixtures and equipment shall be approved for outdoor use. Outdoor receptacles
				or convenience outlets shall be of a gasketed-cover type, for use in wet
				locations.
(b) Outside Heating
				and/or Air-Conditioning Equipment. A mobile structure provided with a branch
				circuit designed to energize heating and/or air-conditioning equipment located
				outside and mobile structure, other than room air-conditioners, shall have
				branch-circuit conductors terminate in a listed outlet box, or disconnecting
				means, located on the otside
[sic.]
of the mobile structure. A
				label shall be permanently affixed adjacent to the outlet box and contain the
				following information:
"This connection is for heating and/or air-conditioning
				  equipment. The branch-circuit is rated at not more than _____ amperes, at _____
				  volts, 60-Hertz, _____ conductor ampacity. A disconnecting means shall be
				  located within sight of the equipment.
The correct voltage and ampere rating shall be given. The tag
				  shall be not less than 0.020 inch, etched brass, stainless steel, anodized or
				  alcald aluminum or equivalent. The tag shall not be less than three inches (3")
				  by one and three-fourths inches (1 3/4") minimum size.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-103 - Painting of wiring

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 103.
During painting or staining of the mobile structure, it
				  shall be permitted to paint metal raceway (except where grounding continuity
				  would be reduced) or the sheath of the nonmetallic cable. Some arrangement,
				  however, shall be made so that no point shall be applied to the individual
				  wires, as the color coding may be obliterated by the
				  painting.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 15 - INDUSTRIALIZED BUILDING SYSTEMS › Rule 2 - Indiana Mobile Structures Code › Section 2-104 - Polarization

Current through July 10, 2024
Authority: IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15
Sec. 104.
(a) The
				identified (white) conductor shall be employed for grounded circuit conductors
				only and shall be connected to the identified (white) terminal or lead on
				receptacle outlets and fixtures. It shall be the unswitched wire in switched
				circuits, except that a cable containing an identified conductor (white) shall
				be permitted for single-pole three (3) way or four (4) way switch loops where
				the connections are made so that the unidentified conductor is the return
				conductor from the switch to the outlet. Painting of the terminal end of the
				wire shall not be required.
(b) If
				the identified (white) conductor of a cable is used for other than grounded
				conductors or for other than switch loops as explained above (for a two hundred
				thirty (230) volt circuit, for example), the conductor shall be finished in a
				color other than white at each outlet where the conductors are visible and
				accessible.
(c) Green-colored wires
				or green with yellow stripes shall be used for grounding conductors
				only.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.3 - Indiana Plumbing Code, 1999 Edition (Repealed

Current through July 10, 2024
This version of rule effective 90 days after filing with the
				  Publisher. This version of rule was filed with the Publisher on September 25,
				  2012.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-1 - Adoption by reference

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 1.
(a) That
				certain document, being titled the International Plumbing Code, 2006 edition,
				second printing, published by the International Code Council, Inc., 500 New
				Jersey Avenue NW, Sixth Floor, Washington, D.C. 20001-2070, be and the same is
				hereby adopted by reference as if fully set out in this rule, save and except
				those amendments made in this rule.
(b) Wherever the term "this code" is used
				within this rule, it shall mean the 2012 Indiana Plumbing Code.
(c) This rule is available for review and
				reference at the:
Legal and Code Services Section
Indiana Department of Homeland Security
Indiana Government Center South
302 West Washington Street, Room W246
Indianapolis, Indiana 46204
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-2 - Chapter 1; administration

Current through July 10, 2024
Authority: IC 22-13
Affected: IC 4-21.5; IC 22-12-7; IC 22-13; IC 22-14; IC
				  22-15; IC 25-28.5; IC 36-7-2-9
Sec. 2.
Delete Chapter 1 and insert to read as follows:
(a) 101.1 Title. This rule shall be known as
				the 2012 Indiana Plumbing Code and shall be published, except incorporated
				documents, by the Department of Homeland Security for general distribution and
				use under that title.
(b) 101.2
				Scope.
(1) The provisions of this code shall
				apply to the construction, alteration, and addition to plumbing equipment and
				systems regulated by this code for Class 1 structures, except townhouses,
				within the Class 1 structure and up to five (5) feet (1,524 mm) outside of any
				portion of the Class 1 structure.
(2) Compliance with this code for Class 2
				structures or Class 1 townhouses is evidence of compliance with the Indiana
				Residential Code (675 IAC 14).
(3)
				This code does not regulate licensure requirements for plumbers. Such licensure
				requirements are set out in IC 25-28.5.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-3 - Chapter 2; definitions

Current through July 10, 2024
Authority: IC 22-13
Affected: IC 10-19-2; IC 22-12; IC 22-13; IC 22-14; IC 22-15;
				  IC 25-4; IC 25-31; IC 36-7-2-9
Sec. 3.
Chapter 2 is amended to read as follows:
(a) Amend Section 201.3 by deleting the text
				and inserting the following: Where terms are not defined in this code and are
				defined in the Indiana Building Code (675 IAC 13), the Indiana Electrical Code
				(675 IAC 17), the Indiana Mechanical Code (675 IAC 18), the Indiana Fire Code
				(675 IAC 22), or the Indiana Fuel Gas Code (675 IAC 25), such terms shall have
				the meanings ascribed to them in those codes.
(b) Amend Section 202 Definitions, as
				follows:
(1) Delete the definition of
				Approved and insert to read as follows:
APPROVED as to materials, equipment, design of products, and
				  types of construction, means acceptance by the code official by one (1) of the
				  following methods:
(i) investigation
				or tests conducted by nationally recognized authorities; or
(ii) investigation or tests conducted by
				technical or scientific organizations; or
(iii) nationally accepted principles.
The investigation, tests, or principles shall establish that
				  the materials, equipment, design of products, and construction are safe for
				  their intended purposes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-4 - Chapter 3; general regulations

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 4.
Chapter 3 is amended as follows:
(a) Amend Section 301.1.1 to read as follows:
				See Section 101.2.
(b) Amend
				Section 301.3 to add an exception to read as follows:
Exception: Bathtubs, showers, lavatories, clothes washers,
				  air conditioning condensation, laundry trays, and process water that is exposed
				  only to heat transfer and no other contamination shall not be required to
				  discharge to the sanitary drainage system where such fixtures discharge to a
				  gray water system in accordance with Appendix C.
(c) Amend Section 301.7 to read as follows:
				See Section 101.7.
(d) Amend
				Section 304.4 by deleting the text after "protected" and inserting "with an
				impervious material".
(e) Amend
				Section 305.3 by adding a third sentence to read as follows: No plumbing pipes
				shall be directly embedded in concrete or masonry.
(f) Amend Section 305.6 as follows:
(1) In the first sentence, delete
				"water".
(2) Delete the last
				sentence in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-5 - Chapter 4; fixtures, faucets, and fixture fittings

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 5.
Chapter 4 is amended as follows:
(a) Delete Section 403 in its entirety and
				insert: See Chapter 29 of the Indiana Building Code.
(b) Delete Section 404 in its entirety and
				insert: See Chapter 29 of the Indiana Building Code.
(c) Delete Section 405.2 and insert: See
				Chapter 29 of the Indiana Building Code.
(d) Delete Section 405.3 and insert: See
				Chapter 29 of the Indiana Building Code.
(e) Delete Section 405.3.1 and insert: See
				Chapter 29 of the Indiana Building Code.
(f) Delete Section 410.1 and insert: See
				Chapter 29 of the Indiana Building Code.
(g) Delete Section 410.2 and insert: See
				Chapter 29 of the Indiana Building Code.
(h) Amend Section 413.4 by adding a second
				sentence to read as follows: The cold water supply shall be protected against
				backflow by an air gap or a backflow preventer in accordance with Section
				608.
(i) Amend Section 416.5 to add
				an exception to read as follows:
Exception: An ASSE 1070 point of use device may be omitted if
				  the fixture is supplied with tempered water through an ASSE 1017 master mixing
				  valve.
(j) Amend Section
				419.1 to insert, after "ASME A112.19.2M", "ASME A112.19.19, Vitreous China
				Nonwater Urinals, 2006 edition,".
(k) Delete the last sentence in Section 419.2
				and insert: See Chapter 29 of the Indiana Building Code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-6 - Chapter 5; water heaters

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 6.
Chapter 5 is amended as follows:
(a) Add Section 502.1.1 Elevation of ignition
				source to read as follows: Elevation of ignition source. Equipment and
				appliances having an ignition source and located in hazardous locations and
				public garages, private garages, repair garages, automotive
				motor-fuel-dispensing facilities, and parking garages shall be elevated such
				that the source of ignition is not less than eighteen (18) inches (457 mm)
				above the floor surface on which the equipment or appliance rests. Such
				equipment and appliances shall not be installed in Group H occupancies or
				control areas where open use, handling, or dispensing of combustible,
				flammable, or explosive materials occur. For purposes of this section, rooms or
				spaces that are not part of the living space of a dwelling unit and that
				communicate directly with a private garage through openings shall be considered
				to be part of the private garage.
(b) Add Section 502.1.1.1, Parking garages to
				read as follows: Parking garages. Connection of a parking garage with any room
				in which there is a fuel-fired appliance shall be by means of a vestibule
				providing a two-door separation, except that a single door is permitted where
				the sources of ignition in the appliances are elevated in accordance with
				Section 304.3 of the Indiana Mechanical Code.
Exception: This section shall not apply to appliance
				  installations complying with Section 304.5 of the Indiana Mechanical
				  Code.
(c) Add Section
				502.2.1, Prohibited locations to read as follows: Prohibited locations.
				Fuel-fired appliances shall not be located in, or obtain combustion air from,
				any of the following rooms or spaces:
(1)
				Sleeping rooms.
(2)
				Bathrooms.
(3) Toilet
				rooms.
(4) Storage
				closets.
(5) Surgical rooms.
Exception: This section shall not apply to the following
				  appliances:
(i) Direct-vent appliances
				that obtain all combustion air directly from the outdoors.
(ii) Solid fuel-fired appliances provided
				that the room is not a confined space and the building is not of unusually
				tight construction.
(iii)
				Appliances installed in a dedicated enclosure in which all combustion air is
				taken directly from the outdoors, in accordance with Section 703 of the Indiana
				Mechanical Code. Access to such enclosure shall be through a solid door,
				weather-stripped in accordance with the exterior air leakage requirements of
				the Indiana Energy Conservation Code and equipped with an approved self-closing
				device.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-7 - Chapter 6; water supply and distribution

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 7.
Chapter 6 is amended as follows:
(a) Delete Section 602.3 in its entirety
				without substitution.
(b) Amend
				Section 604.9 to read as follows:
(1) Add a
				new second sentence as follows: An air chamber is not a water hammer
				arrestor.
(2) Delete the last
				sentence in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-8 - Chapter 7; sanitary drainage

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 8.
Chapter 7 is amended as follows:
(a) Amend Table 704.1 as follows: delete
				"0.083.3 mm/m" and insert "83.3 mm/m".
(b) Amend Section 705.8.2 as follows: delete
				"purple" and "not purple in color and," without substitution.
(c) Amend Table 702.2 as follows: under
				"Copper or copper alloy tubing", delete without substitution "M or
				DWV".
(d) Amend Section 705.14.2 as
				follows: delete "purple" and "not purple in color and" without
				substitution.
(e) Amend Section
				706.3 as follows: after "combination fittings", delete "side inlets
				or".
(f) Delete the fourth sentence
				in Section 708.3.5 without substitution.
(g) Amend Table 710.1(2) as follows: In the
				second column, delete "2,900" and insert "3,900".
(h) Add Section 710.3 to read as follows:
				710.3 Minimum underground drainage size. The minimum pipe size installed
				underground in a sanitary drainage system within a building shall be two (2)
				inch nominal (50.8 mm) pipe size.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-9 - Chapter 8; indirect/special waste

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 9.
Chapter 8 is amended as follows: Amend Section 802.4 by
				  inserting a new second sentence to read as follows: A trap for a clothes-washer
				  standpipe receptor shall not be installed below the floor.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-10 - Chapter 9; vents

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 10.
Chapter 9 is amended as follows:
(a) Amend Section 901.2.1 by adding an
				exception to read as follows:
Exception: Floor drains.
(b) Amend Section 904.1, in the first
				sentence, to delete "[number] inches (mm)" and insert "six (6) inches (152.4
				mm)".
(c) Amend Section 917.1 by
				deleting: "Stack type air admittance valves shall conform to ASSE 1050" without
				substitution.
(d) Delete the text
				of Section 917.3 and insert as follows: Where permitted. Individual branch and
				circuit vents shall be permitted to terminate with a connection to an
				individual or branch-type air admittance valve. Individual and branch-type air
				admittance valves shall vent only fixtures that are on the same floor level and
				connect to a horizontal branch drain. The horizontal branch drain having
				individual and branch-type air admittance valves shall conform to Section 917.3
				or Section 917.3.2.
(e) Delete the
				text of Section 917.3.3 and insert as follows: Stack. Air admittance valves
				shall not serve as the vent terminal for vent stacks or stack vents.
(f) Amend Section 917.4 by deleting: "Stack
				type air admittance valves shall be located not less than six (6) inches (152
				mm) above the flood level rim of the highest fixture being vented.".
(g) Amend Section 917.8 by adding a second
				sentence to read as follows: Air admittance valves shall not be used to vent
				sump pits.
(h) Amend Section 918.2
				(Equation 9-1) as follows: delete "Qv (gpm) = 27.8
				rs2/3 (1-rs) D8/3" and insert
				"Qv (gpm) = 27.8
				rs2/3
				(1-rs) D8/3".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-11 - Chapter 10; traps, interceptors, and separators

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 11.
Chapter 10 is amended as follows:
(a) Amend Section 1002.1 as follows: in
				exception 2, after "fixture", insert "up to three (3) compartments".
(b) Amend Section 1003.1 to add a second
				sentence to read as follows: A cleanout shall be installed immediately
				downstream of the interceptor or separator.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-12 - Chapter 11; storm drainage

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 12.
Chapter 11 is amended as follows:
(a) Delete Section 1107.2 without
				substitution.
(b) Add Section
				1113.1.5 to read as follows: Water powered sump pumps. Water powered sump pumps
				shall comply with Section 608 of this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-13 - Chapter 12; special piping and storage systems

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 13.
Chapter 12 is amended as follows: Delete the text of Chapter
				  12, Special Piping and Storage Systems and insert: See the Indiana Fire Code
				  (675 IAC 22).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-14 - Chapter 13; referenced standards

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 14.
Referenced standards are amended as follows:
(a) Amend the first paragraph by deleting
				"Section 102.8" and inserting "See Section 101.3".
(b) Delete the following standard from the
				list of ASSE Standards in its entirety without substitution:
Standard Reference Number
Title
Referenced in Code Section Number
ASSE 1050-02
Performance Requirements for Stack Air Admittance
							 Valves for Sanitary Drainage
917.1
(c)
				In the reference to NFPA 50-01, delete "01 edition" and insert "as adopted at
				675
				IAC 28-1-16 ".
(d) In the reference to NFPA 51-02, delete
				"02 edition" and insert "as adopted at
				675
				IAC 28-1-18 ".
(e) In the reference to NFPA 70-05, delete
				"05 edition" and insert "as adopted at 675 IAC 17".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-15 - Appendix A; plumbing permits fee schedule

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 15.
Delete the text of Appendix A in its entirety and insert: See
				  local ordinance.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-16 - Appendix B; rate of rainfall for various cities

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 16.
Appendix B is not adopted and is for informational purposes
				  only.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-17 - Appendix C; gray water recycling systems

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 17.
Appendix C is adopted in its entirety except as
				  amended:
(a) In Section C101.2, delete
				the text of the definition of GRAY WATER and insert to read as follows: GRAY
				WATER means waste water discharged from lavatories, bathtubs, showers, clothes
				washers, laundry trays, condensate cooling coils, and evaporators.
(b) Delete Section C103 in its entirety
				without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-18 - Appendix D; degree day and design temperatures

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 18.
Appendix D is not adopted and is for informational purposes
				  only.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-19 - Appendix E; sizing of water piping system

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 19.
Appendix E is adopted except as amended. Amend Section E201.1
				  as follows:
(1) In item 4, delete the
				reference to "Table E201.1" and insert "Table E103.3(2)".
(2) In item 5, delete the reference to "Table
				E202.1" and insert "Table E203.3(2)".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-20 - Appendix F; structural safety

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 20.
Appendix F is not adopted and is for informational purposes
				  only. For requirements for cutting, notching, and boring in wood members, see
				  the Indiana Building Code (675 IAC 13) or Indiana Residential Code (675 IAC
				  14).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-21 - Appendix G; vacuum drainage system

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 21.
Appendix G is not adopted and is for informational purposes
				  only.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 1.4 - 2012 Indiana Plumbing Code › Section 1.4-22 - ASME 112.19.19-2006, Vitreous China Nonwater Urinals

Current through July 10, 2024
Authority: IC 22-13-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7-2-9
Sec. 22.
(a) That
				certain document being titled ASME A112.19.19, Vitreous China Nonwater Urinals,
				2006 edition, as published by The American Society of Mechanical Engineers,
				Three Park Avenue, New York, NY 10016-5990, is hereby adopted by reference as
				if fully set out in this rule save and except those revisions made in this
				rule.
(b) Amend Paragraph 1.3 as
				follows:
(1) Delete the second sentence in
				its entirety without substitution.
(2) In the reference to ANSI/ICC A117.1,
				insert, after "Facilities", ", as adopted by the Commission in the Indiana
				Building Code in effect at the time of construction, alteration or
				addition".
(3) In the reference to
				ASME A112.6.1M, insert, after "Use", ", the 1997 edition".
(4) In the reference to ASME A112.6.2,
				insert, after "Tanks", ", the 2000 edition".
(5) In the reference to ASME A112.19.2,
				insert, after "Tanks", ", the 2003 edition".
(6) In the reference to ASME A112.19.5,
				insert, after "Urinals", ", the 1999 edition".
(7) In the reference to ASME A112.19.12,
				insert, after "Systems", ", the 2000 edition".
(8) In the reference to UL 969, insert, after
				"Systems", "effective on 12/23/2005".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 16 - PLUMBING CODE › Rule 2 - American Society of Sanitary Engineers Standard 1051-1998 (Repealed)

Current through July 10, 2024
This version of rule effective 90 days after filing with the
				  Publisher. This version of rule was filed with the Publisher on September 25,
				  2012.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 1.
That certain document, being titled as National Electrical
				  Code, 2008 Edition, first printing, published by the National Fire Protection
				  Association, One Batterymarch Park, Quincy, Massachusetts 02169-7471, is hereby
				  incorporated by reference and made a part of the rule, except those portions as
				  are amended and adopted in sections 3 through 30 of this rule
[renumbered by the Publisher as sections 3 through 27 of this
				  rule]
.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-2 - Title; availability

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 2.
(a) This
				rule shall be known as the Indiana Electrical Code, 2009 Edition, and shall be
				published, except for incorporated documents, by the department of homeland
				security, legal and code services, for general distribution and use under the
				title. Whenever the term "this code" is used within this rule, including
				incorporated documents, it shall mean the 2009 Indiana Electrical
				Code.
(b) This rule, with the
				incorporated National Electrical Code, 2008 Edition, is available for review
				and reference at the Department of Homeland Security, 402 West Washington
				Street, Room W246, Indianapolis, Indiana 46204.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-3 - Section 90.2; scope

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 3.
Section 90.2 is amended to read as follows:
(A) Covered. This code covers: Installations
				of electrical conductors and equipment within or on Class 1 and Class 2
				structures, including industrialized building systems, and other premises
				wiring covered by rules of the Commission in this title.
Class 1 and Class 2 structures covered by the Indiana
				  Residential Code shall be made to comply with the provisions of this code, or
				  the electrical provisions of the Indiana Residential Code (675 IAC 14).
(B) Not covered. This code does
				not cover:
(1) Installations in ships,
				watercraft, railway rolling stock, aircraft, automotive vehicles, and buildings
				or structures that are not Class 1 or Class 2 structures.
(2) Installations in underground
				mines.
(3) Installations of
				railways for generation, transformation, transmission, or distribution of power
				used exclusively for operation of rolling stock or installations used
				exclusively for signaling and communication purposes.
(4) Installations of communication equipment
				under the exclusive control of communication utilities, located outdoors or in
				building spaces used exclusively for such installations.
(5) Installations, including associated
				lighting under the exclusive control of electric utilities for the purpose of
				communication, or metering; or for the generation, control, transformation,
				transmission, and distribution of electric energy located in buildings used
				exclusively by utilities for such purposes or located outdoors on property
				owned or leased by the utility or on public highways, streets, roads, etc., or
				outdoors on private property by established rights such as easements.
(6) Installations of electrical wiring,
				equipment, and devices, factory installed in manufactured homes under the
				authority of the U.S. Department of Housing and Urban Development
				(HUD).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-4 - Section 90.4; enforcement

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 4.
Section 90.4 is amended to read as follows: Requirements
				  covering enforcement, granting of variances, and approval of alternate methods
				  or materials are covered in Indiana statutes and 675 IAC 12, the General
				  Administrative Rules of the commission.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-5 - Section 90.6; formal interpretations

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 5.
Section 90.6 is deleted in its entirety without
				  substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-6 - Section 90.8; wiring planning

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 6.
Section 90.8 is deleted in its entirety without
				  substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-7 - Section 90.9; units of measurement

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 7.
Delete the text of Section 90.9 and substitute the
				  following: For the purpose of this code, the measurement system is the English
				  (U.S. customary or inch-pound) system. Compliance with the numbers shown in the
				  inch-pound system shall constitute compliance with this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-8 - Article 100; definitions

Current through July 10, 2024
Authority: IC
				  22-13-2-2;
				  IC
				  22-13-2-13
Affected: IC 10-19-2; IC 22-12; IC
				  22-13-2-7;
				  IC
				  22-13-2-11;
				  IC 22-14; IC
				  22-15-2-7; IC
				  36-7-2-9;
				  IC
				  36-8-17-8
Sec. 8.
(a) In Part
				I of Article 100, delete the text of the definition of APPROVED and substitute
				to read as follows: APPROVED. Acceptance by the AUTHORITY HAVING JURISDICTION
				by one of the following methods:
(1)
				investigation or tests conducted by recognized authorities; or
(2) investigation or tests conducted by
				technical or scientific organizations; or
(3) accepted principles.
The investigation, tests, or principles shall establish that
				  the materials, equipments, and types of construction are safe for their
				  intended purpose.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-9 - Section 210.12(B); dwelling units

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 9.
Delete Section 210.12(B) without
				  substitution.
Agency cited as
					 675 IAC
					 17-1.8-10, which was renumbered by the Publisher as
					 675 IAC 17-1.8-9.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-10 - Section 225.30(B); special occupancies

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 10.
In Section 225.30(B), special occupancies, delete "By
				  special permission" and insert "When approved".
Agency cited as
					 675 IAC
					 17-1.8-11, which was renumbered by the Publisher as
					 675 IAC 17-1.8-10.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-11 - Section 230.2; number of services

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 11.
(a) In the
				second sentence of Section 230.2, after "location", insert "as close as
				practical".
(b) In Section
				230.2(B), special occupancies, delete "By special permission" and insert "When
				approved".
Agency cited as
					 675 IAC
					 17-1.8-12, which was renumbered by the Publisher as
					 675 IAC 17-1.8-11.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-12 - Section 250.104(B); other metal piping

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 12.
(a) Change
				the next to last sentence of Section 250.104(B) to read as follows: The
				equipment grounding conductor for the circuit that is likely to energize the
				piping shall be permitted to serve as the bonding means if connected using a
				fixed wiring method.
(b) Add a new
				sentence at the end of Section 250.104(B) to read as follows: All metal gas
				piping upstream from the equipment shutoff valve(s) shall be electrically
				continuous.
Agency cited as
					 675 IAC
					 17-1.8-13, which was renumbered by the Publisher as
					 675 IAC 17-1.8-12.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-13 - Section 300.3; conductors

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 13.
Add Section 300.3(D), entitled "Separation from corrugated
				  stainless steel tubing", and add text to read as follows: All wiring methods
				  shall be isolated from corrugated stainless steel tubing by a space separation
				  of at least 2 inches except where the bonding connection is made.
Agency cited as
					 675 IAC
					 17-1.8-14, which was renumbered by the Publisher as
					 675 IAC 17-1.8-13.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-14 - Table 314.16(A); metal boxes

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 14.
In the line for 4 x 1 1/4 inch round/octagonal boxes and in
				  the column for 8AWG conductor, delete "5" and insert "4".
Agency cited as
					 675 IAC
					 17-1.8-15, which was renumbered by the Publisher as
					 675 IAC 17-1.8-14.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-15 - Section 334.10; uses permitted

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 15.
(a) Delete
				the text of (2) in Section 334.10 and substitute: (2) In any building or
				structure not exceeding three stories (see Section 362.10 for the definition of
				STORY).
(a) For exposed work except
				as prohibited in Section 334.12.
(b) Concealed within walls, floors, and
				ceilings except as prohibited in Section 334.12.
(b) Delete the text of (3) in Section 334.10
				and substitute: (3) In any building or structure exceeding three stories (see
				Section 362.10 for the definition of STORY), Type NM, Type NMC, and Type NMS
				cables shall be concealed within walls, floors, and ceilings that provide a
				thermal barrier of material that has at least a 15-minute finish rating
				identified in listings of fire-rated assemblies. The 15-minute-finish-rated
				thermal barrier shall be permitted to be used for combustible walls, floors,
				and ceilings, except as prohibited in Section 334.12.
Exception: Where the building is provided with an approved
				  automatic sprinkler system throughout, Type NM, Type NMC, and Type NMS cables
				  are permitted to be used within walls, floors, ceilings, exposed or concealed,
				  in buildings exceeding three stories.
Agency cited as
					 675 IAC
					 17-1.8-16, which was renumbered by the Publisher as
					 675 IAC 17-1.8-15.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-16 - Section 334.12; uses not permitted

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 16.
In Section 334.12(A):
(1) delete the exception to Item (1) without
				substitution; and
(2) delete Item
				(2) without substitution.
Agency cited as
					 675 IAC
					 17-1.8-17, which was renumbered by the Publisher as
					 675 IAC 17-1.8-16.