reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1694 - Hazardous materials

Current through Vol. 24-12, July 15, 2024
Rule 44. Sections 60.1.2.3, 60.1.2.3.1, 60.1.2.3.1.1,
					 60.1.2.3.1.2, 60.1.2.3.1.3, 60.1.2.3.2,60.1.3.3.3, 60.1.4.2.2, 60.2.3,
					 60.2.3.1, 60.2.3.2 and 60.3.2.5.1.1 of chapter 53 of the code are deleted and
					 sections 60.1.1.2, 60.1.2.4.1, 60.1.2.4.2, 60.1.2.4.3.1, 60.1.2.5.1,
					 60.1.2.5.1.2, 60.1.2.5.2, 60.1.2.6.3 and 60.1.2.21 of chapter 60 of the code
					 are amended to read as follows:
60.1.1.2 Buildings, and portions thereof,
				  containing high hazard contents limited to the following shall not be required
				  to comply with this chapter:
(1) Flammable and
				  combustible liquids associated with application of flammable finishes and
				  complying with chapter 43.
(2)
				  Flammable and combustible liquids associated with wholesale and retail sales
				  and storage in mercantile occupancies and complying with chapter 66.
(3) Class IIIA and class IIIB combustible
				  liquid solvents in closed systems employing listed cleaning equipment complying
				  with chapter 24.
(4) Refrigerants
				  and refrigerant oil contained within closed-cycle refrigeration systems
				  complying with chapter 53 and the building code.
(5) Flammable and combustible liquid
				  beverages in liquor stores and distributors without bulk storage.
(6) High hazard contents stored or used in
				  farm buildings or similar occupancies for on-premise agricultural
				  use.
(7) Corrosive materials in
				  stationary batteries utilized for facility emergency power, uninterrupted power
				  supply, or similar purposes, provided that the batteries are provided with
				  safety venting caps and ventilation is provided in accordance with chapter
				  52.
(8) Corrosive materials
				  displayed in original packaging in mercantile occupancies and intended for
				  personal or household use or as building materials.
(9) Aerosol products in storage or mercantile
				  occupancies and complying with chapter 61.
(10) Installation of fuel gas distribution
				  systems and associated equipment in accordance with section
				  11.4
				  and chapter 69 as referenced in the building code.
(11) Consumer fireworks, 1.4G in mercantile
				  occupancies complying with section 65.11.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1695 - Aerosol products

Current through Vol. 24-12, July 15, 2024
Rule 45. Sections 61.1.2, 61.4.2, 61.4.2.1, 61.4.2.1.1,
					 61.4.2.1.3, 61.4.2.2, 61.4.2.3, 61.4.3, 61.4.3.1, 61.4.3.1.1, 61.4.3.2, 61.4.4,
					 61.4.5, 61.4.6, 61.4.6.1, 61.4.6.2, 61.4.6.4, 61.4.6.4.1, 61.4.6.4.1.1,
					 61.4.6.4.1.2, 61.4.6.4.1.3, 61.4.6.4.2, 61.4.6.5, 61.5.2, 61.5.2.1, 61.5.2.2,
					 61.5.3, 61.5.3.1, 61.5.3.1.1 and 61.5.3.1.1.1 of chapter 61 of the code are
					 deleted to read as follows:
61.1.2
				  Deleted.
61.4.2 Deleted.
61.4.2.1 Deleted.
61.4.2.1.1 Deleted.
61.4.2.1.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1700 - Oxidizers and organic pesticides

Current through Vol. 24-12, July 15, 2024
Rule 50. Sections 70.1.2, 70.2.4.1.1, 70.2.4.1.1.1,
					 70.2.4.1.2, 70.2.4.1.2.1, 70.2.4.1.2.2, 70.2.4.1.2.3, 70.2.4.1.2.4,
					 70.2.4.1.2.4.1, 70.2.4.1.2.5, 70.2.4.1.3, 70.2.4.5, 70.2.4.5.1, 70.2.4.5.1.1,
					 70.2.4.5.1.2, 70.2.4.5.2, 70.2.4.5.2.1, 70.2.4.5.2.2, 70.2.4.5.3, 70.2.4.8.1,
					 70.2.4.8.1.1, 70.2.4.8.1.2, 70.2.4.8.2, 70.2.4.8.2.1, 70.2.4.8.2.2,
					 70.2.4.8.2.2.1, 70.2.4.8.2.2.2, 70.2.4.8.3, 70.2.4.8.3.1, 70.2.4.8.3.2,
					 70.2.4.8.3.3, 70.2.7.4, 70.2.7.4.1, 70.2.7.4.2, 70.2.7.4.3, 70.2.7.4.4,
					 70.2.7.4.4.1, 70.2.8.4, 70.2.8.4.1, 70.2.8.4.2, 70.3.4.2, 70.3.4.3, 70.3.4.6.2,
					 70.3.4.6.2.1, 70.3.4.6.3, 70.3.5.3, 70.3.5.5, 70.3.6.3, 70.3.6.3.1, 70.3.6.3.2
					 and 70.3.6.3.3 of chapter 70 of the code are deleted and section 70.2.4.6.3 of
					 chapter 70 of the code is amended to read as follows:
70.1.2 Deleted.
70.2.4.1.1 Deleted.
70.2.4.1.1.1 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1700a - Pyrophoric solids and liquids

Current through Vol. 24-12, July 15, 2024
Rule 50a. Sections 71.1, 71.2, 71.2.1 and 71.2.2 of chapter
					 71 of the code are deleted to read as follows:
71.1 Deleted.
71.2 Deleted.
71.2.1 Deleted.
71.2.2 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1700b - Unstable (reactive) solids and liquids

Current through Vol. 24-12, July 15, 2024
Rule 50b. Sections 72.1, 72.2, 72.2.1, 72.2.1.1, 72.2.1.2,
					 72.2.1.3, 72.2.2, 72.2.2.1 and 72.2.2.2 of chapter 72 of the code are deleted
					 to read as follows:
72.1
				  Deleted.
72.2 Deleted.
72.2.1 Deleted.
72.2.1.1 Deleted.
72.2.1.2 Deleted.
72.2.1.3 Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1701 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 1. These rules apply to penal facilities, described in
					 section 62 of 1953 PA 232, MCL
					 791.262,
					 as they pertain to the fire safety requirements for the construction,
					 operation, or maintenance of all new penal facilities and all existing penal
					 facilities.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1703 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 3. As used in these rules:
(a) "Act" means 1941 PA 207, MCL
				  29.1 to
				  29.33.
(b) "Authority having jurisdiction" means the
				  director of the Michigan department of licensing and regulatory affairs, an
				  employee of the department of licensing and regulatory affairs appointed by the
				  director to implement the act, or an employee of a city, village, or township
				  delegated to enforce the code under the provisions of section 2b, MCL
				  29.2b,
				  of the act.
(c) "Code" means
				  national fire protection association standard no. 101, 2012 edition, entitled
				  "Life Safety Code."
(d) "Cosmetic
				  remodeling" means surface changes made solely to the wall, floor, or ceiling
				  that do not decrease the fire rating of the wall, floor, or ceiling, including
				  the replacement of windows and doors.
(e) "Existing" means a building constructed
				  and occupied as a penal facility before the effective date of these
				  rules.
(f) "Maintenance" means
				  repair that is required to keep the building and its component parts in an
				  operative condition at all times. "Maintenance" includes the replacement of a
				  building's components when, for any reason, they become undependable or
				  inoperable. "Maintenance" does not include renovation.
(g) "Penal facility" means a detention or
				  correctional occupancy that provides sleeping facilities for 1 or more
				  residents and that is occupied by persons who are generally prevented from
				  exiting an area because of security measures not under the occupants' control.
				  Only the penal facilities as described in section 62 of 1953 PA 232, MCL
				  791.262,
				  are considered a "penal facility".
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1704 - Plans and specifications

Current through Vol. 24-12, July 15, 2024
Rule 4.
(1) A
				  penal facility or designated representative of that facility shall submit plans
				  and specifications to the bureau of fire services for all projects that involve
				  construction, remodeling, renovation, modification, reconstruction, or an
				  addition.
(2) A penal facility or
				  designated representative of that facility need not submit plans and
				  specifications to the bureau of fire services for routine maintenance
				  functions; however, the penal facility or designated representative of that
				  facility shall ensure that all work is in compliance with these
				  rules.
(3) Plans and specifications
				  for work that involves the practice of architecture or engineering, as defined
				  by the provisions of article 20 of the occupational code, 1980 PA 299, MCL
				  339.2001 to
				  339.2014,
				  shall bear the seal of an architect or professional engineer who is licensed
				  pursuant to the occupational code.
(4) Plans and specifications shall contain
				  all of the following information, as applicable:
(a) A complete floor plan and layout of the
				  building drawn accurately to scale.
(b) The use of each room.
(c) The dimensions of each room.
(d) The size, location, direction of swing,
				  and fire rating of each door and frame assembly.
(e) The size and location of
				  windows.
(f) The wall construction,
				  including the fire-resistance rating.
(g) The type of construction as identified by
				  the provisions of the national fire protection association standard no. 220,
				  entitled "Standard for Types of Building Construction," as adopted in
				  R
				  29.1702.
(h) The number of stories, including basement
				  and attic areas.
(i) The interior
				  finish classification.
(j) The
				  location of fuel-fired equipment.
(k) The type of furnace and water
				  heater.
(l) Air-handling system
				  specifications.
(m) Fire detection
				  and alarm system plans and specifications that are in compliance with the
				  provisions of the act.
(n)
				  Sprinkler or other suppression system plans and specifications that are in
				  compliance with the provisions of the act.
(o) The type, size, and location of fire
				  extinguishers.
(p) Other pertinent
				  information that is required to determine compliance with these
				  rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1705 - Inspection during construction; approval for occupancy

Current through Vol. 24-12, July 15, 2024
Rule 5.
(1) During
				  construction, renovation, modification, reconstruction, addition, or
				  remodeling, the architect, professional engineer, or penal facilitys designated
				  representative shall notify the bureau of fire services, in writing, when the
				  building is ready for inspection under both of the following conditions:
(a) When the building is framed and
				  mechanical systems are substantially complete, but before
				  concealment.
(b) Upon completion of
				  construction.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1706 - Projects affecting outside configuration of building; site plan and specifications; bureau of fire services or local fire department specifications; fire safety measures during construction

Current through Vol. 24-12, July 15, 2024
Rule 6.
(1) For a
				  project that involves construction, addition, or remodeling that affects the
				  outside configuration of a building, and is part of the building plans and
				  specifications otherwise required by these rules, the penal facility or
				  designated representative of that facility shall provide the bureau of fire
				  services and the local fire department with a site plan and specifications that
				  detail all of the following:
(a) The
				  available water supply.
(b) Hydrant
				  locations.
(c) Vehicle access
				  routes.
(d) Fire lanes.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1707 - Electrical equipment; inspections; certificate

Current through Vol. 24-12, July 15, 2024
Rule 7.
(1) The
				  penal facility or a designated representative of that facility shall ensure
				  that the electrical wiring and equipment, including an emergency supply if
				  installed, complies with the applicable provisions of the Michigan electrical
				  code,
				  R 408.30801 to
				  R
				  408.30880. Copies of the rules are available from the
				  Michigan Department of licensing and regulatory affairs, Bureau of Construction
				  Codes, 611 West Ottawa St., First Floor, Lansing, MI 48909.
(2) The electrical inspection shall be made
				  by an electrical inspection authority acceptable to the bureau of fire
				  services. The electrical inspection authority shall issue a final certificate
				  of compliance covering the installation and the penal institution or designated
				  representative shall provide a copy of the certificate to the bureau of fire
				  services.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1708 - Universal amendments

Current through Vol. 24-12, July 15, 2024
Rule 8. Sections 4.6.10.1, 8.7.3.1, 9.1.1, 9.1.2, 9.4.2.1,
					 9.4.2.2, and 43.1.2.1 of the code adopted by reference in
					 R
					 29.1702 are amended and sections 9.4.3.1, 9.4.3.2, and
					 43.6.4.3 are deleted, as follows:
4.6.10.1. A person may occupy a building or
				  portion of a building during construction, repair, alterations, renovations,
				  modification, reconstruction, or additions only if all means of egress and all
				  fire protection features in the building and on-site are in place and
				  continuously maintained for the part occupied and if the occupied portion is
				  separated from the part under construction by a wall that has a
				  1-hour-fire-resistance rating. The temporary 1-hour-rated wall that is used for
				  separation may be constructed of combustible material. Instead of having all
				  means of egress and fire protection features in place, the penal facility or
				  designated representative of that facility may take other measures that would
				  provide equivalent safety if approved by the bureau of fire services. NFPA 241
				  standard for safeguarding construction, alteration, and demolition operations,
				  may be consulted for further guidance.
8.7.3.1 The penal facility or designated
				  representative shall store and handle flammable and combustible liquids in
				  compliance with R 29.5101 to R 29.5516.
9.1.1. The penal facility or designated
				  representative of that facility shall ensure that equipment that utilizes gas
				  and related gas piping is installed in compliance with the provisions of NFPA
				  54, National Fuel Gas Code, and NFPA 58, liquefied petroleum gas code, as
				  adopted under
				  R
				  29.1702, or rules promulgated under the act.
9.1.2. Electrical wiring and equipment shall
				  be in compliance with the Michigan electrical code,
				  R 408.30801 to
				  R
				  408.30880.
9.4.2.1. The penal facility or designated
				  representative of that facility shall ensure that new elevators, escalators,
				  dumbwaiters, and moving walks are installed in compliance with the Michigan
				  elevator code,
				  R
				  408.7001 to R 408.8699.
9.4.2.2. The penal facility or designated
				  representative shall ensure that existing elevators, escalators, dumbwaiters,
				  and moving walks are in compliance with the Michigan elevator code,
				  R
				  408.7001 to R 408.8699.
9.4.3.1. Deleted
9.4.3.2.  Deleted
43.1.2.1. The portion or portions of a
				  building undergoing repair, renovation, modification, or reconstruction shall
				  comply with both of the following:
(1)
				  Requirements of the applicable existing occupancy chapters.
(2)  Requirements of the applicable section
				  of this chapter.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1710 - Fire reporting

Current through Vol. 24-12, July 15, 2024
Rule 10.
(1) Upon
				  discovery of any unwanted fire, regardless of magnitude, the facility staff
				  member shall immediately notify the penal facility control center.
(2) Whenever an unwanted fire occurs, or upon
				  discovery of an unwanted fire, even though it has been extinguished, the
				  facility staff member shall immediately notify the facility control center of
				  the existence of the fire, the circumstances of the fire, and the location of
				  the fire. This requirement does not prohibit the penal facility from using all
				  diligence necessary to extinguish the fire prior to the arrival of the fire
				  department.
(3) Whenever a fire
				  requires the local fire department to respond, the penal facility or the
				  designated representative shall notify the bureau of fire services of all
				  details of the fire not later than the end of the next business day following
				  the incident.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 2 - NEW PENAL FACILITIES › Section R. 29.1721 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 21. This part applies to fire safety requirements for
					 the construction, operation, or maintenance of all new penal
					 facilities.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 2 - NEW PENAL FACILITIES › Section R. 29.1723 - Amendments to chapter 22 of the code

Current through Vol. 24-12, July 15, 2024
Rule 23. Section 22.7.7 of the code is amended, as
					 follows:
Section 22.7.7. Doors and door hardware not in proper
					 operating condition shall be repaired or replaced without undue delay.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Penal Facilities Institutions Fire Safety › Part 3 - EXISTING PENAL FACILITIES › Section R. 29.1733 - Amendments to chapter 23 of the code

Current through Vol. 24-12, July 15, 2024
Rule 33. Sections 23.1.6.1, 23.3.5.2, 23.3.8, and 23.7.7 of
					 the code are amended, table 23.1.6.1 of the code is deleted and sections
					 23.1.6.3, 23.1.6.4, 23.2.3.2.1, 23.3.8.1, 23.4.3.1, and 23.7.5.1 are added to
					 the code to read as follows:
23.1.6.1
				  Detention and correctional occupancies shall be limited to the following types
				  of building construction, unless otherwise provided in Section 23.1.6.3 or
				  Section 23.1.6.4:
Type of construction
Below 1st story
1st story
2nd story
3rd story
4th story and above
I (443)
A.S.
A.S.
A.S.
A.S.
A.S.
I (332)
A.S.
A.S.
A.S.
A.S.
A.S.
II (222)
A.S.
A.S.
A.S.
A.S.
A.S.
II (111)
A.S.
A.S.
A.S.
N.P.
N.P.
III (211)
A.S.
A.S.
A.S.
N.P.
N.P.
IV (2HH)
A.S.
A.S.
A.S.
N.P.
N.P.
V (111)
A.S.
A.S.
A.S.
N.P.
N.P.
II (000)
A.S.
A.S.
A.S.
N.P.
N.P.
III (200)
A.S.
A.S.
A.S.
N.P.
N.P.
V (000)
A.S.
A.S.
A.S.
N.P.
N.P.
A. S.: Permitted if the entire building is protected
					 throughout by an approved automatic sprinkler system in accordance with section
					 9.7.1.1(1) of the code. N.P.: Not permitted.
Table 23.1.6.1. Deleted.
23.1.6.3. Existing penal facilities built
				  prior to November 17, 1982 shall be constructed of fire-resistive construction
				  and not attached to a wooden building, except for penal facilities that house
				  low security day-parole inmates, or for a multi-purpose room. A building of
				  combustible construction may be attached to a jail if both of the following
				  apply:
(a) A 2-hour fire rated noncombustible
				  separation is maintained between the buildings with a 90-minute fire rated door
				  and no other openings allowed.
(b)
				  An automatic smoke detection system is installed in the combustible building
				  that activates an alarm within a control center in case of fire.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1801 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 1.
(1)
					 These rules apply to all of the following new and existing health care and
					 mental health care facilities:
(a)
					 Freestanding surgical outpatient facilities.
(b) Hospitals.
(c) Nursing homes.
(d) Homes for the aged.
(e) Psychiatric hospitals and psychiatric
					 units.
(f) Hospice
					 residences.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1804 - Plans and specifications

Current through Vol. 24-12, July 15, 2024
Rule 4.
(1) A
					 health care facility, or designated representative, shall submit plans and
					 specifications to the bureau of fire services for all projects that involve
					 construction, remodeling, renovation, modification, reconstruction, or an
					 addition.
(2) A health care
					 facility is not required to submit plans and specifications for routine
					 maintenance functions; however, a health care facility shall ensure that all
					 work is in compliance with these rules.
(3) Plans and specifications for work that
					 involves the practices of architecture or engineering, as defined by the
					 provisions of article 20 of the occupational code, 1980 PA 299, MCL 339.2001 to
					 339.2014, shall bear the seal of an architect or professional engineer who is
					 licensed pursuant to the occupational code.
(4) Plans and specifications shall contain
					 all of the following information, as applicable:
(a) A complete floor plan and layout of the
					 building drawn accurately to scale.
(b) The use of each room.
(c) The dimensions of each room.
(d) The size, location, direction of swing,
					 and fire rating of each door and frame assembly.
(e) The size and location of
					 windows.
(f) The wall construction,
					 including the fire-resistance rating.
(g) The type of construction as identified in
					 the national fire protection association standard no. 220, entitled "Standard
					 on Types of Building Construction," as adopted in these rules.
(h) The number of stories, including basement
					 and attic areas.
(i) The interior
					 finish classification.
(j) The
					 location of fuel-fired equipment.
(k) The type of furnace and water
					 heater.
(l) Air-handling system
					 specifications.
(m) Fire detection
					 and alarm system plans and specifications that are in compliance with the
					 provisions of the act.
(n)
					 Sprinkler or other suppression system plans and specifications that are in
					 compliance with the provisions of the act.
(o) The type, size, and location of fire
					 extinguishers.
(p) Other pertinent
					 information that is required to determine compliance with these
					 rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1805 - Inspections during construction; approval for occupancy

Current through Vol. 24-12, July 15, 2024
Rule 5.
(1)
					 During construction, renovation, modification, reconstruction, addition, or
					 remodeling, the architect, professional engineer, or owner's representative
					 shall notify the bureau of fire services, in writing, when the building is
					 ready for inspection under both of the following conditions:
(a) When the building is framed and
					 mechanical systems are substantially complete, but before
					 concealment.
(b) Upon completion of
					 construction.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1806 - Projects affecting outside configuration of building; site plan and specifications; bureau of fire services or local fire department specifications; fire safety measures during construction

Current through Vol. 24-12, July 15, 2024
Rule 6.
(1) For
					 projects that involve construction, addition, renovation, modification,
					 reconstruction or remodeling which affect the outside configuration of a
					 building, and as part of the building plans and specifications otherwise
					 required by these rules, before the construction begins, the owner or the
					 owner's authorized representative shall provide the bureau of fire services and
					 the local fire department with a site plan and specifications that detail all
					 of the following:
(a) The available water
					 supply.
(b) Hydrant
					 locations.
(c) Vehicle access
					 routes.
(d) Fire lanes.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1807 - Electrical equipment; inspections; certificate

Current through Vol. 24-12, July 15, 2024
Rule 7.
(1) The
					 health care facility or authorized representative shall ensure that the
					 electrical wiring and equipment, including an emergency electrical supply if
					 installed, complies with the applicable provisions of the Michigan electrical
					 code, R 408.30801of the Michigan Administrative Code.Copies of the rules are
					 available as specified in
					 R
					 29.1902.
(2) Electrical inspection shall be made by an
					 electrical inspection authority acceptable to the bureau of fire services. The
					 authority shall issue a final certification of compliance covering the
					 installation. The health care facility, or authorized representative shall
					 provide a copy of the certificate to the bureau of fire services.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1808 - Universal amendments

Current through Vol. 24-12, July 15, 2024
Rule 8. Sections 4.6.10.1, 8.7.3.1, 9.4.2.1, and 9.4.2.2
						of the code adopted by reference in
						R 29.1802 of these rules are amended
						and sections 9.1.2, 9.4.3.1, and 9.4.3.2 are deleted, as follows:
4.6.10.1. A person may occupy a building or
					 portion of a building during construction, repair, alterations, renovations,
					 modification, reconstruction or additions only if all means of egress and all
					 fire protection features in the building and on-site are in place and
					 continuously maintained for the part occupied and if the occupied portion is
					 separated from the part under construction by a wall that has a
					 1-hour-fire-resistance rating. The temporary 1-hour-rated wall that is used for
					 this separation may be constructed of combustible material. Instead of having
					 all means of egress and fire protection features in place, the health care
					 facility may take other measures that would provide equivalent safety if
					 approved by the bureau of fire services. A health care facility or part of a
					 health care facility shall not be occupied, in whole or in part, without
					 approval from the bureau of fire services and the bureau of community and
					 health systems.
8.7.3.1. The
					 health care facility shall store and handle flammable and combustible liquids
					 in compliance with
					 R
					 29.5601 to
					 R
					 29.5917 promulgated by the Michigan department of
					 licensing and regulatory affairs, bureau of fire services under the provisions
					 of the act.
9.1.2. Deleted.
9.4.2.1. The health care facility
					 shall ensure that new elevators, escalators, dumbwaiters, and moving walks are
					 installed in compliance with the Michigan elevator rules,
					 R
					 408.7001 to
					 R 408.7103, promulgated by the
					 Michigan department of licensing and regulatory affairs, bureau of construction
					 codes.
9.4.2.2. The health care
					 facility shall ensure that existing elevators, escalators, dumbwaiters, and
					 moving walks are in compliance with the Michigan elevator rules,
					 R
					 408.7001 to
					 R 408.7103, promulgated by the
					 Michigan licensing and regulatory affairs, bureau of construction
					 codes.
9.4.3.1. Deleted.
9.4.3.2. Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1809 - Fire reporting

Current through Vol. 24-12, July 15, 2024
Rule 9.
(1) Upon
					 discovery of any unwanted fire, regardless of magnitude, the person in control
					 of the building shall immediately notify the local fire department.
(2) Whenever an unwanted fire occurs, or upon
					 discovery of a unwanted fire, even though it has been extinguished, the person
					 in control of the building shall immediately notify the local fire department
					 of the existence of the fire, circumstances, and the location of the fire. This
					 requirement does not prohibit the facility from using all diligence necessary
					 to extinguish the fire prior to the arrival of the fire department.
(3) The administrator or designee shall
					 notify the bureau of fire services of all details of the fire not later than
					 the end of the next business day following the incident.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 1 - GENERAL PROVISIONS › Section R. 29.1810 - Rescission

Current through Vol. 24-12, July 15, 2024
Rule 10. R 29.1001 to R 29.1053 of the Michigan
						Administrative Code are rescinded.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 2 - FREESTANDING SURGICAL OUTPATIENT FACILITIES › Section R. 29.1821 - Life safety code; existing type I freestanding surgical outpatient facilities; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 21. The provisions of chapters 1 to 11, 21, 39, and
						43 of the code that apply to existing business occupancies are adopted by
						reference, and are available for review as specified in
						R 29.1802, and apply to type I
						freestanding surgical outpatient facilities.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 2 - FREESTANDING SURGICAL OUTPATIENT FACILITIES › Section R. 29.1822 - Life safety code; existing type II freestanding surgical outpatient facilities; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 22. The provisions of chapters 1 to 11, 21, 39, and
						43 of the code that apply to existing ambulatory health care centers and
						existing business occupancies are adopted by reference in
						R 29.1802 and apply to existing type
						II freestanding surgical outpatient facilities.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 2 - FREESTANDING SURGICAL OUTPATIENT FACILITIES › Section R. 29.1823 - Life safety code; new type I freestanding surgical outpatient facilities; adoption by reference; amendments

Current through Vol. 24-12, July 15, 2024
Rule 23.
(1) The
					 provisions of chapters 1 to 11, 20, and 38 of the code that apply to new
					 business occupancies apply to new type I freestanding surgical outpatient
					 facilities and, except for the amendments to the provisions specified in these
					 rules, are adopted by reference in
					 R 29.1802.
(2) Section
					 38.1.1.1
					 of the code is amended to read as follows:
38.1.1.1 The requirements of this chapter
					 shall apply to new buildings or portions thereof used as business occupancies.
					 National fire protection association standard no. 101A entitled "Guide on
					 Alternative Approaches to Life Safety," as adopted in
					 R
					 29.1801 of these rules, does not apply to the design
					 of new freestanding surgical outpatient facilities construction.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 2 - FREESTANDING SURGICAL OUTPATIENT FACILITIES › Section R. 29.1824 - Life safety code; new type II freestanding surgical outpatient facilities; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 24.
(1) The
					 provisions of chapters 1 to 11, 20, and 38 of the code that apply to new
					 ambulatory health care centers and new business occupancies apply to new type
					 II freestanding surgical outpatient facilities and, except for the amendments
					 to the provisions specified in these rules, are adopted by reference in
					 R
					 29.1801.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 3 - HOSPITALS; MENTAL HOSPITALS › Section R. 29.1831 - Life safety code; existing hospitals, mental hospitals, psychiatric hospitals, and psychiatric units; adoption by reference; amendment

Current through Vol. 24-12, July 15, 2024
Rule 31. Existing hospitals, mental hospitals,
						psychiatric hospitals, and psychiatric units shall comply with the following
						provisions of chapters 1 to 10, 11, 19, and 43 of the code that apply to
						existing health care occupancies, which are adopted by reference in
						R 29.1802 except for the amendments
						in these rules. Section 19.3.6.3.6 of the code is deleted.19.3.6.3.6.
						Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 3 - HOSPITALS; MENTAL HOSPITALS › Section R. 29.1832 - Life safety code; new hospitals, mental hospitals, psychiatric hospitals, and psychiatric units; adoption by reference; amendment

Current through Vol. 24-12, July 15, 2024
Rule 32.
(1) The
					 provisions of chapters 1 to 10, 11, 18, and 43 of the code that apply to new
					 hospitals, new mental hospitals, new psychiatric hospitals, and new psychiatric
					 units are adopted by reference in
					 R 29.1802.
(2) Section 18.3.6.3.9.2 of the code is
					 deleted and Section 18.4.3.7.2.1 of the code is amended to read as follows:
18.3.6.3.9.2 Deleted
18.4.3.7.2.1 Where the smoke compartment
					 being modified is not protected throughout by an approved, supervised automatic
					 sprinkler system in accordance with 19.3.5.7, all of the following shall apply:
(1) Doors protecting corridor openings shall
					 be constructed of 1-3/4 in. (44 mm) thick, solid-bonded core wood or of
					 construction that resists the passage of fire for a minimum of 20
					 minutes.
(2) Door frames shall be
					 labeled or of steel construction.
(3) Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 4 - NURSING HOMES › Section R. 29.1841 - Life safety code; existing nursing homes; amendment; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 41. Existing nursing homes shall comply with the
						provisions of chapters 1 to 10, 11, 19, and 43 of the code, which are adopted
						by reference in
						R 29.1802. Section 19.3.5.1 of the
						code is amended to read as follows:
19.3.5.1. Buildings containing nursing homes
					 shall be protected throughout by an approved, supervised automatic sprinkler
					 system in accordance with Section 9.7, unless otherwise permitted by 19.3.5.4.
					 The facility owner or designated representative shall comply with this
					 requirement by July 28, 2019.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 4 - NURSING HOMES › Section R. 29.1842 - Life safety code; new nursing homes; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 42.
(1) The
					 provisions of chapters 1 to 10, 11, 18, and 43 of the code that apply to new
					 nursing home occupancies are adopted by reference in R 19.1802.
(2) Section 18.4.3.7.2.1 is amended to read
					 as follows:
18.4.3.7.2.1 Where the smoke
					 compartment being modified is not protected throughout by an approved,
					 supervised automatic sprinkler system in accordance with 19.3.5.7, all of the
					 following shall apply:
(1) Doors protecting
					 corridor openings shall be constructed of 1-3/4 in. (44 mm) thick, solid-bonded
					 core wood or of construction that resists the passage of fire for a minimum of
					 20 minutes.
(2) Door frames shall
					 be labeled or of steel construction.
(3) Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 5 - HOMES FOR THE AGED › Section R. 29.1851 - Life safety code; existing homes for the aged; adoption by reference; amendments

Current through Vol. 24-12, July 15, 2024
Rule 51. Part A. Existing licensed homes for the aged
						shall comply with the provisions of chapters 1 to 10, 11, 19, and 43 of the
						code that apply to existing health care occupancies, which are adopted by
						reference in
						R 29.1802, except for the provisions
						of the chapters amended by these rules.
Section 19.3.7.4 is amended, and sections 19.3.5.5 and
						19.3.6.1.1 are added to the code, to read as follows:
19.3.5.5. Existing licensed home for the aged
					 facilities shall only house mobile residents unless the smoke compartments that
					 house non-mobile residents are protected throughout by an automatic
					 extinguishing system that is in compliance with section 19.3.5.3 of the
					 code.
19.3.6.1.1 To provide for the
					 physical needs of residents, seating locations within corridors shall be
					 limited in number and only allowed where essential, such as waiting areas at
					 elevators or outside transportation, and shall meet the following criteria:
(a) Seating shall not impede on the required
					 width of the corridor and shall be limited to seating which will accommodate up
					 to 2 persons per location.
(b)
					 Seating arrangements shall be of metal or wood construction or upholstered
					 furniture complying with 1 of the following provisions:
(i) The furniture shall meet the criteria
					 specified in 10.3.2.1 and 10.3.3.
(ii) The furniture shall be in a building
					 protected throughout by an approved, supervised automatic sprinkler system in
					 accordance with 9.7.1.1 (1).
(c) Pads or cushions used on metal or wood
					 construction or furniture shall meet the requirements of paragraph (i) of
					 subdivision (b) of this rule, or NFPA 701.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 5 - HOMES FOR THE AGED › Section R. 29.1852 - Life safety code; new homes for the aged; adoption by reference; amendment

Current through Vol. 24-12, July 15, 2024
Rule 52. Part A.
(1) The provisions of chapters 1 to 10, 11,
					 18, and 43 of the code that apply to new limited care occupancies, except as
					 amended by these rules, are adopted by reference in
					 R 29.1802 of these rules.
(2) Section 18.3.6.1.1 is added to the code,
					 to read as follows:
18.3.6.1.1 To provide for
					 the physical needs of residents, seating locations within corridors shall be
					 limited in number and only allowed where essential, such as waiting areas at
					 elevators or outside transportation, and shall meet the following criteria:
(a) Seating shall not impede on the required
					 width of the corridor and shall be limited to seating which will accommodate up
					 to 2 persons per location.
(b)Seating arrangements shall be of metal or
					 wood construction or upholstered furniture complying with 1 of the following
					 provisions:
(i) The furniture shall meet the
					 criteria specified in 10.3.2.1 and 10.3.3.
(ii) The furniture shall be in a building
					 protected throughout by an approved, supervised automatic sprinkler system in
					 accordance with 9.7.1.1(1).
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › State Fire Safety Board › Health Care Facilities Fire Safety Rules › Part 7 - HOSPICE FACILITIES › Section R. 29.1871 - Code; new and existing hospice residences; adoption by reference; amendment

Current through Vol. 24-12, July 15, 2024
Rule 71.
(1) The
					 provisions of chapters 1 to 10, 11, 18, and 43 of the code that apply to new
					 hospice occupancies, except as amended by these rules, are adopted by reference
					 in
					 R
					 29.1801.
(2) The provisions of chapters 1 to 10, 11,
					 19, and 43 of the code that apply to existing hospice occupancies, except as
					 amended by these rules, are adopted by reference in
					 R
					 29.1801.
Section 18.4.3.7.2.1 of the code is amended to read as
						follows:
18.4.3.7.2.1 Where the smoke
					 compartment being modified is not protected throughout by an approved,
					 supervised automatic sprinkler system in accordance with 19.3.5.7, all of the
					 following shall apply:
(a) Doors protecting
					 corridor openings shall be constructed of 1-3/4 in. (44 mm) thick, solid-bonded
					 core wood or of construction that resists the passage of fire for a minimum of
					 20 minutes.
(b) Door frames shall
					 be labeled or of steel construction.
(c) Deleted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › New and Existing School, College and University Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1901 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 1. These rules apply to all new and existing school,
					 college, and university facilities used for instructional purposes as defined
					 by these rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › New and Existing School, College and University Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1903 - Definitions.

Current through Vol. 24-12, July 15, 2024
Rule 3.
As used in these rules:
(a) "Act" means 1941 PA 207, MCL 29.1 to
				  29.34
(b) "Authority having
				  jurisdiction" means the director of the department of licensing and regulatory
				  affairs, an employee of the department of licensing and regulatory affairs
				  appointed by the director to implement the act, or an employee of a city,
				  village, or township delegated authority to enforce the code under section 2b
				  of the act.
(c) "Code" means
				  national fire protection association pamphlet no. 101, 2012 edition, entitled
				  "Life Safety Code."
(d) "College"
				  or "university" means a junior college, community college, college, or
				  university that is duly authorized to grant degrees by 1 of the following:
(i) Article VIII of the Michigan Constitution
				  of 1963.
(ii) The Michigan
				  legislature.
(iii) Action by the
				  state board of education.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › New and Existing School, College and University Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1904 - Plans and specifications

Current through Vol. 24-12, July 15, 2024
Rule 4.
(1) A
				  school, college, university, or designated representative shall submit plans
				  and specifications to the bureau of fire services for all projects that involve
				  construction, remodeling, renovation, modification, reconstruction, or an
				  addition.
(2) A school, college, or
				  university need not submit plans and specifications to the bureau of fire
				  services for routine maintenance functions or cosmetic remodeling; however, a
				  school, college, or university shall ensure that all work is in compliance with
				  these rules.
(3) Plans and
				  specifications for work that involves the practice of architecture or
				  engineering, as defined by the provisions of article 20 of the occupational
				  code, 1980 PA 299, MCL 339.2001 to 339.2014, shall bear the seal of an
				  architect or professional engineer who is licensed pursuant to the occupational
				  code. If a public works project consisting of construction, renovation,
				  modification, reconstruction, or an addition is estimated to cost less than $1
				  5,000.00, it is not necessary to employ a registered architect or engineer, but
				  the plans for the building shall be submitted to the bureau of fire services
				  for approval pursuant to section 5a of 1937 PA 306, MCL 388.855a.
(4) Plans and specifications shall contain
				  all of the following information, as applicable:
(a) A complete floor plan and layout of the
				  building drawn accurately to scale.
(b) The use of each room.
(c) The dimensions of each room.
(d) The size, location, direction of swing,
				  and fire rating of each door and frame assembly.
(e) The size and location of
				  windows.
(f) The wall construction,
				  including the fire-resistance rating.
(g) The type of construction as identified in
				  national fire protection association pamphlet no. 220, entitled "Standard on
				  Types of Building Construction," as adopted in these rules.
(h) The number of stories, including basement
				  and attic areas.
(i) The interior
				  finish classification.
(j) The
				  location of fuel-fired equipment.
(k) The type of furnace and water
				  heater.
(l) Air-handling
				  systems.
(m) Fire detection and
				  alarm system plans and specifications in compliance with the provisions of the
				  act.
(n) Sprinkler or other
				  suppression system plans and specifications in compliance with the provisions
				  of the act.
(o) The type, size, and
				  location of fire extinguishers.
(p)
				  Other pertinent information that is required to determine compliance with these
				  rules.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › New and Existing School, College and University Fire Safety › Part 1 - GENERAL PROVISIONS › Section R. 29.1905 - Inspection during construction; inspection of existing facilities; approval for occupancy

Current through Vol. 24-12, July 15, 2024
Rule 5.
(1) During
				  construction, renovation, modification, reconstruction, addition, or
				  remodeling, the architect, professional engineer, or owner's representative
				  shall notify the bureau of fire services when the building is ready for
				  inspection under both of the following conditions:
(a) When the building is framed and
				  mechanical systems are substantially complete, but before
				  concealment.
(b) Upon completion of
				  construction.