reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30758a - High and low drinking fountains minimum number

Current through Vol. 24-12, July 15, 2024
Rule 758a. Section
						  410.3.1 is added to the code to
						  read as follows:
410.3.1. High and low
						drinking fountains minimum number. Where drinking fountains are required, no
						fewer than 2 drinking fountains shall be provided. One drinking fountain shall
						comply with the requirements for people who use a wheelchair, and 1 drinking
						fountain shall comply with the requirements for standing individuals.
Exceptions:
1.
						A single drinking fountain with 2 separate spouts that complies with the
						requirements for individuals who use a wheelchair and standing individuals
						shall be allowed to be substituted for 2 separate drinking fountains.
2. Where drinking fountains are primarily for
						children's use, the drinking fountains for people using wheelchairs shall be
						allowed to comply with the children's provisions in ICC A117.1 and drinking
						fountains for standing children shall be allowed to have the spout at 30
						inches, 762 mm, minimum above the floor.
3. Referencing building code for all height
						requirements of drinking fountains and water
						coolers.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30758b - Water supply

Current through Vol. 24-12, July 15, 2024
Rule 758b Section
						  411.3 is added to the code to
						  read as follows:
411.3. Water supply.
						Where hot and cold water are supplied to an emergency shower or eyewash
						station, the temperature of the water supply shall only be controlled by
						temperature-actuated mixing value complying with ASSE 1071. Where water is
						supplied directly to an emergency shower or eyewash station from a water
						heater, the water heater shall comply with ASSE 1085, See section
						607.1.2.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30762 - Floor drains; public toilet rooms

Current through Vol. 24-12, July 15, 2024
Rule 762. Section
						  413.5 is added to the code to
						  read as follows:
413.5. Floor drains;
						public toilet rooms. In all public toilet rooms that contain a combination of 3
						or more water closets or urinals, at least 1 approved floor drain shall be
						installed connecting to the sanitary system. However, stall urinals may serve
						as floor drains if the entire floor can be drained to the
						urinals.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30777 - Scope; water service; distance limits; method of installations

Current through Vol. 24-12, July 15, 2024
Rule 777. Section 601.1 of the code is amended to read
						  as follows:
601.1. Scope. The
						provisions of this article shall control the design and installation of water
						supply systems, both hot and cold. Refer to 1976 PA 399, MCL 325.1001 to
						325.1023, for additional requirements on water supply systems pertaining to
						establishments that are subject to regulation or licensure, or both, by the
						department of environmental quality.
Compliance with the provisions of this article,
						  however, does not relieve any person from complying with the additional
						  requirements imposed upon water supply systems pursuant to authority vested in
						  the Michigan department of environmental quality under 1976 PA 399, MCL
						  325.1001 to 325.1023, 1978 PA 368, MCL 333.1101 to 333.25211, and 1987 PA 96,
						  MCL 125.2301 to 125.2350, or other applicable provisions of state
						  law.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30785 - Requirements for discharge piping

Current through Vol. 24-12, July 15, 2024
Rule 785. Section 504.6 of the code is amended to read
						  as follows:
504.6. Requirements for
						discharge piping.
(1) Relief valves shall not
						discharge so as to be a hazard, a potential cause of damage, or a nuisance. A
						relief valve discharge pipe shall be provided for each individual relief valve
						and shall meet all of the following:
(a)
						Shall terminate atmospherically not more than 4 inches (1220 mm) from the floor
						with an unthreaded end.
(b) Shall
						not be interconnected.
(c) Valves
						shall not be connected in the relief valve discharge pipe.
(d) Shall be rigid pipe approved for water
						distribution, with a minimum temperature rating of 210 degrees
						Fahrenheit.
(e) Shall have the same
						nominal inside diameter as the relief valve outlet and shall drain by gravity
						flow.
(f) Shall discharge to the
						floor, to the pan serving the water heater or storage tank, or to a waste
						receptor.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30791 - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 791.
(1)
						Section 202 of the code is amended to amend the definition of code official and
						add the definition of act.
(2)
						"Act" means the Stille-DeRossett-Hale single state construction code act, 1972
						PA 230, MCL 125.1501 to 125.1531.
(3) "Code official" means individual who is
						registered pursuant to article 10 of the skilled trades regulation act, 2016 PA
						407, MCL 339.6001 to 339.6023, and who is authorized to conduct the inspections
						needed to determine compliance with the provisions of this code. Construction
						or work that requires a permit shall be subject to inspection by the code
						official. This construction or work shall remain visible and be accessible for
						inspection purposes until approved.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30792 - Food utensils, dishes, pots and pans sinks

Current through Vol. 24-12, July 15, 2024
Rule 792.
Section 802.1.8 of the code is amended to read as
						  follows:
802.1.8. Food utensils,
						dishes, pots and pans sinks. Sinks used for the washing, rinsing, or sanitizing
						of utensils, dishes, pots, pans, or service ware where used in the preparation,
						serving, or eating of food shall discharge indirectly through an air gap or an
						air break to the drainage system.
Exception: When required, a washing sink or wash
						  compartment shall be directly connected to a hydromechanical grease
						  interceptor. The outlet of a hydromechanical grease interceptor shall directly
						  connect to the sanitary drainage system.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30801 - National electrical code; adoptions by reference; inspection; purchase

Current through Vol. 24-12, July 15, 2024
Rule 801
(1)
					 The standards contained in the national electrical code 2023 second printing
					 edition, including TIA 70-23-1 to 70-23-13, Errata 70-23-1 to 70-23-6, and
					 Annex H, except sections
					 80.2,
					 80.5,
					 80.15,
					 80.23,
					 80.27,
					 80.29,
					 80.31,
					 80.33,
					 80.35, and
					 90.6, as published by the national
					 fire protection association (NFPA), shall govern the installation, replacement,
					 alteration, relocation, and use of electrical systems or material. With the
					 exceptions noted, the national electrical code is adopted in these rules by
					 reference.
(2) All references to
					 the ANSI/ASME A17.1 2016, safety code for elevators and escalators mean the
					 Michigan elevator code and all references to the national electrical code mean
					 the Michigan electrical code.
(3)
					 NFPA 110, standard for emergency and standby power systems, 2019 edition and
					 NFPA 111, standard on stored electrical energy emergency and standby power
					 systems, 2019 edition, are adopted by reference in these rules.
(4) The codes are available for inspection at
					 the Lansing office of the Michigan Department of Licensing and Regulatory
					 Affairs, Bureau of Construction Codes, 611 West Ottawa Street, First Floor
					 Ottawa Building, Lansing, Michigan 48933.
(5) The National Electrical Code, NFPA 110
					 and NFPA 111 may be purchased from the National Fire Protection Association, 1
					 Batterymarch Park, Quincy, Massachusetts 02169, or through the bureau's website
					 at
www.michigan.gov/bcc
, at a cost as
					 of the time of adoption of these rules of $153.00 for the National Electrical
					 Code, $149.00 for the NFPA 110, and $149.00 for the NFPA 111 each,
					 respectively.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30807 - Title

Current through Vol. 24-12, July 15, 2024
Rule 807. Section 80.7 is amended to the code to read as
						follows:
80.7. Title. These rules
					 shall be known as the Michigan electrical code, hereinafter referred to as "the
					 code."
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30808 - Scope

Current through Vol. 24-12, July 15, 2024
Rule 808. Section
						80.1 is amended to read as
						follows:
80.1 Scope. The following
					 are covered:
(1) The inspection of electrical
					 installations as covered by 90.2.
(2) The review of construction plans,
					 drawings, and specifications for electrical systems.
(3) The design, alteration, modification,
					 construction, maintenance, and testing of electrical systems and
					 equipment.
(4) The regulation and
					 control of electrical installations at special events, including, but not
					 limited to, exhibits, trade shows, amusement parks, and other similar special
					 occupancies.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30810 - Authority

Current through Vol. 24-12, July 15, 2024
Rule 810. Section
						80.13 is added to the code to read
						as follows:
80.13. Authority. Where
					 used in this article, the term authority having jurisdiction shall include the
					 electrical inspector or other individuals designated by the governing body.
					 This code shall be administered and enforced by the authority having
					 jurisdiction designated by the governing authority as follows:
(1) Disconnection. When the use of electrical
					 equipment or its installations is found to be dangerous to human life or
					 property, the authority having jurisdiction may have the premises disconnected
					 from its source of electric supply. When this equipment or installation has
					 been condemned or disconnected, a notice shall be placed on the equipment or
					 installation listing the causes for the condemnation, the disconnection, or
					 both, and the penalty for the unlawful use of the equipment or installation.
					 Written notice of this condemnation or disconnection and the causes of it shall
					 be given within 24 hours to the owners, the occupant, or both, of the building,
					 structure, or premises. It is unlawful for an individual to remove this notice,
					 to reconnect the electrical equipment to its source of electric supply, or to
					 use or permit to be used electric power in electrical equipment until the
					 causes for the condemnation or disconnection have been remedied to the
					 satisfaction of the inspection authorities.
(2) Delegate authority. The authority having
					 jurisdiction may delegate to other qualified individuals the powers as
					 necessary for the proper administration and enforcement of this
					 code.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30811 - Duties and powers of code official

Current through Vol. 24-12, July 15, 2024
Rule 811. Section 80. 14 is added to the code to read as
						follows:
80.14. Duties and powers of
					 the code official. The code official is authorized and directed to enforce the
					 provisions of this code. The code official may render interpretations of this
					 code and adopt policies and procedures in order to clarify the application of
					 its provisions. These interpretations, policies, and procedures shall be in
					 compliance with the intent and purpose of this code. These policies and
					 procedures shall not have the effect of waiving requirements specifically
					 provided for in this code.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30815 - Maintenance of existing wiring and equipment

Current through Vol. 24-12, July 15, 2024
Rule 815. Section 80.18 of the code is added to read as
						follows:
80.18. Maintenance of
					 existing wiring and equipment. Every building, structure, or part thereof shall
					 be kept in good electrical repair by the owner.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30819 - Plans and specifications

Current through Vol. 24-12, July 15, 2024
Rule 819. Sections
						80.21,
						80.21.1, and 80.21.2 are added to
						the code to read as follows:
80.21.
					 Plans required. An applicant shall submit a detailed set of plans and
					 specifications with the application for an electrical permit for wiring or
					 alteration to an electrical system if the system requires installation of
					 electrical equipment that has an ampacity of more than 400 amperes, at 1,000
					 volts or less, for the service or feeder and if the calculated floor area in a
					 building is more than 3,500 square feet. The enforcing agency may request plans
					 for projects that include an unusual design. Plans and specifications shall
					 conform to the following:
(a) Lighting
					 layout.
(b) Circuiting.
(c) Switching.
(d) Conductor and raceway sizes.
(e) Wattage schedule.
(f) Service location and riser
					 diagram.
(g) Load calculations and
					 available fault current calculations.
(h) A proposed method of construction that is
					 drawn with symbols of a standard form.
All conductors are assumed to be copper unless otherwise
						stated in the plan. Specifications, when provided, shall also include the
						information listed in this rule. The selection of suitable disconnect and
						overcurrent devices to provide proper coordination and interrupting capacity
						for a wiring system is the responsibility of the designer. The enforcing
						agency, when approving electrical plans, does not assume responsibility for the
						design or for deviations from electrical drawings. The permit holder shall
						ensure that the plans and specifications approved by the enforcing agency, or a
						certified copy of the plans and specifications, where required, are available
						on the jobsite for the use of the enforcing agency.
80.21.1. Plan revisions. Work shall be
					 installed pursuant to the code and approved construction documents, and changes
					 made during construction that are not in compliance with the approved
					 construction documents shall be resubmitted for approval as an amended set of
					 construction documents.
80.21.2.
					 Information on construction documents. Construction documents shall be
					 dimensioned and drawn on suitable material. Electronic media documents may be
					 submitted when approved by the enforcing agency. Construction documents shall
					 be of sufficient clarity to indicate the location, nature, and extent of the
					 work proposed and show in detail that it will conform to the provisions of this
					 code and relevant laws, ordinances, rules, and regulations as determined by the
					 enforcing agency.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30820 - Representative on jobsite

Current through Vol. 24-12, July 15, 2024
Rule 820. Section 80. 20 is added to the code to read as
						follows:
80.20. Representative on
					 jobsite. The enforcing agency reserves the right to require a representative of
					 the permit holder to be on the job when an inspection is made.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30823 - Connection to electricity supply

Current through Vol. 24-12, July 15, 2024
Rule 823. Section
						80.25 is amended to the code to
						read as follows:
80.25. Connection to
					 electricity supply. Connections to the electric supply shall conform to
					 subdivisions (a) and (b).
(a) Supply
					 electricity. Except where work is done under an annual permit and except as
					 otherwise provided in section
					 80.25, it is unlawful for an
					 individual, firm, or corporation to make connection to a supply of electricity
					 or to supply electricity to electrical equipment installation for which a
					 permit is required or that has been disconnected or ordered to be
					 disconnected.
(b) Utility emergency
					 connections. The governing utility may reconnect the electrical service, before
					 approval by the enforcing agency, following emergency repairs performed by an
					 electrical contractor licensed pursuant to article 7 of the skilled trades
					 regulation act, 2016 PA 407, MCL
					 339.5701 to
					 339.5739. The electrical
					 contractor shall secure a permit by the next business day after the work is
					 completed. This requirement is not applicable to new service connections,
					 upgrades, structural fires, or other planned
					 modifications.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30827 - Service equipment

Current through Vol. 24-12, July 15, 2024
Rule 827. Section 80. 26 is added to the code to read as
						follows:
80.26. Service equipment. The
					 enforcing agency shall approve service equipment installed, altered, or
					 repaired before the load side of the meter is energized.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30838 - NFPA code; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 838. Sections
						700.9 and
						701.9 of the code are amended to
						read as follows:
700.9. Installation.
					 Emergency systems shall be installed pursuant to NFPA 110 and NFPA 111, 2019
					 editions, which are adopted by reference in
					 R 408.30801.
701.9. Installation. Legally required standby
					 systems shall be installed pursuant to NFPA 110 and NFPA 111, 2019 editions,
					 which are adopted by reference in
					 R 408.30801.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30870 - NFPA code; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 870 Section
						230.85 is added to the code to
						read as follows:
230.85 Emergency
					 disconnects. For 1- and 2-family dwelling units, an emergency disconnecting
					 means shall be installed.
(A) General.
(1) Location. The disconnecting means shall
					 be installed in a readily accessible outdoor location on or within sight of the
					 dwelling unit.
Exception: Where the requirements of section
						225.41 are met, this section
						shall not apply.
(2) Rating.
					 The disconnecting means shall have a short-circuit current rating equal to or
					 greater than the available fault current.
(3) Grouping. If more than 1 disconnecting
					 means are provided, they shall be grouped.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30871 - Bonding other metal piping

Current through Vol. 24-12, July 15, 2024
Rule 871. Section 250. 104(B) of the code is amended to
						read as follows:
250.104(B). Bonding
					 other metal piping.
(1) Other metal piping. If
					 installed in or attached to a building or structure, a metal piping system,
					 including gas piping, capable of becoming energized shall be bonded to any of
					 the following:
(a) Equipment grounding
					 conductor for the circuit that is likely to energize the piping
					 system.
(b) Service equipment
					 enclosure.
(c) Grounded conductor
					 at the service.
(d) Grounding
					 electrode conductor, if of sufficient size.
(e) One or more grounding electrodes used, if
					 the grounding electrode conductor or bonding jumper to the grounding electrode
					 is of sufficient size.
The bonding conductor or conductors, or the jumper or
						jumpers shall be sized in accordance with table 250.122, and equipment
						grounding conductors shall be sized in accordance with table 250.122 using the
						rating of the circuit that is likely to energize the piping system or systems.
						The points of attachment of the bonding jumper or jumpers shall be
						accessible.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 8 - ELECTRICAL CODE › Section R. 408.30873 - Uses permitted

Current through Vol. 24-12, July 15, 2024
Rule 873. Sections
						334.10 and
						334.12(A) of the
						code are amended to read as follows:
334.10. Uses Permitted. Type NM and type NMC
					 cables may be used in the following, except as prohibited in section
					 334.12:
(1) One- and 2-family dwellings and their
					 attached or detached garages and storage buildings.
(2) Multifamily dwellings and their detached
					 garages.
(3) In other structures
					 exceeding 1 floor above grade, cables shall be concealed within walls, floors,
					 or ceilings that provide a thermal barrier of material that has not less than a
					 15-minute finish rating as identified in listings of fire rated assemblies
					 pursuant to the Michigan building code.
(4) Cable trays in structures permitted to be
					 types III, IV, or V where the cables are identified for the
					 use.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30901a - International mechanical code; adoption by reference

Current through Vol. 24-12, July 15, 2024
Rule 901a.
(1)
						The provisions of the international mechanical code, 2021 edition, except for
						sections 103.1 to
						103.3,
						104.2,
						104.8,
						104.8.1, 106.1.1, 106.1.2, 106.3,
						106.3.2, 106.4.5, 109.1 to 109.6, 112.2.5 to 112.2.5.3, 113.1 to 113.4, 114.1,
						115.3, 116.1 to 116.4, 1101.9, 1102.3, appendix B, and appendix C, govern the
						construction, alteration, relocation, demolition, use, and occupancy of
						buildings and structures. With the exceptions noted, the code is adopted in
						these rules by reference.
(2) All
						references to the International Building Code, International Residential Code,
						International Energy Conservation Code, National Electrical Code, International
						Mechanical Code, and International Plumbing Code mean the Michigan Building
						Code, Michigan Residential Code, Michigan Energy Code, Michigan Electrical
						Code, Michigan Mechanical Code, and Michigan Plumbing Code
						respectively.
(3) ASHRAE 15-2022
						edition: Safety Standard for Refrigeration Systems and ASHRAE 34-2022 edition:
						Designation and Safety Classification of Refrigerants can be purchased at
www.techstreet.com/ashrae
for
						$178.00. UL/CSA 60335-2-40-2022 edition: Household and Similar Electrical
						Appliances-Safety-Part 2-40: Particular Requirements for Electrical Heat Pumps,
						Air Conditioners and Dehumidifiers can be purchased at
www.shopulstandards.com
for
						$521.00. UL/CSA 60335-2-89-2021 edition: Household and Similar Electrical
						Appliances-Safety-Part 2-89: Particular Requirements for Commercial
						Refrigerating Appliances with an incorporated or Remote Refrigerant Unit or
						Compressor can be purchased at
www.shopulstandards.com
for $519.00.
						Inspection of standards are available at the Michigan Department of Licensing
						and Regulatory Affairs, Bureau of Construction Codes, 611 W. Ottawa Street
						First Floor Ottawa Building, Lansing, Michigan 48933, or purchased through the
						bureau's website at
www.michigan.gov/bcc
. Additionally, the
						standards adopted are available for purchase from
www.techstreet.com/ashrae
and
www.shopulstandards.com
.
The cost for purchase of the individual standard is noted in this subrule.
(4) The 2021 Michigan Mechanical
						code is available for inspection and purchase at the Department of Licensing
						and Regulatory Affairs, Bureau of Construction Codes, 611 West Ottawa Street,
						First Floor Ottawa Building, Lansing, Michigan 48933. The code may be purchased
						from the International Code Council, through the bureau of construction code's
						website at
www.michigan.gov/bcc
, at a
						cost as of the time of adoption of these rules of $87.50 for each code
						book.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30904a - Right of entry

Current through Vol. 24-12, July 15, 2024
Rule 904a. Section
						  104.4 of the code is amended to
						  read as follows:
104.4. If a building
						or premises are occupied, the code official shall present credentials to the
						occupant and request entry. If a building or premises is unoccupied, the code
						official shall first make a reasonable effort to locate either the owner, the
						owner's authorized agent, or another person having care or control of the
						building or premises and request entry. If entry is refused, the code official
						has recourse to every remedy provided by law to secure entry. If a code
						official obtains a proper inspection warrant or other remedy provided by law to
						secure entry, the owner, owner's authorized agent or occupant or person having
						charge, care or control of the building or premises shall not fail or neglect,
						after a proper request is made as provided in this rule, to allow the code
						official prompt entry into the building or premises to inspect or examine the
						building or premises pursuant to this code.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30905a - Definitions

Current through Vol. 24-12, July 15, 2024
Rule 905a. The following definitions are added to
						  section 202 as follows:
(a) "Act"
						means the Stille-DeRossett-Hale single state construction code act, 1972 PA
						230, MCL 125.1501 to
						125.1531.
(b) "Cold weather months" means November 1
						through April 1 in Michigan Energy Code climate zone 5A and from October 15
						through May 1 in Michigan Energy Code climate zones 6A and 7.
(c) "Occupiable space" means a room or
						enclosed space designed for regular or non-regular human occupancy in which
						individuals congregate for activities, amusement, educational or similar
						purposes, or in which occupants are engaged at labor, and which is equipped
						with means of egress, heat, light, and ventilation facilities meeting the
						requirements of this code. Occupiable space does not include those spaces that
						are intended primarily for other purposes such as storage rooms and equipment
						rooms.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30906a - Work permit; submitting plans and specifications to authority

Current through Vol. 24-12, July 15, 2024
Rule 906a. Sections
						  106.2,
						  106.3.1 106.4, 106.4.3, 106.4.4
						  of the code are amended to read as follows:
106.2. Permits not required. A person is not
						required to obtain a permit to perform mechanical work on any of the following
						items:
(a) A portable heating or gas appliance
						that has inputs of less than 30,000 Btu's per hour.
(b) Portable ventilation appliances and
						equipment.
(c) A portable cooling
						unit.
(d) Steam, hot water, or
						chilled water piping within any heating or cooling equipment or appliances
						regulated by the code.
(e) Except
						for a heat exchanger, replacement of any manufacturer installed part on a
						listed and labeled appliance or listed and labeled equipment, if the
						replacement does not alter the approval of the appliance or equipment or make
						the appliance or equipment unsafe.
(f) Self-contained refrigeration systems that
						contain 10 pounds or less of refrigerant, or that are actuated by motors of 1.5
						horsepower or less.
(g) Portable
						fuel cell appliances that are not connected to a fixed piping system and are
						not interconnected to a power grid.
(h) An oil burner that does not require
						connection to a flue, such as an oil stove and a heater equipped with a
						wick.
(i) Installing gas piping
						limited to 10 feet in length and not more than 6 fittings when changing or
						relocating a gas meter or regulator.
(j) When installing geothermal vertical
						closed loops under the supervision of a mechanical contractor licensed in HVAC
						as long as the company meets both the following:
(1) Has obtained a certificate of
						registration as a well drilling contractor pursuant to part 127 of the public
						health code,1978 PA 368, MCL
						333.12701 to
						333.12771.
(2) Has installed the geothermal vertical
						closed loops in accordance with the department of environment, Great Lakes, and
						energy's best practices regarding geothermal heat pump closed loops.
Exemption from the permit requirements of this code
						  shall not grant authorization for work to be done in violation of the
						  provisions of this code or other laws or ordinances of this
						  jurisdiction.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30907a - Fees

Current through Vol. 24-12, July 15, 2024
Rule 907a. Section 106.5 of the code is amended to read
						  as follows:
106.5. Fees. The fees
						prescribed by the act shall be paid to the enforcing agency of the jurisdiction
						before a permit to begin work for new construction, alteration, removal,
						demolition, or other building operation may be issued. In addition, an
						amendment to a permit necessitating an additional fee shall not be approved
						until the additional fee is paid.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30909a - Violations

Current through Vol. 24-12, July 15, 2024
Rule 909a. Section 108.4 of the code is amended to read
						  as follows:
108.4 Violation penalties.
						Any person who violates a provision of this code, who fails to conform with any
						of the requirements thereof, or who erects, installs, alters, or repairs
						mechanical work in violation of the approved construction documents or
						directive of the enforcing agency, or a permit or certificate issued under the
						provisions of this code, shall be fined in accordance with the act.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30918 - Violation penalties

Current through Vol. 24-12, July 15, 2024
Rule 918. Section
						  115.4 of the code is amended to
						  read as follows:
115.4 Violation
						penalties. A person that violates a provision of the code, that fails to
						conform with any of the requirements of the code, or that erects, installs,
						alters, or repairs mechanical work in violation of the approved construction
						documents or directive of the enforcing agency, or a permit or certificate
						issued under the provisions of the code is subject to review, which may result
						in licensing action pursuant to the skilled trades regulation act, 2016 PA 407,
						MCL 339.5101 to
						339.6133
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30923a - Equipment installation

Current through Vol. 24-12, July 15, 2024
Rule 923a. Section
						  301.10.1 is added to the code and
						  section 309.1 of the code is amended to
						  read as follows:
301.10.1. Electrical
						disconnect. The mechanical contractor shall ensure that all equipment is
						equipped with an externally accessible electrical disconnect switch on, or
						within 6 feet of, the equipment. The disconnect shall be permanently
						identified.
309.1. Occupiable space
						heating systems. Interior spaces intended for human occupancy shall be provided
						with heating facilities capable of maintaining a minimum interior room
						temperature of 68 degrees Fahrenheit, 20 degrees Celsius, at a point 3 feet,
						914 millimeters, above the floor and 2 feet, 609.6 millimeters, from exterior
						walls at the required design temperature. The installation of portable space
						heaters shall not be used to comply with this section.
Exception:
1.
						Interior spaces where the primary purpose is not associated with human
						comfort.
2. Interior, seasonal
						spaces that are unoccupied during cold weather months, including restrooms,
						shower buildings, day use restrooms, concession stands, press boxes, ticket
						booths and locker rooms.
3. Group
						F, H, S or U occupancies.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30928a - Solid fuel burning equipment

Current through Vol. 24-12, July 15, 2024
Rule 928a. Section
						  901.5 is added to the code to
						  read as follows:
901.5 Solid fuel
						burning equipment. Solid fuel burning equipment shall be listed and labeled in
						accordance with section
						304.1 of the code and installed
						in accordance with the manufacturer's instructions and NFPA 211-2019
						requirements.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30935a - Performance test

Current through Vol. 24-12, July 15, 2024
Rule 935a. Section
						  507.6.1.1 is added to the code to
						  read as follows:
507.6.1.1 Capture and
						containment procedure. The field test identified in section
						507.6.1 of the code shall be
						conducted in accordance with the smoke testing procedures established by the
						bureau of construction codes, which are available at no cost from the bureau of
						construction code's website at
www.michigan.gov/bcc
, or from the Michigan
						Department of Licensing and Regulatory Affairs, Bureau of Construction Codes,
						611 West Ottawa Street, First Floor Ottawa Building, Lansing, Michigan
						48933.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30936a - Scope of article

Current through Vol. 24-12, July 15, 2024
Rule 936a. Section
						  1001.2 is added to the to read
						  as follows:
1001.2. Boilers. In
						addition to the other provisions of the code, this article governs the
						installation, alteration, and repair of water heaters and boilers. The
						installation of boilers shall comply with the provisions of this code and the
						skilled trades regulation act, 2016 PA407, MCL
						339.5101 to
						339.6133.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30945a - Ventilation; exhaust

Current through Vol. 24-12, July 15, 2024
Rule 945a. Sections
						  501.3,
						  504.4, and
						  504.9.2, of the code are amended
						  to read as follows:
501.3 Exhaust
						discharge. The air removed by every mechanical exhaust system shall be
						discharged outdoors at a point where it will not cause a public nuisance and
						not less than the distances specified in section
						501.3.1 of the code. The air
						shall be discharged to a location from which it cannot again be readily drawn
						in by a ventilating system. Air shall not be exhausted into an attic or a crawl
						space, be directed onto walkways, or terminate within 3 feet of a ventilated
						section in a soffit.
Exceptions:
1.
						Whole-house ventilation-type attic fans shall be permitted to discharge into
						the attic space of dwelling units that have private attics.
2. Commercial cooking recirculating
						systems.
3. When installed in
						accordance with the manufacturer's instructions and when mechanical or natural
						ventilation is otherwise provided in accordance with chapter 4 of the code,
						listed and labeled domestic ductless range hoods shall not be required to
						discharge to the outdoors.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30946 - Alterations and repairs

Current through Vol. 24-12, July 15, 2024
Rule 946. Section
						  1001.3 is added to the code to
						  read as follows:
1001.3. Alterations
						and repairs to boilers shall be in accordance with the skilled trades
						regulation act, 2016 PA 407, MCL
						339.5101 to
						339.6133.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30947b - Refrigerants other than ammonia

Current through Vol. 24-12, July 15, 2024
Rule 947b. Section
						  1101.1.1 of the code is amended
						  to read as follows:
1101.1.1
						Refrigerants other than ammonia. Refrigerant piping design and installation for
						systems containing a refrigerant other than ammonia, including pressure vessels
						and pressure relief devices, shall comply with this chapter and ASHRAE 15.
						System using A2L refrigerants shall comply with ASHRAE 15.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30995a - Automatic sprinkler systems generally

Current through Vol. 24-12, July 15, 2024
Rule 995a. Sections
						  1600.0,
						  1600.1, and
						  1600.2 are added to the code to
						  read as follows:
1600.0. Automatic
						sprinkler systems; fire suppression systems.
1600.1 Scope. The provisions of this article
						provide the minimum requirements for the design and installation of automatic
						sprinkler systems in all occupancies, except for 1- and 2-family
						dwellings.
1600.2. Installations.
						Installations shall be in compliance with the provisions of the code. Fire
						suppression systems shall be in compliance with the provisions of the building
						code and shall be installed in accordance with the code and NFPA-13-2019 or
						NFPA-13D-2019 or NFPA-13R-2019, and NFPA-24-2019, and standards of the National
						Fire Protection Association listed in chapter 15.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 9A - MECHANICAL CODE › AMENDMENTS AND ADDITIONS TO BASIC MECHANICAL CODE › Section R. 408.30996 - Process piping

Current through Vol. 24-12, July 15, 2024
Rule 996. Sections
						  1700.0 and
						  1700.1 are added to the code to
						  read as follows:
1700.0. Process
						piping.
1700.1 Scope. The provisions of this
						chapter provide the minimum requirements for the design and installation of
						process piping systems pursuant to ASME B31.3-2022.
1700.2 Process piping. Piping which is not
						part of a refrigeration system or part of a system designed to provide air
						conditioning. Process piping includes pipes which transfer chemicals and other
						fluids, gases, or vapors for systems other than air conditioning systems as
						covered by the Michigan mechanical code.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 10 - MICHIGAN UNIFORM ENERGY CODE › Section R. 408.31059 - Applicable code

Current through Vol. 24-12, July 15, 2024
Rule 1059. The residential provisions of the
						international energy conservation code, 2015 edition, except for sections
						R107.2 to R107.5, R301.2, R301.3, R402.3.2, and Table R303.1.3(3), govern the
						energy efficiency for the design and construction of residential buildings and,
						with exceptions noted, the international energy conservation code is adopted by
						reference in these rules. All references to the international building code,
						international residential code, international energy conservation code,
						international electrical code, international existing building code,
						international mechanical code, and international plumbing code mean the
						Michigan building code, Michigan residential code, Michigan energy code,
						Michigan electrical code, Michigan rehabilitation code for existing buildings,
						Michigan mechanical code, and Michigan plumbing code respectively. The Michigan
						energy code is available for inspection or purchase at the Okemos office of the
						Michigan Department of Licensing and Regulatory Affairs, Bureau of Construction
						Codes, 2501 Woodlake Circle, Okemos, Michigan 48864, at a cost as of the time
						of adoption of these rules of $44.00 or may be purchased from the International
						Code Council, 500 New Jersey Avenue, N.W., 6th
						Floor, Washington, D.C. 20001.