reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-20.1 - "Hydrostatic leak test" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 20.1.
"Hydrostatic leak test" means a test performed by filling a
				  boiler or unfired pressure vessel with water or other incompressible liquid and
				  pressurizing the vessel to a predetermined pressure. This method of testing is
				  used to detect leaks and to determine the overall integrity of the vessel,
				  especially after a repair or alteration has been performed.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-21 - "Inspection agency" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6-4
Sec. 21.
"Inspection agency" means an authorized inspection agency
				  described in IC 22-15-6-4.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-21 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-21 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-22

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-22 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-22 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-23 - "Inspector" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-2
Sec. 23.
"Inspector" means any inspector who holds an Indiana boiler
				  and pressure vessel inspector's license issued under IC 22-15-6-5.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-23 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-23 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-24

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-24 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-24 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-25 - "Inspector's license" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6-5
Sec. 25.
"Inspector's license" means the license issued as set forth
				  in IC 22-15-6-5.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-25 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-25 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-25.1 - "Instant-on water heater" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 25.1.
"Instant-on water heater" (also known as a tankless water
				  heater or instantaneous water heater) means a water heater in which water is
				  heated by direct flame or passes over or through a heating coil or element to
				  produce rapid heating of potable water that does not exceed any of the
				  following limits:
(1) Two hundred
				thousand (200,000) Btu per hour (or fifty-seven (57) kW) heat input.
(2) One hundred sixty (160) psig
				MAWP.
(3) Two hundred ten (210)
				degrees Fahrenheit outlet water temperature.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-26 - "Internal inspection" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6-5
Sec. 26.
"Internal inspection" means an inspection in accordance with
				  Part 2 of the NBIC or API 510 that includes the examination of the interior
				  surface of pressure parts of a boiler or unfired pressure vessel.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-26 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-26 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-27 - "Low pressure heating boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 27.
"Low pressure heating boiler" means a boiler that does not
				  exceed any of the following limits:
(1) Fifteen (15) psig MAWP for steam.
(2) One hundred sixty (160) psig
				MAWP and two hundred fifty (250) degrees Fahrenheit outlet temperature for
				water.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-27 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-27 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-28

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-28 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-28 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-28.1 - "MAWP" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 28.1.
"MAWP" means maximum allowable working pressure designated
				  by the manufacturer.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-29 - "Miniature boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 29.
"Miniature boiler" means any boiler that does not exceed any
				  of the following limits:
(1) Sixteen
				(16) inches inside diameter of shell.
(2) Five (5) cubic feet gross volume
				(exclusive of casing and insulation).
(3) Twenty (20) square feet of heating
				surface.
(4) One hundred (100) psig
				MAWP.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-29 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-29 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-30 - "Model boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 30.
"Model boiler" means any boiler that does not exceed any of
				  the following limits:
(1) Two (2)
				cubic feet total gross volume (exclusive of casing and insulation).
(2) One and one-half (11/2) square feet of
				grate area.
(3) One hundred (100)
				psig MAWP.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-30 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-30 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-30.1 - "Modular boiler" defined

Current through July 10, 2024
Sec. 30.1.
"Modular boiler" means a packaged boiler system normally
				  consisting of a series of three (3) or more packaged boilers that operate in a
				  parallel or series to provide a varying supply of steam.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-31 - "National Board" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 31.
"National Board" means the National Board of Boiler and
				  Pressure Vessel Inspectors.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-31 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-31 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-31.1 - "National Board Commission" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 31.1.
"National Board Commission" means the license issued to an
				  inspector by the NBBI.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-31.2 - "NBBI" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 31.2.
"NBBI" means the National Board of Boiler and Pressure
				  Vessel Inspectors.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-32 - "NBIC" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 32.
"NBIC" means the National Board Inspection Code as set forth
				  in 680 IAC 2-1-1(a)(3)675 IAC
				  30-1-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-32 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-32 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-33 - "New installation" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 33.
"New installation" means any boiler or unfired pressure
				  vessel installed and placed in operation after July 1, 1953, which was the
				  effective date of the Indiana Boiler and Pressure Vessel Law and that was the
				  first statewide requirement for boilers and unfired pressure vessels to be
				  constructed, installed, inspected, and repaired to a standard.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-33 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-33 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-34 - "Nonstandard boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 34.
"Nonstandard boiler" means a boiler that does not bear an
				  API-ASME or ASME B&PVC certification mark.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-34 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-34 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-34.1 - "Nonstandard unfired pressure vessel" defined

Current through July 10, 2024
Sec. 34.1.
"Nonstandard unfired pressure vessel" means an unfired
				  pressure vessel that does not bear an API-ASME or ASME B&PVC certification
				  mark.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-35 - "Operating permit" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6-2
Sec. 35. "Operating permit" means the permit required to
				  operate a boiler or unfired pressure vessel as set forth in IC 22-15-6-2.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-35 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-35 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-35.1 - "Operating permit inspection" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6-2
Sec. 35.1.
"Operating permit inspection" means an inspection of a
				  boiler or unfired pressure vessel conducted pursuant to the requirements in
				  Part 2 of the NBIC or API 510, the report that is required to be submitted to
				  qualify for an operating permit.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-36 - "Owner or user" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 36.
"Owner or user" means any person, as defined in IC
				  22-12-1-18, owning or operating any boiler or unfired pressure vessel within
				  the state of Indiana.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-36 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-36 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-37

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-4-37 ) to the Fire Prevention and Building
					 Safety Commission ( 675 IAC 30-4-37 ) by P.L. 249-2019, SECTION 15, effective
					 July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-37.1 - "Person" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-1-18; IC 22-15-6-5
Sec. 37.1.
"Person" has the meaning set forth in IC 22-12-1-18.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-38 - "Place of public assembly" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 38.
"Place of public assembly" means a location:
(1) at which persons assemble for civic,
				educational, religious, social, or recreational purposes;
(2) that is provided by a common carrier for
				passengers awaiting transportation; or
(3) in which persons are:
(A) housed to receive medical, charitable, or
				other care or treatment; or
(B)
				held or detained for public, civic, or correctional purposes.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-38.1 - "Pool/spa heater" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 38.1.
"Pool/spa heater" means a heater used to heat water for use
				  in pools or spas that:
(1) has no
				intervening valves on the return or discharge piping, has no reduction in size
				in the return or discharge, and does not generate more than circulating pump
				pressure;
(2) does not exceed two
				hundred thousand (200,000) Btu per hour heat input; and
(3) does not exceed two hundred ten (210)
				degrees Fahrenheit outlet water temperature.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-38.2 - "Portable boiler" defined

Current through July 10, 2024
Sec. 38.2.
"Portable boiler" means a boiler that is primarily intended
				  for temporary location, and its construction and usage allow it to be readily
				  moved from one (1) location to another.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-39 - "Power boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 39
"Power boiler" means a boiler in which steam or other vapor
				  is generated at an internal pressure greater than fifteen (15) psig for use
				  external to itself and that exceeds the limits of a a miniature boiler, a low
				  pressure heating boiler, a hot water supply boiler, a steam cleaner, or a model
				  boiler, as defined in this rule. The term shall include heat recovery steam
				  generators (HRSG boilers).
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-39 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-39 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-40 - "Psi" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 40.
"Psi" means pounds per square inch.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-40 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-40 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-41 - "Psig" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 41.
"Psig" means pounds per square inch gage.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-41 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-41 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-42 - "Reinstalled boiler or unfired pressure vessel" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 42.
"Reinstalled boiler or unfired pressure vessel" means a
				  boiler or unfired pressure vessel removed from its original setting and erected
				  at the same location, or erected at a new location without change of ownership.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-4-42 ) to the Fire Prevention and Building
					 Safety Commission ( 675 IAC 30-4-42 ) by P.L. 249-2019, SECTION 15, effective
					 July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-42.1 - "Repair" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 42.1.
"Repair" means the work necessary to restore a
				  pressure-retaining item to a safe and satisfactory operating condition in
				  accordance with Part 3 of the NBIC.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-43

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-43 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-43 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-44 - "Secondhand boiler or unfired pressure vessel" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 44.
"Secondhand boiler or unfired pressure vessel" means a boiler
				  or unfired pressure vessel of which both the location and ownership have been
				  changed.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680
					 IAC 2-4-44 ) to the Fire Prevention and Building
					 Safety Commission ( 675 IAC 30-4-44 ) by P.L. 249-2019, SECTION 15, effective
					 July 1, 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-45 - "Service water heater" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 45.
"Service water heater" means a water heater that exceeds any
				  of the limits for domestic water heaters as defined in section 15 of this rule,
				  but does not exceed any of the following limits:
(1) One hundred twenty (120) gallons nominal
				water containing capacity.
(2) Two
				hundred thousand (200,000) Btu per hour heat input.
(3) One hundred sixty (160) psig
				MAWP.
(4) Two hundred ten degrees
				(210) Fahrenheit outlet water temperature.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-45 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-45 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-46

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-46 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-46 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-47 - "Standard boiler or unfired pressure vessel" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 47.
"Standard boiler or unfired pressure vessel" means a boiler
				  or unfired pressure vessel that bears the ASME B&PVC certification
				  mark.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-47 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-47 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-48

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-4-48 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-4-48 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-48.1 - "State registration number" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 48.1.
"State registration number" means a number assigned to a
				  boiler or unfired pressure vessel by an inspector upon completion of the first
				  operating permit inspection, thereby registering the item with the
				  state.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-49 - "Steam cleaner" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 49.
"Steam cleaner" means a hot water boiler typically used for
				  cleaning purposes, without any steam space, from which water flashes into steam
				  when released through a manually operated nozzle that does not exceed any of
				  the following limits:
(1)
				Three-fourths (3/4) inch diameter tube or pipe size.
(2) Tube or pipe are not attached to a drum
				or header.
(3) Nominal water
				containing capacity of six (6) gallons.
(4) Water temperature of three hundred fifty
				(350) degrees Fahrenheit.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-49 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-49 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-49.1 - "Steam kettle" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 49.1.
"Steam kettle" means a vessel (open or closed) having an
				  external jacket containing steam used to provide uniform heating of the
				  kettle's contents.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-49.2 - "Thermal fluid heater" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 49.2.
"Thermal fluid heater" (also known as a hot oil heater or
				  hot oil furnace) means a closed vessel in which a heat transfer other than
				  water is heated by the direct application of heat from a thermal energy source,
				  but no vaporization takes places within the vessel.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-50 - "Unfired pressure vessel" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 50.
"Unfired pressure vessel" means a closed vessel in which
				  internal pressure is generated from an external source or from an indirect
				  application of heat. An unfired pressure vessel may contain more than one (1)
				  pressure retaining chamber (for example, a heat exchanger or jacketed
				  vessel).
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-4-50 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-4-50 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-50.1 - "Vessel" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 50.1.
"Vessel" means a generic term that refers to any boiler or
				  unfired pressure vessel.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-51 - "Waste heat boiler" defined

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 51.
(a) "Waste
				heat boiler" means a closed vessel that is intended to be operated under
				pressure for the purpose of heating water or generating steam for external use
				by the application of heat.
(b) The
				configuration of the unit shall govern the sections of this article applicable
				to its design, construction, fabrication, and inspection as follows:
(1) If the unit contains tubes, drums, and
				accessories commonly associated with boilers, the sections applicable to power
				boilers shall apply.
(2) If the
				unit contains a shell, tube bundle, and channel commonly associated with heat
				exchangers, the sections applicable to unfired pressure vessels shall apply.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 4 - Definitions › Section 4-52 - "Water softener" defined

Current through July 10, 2024
Sec. 52.
"Water softener" means a vessel used to reduce the
				  concentrations of certain minerals (primarily calcium and magnesium) that
				  produces either water or a product that is not materially more hazardous than
				  water, where the temperature of the vessel's contents does not exceed one
				  hundred eighty (180) degrees Fahrenheit.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-1 - Inspections

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-12-7; IC 22-15-6-1
Sec. 1.
(a) All
				boilers and unfired pressure vessels not exempted by 675 IAC30-1-2 or
				675 IAC 30-1-5 shall
				be inspected at intervals as specified in
				675 IAC
				30-3-9.
(b) In making inspections of boilers and
				unfired pressure vessels, inspectors may use either:
(1) the codes in effect at the time of
				manufacture, repair, or installation of the unit; or
(2) the codes adopted in
				675 IAC
				30-1-1, if not more stringent.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-2 - Preparation for inspection

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 2.
(a) The
				owner or user of a boiler or unfired pressure vessel required to be inspected
				shall prepare the boiler or vessel for the proposed inspection at an agreed
				upon time established by the inspector and the owner or user.
(b) For internal inspection of boilers and
				unfired pressure vessels, the inspector shall specify the nature and extent of
				preparatory work expected to be completed prior to the inspector's arrival,
				which shall include, but is not limited to, the following, as applicable for
				the equipment design:
(1) Isolating the
				boiler or unfired pressure vessel from its source of pressure.
(2) Isolating and securing the fuel
				source.
(3) Draining liquid that is
				present.
(4) Venting and purging
				the boiler or unfired pressure vessel of toxic, explosive, or other harmful
				gases or vapors.
(5) Cooling and
				thoroughly cleaning the interior of the boiler or unfired pressure vessel and
				its surroundings.
(6) Providing
				safeguards to prevent leakage or accidental inflow of steam, hot water, or
				other harmful substances into the boiler or unfired pressure vessel.
(7) Removing manhole plates, handhole plates,
				and other inspection opening closures, wash-out plugs, and plugs in water
				column connections.
(8)
				Establishing means of access to the surfaces to be inspected where these do not
				already exist.
(9) Removing
				internal fittings and appurtenances, where applicable.
(10) Removing the grates, in the case of an
				internally fired boiler.
(11)
				Removing insulation material, masonry, or other parts so that an inspection can
				be made.
If a boiler or unfired pressure vessel has not been properly
				  prepared for internal inspection, the inspector may decline to perform the
				  inspection and the operating permit will be withheld until the owner or user
				  complies with the requirements.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-3

Current through July 10, 2024
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC
					 2-5-3 ) to the Fire Prevention and Building Safety
					 Commission ( 675 IAC 30-5-3 ) by P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-4 - Lap seam cracks

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 4.
The shell or drum of a boiler or unfired pressure vessel in
				  which a lap seam crack is discovered along a longitudinal riveted joint shall
				  be immediately discontinued from use.
Transferred from the Boiler and Pressure Vessel Rules Board
					 (
					 680 IAC 2-5-4 )
					 to the Fire Prevention and Building Safety Commission ( 675 IAC 30-5-4 ) by
					 P.L. 249-2019, SECTION 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-5 - Hydrostatic leak tests; alternative tests

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 5.
(a) The
				pressure of a hydrostatic leak test, when performed on a boiler or unfired
				pressure vessel of riveted or welded construction, except a locomotive boiler,
				shall not exceed the original hydrostatic test pressure. The pressure of a
				hydrostatic leak test performed on a locomotive boiler shall not exceed one and
				one-fourth (1 1/4) times the MAWP. During the hydrostatic leak test, the safety
				valve or valves shall be removed, or each valve disk shall be held down by
				means of a testing clamp and not by applying additional load to the spring with
				the compression screw. The minimum water temperature used to perform a
				hydrostatic leak test shall meet the requirements of the applicable
				construction or repair code; however, the maximum water temperature shall not
				exceed one hundred twenty (120) degrees Fahrenheit.
(b) If the inspector and the owner or user so
				agree, other examinations or tests in accordance with the ASME B&PVC or
				Part 3 of the NBIC may be substituted for the leak test required by this
				section.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-5 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-5 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-6 - Safety appliances; removal or alteration

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 6.
(a) No
				person, except under the direction of an inspector, shall remove, or alter, any
				safety appliance prescribed by this article while a boiler or unfired pressure
				vessel is in operation, except for the purpose of making emergency
				repairs.
(b) If a safety appliance
				is repaired during an outage of a boiler or unfired pressure vessel, it must be
				reinstalled in accordance with the provisions of this article.
(c) The resetting of a safety appliance at a
				new pressure shall be done only with the approval of an inspector.
(d) No person shall in any manner load a
				safety valve to maintain a working pressure in excess of the MAWP of the boiler
				or unfired pressure vessel.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-6 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-6 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-7 - Low water fuel cut-off devices

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 7.
(a) All
				automatically-fired steam or vapor boilers, excepting boilers having a constant
				attendant who has no other duties while the boiler is in operation, shall be
				equipped with an automatic low water fuel cut-off device so constructed that
				the water inlet valve cannot feed water into the boiler through the float
				chamber, and located to automatically cut off the fuel supply when the surface
				of the water falls to the lowest safe water line. This point may not be lower
				than the bottom of the water gauge glass.
(b) Such a fuel cut-off device may be
				attached directly to a boiler or to the tapped openings provided for attaching
				a water gauge glass directly to a boiler, provided that such connections from
				the boiler are nonferrous tees or Ys not less than one-half (1/2) inch pipe
				size between the boiler and the water gauge glass. The water gauge glass shall
				be attached as close as possible to the boiler. The ends of all nipples shall
				be reamed to full size.
(c) Designs
				embodying a float bowl shall have a vertical straight-a-way valved drain pipe
				at the lowest point in the water equalizing pipe connections by which the bowl
				and the equalizing pipe can be flushed and the device tested.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-7 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-7 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-8 - Blow-off tanks; outlets and discharges

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 8.
(a) Blow-off
				piping from a power boiler or a miniature boiler shall not discharge directly
				into a sewer.
(b) A blow-off tank
				shall be used where conditions do not provide an adequate and safe open
				discharge. A blow-off tank and associated piping shall meet the following
				requirements:
(1) The cross-sectional area of
				the outlet from the blow-off tank shall be twice the cross-sectional area of
				the inlet pipe and made to extend internally within eight (8) inches from the
				bottom of the tank.
(2) The vent
				pipe shall have a cross-sectional area at least four (4) times the
				cross-sectional area of the inlet pipe, or the blow-off tank shall meet one (1)
				of the following requirements:
(A) It shall
				be constructed for a pressure equal to that allowed on the boiler to which it
				is attached.
(B) It shall be
				equipped with a safety valve or valves of sufficient capacity to prevent the
				pressure from exceeding the safe working pressure of the tank.
(3) There shall be no valve or
				other possible obstructions, such as water pockets, between the tank and the
				discharge end of the vent pipe.
(4)
				All pipe connections between the tanks and the boiler shall be as direct as
				possible and shall conform to the ASME B&PVC.
(5) A manhole or an access opening shall be
				provided.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-9 - Location of discharge piping outlets

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 9.
The discharge of a safety valve, a blow-off pipe, or any
				  other discharge piping outlet shall be adequately supported and located to
				  prevent injury to personnel.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-9 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-9 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-10 - Pressure reducing valves; relief or safety valves; hand-controlled bypasses

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 10.
(a) Where
				pressure reducing valves are used, one (1) or more relief or safety valves
				shall be provided on the low pressure side of the pressure reducing valve in
				case the boiler or unfired pressure vessel on the low pressure side does not
				meet the pressure requirements for the high pressure side. The combined
				discharge capacity of the relief or safety valves shall be such that the
				pressure rating of the boilers or unfired pressure vessels shall not be
				exceeded in case the pressure reducing valve sticks open. The relief or safety
				valves shall be located adjacent to or as close as possible to the pressure
				reducing valves. Protection shall be provided to prevent injury or damage
				caused by the escaping fluid from the discharge of the relief or safety valves
				if vented to the atmosphere.
(b)
				The use of hand-controlled bypasses around pressure reducing valves is
				permissible. Such a bypass shall not be greater in capacity than the pressure
				reducing valve unless the boiler or unfired pressure vessel downstream
				therefrom is adequately protected by relief or safety valves or meets the
				requirements of the high pressure system. A pressure gauge shall be installed
				on the low pressure side of such a pressure reducing valve.
All pressure relief valves covered by this article must be
				  repaired by an organization in possession of a valid "VR" or "VR/NR"
				  Certificate of Authorization issued by the NBBI.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-10 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-10 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-11 - Repairs or alterations to boilers and pressure vessels

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-13-2-11; IC 22-15-6
Sec. 11.
(a) This
				section covers rules for repairs and alterations to boilers and unfired
				pressure vessels. Where applicable rules for a repair or alteration are not
				provided by this rule, details of design and construction shall be consistent
				with the rules in the ASME B&PVC, or the rules for repairs contained in
				Part 3 of the NBIC, the API 510, or the code to which the item was originally
				constructed.
(b) Each boiler and
				unfired pressure vessel covered by this article must be repaired by an
				organization in possession of a valid "R" or "NR" Certificate of Authorization
				issued by the NBBI. The following are clarifications for repairs:
(1) Repairs may be categorized as repairs or
				routine repairs as defined in Part 3 of the NBIC.
(2) Rerolled replacement tubes shall be
				considered a repair and shall be performed in accordance with Part 3 of the
				NBIC.
(3) Rerolling an existing
				tube is not considered a repair.
(4) Seal welding or explosive welding of tube
				plugs shall be considered a repair and shall be performed in accordance with
				Part 3 of the NBIC.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-12 - Shop inspections; fees

Current through July 10, 2024
Authority: IC 22-12-2-8; IC 22-15-6-2
Affected: IC 22-15-6
Sec. 12.
If performed by request, a fee for an inspection made by a
				  state inspector may be charged in accordance with the operating permit
				  inspection fees listed in
				  675
				  IAC 12-3-13, regardless of whether the inspection is
				  being performed for purposes of obtaining an operating permit.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-12 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-12 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-13 - Masonry or structural supports

Current through July 10, 2024
Authority: IC 22-12-2-8
Affected: IC 22-15-6
Sec. 13.
Each boiler or unfired pressure vessel shall be supported by
				  masonry or structural supports of sufficient strength and rigidity to safely
				  support the equipment. There shall be no excessive vibration in either the
				  boiler or unfired pressure vessel or its connecting piping.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-13 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-13 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-14 - Service water heaters; exceptions; relief valves

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 14.
A service water heater, as defined in
				  675 IAC
				  30-4-45, need not be a code vessel; however, it shall
				  be provided with a properly sized ASME temperature and pressure relief valve.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-14 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-14 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 30 - INDIANA BOILER AND PRESSURE VESSEL RULES › Rule 5 - General Requirements › Section 5-15 - Conditions not covered by this rule

Current through July 10, 2024
Authority: IC 22-13-2-8
Affected: IC 22-15-6
Sec. 15.
Any condition not covered by this rule shall comply with the
				  applicable provisions of the codes adopted in
				  675 IAC
				  30-1-1.
Transferred from the Boiler and Pressure Vessel Rules Board
					 ( 680 IAC 2-5-15 ) to the Fire Prevention and Building Safety Commission ( 675
					 IAC 30-5-15 ) by P.L. 249-2019,
					 SECTION
					 15, effective July 1,
					 2019.