reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-80 - Section R802.1.1; sawn lumber

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 80.
Change the text of SECTION R802.1.1 to read as
				  follows:
Sawn lumber shall be identified by a grade mark of an
				  accredited lumber grading or inspection agency and have design values certified
				  by an accreditation body that complies with DOC PS 20.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-81 - Section R802.10.1; truss design drawings

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 81.
Change the text of the first sentence of SECTION R802.10.1
				  to read as follows:
Truss design drawings shall be provided to the building
				  official as required by the General Administrative Rules (675 IAC 12) for Class
				  1 structures or by local ordinance for Class 2 structures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-82 - Section R803.2.1; identification and grade

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 82.
Delete the words "or certificate of inspection issued by an
				  approved agency" from the text of SECTION R803.2.1 without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-83 - Section R806.1; ventilation required

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 83.
Add an EXCEPTION to SECTION R806.1 to read as
				  follows:
EXCEPTION: Mechanical ventilation is permitted provided the
				  following conditions are met:
1. The
				installation complies with manufacturer's instructions.
2. A humidistat is included with the
				installation.
3. An ammeter or
				equivalent device is installed in a readily visible location.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-84 - Section R902.4 rooftop-mounted photovoltaic panel systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 84.
Delete the text of the last sentence of SECTION R902.4
				  without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-85 - Section R905.2.6; attachment

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 85.
Delete the words "approved" from the text of SECTION
				  R905.2.6 without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-86 - Section R905.2.8; flashing

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 86.
Delete the word "approved" from the text of SECTION R905.2.8
				  without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-87 - Section R905.2.8.4; other flashing

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 87.
Delete the word "printed" from the text of SECTION
				  R905.2.8.4 without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-88 - Figure R1003.9; termination

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 88.
Add FIGURE R1003.9 after SECTION R1003.9 as follows:
FIGURE R1003.9 TERMINATION
Click here to view
				  Image
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-89 - Section N1101.5; construction documents

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 89.
Delete SECTION N1101.5 and SECTION N1101.5.1 and substitute
				  to read as follows:
SECTION N1101.5 CONSTRUCTION DOCUMENTS.
Energy conservation construction documents shall be submitted
				  for Class 1 structures as required by the General Administrative Rules ( 675
				  IAC 12-6 ) and for Class 2 structures as required by local
				  ordinance.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-90 - Section N1101.6; defined terms

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 90.
Change SECTION N1101.6 as follows:
(1) Change the definition of HEATED SLAB in
				SECTION N1101.6 to read as follows:
HEATED SLAB. Slab-on-grade construction in which the heating
				  elements, hydronic tubing, or hot air distribution system is in contact with,
				  or placed within the slab.
(2) Change the definition of RESIDENTIAL
				BUILDING in SECTION N1101.6 to read as follows:
RESIDENTIAL BUILDING. For this chapter, includes detached one
				  and two family dwellings, townhouses, applicable Class 1 structures, and their
				  accessory structures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-91 - Table N1102.1.2; insulation and fenestration requirements by component [a]

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 91.
Delete TABLE N1102.1.2 and substitute to read as
				  follows:
TABLE N1102.1.2 INSULATION AND FENESTRATION REQUIREMENTS BY
				  COMPONENTa
CLIMATE ZONE
FENESTRATION U-FACTOR
SKYLIGHT U-FACTORb
CEILING R-VALUE
WOOD FRAME RVALUE
MASS WALL R-VALUEg
FLOOR RVALUE
BASEMENT WALL R-VALUEc
SLAB RVALUE AND DEPTHd
CRAWL SPACE RVALUE
4
0.35
0.60
38
15
5/10
19
10/13
10; 2 feet
10/13
5
0.35
0.60
38
20 or 13+5f
13/17
30e
10/13
10; 2 feet
10/13
a. R-values are
				minimums. U-factors are maximums. Batts compressed into a framing cavity such
				that the R-value is reduced by R-1 or more shall be marked with the compressed
				batt R-value in addition to the full thickness R-value.
b. The fenestration U-factor column excludes
				skylights.
c. The first R-value
				applies to continuous insulation, the second to framing cavity insulation;
				either insulation meets the requirement.
d. Minimum of R-5 shall be provided under the
				full slab area of heated slabs in addition to the required slab edge insulation
				R-value for slab as indicated in the table. The slab edge insulation for heated
				slabs shall not be required to extend below the slab.
e. R-30 or insulation sufficient to fill the
				framing cavity, R-19 minimum.
f."13+5" means R-13 cavity insulation with an
				additional R-5 insulated sheathing applied to the exterior of the wall. If
				structural sheathing covers 25% or less of the exterior, R-5 sheathing is not
				required where structural sheathing is used. If structural sheathing covers
				more than 25% of exterior, structural sheathing shall be supplemented with
				insulated sheathing of at least R-2.
g. The second R-value applies when more than
				half the insulation is on the interior.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-92 - Table N1102.1.4; equivalent U-factors [a]

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 92.
Delete TABLE N1102.1.4 and substitute to read as
				  follows:
TABLE N1102.1.4 EQUIVALENT
				  U-FACTORSa
CLIMATE ZONE
FENESTRATION U-FACTOR
SKYLIGHT U-FACTOR
CEILING U-FACTOR
FRAME WALL U-FACTOR
MASS WALL U-FACTORb
FLOOR U-FACTOR
BASEMENT WALL U-FACTOR
CRAWL SPACE WALL U-FACTOR
4
0.35
0.60
0.030
0.082
0.141
0.047
0.059
0.065
5
0.35
0.60
0.030
0.067
0.082
0.033
0.059
0.065
a.Non-fenestration U-factors shall be
				obtained from measurement, calculation, or an approved source.
b. When more than half the insulation is on
				the interior, the mass wall U-factors shall be a maximum of 0.10 in zone 4 and
				the same as the frame wall U-factor (0.057) in zone 5.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-93 - Table N1102.2.6; steel frame ceiling, wall and floor insulation R-values

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 93.
Delete TABLE N1102.2.6 and substitute to read as
				  follows:
TABLE N1102.2.6
STEEL FRAME CEILING, WALL AND FLOOR INSULATION
				  R-VALUES
WOOD FRAME R-VALUE REQUIREMENTS
COLD-FORMED STEEL EQUIVALENT
							 R-VALUEa
Steel Truss
							 Ceilings
a
R-30
R-38 or R-30 + 3 or R-26 + 5
R-38
R-49 or R-38 + 3
R-49
R-38 + 5
Steel Joist
							 Ceilingsb
R-30
R-38 in 2 x 4 or 2 x 6 or 2 x 8; R-49 in any framing
R-38
R-49 in 2 x 4 or 2 x 6 or 2 x 8 or 2 x 10
Steel Framed Wall
R-13
R-13 + 5 or R-15 + 4 or R-21 + 3 or R-0 + 10
R-15
R-11 + 5 or R-13 + 4 or R-21 + 3 or R-0 + 15
R-19
R-13 + 9 or R-19 + 8 or R-25 + 7
R-21
R-13 +10 or R-19 + 9 or R-25 + 8
Steel Joist Floor
R-13
R-19 in 2 x 6 or R-19 + R-6 in 2 x 8 or 2 x 10
R-19
R-19 + R-6 in 2 x 6 or R-19 + R-12 in 2 x 8 or 2 x 10
For SI: 1 inch= 25.4 mm.
a. Cavity insulation R-value is listed first,
				followed by continuous insulation R-value.
b. Insulation exceeding the height of the
				framing shall cover the framing.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-94 - Section N1102.4.1.1; installation

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 94.
Delete the text of the last sentence of SECTION N1102.4.1.1
				  without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-95 - Section N1102.4.1.2; verification

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 95.
Change the title and text of SECTION N1102.4.1.2 to read as
				  follows: SECTION N1102.4.1.2 VERIFICATION.
The building or dwelling unit shall be visually inspected for
				  verification of compliance with TABLE N1102.4.1.1, or tested and verified as
				  having an air leakage rate of not exceeding five air changes per hour. Testing
				  shall be conducted in accordance with RESNET/ICC 380, ASTM E779, or ASTM E1827
				  and reported at a pressure of 0.2 inch w.g. (50 Pascals). Where required by the
				  building official, testing shall be conducted by an approved third party. A
				  written report of the results of the test shall be signed by the party
				  conducting the test and provided to the building official. Testing shall be
				  performed at any time after creation of all penetrations of the building
				  thermal envelope. During testing:
1.Exterior windows and doors, fireplace
				doors, and stove doors shall be closed, but not sealed, beyond the intended
				weatherstripping or other infiltration control measures.
2. Dampers including exhaust, intake, makeup
				air, backdraft, and flue dampers shall be closed, but not sealed beyond
				intended infiltration control measures.
3. Interior doors, where installed at the
				time of the test, shall be open.
4.Exterior or interior terminations for
				continuous ventilation systems shall be sealed.
5. Heating and cooling systems, where
				installed at the time of the test, shall be turned off.
6. Supply and return registers, where
				installed at the time of the test, shall be fully open.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-96 - Section N1103.3.1; insulation (prescriptive)

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 96.
Change the text of SECTION N1103.3.1 to read as
				  follows:
Supply and return ducts in attics shall be insulated to an
				  R-value of not less than R-8 for ducts 3 inches (76 mm) in diameter and larger
				  and not less than R-6 for ducts smaller than 3 inches (76 mm) in diameter.
				  Supply and return ducts in other portions of the building shall be insulated to
				  not less than R-6 for ducts 3 inches (76 mm) in diameter and larger and to not
				  less than R-4.2 for ducts smaller than 3 inches (76 mm) in diameter.
EXCEPTION: Ducts or portions thereof located completely
				  inside the building thermal envelope.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-97 - Section N1103.3.3; duct testing (mandatory)

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 97.
Change the text of SECTION N1103.3.3 to read as
				  follows:
Ducts shall be pressure tested to determine air leakage by
				  one of the following methods:
1.Rough-in test: Total leakage shall be
				measured with a pressure differential of 0.1 inch w.g. (25 Pa) across the
				system, including the manufacturer's air handler enclosure if installed at the
				time of the test. Registers shall be taped or otherwise sealed during the
				test.
2. Postconstruction test:
				Leakage to outside shall be measured with a pressure differential of 0.1 inch
				w.g. (25 Pa) across the entire system, including the manufacturer's air handler
				enclosure. Registers shall be taped or otherwise sealed during the
				test.
EXCEPTIONS:
1. A
				duct air-leakage test shall not be required where the ducts and air handlers
				are located entirely within the building thermal envelope.
2. A duct air-leakage test shall not be
				required for ducts serving heat or energy recovery ventilators that are not
				integrated with ducts serving heating or cooling systems.
A written report of the results of the test shall be signed
				  by the party conducting the test and provided to the building official.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-98 - Section N1103.3.4; duct leakage (prescriptive)

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 98.
Change the text of SECTION N1103.3.4 to read as
				  follows:
The total leakage of the ducts, where measured in accordance
				  with Section N1103.3.3 (R403.3.3), shall be as follows:
1. Rough-in test: The total leakage shall be
				less than or equal to 4 cubic feet per minute (113.3 L/min) per 100 square feet
				(9.29 m2) of conditioned floor area where the air
				handler is installed at the time of the test. Where the air handler is not
				installed at the time of the test, the total leakage shall be less than or
				equal to 3 cubic feet per minute (85 L/min) per 100 square feet (9.29
				m2) of conditioned floor area.
2. Postconstruction test: Leakage to outside
				shall be less than or equal to 4 cubic feet per minute (113.3 L/min) per 100
				square feet (9.29 m2) of conditioned floor
				area.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-99 - Section N1103.3.5; building cavities (mandatory)

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 99.
Change the text of SECTION N1103.3.5 to read as
				  follows:
Building framing cavities shall not be used as supply ducts
				  or plenums.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-100 - Section N1103.6; mechanical ventilation (mandatory)

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 100.
Change the text of SECTION N1103.6 to read as
				  follows:
The building shall be provided with ventilation that complies
				  with the requirements of Section M1505 or with other approved means of
				  ventilation. Outdoor air intakes and exhausts shall have automatic or gravity
				  dampers that close when the ventilation system is not operating.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-101 - Section N1105.3; performance based compliance

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 101.
Delete the text of the last sentence of SECTION N1105.3
				  without substitution. The EXCEPTION of SECTION N1105.3 is retained as written
				  without amendment.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-102 - Section N1105.4.2; compliance report

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 102.
Change the text of SECTION N1105.4.2 to read as
				  follows:
Compliance software tools shall generate a report that
				  documents that the proposed design complies with Section N1105.3. A compliance
				  report on the proposed design shall be submitted for Class 1 structures as
				  required by the General Administrative Rules (675 IAC 12) and as required by
				  local ordinance for Class 2 structures. Upon completion of the building, a
				  compliance report based on the as-built condition of the building shall be
				  submitted to the building official before a certificate of occupancy is issued.
				  Batch sampling of buildings to determine energy code compliance shall only be
				  allowed for stacked multiple-family units.
Compliance reports shall include information in accordance
				  with Sections N1105.4.2.1 and N1105.4.2.2. Where the proposed design of a
				  building could be built on different sites where the cardinal orientation of
				  the building on each site is different, compliance of the proposed design for
				  the purposes of the application for the building permit shall be based on the
				  worst case orientation, worst case configuration, worst case building air
				  leakage, and worst case duct leakage. Such worst case parameters shall be used
				  as inputs to the compliance software for energy analysis.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-103 - Table N1105.5.2(1); specifications for the standard reference and proposed designs

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 103.
Change the STANDARD REFERENCE DESIGN specifications for AIR
				  EXCHANGE RATE in TABLE N1105.5.2(1) to read as follows:
BUILDING COMPONENT
STANDARD REFERENCE DESIGN
PROPOSED DESIGN
Air exchange rate
The air leakage rate at a pressure of 0.2 inch w.g.
							 (50 Pa) shall be 5 air changes per hour. The mechanical ventilation rate shall
							 be in addition to the air leakage rate and shall be the same as in the proposed
							 design, but not greater than 0.01 x CFA + 7.5 x (Nbr +
							 1) where: CFA = conditioned floor area, ft2.
							 Nbr = number of bedrooms. Energy recovery shall not be
							 assumed for mechanical ventilation.
The measured air exchange
							 ratea. The mechanical ventilation
							 rateb shall be in addition to the air leakage rate
							 and shall be as proposed.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-104 - Section N1107.1; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 104.
Change the text of SECTION N1107.1 to read as
				  follows:
The provisions of Sections N1107 through N1111 shall control
				  the alteration, addition and change of occupancy of existing buildings and
				  structures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-105 - Section N1107.1.1; additions and alterations: general

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 105.
Change the title and text of SECTION N1107.1.1 to read as
				  follows:
SECTION N1107.1.1 ADDITIONS AND ALTERATIONS: GENERAL.
Additions and alterations to an existing building, building
				  system or portion thereof shall comply with Section N1108, N1109, or N1110.
				  Unaltered portions of the existing building or building supply system shall not
				  be required to comply with this chapter.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-106 - Section N1107.3; maintenance

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 106.
Change the text of SECTION N1107.3 to read as
				  follows:
The requirements of this chapter shall not provide the basis
				  for removal or abrogation of energy conservation, fire protection and safety
				  systems, and devices in existing structures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-107 - Section N1107.4; compliance

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 107.
Delete the text of SECTION N1107.4 and substitute to read as
				  follows: Alterations, additions, changes in occupancy, or relocation of
				  existing buildings shall comply with this chapter and the General
				  Administrative Rules (675 IAC 12).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-108 - Section N1107.5; new and replacement materials

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 108.
Change the text of SECTION N1107.5 to read as
				  follows:
Except as otherwise required or permitted by this code,
				  materials permitted by the applicable code for new construction shall be used.
				  Hazardous materials shall not be used where the code for new construction would
				  not allow their use in buildings of similar occupancy, purpose, and location.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-109 - Section N1107.6; historic buildings

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 109.
Delete the text of SECTION N1107.6 and substitute to read as
				  follows: See General Administrative Rules (675 IAC 12).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-110 - Section M1201.1; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 110.
Change the text of SECTION M1201.1 to read as
				  follows:
The provisions of Chapters 12 through 24 of this code shall
				  regulate the design, installation, alteration, and inspection of mechanical
				  systems that are permanently installed and used to control environmental
				  conditions within buildings. These chapters shall also regulate those
				  mechanical systems, system components, equipment, and appliances specifically
				  addressed in this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-111 - Section M1201.2; application

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 111.
Delete SECTION M1201.2 in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-112 - Section M1202; application

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 112.
Delete SECTION M1202 and substitute to read as
				  follows:
For existing installations see Chapter 1 of this code and the
				  General Administrative Rules (675 IAC 12).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-113 - Section M1301.2; identification

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 113.
Change the text of SECTION M1301.2 to read as
				  follows:
Each uncut length of pipe and tubing and each pipe fitting
				  utilized in a mechanical system shall bear the identification of the
				  manufacturer.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-114 - Section M1302.1; listed and labeled

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 114.
Change the text of SECTION M1302.1 to read as
				  follows:
Appliances regulated by this code shall be listed and labeled
				  for the application in which they are installed and used, unless otherwise
				  approved in accordance with Section R106.1.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-115 - Section M1305.1; appliance access for inspection service, repair, and replacement

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 115.
Change the text of SECTION M1305.1 to read as
				  follows:
Appliances shall be located to allow for access for
				  inspection, service, repair, and replacement without removing permanent
				  construction, or any other piping or ducts not connected to the appliance being
				  inspected, serviced, repaired, or replaced. A level working space not less than
				  30 inches deep and 30 inches wide (762 mm by 762 mm) shall be provided in front
				  of the control side to service an appliance.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-116 - Section M1305.1.3.1; ground clearance

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 116.
Change the text of SECTION M1305.1.3.1 to read as
				  follows:
Equipment and appliances supported from the ground shall be
				  level and firmly supported on a concrete slab or other approved material not
				  less than 2 inches (51 mm) above the finished grade. Such support shall be in
				  accordance with the manufacturer's installation instructions. Appliances
				  suspended from the floor shall have a clearance of not less than 6 inches (152
				  mm) from the ground.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-117 - Section M1307.3.1; protection from impact

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 117.
Delete the text of SECTION M1307.3.1 and substitute to read
				  as follows:
Building appliances and their appurtenances shall be
				  installed outside the intended vehicle travel path. Vehicle travel path shall
				  be determined by the garage door rough opening width. When building appliances
				  and their appurtenances cannot be installed outside the vehicle travel path due
				  to design and construction restraints, such appliances shall be protected by
				  one of the following methods:
1.Installed in an adjacent but separate
				equipment room within the garage;
2. Installed in an adjacent equipment alcove
				within the garage that has a raised floor or platform that is at least
				twenty-four (24) inches higher than the garage floor;
3. Install bollards that are a minimum three
				(3) inch diameter schedule forty (40) steel pipe embedded a minimum of eighteen
				(18) inches below grade and at least twenty-four (24) inches above the garage
				floor with pipe cap;
4. Install
				bollards that are a minimum three (3) inch diameter schedule 40 steel pipe with
				a welded eight (8) inches by eight (8) inches by one-quarter (1/4) inch base
				plate anchored to the garage floor slab using one-half (1/2) inch wedge anchors
				or equivalent with a minimum embedment of two and one-fourth (2 1/4) inches.
				Height of bollard to be at least twenty-four (24) inches above garage floor
				with pipe cap; or
5. Install a
				minimum seventy-two (72) inches long by six (6) inches wide by four (4) inches
				high bumper curb that is anchored to the concrete floor.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-118 - Section M1411.3.1; auxiliary and secondary drain systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 118.
Add ITEM 5 to SECTION M1411.3.1 to read as follows:
5. When installed on a water-resistant floor
				sloped to a floor drain in the same room or space.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-119 - Section M1502.4.2; duct installation

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 119.
Change the text of SECTION M1502.4.2 to read as
				  follows:
Exhaust ducts shall be supported at intervals not to exceed
				  twelve (12) feet (3,658 mm) and shall be secured in place. The insert end of
				  the duct shall extend into the adjoining duct or fitting in the direction of
				  airflow. Exhaust duct joints shall be sealed in accordance with Section
				  M1601.4.1 and shall be fastened mechanically or by other approved methods.
				  Ducts shall not be joined with screws or similar fasteners that protrude more
				  than c inch (3.2 mm) into the inside of the duct. Where dryer exhaust ducts are
				  enclosed in wall or ceiling cavities, such cavities shall allow the
				  installation of the duct without deformation.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-120 - Section M1601.1.2; underground duct systems

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 120.
Change the text of SECTION M1601.1.2 to read as
				  follows:
Underground duct systems shall be constructed of approved
				  concrete, clay, metal, or plastic. The maximum design temperature for systems
				  utilizing plastic duct and fittings shall be 150°F (66°C). Metal ducts
				  shall be protected from corrosion in an approved manner or shall be completely
				  encased in concrete not less than 2 inches (51 mm) thick. Nonmetallic ducts
				  shall be installed in accordance with the manufacturer's instructions. Plastic
				  pipe and fitting materials shall conform to cell classification 12454-B of ASTM
				  D1248 or ASTM D1784 and external loading properties of ASTM D2412. Ducts shall
				  slope to a drainage point that has access. Ducts shall be sealed according to
				  the manufacturer's installation instructions or Section M1601.4 prior to
				  encasing the ducts in concrete or direct burial. Metallic ducts that have an
				  approved protective coating and nonmetallic ducts shall be installed in
				  accordance with the manufacturer's instructions.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-121 - Section M1601.4.5; fireblocking

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 121.
Change the text of SECTION M1601.4.5 to read as
				  follows:
Duct installations shall be fireblocked in accordance with
				  Section R302.11.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-122 - Section M1602.2; return air openings

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 122.
Delete ITEM 6 of SECTION M1602.2 without substitution, and
				  renumber ITEM 7 of SECTION M1602.2 to read as ITEM 6.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-123 - Section M1801.9; fireblocking

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 123.
Change the text of SECTION M1801.9 to read as
				  follows:
Vent and chimney installations shall be fireblocked in
				  accordance with Sections R302.11 and R1003.19.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-124 - Section M2001.1.2; regulated boilers

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 124.
Add SECTION M2001.1.2 to read as follows:
SECTION M2001.1.2 REGULATED BOILERS.
Boilers and pressure vessels regulated pursuant to IC 22-15-6
				  are not regulated by this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-125 - Section M2201.3; underground tanks

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 125.
Delete the text of SECTION M2201.3 and substitute to read as
				  follows:
Excavations for underground tanks shall not undermine the
				  foundations of existing structures. Underground tanks shall be set on firm
				  foundations and surrounded with at least 6 inches (152.4 mm) of noncorrosive
				  inert material, such as clean sand or gravel well tamped in place or in
				  accordance with the manufacturer's installation instructions. Tanks shall be
				  covered with a minimum of 2 feet (609.6 mm) of earth or shall be covered by not
				  less than 1 foot (304.8 mm) of earth, on top of which shall be placed a slab of
				  reinforced concrete not less than 4 inches (101.6 mm) thick. When underground
				  tanks are, or are likely to be, subjected to traffic, they shall be protected
				  against damage from vehicles passing over them by at least 3 feet (914.4 mm) of
				  earth cover, or 18 inches (457.2 mm) of well-tamped earth plus 6 inches (152.4
				  mm) of reinforced concrete, or 8 inches (203.2 mm) of asphaltic concrete. When
				  asphaltic or reinforced concrete paving is used as part of the protection, it
				  shall extend at least 1 foot (304.8 mm) horizontally beyond the outline of the
				  tank in all directions. The clearance from the tank to the nearest wall of a
				  basement, pit, or property line shall not be less than 1 foot (305 mm).
				  Corrosion protection shall be provided in accordance with Section M2203.7.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-126 - Section M2301.1; general

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 126.
Change the text of SECTION M2301.1 to read as
				  follows:
This section provides for the design, construction,
				  installation, and alteration of equipment and systems using solar thermal
				  energy to provide space heating or cooling, hot water heating, and swimming
				  pool heating.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-127 - Section G2401.1; application

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 127.
Change the second paragraph of the text of SECTION G2401.1
				  to read as follows:
Coverage of piping systems shall extend from the point of
				  delivery to the outlet of the appliance shutoff valves (see definition of
				  "point of delivery"). Piping systems requirements shall include design,
				  materials, components, fabrication, assembly, installation, and testing.
				  Requirements for gas appliances and related accessories shall include
				  installation, combustion, and ventilation air and venting and connections to
				  piping systems.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-128 - Section G2403; general definitions

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 128.
Change SECTION G2403 as follows:
(1) Change the title of SECTION G2403 to read
				as follows:
SECTION G2403 (202) GENERAL DEFINITIONS FOR THE PURPOSE OF
				  CHAPTER 24 ONLY.
(2) Change
				the definition of APPROVED to read as follows:
APPROVED means, as to materials, equipment, appliances,
				  methods of design, and types of construction, acceptance by the building
				  official by one (1) of the following methods:
(1) investigation or tests conducted by
				recognized authorities;
(2)
				investigation or tests conducted by technical or scientific organizations;
				or
(3) accepted principles.
The investigation, tests, or principles shall establish that
				  the materials, equipment, appliances, methods of design, and types of
				  construction are safe for their intended purpose.
(3) Add a sentence to the end of the
				definition of BOILER, LOW-PRESSURE to read as follows: This definition is not
				applicable to boilers and pressure vessels regulated pursuant to IC
				22-15-6.
(4) Add the following to
				the end of the definition of MODULATING: NFPA 58. See
				675
				IAC 22-2.2-14
[
				675
				IAC 22-2.2-14 was repealed filed Mar 18, 2008, 2:30
				p.m.: 20080423-IR-675070478FRA, eff 90 days after filing with the
				Publisher]
.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-129 - Section G2404.5; reserved

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 129.
Change SECTION G2404.5 as follows:
(1) Change the title of SECTION G2404.5 to
				read as follows:
SECTION G2404.5 RESERVED.
(2) Delete the text of SECTION G2404.5
				without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-130 - Section G2404.10; auxiliary drain pan

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 130.
Change the title "EXCEPTION" in SECTION G2404.10 to read as
				  "EXCEPTIONS", number the first exception as "1.", and add a second exception to
				  SECTION G2404.10 to read as follows: 2. An auxiliary drain pan shall not be
				  required for appliances installed on a water-resistant floor that slopes to a
				  drain.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-131 - Section G2405.1; structural safety

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 131.
Change the text of SECTION G2405.1 to read as
				  follows:
The building shall not be weakened by the installation of any
				  gas piping. In the process of installing or altering any gas piping, the
				  finished floors, walls, ceilings, tile work, or any other part of the building
				  or premises that is required to be changed or replaced shall be left in a safe
				  structural condition in accordance with the requirements of this code.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-132 - Section G2408.4; clearances from grade

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 132.
Change the text of SECTION G2408.4 to read as
				  follows:
Equipment and appliances installed at grade level shall be
				  supported on a level concrete slab or other approved material extending not
				  less than 2 inches (52 mm) above adjoining grade or shall be suspended not less
				  than 6 inches (152 mm) above adjoining grade. Such supports shall be installed
				  in accordance with the manufacturer's instructions.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-133 - Section G2411.2.1; point of connection

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 133.
Change the text of SECTION G2411.2.1 to read as
				  follows:
The bonding jumper shall connect to a metallic pipe, pipe
				  fitting, or CSST fitting.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 14 - ONE AND TWO FAMILY DWELLING CODE › Rule 4.4 - 2020 Indiana Residential Code › Section 4.4-134 - Section G2411.2.6; separation

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-2.5; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 134.
Add SECTION G2411.2.6 to read as follows: SECTION G2411.2.6
				  SEPARATION.
Except where connected to appliances and at bonding
				  connections, corrugated stainless steel tubing that is not listed with an
				  arc-resistant jacket or coating system in accordance with ANSI LC1/CSA 6.26
				  shall be isolated from metal gas piping, metal water piping, metal air ducts,
				  metal structural framing, and all electrical wiring methods by a separation
				  space of at least 2 inches.