reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 5.1 - Storage and Treatment of Septage › Section 5.1-5 - Alternate design and construction or innovative technology

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12
Sec. 5.
(a) The use
				of a design or construction approach other than the requirements specified in
				this article or an innovative technology may be proposed to the department by
				the applicant in accordance with the following:
(1) The proposal for the alternative design,
				construction, or innovative technology must be accompanied by documentation
				that ensures that the provisions of this article are met.
(2) The proposal must comply with all
				applicable environmental rules and laws.
(3) The proposal must be submitted with a
				septage management permit application.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 5.1 - Storage and Treatment of Septage › Section 5.1-6 - Operational requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12
Sec. 6.
(a) A storage
				or treatment facility must be maintained and operated to prevent any threats to
				human health or the environment as follows:
(1) An all-weather off-loading area with
				containment for spill cleanup must be provided where the vehicle contents are
				received by the storage or treatment facility.
(2) Unauthorized access to the storage or
				treatment facility must be prevented by locks, and the storage or treatment
				facility must be fenced and posted.
(3) The storage or treatment facility must be
				maintained so there is no discharge or seepage of septage other than controlled
				removal for final disposal of the septage.
(4) The storage or treatment facility must be
				maintained to prevent safety hazards or disease vector conditions.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 5.1 - Storage and Treatment of Septage › Section 5.1-7 - Closure

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12
Sec. 7.
(a) A storage
				or treatment facility that is no longer being operated or used must be
				closed.
(b) The person or persons
				who signed the statement submitted in accordance with section 1(a)(7) of this
				rule must close the storage or treatment facility in accordance with the
				following:
(1) The commissioner shall be
				notified at least thirty (30) days in advance that the storage or treatment
				facility is to be closed.
(2)
				Closure, as described in this section, must be completed within one hundred
				twenty (120) days after the notification required in subdivision (1).
(3) The contents of a storage or treatment
				facility must be disposed of in a manner consistent with
				327 IAC 7.1-7
				or
				327 IAC
				7.1-8.
(4)
				Aboveground structures must be dismantled and removed.
(5) A certification statement indicating that
				the requirements of this section have been met must be sent to the commissioner
				within thirty (30) days after completion of closure. The closure certification
				will be deemed adequate unless, within ninety (90) days of receipt of the
				closure certification and subsequent review, the commissioner issues a notice
				of deficiency of closure, including actions necessary to correct the
				deficiency.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 6 - Septage Vehicle Operation › Section 6-1 - Vehicle requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12-2.2
Sec. 1.
(a) A copy of
				the current septage management permit issued by the commissioner must be
				maintained in the vehicle at all times.
(b) A septage management vehicle is subject
				to the following conditions and any additional conditions contained in the
				septage management permit:
(1) The vehicle
				must be used only as authorized by this rule and in compliance with any
				applicable restrictions or conditions stated in the septage management
				permit.
(2) The vehicle must not be
				used for the transport of any of the following:
(A) A hazardous waste that is regulated under
				329 IAC 3.1.
(B) Septage containing
				polychlorinated biphenyls (PCBs) equal to or greater than two (2) milligrams
				per kilogram on a dry weight basis.
(C) Petroleum based products.
(D) Pesticides.
(3) The vehicles and equipment used in
				cleaning sewage disposal systems or transporting septage must not be used for
				purposes other than the hauling of wastewater as defined in
				327 IAC
				3-1-2(23), animal wastes, landfill
				leachate, or biosolids as defined in
				327 IAC
				6.1-2-7, without prior written permission of the
				commissioner.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 6 - Septage Vehicle Operation › Section 6-2 - Vehicle tank requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12
Sec. 2.
The septage management vehicle must be equipped with a
				  leak-proof tank suitable for containment of septage from cleaning sewage
				  disposal systems and must meet the following requirements unless otherwise
				  specified in a septage management permit:
(1) The tank must be securely affixed to the
				vehicle chassis.
(2) The tank must
				have a capacity of at least:
(A) one thousand
				(1,000) gallons when pumping commercial or residential sewage disposal systems;
				or
(B) two hundred fifty (250)
				gallons when pumping portable toilets or grease interceptors or
				traps.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 6 - Septage Vehicle Operation › Section 6-3 - Vehicle pumping system requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12
Sec. 3.
A vehicle pumping system must meet the following
				  requirements:
(1) The inlet and
				discharge of the sewage pumps must be a minimum of two and one-half (2
				½) inches in diameter.
(2)
				The vehicle engine intake manifold must not be used as a vacuum
				source.
(3) The pump installation
				must prevent leakage.
(4) All
				exposed connections or openings must be made watertight with caps or plugs when
				the pumping system is being used to transfer liquid or septage.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 6 - Septage Vehicle Operation › Section 6-4 - Vehicle hose requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12
Sec. 4.
A vehicle hose must meet the following requirements:
(1) The hose must:
(A) be maintained in good
				condition;
(B) have an inside
				diameter of not less than two and one-half (2 ½) inches; and
(C) be equipped with leakproof
				connectors.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 6 - Septage Vehicle Operation › Section 6-6 - Vehicle identification requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12
Sec. 6.
A septage management vehicle must meet the following vehicle
				  identification requirements:
(1) Both
				vehicle doors or both vertical front quarters of the tank must have the
				following information:
(A) The business
				name.
(B) The business phone
				number.
(C) The word "IDEM"
				followed by the assigned septage management permit number.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 7 - Septage Disposal › Section 7-1 - Disposal requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12
Sec. 1.
(a) Septage
				disposal may be accomplished through:
(1)
				discharge into a wastewater treatment plant that has a valid National Pollutant
				Discharge Elimination System (NPDES) permit;
(2) disposal at a permitted municipal solid
				waste landfill;
(3) disposal at a
				permitted septage treatment facility;
(4) disposal at a permitted solid waste
				processing facility in accordance with 329 IAC 11;
(5) disposal at a permitted biomass facility
				in accordance with 329 IAC 11.5;
(6) for grease only, disposal at an approved
				biomass facility at a confined feeding operation in accordance with 327 IAC 19;
				or
(7) land application in
				accordance with
				327 IAC
				7.1-8.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-1 - Application requirements for land application of septage

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-15-8; IC 13-18-12; IC 25-31.5
Sec. 1.
(a) Septage
				may only be applied to the land as follows:
(1) The only forms of septage that may be
				applied to the land are:
(A) domestic
				septage;
(B) grease; or
(C) a combination of domestic septage and
				grease.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-2 - Land application site prohibitions

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12
Sec. 2.
The application of septage at a land application site must
				  not:
(1) cause or contribute to the
				taking of any endangered or threatened species of plants, fish, or
				wildlife;
(2) result in the
				destruction or adverse modification of the critical habitat of endangered or
				threatened species as identified in
				50 CFR
				17.11 * and
				50 CFR
				17.12 *;
(3) cause a discharge of pollutants into
				waters of the state that is in violation of the requirements of the National
				Pollutant Discharge Elimination System (NPDES) program under 327 IAC
				5;
(4) cause nonpoint source
				pollution to waters of the state;
(5) contaminate a drinking water
				source;
(6) cause soil
				erosion;
(7) be in a flood
				plain;
(8) be on a land application
				site that has a soil concentration of phosphorus of more than two hundred (200)
				parts per million;
(9) be from a
				portable sanitary unit or type III marine sanitation device; or
(10) be made to sites where manure or
				biosolids, as defined in
				327 IAC
				6.1-2-7, are applied.
*These documents are incorporated by reference. Copies may be
				  obtained from the Government Publishing Office,
www.gpo.gov
, or are available for review at the
				  Indiana Department of Environmental Management, Office of Legal Counsel,
				  Indiana Government Center North, 100 North Senate Avenue, Thirteenth Floor,
				  Indianapolis, Indiana 46204.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-3 - Land application approval

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12; IC 13-30-10; IC
				  36-9-30-35
Sec. 3.
The commissioner may issue or renew requirements for land
				  application in a septage management permit only after the following:
(1) Receipt by the department of a completed
				application in accordance with section 1 of this rule.
(2) A review of the proposed land application
				site to determine if the site and proposed methods of application will comply
				with the requirements of this rule.
(3) A valid septage management permit:
(A) has been issued to the applicant under
				this article; or
(B) will be issued
				at the same time as the land application requirements.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-5 - Operational requirements

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12
Sec. 5.
A person land applying septage must comply with the
				  following conditions and any additional requirements in a septage management
				  permit issued by the commissioner:
(1)
				The valid septage management permit or copy of the septage management permit
				must be carried in any vehicle disposing of septage at an application site at
				all times.
(2) The septage
				management permit or copy of the septage management permit must be available
				for inspection by the department or any law enforcement officer.
(3) The property on which the septage land
				application site is located must be posted with signs:
(A) reading, "NO TRESPASSING"; and
(B) along all access points to the
				site.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-7 - Land application rates, record keeping, and reporting

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12
Sec. 7.
(a) Except as
				approved by the commissioner under subdivision (4), the amount of septage to be
				applied must not exceed the following:
(1) For
				a soil phosphorus concentration of fifty (50) parts per million or less, the
				annual application rate for septage based on the nitrogen requirement of the
				crop grown on the land application site must not exceed the following:
(A) Fifty-three thousand (53,000) gallons per
				acre based on a corn crop grown during the next growing season.
(B) Thirty-eight thousand (38,000) gallons
				per acre based on an alfalfa, soybean, wheat, or hay crop grown during the next
				growing season.
(C) Nineteen
				thousand (19,000) gallons per acre based on land that is grass, pasture, or set
				aside for continued growth during the current growing season.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-8 - Land application setbacks

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12
Sec. 8.
Septage must not be incorporated or injected or be allowed
				  to drain closer to the features of interest than the following minimum
				  setbacks:
Features of Interest
Potable water supplies
500 feet
Lakes, ponds, streams, intermittent waterways,
							 surface water impoundments, wetlands, or other bodies of water
100
							 feet
Drainage inlets and tile systems
50
							 feet
Rock outcrops, sinkholes, or undrained
							 depressions
50 feet
Residences, places of business, or public gathering
							 places
500 feet
Public roads
200 feet
Property lines or easements
50 feet
Historic sites
1,000 feet
Critical habitats of endangered or threatened
							 species
1,000 feet
Public water supply well or public water supply
							 surface intake structure
1,000 feet
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-9 - Land application management practices

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-18-12-4
Affected: IC 13-18-12; IC 25-31.5
Sec. 9.
(a) The land
				application of septage must be performed in accordance with the following:
(1) Prior to land application, loads
				containing domestic septage must be treated to reduce pathogens as follows:
(A) If the load is domestic septage only:
(i) the pH must be raised to twelve (12) or
				higher by addition of alkaline material and, without the addition of more
				alkaline material, must remain at twelve (12) or higher for at least thirty
				(30) minutes; and
(ii) the
				procedure must be done at a minimum of two (2) times, once at the start of
				thirty (30) minutes and once at the end of thirty (30) minutes.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 7.1 - WASTEWATER MANAGEMENT › Rule 8 - Land Application of Septage › Section 8-10 - Limitations and restrictions regarding land use and crop management

Current through July 10, 2024
Authority: IC 13-14-8; IC
				  13-18-12-4
Affected: IC 13-18-12
Sec. 10.
(a) The
				limitations and restrictions on land use and crop management where grease only
				has been land applied are as follows:
(1)
				Access to the site by the public must be prohibited for twelve (12) months
				following the last grease application.
(2) Access to the site by animals whose
				products are consumed by humans must be prevented for at least thirty (30) days
				following the last grease application.
(3) Food crops for direct human consumption
				must not be grown for eighteen (18) months following the last grease
				application.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 1 - Public Water Supply Direct Additive and Indirect Additive Standards › Section 1-1 - Community water system; fluoridation; phosphate additives

Current through July 10, 2024
Authority: IC
				  13-14-8; IC
				  13-14-9; IC
				  13-15-1-2;
				  IC
				  13-15-2-1;
				  IC
				  13-18-3-1; IC
				  13-18-4-1
Affected: IC
				  13-13-5-1;
				  IC 13-18-2
Sec. 1.
Each community water system that adds a fluoride or
				  phosphate compound shall comply with the following:
(1) Fluoride compounds may be added to such
				water supplies after receiving a construction permit from the commissioner
				providing the total content of fluoride ion (F-)
				after such addition does not exceed two (2.0) milligrams per liter (mg/l)
				unless the public water system is a participant in an Indiana state department
				of health approved school fluoride adjustment program for which the
				concentration of fluoride in a school water supply shall not exceed five and
				one-half (5.5) mg/l.
(2) Phosphate
				additives may be added to the water for treatment of iron, manganese, scale,
				and corrosion problems after receiving a construction permit from the
				commissioner. Such direct additives shall be in conformance with section 2 of
				this rule. Total phosphate concentration shall not exceed ten (10) mg/l
				measured as PO4. Product may be provided in liquid or
				dry form. Containers in which the agents are packaged shall be labeled
				indicating product information and general instructions for use. At a minimum,
				the label must display the name and application of product, percentage
				phosphate concentration as PO4, and certification of
				American National Standards Institute (ANSI)/National Sanitation Foundation
				(NSF) International Standard 60, NSF Listings, Drinking Water Treatment
				Chemicals-Health Effects. In addition, if it is provided in liquid form, the
				label shall specify pH and specific gravity. The containers must also be marked
				identifying manufacturing batch number. All liquid products must be treated for
				bacteria control at the time of manufacture with a potably approved bacteria
				control agent.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 1 - Public Water Supply Direct Additive and Indirect Additive Standards › Section 1-2 - Drinking water direct additives and indirect additives; certification requirements

Current through July 10, 2024
Authority: IC
				  13-14-8; IC
				  13-14-9; IC
				  13-15-1-2;
				  IC
				  13-15-2-1;
				  IC
				  13-18-3-1; IC
				  13-18-4-1
Affected: IC
				  13-11-2; IC
				  13-13-5-1;
				  IC 13-18-2
Sec. 2.
(a) All
				public water systems shall comply with this section before the conclusion of
				ninety (90) days from the effective date of this rule.
(b) All direct additives in public water
				systems shall be certified for conformance to American National Standards
				Institute (ANSI)/National Sanitation Foundation (NSF) International Standard
				60, NSF Listings, Drinking Water Treatment Chemicals-Health Effects. All public
				water systems must compile and maintain on file for inspection by the
				commissioner a list of all direct additives used that come into contact with
				the drinking water. This list must contain the name, the description, and the
				manufacturer of the product and whether the direct additive is certified under
				this section. The list must be maintained as long as the direct additives are
				used by the public water system.
(c) The following new or modified indirect
				additives in public water systems shall be certified for conformance to
				American National Standards Institute (ANSI)/National Sanitation Foundation
				(NSF) International Standard 61, Drinking Water System Components-Health
				Effects, except Section 9, Mechanical Plumbing Product:
(1) All indirect additives found in finished
				water storage facilities, including lubricants, tank coatings, paints, and
				epoxies.
(2) All indirect additives
				between all entry points to the distribution system and the premises of the
				consumer.
(3) All filter and
				membrane media.
(4) All indirect
				additives that are classified in a category of indirect additives for which
				American National Standards Institute (ANSI)/National Sanitation Foundation
				(NSF) International Standard 61 is available.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 1 - Public Water Supply Direct Additive and Indirect Additive Standards › Section 1-3 - Definitions

Current through July 10, 2024
Authority: IC 13-14-8; IC 13-14-9; IC 13-15-1-2; IC
				  13-15-2-1; IC 13-18-3-1; IC 13-18-4-1
Affected: IC 13-11-2; IC 13-13-5-1; IC 13-18-2
Sec. 3.
In addition to the definitions in IC 13-11-2, the following
				  definitions apply throughout this rule:
(1) "Direct additives" means additives that
				are used in public water systems for the treatment of raw water and to protect
				drinking water during storage and distribution. Examples of direct additives
				include the following:
(A) Agents used for
				coagulation and flocculation.
(B)
				Corrosion and scale control.
(C)
				Softening.
(D)
				Sequestering.
(E)
				Precipitation.
(F) pH
				adjustment.
(G) Disinfection and
				oxidation.
(H) Miscellaneous
				treatment applications.
(I)
				Miscellaneous water supply products.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 1 - Public Water Supply Direct Additive and Indirect Additive Standards › Section 1-4 - Incorporation by reference

Current through July 10, 2024
Authority: IC
				  13-14-8; IC
				  13-14-9; IC
				  13-15-1-2;
				  IC
				  13-15-2-1;
				  IC
				  13-18-3-1; IC
				  13-18-4-1
Affected: IC
				  13-11-2; IC
				  13-13-5-1;
				  IC 13-14-8
Sec. 4.
The following materials, including titles and the names and
				  addresses of where they may be located for inspection and copying, are
				  incorporated by reference into this rule:
(1) "Drinking Water Treatment
				Chemicals-Health Effects", November 15, 2004, National Sanitation Foundation
				(NSF) International, 3475 Plymouth Road, Ann Arbor, Michigan, 48113-0140 or
				from the Indiana Department of Environmental Management, Office of Water
				Quality, Indiana Government Center-North, 100 North Senate Avenue, Room N1255,
				Indianapolis, Indiana 46204.
(2)
				"Drinking Water System Components-Health Effects", November 15, 2004, National
				Sanitation Foundation (NSF) International, 3475 Plymouth Road, Ann Arbor,
				Michigan 48113-0140 or from the Indiana Department of Environmental Management,
				Office of Water Quality, Indiana Government Center-North, 100 North Senate
				Avenue, Room N1255, Indianapolis, Indiana 46204.
Notwithstanding language to the contrary in the primarily
				  incorporated documents, the version of all secondarily incorporated documents,
				  which are documents referred to in the primarily incorporated documents, shall
				  be the version in effect on the date of final adoption of this rule.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-2 - Applicability of rule; modification of monitoring requirements

Current through July 10, 2024
Authority: IC 13-13-5; IC 13-14-8-7; IC 13-14-9; IC 13-18-3;
				  IC 13-18-16
Affected: IC 13-18
Sec. 2.
(a) Each
				public water system shall comply with all of the provisions of this rule and
				327 IAC 8-2.1 unless the public water system meets all of the following
				conditions:
(1) Consists only of distribution
				and storage facilities and does not have collection and treatment
				facilities.
(2) Obtains all of its
				water from, but is not owned or operated by, a public water system to which
				this article applies.
(3) Does not
				sell water to any person.
(4) Is
				not a carrier which conveys passengers in interstate commerce.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-3 - Analytical methods

Current through July 10, 2024
Authority: IC 13-1-3-4; IC 13-7
Affected: IC 13-1-3-4; IC 13-7
Sec. 3.
Except as otherwise provided by this rule, the analytical
				  procedures used as methods of analysis to determine the quality of water
				  sampled shall be in accordance with this rule.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-4 - Inorganic chemicals; maximum contaminant levels

Current through July 10, 2024
Authority: IC 13-13-5; IC 13-14-8-7; IC 13-14-9; IC 13-18-3;
				  IC 13-18-16
Affected: IC 13-18
Sec. 4.
(a) The
				following MCLs for inorganic chemicals apply to all CWSs, NTNCWSs, and TWSs
				except as provided in subsection (b):
Contaminant
Level in Milligrams Per Liter
Nitrate
10 (as nitrogen)
Nitrite
1 (as nitrogen)
Nitrate and nitrite
10 (as nitrogen)
(b)
				The commissioner may allow nitrate levels up to, but not to exceed, twenty (20)
				milligrams per liter in a noncommunity water system if the supplier of water
				meets all of the following conditions:
(1)
				Such water will not be available to children under six (6) months of
				age.
(2) There will be continuous
				posting of the fact that nitrate levels exceed ten (10) milligrams per liter
				and the potential health effects of exposure.
(3) Local and state public health authorities
				shall be notified annually of nitrate levels that exceed ten (10) milligrams
				per liter.
(4) No adverse health
				effects shall result.
(5) The
				commissioner may require additional notice to the public as provided by
				327
				IAC 8-2.1-14.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-4.2 - Analytical methods for inorganic chemical testing

Current through July 10, 2024
Authority: IC 13-13-5; IC 13-14-8-7; IC 13-14-9; IC 13-18-3;
				  IC 13-18-16
Affected: IC 13-11-2; IC 13-14-8; IC 13-18-1; IC
				  13-18-2
Sec. 4.2.
(a)
				Analyses conducted to determine compliance with section 4 of this rule shall be
				made in accordance with one (1) of the following methods* for each contaminant
				or with the alternative methods listed in Appendix A to Subpart C of 40 CFR
				141. Criteria for analyzing arsenic, barium, beryllium, cadmium, calcium,
				chromium, copper, lead, nickel, selenium, sodium, and thallium with digestion
				or directly without digestion, and other analytical test procedures are
				contained in Technical Notes on Drinking Water Methods, EPA-600/R-94-173,
				October 1994. This document is available from the National Service Center for
				Environmental Publications (NSCEP), P.O. Box 42419, Cincinnati, OH 45242-0419
				or http://www.epa.gov/nscep/:
(1) Antimony as
				follows:
(A) Atomic
				absorption1; furnace, Method 3113B*.
(B) Atomic absorption; platform, Method
				200.9*.
(C) ICP-mass spectrometry,
				Method 200.8*.
(D) Hydride-atomic
				absorption, Method D 3697-92*.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-5 - Organic chemicals other than volatile compounds; maximum contaminant levels

Current through July 10, 2024
Authority: IC 13-13-5; IC 13-14-8-7; IC 13-14-9; IC 13-18-3;
				  IC 13-18-16
Affected: IC 13-18
Sec. 5.
(a) The MCLs
				for the following synthetic organic chemicals apply to all CWSs and NTNCWSs:
CAS No.
Contaminant
MCL (mg/L)
15972-60-8
Alachlor
0.002
1912-24-9
Atrazine
0.003
50-32-8
Benzo(a)pyrene
0.0002
1563-66-2
Carbofuran
0.04
57-74-9
Chlordane
0.002
75-99-0
Dalapon
0.2
96-12-8
1,2-dibromo-3-chloropropane (DBCP)
0.0002
103-23-1
Di(2-ethylhexyl)adipate
0.4
117-81-7
Di(2-ethylhexyl)phthalate
0.006
88-85-7
Dinoseb
0.007
85-00-7
Diquat
0.02
94-75-7
2,4-D
0.07
145-73-3
Endothall
0.1
72-20-8
Endrin
0.002
106-93-4
Ethylene dibromide
0.00005
1071-53-6
Glyphosate
0.7
76-44-8
Heptachlor
0.0004
1024-57-3
Heptachlor epoxide
0.0002
118-74-1
Hexachlorobenzene
0.001
77-47-4
Hexachlorocyclopentadiene
0.05
58-89-9
Lindane
0.0002
72-43-5
Methoxychlor
0.04
23135-22-0
Oxamyl (vydate)
0.2
1918-02-1
Picloram
0.5
1336-36-3
Polychlorinated biphenyls
0.0005
87-86-5
Pentachlorophenol
0.001
122-34-9
Simazine
0.004
8001-35-2
Toxaphene
0.003
1746-01-6
2,3,7,8-TCDD (dioxin)
3 × 10-8
93-72-1
2,4,5-TP
0.05
(b)
				For the synthetic organic chemicals listed in this section other than TTHM:
(1) monitoring frequency is specified in
				section 5.1 of this rule; and
(2)
				analytical methods are specified in section 5.2 of this rule.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-5.1 - Collection of samples for organic chemical testing other than volatile organic compounds and total trihalomethanes

Current through July 10, 2024
Authority: IC 13-13-5; IC 13-14-8-7; IC 13-14-9; IC 13-18-3;
				  IC 13-18-16
Affected: IC 13-18
Sec. 5.1.
To determine compliance with section 5(a) of this rule,
				  collection of samples for organic chemical testing, other than volatile organic
				  compounds and TTHMs, shall be made as follows:
(1) Ground water systems shall take a minimum
				of one (1) sample at every entry point to the distribution system that is
				representative of each well after treatment (hereafter called a sampling
				point). Each sample must be taken at the same sampling point unless conditions
				make another sampling point more representative of each source or treatment
				plant.
(2) Surface water systems,
				including those systems with a combination of surface and ground sources, shall
				take a minimum of one (1) sample at points in the distribution system that are
				representative of each source or at each entry point to the distribution system
				after treatment (hereafter called a sampling point). Each sample must be taken
				at the same sampling point unless conditions make another sampling point more
				representative of each source or treatment plant.
(3) If the system draws water from more than
				one (1) source and the sources are combined before distribution, the system
				must sample at an entry point to the distribution system during periods of
				normal operating conditions, such as when water representative of all sources
				is being used.
(4) The monitoring
				frequency is as follows:
(A) Each CWS and
				NTNCWS shall take four (4) consecutive quarterly samples for each contaminant
				listed in section 5(a) of this rule during each compliance period beginning
				with the initial compliance period.
(B) Systems serving more than three thousand
				three hundred (3,300) persons that do not detect a contaminant in the initial
				compliance period may reduce the sampling frequency to a minimum of two (2)
				quarterly samples in one (1) year during each repeat compliance
				period.
(C) Systems serving less
				than or equal to three thousand three hundred (3,300) persons that do not
				detect a contaminant in the initial compliance period may reduce the sampling
				frequency to a minimum of one (1) sample during each repeat compliance
				period.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-5.4 - Volatile organic compounds; maximum contaminant levels for community water systems and nontransient noncommunity water systems

Current through July 10, 2024
Authority: IC 13-1-3-4; IC 13-7
Affected: IC 13-7
Sec. 5.4.
(a) The
				following MCLs for volatile organic compounds (VOCs) apply to community water
				systems and nontransient noncommunity water systems:
CAS No.
Contaminant
Level in Milligrams Per Liter
71-43-2
Benzene
0.005
75-01-4
Vinyl chloride
0.002
56-23-5
Carbon tetrachloride
0.005
107-06-2
1,2-dichloroethane
0.005
79-01-6
Trichloroethylene
0.005
75-35-4
1,1-dichloroethylene
0.007
71-55-6
1,1,1-trichloroethane
0.2
106-46-7
para-dichlorobenzene
0.075
156-59-2
cis-1,2-dichloroethylene
0.07
78-87-5
1,2-dichloropropane
0.005
100-41-4
Ethylbenzene
0.7
108-90-7
Monochlorobenzene
0.1
95-50-1
ortho-dichlorobenzene
0.6
100-42-5
Styrene
0.1
127-18-4
Tetrachloroethylene
0.005
108-88-3
Toluene
1
156-60-5
trans-1,2-dichloroethylene
0.1
1330-20-7
Xylenes (total)
10
75-09-2
Dichloromethane
0.005
120-82-1
1,2,4-trichlorobenzene
0.07
79-00-5
1,1,2-trichloroethane
0.005
(b)
				BAT for achieving compliance with the MCL for the volatile organic compounds
				listed in subsection (a) is:
(1) central
				treatment using packed tower aeration except toluene;
(2) central treatment using granular
				activated carbon for each chemical except vinyl chloride and dichloromethane;
				or
(3) other means available for
				achieving compliance with the maximum contaminant levels identified in
				subsection (a).
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-5.6 - Analytical methods for volatile organic compounds

Current through July 10, 2024
Authority: IC 13-13-5; IC 13-14-8-7; IC 13-14-9; IC 13-18-3;
				  IC 13-18-16
Affected: IC 13-18
Sec. 5.6.
(a)
				Analysis for the contaminants listed in section 5.5 of this rule shall be
				conducted using the following U.S. EPA methods or their equivalent as approved
				by EPA or with the alternative methods listed in Appendix A to Subpart C of 40
				CFR 141:
(1) Benzene, as described in Method
				502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(2) Carbon tetrachloride, as described in
				Method 502.2, Rev 2.1*, Method 524.2, Rev 4.1*, or Method 551.1, Rev
				1.0*.
(3) Chlorobenzene, as
				described in Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(4) 1,2-dichlorobenzene, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(5) 1,4-dichlorobenzene, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(6) 1,2-dichloroethane, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(7) cis-dichloroethylene, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(8) trans-dichloroethylene, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(9) Dichloromethane, as described in Method
				502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(10) 1,2-dichloropropane, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(11) Ethylbenzene, as described in Method
				502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(12) Styrene, as described in Method 502.2,
				Rev 2.1* or Method 524.2, Rev 4.1*.
(13) Tetrachloroethylene, as described in
				Method 502.2, Rev 2.1*, Method 524.2, Rev 4.1*, or Method 551.1, Rev
				1.0*.
(14) 1,1,1-trichloroethane,
				as described in Method 502.2, Rev 2.1*, Method 524.2, Rev 4.1*, or Method
				551.1, Rev 1.0*.
(15)
				Trichloroethylene, as described in Method 502.2, Rev 2.1*, Method 524.2, Rev
				4.1*, or Method 551.1, Rev 1.0*.
(16) Toluene, as described in Method 502.2,
				Rev 2.1* or Method 524.2, Rev 4.1*.
(17) 1,2,4-trichlorobenzene, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(18) 1,1-dichloroethylene, as described in
				Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(19) 1,1,2-trichloroethane, as described in
				Method 502.2, Rev 2.1*, Method 524.2, Rev 4.1*, or Method 551.1, Rev
				1.0*.
(20) Vinyl chloride, as
				described in Method 502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
(21) Xylenes (total), as described in Method
				502.2, Rev 2.1* or Method 524.2, Rev 4.1*.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-7 - Microbiological contaminants; maximum contaminant levels for all PWSs

Current through July 10, 2024
Authority: IC 13-13-5; IC
				  13-14-8-2;
				  IC
				  13-14-8-7; IC
				  13-18-3-1; IC
				  13-18-3-2;
				  IC
				  13-18-16-8; IC
				  13-18-16-9
Affected: IC 13-18-2; IC 13-18-16
Sec. 7.
(a) Until
				March 31, 2016, the total coliform MCL applies to all PWSs and is based on the
				presence or absence of total coliforms in a sample, rather than coliform
				density. The PWS is in compliance with the MCL for total coliforms if it meets
				the following:
(1) Not more than five and
				zero-tenths percent (5.0%) of the samples collected during a month are total
				coliform-positive for a PWS that collects at least forty (40) samples per
				month.
(2) Not more than one (1)
				sample collected during a month is total coliform-positive for a PWS that
				collects fewer than forty (40) samples per month.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-8 - Collection of samples for total coliform bacteria testing

Current through July 10, 2024
Authority: IC 13-13-5; IC
				  13-14-8-2;
				  IC
				  13-14-8-7; IC
				  13-18-3-1; IC
				  13-18-3-2;
				  IC
				  13-18-16-8; IC
				  13-18-16-9
Affected: IC 13-18-2; IC 13-18-16
Sec. 8.
(a) A PWS
				must collect total coliform samples at sites that are representative of water
				throughout the distribution system as follows:
(1) According to a written sample siting plan
				approved by the commissioner.
(2)
				Beginning on April I, 2016, each PWS, based on the population served by the
				PWS, must meet the monitoring requirements of 40 CFR 141, Subpart Y*.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-8.1 - Repeat monitoring for total coliform bacteria

Current through July 10, 2024
Authority: IC 13-13-5; IC
				  13-14-8-2;
				  IC
				  13-14-8-7; IC
				  13-18-3-1; IC
				  13-18-3-2;
				  IC
				  13-18-16-8; IC
				  13-18-16-9
Affected: IC 13-18-2; IC 13-18-16
Sec. 8.1.
(a) If a
				routine sample is total coliform-positive, the PWS must collect a set of repeat
				samples within twenty-four (24) hours of being notified by the laboratory or
				the commissioner of the positive result. The provisions of this section are
				applicable until all required repeat monitoring under this section and fecal
				coliform or E. coli testing required under section 8.3 of this rule that was
				initiated by a total coliform positive sample taken before April 1, 2016, is
				completed as well as analytical method, reporting, record keeping, public
				notification, and consumer confidence report requirements associated with that
				monitoring and testing. The following apply to repeat monitoring:
(1) A PWS that collects:
(A) more than one (1) routine sample per
				month must collect no fewer than three (3) repeat samples for each total
				coliform-positive sample found; or
(B) one (1) routine sample per month or fewer
				must collect no fewer than four (4) repeat samples for each total
				coliform-positive sample found.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-8.2 - Sanitary surveys

Current through July 10, 2024
Authority: IC 13-13-5; IC
				  13-14-8-2;
				  IC
				  13-14-8-7; IC
				  13-8-3-1; IC
				  13-18-3-2;
				  IC
				  13-18-16-8; IC
				  13-18-16-9
Affected: IC
				  13-13-5-2;
				  IC 13-18-2; IC 13-18-11; IC 13-18-16
Sec. 8.2.
(a) The
				following conditions apply to the conducting of sanitary surveys:
(1) Beginning on:
(A) January 1, 2002, a Subpart H system must
				undergo a sanitary survey every three (3) years; and
(B) December 1, 2009:
(i) a CWS using ground water must undergo a
				sanitary survey every three (3) years; and
(ii) an NCWS using ground water must undergo
				a sanitary survey every five (5) years.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-8.3 - Collection of samples for fecal coliforms or E. coli testing

Current through July 10, 2024
Authority: IC 13-13-5; IC
				  13-14-8-2;
				  IC
				  13-14-8-7; IC
				  13-18-3-1; IC
				  13-18-3-2;
				  IC
				  13-18-16-8; IC
				  13-18-16-9
Affected: IC 13-18-2; IC 13-18-16
Sec. 8.3.
(a) The
				provisions of this section are applicable to a PWS until all required repeat
				monitoring under section 8.1 of this rule and fecal coliform or Escherichia
				coli (E. coli) testing required under this section that was initiated by a
				total coliform positive sample taken before April 1, 2016, is completed as well
				as analytical method, reporting, record keeping, public notification, and
				consumer confidence report requirements associated with that monitoring and
				testing.
(b) If any routine or
				repeat sample is total coliform-positive, the PWS must do the following:
(1) Analyze the total coliform-positive
				culture medium to determine if fecal coliforms are present, except that the PWS
				may test for E. coli in lieu of fecal coliforms.
(2) If fecal coliforms or E. coli are
				present, the PWS shall notify the commissioner by the end of the same business
				day that the PWS is notified of the test results.
(3) If the PWS is notified of the result
				after the close of business, the PWS shall notify the commissioner before the
				end of the next business day.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-8.5 - Requirement for filtration and disinfection

Current through July 10, 2024
Authority: IC 13-13-5-1; IC 13-14-8-2; IC 13-14-8-7; IC
				  13-18-3-2
Affected: IC 13-12-3-1; IC 13-13-5-2; IC 13-14-9; IC
				  13-18-11
Sec. 8.5.
(a)
				Effective June 29, 1993, a public water system that uses a surface water source
				must provide filtration in accordance with this section.
(b) A public water system that uses a ground
				water source under the direct influence of surface water shall provide
				filtration in accordance with this section beginning eighteen (18) months after
				the commissioner determines that it is under the direct influence of surface
				water from the date specified in section 8.2 of this rule.
(c) A public water system that uses a surface
				water source or a ground water source under the direct influence of surface
				water must provide treatment consisting of both disinfection, as specified in
				section 8.6 of this rule, and filtration treatment. Filtration treatment shall
				be done by one (1) of the following techniques, and the turbidity level of
				representative samples of a system's filtered water, regardless of filtration
				technique used, shall at no time exceed five (5) nephelometric turbidity units
				(NTU) in any given sample, measured as specified in section 8.7 of this rule:
(1) For systems using conventional filtration
				or direct filtration, the turbidity level of representative samples of a
				system's filtered water must be less than or equal to one-half (0.5) NTU in at
				least ninety-five percent (95%) of the total number of measurements taken each
				month, measured as specified in sections 8.7(4) and 8.8(b) of this rule, except
				that if the commissioner determines that the system is capable of achieving at
				least ninety-nine and nine-tenths percent (99.9%) removal or inactivation, or
				both, of Giardia lamblia cysts at some turbidity level higher than one-half
				(0.5) NTU in at least ninety-five percent (95%) of the total number of
				measurements taken each month, the commissioner may substitute this higher
				turbidity limit for that system. However, in no case may the commissioner
				approve a turbidity limit that allows more than one (1) NTU in more than five
				percent (5%) of the samples taken each month, measured as specified in sections
				8.7(4) and 8.8(b) of this rule. Upon the effective date of this rule, systems
				serving a population of:
(A) at least ten
				thousand (10,000) individuals; and
(B) beginning January 1, 2005, fewer than ten
				thousand (10,000) individuals;
shall meet the turbidity requirements in
				  327 IAC
				  8-2.6-3.
Indiana Administrative Code › Title 327 - WATER POLLUTION CONTROL DIVISION › Article 8 - PUBLIC WATER SUPPLY › Rule 2 - Drinking Water Standards › Section 2-8.6 - Disinfection treatment

Current through July 10, 2024
Authority: IC 13-13-5-1; IC 13-14-8-7; IC 13-18-3; IC
				  13-18-16
Affected: IC 13-18
Sec. 8.6.
Effective June 29, 1993, each PWS that provides filtration
				  treatment must provide disinfection treatment as follows:
(1) The disinfection treatment must be
				sufficient to ensure that the total treatment processes of that system achieve:
(A) at least ninety-nine and nine-tenths
				percent (99.9%) (3-log) inactivation or removal of Giardia lamblia cysts;
				and
(B) at least ninety-nine and
				ninety-nine hundredths percent (99.99%) (4-log) inactivation or removal of
				viruses, as determined by the commissioner.