reglab/statecodes huggingface dataset:
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7047b - Capacity

Current through Vol. 24-12, July 15, 2024
Rule 47b. Section 5.3.1.10.1 of the ASME A17.1 is amended
						to read as follows: 5.3.1.10.1. The maximum inside net platform area shall not
						exceed 1.7m2 (18 ft2).
						The minimum rated load shall be not less than the following:
(a) For net platform areas up to and
					 including 1.1 m2 (12
					 ft2), the rated load shall be not less than 195
					 kg/m2 (40 lb/ft2) or 159
					 kg (350 lb), whichever is greater.
(b) For net platform areas greater than 1.1
					 m2 (12 ft2), the rated
					 load shall be based upon 305 kg/m2 (62.5
					 lb/ft2).
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7048 - Buffers and buffer supports

Current through Vol. 24-12, July 15, 2024
Rule 48. Section 5.3.1.14.1 of the ASME A17.1 code is
						amended to read as follows:
5.3.1.14.1
					 The car and counterweight shall be provided with spring or equivalent type
					 buffers. They shall be designed and installed so that they will not be fully
					 compressed when struck by car with its rated load or by the counterweight
					 traveling at 125% of the rated speed, or at governor tripping speed where a
					 governor-operated safety is used.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7048a - Rupture or overspeed valve

Current through Vol. 24-12, July 15, 2024
Rule 48a. Section
						5.3.2.2.2 of the ASME A17.1 code is
						amended to read as follows: A pressure switch must be provided to remove power
						from the pump motor and the control valve unless there is positive pressure at
						the control valve.
A rupture or overspeed valve must be provided on all
						roped hydraulic jacks, either cable or chain, to stop the flow of fluid and
						arrest the descent of the car in the event of line or pipe
						rupture.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7049 - Buffers

Current through Vol. 24-12, July 15, 2024
Rule 49. Section 5.4.10.1 of the ASME A17.1 code is
						amended to read as follows:
5.4.10.1
					 For rated speeds not exceeding 0.25 m/s (50 ft/min), spring or equivalent type
					 buffers are required. Bumpers or solid stops shall not be permitted.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7051 - Type of operation

Current through Vol. 24-12, July 15, 2024
Rule 51. Section 5.4.15.1 of the ASME A17.1 code is
						amended to read as follows:
5.4.15.1.
					 The inclined elevator shall be operated by weatherproof constant pressure key
					 switches or constant pressure switch or button at each landing and on the car.
					 Key-operated switches shall be of the spring-return type and shall be operated
					 by a cylinder type lock having not less than 5-pin or 5-disk combination with
					 the key removable only when the switch is in the off position. Constant
					 pressure switches and buttons shall be hand operated and controlled by an
					 adjacent on-off key switch with the key removable only when the key is in the
					 off position. The key shall be group 4 security in compliance with section
					 8.1 of the
					 ASME A17.1 code.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7052 - Electrical equipment and wiring requirements

Current through Vol. 24-12, July 15, 2024
Rule 52. Section 5.4.15.5.1 of the ASME A17.1 code is
						amended to read as follows:
5.4.15.5.1. All electrical equipment and
					 wiring shall conform to the requirements of the Michigan electrical code and
					 ASME A17.1 sections 5.3.1.18.4, 5.3.1.18.5 and 5.3.1.18.6. A fused disconnect
					 switch or a circuit breaker shall be installed within the machine enclosure and
					 connected to the power supply line to each electric motor. A hoisting motor
					 shall have a manually reset type of electrical overload device.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7054 - Skirt deflector devices

Current through Vol. 24-12, July 15, 2024
Rule 54. Section
						6.1.3.3.10 of the ASME A17.1 code
						is amended to read as follows:
6.1.3.3.10 Deflector devices are permitted.
					 Where provided, deflector devices must extend from skirt panels parallel to the
					 escalator path of travel. Means to secure these deflector devices may be on the
					 exposed surface of the skirt. All fasteners must be of steel with machine screw
					 threads. Any exposed fastener heads shall be of the tamper-resistant type and
					 flush to within 1 mm, or 0.04 inch
(1) Rigid
					 elements must comply with the following conditions:
(a) Horizontal protrusions extending above
					 the step must be 18 mm, or 0.75 inch maximum. Corners or changes in profile
					 must be rounded or beveled.
The exposed surfaces of such elements must be smooth and
						permanently treated with a low-friction material.
(b) On the incline, the area of any
					 protrusion must lie entirely offset outward from a line beginning on the
					 vertical portion of the skirt panel measured 25 mm, or 1 inch vertically above
					 the step nose line. The lower surface must be beveled not less than 10 degrees
					 upward and the upper surface must be beveled not less than 15 degrees downward
					 in compliance with Figure 6.1.3.3.10 of the ASME A17.1 code.
(c) At the upper and lower landing, any
					 protrusion must lie entirely above a line beginning on the vertical portion of
					 the skirt panel 50 mm, or 2 inches, above the step nose line. The lower surface
					 must be beveled not less than 10 degrees upward and the upper surface must be
					 beveled not less than 15 degrees downward. Any rigid elements at the landings
					 must smoothly blend into the rigid elements along the incline in accordance
					 with the radius of curvature of the transition zone.
(d) If attached to the skirt, rigid elements
					 must withstand a force of 900 N (200 lbf) perpendicular to the line of
					 attachment of the element without detachment or permanent deformation. The
					 force shall be applied to an area of 645 mm' (1 inch').
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7054b - Listed and certified devices

Current through Vol. 24-12, July 15, 2024
Rule 54b. Section
						8.6.3.7.2
						is amended to the ASME A17.1 code to read as follows:
8.6.3.7.2 Where a listed or certified device
					 or component is replaced, the replacement shall be manufactured to the
					 specifications at the time the device or component was originally certified,
					 engineering tested or type tested in accordance with section
					 8.3
					 of the ASME A17-1 code. Upon request, the contractor shall provide the
					 department supporting documentation of compliance with the original
					 specifications. Documents shall be signed and sealed by a licensed professional
					 engineer acting within his or her discipline.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7055 - Record of oil usage

Current through Vol. 24-12, July 15, 2024
Rule 55. Section
						8.6.5.7
						of the ASME A17.1 code is amended to read as follows:
8.6.5.7. For systems where part of the
					 cylinder or piping, or both, are not exposed for visible inspection, a written
					 record shall be kept of the quantity of hydraulic fluid added to the system and
					 emptied from leakage collection containers and pans. The written record shall
					 be kept in the machine room. If the quantity of hydraulic fluid loss cannot be
					 accounted for, then the test specified in section 8.6.5.15.3 of
					 R 408.7060 shall be done.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7055a - Periodic test

Current through Vol. 24-12, July 15, 2024
Rule 55a. Section
						8.6.7.4.1
						of the ASME A17.1 code is amended to read as follows:
8.6.7.4.1.
(1) Private residence inclined elevators and
					 lifts should be subject to the periodic tests specified in 8.6.4.19, 8.6.4.20,
					 and 8.6.4.14 to 8.6.5.16. The test requirements shall apply to the
					 corresponding requirements in 5.4. Any additional requirements for this
					 equipment should also be checked during these tests.
(2) Private residence inclined elevators
					 installed under the requirements of the act for use by multiple, shall be
					 subject to the periodic tests specified in 8.6.4.19, 8.6.4.20, and 8.6.5.14 to
					 8.6.5.16. The test requirements shall apply to the corresponding requirements
					 in 5.4. Any additional requirements for this equipment shall also be checked
					 during these tests.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7056 - Firefighters' emergency operation

Current through Vol. 24-12, July 15, 2024
Rule 56. Section
						8.6.11.1
						of the ASME A17.1 code is amended to read as follows:
8.6.11.1. All elevators provided with
					 firefighters' emergency operation shall be subjected quarterly to phase I
					 recall by use of the key switch, and a minimum of 1-floor operation on phase
					 II. Deficiencies shall be corrected. An accessible written record of test
					 results shall be maintained in the machine room.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7057 - Applicability of alteration requirements

Current through Vol. 24-12, July 15, 2024
Rule 57. Section
						8.7.1.1 of the ASME A17.1 code is
						amended to read as follows:
8.7.1.1
(1) If an alteration is performed to the
					 elevator or any of its subsystems, regardless of any other requirements of
					 section 8.7 of the ASME A17.1 code, then
					 the alteration, at a minimum, must conform to both of the following
					 requirements:
(a) This state's elevator laws
					 and rules at the time of installation.
(b) This state's elevator laws and rules for
					 the alteration at the time of any alteration.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7057a - Bottom car clearances

Current through Vol. 24-12, July 15, 2024
Rule 57a. Section
						2.15.9.2(c) of ASME A17.1 is
						amended to read as follows:
2.15.9.2(c). Where the installation is the
					 result of replacement or alteration utilizing an existing hoistway and pit, the
					 toe guard may be reduced in length utilizing an existing hoistway and pit,
					 provided the car speed does not exceed 150 feet per minute. The toe guard may
					 be reduced in length proportionate to the maximum length the pit depth will
					 allow complying with section
					 2.4.1.5. At no time may the toe
					 guard be shorter than the leveling or truck zone plus 75mm, or 3
					 inches.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7058 - Cylinders

Current through Vol. 24-12, July 15, 2024
Rule 58. Section
						8.7.3.23.3
						of the ASME A17.1 code is amended to read as follows: 8.7.3.23.3. Where a
						cylinder is installed, replaced, or altered, it shall conform to section 3.18.3
						of the ASME A17.1 code. Sleeving of a cylinder shall not be permitted. If the
						plunger is not equipped with a stop ring conforming to section 3.18.4.1 of the
						ASME A17.1 code, the installation shall also conform to sections 3.18.1.2 and
						3.18.2 of the ASME A17.1 code.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7058a - Escalator electrical protective devices

Current through Vol. 24-12, July 15, 2024
Rule 58a. Section
						6.1.6.3 of the ASME A17.1 code is
						amended to read as follows:
6.1.6.3.
					 Electrical protective devices must be provided pursuant to 6.1.6.3 through
					 6.1.6.3.16 and be the manually resetting type. Automatic resetting of a safety
					 device within these codes is prohibited.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7058b - Moving walk electrical protective devices

Current through Vol. 24-12, July 15, 2024
Rule 58b. Section
						6.2.6.3 of the ASME A17.1 code is
						amended to read as follows:
6.2.6.3.
					 Electrical protective devices must be provided pursuant to 6.2.6.3.1 through
					 6.2.6.3.12 and be the manually resetting type. Automatic resetting of a safety
					 device within these codes is prohibited.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7058c - Escalator handrail speed-monitoring device

Current through Vol. 24-12, July 15, 2024
Rule 58c. Requirement 6.1.6.4 of the ASME A17.1 code is
						amended to read as follows: A handrail speed monitoring device must be provided
						that will cause the activation of the alarm required by 6.1.6.3.1(b) without
						any intentional delay, whenever the speed of either handrail deviates from the
						step speed by 15% or more. The device must also cause electric power to be
						removed from the driving-machine motor and brake when the speed deviation of
						15% or more is continuous within a 2 s to 6 s range. The device must be of the
						manual reset type. Automatic resetting of a safety device within these codes is
						prohibited.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7058d - Moving walk handrail speed-monitoring device

Current through Vol. 24-12, July 15, 2024
Rule 58d. Requirement 6.2.6.4 of the ASME A17.1 code is
						amended to read as follows: A Handrail Speed Monitoring Device must be provided
						that will cause the activation of the alarm required by 6.2.6.3.1(b) without
						any intentional delay whenever the speed of either handrail deviates from the
						treadway speed by 15% or more. The device must also cause electric power to be
						removed from the driving-machine motor and brake when the speed deviation of
						15% or more is continuous within a 2 s to 6 s range. The device must be of the
						manual reset type. Automatic resetting of a safety device within these codes is
						prohibited.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7059 - Acceptance inspection and tests

Current through Vol. 24-12, July 15, 2024
Rule 59. Section 8.10.1.1.1 of the ASME A17.1 code is
						amended to read as follows:
8.10.1.1.1. The acceptance inspection shall
					 be made by an inspector employed by the authority having jurisdiction. All
					 parts of the installation shall be inspected for conformity with the
					 requirements of the Michigan elevator laws and rules and section 8.10 of the
					 ASME A17.1 code. The American society of mechanical engineers A17.2-2012, guide
					 for inspection of elevators, escalators, and moving walks, ASME, a copy of
					 which is adopted by reference in
					 R
					 408.7024, is recommended as a guide in making the
					 inspection. Balance load and maximum normal speeds with maximum rated load and
					 no load shall be determined and recorded on forms furnished by the
					 department.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7059a - Periodic test tags

Current through Vol. 24-12, July 15, 2024
Rule 59a. Section
						8.10.1.1.1 of the ASME A17.1 code
						is amended to read as follows:
8.10.1.1.1. The acceptance inspection must be
					 made by an inspector employed by the authority having jurisdiction. All parts
					 of the installation must be inspected for conformity with the requirements of
					 this state's elevator laws, these rules, and section
					 8.10 of the ASME A17.1 and ASME
					 17.2. An approved paper tag must be installed in the machine room or machine
					 space for all periodic tests.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7060 - Three-year inspection and test requirements

Current through Vol. 24-12, July 15, 2024
Rule 60. Section
						8.6.5.15.3 is added to the ASME
						A17.1 code to read as follows:
8.6.5.15.3.
(1) Cylinders must be tested at intervals of
					 not more than 36 months.
(2)
					 Three-year inspection and test requirements are as follow:
(a) The relief valve setting must comply with
					 section 3.19.4.2 of the ASME A17.1 code.
					 The relief valve must be resealed if the relief valve setting is altered or if
					 the seal is broken.
(b) Test the
					 relief valve setting by first inching the empty car upward to engage the
					 plunger stop ring or to engage other suitable blocking provided and then apply
					 pressure from the pump to check the setting. A copy of test forms must be
					 maintained on site in the machine room or space available to elevator personnel
					 pursuant to section
					 8.6.1.4.1 of ASME A17.1. Procedures
					 for set test are as follows:
(i) Put rated
					 load in the car and locate it at any convenient level.
(ii) Open the disconnect switch and locate
					 the elevation of the platform with respect to a convenient reference.
(iii) For cylinders that are not completely
					 exposed, after not less than 2 hours, note the position of the platform with
					 respect to the chosen reference. For cylinders that are completely exposed,
					 after not less than 30 minutes, note the position of the platform with respect
					 to the chosen reference. A change in the car position during a cylinder test
					 that cannot be accounted for by visible oil leakage or temperature change of
					 the oil indicates a failure of some type requiring further inspections, tests,
					 or repairs. An accessible written record of all oil levels and all oil added
					 must be maintained in the machine room.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 3 - ASME A17.1 MODIFICATIONS › Section R. 408.7060a - Private residence elevators and private residence inclined elevators

Current through Vol. 24-12, July 15, 2024
Rule 60a. Section
						8.11.5.2
						of the ASME A17.1 code is amended to read as follows:
8.11.5.2.
(1) Private residence elevators should be
					 subject to the periodic inspections specified in 8.11.2 and 8.11.3. The
					 inspection requirements shall apply to the corresponding requirements in 5.3
					 and 5.4. Any additional requirements for this equipment should also be checked
					 during these inspections.
(2)
					 Private residence inclined elevators installed under the requirements of the
					 act for use by multiple residences, shall be subject to the periodic
					 inspections specified in 8.11.2 and 8.11.3. The inspection requirements shall
					 apply to the corresponding requirements in 5.3 and 5.4. Any additional
					 requirements for this equipment shall also be checked during these
					 inspections.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 4 - ASME A18.1 MODIFICATIONS › Section R. 408.7061 - Runway enclosure

Current through Vol. 24-12, July 15, 2024
Rule 61. Section
						2.1.1.1 of
						the ASME A18.1 code is amended to read as follows:
2.1.1.1 The runway shall be guarded by a
					 solid enclosure extending from the lowest landing to a height at least equal to
					 the height of the platform enclosure above the uppermost landing, in no case
					 less than 42 inches (1067 mm) above the uppermost landing. The enclosure shall
					 withstand, without permanent deformation, a force of 125 lbf (556 n) applied on
					 any 4 inch (102 mm) by 4 inch (102 mm) area. The interior of the runway
					 enclosure shall present a smooth surface.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 4 - ASME A18.1 MODIFICATIONS › Section R. 408.7062 - Runway entrance

Current through Vol. 24-12, July 15, 2024
Rule 62. Section
						2.1.1.2 of the ASME A18.1 code is
						amended to read as follows: 2.1.1.2 The runway entrance must be guarded at the
						upper landing by a door of unperforated construction not wider than the
						platform plus 1 inch, or 25.4 millimeters. The door must be self-closing or
						power operated and guard the entire opening to a height equal to or higher than
						the height of the platform enclosure. The openings created in the runway by
						these doors must provide a minimum vertical clearance of 6 feet 8 inches. The
						doors must guard the entire area of the openings except for space necessary for
						operation. Space necessary for operation must reject a ball 12 mm, or 0.5
						inches
,
in diameter. The lift side of the landing doors and sill
						must present a smooth surface located not closer than 10 mm, or 0.375 inches,
						or more than 20 mm, or 0.75 inches, from the platform floor.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 4 - ASME A18.1 MODIFICATIONS › Section R. 408.7062a - Portable and temporary vertical platform lifts

Current through Vol. 24-12, July 15, 2024
Rule 62a. Section
						2.1.3 of the
						ASME A18.1 code is amended to read as follows:
2.1.3 Portable and temporary vertical
					 platform lifts may only be installed for temporary use and shall meet all of
					 the following conditions:
(a) The portable or
					 temporary platform lift may only be in place and in use for a maximum of 14
					 days. The 14 days begin on the date of the approval, which is given at the time
					 of the installation inspection by the elevator safety division. The lift shall
					 be removed from the site on or before the 16th day. In special situations a 1
					 time renewal may be granted by the department.
(b) The lift shall be attendant-operated in
					 accordance with the requirements of 2.10.2.
(c) A key operated switch shall be provided
					 at the operator station which will allow the up and down control switches to
					 become effective only when the key is in the on position. The key operated
					 switch shall be operated by a lock having 5-pin or 5-disk combination with a
					 key removable only in the off position. Anytime the lift is not being operated,
					 the key switch shall be in the off position and the key shall be
					 removed.
(d) The platform lift
					 shall be positioned to prevent lateral movement during use.
(e) Site specific drawings, which clearly
					 show the location of the lift with regards to the area to be accessed, shall be
					 submitted with the permit application.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 4 - ASME A18.1 MODIFICATIONS › Section R. 408.7066 - Guarding

Current through Vol. 24-12, July 15, 2024
Rule 66. Section 5.1.1.2 of the ASME A18.1 code is
						amended to read as follows:
5.1.1.2 A
					 smooth vertical fascia of unperforated construction shall be provided from the
					 top terminal landing sill and any intermediate landing sill to the level of the
					 bottom terminal landing sill. Openings necessary for operation shall reject a
					 ball 12 mm (0.5 in.) diameter. The fascia shall be equal to or stronger than
					 1.5 mm (0.0598 in.) sheet steel and guard the full width of the platform. The
					 surface shall not be permanently deformed when a force of 550 N (125 lbf) is
					 applied on any 100 mm (4 in.) by 100 mm (4 in.) area.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 4 - ASME A18.1 MODIFICATIONS › Section R. 408.7068 - Inspection and test requirements for altered installations

Current through Vol. 24-12, July 15, 2024
Rule 68. Section 10.5 of the ASME A18.1 code is amended
						to read as follows:
10.5
(1) If any alteration is performed,
					 regardless of any other requirements of the standard, then the installation, at
					 a minimum, shall conform to the requirements of the Michigan elevator laws and
					 rules and the applicable code requirements.
(2) The alteration shall not begin until a
					 permit is obtained from the department and the elevator shall not be placed
					 into service until it has been inspected and tested in the presence of a
					 general elevator inspector, except as provided in section 15 of the
					 act.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 5 - ASME A90-1 MODIFICATIONS › Section R. 408.7069 - Applicability of national standard and rules of board

Current through Vol. 24-12, July 15, 2024
Rule 69.
(1)
					 This rule applies to manlifts, as described in the ASME A90.1-2009, which is
					 adopted by reference in
					 R
					 408.7003, that are used only to carry plant personnel
					 in granaries, flour mills, parking garages, and similar buildings or
					 occupancies. Belt manlifts shall not be used by the public and, if located in
					 buildings to which the public has access, shall be located in an enclosure that
					 is protected by self-closing, spring-locked doors. Keys to the doors shall be
					 available to employees. The use of belt manlifts during construction is
					 prohibited.
(2) The hoistway
					 enclosure shall comply with the Michigan building code,
					 R
					 408.30401 to
					 R
					 408.30547, and shall maintain the fire rating of the
					 structure.
(3) The travel of any
					 single belt manlift installed after February 14, 1968 shall not exceed 100
					 feet.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7071 - Location

Current through Vol. 24-12, July 15, 2024
Rule 71. Section
						5.4.8 of the ANSI A10.4 standard is
						amended to read as follows: 5.4.8.
(1)
					 A personnel hoist must be installed not less than 10 feet from any other
					 lifting or lowering apparatus except other personnel hoists.
(2) A hoistway may not be located either
					 partially or wholly over sidewalks or passageways.
(3) If tower cranes or any other lifting or
					 lowering apparatus are installed such that the boom, load, or trolley may go
					 over or into the 10-foot restricted area, then the personnel hoist must be
					 unoccupied anytime the boom
,
or trolley passes over the restricted
					 area. The evacuation of the personnel hoist must be the responsibility of the
					 crane operator and the general contractor.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7072 - Hoistway doors and gates

Current through Vol. 24-12, July 15, 2024
Rule 72. Section
						6.2.2
						of the ANSI A10.4 standard is amended to read as follows:
6.2.2
(1)
					 Each hoistway door shall be equipped with an approved interlock.
(2) Sliding doors and gates shall be
					 constructed of metal and shall be of a design which will reject a ball 1-1/2
					 inches in diameter.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7074 - Car enclosure tops

Current through Vol. 24-12, July 15, 2024
Rule 74. Section 17.7 of the ANSI A10.4 standard is
						amended to read as follows:
17.7 Tops
					 of car enclosures shall be so designed and installed to be capable of
					 sustaining a load of 300 pounds (136 kg) on any square area 2 feet (0.6 m) on a
					 side and 100 pounds (45 kg) applied at any point. Simultaneous application of
					 these loads is not required. The personnel hoist shall have overhead protection
					 equivalent to 2-inch plank. The planks shall be secured.
The exit cover shall be hinged and locked and open
						outward.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7075 - Use of winding drum machines

Current through Vol. 24-12, July 15, 2024
Rule 75. Section 22.2 of the ANSI A10.4 standard is
						amended to read as follows:
22.2
					 Winding drum machines may be used irrespective of car travel if the drums are
					 grooved for hoisting wire rope. Grooves shall be machine finished and shall be
					 of the helical or parallel type. Only 1 layer of rope may be on the
					 drum.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7076 - Car speed

Current through Vol. 24-12, July 15, 2024
Rule 76. Section 22.3 of the ANSI A10.4 standard is
						amended to read as follows:
22.3 The
					 rated speed shall not be more than 300 feet per minute.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7077 - Emergency stop switch

Current through Vol. 24-12, July 15, 2024
Rule 77. Section
						24.2.4
						of the ANSI A10.4 standard is amended to read as follows:
24.2.4 An emergency stop switch shall be
					 provided in the car and located in or adjacent to the car operating panel. When
					 opened, the switch shall cause the electric power to be removed from the hoist
					 driving-machine motor and brake. Emergency stop switches shall have all of the
					 following characteristics:
(1) Manually
					 opened and closed type.
(2) Red
					 operating handles or buttons.
(3)
					 Conspicuously and permanently marked "stop."
(4) Positively opened mechanically and the
					 opening shall not be solely dependent on springs.
(5) Capability of being locked out of use
					 when the operator leaves the car.
(6) Operation of the emergency stop switch
					 shall not require manual resetting of the control panels.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7078 - Voltages permitted in hoistway or on car

Current through Vol. 24-12, July 15, 2024
Rule 78. Section
						24.3.1 of the
						ANSI A10.4 standard is amended to read as follows:
24.3.1 The maximum system or circuit
					 potential permitted on any equipment in the hoistway or on the car shall be not
					 more than 600 volts. If the potential exceeds 120 volts, then either a
					 grounding conductor shall be incorporated in the traveling cable or a separate
					 grounding conductor shall be installed. A visual indicator shall be included in
					 the grounding circuit, so arranged as to indicate continuously the continuity
					 of the grounding conductor. The type and size of the grounding conductor and
					 the grounding fastening means shall conform to the requirements of the Michigan
					 electrical code. The grounding circuit shall include a device which will
					 interrupt the electric circuit to the load if a ground fault occurs.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7079 - Rated load safety test

Current through Vol. 24-12, July 15, 2024
Rule 79. Section
						26.4.8 of the ANSI A10.4 standard
						is amended to read as follows:
26.4.8 A
					 rated load safety test, as required by section
					 26.2.1.1 of the ANSI A10.4
					 standard, must be performed by a licensed elevator contractor in the presence
					 of a general elevator inspector every 90 days. Periodic inspections may be
					 conducted every 30 days and the appropriate fees assessed at the discretion of
					 the department.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7080 - Operation

Current through Vol. 24-12, July 15, 2024
Rule 80. Section 30 of the ANSI A10.4 standard is amended
						to read as follows:
30 Hoists shall be operated in compliance with the
						manufacturing specifications, rules and recommendations, and with the governing
						authority. This shall consist of items, functions, and criteria pertaining to
						the hoist use and shall be a part of an operational maintenance and inspection
						log. Either of the following signal systems shall be provided:
(a) An approved signal device to enable
					 persons on each landing to signal the operator to stop and an emergency bell to
					 signal the operator to return to the bottom landing.
(b) An approved type voice communication
					 system between the car and landings and the project manager or job site
					 superintendent's office.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7081 - Authorized uses

Current through Vol. 24-12, July 15, 2024
Rule 81. Section 30.1 of the ANSI A10.4 standard is
						amended to read as follows:
30.1
(1) Only workers and other authorized
					 personnel associated with the work being done may ride on a personnel
					 hoist.
(2) A personnel hoist may be
					 used for carrying materials if it is designed and installed for the type of
					 load to be used and if no passengers are carried during the time materials are
					 being carried except those necessary to handle the materials.
(3) The load on a personnel hoist shall not
					 exceed the maximum rated load established by the department.
(4) Hoists shall be operated by competent,
					 qualified, and authorized personnel using manual operating devices of the
					 continuous pressure type located inside the hoist car only.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 6 - ANSI A10.4 MODIFICATIONS › Section R. 408.7081a - Operators

Current through Vol. 24-12, July 15, 2024
Rule 81a. Section
						30.3 of the ANSI A10.4 standard is
						amended to read as follows:
30.3 The
					 user shall ensure that the operators are knowledgeable and capable of
					 performing the duties outlined in the operating manual and are capable of
					 recording such activity in their log. A list certifying the training of any
					 operator must be kept in the on-site documentation. Only authorized personnel
					 listed in that document may operate the lift.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7082 - Applicability

Current through Vol. 24-12, July 15, 2024
Rule 82. The rules in this subpart apply to electric
						powered elevators used in sewage lift stations.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7083 - Public access

Current through Vol. 24-12, July 15, 2024
Rule 83. A sewage lift station personnel elevator shall
						not be accessible to the general public and shall be limited to use by
						employees only.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7084 - Location, counterweights, and speed

Current through Vol. 24-12, July 15, 2024
Rule 84.
(1) The
					 elevator may be installed in the entrance well.
(2) When counterweights and buffers are
					 provided, the applicable rules shall apply.
(3) The rated speed of a car shall not exceed
					 35 feet per minute.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7085 - Guarding exposed equipment

Current through Vol. 24-12, July 15, 2024
Rule 85. Exposed gears, sprockets, tape or rope sheaves,
						drums of selectors, floor controllers, signal machines and the ropes, chains or
						tapes for driving them shall be guarded to protect against accidental
						contact.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7086 - Supports and foundations

Current through Vol. 24-12, July 15, 2024
Rule 86.
(1)
					 Machines, machinery, and sheaves shall be supported and maintained in place so
					 as to prevent any part from becoming loose or displaced.
(2) Supporting beams shall be of steel. Beams
					 are not required under machines, sheaves and machinery, or control equipment
					 which are supported on floors provided that the floors are designed and
					 installed to support the load imposed on the floor.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7087 - Distance from car platform to floor level

Current through Vol. 24-12, July 15, 2024
Rule 87. The distance from the top of a car platform at
						the lowest landing shall be not more than 20 inches above the floor level. The
						means of descent from the car platform shall not constitute a
						hazard.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7088 - Car and counterweight clearances

Current through Vol. 24-12, July 15, 2024
Rule 88.
(1) If
					 a car platform is level with the lowest landing, then the car buffer striker
					 plates shall not be in contact with the buffers.
(2) If the car is at its extreme limit of
					 normal travel, then there shall be not less than 6 inches between the top of
					 the car crosshead and the nearest obstruction.
(3) If the counterweights are resting on
					 their buffers, then there shall be not less than 3 inches between the top of
					 the car crosshead and the nearest obstruction.
(4) If the car is resting on its buffers
					 there shall be not less than 3 inches clearance between the top of the
					 counterweights and the nearest obstruction.
(5) The clearances between the car and the
					 hoistway enclosure, hoistway sill, or any obstruction shall be not less than
					 3/4 inch.
(6) The clearance between
					 the car platform sill and hoistway edge shall be not more than 5
					 inches.
(7) The underside of a
					 projection into the hatch shall be beveled at an angle of not less than 75
					 degrees with the horizontal unless protected by a safety device to stop the
					 ascending car.
(8) The top of the
					 lower landing entrance shall be provided with a safety device to stop the
					 ascending car if for any reason an overhanging obstruction on the car comes in
					 contact with a shear hazard.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7089 - Landing openings

Current through Vol. 24-12, July 15, 2024
Rule 89.
(1) If
					 an upper landing side entrance door is provided, then the entrance shall be not
					 less than 6 1/2 feet in height.
(2)
					 The top of the hoistway shall be provided with an overlapping, self-locking
					 hinged cover designed to lock the closed side entrance door when the lift
					 station is unoccupied.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7090 - Locking devices

Current through Vol. 24-12, July 15, 2024
Rule 90.
(1) The
					 hinged cover and the upper landing side entrance door, when provided, shall be
					 provided with a mechanical latch and an electrical contact designed to be
					 operated from inside the hoistway.
(2) A locking device shall be provided to
					 prevent the top hinged cover from locking the upper landing side entrance door
					 when the lift station is occupied.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7091 - Guide rails

Current through Vol. 24-12, July 15, 2024
Rule 91.
(1) A
					 car and counterweight shall be provided with guide rails of steel.
(2) A guide rail shall be securely fastened
					 with through bolts or clips of strength, design, and spacing as follows:
(a) A guide rail and its fastenings shall not
					 deflect more than 1/4 inch under normal operations.
(b) A guide rail and its fastenings shall
					 withstand the application of the safety when stopping the car with a rated load
					 or when stopping the counterweights.
(c) A guide rail shall rest on supports and
					 extend at the top of the hoistway to prevent the guide shoes from running off
					 the guide rail if the car or the counterweight travels beyond the terminal
					 landings.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7092 - Frames, enclosures, platforms, capacity, and final limits

Current through Vol. 24-12, July 15, 2024
Rule 92.
(1) A
					 car frame and platform shall be of metal. Frame members shall be securely
					 bolted and braced. The factor of safety shall not be less than 4 with a
					 uniformly distributed rated load.
(2) The car shall be enclosed to the extent
					 necessary to afford reasonable protection.
(3) The platform area shall not exceed 5
					 square feet.
(4) The rated capacity
					 shall be not less than 300 pounds.
(5) The limit of travel for the elevator
					 shall be not more than 50 feet.
Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Elevator Safety Board › Michigan Elevator Rules › Chapter 7 - SEWER LIFT STATION PERSONNEL ELEVATORS › Section R. 408.7093 - Emergency exits

Current through Vol. 24-12, July 15, 2024
Rule 93. A car shall be provided with an emergency exit
						giving egress from the car to an emergency ladder from any location in the
						hoistway and shall be provided with electrical contacts to prevent movement of
						the car while the emergency exit is open.