reglab/statecodes huggingface dataset:
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-17 - Section 362.10; uses permitted

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 17.
(a) Delete
				the first two (2) sentences of text in Section 362.10 and substitute to read as
				follows: For the purpose of this section, a story is that portion of a building
				included between the upper surface of any floor and the upper surface of the
				floor next above, except that the topmost story shall be that portion of a
				building included between the upper surface of the topmost floor and the
				ceiling or roof above. If the finished floor level directly above a usable or
				unused under-floor space is more than 6 feet above grade for more than 50
				percent of the total perimeter or is more than 12 feet above grade at any
				point, such usable or unused underfloor space shall be considered as a
				story.
(b) In Item (1) under
				Section 362.10, delete "floors above grade" and substitute "stories".
(c) In Item (2) under Section 362.10, delete
				"floors above grade" and substitute "stories".
(d) In Section 362.10, delete the exception
				to items (2) and (5) and add a statement to items (2) and (5) to read as
				follows: Where the building is provided with an approved automatic sprinkler
				system throughout, ENT is permitted to be used within walls, floors, and
				ceilings, exposed or concealed, in buildings exceeding three stories.
Agency cited as
					 675 IAC
					 17-1.8-18, which was renumbered by the Publisher as
					 675 IAC 17-1.8-17.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-18 - Section 362.12; uses not permitted

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 18.
In Item (7) under Section 362.12, uses not permitted, add
				  362.10(2) to the listed sections.
Agency cited as
					 675
					 IAC 17-1.8-19, which was renumbered by the Publisher
					 as 675 IAC 17-1.8-18.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-19 - Section 406.11; tamper-resistant receptacles in dwelling units

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 19.
Delete Section 406.11 without
				  substitution.
Agency cited as
					 675 IAC
					 17-1.8-21, which was renumbered by the Publisher as
					 675 IAC 17-1.8-19.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-20 - Section 430.111(B)(3); oil switch

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 20.
In the first sentence of Section 430.111(B)(3), delete "by
				  special permission" and substitute "when approved".
Agency cited as
					 675 IAC
					 17-1.8-23, which was renumbered by the Publisher as
					 675 IAC 17-1.8-20.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-21 - Section 525.5; overhead conductor clearances

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 21.
In the first sentence of Section 525.5(B)(1), delete "4.5 m
				  (15 ft)" and insert "10 ft".
Agency cited as
					 675 IAC
					 17-1.8-24, which was renumbered by the Publisher as
					 675 IAC 17-1.8-21.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-22 - Section 547.1; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 22.
Change Section 547.1 to read as follows: The provisions of
				  this article shall apply to the following agricultural buildings or that part
				  of a building or adjacent areas of similar or like nature as specified in
				  547.1(A) and (B) below, unless the building is not a Class 1 structure.
				  Agricultural buildings that are not Class 1 structures may be regulated by
				  local ordinance.
Agency cited as
					 675 IAC
					 17-1.8-25, which was renumbered by the Publisher as
					 675 IAC 17-1.8-22.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-23 - Section 550.4; general requirements

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 23.
Add a second sentence to Section 550.4(B) to read as
				  follows: Modular homes, constructed under 675 IAC 15, Industrialized Building
				  Systems, shall comply with the provisions of Article 545 of this
				  code.
Agency cited as
					 675 IAC
					 17-1.8-26, which was renumbered by the Publisher as
					 675 IAC 17-1.8-23.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-24 - Section 600.1; scope

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 24.
Delete the first sentence of Section 600.1 and substitute to
				  read as follows: This article covers the installation of conductors and
				  equipment for electric signs and outline lighting as defined in Article 100 of
				  this code that are within or connected to Class 1 or Class 2 buildings or
				  structures.
Agency cited as
					 675 IAC
					 17-1.8-27, which was renumbered by the Publisher as
					 675 IAC 17-1.8-24.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-25 - Section 680.26(B)(1); conductive pool shells

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 25.
(a) After
				the first sentence of 680.26(B)(1)(a), insert a new sentence to read as
				follows: Reinforcing steel shall not extend into soil beyond the concrete
				envelope.
(b) After
				680.26(B)(1)(b), insert an exception to read as follows: Exception to (b): The
				equipotential bonding grid shall not be required to be installed under the
				bottom or vertically along the walls of vinyl lined polymer wall, fiberglass
				composite, or other pools constructed of nonconductive materials.
Agency cited as 675 IAC 17-1.8-28, which was renumbered by
					 the Publisher as 675 IAC 17-1.8-25.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-26 - Section 680.26(B)(2); perimeter surfaces

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 26.
In the first sentence of 680.26(B)(2), delete the text
				  following "concrete" and insert to read as follows: ", asphalt, flagstone,
				  brick, tile, concrete pavers, and other paving materials considered to be
				  conductive.".
Agency cited as 675 IAC 17-1.8-29, which was renumbered by
					 the Publisher as 675 IAC 17-1.8-26.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 17 - ELECTRICAL CODES › Rule 1.8 - Indiana Electrical Code, 2009 Edition › Section 1.8-27 - Section 680.26(B)(2)(b); alternate means

Current through July 10, 2024
Authority: IC 22-13-2-2; IC 22-13-2-13
Affected: IC 22-12; IC 22-13; IC 22-14; IC 22-15; IC
				  36-7
Sec. 27.
(a) Delete
				the text of 680.26(B)(2)(b) and substitute to read as follows: Alternate means.
				Where structural reinforcing steel is not available or is encapsulated in a
				nonconductive compound, a copper grid shall be installed within concrete or
				under other surfaces in accordance with 680.26(B)(1)(b).
(b) After 680.26(B)(2)(b), insert an
				exception to read as follows: Exception to (b): The equipotential bonding grid
				shall not be required to be installed under pool decks of nonconductive
				materials.
Agency cited as 675 IAC 17-1.8-30, which was renumbered by
					 the Publisher as 675 IAC 17-1.8-27.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 1.
(a) That
				certain document being titled the International Mechanical Code, 2012 Edition,
				first printing dated April 2011, as published by the International Code
				Council, Inc., 4051 West Flossmoor Road, Country Club Hills, Illinois
				60478-5795, is hereby adopted by reference as if fully set out in this rule
				save and except those revisions made in this rule.
(b) This rule is available to review and
				reference at:
Legal and Code Services Section
Indiana Department of Homeland Security
Indiana Government Center South 302 West Washington Street,
				  Room W246
Indianapolis, Indiana 46204
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-2 - Chapter 1; administration

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 4-21.5; IC 4-22-7-7; IC 22-12-7; IC 22-13-2-7;
				  IC 22-13-5; IC 22-14; IC 36-8-17
Sec. 2.
Delete Chapter 1 and insert to read as follows:
(a) 101.1 Title. This rule shall be known as
				the 2014 Indiana Mechanical Code and shall be published, except incorporated
				documents by the Department of Homeland Security for general distribution and
				use under that title. Wherever the term "this code" is used throughout this
				rule, it shall mean the 2014 Indiana Mechanical Code.
(b) 101.2 Scope.
(1) The scope and purpose of this code is to
				establish the minimum requirements for the following:
(A) Construction, addition, alteration,
				erection, or assembly of any part of a Class 1 structure at the site where the
				structure will be used.
(B)
				Installation of any part of the permanent heating, ventilating, air
				conditioning, electrical, plumbing, sanitary, emergency detection, emergency
				communication, or fire or explosion suppression systems for a Class 1 structure
				at the site where it will be used.
(C) Work undertaken to alter, remodel,
				rehabilitate, or add to any part of a Class 1 structure.
(D) Safeguarding life or property from the
				hazards of fire and explosion for Class 1 structures.
(E) Fabrication of any part of a Class 1
				industrialized building system for installation, assembly, or use at another
				site, except mobile structures.
(F)
				Work undertaken to relocate any part of a Class 1 structure except a mobile
				structure.
(G) Assembly of a Class
				1 industrialized building system that is not covered by subdivision (E), except
				mobile structures.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-4 - Chapter 3; general regulations

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 4.
(a) In
				Section 301.2, Energy utilization, insert "Class 1" after "all" and before
				"structures".
(b) Amend Section
				301.3 by adding an exception to read as follows, Exception: The manufacturer
				identification for fittings and pipe nipples shall be on each piece or shall be
				printed on the fitting or nipple packaging or provided documentation.
(c) Amend Section 301.5, in the second
				sentence, to delete "an approved" in both places and insert "a".
(d) In Section 301.7, Listed and labeled,
				delete the text "in accordance with Section 105".
(e) Delete Section 301.8 Labeling in its
				entirety.
(f) Delete the text of
				Section 301.16, Flood hazard, and insert See local ordinance.
(g) Delete Section 301.17 Rodent proofing in
				its entirety.
(h) Delete the text
				of Section 304.1, General, and insert to read as follows: Equipment and
				appliances shall be installed in accordance with the conditions of the listing,
				the manufacturer's installation instructions, and this code unless otherwise
				approved.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-5 - Chapter 4; ventilation

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 5.
(a) Amend
				Section 401.2 to add the letter "R" after "Section" and before
				"402.4.1.2".
(b) Amend Section
				401.4 by deleting "501.2.1" and inserting "501.3.1".
(c) Delete Section 401.6 Contaminant sources
				in its entirety.
(d) Amend Table
				403.3 by adding the following table:
Table 403.3 MINIMUM VENTILATION RATES
OCCUPANCY CLASSIFICATION
OCCUPANT DENSITY #/1000
								FT2
															a
PEOPLE OUTDOOR AIRFLOW RATE IN BREATHING ZONE,
								Rp CFM/PERSON
AREA OUTDOOR AIRFLOW RATE IN BREATHING ZONE,
								Ra CFM/ FT2
															a
EXHAUST AIRFLOW RATE CFM/
								FT2
															a
Hotels, motels, resorts and dormitories
Multipurpose assembly
Bathrooms/toilets-privateg
Bedroom/living room
Conference/meeting
Dormitory sleeping areas
Gambling casinos
Lobbies/prefunction
120
10
50
20
120
30
5
-
5
5
5
7.5
7.5
0.06
-
0.06
0.06
0.06
0.18
0.06
-
25/50f
-
-
-
-
-
(e)
				Delete the text of Section 406.1, General, and insert the following:
				Uninhabited spaces, such as crawl spaces and attics, shall be provided with
				natural ventilation openings as required by the Indiana Building Code (675 IAC
				13).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-7 - Chapter 6; duct systems

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 7.
(a) Amend
				Section 602.2.1.4 by deleting the text in its entirety and inserting the
				following: 602.2.1.4 Combustible electrical equipment. Combustible electrical
				equipment exposed within a plenum shall have a peak rate of heat release not
				greater than 100 kilo watts, a peak optical density not greater than 0.50 and
				an average optical density not greater than 0.15 when tested in accordance with
				Ul 2043. Combustible electrical equipment shall be listed and
				labeled.
(b) Delete Section
				602.2.1.4.1 in its entirety.
(c)
				Delete Section 602.2.1.4.2 in its entirety.
(d) Amend Section 607.5.4 by deleting the
				text of Exception 2 and inserting the following: Exception 2. Smoke dampers
				shall not be required in duct penetrations of smoke barriers in fully ducted
				heating, ventilating, and air conditioning systems in smoke compartments
				protected throughout with quick response sprinklers.
(e) Amend Section 607.5.5, after the word
				"fire", by deleting "and smoke" without substitution.
(f) Amend Section 607.5.5 by deleting
				Exception 2 without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-8 - Chapter 8; chimneys and vents

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 8.
Amend TABLE 803.10.6, CONNECTOR CLEARANCE TO COMBUSTIBLES,
				  in the text at the bottom of the MINIMUM CLEARANCE (inches) column, to delete
				  "As determined by the code official" and insert "as approved by the code
				  official".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-9 - Chapter 9; specific appliances, fireplaces and solid fuel-burning equipment

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 9.
(a) Amend
				Section 908 to add the word "components" after the word "towers".
(b) Add Section 917.4 to read as follows:
				Deep fat fryers. Deep fat fryers shall be installed with at least a minimum of
				sixteen (16) inches of clearance from any open flame from adjacent cooking
				appliances.
Exception: When a steel baffle plate installed between the
				  deep fat fryer and the open flame at least eight (8) inches high as measured
				  from the higher horizontal plane, the sixteen (16) inches clearance shall not
				  apply.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-10 - Chapter 10; boilers, water heaters, and pressure vessels

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC
				  22-13-2-9;
				  IC 22-14; IC 36-8-17
Sec. 10.
(a) Amend
				Section 1001.1 by inserting Exception 8 to read as follows: Boilers, water
				heaters, and pressure vessels regulated by the Boiler and Pressure Vessel Board
				(680 IAC
[675 IAC 30]
) under IC
				22-13-2-9
				are not regulated by this code.
(b)
				Amend Section 1003.3, Welding, by inserting "approved" before "nationally".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-11 - Chapter 11; refrigeration

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 11.
(a) Delete
				Section 1101.10 in its entirety without substitution.
(b) Amend Section 1105.6.3 by inserting after
				"multispeed fans shall be allowed to be", the words "30 air changes per
				hour".
(c) Amend Section 1106.5 to
				read as follows: Remote controls. Where flammable refrigerants are used, remote
				control of the mechanical equipment and appliances located in the machinery
				room shall comply with Sections 1106.5.1 and 1106.5.2 shall be provided at an
				approved location immediately outside the machinery room and adjacent to its
				principal entrance.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 18 - MECHANICAL CODE › Rule 1.6 - 2014 Indiana Mechanical Code › Section 1.6-12 - Adoption by reference; ASME B16.51

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12-7; IC 22-13; IC 22-14; IC 36-8-17
Sec. 12.
(a) That
				certain document being titled ASME B16.51, Copper and Copper Alloy
				Press-Connect Pressure Fittings, 2011 edition, as published by The American
				Society of Mechanical Engineers, Three Park Avenue, New York, NY 10016-5990, is
				hereby adopted by reference as if fully set out in this rule save and except
				those revisions made in this rule.
(b) Amend Table 1202.5 to insert, after
				"Copper and copper alloys standards", "ASME B16.51 2011".
(c) Amend Section 13 by deleting, in the
				first sentence, "The manufacturer of press" and inserting "Press".
(d) Amend Section 14.1 to delete the first
				sentence and insert to read as follows: Test reports demonstrating compliance
				with this Standard shall be provided to the code official upon
				request.
(e) Amend Figure 1 Method
				of Designating Laying Lengths of Fittings and Openings of Reducing Fittings,
				GENERAL NOTES: (d) to insert, after "shall be", "as".
(f) Amend Table 1 Dimensions of Press-Connect
				Ends, GENERAL NOTES: (c) to insert, after "shall be", "as".
(g) Amend Mandatory Appendix I, Table I-1
				Dimensions of Press-Connect Ends, GENERAL NOTES: (c) to insert, after "shall
				be", "as".
(h) Amend Mandatory
				Appendix II, References as follows:
(1) Delete
				the second sentence in its entirety without substitution.
(2) Insert, after "ANSI/ASME B1.20.1, Pipe
				Threads, General Purpose (Inch)", "Edition: 13, Date: 11/15/13".
(3) Insert, after "ASME B4.4M, Inspection of
				Workpieces", "Edition 81, Date: 1994".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-1 - Adoption by reference

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 1.
That certain document, being titled the Energy Standard for
				  Buildings Except Low-Rise Residential Buildings, I-P Edition, ANSI/ASHRAE 90.1,
				  2007 Edition, published by the American Society of Heating, Refrigerating and
				  Air-Conditioning Engineers, Inc. 1791 Tullie Circle NE, Atlanta, Georgia 30329,
				  is hereby adopted by reference as if fully set out in this rule save and except
				  those revisions made in sections 2 through 11 of this rule.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-2 - Section 2 amendments

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 2.
Section 2 is amended as follows:
(1) In Subsection 2.1a., delete item 3
				without substitution.
(2) In
				Subsection 2.3a., delete "multi-family structures of three stories or fewer
				above grade" and substitute "two-family dwellings".
(3) Amend Subsection 2.3c. by deleting the
				text and substituting as follows: "building systems and equipment dedicated to
				manufacturing processes where operating requirements are primarily intended for
				the manufactured product or process and not for human comfort.".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-3 - Section 3 amendments

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 10-19-7; IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9; IC 36-8-17-9
Sec. 3.
Section 3 is amended as follows:
(1) Amend Section 3.1, in the last sentence,
				to delete "accepted by the adopted authority" without substitution.
(2) Amend Section 3.2 Definitions as follows:
(A) Insert the definition of "approved" as
				follows: "Approved means as to materials, equipment, design, and types of
				construction, acceptance by the code official by one (1) of the following
				methods:
(i) Investigation or tests conducted
				by recognized authorities; or
(ii)
				Investigation or tests conducted by technical or scientific organizations;
				or
(iii) Accepted principles.
The investigation, tests, or principles shall establish that
				  the materials, equipment, and types of construction are safe for the intended
				  purpose.".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-4 - Section 4 amendments

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 36-7-2-9
Sec. 4.
Amend Section 4 as follows:
(1) Amend Section 4.1.1.3 to insert at the
				end of the sentence, "if a construction design release is required for the
				alterations".
(2) Delete Section
				4.1.1.4 in its entirety without substitution.
(3) Delete Section 4.1.1.5 in its entirety
				without substitution.
(4) Amend
				Section 4.1.2 to delete the text and insert "see 675 IAC 12".
(5) Amend Section 4.1.3 to delete the text
				and insert "see
				675 IAC 12-6-11".
(6) Delete Section 4.1.4 in its entirety
				without substitution.
(7) Delete
				Section 4.1.5 in its entirety without substitution.
(8) Amend Section 4.2.1.2 to delete the
				exception without substitution.
(9)
				Amend Section 4.2.1.3, exception b, to delete "of any calculation methods
				acceptable to the authority having jurisdiction" and insert "acceptable
				calculation methods approved by the division".
(10) Amend Section 4.2.2 to delete the text
				and insert "see
				675 IAC 12-6".
(11) Delete Section 4.2.2.2 in its entirety
				without substitution.
(12) Amend
				Section 4.2.3 to read as follows: "Materials and equipment shall be labeled in
				an approved manner.".
(13) Delete
				Section 4.2.4 without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-5 - Section 5 amendments

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC 36-7-2-9
Sec. 5.
Amend Section 5 as follows:
(1) Amend Section 5.1.2.2 to delete
				everything after the word "construction" and insert "in accordance with the
				rules of the Commission at
				675 IAC 12-4-7".
(2) Delete Section 5.1.2.3 in its entirety
				without substitution.
(3) Delete
				Section 5.2.2 in its entirety without substitution.
(4) Delete Section 5.1.4.2 in its entirety
				without substitution.
(5) Delete
				Section 5.7 in its entirety and substitute as follows:
5.7 Submittals compliance; alternative
				methods and materials
5.7.1 For construction
				projects filed for which a design professional is required under
				675 IAC 12-6-9(a)
				 and where energy conservation details are
				required by
				675 IAC
				12-6-7(g)(15), one of the following,
				sealed and signed by the design professional, shall be submitted:
(a) A Compliance Report, from an accepted
				computer compliance tool such as ComCheck (
www.energycodes.gov/comcheck/
) or
				other prescriptive compliance software or other methods approved by the
				Division, demonstrating compliance with the requirements of the Indiana Energy
				Conservation Code, 2010 edition (675 IAC
				19-4).
(b)
				A report from a comprehensive energy modeling program and an affidavit signed
				and sealed by the design professional affirming that the tools used to simulate
				the design energy performance indicate that the submitted design will meet or
				exceed the requirements of the Indiana Energy Conservation Code, 2010 edition
				(675 IAC
				19-4).
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-6 - Section 6 amendments

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 6.
Amend Section 6 as follows:
(1) Amend Section 6.4.3.1.2, Exception b, by
				deleting the text and substituting as follows: Special occupancy or special
				applications where wide temperature ranges are not acceptable (such as
				production clean rooms, labs, museums, some areas of hospitals).
(2) Delete Section 6.4.3.7, Exception b,
				without substitution.
(3) Amend
				Section 6.4.4.1.3, Exception b, by inserting, after "inclusive", "or piping
				that has temperatures at least 2°F above the space dew point
				temperature".
(4) Delete Section
				6.4.4.2.2 in its entirety without substitution.
(5) Amend Table 6.4.4.2A by amending the
				heading in the fourth column to read "Return and Outside".
(6) Amend Section 6.5.1 to add Exception j as
				follows: j. Specialty industrial/lab/hospital areas where strict zone air
				pressure controls are employed.
(7)
				Amend Subsection 6.5.2.2.2a. to delete "15°F" and insert
				"4°F".
(8) Amend Subsection
				6.5.2.3d. to insert, after "surgical suites", "specialty labs and clean rooms".
				Delete the last sentence without substitution.
(9) Amend Section 6.5.3.2.2 to add an
				exception as follows: Exception: Systems used for lab manifold exhaust where
				positioning of the static pressure sensor(s) in locations required in this
				section creates additional calibration, testing, and troubleshooting tasks that
				would not otherwise have to be performed.
(10) Amend Section 6.5.6.1, Exception c, to
				add, after "fumes", "gases, vapors, mists, or particulates".
(11) Amend Section 6.5.6.1 to add a new
				Exception j as follows: j. Specialty industrial/lab/hospital areas where strict
				zone air pressure controls are employed.
(12) Amend Section 6.5.6.2.2 to add a new
				Exception c as follows: c. Facilities that connect to existing service hot
				water systems meeting the exception in Section 7.1.1.2.
(13) Amend Subsection 6.5.7.2a. to add an
				exception as follows: Exception: VAV control of all lab rooms is not required
				if thermal or health and safety criteria mandate constant volume
				control.
(14) Amend Subsection
				6.5.7.2b. to delete "no humidification added".
(15) Amend Section 6.7.1 to delete "authority
				having jurisdiction" and insert "division".
(16) Delete Section 6.7.2 in its entirety
				without substitution.
(17) Amend
				the title of Table 6.8.2A to amend the heading "Supply Ducts" to read "Supply
				and Outside Air Ducts".
(18) Amend
				the title of Table 6.8.2B to amend the heading "Supply Ducts" to read "Supply
				and Outside Air Ducts".
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-7 - Section 7 amendments

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 7.
Amend Section 7 as follows:
(1) Delete Section 7.1.1.3 in its entirety
				without substitution.
(2) Amend
				Section 7.4.1 to delete all of the text after the words "engineering standards"
				without substitution.
(3) Amend
				Subsection 7.5.1b. to delete the text and insert, "A nationally recognized
				standard shows that the use of a single heat source will consume less energy
				than separate units.".
(4) Delete
				Section 7.7 in its entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-8 - Section 8 amendments

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 8.
Amend Section 8 as follows: Delete Section 8.7 in its
				  entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-9 - Section 9 amendments

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 9.
(a) Amend
				Section 9.1.1 to add Exception e and Exception f as follows:
e. Specialty lighting used in research areas
				that has material effects on test data.
f. Specialty lighting required for high
				security video monitoring.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-10 - Section 10 amendments

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 10.
Amend Section 10 as follows: Delete Section 10 in its
				  entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 19 - ENERGY CONSERVATION CODES › Rule 4 - 2010 Indiana Energy Conservation Code › Section 4-11 - Section 11 amendments

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-14; IC
				  36-7-2-9
Sec. 11.
Amend Section 11 as follows: Delete Section 11 in its
				  entirety without substitution.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-1 - Title and availability

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 1.
(a) This
				article shall be known as the Indiana Swimming Pool, Spa and Water Attraction
				Code, third edition. Whenever the term "this code" is used in this article, it
				shall mean the Indiana Swimming Pool, Spa and Water Attraction Code, third
				edition.
(b) The Indiana Swimming
				Pool, Spa and Water Attraction Code is available at the Department of Homeland
				Security, Code Services Section, Indiana Government Center South, 302 West
				Washington Street, Room W246, Indianapolis, Indiana 46204.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-2 - Definitions; general

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 2.
For the purpose of this code, the definitions in this rule
				  apply throughout this article.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-3 - Definitions "A"

Current through July 10, 2024
Authority: IC 22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 3.
(a)
				"Abrasion hazard" means a sharp or rough surface that could cause injury under
				normal use.
(b) "Accessible" means,
				when applied to a fixture, connection, appliance, or equipment, having access
				thereto, but may require the removal of an access panel, door, or similar
				obstruction. "Readily accessible" means direct access without the necessity of
				removing any panel, door, or similar obstruction.
(c) "Agitation" means the mechanical or
				manual movement to dislodge the filter aid and dirt from the filter
				element.
(d) "Airbreak" means a
				physical separation that may be a low inlet into the indirect waste receptor
				from the fixture, appliance, or device indirectly connected.
(e) "Air bump assist backwash" means, in a
				diatomite type filter, the compressing of a volume of air in the filter
				effluent chamber (by means of an air compressor or by the water pressure from
				the recirculating pump) that, when released, rapidly decompresses and forces
				water in the filter tank through the elements in a reverse direction dislodging
				the filter aid and accumulated dirt and carrying them to waste.
(f) "Airgap" means the unobstructed vertical
				distance through the free atmosphere between the lowest opening from any pipe
				or faucet conveying water or waste to a tank, plumbing fixture receptor, or
				other device and the flood level rim of the receptacle.
(g) "Air induction system" means a system
				whereby a volume of air (only) is induced into hollow ducts built into a spa
				floor, bench, or other location. The air induction system is activated by a
				separate air power unit (blower).
(h) "Approved" means, as to materials,
				equipment, design, and types of construction, acceptance by the code official
				by one (1) of the following methods:
(1)
				Investigation or tests conducted by recognized authorities.
(2) Investigation or tests conducted by
				technical or scientific organizations.
(3) Accepted principles.
The investigation, tests, or principles shall establish that
				  the materials, equipment, and types of construction are safe for the intended
				  purpose.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-4 - Definitions "B"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 4.
(a)
				"Backwash" means the process of thoroughly cleaning the filter medium or
				elements, or both, by the reverse flow of water.
(b) "Backwash cycle" means the time required
				to backwash the filter system thoroughly.
(c) "Backwash pipe" means a type of filter
				waste discharge piping as defined in section 8(o) of this rule.
(d) "Backwash rate" means the rate of
				application of water through a filter during the backwash cycle expressed in
				gallons per minute per square foot of effective filter area.
(e) "Basin" means any vessel:
(1) constructed of man-made materials;
				and
(2) designed to hold water to
				be used as a swimming pool, spa, or water attraction.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-5 - Definitions "C"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC
				  36-7-2-9;
				  IC
				  36-8-17-9
Sec. 5.
(a)
				"Cartridge" means a filter component of either the depth or surface type having
				fixed dimensions and designed to remove suspended particles from water flowing
				through the unit.
(b) "Cartridge,
				depth type" means a filter cartridge with a medium relying on penetration of
				particulates into the medium for removal and providing adequate holding
				capacity of such particulates.
(c)
				"Cartridge, surface type" means a filter cartridge with a medium relying on
				retention of particles on the surface of the cartridge for removal.
(d) "Chemical feeder" means any device used
				to feed chemicals such as sanitizers, pH adjusters, algicide, etc. into a pool
				or spa.
(e) "Chemical feeder output
				rate" means the weight or volume of active ingredients delivered by a chemical
				feeder expressed in units of weight of volume and time.
(f) "Chemical feed rate indicator" means a
				mechanism that will produce reproducible results expressed in units of weight
				or volume of chemical per unit of time or per unit of volume of water. The
				mechanism may:
(1) be a direct reading
				instrument; or
(2) require the use
				of a reference chart.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-6 - Definitions "D"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 6.
(a) "Decks"
				means those areas surrounding a pool which are specifically constructed or
				installed for use by bathers.
(b)
				"Deep areas" means the portions of a pool having water depths in excess of five
				(5) feet.
(c) "Design head" means
				the total head requirement of the circulation system at the design rate of
				flow.
(d) "Design rate of flow
				(design filter rate)" means the rate of flow in a system which is used for
				design calculation. (The volume of the pool, spa, or hot tub in gallons divided
				by the number of minutes in the turnover time.)
(e) "Diatomite filter" means one designed to
				filter water through a thin layer of filter aid such as diatomaceous earth or
				volcanic ash. Diatomite filters may be of the pressure or vacuum
				type.
(f) "Distribution system,
				upper" means those devices designed to distribute the water entering a sand
				type filter in a manner such as to prevent movement or migration of the filter
				media. This system shall also properly collect water during filter backwashing
				unless other means are provided.
(g) "Distribution system, lower" means those
				devices used in the bottom of a sand type filter to collect the water uniformly
				during the filtering and to distribute the backwash water uniformly during the
				backwashing.
(h) "Diving board"
				means a recreational mechanism for entering a swimming pool, consisting of a
				semirigid board that derives its elasticity through the use of a fulcrum
				mounted below the board.
(i)
				"Diving equipment, competitive" means competitive diving equipment including
				competitive diving boards and fulcrum setting diving stands intended to provide
				adjustment for competitive diving.
(j) "Diving equipment, manufactured" means
				manufactured diving equipment and shall include diving boards, jump boards,
				spring boards, and starting platforms. Architectural features such as
				decorative rocks and elevated bond beams are not considered to be manufactured
				diving equipment.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-7 - Definitions "E"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 7.
"Effective filtration area" means the total surface area
				  through which the design flow rate will be maintained during filtration.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-8 - Definitions "F"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 8.
(a) "Face
				piping" means the piping, with all valves and fittings, that is used to connect
				the filter system together as a unit.
(b) "Family pool" means a residential
				swimming pool.
(c) "Filter" means a
				device that separates solid particles from water by circulating the water
				through a porous substance (a filter medium element).
(d) "Filter aid" means a type of finely
				divided media used to coat a septum type filter, usually diatomaceous earth or
				volcanic ash. (Note: Alum, as used on the bed of a sand filter, is also
				referred to as a filter aid.)
(e)
				"Filter, cartridge" means a filter that uses a porous cartridge as its filter
				medium.
(f) "Filter cycle" means
				the operating time between cleaning or backwash cycles.
(g) "Filter, diatomaceous earth" means a
				filter that uses a thin layer of diatomaceous earth as its filter medium that
				periodically must be replaced.
(h)
				"Filter element" means that part of a filter that supports the surface upon
				which the filter aid is deposited (usually in diatomite filters).
(i) "Filter media" means the finely graded
				material that entraps suspended particles (sand, anthracite, etc.).
(j) "Filter, permanent medium" means a filter
				that under normal use will not have to be replaced.
(k) "Filter rate" means the rate of
				application of water to a filter expressed in gallons per minute per square
				foot of effective filter area.
(l)
				"Filter rock" means graded, rounded rock or gravel, or both, not subject to
				degradation by common pool chemical used to support filter media.
(m) "Filter sand" means a specially graded
				type of permanent filter media.
(n)
				"Filter septum" means that part of the filter element in a diatomite type
				filter upon which a cake of diatomite or other nonpermanent filter aid may be
				deposited.
(o) "Filter waste
				discharge piping" means piping that conducts wastewater from a filter to a
				drainage system. Connection to drainage system is made through an airgap or
				other approved method.
(p) "Floor"
				means the interior bottom pool surface and consists of that surface from a
				horizontal plane up to a maximum of a forty-five (45) degree slope.
(q) "Flow balance valve" means a device to
				regulate the effluent from the skimmer housing of each of a combination of two
				(2) or more surface skimmers.
(r)
				"Freeboard" means the clear vertical distance in a sand type filter between the
				top of the filter media and the lowest outlet of the upper distribution
				system.
(s) "Fresh water" means
				water having a specific conductivity less than a solution containing six
				thousand (6,000) parts per million of sodium chloride.
(t) "Friction loss" means the pressure drop
				expressed in feet of water or psi caused by liquid flowing through the piping
				and fittings.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-9 - Definitions "H"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 9.
(a) "Head
				loss" means the total pressure drop in pounds per square inch (kilo Pascals) or
				feet (meters) or head between the inlet and the outlet of a
				component.
(b) "High rate sand
				filter" means a sand filter designed for flows in excess of five (5) gallons
				per minute per square foot.
(c)
				"Hydrojet booster pump system" means a system whereby one (1) or more hydrojets
				are activated by the use of a pump which is completely independent of the
				filtration and heating system of a spa.
(d) "Hydrojets" means a fitting which blends
				air and water creating a high velocity, turbulent stream of air enriched water.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-10 - Definitions "I"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 10.
(a)
				"Indirect waste pipe" means a pipe that does not connect directly with the
				drainage system but conveys liquid wastes by discharging into a plumbing
				fixture, interceptor, or receptacle that is directly connected to the drainage
				system.
(b) "Inlet fitting" means a
				fitting or fixture through which circulated or hydrojetted water enters a pool,
				spa, or hot tub.
(c) "Interactive
				play attraction" means a water attraction, including devices using sprayed,
				jetted, or other water sources contacting the users and not incorporating a
				basin and standing or captured water as part of the user activity area, such as
				splash pads and spray pads.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-11 - Definitions "J"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 11.
"Jump board" means a recreational mechanism that has a coil
				  spring, leaf spring, or comparable device located beneath the board that is
				  activated by the force exerted in jumping on the board.
Indiana Administrative Code › Title 675 - FIRE PREVENTION AND BUILDING SAFETY COMMISSION › Article 20 - SWIMMING POOL CODE › Rule 1.1 - General Provisions and Definitions › Section 1.1-12 - Definitions "L"

Current through July 10, 2024
Authority: IC
				  22-13-2-2
Affected: IC 22-12; IC 22-13; IC 22-15; IC 36-7
Sec. 12.
(a)
				"Ladders" mean the following:
(1) "Deck
				ladder" means a ladder for deck access from outside the pool.
(2) "In-pool ladder" means a ladder located
				in a pool to provide ingress and egress from the deck.
(3) "Limited access ladder" means a ladder
				with provision for making entry inaccessible when a pool is not in use, that
				is, swing-up, slide-up, or equivalent.