Mississippi Administrative Code › Title 11 - Mississippi Department of Environmental Quality › Part 5 - Underground Storage Tank Regulations › Chapter 2 - Mississippi Commission on Environmental Quality Underground Storage Tanks Regulations Technical Standards and Corrective Action Requirements for Owners and Operators of Underground Storage Tanks (UST) (Adopted March 22, 1989; Amended August 25, 2011, Last Amended August 23, 2018) › Appendix 11-5-2-280.1 - GUIDELINES FOR THE EVALUATION OF UNDERGROUND STORAGE TANK CATHODIC PROTECTION SYSTEMS › Section 11-5-2-280.1-6 - CATHODIC PROTECTION TESTING › Section 11-5-2-280.1-6.10 - Cathodic Protection Test Locations › Section 11-5-2-280.1-6.10.3 - Tanks Protected by Impressed Current

Current through June 25, 2024
With impressed current cathodic protection systems,
						  tank potentials are required to be measured with the reference electrode placed
						  locally. Where the location of the anodes is known and they are relatively
						  evenly distributed about the tank bed, the appropriate location to place the
						  reference electrode would be in the soil at the middle of the tank (See Figure
						  9). However, if access to the soil is not available at the middle of the tank,
						  the reference electrode may be placed in the soil at any point along the
						  centerline of the tank similar to that described in Section 6.10.1.
Click Here To View
						  Image
As with the evaluation of any cathodic protection
						  system, the location of the anodes in relation to reference electrode placement
						  can be of critical importance. When selecting the appropriate local placement,
						  it is necessary to place the reference electrode at the point over the
						  structure that is the most distant from any active anode due to the effects of
						  attenuation. Attenuation of the cathodic protection current may occur whereby
						  effective protection is not achieved at some point along a UST system. For
						  instance, if all of the active anodes are along one side of a tank bed, current
						  distribution and attenuation may prevent sufficient protective current from
						  reaching the side of the tanks away from the anodes. The preferred placement of
						  the reference electrode would be along the centerline of the tanks at the end
						  opposite to that where the anodes are installed (See Figure 10).
Click Here To View
						  Image
If it is not known where the anodes are installed, at
						  least one measurement is required along the centerline of the tank. Testing
						  should be conducted at as many locations along the centerline of the tank as
						  are available. If soil access is available at each end of the tank and in the
						  middle, all three structure-to-soil potentials should be recorded. If any one
						  of the measured potentials does not meet one of the acceptable criteria, the
						  structure should be failed.
In addition, if it is possible to measure the
						  individual circuits in an impressed current system, a determination can be made
						  as to which anodes are functional and how the current is distributed throughout
						  the groundbed. How the current is distributed should be considered when
						  choosing reference electrode placement when conducting a structure-to-soil
						  potential survey. If for instance it is known that the majority of the
						  rectifier output current is directed to only those anodes along one end of a
						  tank bed, the reference electrode should be placed at the opposite end of the
						  tank bed.