reglab/statecodes huggingface dataset:
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 11 - Storm Drainage › Section XIV-1107 - Conductors and Connections

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Protection. Rain water conductors installed along alleyways, driveways, or
				other locations where they may be exposed to damage shall be
				protected.
B. Separation of Storm
				Drainage from Sanitary Sewers. The sanitary sewer and storm drainage systems of
				a building shall be entirely separate.
C. Floor Drains. Floor drains shall not be
				connected to a storm drain.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 11 - Storm Drainage › Section XIV-1109 - Roof Drains

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Material. Roof drains shall be of an approved corrosion resistant material with
				adequate strainer area and shall comply with the applicable standards in Table
				303 of this code.
B. Strainers.
				When roof drains are provided they shall have strainers extending not less than
				4 inches (102 mm) above the surface of the roof immediately adjacent to the
				roof drain. Strainers shall have an available inlet area, above roof level, of
				not less than one and a half times the area of the conductor or leader to which
				the drain is connected.
C. Flat
				Decks. Roof drain strainers for use on sun decks, parking decks, and similar
				areas, normally serviced and maintained, may be of the flat surface type, level
				with the deck and shall have an available inlet area not less than two times
				the area of the conductor or leader to which the drain is connected.
D. Roof Drain Flashings. The connection
				between roofs and roof drains which pass through the roof and into the interior
				of the building shall be made watertight by the use of proper flashing
				material.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 11 - Storm Drainage › Section XIV-1111 - Size of Leaders and Storm Drains

Current through Register Vol. 50, No. 6, June 20, 2024
A. Vertical Leaders. Vertical leaders shall
				be sized for the maximum projected roof area, according to Table 1111.A of this
				code below. If a vertical offset is 45 degrees or less, the leader can be sized
				as a vertical pipe. If the offset is greater than 45 degrees, the pipe must be
				sized as a horizontal pipe.
Table 1111.A
Size of Vertical Leaders
Size of Leader or
							 Conductor1 (in)
Maximum Projected Roof Area (sq ft)
2
720
2 1/2
1300
3
2200
4
4600
5
8650
6
13,500
8
29,000
NOTE:
1. The
				equivalent diameter of square or rectangular leader may be taken as the
				diameter of that circle which may be inscribed within the cross-sectional area
				of the leader. See also §1111. B.2 of this code.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 11 - Storm Drainage › Section XIV-1113 - Secondary (Emergency) Roof Drains

Current through Register Vol. 50, No. 6, June 20, 2024
A. Secondary Drainage Required. Secondary
				(emergency) roof drains or scuppers shall be provided where the roof perimeter
				construction extends above the roof in such a manner that water would be
				entrapped should the primary drains allow buildup for any reason.
B. Separate Systems Required. Secondary roof
				drain systems shall have piping and point of discharge separate from the
				primary system. Discharge shall be above grade(G) in a
				location which would normally be observed by the building occupants or
				maintenance personnel.
C. Maximum
				Rainfall Rate for Secondary Drains. Secondary (emergency) roof drain systems or
				scuppers shall be sized based on the flow rate caused by the 100-year 15 minute
				precipitation as indicated in Figure 1113.C of this Part. The flow through the
				primary system shall not be considered when sizing the secondary roof drain
				system.
Click Here To View
				  Image
Figure 1113.C - Rainfall Rate for Primary Roof Drains
				  (in./hr.)
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 11 - Storm Drainage › Section XIV-1115 - Values for Continuous Flow

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Where there is a continuous or semicontinuous discharge into the building storm
				drain or building storm sewer, as from a pump, ejector, air conditioning plant,
				or similar device, each gallon per minute of such discharge shall be computed
				as being equivalent to 24 sq ft (2.23 m2) of roof
				area, based upon a 4-inch (102 mm) rainfall.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 11 - Storm Drainage › Section XIV-1117 - Additional Information for Storm Drainage

Current through Register Vol. 50, No. 6, June 20, 2024
A. Additional information for storm drainage
				is contained in Chapter 18 (Appendices) of this code,
				§1803 (Appendix A - Roof Drain Sizing Method).
				Such additional information in Chapter 18 shall not be construed as superceding
				any pertinent regulation(s) contained in Chapters 1-17 of this code.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 12 - Alternate Designed Plumbing Systems › Section XIV-1201 - General

Current through Register Vol. 50, No. 6, June 20, 2024
A. Approval of
				alternate designed plumbing systems will be considered on an individual
				basis.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 12 - Alternate Designed Plumbing Systems › Section XIV-1203 - Requirements for Approval

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Plans and Specifications. Plans and specifications for any proposed alternate
				designed plumbing system shall be submitted to the state health officer for
				review and approval prior to construction. Such plans and specifications shall
				be appropriately sealed and signed by a Louisiana Registered Professional
				Engineer registered in either civil or mechanical engineering.
B. Responsibility of Professional Engineer.
				The Professional Engineer referenced in §1203. A of this code shall be
				responsible for:
1. certifying the system
				design;
2. inspecting the system
				during installation;
3. certifying
				that the installed system is in compliance with the approved design
				specifications;
4. supervising any
				test(s) performed on the system; and,
5. certifying the results of any required
				testing.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 12 - Alternate Designed Plumbing Systems › Section XIV-1207 - Third Party Notification

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				After installation of any alternate designed plumbing system, the owner shall
				notify third parties of its existence by having a document recorded in the
				Clerk of Court's conveyance records in the parish in which such alternate
				designed plumbing system has been installed. The document so recorded shall
				reference a prior conveyance record (COB/folio) of the parcel of ground upon
				which the alternate designed plumbing system is located (e.g., the conveyance
				recording a previous Act of Sale of the parcel of ground). The document will
				state that the plumbing of the building located on this particular parcel of
				ground contains an "alternate designed plumbing system" which cannot be
				modified in any manner by future owners/lessees without first obtaining an
				approval of such proposed modifications from the state health officer in accord
				with the requirements of Chapter 12 (Alternate Designed Plumbing Systems) of
				this code. Proof of recordation shall be provided to the state health officer
				and the local plumbing official prior to issuance of a building occupancy
				permit.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 13 - Medical Facilities Plumbing Systems [formerly Appendix G - Medical Facilities Plumbing Systems] › Section XIV-1301 - General

Current through Register Vol. 50, No. 6, June 20, 2024
A. Scope. The
				following Subparagraphs provide the scope of this Chapter.
1. The provisions of this Chapter are
				intended to set out those items of hospital/medical facilities plumbing systems
				which differ from plumbing systems in other buildings. Special care shall be
				accorded the hospital plumbing system because of its direct relationship to
				adequate medical care and the need for added protection for patients and
				hospital personnel from health hazards.
2. It is understood that hospital/medical
				facilities plumbing systems shall conform not only to the requirements of this
				Chapter, but also to the requirements contained in the other Chapters of this
				code.
3. The provisions of this
				Chapter shall apply to plumbing installations in clinics, doctors' offices,
				nursing homes, and other medical facilities, etc., as well as in hospital
				installations.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 13 - Medical Facilities Plumbing Systems [formerly Appendix G - Medical Facilities Plumbing Systems] › Section XIV-1307 - Water Supply

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Water Service. All hospitals should have dual services installed in a manner to
				provide an uninterrupted supply of water in case of a water main break,
				etc.
B. Hot Water Distribution
				System. Hot water circulating mains and risers should be run from the hot water
				storage tank to a point directly below the highest fixture at the end of each
				branch main. Where the building is higher than three stories, each riser shall
				be circulated. Each main, branch main, riser and branch to a group of fixtures
				of the water system shall be valved.
C. Vacuum Breaker Installations. The
				following shall be considered concerning the installation and use of vacuum
				breakers.
1. For ordinary hose connections,
				the maximum height at which any hose is to be used shall be treated as its
				flood level.
2. Where low volume
				flows might cause leaking or spitting at the vacuum breaker parts, back
				pressure may be developed by installing an acceptable minimum orifice valve on
				the discharge side of the vacuum breaker. This shall be in addition to the
				regular control valve. This type of installation shall be subject to review and
				acceptance by the plumbing official before installation.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 13 - Medical Facilities Plumbing Systems [formerly Appendix G - Medical Facilities Plumbing Systems] › Section XIV-1309 - Medical Gas and Medical Vacuum Systems

Current through Register Vol. 50, No. 6, June 20, 2024
A. Where medical gas and medical vacuum
				systems are installed, the gas piping, outlets, manifold rooms and storage
				rooms shall be installed in accordance with all of the requirements of the NFPA
				99 by individuals properly licensed by the State Plumbing Board of Louisiana
				(see LAC 46:LV).
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 14 - Reference Standards › Section XIV-1401 - Scope

Current through Register Vol. 50, No. 6, June 20, 2024
A. This Chapter
				contains the designations, names and edition of standards referenced in this
				code listed alpha-numerically and the Section numbers where they are
				referenced.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1501 - General

Current through Register Vol. 50, No. 6, June 20, 2024
A. With the
				exception of
				§1523 of this code, the requirements set
				forth in this Chapter shall apply specifically to all new travel trailer parks,
				and to additions to existing parks as herein defined, and are to provide
				minimum standards for sanitation and plumbing installation within these parks,
				for the accommodations, use and parking of travel trailers. Plumbing
				installations within travel trailers shall be installed in accordance with NFPA
				1192.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1505 - General Regulations

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Governing Provisions. Other general provisions of this code shall govern the
				installation of plumbing systems in travel trailer parks, except where special
				conditions or construction are specifically defined in this Chapter.
B. Travel Trailer Sites. Travel trailers
				shall comply with the following when parked in a travel trailer park.
1. Travel trailers shall not hereafter be
				parked in any travel trailer park unless there are provided plumbing and
				sanitation facilities installed and maintained in conformity with these
				regulations. Every travel trailer shall provide a gastight and watertight
				connection for sewage disposal which shall be connected to an underground
				sewage collection system discharging into a community sewerage system, a
				commercial treatment facility, or an individual sewerage system which has been
				approved by the state health officer.
2. No dependent travel trailer shall be
				parked at any time in a space designed and designated for an independent travel
				trailer unless public toilet and bath facilities are available within 200 ft
				(61 m) of the dependent travel trailer.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1507 - Plans and Specifications

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				The owner or operator of every travel trailer park, before providing areas of
				space for the use and accommodation of travel trailers, shall make application
				for a permit (where such permit is required by state, parish, city or other
				local laws or ordinances) or, regardless of whether or not an actual permit is
				required, shall file two sets of plans and specifications with the
				department(s) having jurisdiction for their review and approval. The plans and
				specifications shall be in detail and shall include/comply with the following:
1. a scaled plot plan of the park, indicating
				the spaces, area or portion of the park for the parking of travel
				trailers;
2. the size, location and
				specification of the park drainage system;
3. the size, location and specification of
				water supply lines;
4. the size,
				location and layout of service building (see
				§1509 of this code);
5. the size, location, specification and
				layout of the fire protection system, if applicable;
6. a scaled layout of typical trailer
				sites;
7. applications/submittals
				shall bear the approval of the local enforcement agencies as to compliance with
				city or parish plumbing, zoning and health ordinances;
8. plumbing required by this Chapter shall
				comply with all city, parish and state plumbing and health ordinances and
				regulations;
9. the issuance of a
				permit (or an approval of a submittal) shall not constitute approval of any
				violation of this code or violation of any city or parish ordinance or
				regulation; and,
10. an approved
				set of plans and specifications and a copy of the permit (or written approval
				of a submittal) shall be kept on the park premises until the final inspection
				has been made.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1509 - Service Buildings

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each
				travel trailer park shall have at least one service building to provide
				necessary sanitation and laundry facilities as specified in §1509. B of this code. The service building shall be of permanent construction
				with an interior finish of moisture resistant material which will stand
				frequent washing and cleaning and the building shall be well-lighted and
				ventilated at all times.
B. Service
				Building for Independent Trailers
1. The
				service building(s) of only independent travel trailer parks shall have a
				minimum of one water closet, one lavatory, one shower or bathtub for females
				and one water closet, one lavatory, and one shower or bathtub for males. In
				addition, at least one laundry tray or clothes washing machine and one drinking
				fountain shall be provided.
2. The
				laundry tray or clothes washing machine and drinking fountain shall be located
				in a common area. None of these fixtures shall be located within any toilet
				room.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1511 - Materials

Current through Register Vol. 50, No. 6, June 20, 2024
A. Unless otherwise
				provided for in this Chapter, all piping fixtures or devices used in the
				installation of drainage and water distribution systems for travel trailer
				parks, or parts thereof, shall conform to the quality and weights of materials
				required by the
Louisiana State Plumbing Code
.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1513 - General Regulations

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Unless otherwise provided for in this Chapter, all plumbing fixtures, piping
				drains, appurtenances and appliances designed and used in a park drainage,
				water distribution system and service connections shall be installed in
				conformance with the Louisiana State Plumbing Code.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1517 - Water Distribution System

Current through Register Vol. 50, No. 6, June 20, 2024
A. General. Every travel trailer site shall
				be provided with an individual branch water service line delivering potable
				water. The outlet of the branch water service line shall terminate on the left
				side of the site of the travel trailer.
B. Minimum Size. Water service lines to each
				trailer site shall be sized to provide a minimum of 8 gpm (0.505 L/s) at the
				point of connection with the trailer's water distribution system. All water
				service lines shall be a minimum of - inch.
C. Backflow. A minimum of a double check
				valve assembly backflow preventer shall be installed on the water service line
				to each independent trailer at, or near, the trailer's water service
				connection. Backflow preventer devices shall meet the requirements of §609. B and Table 609 of this code. Check valves shall be designed and maintained to
				close drip tight at a reduced pressure of not less than 1 nor more than 5 psi
				(6.9 to 34.5 kPa). Check valves must be identified with the manufacturer's name
				and model number.
D. Separate
				Service Shutoff. A separate service shutoff valve shall be installed in each
				water service line on the supply side of the backflow preventer device. Per
				§617. A of this code, such separate shutoff valve shall be a full port ball
				valve.
E. Water Service
				Connections. The water service connection from the water service line to the
				trailer shall be not less than 1/2-inch diameter. A rigid pipe shall not be
				used. Flexible metal tubing is permitted. Fittings at either end shall be of a
				quick disconnect type not requiring any special tools or knowledge to install
				or remove.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1519 - Travel Trailer Connections

Current through Register Vol. 50, No. 6, June 20, 2024
A. Responsibility. When it is evident that
				there exists, or may exist, a violation of these rules, the owner, operator,
				lessee, person in charge of the park, or any other person causing a violation
				shall cause it to be corrected immediately or disconnect the service connection
				and travel trailer drain connection from the respective park water service line
				and sewer lateral.
B. Drain
				Connections. Travel trailer drain connections shall be of approved semi rigid
				or flexible reinforced hose having smooth interior surfaces of not less than
				3-inch inside diameter. Drain connections shall be equipped with a standard
				quick disconnect screw or clamp type fitting, not less in size than the outlet.
				Drain connections shall be gastight and no longer than necessary to make the
				connection between the travel trailer outlet and the trap inlet on the
				site.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2), (3), (7), (9), (16), (17), and
				  (20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1521 - Maintenance

Current through Register Vol. 50, No. 6, June 20, 2024
A. All devices or
				safeguards required by this Chapter shall be maintained in good working order
				by the owner, operator, or lessee of the travel trailer park or his designated
				agent.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 15 - Travel Trailers and Travel Trailer Parks [formerly Appendix B - Travel Trailers and Travel Trailer Parks] › Section XIV-1523 - Individual Travel Trailers

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Individual travel trailers located within previously constructed travel trailer
				parks shall be provided with a trailer trap in accord with §1003. E of this
				code.
Click Here To View
				  Image
Figure 1523.A - Trailer Trap and
				  Vent
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1601 - Purpose, Application and Scope

Current through Register Vol. 50, No. 6, June 20, 2024
A. With the exception of
				§1623 of this code, the requirements set
				forth in this Chapter shall apply specifically to all new mobile/manufactured
				home parks, and to additions to existing parks as herein defined, and are to
				provide minimum standards for sanitation and plumbing installation within these
				parks, for the accommodation, use and parking of mobile/manufactured homes.
				Plumbing installations within mobile/manufactured homes shall be installed in
				accordance with NFPA 1192.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1603 - Definitions

Current through Register Vol. 50, No. 6, June 20, 2024
A. Definitions
				contained in Chapter 2 and
				Section 1503 of this code shall also apply to
				this Chapter, except where the following special definition shall apply.
Mobile/Manufactured Home-
a vehicular,
				  portable structure built on a chassis and designed to be used as a dwelling
				  without a permanent foundation when connected to indicated utilities per NFPA
				  1192.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1605 - General Regulations

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Other general provisions of this code shall govern the installation of plumbing
				systems in mobile/manufactured home parks, except where special conditions or
				construction are specifically defined in this Chapter.
B. Mobile/manufactured homes shall not
				hereafter be parked in any mobile/manufactured home park unless plumbing and
				sanitation facilities have been installed and maintained in conformity with
				these regulations. Every mobile/manufactured home shall provide a gastight and
				watertight connection for sewage disposal which shall be connected to an
				underground sewage collection system discharging into a community sewerage
				system, a commercial treatment facility, or an individual sewerage system which
				has been approved by the state health officer.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1607 - Plans and Specifications

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				The owner or operator of every mobile/manufactured home park, or the plumbing
				contractor employed by him before providing areas of space for the use and
				accommodation of mobile/manufactured homes, shall make application for a permit
				(where such permit is required by state, parish, city or other local laws or
				ordinances) or regardless of whether or not an actual permit is required, shall
				file two sets of plans and specifications with the department(s) having
				jurisdiction for their review and approval. The plans and specifications shall
				be in detail and shall include/comply with the following:
1. a scaled plot plan of the park, indicating
				the spaces, area or portion of the park for the parking of mobile/manufactured
				homes;
2. size, location and
				specification of park drainage system;
3. size, location and specification of water
				supply lines;
4. size, location and
				layout of service building, if applicable (see
				§1619 of this code);
5. size, location, specification and layout
				of the fire protection system, if applicable;
6. a scaled layout of typical
				mobile/manufactured home sites;
7.
				applications/submittals shall bear the approval of the local enforcement
				agencies as to compliance with city or parish plumbing, zoning and health
				ordinances;
8. plumbing required by
				this Chapter shall comply with all city, parish and state plumbing and health
				ordinances and regulations;
9. the
				issuance of a permit (or an approval of a submittal) shall not constitute
				approval of any violation of this code or violation of any city or parish
				ordinance or regulation; and
10. an
				approved set of plans and specifications and a copy of the permit (or written
				approval of a submittal) shall be kept on the park premises until the final
				inspection has been made.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1609 - Materials

Current through Register Vol. 50, No. 6, June 20, 2024
A. Unless otherwise
				provided for in this Chapter, all piping fixtures or devices used in the
				installation of drainage and water distribution systems for mobile/manufactured
				home parks, or parts thereof, shall conform to the quality and weights of
				materials required by the Louisiana State Plumbing Code.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1611 - General Regulations

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Unless otherwise provided for in this Chapter, all plumbing fixtures, piping,
				drains, appurtenances and appliances designed and used in a park drainage,
				water distribution system and service connections shall be installed in
				conformance with the Louisiana State Plumbing Code.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1615 - Water Supply and Distribution Systems

Current through Register Vol. 50, No. 6, June 20, 2024
A. General. Every mobile/manufactured home
				site shall be provided with an individual branch water service line delivering
				potable water. The outlet of the branch water service line shall terminate on
				the left side of the site of the mobile/manufactured home.
B. Minimum Size. Water service lines to each
				mobile/manufactured home site shall be sized to provide a minimum of 17 gpm
				(1.1 L/s) at the point of connection with the mobile/manufactured home's water
				distribution system. All water service lines shall be a minimum of
				3/4-inch.
C. Separate Service
				Shutoff. A separate service shutoff valve shall be installed in each water
				service line. Per §617. A of this code, such separate shutoff valve shall be a
				full port ball valve.
D. Water
				Service Connections. The water service connection from the water service line
				to the mobile/manufactured home shall be not less than 1/2-inch diameter. A
				rigid pipe shall not be used. Flexible metal tubing is permitted. Fittings at
				either end shall be of a quick disconnect type not requiring any special tools
				or knowledge to install or remove.
E. Water Supply System Design. The water
				supply system shall be designed to provide a minimum of 150 gallons (568 L) per
				day for each mobile/manufactured home, plus such additional volume as may be
				required for fire protection of the park, service buildings and other community
				facilities.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1617 - Mobile/Manufactured Home Connections

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Responsibility. When it is evident that there exists, or may exist, a violation
				of these rules, the owner, operator, lessee, person in charge of the park or
				any other person causing a violation shall cause it to be corrected immediately
				or disconnect the service connections and mobile/manufactured home drain
				connection from the respective park water service line and sewer
				lateral.
B. Drain Connections.
				Mobile/manufactured home drain connections shall be of approved semi-rigid pipe
				having smooth interior surfaces of not less than 3-inch inside diameter. Drain
				connections shall be equipped with a standard quick disconnect screw, clamp
				type fitting or solvent welder, not less in size than the outlet. Drain
				connections shall be gastight and no longer than necessary to make the
				connection between the mobile/manufactured home outlet and the trap inlet on
				the site.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1619 - Service Buildings

Current through Register Vol. 50, No. 6, June 20, 2024
A. Each
				mobile/manufactured home park serving travel trailers shall have at least one
				service building to provide minimum sanitation and laundry facilities in accord
				with
				§1509 of this code.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1621 - Maintenance

Current through Register Vol. 50, No. 6, June 20, 2024
A. All devices or
				safeguards required by this Chapter shall be maintained in good working order
				by the owner, operator, or lessee of the mobile/manufactured home park or his
				designated agent.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 16 - Mobile/Manufactured Homes and Mobile/Manufactured Home Parks [formerly Appendix C - Mobile/ Manufactured Homes and Mobile/Manufactured Home Parks] › Section XIV-1623 - Individual Mobile/Manufactured Homes

Current through Register Vol. 50, No. 6, June 20, 2024
A. Individual mobile/manufactured homes
				located within previously constructed mobile/manufactured home parks shall be
				provided with a trailer trap in accord with §1003. E of this code.
Click Here To View
				  Image
Figure 1623.A - Trailer Trap and
				  Vent
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 17 - Sewerage System Regulations [formerly Appendix E - Private Sewage Disposal] › Section XIV-1701 - General

Current through Register Vol. 50, No. 6, June 20, 2024
A. Refer to Part
				XIII (Sewage Disposal) of the State of Louisiana Sanitary Code (LAC 51:XIII)
				for applicable sewage disposal regulations.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 18 - Appendices › Section XIV-1801 - Scope

Current through Register Vol. 50, No. 6, June 20, 2024
A. The provisions
				of the appendices contained in this Chapter are designed for informational
				purposes only. When the word "shall' is used in one or more provisions of this
				Chapter, it is advisable to take the provision seriously and as though it were
				an actual requirement. Doing so will assist in ensuring compliance with the
				actual requirements of Chapters 1-17.
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 18 - Appendices › Section XIV-1805 - Appendix B - Sizing of Water Piping System [formerly Appendix F - Sizing of Water Piping System]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				Scope. This Appendix outlines a procedure for sizing a water piping system.
				This design procedure is based on the minimum static pressure available from
				the supply source, the head charges in the system due to friction and
				elevation, and the rates of flow necessary for operation of various fixtures.
1. Because of the variable conditions
				encountered in hydraulic design, it is impractical to specify definite and
				detailed rules for sizing of the water piping system. Accordingly, other sizing
				or design methods conforming to good engineering practice standards are
				acceptable alternates to that presented herein.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 18 - Appendices › Section XIV-1809 - Appendix D-Vacuum Drainage Systems [formerly Appendix K-Vacuum Drainage Systems]

Current through Register Vol. 50, No. 6, June 20, 2024
A.
				System. A vacuum drainage system shall comply with the following.
1. General. Since a vacuum drainage system is
				considered an alternate designed plumbing system, the requirements of Chapter
				12 of this code shall apply and such systems shall be considered on an
				individual basis.
2. System Design.
				Vacuum drainage systems shall be designed in accordance with manufacturer's
				specifications. The system arrangement, including piping, tank assemblies,
				vacuum pump assembly and other components necessary for proper function of the
				system shall be in accordance with manufacturer's specifications. In general,
				vacuum drainage systems may be considered for approval by the state health
				officer for use on handling island display refrigerator/freezer condensate
				wastes in grocery stores. Such wastes from display refrigerators/freezers
				handling meat or dairy products or other products containing fats, grease or
				oils shall discharge, in an approved manner, through an approved grease trap
				prior to discharge into the sanitary sewer system. Also, any food items stored
				below any portion of a vacuum drainage system (for example, in-the-ceiling
				vacuum waste piping located above food shelves or food preparation areas) shall
				be protected from potential contamination by adequate shielding to intercept
				any potential drips (in accord with LAC 51:XXIII.1503.A.6). Vacuum drainage
				systems for liquid wastes from other types of plumbing fixtures, such as sinks,
				water closets, etc., are discouraged. A standby emergency generator,
				permanently wired to automatically operate the vacuum pump motor upon lost of
				the normal power source, should be installed to ensure continuous operation of
				a vacuum drainage system.
3. Plans
				and specifications. Plans and specifications for such systems shall be designed
				by a Louisiana Registered Professional Engineer registered in either civil or
				mechanical engineering and submitted to the state health officer for review and
				approval prior to installation.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 18 - Appendices › Section XIV-1811 - Appendix E - Alternate Designed Plumbing Systems [formerly Appendix L - Alternate Designed Plumbing Systems]

Current through Register Vol. 50, No. 6, June 20, 2024
A. General. Pursuant to the requirements of
				Chapter 12 of this code, the approval of alternate designed plumbing systems
				shall be considered on an individual basis.
1. Scope. The provisions of this appendix
				shall assist in governing the materials, design and installation of
				non-prescriptive plumbing systems, also known as alternate designed plumbing
				systems. In accord with the requirements of Chapter 12 of this code, any one of
				the systems mentioned in this appendix shall be designed by a Louisiana
				registered professional engineer registered in either civil or mechanical
				engineering. Any alternate designed plumbing system shall not be installed
				until the plans and specifications have been reviewed and approved by the state
				health officer, pursuant to the requirements of Chapter 12 of this
				code.
2. General System Provisions.
				Discharge pipe systems shall comprise the minimum of pipe work necessary to
				carry away the foul water from the building quickly and quietly, with freedom
				from nuisance or risk of injury to health.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XIV - Plumbing › Chapter 18 - Appendices › Section XIV-1813 - Metric Conversions

Current through Register Vol. 50, No. 6, June 20, 2024
A. For
				convenience, the following may be used to convert English units of measurement
				to Metric units of measurement.
Table 1813.A
Unit of Measure
STARTING WITH the English unit of
							 measurement
MULTIPLY BY
TO GET the Metric unit of
							 measurement
Length
inches
ft
25.4
0.3048
mm
m
Area
sq in
sq ft
645.16
0.0929
mm2
m2
Volume
cu in
cu ft
gal
0.01639
28.3169
3.785
L
L
L
Mass
lb
0.4536
kg
Mass/unit length
plf (lb/ft)
1.4882
kg/m
Mass/unit area
psf (lb/sq ft)
4.882
kg/m2
Mass density
pcf (lb/cu ft)
16.02
kg/m3
Force
lb
4.4482
N
Force/unit length
plf (lb/ft)
14.5939
N/m
Pressure
psi
psf (lb/sq ft)
in. of Hg @ 60°F
6.895
47.88
3.37685
kPa
Pa
kPa
stress, modulus of elasticity
psi
psf (lb/sq ft)
6.895
47.88
kPa
Pa
Second moment of area
In4
416,231
Mm4
Section modulus
In3
16,387.064
mm3
Temperature
°F-32
°F + 459.67
5/9
5/9
°C
K
Energy, work, quantity of heat
kWh
Btu
ft.lb (force)
3.6
1055
1.3558
MJ
J
J
Power
ton (refrig)
Btu/s
hp (electric)
Btu/h
3.517
1.0543
745.7
0.2931
kW
kW
W
W
Thermal conductance (U value)
Btu/f2. h. °F
5.6783
W/m2. K
Thermal resistance (R value)
Ft2. h. °F/Btu
0.1761
M2. K/W
Flow
gpm
cfm
0.0631
0.4719
L/s
L/s
Illuminance
foot-candle (Im/sq ft)
10.76
Ix (lux)
Velocity (speed)
mph
0.447
m/s
Plane angle
°(angle)
0.01745
rad
AUTHORITY NOTE:
				  Promulgated in accordance with
				  R.S.
				  40:4(A)(7) and
				  R.S.
				  40:5(2)(3)(7)(9)(16)(17)(20).
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XV - Hotels, Lodging Houses, Boarding Houses › Chapter 1 - General › Section XV-101 - Definitions [formerly paragraph 15:001]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Unless otherwise specifically provided
				herein, the following words and terms used in this Part of the sanitary code
				and all other Parts which are adopted or may be adopted are defined for the
				purpose thereof as follows.
Boarding House
-a building or group of
				  buildings where persons are supplied with, and charged for, sleeping
				  accommodations and meals for fixed periods of time.
Hotel
-a building where transient guests are
				  usually received without stipulated engagement as to the duration of their stay
				  and are supplied with, and charged for, lodging or meals or both, and such
				  services and attention as are necessarily incident to the use of such places as
				  a temporary abode. This definition includes motels.
Lodging House
-a building or group of
				  buildings where persons are supplied with, and charged for, sleeping
				  accommodations but not meals.
Proprietor
-a person as defined in Part I,
				  who owns or operates a hotel, lodging house or boarding
				  house.
AUTHORITY NOTE: The
				  first general authority for promulgation of the sanitary code is in
				  R.S.
				  36:258 (B), with more particular provisions
				  found in Chapters 1 and 4 of Title 40 of the Louisiana Revised Statutes. This
				  Part is promulgated in accordance with the specific provisions of R. S. 40: 4
				  (A)(5) and R.S. 40: 5.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XV - Hotels, Lodging Houses, Boarding Houses › Chapter 1 - General › Section XV-103 - Permits [formerly paragraph 15:002-1]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Any person operating a hotel, lodging
				house or boarding house must obtain a permit from the state health
				officer.
B. [Formerly paragraph
				15:002-2] Such permits are non-transferable.
AUTHORITY NOTE:
				  Promulgated in accordance with R.S. 40: 4 (A)(5) and
				  R.S.
				  40:5.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XV - Hotels, Lodging Houses, Boarding Houses › Chapter 1 - General › Section XV-105 - Plans and Specifications [formerly paragraph 15:003]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Any person constructing, expanding, or
				renovating a hotel, lodging house or boarding house shall submit plans to and
				acquire approval of the state health officer.
AUTHORITY NOTE:
				  Promulgated in accordance with R.S. 40: 4 (A)(5) and
				  R.S.
				  40:5.
Louisiana Administrative Code › Title 51 - PUBLIC HEALTH-SANITARY CODE › Part XV - Hotels, Lodging Houses, Boarding Houses › Chapter 1 - General › Section XV-107 - Water Supply [formerly paragraph 15:004]

Current through Register Vol. 50, No. 6, June 20, 2024
A. Enough potable water under pressure to
				supply a minimum of 50 gallons per person per day shall be provided for
				drinking, cooking and washing purposes. Water supplied to hotels, lodging
				houses and boarding houses shall conform to the requirements of Part XII of
				this Code.
B. [Formerly paragraph
				15:005] Required Reports. Where a water treatment process is employed, accurate
				and complete daily reports on the report on the operation thereof shall be kept
				and submitted at monthly intervals to the state health officer in the parish in
				which the water supply is located, on a form prescribed by the state health
				officer.
1. [Formerly paragraph 15:006] Any
				failure of adequate treatment, change in treatment, process or equipment, or
				any change in source of water supply, shall be reported immediately to the
				state health officer.