reglab/statecodes huggingface dataset:
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 5 - Laboratory and Analytical Requirements › Section 10 CSR 60-5.020 - Laboratory Certification

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This amendment clarifies the application
				  process for laboratories requiring certification from the department for the
				  analysis of public drinking water samples, updates language on the source of
				  performance evaluation samples, updates regulatory citations, and adds new
				  sections for provisional certification, interim certification, denial,
				  revocation, and reporting of significant changes.
(1) For the purpose of determining compliance
				with this chapter, analytical results will be acceptable only if the samples
				have been analyzed by a laboratory certified by the department.
(A) Any laboratory seeking certification from
				the department for chemical or bacteriological analyses shall-
1. Submit a completed application, in a
				format provided by the department, with the applicable fee(s) pursuant to
				10 CSR
				60-16.020;
2. Successfully pass a certification audit
				conducted by the department or the Department of Health and Senior Services;
				and
3. Demonstrate proficiency
				pursuant to the requirements of this rule through the analysis of performance
				evaluation samples.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 6 - Enforcement › Section 10 CSR 60-6.010 - Procedures and Requirements for Variances

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule sets forth procedures and
				  requirements for requesting and granting variances for any size of public water
				  system.
(1) Conditions of
				Variance. The department may grant one (1) or more variances to any public
				water system from any maximum contaminant level (MCL) requirement, except for
				those MCL violations that present an acute, short-term risk to public health,
				and any specified treatment technique.
(A) A
				variance from an MCL may be granted to a public water system upon a finding
				that, due to characteristics of raw water sources which are reasonably
				available, the system cannot meet the MCL requirement-
1. On the condition that the system installs
				the best available technology, treatment techniques or other means, which the
				department, taking cost into consideration, finds generally available and based
				upon an evaluation satisfactory to the department that indicates that
				alternative sources of water are not reasonably available to the system;
				and
2. The granting of a variance
				will not result in an unreasonable risk to persons served by the
				system.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 6 - Enforcement › Section 10 CSR 60-6.020 - Procedures and Requirements for Exemptions

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes requirements for
				  requesting exemptions to maximum contaminant levels and treatment
				  techniques.
(1) Conditions of
				Exemption. The department may exempt a public water system from any maximum
				contaminant level (MCL) requirement, except for those MCL violations that
				present an acute, short-term risk to public health, or any treatment technique
				requirement, or both, upon a finding that-
(A)
				Due to compelling factors (which may include economic factors, including
				qualification of the public water system as a system serving a disadvantaged
				community), the public water system is unable to comply with the contaminant
				level or treatment technique requirement or to implement measures to develop an
				alternative source of water supply;
(B) The public water system was in operation
				on the effective date of the contaminant level or treatment technique
				requirement, or for a public water system that was not in operation by that
				date, no reasonable alternative source of drinking water is available to the
				system;
(C) The granting of the
				exemption will not result in an unreasonable risk to the health of persons
				served by the system; and
(D)
				Management or restructuring changes (or both) cannot reasonably be made that
				will result in compliance with sections 640.100-640.140, RSMo or rules
				promulgated thereunder, or if compliance cannot be achieved, improve the
				quality of the drinking water.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 6 - Enforcement › Section 10 CSR 60-6.030 - Schedules for Variances and Exemptions

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes schedules for
				  compliance with conditions of general variances granted under
				  10 CSR
				  60-6.010 to any size public water system and
				  exemptions granted under
				  10 CSR
				  60-6.020.
(1) Schedules for variances granted under
				10 CSR
				60-6.010.
(A)
				Compliance and Implementation. The department shall provide a schedule for-
1. Compliance (including increments of
				progress) by the public water system with each contaminant level requirement
				covered by the variance; and
2.
				Implementation by the public water system of the control measures the
				department may require for each contaminant covered by the variance.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 6 - Enforcement › Section 10 CSR 60-6.040 - Public Hearings on Variance, Variance Schedules, Exemptions and Exemption Schedules

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes requirements for
				  public hearings on variances, exemptions, variance schedules and exemption
				  schedules.
(1) Hearing
				Required. Before a variance, variance schedule, exemption or exemption schedule
				proposed by the department as required by
				10 CSR
				60-6.010 and
				10 CSR
				60-6.020 may take effect, the department shall provide
				notice and opportunity for public hearing on the variance, variance schedule,
				exemption or exemption schedule. Any hearing held pursuant to this section
				shall be held in an area where distribution is made by the supplier of water
				requesting a variance or exemption. A notice given pursuant to this section may
				cover the granting of more than one (1) variance, variance schedule, exemption
				or exemption schedule. A hearing held pursuant to the notice shall include each
				of the variances, variance schedules, exemptions or exemption schedules covered
				by the notice. The notice shall include a summary of the proposed variance,
				variance schedule, exemption or exemption schedule as specified in the notice
				and that they also may request a public hearing on the proposed variance,
				variance schedule, exemption or exemption schedule.
(2) Notice of Hearing Required. Public notice
				of an opportunity for hearing on a variance, variance schedule, exemption or
				exemption schedule shall be circulated in a manner designed to inform
				interested and potentially interested persons of the proposed variance,
				variance schedule, exemption or exemption schedule and shall include at least
				the following:
(A) Posting of a notice in the
				principal post office of each community or area served by the public water
				system and publication of a notice in a newspaper(s) of general circulation in
				the area served by the public water system; and
(B) Mailing of a notice to other appropriate
				state or local agencies at the department's discretion.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 6 - Enforcement › Section 10 CSR 60-6.060 - Waivers From Baseline Monitoring Requirements

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This amendment removes the requirement that
				  public water systems must submit requests for waivers that meet department
				  specifications. It also removes incorrect citations due to rule
				  rescissions.
(1) Waivers may
				be granted by the department in accordance with the criteria in sections (2)
				and (3) of this rule. The department may initiate the evaluation and issue a
				waiver based on its evaluation of the criteria in sections (2) and (3) of this
				rule. A public water system may submit a written request and supporting
				documentation for a waiver in accordance with sections (2) and (3) of this rule
				at any time if the department has not issued or denied a waiver.
(2) Use waivers may be granted if it is
				determined that there has been no previous use of a contaminant within a given
				boundary, and that the public water supply system is in no danger of
				contamination from the specified contaminant. Use waivers are based on the use,
				or absence of use, of a potentially harmful contaminant within a given
				boundary. The boundary size will be determined by the department and can range
				from a single water system to statewide. Use waivers obtained for asbestos and
				synthetic organic chemicals (SOCs) may relieve the system of any sampling
				requirements. Use waivers will not be granted for volatile organic chemicals
				listed in 10 CSR
				60-4.100(2) or for inorganic
				chemicals listed in 10 CSR
				60-4.030(1) other than asbestos.
(A) Asbestos listed in
				10 CSR
				60-4.030(1) -Waivers from analysis
				for asbestos in a water system will be based on the existence of
				asbestos-cement piping within the water system or asbestos contamination within
				the source water. If any asbestos-cement piping is present in any part of the
				treatment/distribution system, or if the source water is known to or suspected
				to contain asbestos, waivers will not be granted.
(B) SOCs listed in
				10 CSR
				60-4.040 -Waivers from analysis for SOCs in a water
				system will be based on knowledge of previous use (including transportation,
				storage, or previous disposal) within a given boundary. If a given SOC has been
				detected within a water system, a waiver will not be granted to that
				system.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 7 - Reporting › Section 10 CSR 60-7.020 - Reporting Requirements for Lead and Copper Monitoring

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes requirements for
				  reports of water sample analyses and monitoring for lead and
				  copper.
(1) Reporting
				requirements for lead and copper tap water monitoring and for water quality
				parameter monitoring.
(A) Except as provided
				in paragraph (1)(A)7. of this rule, a water system shall report to the
				department the information required by this subsection for all tap water
				samples and all water quality parameter samples specified in
				10
				CSR 60-15.080 within the first ten (10) days following
				the end of each applicable monitoring period specified in
				10
				CSR 60-15.070,
				10
				CSR 60-15.080, and
				10
				CSR 60-15.090 (such as, every six (6) months,
				annually, or every three (3) years). For monitoring periods with a duration
				less than six (6) months, the end of the monitoring period is the last date
				samples can be collected during that period as specified in
				10
				CSR 60-15.070 and
				10
				CSR 60-15.080. The water system shall report-
1. The results of all tap samples for lead
				and copper including the location of each site and the criteria under
				10
				CSR 60-15.070(1) under which the site
				was selected for the system's sampling pool;
2. Documentation for each tap water lead or
				copper sample for which the water system requests invalidation pursuant to
				10
				CSR 60-15.070(6);
3. The ninetieth percentile lead and copper
				concentrations measured from among all lead and copper tap water samples
				collected during each monitoring period (calculated in accordance with
				10 CSR
				60-15.010(3)(C) ), unless the
				department calculates the system's ninetieth percentile lead and copper levels
				under section (8) of this rule;
4.
				With the exception of initial tap sampling conducted pursuant to
				10
				CSR 60-15.070(4)(A), the system shall
				specify any site which was not sampled during previous monitoring periods and
				include an explanation of why sampling sites have changed;
5. The results of all tap samples for pH and,
				where applicable, alkalinity, calcium, conductivity, temperature, and
				orthophosphate or silica collected under
				10
				CSR 60-15.080(2)-(5);
6. The results of all samples collected at
				the entry point(s) to the distribution system for applicable water quality
				parameters under
				10
				CSR 60-15.080(2)-(5); and
7. A water system shall report the results of
				all water quality parameter samples collected under
				10
				CSR 60-15.080(3)-(6) during each six-
				(6-) month monitoring period specified in
				10
				CSR 60-15.080(4) within the first ten
				(10) days following the end of the monitoring period unless the department has
				specified a more frequent reporting requirement.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 8 - Public Notification › Section 10 CSR 60-8.010 - Public Notification of Conditions Affecting a Public Water Supply

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: The amendment corrects rule citations due to
				  amendments to other regulations in 10 CSR 60, removes outdated rule language
				  and provides clarification on existing regulations
.
(1) General Information and Requirements.
(A) Types of Violations and Other Situations
				Requiring Public Notice.
1. Failure to comply
				with an applicable maximum contaminant level (MCL) or maximum residual
				disinfectant levels (MRDL).
2.
				Failure to comply with a prescribed treatment technique.
3. Failure to perform required water quality
				monitoring as required by drinking water regulations.
4. Failure to comply with testing procedures
				as prescribed by a drinking water regulation.
5. Operation under a variance or an
				exemption.
6. Failure to comply
				with the requirements of any schedule that has been set under a variance or
				exemption.
7. Special public
				notice.
8. Occurrence of a
				waterborne disease outbreak or other water-borne emergency.
9. Exceedance of the nitrate MCL by
				noncommunity water systems where granted permission by the
				department;
10. Exceedance of the
				secondary maximum contaminant level (SMCL) for fluoride.
11. Availability of unregulated contaminant
				monitoring data.
12. Other
				violations and situations determined by the department to require a public
				notice.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 8 - Public Notification › Section 10 CSR 60-8.030 - Consumer Confidence Reports

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: The amendment corrects rule citations due to
				  amendments and rescissions of other regulations in 10 CSR 60 and removes
				  outdated rule language and provides clarification on existing
				  regulations.
(1)
				Applicability, Definitions, and General Requirements.
(A) This rule applies only to community water
				systems.
(B) The definitions in
				10 CSR 60-2.015 apply
				to this rule with the following exceptions:
1.
				For the purpose of this rule, customers are defined as billing units or service
				connections to which water is delivered by a community water system;
				and
2. For the purpose of this
				rule, detected means at or above the levels prescribed by
				10 CSR
				60-5.010(8) for organic, inorganic,
				and radioactive contaminants and disinfection byproducts.
(C) Each existing community water system must
				deliver its report to customers by July 1 annually. The report must contain
				data collected during, or prior to, the previous calendar year as prescribed in
				paragraph (2)(D)3. of this rule.
(D) A new community water system must deliver
				its first report to customers by July 1 of the year after its first full
				calendar year in operation and annually thereafter.
(E) A community water system that sells water
				to another community water system must deliver to the purchasing water system
				the information required in subsection (2)(B), and any information required in
				subsections (2)(D) through (2)(G) of this rule for monitoring conducted at the
				source or entrypoint to the distribution system. The required information from
				the seller must be provided no later than April 1 annually or on a date
				mutually agreed upon by the seller and the purchaser that is documented in
				writing and signed by both parties.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 9 - Record Maintenance › Section 10 CSR 60-9.010 - Requirements for Maintaining Public Water System Records

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: The purpose of this rulemaking is to clarify
				  regulatory requirements for record maintenance by water suppliers at their
				  premises for the indicated time period.
(1) All suppliers of water to a public water
				system must retain records on their premises or at a convenient location near
				their premises as follows:
(A) Records of
				microbiological analyses, turbidity analyses, and operational analyses must be
				retained for a minimum of five (5) years. Records of chemical analyses must be
				retained for a minimum of ten (10) years. Actual laboratory reports used in the
				previous analyses must be retained for the appropriate period given previously.
				In lieu of an original report or copy, laboratory data may be transferred to
				tabular summaries provided the following information is included: the date,
				address, place, and time of sampling; identification of the sample (that is, a
				routine distribution system sample, check sample, raw or other special purpose
				water sample); date of analysis; laboratory and person responsible for
				performing analysis; analytical method used and the results of the
				analysis;
(B) Records of action
				taken by the system to correct violations of these rules must be retained for a
				period of at least three (3) years after the last action taken to correct the
				violation;
(C) Copies of any
				written reports, summaries, or communications relating to sanitary surveys of
				the system conducted by the system itself, by a private consultant, or by any
				local, state, or federal agency must be retained for at least ten (10) years
				after completion of the sanitary survey;
(D) Records concerning a variance or
				exemption granted to the system must be retained for a period of at least five
				(5) years following the expiration of the variance or exemption;
(E) Original records of all sampling data and
				analyses, reports, surveys, letters, evaluations, schedules, state
				determinations, and any other information required by
				10 CSR
				60-5.010,
				10 CSR
				60-5.020,
				10
				CSR 60-7.020, and
				10 CSR
				60-15.010-10
				CSR 60-15.090 must be retained for no fewer than
				twelve (12) years;
(F) Copies of
				public notices issued pursuant to
				10 CSR
				60-8.010 and certifications issued to the department
				pursuant to 10 CSR
				60-7.010(10) shall be kept for at
				least three (3) years after issuance; and
(G) Copies of monitoring plans shall be kept
				for the same period of time as the records of analyses taken under the plan are
				required to be kept under subsection (1)(A) of this rule, except as specified
				elsewhere in 10 CSR 60.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 10 - Plans and Specifications; Siting Requirements; Recreational Use of Impoundments › Section 10 CSR 60-10.010 - Plans and Specifications

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: The amendment will allow the submittal of
				  engineering reports at the same time as plans and specifications under certain
				  circumstances and allow Owner Supervised Programs to include all waterlines
				  with a pipe diameter smaller than four (4) inches.
PUBLISHER'S NOTE: The secretary of state has
				  determined that the publication of the entire text of the material which is
				  incorporated by reference as a portion of this rule would be unduly cumbersome
				  or expensive. Therefore, the material which is so incorporated is on file with
				  the agency who filed this rule, and with the Office of the Secretary of State.
				  Any interested person may view this material at either agency's headquarters or
				  the same will be made available at the Office of the Secretary of State at a
				  cost not to exceed actual cost of copy reproduction. The entire text of the
				  rule is printed here. This note refers only to the incorporated by reference
				  material.
(1) Report
				Required. When plans are being made by a supplier of water to a community water
				system or subdivision for constructing expansions, modifications, and
				improvements of the water supply source, water treatment facility or for the
				development of a new community water system or subdivision, the supplier of
				water shall submit an engineer-prepared report to the department for review and
				approval. Upon receipt of an engineering report, the department will evaluate
				the report and either approve the report in writing or outline the requirements
				for further investigation.
(A) Written
				approval of the engineering report shall be obtained before construction plans
				and specifications are finalized, unless otherwise approved by the
				department.
(B) Engineering reports
				need not be submitted to the department for facilities constructed under a
				supervised program.
(C) If the
				original approved report is more than two (2) years old, an updated engineering
				report must be submitted before final plans and specifications will be reviewed
				or as deemed necessary by the department.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 10 - Plans and Specifications; Siting Requirements; Recreational Use of Impoundments › Section 10 CSR 60-10.020 - Siting Requirements

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes requirements for
				  siting of new or expanded water systems.
(1) To the extent practicable, all new or
				expanded water systems must not be located on a site which-
(A) Is subject to a significant risk from
				earthquakes, floods, fires, pollution or other disasters which could cause a
				breakdown of the public water system or a portion of the system; and
(B) Except for intake structures, is within
				the floodplain of a one hundred (100)-year flood where appropriate records
				exist.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 10 - Plans and Specifications; Siting Requirements; Recreational Use of Impoundments › Section 10 CSR 60-10.030 - Recreational Use of Public Water Supply Impoundments

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes limitations on
				  recreational use of water supply impoundments.
(1) Every supplier of water to a public water
				supply must apply for and secure the approval of the department before
				permitting the use of public water supply impoundments for recreational usage.
(A) Regulated recreational activities are
				permitted when provisions for these activities are included in the original
				planning, construction and approval of the impoundment and water treatment
				facilities.
(B) Recreational
				activities proposed for existing impoundments will be appraised in the light of
				the effect on the primary purposes of the impoundment, the capability of the
				water treatment works, the physical adaptability of the impoundment to the
				desired recreational use and the maintenance of public confidence in the water
				supply.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 10 - Plans and Specifications; Siting Requirements; Recreational Use of Impoundments › Section 10 CSR 60-10.040 - Prohibition of Lead Pipes, Lead Pipe Fittings and Lead Solder and Flux

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule protects public water systems and
				  the customer water systems connected to the public water systems from the
				  leaching of lead into the drinking water.
(1) This rule applies to all public water
				systems.
(2) For the purpose of
				this rule, the term lead-free, when used with respect to-
(A) Solder and flux, refers to solders and
				flux containing not more than two-tenths percent (0.2%) lead;
(B) Pipes and pipe fittings, refers to pipes
				and pipe fittings containing not more than eight percent (8.0%) lead;
				and
(C) Plumbing fittings and
				fixtures intended by the manufacturer to dispense water for human ingestion,
				refers to fittings and fixtures that are in compliance with standards
				established in accordance with
				42
				U.S.C.300 g - 6(e).
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 11 - Backflow Prevention › Section 10 CSR 60-11.010 - Prevention of Backflow

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This amendment allows the installation of
				  backflow prevention assemblies approved by the American Society of Sanitary
				  Engineering (ASSE).
(1)
				Applicability, Exemptions and Compliance Dates.
(A) Applicability. This rule applies to all
				community water systems.
(B)
				Exemptions.
1. This rule does not apply to
				customer facilities used solely for residential purposes unless a
				cross-connection is specifically identified or the rule indicates
				otherwise.
2. The department may
				issue an exemption from the requirements of paragraphs (3)(A)1. and (3)(B)1. of
				this rule if the customer can demonstrate to the department, the local
				governmental authority (if one exists) and the supplier of water that the
				activities taking place at the customer's facility and the materials used in
				connection with these activities or stored on the premises cannot endanger the
				health of customers or degrade the water quality of the public water system
				should backflow occur, or that any potential risk posed by these materials or
				activities is isolated from the public water system. Those customers granted an
				exemption in accordance with this paragraph shall report to the supplier of
				water any proposed change in process, plumbing or materials used or stored at
				the exempted facility at least fourteen (14) days prior to making the
				change.
3. Any exemption granted
				under paragraph (1)(B)2. of this rule shall be void if the supplier of water,
				local governmental authority (if one exists) or the department determines that
				the customer facility has become an actual or potential backflow hazard, or if
				the customer fails to provide notice at least fourteen (14) days prior to
				making any change in process, plumbing or materials used or stored at the
				facility.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 11 - Backflow Prevention › Section 10 CSR 60-11.030 - Backflow Prevention Assembly Tester Certification

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: The amendment removes a provision that is no
				  longer applicable.
(1)
				Applicability. This rule applies to all persons seeking certification or
				recertification as backflow prevention assembly testers. A certified backflow
				prevention assembly tester shall inspect, test and report on backflow
				prevention assemblies in accordance with applicable requirements in 10 CSR
				6011.010.
(2) Certification
				Requirements.
(A) Any person seeking to be a
				certified backflow prevention assembly tester shall-
1. Satisfactorily complete written and
				performance (hands on) examinations (including questions specific to Missouri
				backflow prevention rules) provided by the American Backflow Prevention
				Association (ABPA) Tester Certification Program or the American Society of
				Sanitary Engineering (ASSE); and
2.
				Ensure that ABPA or ASSE notifies the department that the tester has passed the
				examinations. The department shall not be held liable for any failure of ABPA
				or ASSE to notify the department that a person has passed the written and
				performance examinations.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 12 - Emergency Operations Plan › Section 10 CSR 60-12.010 - Emergency Operations Plan

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: The purpose of this rule is to insure that a
				  supplier of water to a public water system implements an adequate plan for
				  providing drinking water under emergency conditions.
(1) This rule applies only to community water
				systems.
(2) Each supplier of water
				to a community water system shall develop and implement a plan for assuring, to
				the extent practicable, continuous water service under emergency conditions.
				Each supplier of water, existing at the time of promulgation of these
				regulations, shall complete its emergency plan by June 30, 1980.
(A) To facilitate a coordinated response
				under emergency conditions, a supplier of water to a community water system,
				serving more that fifty thousand (50,000) population, shall file two (2) copies
				of its emergency response plan with the department.
(B) A supplier of water to a community water
				system serving less than fifty thousand (50,000) population need not file a
				copy of their plan with the department but must make a copy available to key
				operating personnel and for inspection by department personnel during
				inspection of the water supply facilities.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 13 - Grants and Loans › Section 10 CSR 60-13.020 - Drinking Water State Revolving Fund Program

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule sets forth eligibility and program
				  requirements for financial assistance from the Drinking Water State Revolving
				  Fund program authorized pursuant to section 1452 of the federal Safe Drinking
				  Water Act, as amended, and in section
				  640.107,
				  RSMo.
PUBLISHER'S NOTE: The secretary of state has
				  determined that the publication of the entire text of the material which is
				  incorporated by reference as a portion of this rule would be unduly cumbersome
				  or expensive. This material as incorporated by reference in this rule shall be
				  maintained by the agency at its headquarters and shall be made available to the
				  public for inspection and copying at no more than the actual cost of
				  reproduction. This note applies only to the reference material. The entire text
				  of the rule is printed here
.
(1) Application and Eligibility Requirements.
				This section applies to recipients of financial assistance from the Drinking
				Water State Revolving Fund (DWSRF) program. Recipients of assistance are
				subject to the requirements of this regulation, unless otherwise specified. The
				Code of Federal Regulations referenced in the regulation are incorporated as
				published July 1, 2017. The regulations are incorporated by reference without
				any later amendments or modifications. To obtain a copy, contact the U.S.
				Government Printing Office at 732 North Capitol Street N W, Washington, D.C.,
				20401, toll free at (866) 512-1800 or by visiting
https://bookstore.gpo.gov
. To
				obtain the decennial median household income visit the U.S. Census Bureau
				American Fact Finder webpage
https://factfinder.census.gov/faces/nav/jsf/pages/community_facts.xhtml
,
				contact the U.S. Census Bureau, 4600 Silver Hill Road Suitland, MD 20746, or
				toll free at (800) 923-8282.
(A) Definitions.
1. The terms and definitions in section
				640.107,
				RSMo, 10
				CSR 60-2.015, and
				40
				CFR 35.3505, apply to the rules in this
				chapter.
2. Initiation of
				operation-The date when the first constructed component is capable of being
				used for its intended purpose.
3.
				PSC-Missouri Public Service Commission.
4. EIERA-State Environmental Improvement and
				Energy Resources Authority.
5.
				Loan-Unless stated otherwise, loan generally refers to the agreement to lend
				money to an eligible recipient. The type of agreement could be a loan
				agreement, bond purchase agreement, or other debt instrument.
6. Recipient-The recipient of financial
				assistance from programs supported or secured by the Water and Wastewater Loan
				Fund, the Water and Wastewater Loan Revolving Fund, DWSRF bonds issued by
				EIERA, or state bond funds.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 13 - Grants and Loans › Section 10 CSR 60-13.025 - State Loan Program

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: The amendment removes language that is no
				  longer applicable, clarifies current rule language, updates language to reflect
				  new state and federal requirements, and removes duplicative and unnecessary
				  regulatory requirements.
(1)
				General Requirements.
(A) The department may
				make direct loans to public water systems by purchasing the general obligation
				bonds, revenue bonds, short-term notes, or other acceptable obligation of any
				qualified recipient for the planning, design or construction, or any
				combination of these, of an eligible project.
(B) In addition to the requirements of this
				rule, the department may require the recipient to include those assurances and
				clauses in the loan agreements and bond resolutions as deemed necessary to
				protect the interest of the state and comply with applicable state and federal
				requirements.
(C) If at any time
				during the term of the loan a recipient desires to sell, lease, mortgage or
				otherwise dispose of the infrastructure financed under this rule, the loan
				becomes due and payable upon transfer unless otherwise approved by the
				department.
(D) This rule sets out
				the general format for loans from state funds. The department shall have the
				authority to make specific refinements, variations, or additional requirements
				as may be necessary or desirable in connection with the efficient operation of
				the loan process.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 13 - Grants and Loans › Section 10 CSR 60-13.030 - Environmental Review

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes procedures and
				  requirements for environmental reviews for assistance from the Drinking Water
				  State Revolving Fund program.
(1) General. The purpose of the environmental
				review is to ensure that the project will comply with applicable local, state,
				and federal laws and rules relating to the protection and enhancement of the
				environment. Based upon the staff's review, the director will make formal
				determinations regarding the potential social and environmental impacts of the
				proposed project. As necessary, the determination will include mitigative
				provisions as a condition of the provision of financial assistance for
				construction. No financial assistance will be provided until a final
				environmental determination has been made. Nothing in this rule shall prohibit
				any public, private, or governmental party from seeking administrative or legal
				relief from the determinations of the director.
(2) Basic Environmental Determinations. There
				are three (3) basic environmental determinations that will apply to projects
				proposed to be implemented with assistance from the fund.
(A) Categorical exclusion (CE). The CE
				determination applies to categories of projects that have been shown over time
				not to entail significant impacts on the quality of the human environment.
1. Projects which meet the following criteria
				may be categorically excluded from formal environmental review requirements:
A. The project is directed solely toward
				minor rehabilitation of existing facilities, functional replacement of
				equipment, or toward the construction of related facilities adjoining the
				existing facilities that do not affect the degree of water treatment or the
				capacity of the public water system. Examples include rehabilitation of
				existing equipment and structures, and the construction of small structures on
				existing sites; or
B. New
				underground water lines or structures if located entirely in existing
				rights-of-way that have been previously disturbed and supported by appropriate
				documentation to verify the rights-of-way location(s) and type(s) of previous
				disturbance.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 14 - Operator Certification › Section 10 CSR 60-14.030 - Operator Training

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule establishes criteria for approval
				  of training courses.
(1) Only
				training related to water system operations and maintenance, treatment
				facilities or distribution systems approved by the department will be given
				credit.
(A) Training requirements for renewal
				will be based on the level of certification held by the operator.
(B) Training should include an update of new
				regulation requirements.
(C) Not
				more than one-half (1/2) of the total renewal training hours required in a
				renewal period shall be credited from safety, supervisory, management,
				administration and financial training and general computer courses.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 15 - Lead and Copper › Section 10 CSR 60-15.020 - Applicability of Corrosion Control Treatment Steps to Small, Medium-Size, and Large Water Systems

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This amendment specifies actions required by
				  the department if a water system is not required to perform a corrosion control
				  study. This amendment will modify the Lead and Copper Rule Short Term Revisions
				  (LCRSTR), adopted in May 2012, which is the National Primacy Drinking Water
				  Regulation and must be adopted by primacy state. The previous LCRSTR amendment
				  inadvertently omitted part of a sentence at 10 CSR 60-15.020(2)(A) 2. which by
				  its absence, implied that the department is not required to specify optimal
				  corrosion control treatment if it does not require a system to perform
				  corrosion control studies following exceedance of the lead and copper action
				  level.
(1) A large system
				(serving more than fifty thousand (50,000) persons) shall complete the
				corrosion control treatment steps as follows unless it is deemed to have
				optimized corrosion control under paragraph (1)(B)1. or 2. of this rule.
(A) Treatment Steps and Deadlines for Large
				Systems.
1. The system shall conduct initial
				monitoring (10
				CSR 60-15.070(4)(A) and
				10
				CSR 60-15.080(2)) during two (2)
				consecutive six-(6-) month monitoring periods by January 1, 1993.
2. The system shall complete corrosion
				control studies (10
				CSR 60-15.030(3)) by July 1,
				1994.
3. The department shall
				designate optimal corrosion control treatment (10
				CSR 60-15.030(4)) by January 1,
				1995.
4. The system shall install
				optimal corrosion control treatment (10
				CSR 60-15.030(6)) by January 1,
				1997.
5. The system shall complete
				follow-up sampling (10
				CSR 60-15.070(4)(B) and
				10
				CSR 60-15.080(3)) by January 1,
				1998.
6. The department shall
				review installation of treatment and designate optimal water quality control
				parameters (10
				CSR 60-15.030(7)) by July 1,
				1998.
7. The system shall operate
				in compliance with the department-specified optimal water quality control
				parameters (10
				CSR 60-15.030(8)) and continue to
				conduct tap sampling (10
				CSR 60-15.070(4)(C) and
				10
				CSR 60-15.080(4)) .
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 15 - Lead and Copper › Section 10 CSR 60-15.030 - Description of Corrosion Control Treatment Requirements

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule describes the corrosion control
				  treatment requirements which are applicable to all water systems under
				  10
				  CSR 60-15.020.
(1) Based upon the results of lead and copper
				tap monitoring and water quality parameter monitoring, small- (serving fewer
				than three thousand three hundred (3,300) persons) and medium-size (serving
				three thousand three hundred one to fifty thousand (3,301-50,000) persons)
				water systems exceeding the lead or copper action level shall recommend
				installation of one (1) or more of the corrosion control treatments listed in
				subsection (3)(A), which the system believes constitutes optimal corrosion
				control for that system. The department may require the system to conduct
				additional water quality parameter monitoring in accordance with
				10
				CSR 60-15.080(2) and perform
				corrosion control studies as described in this rule to assist the department in
				reviewing the system's recommendations.
(2) The department may require any small- or
				medium-sized systems that exceed the lead or copper action level to perform
				corrosion control studies under section (3) of this rule to identify optimal
				corrosion control treatment for the system.
(3) Performance of Corrosion Control Studies.
(A) Any public water system performing
				corrosion control studies shall evaluate the effectiveness of each of the
				following treatments and, if appropriate, combinations of the following
				treatments to identify the optimal corrosion control treatment for that system:
1. Alkalinity and pH adjustment;
2. Calcium hardness adjustment; and
3. The addition of a phosphate or silicate
				based corrosion inhibitor at a concentration sufficient to maintain an
				effective residual concentration in all test tap samples.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 15 - Lead and Copper › Section 10 CSR 60-15.040 - Source Water Treatment Requirements

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule describes the required corrosion
				  control treatment steps for a system's source water and establishes treatment
				  requirement deadlines.
(1)
				The following are deadlines for completing source water treatment steps:
(A) A system exceeding the lead or copper
				action level shall complete lead and copper source water monitoring under
				10
				CSR 60-15.090(2) and make a treatment
				recommendation to the department no later than one hundred eighty (180) days
				after the end of the monitoring period during which the lead or copper action
				level was exceeded;
(B) The
				department shall make a determination regarding source water treatment within
				six (6) months after submission of monitoring results under subsection (1)(A)
				of this rule;
(C) If the department
				requires installation of source water treatment, the system shall install the
				treatment within twenty-four (24) months after the completion of subsection
				(1)(B) of this rule;
(D) The system
				shall complete follow-up tap water monitoring and source water monitoring
				within thirty-six (36) months after completion of subsection (1)(B) of this
				rule;
(E) The department shall
				review the system's installation and operation of source water treatment and
				specify maximum permissible source water levels within six (6) months after
				completion of subsection (1)(D) of this rule;
(F) The system shall operate in compliance
				with the department-specified maximum permissible lead and copper source water
				levels and continue source water monitoring.
Missouri Code of State Regulations › Title 10 - DEPARTMENT OF NATURAL RESOURCES › Division 60 - Safe Drinking Water Commission › Chapter 15 - Lead and Copper › Section 10 CSR 60-15.080 - Monitoring Requirements for Water Quality Parameters

Current through Register Vol. 49, No. 14, July 15, 2024
PURPOSE: This rule sets forth the procedures and
				  requirements for monitoring drinking water to determine how corrosive the water
				  is to the distribution system.
(1) General Requirements. All large (serving
				more than fifty thousand (>50,000) persons) water systems and all
				small-(serving less than or equal to three thousand three hundred<=3,300)
				persons) and medium-size (serving three thousand three hundred one to fifty
				thousand (3,301-50,000) persons) systems that exceed the lead or copper action
				level shall monitor water quality parameters in addition to lead and copper in
				accordance with this rule. The requirements of this rule are summarized in the
				table at the end of this rule.
(A) Sample
				Collection Methods.
1. Tap samples shall be
				representative of water quality throughout the distribution system taking into
				account the number of persons served, the different sources of water, the
				different treatment methods employed by the system and seasonal variability.
				Tap sampling under this rule is not required to be conducted at taps targeted
				for lead and copper sampling under
				10
				CSR 60-15.070(1).
(Note: Systems may find it convenient to conduct tap sampling
				  for water quality parameters at sites used for coliform sampling under
				  10
				  CSR 60-4.020(1)(A).)
2. Samples collected at the entry
				point(s) to the distribution system shall be from locations representative of
				each source after treatment. If a system draws water from more than one (1)
				source and the sources are combined before distribution, the system must sample
				at an entry point to the distribution system during periods of normal operating
				conditions (that is, when water is representative of all sources being
				used).