Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Construction Codes › Construction Code Commission General Rules › Construction Code › Part 7 - PLUMBING CODE › AMENDMENTS AND ADDITIONS TO BASIC PLUMBING CODE › Section R. 408.30729 - Water service pipe

Current through Vol. 24-12, July 15, 2024
Rule 729. Table 605.3 and section
						  609.3 of the code are amended to
						  read as follows:
Table 605.3
WATER SERVICE PIPE
MATERIAL
STANDARD
Acrylonitrile butadiene styrene (ABS) plastic
										pipe
ASTM D1527; ASTM D2282
Chlorinated polyvinyl chloride (CPVC) plastic
										pipe
ASTM D2846; ASTM F441; ASTM F442; CSA
										B137.6
Chlorinated polyvinyl
										chloride/aluminum/chlorinated polyvinyl chloride (CPVC/AL/CPVC)
ASTM F2855
Copper or copper-alloy pipe
ASTM B42; ASTM B302
Copper or copper-alloy tubing (Type K, WK, L,
										WL, M or WM)
ASTM B75; ASTM B88; ASTM B251; ASTM
										B447
Cross-linked polyethylene (PEX) plastic pipe
										and tubing
ASTM F876; AWWA C904; CSA B137.5
Cross-linked
										polyethylene/aluminum/cross-linked polyethylene (PEX-AS-PEX) pipe
ASTM F1281; ASTM F2262; B137.10
Cross-linked
										polyethylene/aluminum/high-density polyethylene (PEX-AL-HDPE)
ASTM F1986
Ductile iron water pipe
AWWA C151/A21.51; AWWA C115/A21.15
Galvanized steel pipe
ASTM A53
Polyethylene (PE) plastic pipe
ASTM D2239; ASTM D3035; AWWA C901; CSA
										B137.11
Polyethylene (PE) plastic tubing
ASTM D2737; AWWA C901; CSA B137.1
Polyethylene/aluminum/polyethylene (PE-AL-PE)
										pipe
ASTM F1282; CSA B 137.9
Polyethylene of raised temperature (PE-RT)
										plastic tubing
ASTM F2769; CSA B137.18
Polypropylene (PP) plastic pipe or
										tubing
ASTM F2389; CSA B137.11
Polyvinyl chloride (PVC) plastic pipe
ASTM D1785; ASTM D2241; ASTM D2672; CSA
										B137.3
Stainless steel pipe (Type 304/304L)
ASTM A312; ASTM A778
Stainless steel pipe (Type 316/316L)
ASTM A312; ASTM A778
Chlorinated polyvinyl chloride (CPVC) plastic
										pipe and tubing
ASTM D2846; ASTM F441; ASTM F442; CSA
										B137.6
Chlorinated polyvinyl
										chloride/aluminum/chlorinated polyvinyl chloride (CPVC/AL/CPVC)
ASTM F2855
Copper or copper-alloy pipe
ASTM B-42; ASTM B302; ASTM B43
Copper or copper-alloy tubing (Type K, WK, L,
										WL, M or WM)
ASTM B75; ASTM B88; ASTM B251; ASTM
										B447
Cross-linked polyethylene (PEX) plastic
										tubing
ASTM F876; CSA B137.5
Cross-linked
										polyethylene/aluminum/cross-linked polyethylene (PEX-AL-PEX) pipe
ASTM F1281; ASTM F2262; CSA B137.10
Cross-linked
										polyethylene/aluminum/high-density polyethylene (PEX-AL-HDPE)
ASTM F1986
Ductile iron pipe
AWWA C151/A21.51; AWWA C115/A21.15
Polyethylene/aluminum/polyethylene (PE-AL-PE)
										composite pipe
ASTM F1282
Polyethylene of raised temperature (PE-RT)
										plastic tubing
ASTM F2769; CSA B137.158
Polypropylene (PP) plastic pipe or
										tubing
ASTM F2389; CSA B137.11
Stainless steel pipe (Type 304/304L)
ASTM A312; ASTM A778
Stainless steel pipe (Type 316/316L)
ASTM A312; ASTM A778
(REFERENCE
						  R 408.30732, SECTION
						  605.2.1)
609.3 Hot water. Hot water
						shall be provided to supply all of the hospital fixtures, kitchen, and laundry
						requirements. Special fixtures and equipment shall have hot water supplied at a
						temperature specified by the manufacturer. The hot water system shall be
						installed in accordance with section 607.