Michigan Administrative Code › Department - Licensing and Regulatory Affairs › Bureau of Fire Services › Fire Prevention › Part II - General Fire Safety › Section R. 29.1696 - Compressed gases and cryogenic liquids

Current through Vol. 24-12, July 15, 2024
Rule 46. Sections 63.1.2, 63.1.2.1, 63.1.2.2, 63.1.2.3,
					 63.2.4.3, 63.2.4.4, 63.2.6, 63.2.6.1, 63.2.6.1.1, 63.2.6.1.2, 63.2.10,
					 63.2.10.1, 63.2.10.2, 63.2.10.2.1, 63.2.10.2.2, 63.2.15, 63.2.16.3, 63.2.16.5,
					 63.2.16.6, 63.2.16.7, 63.2.16.7.1, 63.2.16.7.2, 63.2.16.7.3, 63.2.16.8,
					 63.2.16.9, 63.2.16.10, 63.2.16.11, 63.3.1.1, 63.3.1.1.1, 63.3.1.1.2, 63.3.1.2,
					 63.3.1.2.1, 63.3.1.2.2, 63.3.1.2.2.1, 63.3.1.2.2.2, 63.3.1.2.3, 63.3.1.2.4,
					 63.3.1.2.5, 63.3.1.2.5.1, 63.3.1.2.5.2, 63.3.1.2.5.3, 63.3.1.2.5.4,
					 63.3.1.2.5.5, 63.3.1.2.5.6, 63.3.1.3, 63.3.1.3.1, 63.3.1.3.2, 63.3.1.3.3,
					 63.3.1.3.3.1, 63.3.1.3.3.2, 63.3.1.3.4, 63.3.1.3.4.1, 63.3.1.3.4.2, 63.3.1.4,
					 63.3.1.4.1, 63.3.1.4.2, 63.3.1.4.3, 63.3.1.4.3.1, 63.3.1.4.3.2, 63.3.1.4.4,
					 63.3.1.4.4.1, 63.3.1.4.4.2, 63.3.1.5, 63.3.1.5.1, 63.3.1.5.2, 63.3.1.5.3,
					 63.3.1.5.3.1, 63.3.1.5.3.2, 63.3.1.6, 63.3.1.6.1, 63.3.1.6.1.1,
					 63.3.1.6.1.2,63.3.1.6.1.3, 63.3.1.6.2, 63.3.1.6.2.1, 63.3.1.6.2.2,
					 63.3.1.6.2.3, 63.3.1.6.2.4, 63.3.1.6.3,63.3.1.6.3.1, 63.3.1.6.3.2, 63.3.1.6.4,
					 63.3.1.6.5, 63.3.1.6.6, 63.3.1.6.7, 63.3.1.6.7.1,63.3.1.6.7.2, 63.3.1.6.8,
					 63.3.1.6.9, 63.3.1.6.10, 63.3.1.7, 63.3.1.8, 63.3.1.9, 63.3.1.10, 63.3.1.10.1,
					 63.3.1.10.2, 63.3.1.10.3, 63.3.1.10.4, 63.3.1.11, 63.3.1.11.1, 63.3.1.11.2,
					 63.3.1.12, 63.3.1.12.1, 63.3.3.1.2, 63.3.3.1.2.1, 63.3.3.1.2.2, 63.3.3.1.3,
					 63.3.3.1.3.1, 63.3.3.1.3.2, 63.3.3.1.4, 63.3.3.1.4.1, 63.3.3.1.4.2, 63.3.3.1.5,
					 63.3.3.1.5.1, 63.3.3.1.5.2, 63.3.3.1.6, 63.3.3.1.6.1, 63.3.3.1.6.2,
					 63.3.3.1.12, 63.3.3.1.12.1, 63.3.3.1.12.2, 63.3.3.1.13, 63.3.3.1.13.1,
					 63.3.3.1.13.2, 63.3.3.1.13.2.1, 63.3.3.1.13.2.2, 63.3.3.1.13.3, 63.3.6.1.2,
					 63.3.6.4, 63.3.9.3.2.1, 63.3.9.3.2.1.1, 63.3.9.3.2.1.2, 63.3.9.3.2.2,
					 63.3.9.3.2.2.1, 63.3.9.3.2.2.2, 63.3.9.3.2.2.3, 63.3.9.3.2.2.4, 63.3.9.3.3,
					 63.3.9.3.3.1, 63.3.9.3.3.2, 63.3.9.3.4, 63.3.9.3.4.1, 63.3.9.3.4.2,
					 63.3.9.3.4.3, 63.3.9.3.4.3.1, 63.3.9.3.4.3.2, 63.3.9.3.5, 63.3.9.3.6,
					 63.3.9.3.6.1, 63.3.9.3.6.2, 63.3.9.3.6.3, 63.3.9.4, 63.3.9.4.1, 63.3.9.4.2,
					 63.3.9.4.2.1, 63.3.9.4.2.2, 63.3.9.4.2.3, 63.3.9.5, 63.3.9.5.1, 63.3.9.5.2,
					 63.3.9.5.3, 63.3.9.5.4, 63.3.9.6, 63.3.9.6.1, 63.3.9.6.2, 63.3.9.6.3,
					 63.3.9.6.4, 63.3.9.6.4.1, 63.3.9.6.4.2, 63.3.9.6.5, 63.3.9.6.5.1, 63.3.9.6.5.2,
					 63.3.9.6.5.3, 63.3.9.6.5.4, 63.3.9.6.6, 63.3.9.7, 63.4.2.2, 63.4.2.2.1,
					 63.4.2.2.2, 63.4.2.3, 63.4.2.3.1, 63.4.2.3.2, 63.4.2.3.3, 63.4.2.3.4,
					 63.4.2.3.5, 63.4.2.4, 63.4.2.4.1, 63.4.2.4.1.1, 63.4.2.4.1.2, 63.4.2.4.2,
					 63.4.2.4.3, 63.4.2.4.4, 63.4.2.4.4.1, 63.4.2.4.4.2, 63.4.2.4.5, 63.4.2.4.6,
					 63.4.2.4.6.1, 63.4.2.4.6.2, 63.4.2.4.6.2.1, 63.4.2.4.6.2.2, 63.4.2.4.7,
					 63.4.2.4.7.1, 63.4.2.4.7.2, 63.4.2.4.7.2.1, 63.4.2.4.7.2.2, 63.4.2.4.8, 63.4.3,
					 63.4.3.1, 63.4.3.2, 63.4.3.3, 63.4.3.4, 63.4.3.5, 63.4.12.2, 63.4.12.2.1,
					 63.4.12.2.2, 63.4.12.2.3, 63.4.12.2.4, 63.4.12.2.5, 63.4.12.2.5.1,
					 63.4.12.2.5.2, 63.4.12.2.5.3, 63.4.12.2.5.4, 63.4.12.2.5.4.1, 63.4.12.2.6,
					 63.4.12.2.6.1, 63.4.12.2.6.2, 63.4.12.2.6.2.1, 63.4.12.2.6.2.2, 63.4.12.2.6.3,
					 63.4.13.1.4, 63.4.13.1.4.1, 63.4.13.1.4.2, 63.4.13.1.4.3, 63.4.13.2,
					 63.4.13.2.1, 63.4.13.2.2, 63.4.13.3, 63.4.13.4, 63.4.13.5, 63.4.13.5.1,
					 63.4.13.5.2, 63.4.13.6, 63.4.13.6.1, 63.4.13.6.2, 63.4.13.7, 63.4.13.7.1,
					 63.4.13.7.2, 63.4.13.8, 63.4.13.9, 63.4.13.9.1, 63.4.13.9.2, 63.4.13.10.2.3,
					 63.4.13.10.2.3.1, 63.4.13.10.2.3.2, 63.4.13.10.3.2.1, 63.4.13.10.3.2.2,
					 63.4.13.10.3.2.3, 63.4.13.10.3.3, 63.4.13.10.3.4, 63.6 and 63.7 of chapter 63
					 of the code are deleted, section 63.1.1.3 of chapter 63 of the code is amended
					 to read as follows: 63.1.1.3 Exemptions. NFPA 55 shall not apply to the
					 following:
(1) Off-site transportation
				  of materials covered by NFPA 55.
(2) Storage, use, and handling of radioactive
				  gases in accordance with NFPA 801, standard for fire protection for facilities
				  handling radioactive materials.
(3)
				  Storage, use, and handling of medical compressed gases at health care
				  facilities in accordance with NFPA 99, standard for health care
				  facilities.
(4) Except for chapter
				  9 of NFPA 55, storage, use, and handling of bulk oxygen in medical gas systems
				  at health care facilities.
(5)
				  Systems consisting of cylinders of oxygen and cylinders of fuel gas used for
				  welding and cutting in accordance with NFPA 51, standard for the design and
				  installation of oxygenfuel gas systems for welding, cutting, and allied
				  processes.
(6) Acetylene cylinders
				  in acetylene cylinder charging plants in accordance with NFPA 51A, standard for
				  acetylene cylinder charging plants.
(7) Ethylene oxide containers stored,
				  handled, or used for sterilization and fumigation in accordance with NFPA 560,
				  standard for the storage, handling, and use of ethylene oxide for sterilization
				  and fumigation.
(8) Storage, use,
				  and handling of liquefied and nonliquefied compressed gases in laboratory work
				  areas that are in accordance with NFPA 45, standard on fire protection for
				  laboratories using chemicals.
(9)
				  Storage, use, and handling of gases within closed-cycle refrigeration systems
				  complying with the Michigan mechanical code.
(10) LNG handled as a vehicle fuel under NFPA
				  52, vehicular fuel systems code.
63.1.2
				  Deleted.
63.1.2.1 Deleted.
63.1.2.2 Deleted.
63.1.2.3 Deleted.