reglab/statecodes huggingface dataset:
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.150 - Piping - Underground

Current through Register Vol. 48, No. 28, July 12, 2024
a)
			 Metallic piping shall not be surrounded or covered by cinders or other material
			 of corrosive effect, but preferably should be laid in sand, and where carried
			 in conduit, the openings of such conduit must be sealed to prevent escape of
			 liquid except for vent pipes.
b)
			 Pipe lines buried on railroad property shall be laid at a depth of not less
			 than three feet; where they pass under tracks they shall be laid at least four
			 feet below bottom of ties.
c)
			 Piping buried in city streets or under roads shall be sealed in conduit. Joints
			 of conduit shall be sealed to prevent leakage and pitch shall be toward tank
			 yard, and a vent pipe shall be provided.
d) Metallic piping shall be coated with
			 asphaltum or other corrosion resisting material.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.160 - Piping - Joints

Current through Register Vol. 48, No. 28, July 12, 2024
Joints may be welded or of the ordinary screw type; if of the
				screw type they shall be screwed together with litharge and glycerine, lamp
				black or shellac or pipe joint compound.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.170 - Piping - Tests

Current through Register Vol. 48, No. 28, July 12, 2024
After installation, piping shall be tested at a pressure fifty
				per cent in excess of the working pressure for thirty minutes and must be
				proven leak proof.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.180 - Piping - Normal Valves

Current through Register Vol. 48, No. 28, July 12, 2024
a) Each
			 pipe attached to a tank shall be provided with a valve at the tank, with no
			 branches nor outlets between the tank and valve.
b) In case two or more tanks are
			 cross-connected, there shall be a valve at each tank in each cross-connection.
			 Tanks with different classes of liquids shall not be cross-connected.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.190 - Piping - Emergency Internal Check Valves

Current through Register Vol. 48, No. 28, July 12, 2024
In addition to any normal valves, there must be an extra valve
				at each pipe line connection to any tank below normal liquid level, (regardless
				of when installed) which valve is effective inside the tank shell and is
				operated both manually and by an effective heat actuated device which, in case
				of fire, will automatically close the valve to prevent the flow of liquid from
				the tank even though the pipe lines are broken from the tank. These extra
				valves are not required in crude oil tanks in oil fields, on tanks at
				refineries, or on tanks at terminals which are equipped with a swing line or
				where facilities are provided to transfer the contents of the tank to another
				tank in case of fire. On tanks installed prior to April 14, 1977, emergency
				check valves may be external, if the size of the opening is too small to admit
				the smallest emergency check valve provided:
a) The valve used incorporates a shear
			 section, and
b) The valve is so
			 installed that any undue strain beyond the valve will not cause failure between
			 the valve and the tank.
c) When an
			 opening on a previously installed tank is enlarged, an internal valve is
			 installed.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.200 - Diking

Current through Register Vol. 48, No. 28, July 12, 2024
a) Individual tanks
			 or groups of tanks, where deemed necessary by the Office of the State Fire
			 Marshal on account of proximity to waterways, character of topography, or
			 nearness to structures of high value, or to places of residence or public
			 assembly, as defined in 41 Ill. Adm. Code
			 100.30,
			 shall be diked or the yard shall be provided with a curb to prevent the spread
			 of liquid onto other property or waterways. Where a diked enclosure is required
			 under this paragraph, the volumetric capacity of the diked area shall be not
			 less than the aggregate capacity of the tanks within the diked area, or be in
			 accordance with NFPA 30 (1981) Section 2-2.3.3.b.
b) Sufficient distance to meet the
			 requirements of Sections
			 160.200,
			 160.220 and
			 160.230 shall always be
			 allowed for the building of a dike at such time as a dike may be required by
			 subsection (a) above.
c) Distance
			 from the tank shell to the toe of the dike shall be not less than five
			 feet.
d) The product stored within
			 a diked area must not be of a type that would be incompatible with other
			 products in the event of a fire. Alcohol must be separately diked from gasoline
			 or other petroleum products. Petroleum products containing less than 10%
			 alcohol by volume shall be treated as petroleum for the purpose of this
			 Section.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.210 - Dikes Required - Crude Petroleum

Current through Register Vol. 48, No. 28, July 12, 2024
Tanks or groups of tanks containing crude petroleum or other
				liquids which have a tendency to boil over shall be diked.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.220 - Dikes - Capacity

Current through Register Vol. 48, No. 28, July 12, 2024
Dikes surrounding tanks containing crude oil or other flammable
				liquid subject to boil-over, shall have a capacity of not less than the
				capacity of the tank surrounded and in addition shall have a coping or
				deflector pointing inward, so designed and constructed as to minimize the
				effect of the boil-over wave. The dike shall be not less than 50 feet from the
				shell of the tank surrounded.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.230 - Dikes - Material and Construction

Current through Register Vol. 48, No. 28, July 12, 2024
a) Dikes shall be constructed of earth, clay,
			 solid masonry or reinforced concrete not higher than one-half the height of the
			 tank or tanks enclosed, so constructed as to afford protection from leaks,
			 spills, or other discharge of product.
b) Earthwork dikes shall be firmly and
			 compactly built of good earth or clay, from which stones, vegetable matter and
			 other foreign material have been removed. They shall have a flat section at the
			 top not less than two and one-half feet wide and a slope of at least 1 to 1
			 (45°) on both sides.
c) Masonry
			 or concrete dikes shall have footings below the frost line.
d) It is permissible to cover earthwork dikes
			 with gravel or stones not larger than 2" in diameter.
e) If a concrete floor covering is provided
			 for the area enclosed by a concrete dike, a sump shall be provided at some
			 convenient place, attached to which shall be a pump conforming to NFPA #70
			 (1984), Chapter 5, so that any accumulation of water or oil may be removed
			 immediately.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.240 - Dikes - No Openings Permitted

Current through Register Vol. 48, No. 28, July 12, 2024
Embankments or dikes shall be continuous, with no openings for
				piping or roadway.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.250 - Pumphouse

Current through Register Vol. 48, No. 28, July 12, 2024
a) Motors and pumps
			 shall be located in a separate building not less than ten (10) feet from tanks,
			 loading docks, warehouses, garages and property lines, except as provided in
			 Section
			 160.255.
			 Any pumphouse erected after April 14, 1977 shall be of non-combustible
			 construction.
b) The motor shall be
			 of the polyphase, non-sparking or explosion-proof type, and shall be grounded
			 to permanently moist earth.
c) If
			 pumphouse is electrically lighted, lights shall be of the vapor proof type,
			 wiring shall be in sealed conduit, and the light switch shall be of the
			 explosion-proof type, oil bath type, or shall be placed outside the
			 building.
d) Motor starting
			 switches shall be of the explosion-proof type or oil bath type if in an area
			 where explosive concentration of vapors are suspected of being
			 present.
e) Screened openings of
			 not less than 64 square inches each shall be constructed in opposite corners at
			 floor line to provide proper ventilation.
f) All doors of pumphouse shall open
			 outward.
g) Doors shall be left
			 open at all times when pumps are in operation.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.255 - Unenclosed Pumps and Motors

Current through Register Vol. 48, No. 28, July 12, 2024
If pumps and motors are located entirely in the open, with no
				enclosure whatever, they may be located at or under the loading dock. Motors
				and electrical equipment shall comply otherwise with the provisions of Section
				160.250.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.260 - Warehouse

Current through Register Vol. 48, No. 28, July 12, 2024
a) Any warehouses
			 erected after April 14, 1977 or converted for the storage of flammable liquids
			 shall have non-combustible walls, roofs and floors and shall be so constructed
			 that refuse cannot accumulate under the floor.
b) Storage of liquids of Class I or II shall
			 not be permitted except in original sealed containers and no transfer of
			 liquids in such containers to other containers shall be made inside the
			 warehouse.
c) Warehouses shall be
			 kept clean, neat and orderly, and free from accumulation of grease and oil
			 spillage.
d) The National
			 Electrical Code as published in NFPA Standard No. 70, (1984) by the National
			 Fire Protection Association, shall govern the electrical
			 installation.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.270 - Garage

Current through Register Vol. 48, No. 28, July 12, 2024
a) Floor of garage
			 shall be of concrete or other non-combustible material, laid directly on the
			 ground or on a well tamped and puddled fill.
b) Ventilation shall be provided to carry off
			 any flammable gases which may accumulate.
c) No connection to any house drainage or to
			 any sewer system shall be made from any garage waste basin, sink, floor drain
			 or waste, unless a grease trap is provided ahead of such connection. This does
			 not apply to lavatories, toilets or wash basins, utilized exclusively for
			 toilet or personal use, nor to downspouts carrying surface water from the
			 roof.
d) Electrical Installation -
			 The National Electrical Code as published in NFPA Standard No. 70, (1984) by
			 the National Fire Protection Association, shall govern the electrical
			 installation.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.280 - Location of Unloading Dock

Current through Register Vol. 48, No. 28, July 12, 2024
Location of unloading site with reference to railroad tracks
				over which passenger trains are moved shall be subject at all times to the
				regulations of the Bureau of Explosives of the Association of American
				Railroads, and all amendments thereto, (formerly American Railway Association),
				American Railroads Building, 1920 L Street, N.W., Washington, D.C. 20036 as in
				effect on January 1, 1983.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.290 - Location of Loading Dock

Current through Register Vol. 48, No. 28, July 12, 2024
Truck loading docks and platforms shall be located not less
				than twenty-five (25) feet from storage tanks, plant buildings and property
				lines, except installations existing prior to April 14, 1977, which shall be
				not less than ten (10) feet.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.300 - Electrical Equipment

Current through Register Vol. 48, No. 28, July 12, 2024
a) All
			 electric lights at loading or unloading docks shall be of vapor-proof
			 construction. Electric wiring shall be in sealed conduit at docks and switches
			 shall be of the explosion-proof type or placed at least 20 feet from the
			 docks.
b) All electrical
			 installations, appliances, equipment, and wiring shall conform to the
			 provisions of NFPA # 70 (1984) Chapter 5 and applicable sections
			 thereof.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.310 - Pumps and Pipe Lines

Current through Register Vol. 48, No. 28, July 12, 2024
a)
			 Gasoline and naphtha shall never be handled through the same pump and pipe
			 lines as kerosene and fuel oils.
b)
			 Pipe lines shall have a definite color scheme for painting to indicate the
			 product which is being carried by the respective lines. Valves on lines in
			 pumphouse shall be tagged to denote the product handled and controlled by each
			 valve.
c) Pumps delivering to or
			 taking supply from tanks or tank car shall be provided with valves on both
			 suction and discharge of pump. Such valves shall be marked with the testing and
			 listing symbol for their use with flammable and combustible liquids.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.320 - Tank Car Unloading Operations - Grounding

Current through Register Vol. 48, No. 28, July 12, 2024
Before unloading operations are started and before any
				connection or contact is made with piping or other unloading equipment, the
				tank car shall be electrically grounded. Permanent electrical connection of not
				less than No. 0 copper cable shall be made between the rails on which tank cars
				stand and the piping system of the storage plant. This connection may be
				accomplished in two ways. The rails may be bonded by means of standard rail
				bonds and connected to the permanent piping system with No. 0 electrical cable
				connections at each end of the loading or unloading section; or a similar
				connection may be made between each rail on which cars stand and the permanent
				piping system.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.330 - Tank Car Unloading Operations - No Unloading by Gravity

Current through Register Vol. 48, No. 28, July 12, 2024
a) The withdrawal of Class I and II liquids
			 from tank cars through bottom outlets shall not be permitted. Tank cars shall
			 be unloaded through dome (manhole) only. Pumps required to accomplish this
			 shall be in conformity with the National Electrical Code NFPA #70 (1984)
			 Chapter 5, and securely installed.
b) Exception: Fuel oils for heating may be
			 unloaded by gravity.
c) The use of
			 compressed air to discharge contents of tank cars is prohibited, but this shall
			 not be construed to prevent the use of a standard system employing an inert
			 gas, such as carbon dioxide or nitrogen, as pressure generating medium for this
			 purpose.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.340 - Tank Car Unloading Operations - No Unloading to Portable Containers

Current through Register Vol. 48, No. 28, July 12, 2024
Unloading from tank cars to tank trucks or to any other
				portable container shall not be permitted.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.350 - Tank Car Unloading Operations - Dome Covers

Current through Register Vol. 48, No. 28, July 12, 2024
After unloading pipe is inserted into dome of tank car and
				before any pumping is done, the dome shall be tightly covered with wet burlap
				to limit the release of flammable vapors.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.360 - Tank Car Unloading Operations - Other Restrictions

Current through Register Vol. 48, No. 28, July 12, 2024
a) All connections between tank cars and pipe
			 lines shall be in good condition and not permit leakage.
b) Tank cars shall not be left connected to
			 pipe lines except when loading or unloading is going on, and during all such
			 times a person shall be present and in charge.
c) The presence of flame lanterns, flame
			 switch lights or other exposed flame lights or fires during the process of
			 loading or unloading is prohibited.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.365 - Tank Trucks, Tank Wagons, and Portable Tanks

Current through Register Vol. 48, No. 28, July 12, 2024
a) For the purpose of this Part, motor
			 vehicles used for the transport of flammable and combustible liquids shall be
			 classified as follows:
Class A: Motor vehicle transports of 4000 gallons or more
				capacity.
Class B: Motor vehicle transports of over 110 but less than
				4000 gallons capacity.
Class C: Motor vehicle transports of 110 or less gallons
				capacity.
Class A: Transports are further defined as those which are used
				to transport flammable and combustible liquids between terminals and bulk
				plants to service stations and fueling of aircraft.
Class B: Transports are further defined as those which are used
				to transport flammable and combustible liquids from terminals and bulk plants
				to service stations, farm storage sites, construction sites, and for home
				heating fuel deliveries.
Class C: Transports are further defined as those vehicles which
				have tanks added after factory manufacture of the vehicle chassis for the
				purposes of either transporting liquid fuels or added fuel capacity for the
				vehicle to which the tank(s) have been added.
Class A & Class B transport trucks are regulated by both
				the Federal and State of Illinois Departments of Transportation by virtue of
				the fact that their load weight can equal or exceed 1000 pounds.
b) Up to 110 gallons of Class I,
			 II or III liquids may be carried for added fuel capacity provided that:
1) Any such tank is constructed of 18 gauge
			 or heavier steel, or equivalent gauge aluminum.
2) That such tank is securely fastened to
			 either the truck bed or frame in such a manner that it will not separate from
			 the vehicle in the event of a collision.
3) That such tank is permanently connected to
			 the carburetion system of the vehicle by tubing conforming to
			 49 CFR
			 571.301(1983).
4) That such tank is baffled to prevent the
			 sudden shifting of liquid when the vehicle is moving.
5) That such tank is electrically bonded to
			 the vehicle frame.
6) That each
			 tank is clearly labeled with letters at least 2" in height with contrasting
			 background with the product name.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.370 - Truck Loading Operations - Grounding

Current through Register Vol. 48, No. 28, July 12, 2024
Before loading operations begin, tank trucks shall be
				electrically bonded to pipe line by means of a bonding device at loading
				dock.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.380 - Protection of Property - Fencing

Current through Register Vol. 48, No. 28, July 12, 2024
Apparatus dispensing Class I flammable liquids into the fuel
				tanks of motor vehicles of the public shall not be located at a bulk plant
				unless separated by a fence or similar barrier from the area in which bulk
				operations are conducted.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.390 - Protection of Property - Care and Attendance

Current through Register Vol. 48, No. 28, July 12, 2024
a) Property shall be kept free from weeds,
			 high grass, rubbish and litter, and shall be kept neat, clean and orderly
			 throughout.
b) Open light or flame
			 shall not be permitted on the property.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.400 - Protection of Property - Fire Protection

Current through Register Vol. 48, No. 28, July 12, 2024
a) Fire extinguishers of at least 4A: 60 BC
			 rating, foam generators or other agents for extinguishing oil fires shall be
			 provided.
b) Fire extinguishers
			 shall be installed, inspected, maintained and tested in accordance with the
			 requirements of NFPA #10 (1981).
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.410 - Storage of Barrels and Drums - No Storage Within Buildings

Current through Register Vol. 48, No. 28, July 12, 2024
a) Barrels and
			 drums used for Class I liquids, whether full or empty, shall be stored in the
			 open or on an open platform in plant yard. Platforms may be roofed over
			 provided such roof is of noncombustible material.
b) No open lights shall be permitted in such
			 storage yard.
c) Caps, bungs and
			 plugs shall be closed and tightened to prevent the escape of vapor immediately
			 after container is emptied.
d)
			 Class I liquids, such as gasoline and naphtha shall be handled only in barrels
			 or drums painted red and labeled, and no other liquids shall be handled in such
			 red barrels or drums.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.420 - Tank Trucks and Tank Wagons - Double Bulkheads

Current through Register Vol. 48, No. 28, July 12, 2024
Compartment tanks shall be constructed with double bulkheads
				unless they always carry the same class of liquids in the respective
				compartments (CLASS I, II, OR III).
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.425 - Tank Trucks and Tank Wagons - No Manifolding of Different Classes of Liquids

Current through Register Vol. 48, No. 28, July 12, 2024
Compartments of tank trucks and tank wagons carrying different
				classes of liquids shall not be manifolded together. Separate piping and meter
				where installed shall be provided for each class of liquid to eliminate hazard
				of mixing.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.430 - Tank Trucks and Tank Wagons - Distinguishing Numbers; Tags

Current through Register Vol. 48, No. 28, July 12, 2024
a) Each compartment or tank shall be numbered
			 and the same number shall appear on the end of the piping connected with that
			 compartment or tank.
b) A
			 serviceable metal tag shall be fastened securely to each valve, designating the
			 contents of the compartment it controls by lettering not less than one-quarter
			 inch high. Tags shall be painted according to the same color scheme as the pipe
			 lines, Section
			 160.310(b),
			 or placarded in accordance with Illinois Department of Transportation Hazardous
			 Material Transportation Regulations as set forth in 92 Ill. Adm. Code: Subtitle
			 C.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.435 - Tank Trucks and Tank Wagons - Presence of Person Required During Loading and Unloading Operations

Current through Register Vol. 48, No. 28, July 12, 2024
During loading and unloading of tank trucks and tank wagons a
				person shall be present and in charge at all times.
a) The driver, operator, or attendant of any
			 tank vehicle shall not remain in the vehicle but shall not leave the vehicle
			 unattended during the loading or unloading process. Delivery hose, when
			 attached to a tank vehicle, shall be considered to be a part of the tank
			 vehicle.
b) When transferring Class
			 I liquids, motors of tank vehicles or motors of auxillary or portable pumps
			 shall be shut down during making and breaking hose connections. If loading or
			 unloading is done without requiring the use of the motor of the tank vehicle,
			 the motor shall be shut down throughout the transfer operations of Class I
			 liquids.
c) Smoking on or about any
			 tank truck or tank wagon during loading and unloading operations at bulk plants
			 is forbidden. Extreme care shall be taken during these operations to keep fire
			 away and to prevent persons in the vicinity from smoking, lighting matches or
			 carrying any flame or lighted cigar, pipe or cigarette.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.440 - Tank Trucks and Tank Wagons - Valves and Faucets

Current through Register Vol. 48, No. 28, July 12, 2024
a) Faucets shall be of the self-closing
			 type.
b) All outlets of each cargo
			 tank or compartment used for transporting Class I, Class II, or Class III
			 liquids having a viscosity less than 45 seconds Saybolt Universal at 100
			 degrees F. shall be equipped with a shutoff valve located inside the shell; or
			 in the sump when it is an integral part of the shell; and designed so that the
			 valve must be kept closed except during loading and unloading operations. The
			 operating mechanism for the valve shall be provided with a secondary control,
			 remote from the fill openings and discharge faucets, for use in the event of
			 accidents or fire. The control mechanism shall be provided with a fusible
			 section which will permit valves to close automatically in case of fire. In
			 every case there shall be provided between the shutoff valve seat and discharge
			 faucet a shear section which will break under strain unless the discharge
			 piping is so arranged as to afford the same protection and leave the shutoff
			 valve seat intact.
c) The outlets
			 of each cargo tank used for transporting liquids having a viscosity equal to or
			 greater than 45 seconds Saybolt Universal at 100 degrees F. shall be equipped
			 with a shutoff valve, located internally, designed so that the valve will
			 remain operable if the external connection is sheared off.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.450 - Tank Trucks and Tank Wagons - Bumpers

Current through Register Vol. 48, No. 28, July 12, 2024
A heavy bumper shall be provided across the rear to protect all
				faucets in case of a rear end collision.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.460 - Tank Trucks and Tank Wagons - Static Protection

Current through Register Vol. 48, No. 28, July 12, 2024
a) Cargo tanks and vehicle chassis shall be
			 electrically bonded. Provision shall be made in the tank structure and vehicle
			 for the bonding of the vehicle to the fill pipe during the truck loading
			 operations.
b) Grounding - Before
			 loading operations begin, tank trucks shall be electrically bonded to pipe line
			 by means of a bonding device at loading dock.
c) Unloading operations - Unloading hose from
			 tank trucks into underground tank shall have static wire or its equivalent and
			 shall be equipped with a nonferrous nozzle or tight connection metal
			 nipple.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.480 - Retail Sales Prohibited

Current through Register Vol. 48, No. 28, July 12, 2024
a)
			 Retail deliveries from tank trucks or tank wagons of Class I, II or III liquids
			 shall not be permitted in any street or alley of any city, village or town, nor
			 on any highway outside of any city, village or town, nor shall any person
			 deliver fuels into motor vehicle fuel tanks from tank trucks, tank wagons, or
			 other portable containers or tanks except as permitted in 41 Ill. Adm. Code 170
			 and 180, and (b) and (c) below.
b)
			 The delivery of fuel oil used for heating purposes is not restricted by this
			 section.
c) The fueling of
			 emergency vehicles (police cars, fire trucks and ambulances) and, road
			 construction equipment (as permitted in 41 Ill. Adm. Code 170.210 ) and
			 maintenance vehicles and equipment is not restricted by this rule.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.490 - Fire Extinguishers

Current through Register Vol. 48, No. 28, July 12, 2024
Each tank truck or tank wagon shall carry a fire extinguisher
				suitable for extinguishing gasoline and oil fires, such as carbon dioxide, foam
				or powder. Such fire extinguishers shall carry a testing and listing label
				giving the extinguisher a rating for class A & B fires.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 160 - STORAGE, TRANSPORTATION, SALE AND USE OF GASOLINE AND VOLATILE OILS: RULES AND REGULATIONS\ RELATING TO GENERAL STORAGE › Section 160.500 - Approval of Plans

Current through Register Vol. 48, No. 28, July 12, 2024
a)
			 Drawings or blue prints made to scale shall be submitted in triplicate to the
			 Office of the State Fire Marshal and shall be approved before any new
			 installation, addition or remodeling is undertaken.
b) Drawings shall show the plot of ground to
			 be utilized and its immediate surroundings on all sides; the complete layout of
			 tanks, loading and unloading docks, equipment and buildings; the capacity of
			 each tank; kind of liquid to be stored; type of tank supports; type of
			 construction of each building; and all clearances as provided in Section
			 160.30,
			 160.40,
			 160.250,
			 and
			 160.290.
			 In addition, the dimensions of any tank with a capacity of more than 50,000
			 gallons shall be given.
c) Drawings
			 shall show the name of the person, firm or company proposing the installation,
			 the location with respect to city, village or town, and shall name adjacent
			 railroads and streets.
d) Drawings
			 shall designate passenger, freight, passing and side tracks and shall show the
			 clearances between tanks and closest passenger tracks, between tracks at point
			 where tank car will be placed for unloading and nearest passenger tracks; and
			 between unloading dock and closest passenger tracks.
e) Drawings shall be accompanied by an
			 application for approval made out in triplicate on blanks furnished by the
			 State Fire Marshal.
f) Plans will
			 be approved if they meet the requirements of this Part.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 172 - PETROLEUM EQUIPMENT CONTRACTOR LICENSING › Section 172.10 - Purpose

Current through Register Vol. 48, No. 28, July 12, 2024
The Illinois Petroleum Equipment Contractors Licensing Act
				(PECLA) [225 ILCS 729 ] is designed to
				ensure the quality of petroleum or hazardous substance Underground Storage Tank
				(UST) work in Illinois meets the highest standards, as well as all applicable
				statutory and regulatory requirements. Meeting those standards and requirements
				will assure the owners/operators of USTs and the citizens of Illinois that the
				environment, citizen safety and the owner's/operator's businesses are getting
				the best service and protection possible.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 172 - PETROLEUM EQUIPMENT CONTRACTOR LICENSING › Section 172.30 - Definitions

Current through Register Vol. 48, No. 28, July 12, 2024
Unless otherwise provided by the definitions within this
				Section, all terms in this Part shall be as defined in 41 Ill. Adm. Code
				174.100.
"Certified employee" is an individual who performs UST activity
				for an OSFM-licensed contractor and has successfully completed and filed proof
				with OSFM of completion of ICC or other OSFM approved exams for the module in
				which the employee is conducting UST activity or meets requirements under
				Section 172.40(b).
"Contractor Notice of Violation" (CNOV) is a notice to an
				OSFM-licensed contractor identifying specific violations of the UST rules (41
				Ill. Adm. Code 172, 174, 175, 176, and 177).
"License restoration" is the process of an OSFM-licensed
				contractor renewing a license after it has expired.
"Managerial or administrative control" means having authority
				to conduct the affairs of the organization and direct others in the conduct of
				the affairs or business of the organization.
"Non-certified employee" means the employee of a licensed
				contractor who possesses the OSHA training and certification required by
				Section 172.60 and is working under the
				supervision of a certified employee.
"Officer" means:
If the organization is a sole proprietorship, the owner of the
				organization or any person exercising managerial control.
If the organization is a partnership, any partner who has at
				least 10% ownership interest or any partner who exercises managerial
				control.
If the organization is a corporation or other business entity,
				any officer, director or managing member of the corporation or other business
				entity or any person who has at least 10% ownership interest in such
				corporation or other business entity or who exercises managerial
				control.
"Organization" means a business or other entity, including, but
				not limited to, a sole proprietorship, partnership, corporation, limited
				liability company or association and includes units of local government, the
				State of Illinois and the Federal Government.
"PECLA" means Petroleum Equipment Contractor Licensing Act
				[225 ILCS
				729 ].
"Penalty process" means the process by which a contractor may
				be issued a civil monetary penalty or other sanctions including, but not
				limited to, license suspension or license revocation. This process starts with
				an inspection and the issuance of a CNOV and then can lead to either a citation
				imposing a civil penalty or a formal hearing seeking a license revocation,
				suspension, or other action.
"Person" is a natural person or any company, corporation or
				other business entity.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 172 - PETROLEUM EQUIPMENT CONTRACTOR LICENSING › Section 172.40 - Licensure Requirements

Current through Register Vol. 48, No. 28, July 12, 2024
a) No
			 person shall engage in any UST activity without first applying for and
			 obtaining a license from the OSFM. All contractors performing UST activity in
			 Illinois must hold the license required under PECLA and this Part for each
			 module in which work is performed and shall be required to meet the standards
			 for that work module established by 41 Ill. Adm. Code 172, 174, 175, 176 and
			 177 and the requirements of 29 CFR 1910.120. Licensure is for
			 a 2-year period. Applicants for a license to become a contractor must comply
			 with the Petroleum Equipment Contractors Licensing Act [225 ILCS
			 729 ] as evidenced by the licensure submissions
			 required by this Section.
b) An
			 application for a new contractor license shall be made on-line at the UST
			 Applications and Forms page for OSFM's Division of Petroleum and Chemical
			 Safety (DPCS) at the following link:
https://webapps.sfm.illinois.gov/USTPortal/Contractor/Application
.
			 Renewal of licenses shall be applied for at the UST Portal after the licensee
			 logs in to their secure account at the UST Applications and Forms page for DPCS
			 at
https://webapps.sfm.illinois.gov/USTPortal/Home/Login?ReturnUrl=%2fUSTPortal
.
			 The licensure application shall include the following submissions:
1) If seeking a license as a contractor:
A) the State license application and
			 licensing fee required by Section
			 172.70;
B) the names of all of the contractor's
			 certified employees, on the OSFM prescribed form, stating any UST module in
			 which the employee is certified. Contractors are required to be certified if a
			 sole proprietor, or have a certified employee, for each UST module for which
			 they are applying to be licensed;
C) an original annual certificate of general
			 liability insurance in a minimum of $1,000,000 for each occurrence, with the
			 OSFM as certified holder;
D)
			 evidence of a passing score on the required OSFM approved exam for the module
			 for which licensure is being sought. The evidence must be an original
			 certification that includes a photo of the individual taking the exam, supplied
			 by the exam provider, or other copy of the certification as approved by
			 OSFM;
E) proof of successful
			 completion of initial 40-hour OSHA training and subsequent 8-hour refresher
			 course; and
F) evidence of current
			 registration and proof of status of good standing with the Illinois Secretary
			 of State, as applicable for the form of business entity applying for licensure,
			 or if a sole proprietor, evidence of compliance with the Assumed Business Name
			 Act [805
			 ILCS 405 ].
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 172 - PETROLEUM EQUIPMENT CONTRACTOR LICENSING › Section 172.50 - Licensed Contractor's Employee Certifications

Current through Register Vol. 48, No. 28, July 12, 2024
a) A certified employee is an individual who
			 performs a UST activity for a licensed contractor and has successfully
			 completed OSFM prescribed exams for the module in which the employee is
			 conducting the UST activity, or meets other requirements under Section
			 172.40(b).
b) A contractor shall have at least one
			 employee certified for the permitted UST activity, unless the contractor itself
			 is an individual contractor who is so certified.
c) A contractor shall have at least one
			 employee certified in the UST activity for which the permit was issued actively
			 supervising the UST activity being performed on the job site, unless the
			 contractor itself is an individual who is so certified and supervises the work.
			 At all times during UST operations, there shall be a certified employee or
			 certified individual contractor on the job site; subcontractors are not
			 employees.
d) Certified employees
			 of licensed contractors shall possess a wallet card or proof of certification
			 verifying successful passage of OSFM approved exams, or for precision testing
			 or inspection and testing of other UST equipment, proof of certification by the
			 manufacturer. The wallet card or proof of certification must be carried by the
			 certified employee on UST job sites at all times and shall be available upon
			 request by any OSFM representative.
e) Licensed contractors and any of their
			 employees performing a UST activity shall possess OSHA Identification Cards or
			 proof of certification, described in Section
			 172.60, on UST job sites at all
			 times that shall be made available upon request by any OSFM
			 representative.
f) Licensed
			 contractors in all UST activity modules are required to follow the scheduling
			 requirements for date certain and/or time certain schedules established by
			 DPCS. For all permitted inspections, scheduling with OSFM shall be done in
			 advance by the contractor on-line via the UST contractor portal, located at the
			 UST Applications and Forms page for the DPCS at
https://webapps.sfm.illinois.gov/USTPortal/Home/Login?ReturnUrl=%2FUSTPortal
.
			 Submission of any completed testing forms required by OSFM rule shall also be
			 submitted on-line at the UST portal.
g) UST activities may be shut down by any
			 OSFM DPCS manager, supervisor, or STSS if individual contractors or their
			 employees are not in compliance with subsections (a) through (f) of this
			 Section. Such work shall not resume until approval is granted by the
			 OSFM.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 172 - PETROLEUM EQUIPMENT CONTRACTOR LICENSING › Section 172.60 - Possession of OSHA Identification Cards

Current through Register Vol. 48, No. 28, July 12, 2024
a) Licensed contractors, their certified
			 employees and non-certified workers working in a UST activity, and subcontract
			 excavation operators (involved in UST related operations) shall possess, on UST
			 jobsites at all times, 40-hour General Site Worker Program Identification Cards
			 and any valid Refresher Cards that comply with OSHA standards. Cards shall be
			 produced upon request by any OSFM DPCS manager, supervisor, or STSS. The card
			 requirement is applicable only to UST installations, upgrades, repairs, lining,
			 removals, abandonments-in-place and physical interior inspections. All workers
			 in the UST excavation zone shall carry both the 8 hour and 40 hour OSHA cards
			 or certificates or other proof of certification. If a person is unable to
			 produce proof of both cards, that person will be required to leave the
			 excavation zone immediately.
b)
			 Electricians, truck drivers, concrete masons, canopy erectors, crane operators,
			 or underground tank manufacturers or their authorized representatives working
			 in activities that involve their area of specialty only are not required to
			 have the Site Worker Program Identification Card but must comply with the
			 standards established by the OSHA General Site Worker Program (29 CFR
			 1910.120, incorporated by reference in
			 Section 174.210).
c) When permitted UST activity is being
			 conducted, compliance with the OSHA standards will be accomplished by direct
			 (line of sight) supervision by the permit holding licensed contractor or the
			 contractor's certified employee for those people entering the work
			 area.
d) UST activities may be shut
			 down by any OSFM DPCS manager, supervisor, or STSS, if individual contractors
			 or their employees are not in compliance with this Section. Such work shall not
			 resume until approval is granted by the OSFM.
Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 172 - PETROLEUM EQUIPMENT CONTRACTOR LICENSING › Section 172.70 - Fees

Current through Register Vol. 48, No. 28, July 12, 2024
a) All fees are
			 payable at the time of submission of the relevant application. The payment is
			 to be by check or money order payable to "Office of the State Fire Marshal", or
			 by electronic payment via the UST contractor portal (located at the UST
			 Applications and Forms page for the DPCS at
http://webapps.sfm.illinois.gov/USTPortal/Home/Login?Returnurl=%2fUSTPortal
,
			 and is to be from the licensed contractor obtaining the permit. New contractors
			 applying for a license for the first time shall utilize the application for a
			 new contractor license, located at the DPCS UST Applications and Forms page at
https://webapps.sfm.illinois.gov/USTPortal/Contractor/Application
.
			 All licensure fees will be deposited in the Fire Prevention Fund.
b) Fee Schedule:
Type of Fee:
Fee:
Biennial licensing
$1000 per UST module
UST activity permit
$200 each
License restoration
$50 plus $1000 per module
Multiple location license
$50 each location
Change of name if no FEIN change
$0
Change of name with new FEIN or ownership (new
						  license)
$1,000 per UST module
c) All
			 fees paid pursuant to this Part are non-refundable. This shall not preclude the
			 OSFM from refunding accidental overpayment of fees.