reglab/statecodes huggingface dataset:
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1232 - Gas Pipe Size

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The size of each section of a gas piping system shall be
					 calculated as provided in the California Plumbing Code, Chapter 12 or by other
					 standard engineering methods acceptable to the enforcement
					 agency.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Amendment filed 7-6-2004;
					 operative 7-6-2004 pursuant to Government Code section 11343.4 (Register 2004,
					 No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1234 - Fuel Oil Tanks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Tanks used for supplying fuel oil to a unit equipped with
					 oil-burning appliances, shall not be larger than one hundred and fifty (150)
					 gallons capacity. Not more than two (2) tanks with a combined maximum capacity
					 of one hundred and fifty (150) gallons may be installed on any lot.
(a) Tanks shall be located not closer than
				  five (5) feet to a lot line or the nearest side of a roadway.
(b) Tanks shall be located in an area not
				  accessible to motor vehicles or shall be provided with protection from contact
				  by vehicles by means of posts or other barriers approved by the enforcement
				  agency.
(c) Tanks elevated above
				  ground shall be maintained on rigid noncombustible supports of adequate size to
				  support the tank when filled, and installed on concrete foundations or footings
				  to prevent movement or settling. Each tank shall be securely fastened to the
				  supporting frame.
(d) Every tank
				  shall be adequately designed, installed, vented, and maintained to prevent
				  entrance of rain and debris.
(e) A
				  shutoff valve located immediately adjacent to the gravity feed connection of a
				  tank shall be maintained in the supply line to the unit.
(f) Fuel oil connectors from the tank to the
				  unit shall be brass or copper tubing or approved flexible metal hose not
				  smaller than three-eighths ( 3/8 ) inch and shall be protected from physical
				  damage. Aluminum tubing shall not be used.
(g) Valves and connectors shall be listed
				  standard fittings maintained liquid-tight to prevent spillage of fuel oil on
				  the ground.
(h) All fuel oil tanks
				  shall be maintained in safe operating condition by the owner or lessee of the
				  tanks, consistent with this section.
1.
					 Renumbering of former section 1698 to new section 1234, including amendment of
					 section heading and section, filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18610, 18690 and 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1236 - Authority to Order Disconnect of Fuel Gas Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The enforcement agency shall require the
				  gas utility or person supplying gas to a park to disconnect any gas piping or
				  equipment found to be defective and in such condition as to endanger life or
				  property.
(b) Gas piping or
				  equipment which has been ordered disconnected by the enforcement agency shall
				  not be reconnected to a gas supply until a permit has been obtained to alter,
				  repair or reconstruct the gas piping and the work has been inspected and
				  approved by the enforcement agency.
1.
					 Renumbering of former section 1672 to new section 1236, including amendment of
					 section heading and section, filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18550 and 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1240 - Application and Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The requirements of this article shall apply to the construction, installation,
				  arrangement, alteration, use, maintenance, and repair of all plumbing equipment
				  and installations to supply water to, and dispose sewage from, units, accessory
				  buildings or structures and permanent buildings in all parts of the
				  state.
(b) Existing plumbing
				  construction, connections, and installations made before the effective date of
				  the requirements of this chapter may continue in use so long as they were in
				  compliance with requirements in effect at the date of their installation and
				  are not found to be substandard.
1. Repealer
					 and new section filed 8-22-85; effective upon filing pursuant to Government
					 Code Section 11346.2(d) (Register 85, No. 36).
2. Amendment filed
					 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Sections 18300, 18554, 18610 and
						18630, Health and Safety Code. Reference: Sections 18554, 18610 and 18630,
						Health and Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1242 - Application and Scope. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18300 and 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1244 - Permits Required. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18500 and 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1246 - Basic Plumbing Regulations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Except as otherwise permitted or required
				  by this article, all requirements for plumbing equipment and installations
				  outside of permanent buildings in parks shall comply with the California
				  Plumbing Code, with the exception of Chapter 1.
If there is any conflict between the provisions of this
					 chapter and the California Plumbing Code, the provisions of this chapter shall
					 prevail.
(b) All
				  requirements for plumbing equipment and installations within permanent
				  buildings in parks shall comply with the California Plumbing Code, except in a
				  city, county, or city and county, which has assumed enforcement responsibility
				  and has adopted, and is enforcing, a plumbing code equal to or greater than the
				  requirements of this article.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Amendment filed 5-26-87;
					 operative 6-25-87 (Register 87, No. 23).
3. Amendment filed
					 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Sections 18300 and 18630, Health
						and Safety Code. Reference: Sections 18300 and 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1248 - Sewage Disposal

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  All park drainage systems shall discharge into a public sewer or a private
				  sewage disposal system approved by the local health department.
(b) Septic tanks shall not be located within
				  five (5) feet of any unit, accessory building or structure, or permanent
				  building. Leach or disposal fields shall not be located within eight (8) feet
				  of any unit, accessory building or structure, or permanent building.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18554 and 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1250 - Material. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1252 - Installation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Listed nonmetallic pipe and fittings installed in park
					 drainage systems shall be installed in accordance with their listing and
					 applicable standards. When installed under roadways, minimum depth of cover for
					 nonmetallic drain pipe shall be thirty-six (36) inches. The pipe shall be
					 bedded on a minimum of three (3) inches of clean sand and shall be backfilled
					 with a minimum cover depth of six (6) inches of clean sand, granulated earth or
					 similar material. The trench shall then be backfilled in thin layers to a
					 minimum of twelve (12) inches above the top of the nonmetallic pipe with clean
					 earth, which shall not contain stones, boulders or other materials, which would
					 damage or break the pipe.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11356.2(d) (Register 85, No. 36).
2. Amendment filed 7-6-2004;
					 operative 7-6-2004 pursuant to Government Code section 11343.4 (Register 2004,
					 No. 28).
Note: Authority cited: Sections 18300 and 18630, Health
						and Safety Code. Reference: Sections 18610 and 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1254 - Lot Drain Inlet

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each lot shall be provided with a drain inlet not less than three (3) inches in
				  diameter and shall be connected to an approved sewage disposal
				  system.
(b) Drain inlets shall be
				  provided to accommodate a threaded or clamp-type fitting for connecting drain
				  connectors at proper grade. The drain inlet shall be accessible at ground
				  level. The vertical riser of a drain inlet shall not exceed three (3) inches in
				  height above the concrete supporting slab. Drain inlets shall be gas-tight when
				  not in use.
(c) Each drain inlet
				  shall be protected from movement by being encased in a concrete slab not less
				  than three and one-half (3 ½ ) inches in thickness and surrounding the
				  inlet by not less than six (6) inches on any side.
(d) Drain inlets and extensions to grade
				  shall be of material approved for use under or within a building.
(e) The lot drain inlet shall be located
				  within four (4) feet of the outside of the unit, or under the unit within
				  eighteen (18) inches of the exterior wall of the unit.
1. Amendment
					 of section heading, section and NOTE filed 7-6-2004; operative 7-6-2004
					 pursuant to Government Code section 11343.4 (Register 2004, No.
					 28).
2. Amendment of subsection (d) filed 12-26-2006; operative
					 1-2-2007 pursuant to Government Code section 11343.4 (Register 2006, No.
					 52).
Note: Authority cited: Sections 18300 and 18630, Health
						and Safety Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1256 - Location of Lot Drain Inlet. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
					 Amendments filed 8-22-85; effective upon filing pursuant to Government Code
					 Section 11346.2(d) (Register 85, No. 36).
2. Repealer filed
					 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Sections 18300 and 18630, Health
						and Safety Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1258 - Trap

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
When a unit is installed, or proposed to be installed and
					 its plumbing fixtures are not protected by approved traps and vents, a lot
					 drain inlet shall be provided with an approved trap.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1260 - Venting

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where a drain inlet trap is provided, it shall be
					 individually vented with a vent pipe of not less than two (2) inches interior
					 diameter unless the system is a wet vented system as provided in section 1264
					 of this article.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1262 - Vent Location and Support

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All vent pipes in outdoor locations shall be located at
					 least ten (10) feet from an adjoining property line and shall extend at least
					 ten (10) feet above ground level. All vent pipes shall be supported by at least
					 the equivalent of a four (4) inch by four (4) inch nominal dimension redwood
					 post securely anchored in the ground. One-piece galvanized iron vent pipes may
					 be self-supporting if securely anchored at their base in concrete at least
					 twelve (12) inches in depth and extending a minimum four (4) inches out from
					 the pipe.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1264 - Wet Vented Systems

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) In
				  lieu of the individual vents, the park drainage system may be wet vented by
				  means of a combination drain, waste, and vent system. Wet vented systems in
				  which the trap for one or more lots is not individually vented shall be of
				  sufficient size and provided with an adequate vent or vents to assure free
				  circulation of air. Wet vented drainage systems may be permitted only when each
				  such system conforms to Table 1268-1 and Table 1268-2 and all of the following
				  requirements for such systems:
(1) A wet
				  vented drainage system shall have a terminal vent installed not more than
				  fifteen (15) feet downstream from the uppermost trap on any branch line and
				  shall be relief vented at intervals of not more than one hundred (100) feet or
				  portion thereof.
(2) Wet vented
				  drainage laterals shall be not more than six (6) feet in length for three
				  (3)-inch diameter pipe and not more than fifteen (15) feet in length for four
				  (4)-inch diameter pipe.
(3) No
				  vertical drain pipe shall be permitted in any wet vented drainage system,
				  except the tail pipe of the trap or riser of the drain inlet. Tail pipes shall
				  be as short as possible, and in no case shall exceed two (2) feet in
				  length.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1266 - Systems Without Traps

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Terminal or relief vents are not required for drainage
					 systems without traps.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1268 - Pipe Size

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each
				  lot drain inlet shall be assigned a waste loading value of six (6) fixture
				  units and each park drainage system shall be sized according to Table 1268-1 or
				  as provided herein. Drainage laterals shall be not less than three (3) inches
				  in diameter.
(b) A park drainage
				  system in which the grade, slope, or sizing of drainage pipe does not meet the
				  minimums specified in Tables 1268-1 or 1268-2 shall be designed by a registered
				  engineer for a minimum velocity flow of two (2) feet per second.
(c) Park drainage systems installed without
				  P-traps or vents may be sized for individually vented systems in accordance
				  with Table 1268-1.
(d) A park
				  drainage system which exceeds the fixture unit loading of Table 1268-1 shall be
				  designed by a registered engineer.
TABLE 1268-1
Drainage Pipe Diameter and Number of
								Fixture Units on Drainage System
Size of Drainage Pipe
							 (Inches)
Maximum No. of Fixture Units Individually
							 Vented System
Maximum No. of Fixture Units Wet Vented
							 System
Terminal & Relief Vent Wet Vented System
							 (Inches)
3
35
14
2
4
180
35
3
5
356
180
4
6
600
356
4
TABLE 1268-2
Minimum Grade and Slope of Drainage
								Pipe
Pipe Size
								(inches)
Slope per 100 ft.
								(inches)
Pipe Size
								(inches)
Slope per 100 ft.
								(inches)
2
25
6
8
3
20
8
4
4
15
10
3 ½
5
11
12
3
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1270 - Lot Water Service Outlet. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18630, 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1272 - Shutoff Valve. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1274 - Lot Water Service Outlet

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each lot shall be provided with a potable water lot service outlet. The lot
				  water service outlet riser shall be an approved rigid metallic material and not
				  less than three-quarter ( ¾ ) inch nominal pipe size. Each lot water
				  service outlet shall be provided with an accessible water outlet designed for
				  connecting a three-quarter ( ¾ ) inch female swivel hose connection as
				  defined in section 1308 of this chapter, in addition to the unit water
				  connection.
(b) The lot water
				  outlet shall be located within four (4) feet of the outside of the unit, or
				  under the unit within eighteen (18) inches of the exterior wall of the
				  unit.
(c) A separate water service
				  shutoff valve shall be installed in each lot water service outlet at each
				  lot.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Amendment of section heading,
					 section and NOTE filed 7-6-2004; operative 7-6-2004 pursuant to Government Code
					 section 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18630 and 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1276 - Pressure

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Parks
				  constructed between July 11, 1979 and July 6, 2004, shall have water
				  distribution systems capable of providing a pressure not less than fifteen (15)
				  pounds per square inch at each lot at maximum operating conditions. Parks
				  constructed before and after the above dates must be capable of maintaining
				  twenty (20) pounds per square inch at maximum operating conditions.
(b) The testing of a water system in a park
				  to determine the maximum operating condition shall be either performed at the
				  reported time of maximum water pressure loss, if within normal business hours,
				  or measured with twenty-five (25) percent of the required lot water supply
				  outlets, as defined in section 1308 of this chapter, open with the pressure
				  metering device at the end of the tested line.
1. New
					 section filed 7-22-2005; operative 7-22-2005 pursuant to Government Code
					 section 11343.4 (Register 2005, No. 29). For prior history, see Register 2004,
					 No. 28.
2. Editorial correction of HISTORY 1 (Register 2005, No.
					 33).
Note: Authority cited: Sections 18300 and 18630, Health
						and Safety Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1278 - Water Pipe Size

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  quantity of water required to be supplied to each lot shall be as required for
				  six (6) fixture units.
(b) Park
				  water distribution systems shall be designed and installed as set forth in
				  California Plumbing Code, Chapter 6, and Appendix A.
1. Amendment
					 of subsection (b) filed 8-22-85; effective upon filing pursuant to Government
					 Code Section 11346.2(d) (Register 85, No. 36).
2. Amendment filed
					 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Sections 18300 and 18630, Health
						and Safety Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1280 - Mechanical Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where subject to physical damage, all park water service
					 outlets shall be protected by posts, fencing, or other barriers approved by the
					 enforcement agency.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1282 - Mobilehome Water Connector. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
2. Editorial correction of section heading
					 (Register 2005, No. 33).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18550, 18630, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 5 - Plumbing Requirements › Section 1284 - Water Conditioning Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A permit shall be obtained from the
				  enforcement agency prior to installing any regenerating water conditioning
				  equipment on a lot. Approval of the park operator is required on all
				  applications for a permit to install such equipment. Where the water
				  conditioning equipment is of the regenerating type, and the park drainage
				  system discharges into a public sewer, approval of the sanitary district or
				  agency having jurisdiction over the public sewer is required prior to issuance
				  of the permit.
(b) Regenerating
				  water conditioning equipment shall be listed and labeled by an approved listing
				  agency.
(c) Regenerating units
				  shall discharge the effluent of regeneration into a trap not less than one and
				  one-half (1 ½ ) inches in diameter connected to the park drainage
				  system. An approved air gap shall be installed on the discharge line a minimum
				  of twelve (12) inches above the ground. The trap need not be vented.
(d) Electrical supply connections to
				  regenerating water conditioning equipment shall comply with the requirements of
				  this chapter.
1. Amendment
					 of section and NOTE filed 7-6-2004; operative 7-6-2004 pursuant to Government
					 Code section 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18630 and 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1300 - Application and Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  For parks with a permit to construct dated on or after July 7, 2004, fire
				  protection equipment meeting the requirements of the National Fire Protection
				  Association (N.F.P.A.) Standard No. 24, 1995 Edition, which is hereby
				  incorporated by reference, shall be installed and maintained in every park
				  consisting of fifteen (15) or more lots, or parks enlarged to consist of
				  fifteen (15) or more lots. Installation of fire protection equipment is
				  required only for the new lots added.
(b) For parks with a permit to construct
				  dated between September 1, 1968, and July 7, 2004, fire protection equipment
				  meeting the requirements of the National Fire Protection Association (N.F.P.A.)
				  Standard No. 24,1977 Edition, which is hereby incorporated by reference, shall
				  be maintained in every park consisting of fifteen (15) or more lots.
(c) Testing of Private Fire Hydrants. Park
				  owners and operators shall be responsible for the operation and water flow
				  requirements of all private fire hydrants installed in any park, regardless of
				  its age or number of lots in the park, and responsible for compliance with
				  other applicable provisions of this article.
(d) Reciprocity of Enforcement Agencies. The
				  provisions of section 1302 and sections 1316 through 1318 of this article, do
				  not create any obligation for the enforcement agency to report violations to a
				  fire agency, or for the fire agency to report violations to the enforcement
				  agency. However, this subsection does not preclude either enforcement agencies
				  or fire agencies from sharing information related to fire prevention or
				  suppression in parks.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Amendment filed 1-3-2002;
					 operative 1-3-2002 pursuant to Government Code section 11343.4 (Register 2002,
					 No. 1).
3. Amendment filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Sections 18300 and 18691, Health
						and Safety Code. Reference: Section 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1302 - Local Fire Prevention Code Enforcement

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) When the department is the enforcement
				  agency, a fire agency, as defined in this chapter, may elect to assume
				  responsibility to enforce its fire prevention code in parks, within its
				  jurisdictional boundaries, by providing the department with a written thirty
				  (30) day notice pursuant to Health and Safety Code section 18691(d).
(b) The written notice assuming enforcement
				  responsibilities for fire prevention shall clearly identify the geographical
				  boundaries of the jurisdiction of the fire agency and include the name and
				  address of each park located within these geographical boundaries.
(c) The fire agency that has assumed
				  responsibility to enforce its fire prevention code in parks within its
				  jurisdictional boundaries pursuant to this article, shall do all of the
				  following:
(1) Enforce its fire prevention
				  code as it applies to each of the following areas: fire hydrant systems, water
				  supply, fire equipment access, posting of fire equipment access, parking, lot
				  identification, weed abatement, debris abatement, combustible storage abatement
				  and burglar bars.
(2) Apply its
				  fire prevention code provisions only to conditions:
(A) that arise after the adoption of its fire
				  prevention code;
(B) not legally in
				  existence at the adoption of its fire prevention code; or
(C) that, in the opinion of the fire chief,
				  constitute a distinct hazard to life or property.
(3) Upon assuming responsibility to enforce
				  its fire prevention code in parks within its jurisdictional boundaries, the
				  fire agency shall notify all park operators within thirty (30) days of the
				  assumption of enforcement responsibility.
(A)
				  This notification shall include identification of the specific applicable codes
				  that will be enforced, where copies of the identified codes may be obtained,
				  and the scope and proposed time frame of any established or proposed inspection
				  program.
(B) The park operator
				  shall post a copy of the notification in the park as near as possible to the
				  location where the annual permit to operate is posted in order to advise the
				  occupants of the park of the change in enforcement
				  jurisdiction.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1304 - Local Regulations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The provisions of this article are not
				  applicable in parks located within a city, county, or city and county that is
				  the enforcement agency and has adopted and is enforcing a fire prevention code
				  imposing restrictions equal to or greater than the restrictions imposed by this
				  article.
(b) Any reporting
				  requirements imposed by the local agency fire prevention code shall be in
				  addition to, and shall not replace, the reporting requirements of this
				  article.
1. Amendment
					 of section and NOTE filed 1-3-2002; operative 1-3-2002 pursuant to Government
					 Code section 11343.4 (Register 2002, No. 1).
2. Amendment filed
					 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18300 and 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1305 - Fire Fighting Instructions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
In areas where fire department services are not available,
					 the park operator shall be responsible for the instruction of park staff in the
					 use of private park fire protection equipment and their specific duties in the
					 event of fire.
1.
					 Renumbering of former section 1684 to new section 1305, including amendment of
					 section, filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1306 - Permits Required

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No person shall construct, reconstruct, modify, or alter
					 any installations relating to fire protection equipment within a park unless a
					 written permit has been obtained from the enforcement agency with written
					 evidence of approval from the fire agency responsible for fire suppression in
					 the park.
1. Amendment
					 filed 1-3-2002; operative 1-3-2002 pursuant to Government Code section 11343.4
					 (Register 2002, No. 1).
2. Amendment filed 7-6-2004; operative
					 7-6-2004 pursuant to Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18500, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1308 - Lot Installations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
In addition to the water connection to the unit, each lot
					 constructed shall have installed an accessible three-quarter ( ¾ )-inch
					 valved water outlet, with an approved vacuum breaker installed, designed for
					 connecting a three-quarter ( ¾ )-inch female swivel hose connection for
					 fire suppression use.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1310 - Alternate Systems

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where the required water supply is inadequate to comply
					 with the provisions of this article and either outside protection, or local
					 conditions justify reducing this requirement, other hydrant systems may be
					 installed provided the alternate system is approved by the fire agency
					 responsible for fire suppression in the park and by the enforcement
					 agency.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Repealer and new section filed
					 1-3-2002; operative 1-3-2002 pursuant to Government Code section 11343.4
					 (Register 2002, No. 1).
3. Amendment of section heading and section
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Sections 18300 and 18691, Health
						and Safety Code. Reference: Section 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1312 - Private Systems

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) In
				  areas where fire department services are not available, as determined by the
				  enforcement agency, a private fire protection system shall be installed and
				  maintained consisting of hydrant or wet standpipe risers connected to the park
				  water main or a separate system capable of delivering seventy-five (75) gallons
				  per minute at thirty (30) psi with at least two lines open, in addition to the
				  normal requirements of the park, and with the hydrants or wet standpipes
				  located within seventy-five (75) feet of each lot. Each hydrant or wet
				  standpipe shall be provided with an approved one-and-one-half (1 ½ )
				  inch hose valve and connection with one, one-and-one-half (1 ½ ) inch
				  national standard male outlet and shall have connected thereto a minimum of
				  seventy-five (75) feet of one and one-half (1 ½ ) inch cotton or dacron
				  jacketed rubber lined fire hose with an approved cone type nozzle with a
				  minimum one-half ( ½ ) inch orifice. The fire hose shall be mounted on
				  an approved hose rack or reel enclosed in a weather resistant cabinet which
				  shall be painted red and marked "FIRE HOSE" in four (4) inch letters of
				  contrasting color.
(b) In parks
				  constructed prior to September 1, 1968 that have hydrants installed, the
				  hydrants shall be provided with not less than thirty-five (35) pounds water
				  pressure. These hydrants must meet the hose requirements contained in
				  subsection (a) of this section, but are not required to meet the water flow
				  requirements contained in subsection 1316(c) of this Article. In the event this
				  water pressure is not available, seventy-five (75) feet of three-quarter (
				  ¾ ) inch hose with attached cast brass adjustable spray stream, shut-off
				  nozzle, in a weather-protected cabinet which must deliver four and one-half
				  (4.5) gallons of water per minute at any given point within the mobilehome
				  park, may be substituted for one and one-half (1 ½ ) inch diameter hose
				  as specified herein.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Amendment filed 7-6-2004;
					 operative 7-6-2004 pursuant to Government Code section 11343.4 (Register 2004,
					 No. 28).
3. Amendment filed 1-21-2009; operative 1-21-2009 pursuant
					 to Government Code section 11343.4 (Register 2009, No.
					 4).
Note: Authority cited: Sections 18300, 18610 and 18691,
						Health and Safety Code. Reference: Sections 18610 and 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1314 - Care of Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All fire protection and suppression equipment shall be
					 protected against freezing in any areas subject to freezing.
1.
					 Renumbering of former section 1694 to new section 1314, including amendment of
					 section heading and section, filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No. 28). For prior history, see
					 Register 85, No. 36.
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18691, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1316 - Private Fire Hydrant Operation and Water Flow Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Private fire hydrants, as defined in this
				  article, shall meet the operational requirements as prescribed in subsection
				  (b) of this section, and meet the water flow standards prescribed by subsection
				  (c) of this section.
(b) Operation.
				  Private fire hydrants shall have at least the following characteristics in
				  order to be considered operational for the purposes of this article:
(1) valves that operate fully, freely and are
				  properly lubricated,
(2) threads
				  and caps that are undamaged,
(3)
				  reasonable protection from vehicular damage,
(4) outlets on hydrants are fourteen (14)
				  inches to twenty-four (24) inches above grade. Standpipes outlets need not be a
				  specific height, but must be readily accessible.
(5) thirty-six (36) inches of unobstructed
				  access around the hydrants;
(6)
				  locators or markings to clearly identify their location; and
(7) Each one and one-half (1 ½ ) inch
				  hydrant meets the requirements for hoses, locations, storage and storage
				  cabinet marking as defined in section 1312 of this article.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 6 - Fire Protection Standards for Parks › Section 1318 - Private Fire Hydrants with Violations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Correction of Violation. If, at any time,
				  a test undertaken pursuant to this article, or any other test or event,
				  indicates that a private fire hydrant is in violation of any provision of
				  section 1316, within sixty (60) days of the date of the event or the test of
				  the private fire hydrant, the park operator shall obtain a permit to construct
				  from the park enforcement agency, and shall promptly begin and maintain
				  activity to ensure the private fire hydrant meets the minimum requirements of
				  this article. This timeframe may be extended for extenuating circumstances
				  subject to approval by the enforcement agency.
(b) Approval to Use Existing Private Fire
				  Hydrant. Where the water flow test of a private fire hydrant reveals a water
				  flow less than that specified in subsection 1316(c) of this article, and it is
				  determined that the private fire hydrant cannot be repaired to meet the water
				  flow requirement, the park operator may request approval from the fire agency
				  responsible for fire suppression in that park to continue using the existing
				  private fire hydrant. Approval to use the existing private fire hydrant may be
				  granted by an authorized agent for the fire agency responsible for fire
				  suppression in the park, by signing Part VI on the form prescribed in
				  subsection 1317(a).
1. New
					 section filed 1-3-2002; operative 1-3-2002 pursuant to Government Code section
					 11343.4 (Register 2002, No. 1).
2. Change without regulatory effect
					 amending subsection (b) filed 11-7-2002 pursuant to section 100, title 1,
					 California Code of Regulations (Register 2002, No. 45).
3. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Sections 18300 and 18691, Health
						and Safety Code. Reference: Section 18691, Health and Safety
						Code.