reglab/statecodes huggingface dataset:
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1053 - Standards: Compressors

Current through June, 2024
(a) Each compressor
				  shall be equipped with a seal system that includes a barrier fluid system and
				  that prevents leakage of total organic emissions to the atmosphere, except as
				  provided in subsections (h) and (i).
(b) Each compressor seal system as required
				  in subsection (a) shall be:
(1) Operated with
				  the barrier fluid at a pressure that is at all times greater than the
				  compressor stuffing box pressure, or
(2) Equipped with a barrier fluid system that
				  is connected by a closed-vent system to a control device that complies with the
				  requirements of section 11-264-1060, or
(3) Equipped with a system that purges the
				  barrier fluid into a hazardous waste stream with no detectable emissions to
				  atmosphere.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1054 - Standards: Pressure relief devices in gas/vapor service

Current through June, 2024
(a)
				  Except during pressure releases, each pressure relief device in gas/vapor
				  service shall be operated with no detectable emissions, as indicated by an
				  instrument reading of less than five-hundred ppm above background, as measured
				  by the method specified in subsection 11-264-1063(c).
(b)
(1)
				  After each pressure release, the pressure relief device shall be returned to a
				  condition of no detectable emissions, as indicated by an instrument reading of
				  less than five-hundred ppm above background, as soon as practicable, but no
				  later than five calendar days after each pressure release, except as provided
				  in section 11-264-1059.
(2) No
				  later than five calendar days after the pressure release, the pressure relief
				  device shall be monitored to confirm the condition of no detectable emissions,
				  as indicated by an instrument reading of less than five-hundred ppm above
				  background, as measured by the method specified in subsection
				  11-264-1063(c).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1055 - Standards: Sampling connection systems

Current through June, 2024
(a) Each sampling
				  connection system shall be equipped with a closed-purge, closed-loop, or
				  closed-vent system. This system shall collect the sample purge for return to
				  the process or for routing to the appropriate treatment system. Gases displaced
				  during filling of the sample container are not required to be collected or
				  captured.
(b) Each closed-purge,
				  closed-loop, or closed-vent system as required in subsection (a) shall meet one
				  of the following requirements:
(1) Return the
				  purged process fluid directly to the process line;
(2) Collect and recycle the purged process
				  fluid; or
(3) Be designed and
				  operated to capture and transport all the purged process fluid to a waste
				  management unit that complies with the applicable requirements of sections
				  11-264-1084 through 11-264-1086 or a control device that complies with the
				  requirements of section 11-264-1060.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1056 - Standards: Open-ended valves or lines

Current through June, 2024
(a)
(1) Each open-ended valve or line shall be
				  equipped with a cap, blind flange, plug, or a second valve.
(2) The cap, blind flange, plug, or second
				  valve shall seal the open end at all times except during operations requiring
				  hazardous waste stream flow through the open-ended valve or line.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1057 - Standards: Valves in gas/vapor service or in light liquid service

Current through June, 2024
(a) Each valve in gas/vapor or light liquid
				  service shall be monitored monthly to detect leaks by the methods specified in
				  subsection 11-264-1063(b) and shall comply with subsections (b) through (e) ,
				  except as provided in subsections (f), (g), and (h), and sections 11-264-1061
				  and 11-264-1062.
(b) If an
				  instrument reading of ten-thousand ppm or greater is measured, a leak is
				  detected.
(c)
(1) Any valve for which a leak is not
				  detected for two successive months may be monitored the first month of every
				  succeeding quarter, beginning with the next quarter, until a leak is
				  detected.
(2) If a leak is
				  detected, the valve shall be monitored monthly until a leak is not detected for
				  two successive months,
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1058 - Standards: Pumps and valves in heavy liquid service, pressure relief devices in light liquid or heavy liquid service, and flanges and other connectors

Current through June, 2024
(a) Pumps and
				  valves in heavy liquid service, pressure relief devices in light liquid or
				  heavy liquid service, and flanges and other connectors shall be monitored
				  within five days by the method specified in subsection 11-264-1063(b) if
				  evidence of a potential leak is found by visual, audible, olfactory, or any
				  other detection method.
(b) If an
				  instrument reading of ten-thousand ppm or greater is measured, a leak is
				  detected.
(c)
(1) When a leak is detected, it shall be
				  repaired as soon as practicable, but not later than fifteen calendar days after
				  it is detected, except as provided in section 11-264-1059.
(2) The first attempt at repair shall be made
				  no later than five calendar days after each leak is detected.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1059 - Standards: Delay of repair

Current through June, 2024
(a) Delay of repair
				  of equipment for which leaks have been detected will be allowed if the repair
				  is technically infeasible without a hazardous waste management unit shutdown.
				  In such a case, repair of this equipment shall occur before the end of the next
				  hazardous waste management unit shutdown.
(b) Delay of repair of equipment for which
				  leaks have been detected will be allowed for equipment that is isolated from
				  the hazardous waste management unit and that does not continue to contain or
				  contact hazardous waste with organic concentrations at least 10 percent by
				  weight.
(c) Delay of repair for
				  valves will be allowed if:
(1) The owner or
				  operator determines that emissions of purged material resulting from immediate
				  repair are greater than the emissions likely to result from delay of
				  repair.
(2) When repair procedures
				  are effected, the purged material is collected and destroyed or recovered in a
				  control device complying with section 11-264-1060.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1060 - Standards: Closed-vent systems and control devices

Current through June, 2024
(a)
				  Owners or operators of closed-vent systems and control devices subject to this
				  subchapter shall comply with the provisions of section 11-264-1033.
(b)
(1) The
				  owner or operator of an existing facility who cannot install a closed-vent
				  system and control device to comply with the provisions of this subchapter on
				  the effective date that the facility becomes subject to the provisions of this
				  subchapter must prepare an implementation schedule that includes dates by which
				  the closed-vent system and control device will be installed and in operation.
				  The controls must be installed as soon as possible, but the implementation
				  schedule may allow up to 30 months after the effective date that the facility
				  becomes subject to this subchapter for installation and startup.
(2) Any unit that begins operation after
				  December 21, 1990, and is subject to the provisions of this subchapter when
				  operation begins, must comply with the rules immediately (i.e., must have
				  control devices installed and operating on startup of the affected unit); the
				  30-month implementation schedule does not apply.
(3) The owner or operator of any facility in
				  existence on the effective date of a statutory or regulatory amendment that
				  renders the facility subject to this subchapter shall comply with all
				  requirements of this subchapter as soon as practicable but no later than 30
				  months after the amendment's effective date. When control equipment required by
				  this subchapter can not be installed and begin operation by the effective date
				  of the amendment, the facility owner or operator shall prepare an
				  implementation schedule that includes the following information: Specific
				  calendar dates for award or contracts or issuance of purchase orders for the
				  control equipment, initiation of on-site installation of the control equipment,
				  completion of the control equipment installation, and performance of any
				  testing to demonstrate that the installed equipment meets the applicable
				  standards of this subchapter. The owner or operator shall enter the
				  implementation schedule in the operating record or in a permanent, readily
				  available file located at the facility.
(4) Owners and operators of facilities and
				  units that become newly subject to the requirements of this subchapter after
				  December 8, 1997, due to an action other than those described in paragraph (b)
				  (3) must comply with all applicable requirements immediately (i.e., must have
				  control devices installed and operating on the date the facility or unit
				  becomes subject to this subchapter; the 30-month implementation schedule does
				  not apply).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1061 - Alternative standards for valves in gas/vapor service or in light liquid service: percentage of valves allowed to leak

Current through June, 2024
(a) An owner
				  or operator subject to the requirements of section 11-264-1057 may elect to
				  have all valves within a hazardous waste management unit comply with an
				  alternative standard that allows no greater than 2 percent of the valves to
				  leak.
(b) The following
				  requirements shall be met if an owner or operator decides to comply with the
				  alternative standard of allowing 2 percent of valves to leak:
(1) An owner or operator must notify the
				  director that the owner or operator has elected to comply with the requirements
				  of this section.
(2) A performance
				  test as specified in subsection (c) shall be conducted initially upon
				  designation, annually, and at other times requested by the director.
(3) If a valve leak is detected, it shall be
				  repaired in accordance with subsections 11-264-1057(d) and (e).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1062 - Alternative standards for valves in gas/vapor service or in light liquid service: skip period leak detection and repair

Current through June, 2024
(a)
(1) An owner or operator subject to the
				  requirements of section 11-264-1057 may elect for all valves within a hazardous
				  waste management unit to comply with one of the alternative work practices
				  specified in paragraphs (b) (2) and (3).
(2) An owner or operator must notify the
				  director before implementing one of the alternative work practices.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1063 - Test methods and procedures

Current through June, 2024
(a) Each owner or
				  operator subject to the provisions of this subchapter shall comply with the
				  test methods and procedures requirements provided in this section.
(b) Leak detection monitoring, as required in
				  sections 11-264-1052 through 11-264-1062, shall comply with the following
				  requirements:
(1) Monitoring shall comply
				  with Reference Method 21 in 40 CFR Part 60.
(2) The detection instrument shall meet the
				  performance criteria of Reference Method 21.
(3) The instrument shall be calibrated before
				  use on each day of its use by the procedures specified in Reference Method
				  21.
(4) Calibration gases shall be:
(i) Zero air (less than 10 ppm of hydrocarbon
				  in air).
(ii) A mixture of methane
				  or n-hexane and air at a concentration of approximately, but less than,
				  ten-thousand ppm methane or n-hexane.
(5) The instrument probe shall be traversed
				  around all potential leak interfaces as close to the interface as possible as
				  described in Reference Method 21.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1064 - Recordkeeping requirements

Current through June, 2024
(a)
(1) Each owner or operator subject to the
				  provisions of this subchapter shall comply with the recordkeeping requirements
				  of this section.
(2) An owner or
				  operator of more than one hazardous waste management unit subject to the
				  provisions of this subchapter may comply with the recordkeeping requirements
				  for these hazardous waste management units in one recordkeeping system if the
				  system identifies each record by each hazardous waste management
				  unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1065 - Reporting requirements

Current through June, 2024
(a) A semiannual
				  report shall be submitted by owners and operators subject to the requirements
				  of this subchapter to the director by dates specified by the director. The
				  report shall include the following information:
(1) The EPA identification number, name, and
				  address of the facility.
(2) For
				  each month during the semiannual reporting period:
(i) The equipment identification number of
				  each valve for which a leak was not repaired as required in subsection
				  11-264-1057(d).
(ii) The equipment
				  identification number of each pump for which a leak was not repaired as
				  required in subsection 11-264-1052(c) and paragraph 11-264-1052(d)
				  (6).
(iii) The equipment
				  identification number of each compressor for which a leak was not repaired as
				  required in subsection 11-264-1053(g).
(3) Dates of hazardous waste management unit
				  shutdowns that occurred within the semiannual reporting period.
(4) For each month during the semiannual
				  reporting period, dates when the control device installed as required by
				  section 11-264-1052, 11-264-1053, 11-264-1054, or 11-264-1055 exceeded or
				  operated outside of the design specifications as defined in subsection
				  11-264-1064(e) and as indicated by the control device monitoring required by
				  section 11-264-1060 and was not corrected within twenty-four hours, the
				  duration and cause of each exceedance, and any corrective measures
				  taken.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter BB - AIR EMISSION STANDARDS FOR EQUIPMENT LEAKS › Section 11-264-1066 - 11-264-1079 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1080 - Applicability

Current through June, 2024
(a) The requirements of this subchapter apply
				  to owners and operators of all facilities that treat, store, or dispose of
				  hazardous waste in tanks, surface impoundments, or containers subject to either
				  subchapter I, J, or K except as section 11-264-1 and subsection (b) provide
				  otherwise.
(b) The requirements of
				  this subchapter do not apply to the following waste management units at the
				  facility:
(1) A waste management unit that
				  holds hazardous waste placed in the unit before December 6, 1996, and in which
				  no hazardous waste is added to the unit on or after December 6, 1996.
(2) A container that has a design capacity
				  less than or equal to 0.1 m3.
(3) A tank in which an owner or operator has
				  stopped adding hazardous waste and the owner or operator has begun implementing
				  or completed closure pursuant to an approved closure plan.
(4) A surface impoundment in which an owner
				  or operator has stopped adding hazardous waste (except to implement an approved
				  closure plan) and the owner or operator has begun implementing or completed
				  closure pursuant to an approved closure plan.
(5) A waste management unit that is used
				  solely for on-site treatment or storage of hazardous waste that is generated as
				  the result of implementing remedial activities required under the corrective
				  action authorities of RCRA sections 3004 (u) , 3004 (v) or 3008 (h) , CERCLA
				  authorities, section
				  342J-36,
				  HRS, or similar federal or State authorities.
(6) A waste management unit that is used
				  solely for the management of radioactive mixed waste in accordance with all
				  applicable regulations under the authority of the Federal Atomic Energy Act and
				  the Federal Nuclear Waste Policy Act.
(7) A hazardous waste management unit that
				  the owner or operator certifies is equipped with and operating air emission
				  controls in accordance with the requirements of an applicable Federal Clean Air
				  Act regulation codified under 40 CFR part 60, part 61, or part 63. For the
				  purpose of complying with this paragraph, a tank for which the air emission
				  control includes an enclosure, as opposed to a cover, must be in compliance
				  with the enclosure and control device requirements of section 11-264-1084(i),
				  except as provided in section 11-264-1082(c) (5).
(8) A tank that has a process vent as defined
				  in section 11-264-1031.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1081 - Definitions

Current through June, 2024
As used in this subchapter, all terms shall have the
					 meaning given to them in section
					 11-265-1081, chapter 342J, HRS,
					 and chapters 11-260 through 11-266.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1083 - Waste determination procedures

Current through June, 2024
(a) Waste
				  determination procedure to determine average volatile organic (VO)
				  concentration of a hazardous waste at the point of waste origination.
(1) An owner or operator shall determine the
				  average VO concentration at the point of waste origination for each hazardous
				  waste placed in a waste management unit exempted under the provisions of
				  section 11-264-1082(c) (1) from using air emission controls in accordance with
				  standards specified in sections 11-264-1084 through 11-264-1087, as applicable
				  to the waste management unit.
(2)
				  For a waste determination that is required by paragraph (a) (1), the average VO
				  concentration of a hazardous waste at the point of waste origination shall be
				  determined in accordance with the procedures specified in sections
				  11-265-1084(a) (2) through (a) (4).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1084 - Standards: Tanks

Current through June, 2024
(a) The provisions of this section apply to
				  the control of air pollutant emissions from tanks for which section
				  11-264-1082(b) references the use of this section for such air emission
				  control.
(b) The owner or operator
				  shall control air pollutant emissions from each tank subject to this section in
				  accordance with the following requirements as applicable:
(1) For a tank that manages hazardous waste
				  that meets all of the conditions specified in subparagraphs (b) (1) (i) through
				  (b) (1) (iii) , the owner or operator shall control air pollutant emissions
				  from the tank in accordance with the Tank Level 1 controls specified in
				  subsection (c) or the Tank Level 2 controls specified in subsection (d).
(i) The hazardous waste in the tank has a
				  maximum organic vapor pressure which is less than the maximum organic vapor
				  pressure limit for the tank's design capacity category as follows:
(A) For a tank design capacity equal to or
				  greater than 151 m3, the maximum organic vapor
				  pressure limit for the tank is 5.2 kPa.
(B) For a tank design capacity equal to or
				  greater than 75 m3 but less than 151
				  m3, the maximum organic vapor pressure limit for the
				  tank is 27.6 kPa.
(C) For a tank
				  design capacity less than 75 m3, the maximum organic
				  vapor pressure limit for the tank is 76.6 kPa.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1085 - Standards: Surface impoundments

Current through June, 2024
(a) The provisions
				  of this section apply to the control of air pollutant emissions from surface
				  impoundments for which section 11-264-1082(b) references the use of this
				  section for such air emission control.
(b) The owner or operator shall control air
				  pollutant emissions from the surface impoundment by installing and operating
				  either of the following:
(1) A floating
				  membrane cover in accordance with the provisions specified in subsection (c);
				  or
(2) A cover that is vented
				  through a closed-vent system to a control device in accordance with the
				  provisions specified in subsection (d).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1086 - Standards: Containers

Current through June, 2024
(a) The provisions
				  of this section apply to the control of air pollutant emissions from containers
				  for which section 11-264-1082(b) references the use of this section for such
				  air emission control.
(b) General
				  requirements.
(1) The owner or operator shall
				  control air pollutant emissions from each container subject to this section in
				  accordance with the following requirements, as applicable to the container,
				  except when the special provisions for waste stabilization processes specified
				  in paragraph (b) (2) apply to the container.
(i) For a container having a design capacity
				  greater than 0.1 m3 and less than or equal to 0.46
				  m3, the owner or operator shall control air
				  pollutant emissions from the container in accordance with the Container Level 1
				  standards specified in subsection (c).
(ii) For a container having a design capacity
				  greater than 0.46 m3 that is not in light material
				  service, the owner or operator shall control air pollutant emissions from the
				  container in accordance with the Container Level 1 standards specified in
				  subsection (c).
(iii) For a
				  container having a design capacity greater than 0.46
				  m3 that is in light material service, the owner or
				  operator shall control air pollutant emissions from the container in accordance
				  with the Container Level 2 standards specified in subsection (d).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1087 - Standards: Closed-vent systems and control devices

Current through June, 2024
(a)
				  This section applies to each closed-vent system and control device installed
				  and operated by the owner or operator to control air emissions in accordance
				  with standards of this subchapter.
(b) The closed-vent system shall meet the
				  following requirements:
(1) The closed-vent
				  system shall route the gases, vapors, and fumes emitted from the hazardous
				  waste in the waste management unit to a control device that meets the
				  requirements specified in subsection (c).
(2) The closed-vent system shall be designed
				  and operated in accordance with the requirements specified in section
				  11-264-1033(k).
(3) In the case
				  when the closed-vent system includes bypass devices that could be used to
				  divert the gas or vapor stream to the atmosphere before entering the control
				  device, each bypass device shall be equipped with either a flow indicator as
				  specified in subparagraph (b) (3) (i) or a seal or locking device as specified
				  in subparagraph (b) (3) (ii). For the purpose of complying with this paragraph,
				  low leg drains, high point bleeds, analyzer vents, open-ended valves or lines,
				  spring loaded pressure relief valves, and other fittings used for safety
				  purposes are not considered to be bypass devices.
(i) If a flow indicator is used to comply
				  with paragraph (b) (3) , the indicator shall be installed at the inlet to the
				  bypass line used to divert gases and vapors from the closed-vent system to the
				  atmosphere at a point upstream of the control device inlet. For this paragraph,
				  a flow indicator means a device which indicates the presence of either gas or
				  vapor flow in the bypass line.
(ii)
				  If a seal or locking device is used to comply with paragraph (b) (3) , the
				  device shall be placed on the mechanism by which the bypass device position is
				  controlled (e.g., valve handle, damper lever) when the bypass device is in the
				  closed position such that the bypass device cannot be opened without breaking
				  the seal or removing the lock. Examples of such devices include, but are not
				  limited to, a car-seal or a lock-and-key configuration valve. The owner or
				  operator shall visually inspect the seal or closure mechanism at least once
				  every month to verify that the bypass mechanism is maintained in the closed
				  position.
(4) The
				  closed-vent system shall be inspected and monitored by the owner or operator in
				  accordance with the procedure specified in section 11-264-1033(1).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1088 - Inspection and monitoring requirements

Current through June, 2024
(a) The owner or
				  operator shall inspect and monitor air emission control equipment used to
				  comply with this subchapter in accordance with the applicable requirements
				  specified in sections 11-264-1084 through 11-264-1087.
(b) The owner or operator shall develop and
				  implement a written plan and schedule to perform the inspections and monitoring
				  required by subsection (a). The owner or operator shall incorporate this plan
				  and schedule into the facility inspection plan required under section
				  11-264-15.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1089 - Recordkeeping requirements

Current through June, 2024
(a) Each owner or
				  operator of a facility subject to requirements of this subchapter shall record
				  and maintain the information specified in subsections (b) through (j) , as
				  applicable to the facility. Except for air emission control equipment design
				  documentation and information required by subsections (i) and (j) , records
				  required by this section shall be maintained in the operating record for a
				  minimum of 3 years. Air emission control equipment design documentation shall
				  be maintained in the operating record until the air emission control equipment
				  is replaced or otherwise no longer in service. Information required by
				  subsections (i) and (j) shall be maintained in the operating record for as long
				  as the waste management unit is not using air emission controls specified in
				  sections 11-264-1084 through 11-264-1087 in accordance with the conditions
				  specified in section 11-264-1080(d) or section 11-264-1080(b) (7),
				  respectively.
(b) The owner or
				  operator of a tank using air emission controls in accordance with the
				  requirements of section 11-264-1084 shall prepare and maintain records for the
				  tank that include the following information:
(1) For each tank using air emission controls
				  in accordance with the requirements of section 11-264-1084, the owner or
				  operator shall record:
(i) A tank
				  identification number (or other unique identification description as selected
				  by the owner or operator).
(ii) A
				  record for each inspection required by section 11-264-1084 that includes the
				  following information:
(A) Date inspection
				  was conducted.
(B) For each defect
				  detected during the inspection: The location of the defect, a description of
				  the defect, the date of detection, and corrective action taken to repair the
				  defect. In the event that repair of the defect is delayed in accordance with
				  the requirements of section 11-264-1084, the owner or operator shall also
				  record the reason for the delay and the date that completion of repair of the
				  defect is expected.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter CC - AIR EMISSION STANDARDS FOR TANKS, SURFACE IMPOUNDMENTS, AND CONTAINERS › Section 11-264-1091 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter DD - CONTAINMENT BUILDINGS › Section 11-264-1100 - Applicability

Current through June, 2024
The requirements of this subchapter apply to owners or
					 operators who store or treat hazardous waste in units designed and operated
					 under section
					 11-264-1101. The owner or operator
					 is not subject to the definition of land disposal in chapter 11-260 provided
					 that the unit:
(a) Is a completely
				  enclosed, self-supporting structure that is designed and constructed of manmade
				  materials of sufficient strength and thickness to support themselves, the waste
				  contents, and any personnel and heavy equipment that operate within the unit,
				  and to prevent failure due to pressure gradients, settlement, compression, or
				  uplift, physical contact with the hazardous wastes to which they are exposed;
				  climatic conditions; and the stresses of daily operation , including the
				  movement of heavy equipment within the unit and contact of such equipment with
				  containment walls;
(b) Has a
				  primary barrier that is designed to be sufficiently durable to withstand the
				  movement of personnel, wastes, and handling equipment within the
				  unit;
(c) If the unit is used to
				  manage liquids, has:
(1) A primary barrier
				  designed and constructed of materials to prevent migration of hazardous
				  constituents into the barrier;
(2)
				  A liquid collection system designed and constructed of materials to minimize
				  the accumulation of liquid on the primary barrier; and
(3) A secondary containment system designed
				  and constructed of materials to prevent migration of hazardous constituents
				  into the barrier, with a leak detection and liquid collection system capable of
				  detecting, collecting, and removing leaks of hazardous constituents at the
				  earliest practicable time, unless the unit has been granted a variance from the
				  secondary containment system requirements under paragraph 11-264-1101(b)
				  (4);
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter DD - CONTAINMENT BUILDINGS › Section 11-264-1101 - Design and operating standards

Current through June, 2024
(a) All containment
				  buildings must comply with the following design standards:
(1) The containment building must be
				  completely enclosed with a floor, walls, and a roof to prevent exposure to the
				  elements, (e.g., precipitation, wind, run-on), and to assure containment of
				  managed wastes.
(2) The floor and
				  containment walls of the unit, including the secondary containment system if
				  required under subsection (b) of this section, must be designed and constructed
				  of materials of sufficient strength and thickness to support themselves, the
				  waste contents, and any personnel and heavy equipment that operate within the
				  unit, and to prevent failure due to pressure gradients, settlement,
				  compression, or uplift, physical contact with the hazardous wastes to which
				  they are exposed; climatic conditions; and the stresses of daily operation,
				  including the movement of heavy equipment within the unit and contact of such
				  equipment with containment walls. The unit must be designed so that it has
				  sufficient structural strength to prevent collapse or other failure. All
				  surfaces to be in contact with hazardous wastes must be chemically compatible
				  with those wastes. The department will consider standards established by
				  professional organizations generally recognized by the industry such as the
				  American Concrete Institute (ACI) and the American Society of Testing Materials
				  (ASTM) in judging the structural integrity requirements of this subsection. If
				  appropriate to the nature of the waste management operation to take place in
				  the unit, an exception to the structural strength requirement may be made for
				  light-weight doors and windows that meet these criteria:
(i) They provide an effective barrier against
				  fugitive dust emissions under paragraph (c) (1) (iv); and
(ii) The unit is designed and operated in a
				  fashion that assures that wastes will not actually come in contact with these
				  openings.
(3)
				  Incompatible hazardous wastes or treatment reagents must not be placed in the
				  unit or its secondary containment system if they could cause the unit or
				  secondary containment system to leak, corrode, or otherwise fail.
(4) A containment building must have a
				  primary barrier designed to withstand the movement of personnel, waste, and
				  handling equipment in the unit during the operating life of the unit and
				  appropriate for the physical and chemical characteristics of the waste to be
				  managed.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter DD - CONTAINMENT BUILDINGS › Section 11-264-1102 - Closure and post-closure care

Current through June, 2024
(a) At closure of a
				  containment building, the owner or operator must remove or decontaminate all
				  waste residues, contaminated containment system components (liners, etc.,)
				  contaminated subsoils, and structures and equipment contaminated with waste and
				  leachate, and manage them as hazardous waste unless subsection 11-261-3(d)
				  applies. The closure plan, closure activities, cost estimates for closure, and
				  financial responsibility for containment buildings must meet all of the
				  requirements specified in subchapters G and H of this chapter.
(b) If, after removing or decontaminating all
				  residues and making all reasonable efforts to effect removal or decontamination
				  of contaminated components, subsoils, structures, and equipment as required in
				  subsection (a) of this section, the owner or operator finds that not all
				  contaminated subsoils can be practicably removed or decontaminated, he must
				  close the facility and perform post-closure care in accordance with the closure
				  and post-closure requirements that apply to landfills (section 11-264-310 ). In
				  addition, for the purposes of closure, post-closure, and financial
				  responsibility, such a containment building is then considered to be a
				  landfill, and the owner or operator must meet all of the requirements for
				  landfills specified in subchapters G and H of this chapter.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter DD - CONTAINMENT BUILDINGS › Section 11-264-1103 - 11-264-1110 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter EE - HAZARDOUS WASTE MUNITIONS AND EXPLOSIVES STORAGE › Section 11-264-1200 - Applicability

Current through June, 2024
The requirements of this subchapter apply to owners or
					 operators who store munitions and explosive hazardous wastes, except as section
					 11-264-1 provides otherwise.
					 (NOTE: Depending on explosive hazards, hazardous waste munitions and explosives
					 may also be managed in other types of storage units, including containment
					 buildings (chapter
					 11-264, subchapter DD) , tanks
					 (chapter
					 11-264, subchapter J), or containers
					 (chapter
					 11-264, subchapter I); See Section
					 11-266-205 for storage of waste
					 military munitions).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter EE - HAZARDOUS WASTE MUNITIONS AND EXPLOSIVES STORAGE › Section 11-264-1201 - Design and operating standards

Current through June, 2024
(a) Hazardous waste
				  munitions and explosives storage units must be designed and operated with
				  containment systems, controls, and monitoring, that:
(1) Minimize the potential for detonation or
				  other means of release of hazardous waste, hazardous constituents, hazardous
				  decomposition products, or contaminated run-off, to the soil, ground water,
				  surface water, and atmosphere;
(2)
				  Provide a primary barrier, which may be a container (including a shell) or
				  tank, designed to contain the hazardous waste;
(3) For wastes stored outdoors, provide that
				  the waste and containers will not be in standing precipitation;
(4) For liquid wastes, provide a secondary
				  containment system that assures that any released liquids are contained and
				  promptly detected and removed from the waste area, or vapor detection system
				  that assures that any released liquids or vapors are promptly detected and an
				  appropriate response taken (e.g., additional containment, such as overpacking,
				  or removal from the waste area); and
(5) Provide monitoring and inspection
				  procedures that assure the controls and containment systems are working as
				  designed and that releases that may adversely impact human health or the
				  environment are not escaping from the unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter EE - HAZARDOUS WASTE MUNITIONS AND EXPLOSIVES STORAGE › Section 11-264-1202 - Closure and post-closure care

Current through June, 2024
(a) At closure of a
				  magazine or unit which stored hazardous waste under this subchapter, the owner
				  or operator must remove or decontaminate all waste residues, contaminated
				  containment system components, contaminated subsoils, and structures and
				  equipment contaminated with waste, and manage them as hazardous waste unless
				  section 11-261-3(d) applies. The closure plan, closure activities, cost
				  estimates for closure, and financial responsibility for magazines or units must
				  meet all of the requirements specified in subchapters G and H, except that the
				  owner or operator may defer closure of the unit as long as it remains in
				  service as a munitions or explosives magazine or storage unit.
(b) If, after removing or decontaminating all
				  residues and making all reasonable efforts to effect removal or decontamination
				  of contaminated components, subsoils, structures, and equipment as required in
				  subsection (a), the owner or operator finds that not all contaminated subsoils
				  can be practicably removed or decontaminated, he or she must close the facility
				  and perform post-closure care in accordance with the closure and post-closure
				  requirements that apply to landfills (section 11-264-310 ).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264 - HAZADOUS WASTE MANAGEMENT STANDARDS FOR OWNERS AND OPERATERS OF HAZADOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subchapter FF - APPENDICES › Section 11-264-1300 - Appendices

Current through June, 2024
Appendices I, IV, V, and IX to 40 CFR Part 264, revised as
					 of May 25, 1998, and Appendix X, are made a part of this chapter. These
					 Appendices are entitled:
Appendix I - Recordkeeping Instructions
Appendix IV - Cochran's Approximation to the
					 Behrens-Fisher Students' T-Test
Appendix V - Examples of Potentially Incompatible
					 Waste
Appendix IX - Ground-Water Monitoring List
Appendix X - EPA Form 8700-13B
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Section 11-264.1-1 - Incorporation of 40 C.F.R. pact 264

Current through June, 2024
Title 40, part 264 of the Code of Federal Regulations
				  (C.F.R.), published by the Office of the Federal Register, as amended as of
				  July 1, 2020, is made a part of this chapter subject to the substitutions and
				  amendments set forth in sections 11-264.1-2 to 11-264.1-24.