reglab/statecodes huggingface dataset:
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 15.7 - Drip Pads › Section 66264.570 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  requirements of this article apply to owners and operators of facilities that
				  use new or existing drip pads to convey treated wood drippage, precipitation,
				  and/or surface water run-off to an associated collection system. Existing drip
				  pads are those constructed before December 6, 1990 and those for which the
				  owner or operator has a design and has entered into binding financial or other
				  agreements for construction prior to December 6, 1990. All other drip pads are
				  new drip pads. The requirement at section
				  66264.573(b)(3)
				  to install a leak collection system applies only to those drip pads that are
				  constructed after December 24, 1992 except for those constructed after December
				  24, 1992 for which the owner or operator has a design and has entered into
				  binding financial or other agreements for construction prior to December 24,
				  1992.
(b) The owner or operator of
				  any drip pad that is inside or under a structure that provides protection from
				  precipitation so that neither run-off nor run-on is generated is not subject to
				  regulation under sections
				  66264.573(e) or
				  66264.573(f), as
				  appropriate.
(c) The requirements
				  of this article are not applicable to the management of infrequent and
				  incidental drippage in storage yards provided that:
(1) the owner or operator maintains and
				  complies with a written contingency plan that describes how the owner or
				  operator will respond immediately to the discharge of such infrequent and
				  incidental drippage. At a minimum, the contingency plan shall describe how the
				  owner or operator will do the following:
(A)
				  cleanup the drippage;
(B) document
				  the cleanup of the drippage;
(C)
				  retain documents regarding cleanup for three years; and
(D) manage the contaminated media in a manner
				  consistent with Department regulations.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 15.7 - Drip Pads › Section 66264.571 - Assessment of Existing Drip Pad Integrity

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) For each existing drip pad as defined in
				  section 66264.570, the owner or operator
				  shall evaluate the drip pad and determine that it meets all of the requirements
				  of this article, except the requirements for liners and leak detection systems
				  of section
				  66264.573(b). No
				  later than the effective date of this rule, the owner or operator shall obtain
				  and keep on file at the facility, a written assessment of the drip pad,
				  reviewed and certified by an independent, qualified professional engineer
				  registered in California that attests to the results of the evaluation. The
				  assessment shall be reviewed, updated, and re-certified annually until all
				  upgrades, repairs, or modifications necessary to achieve compliance with all of
				  the standards of section
				  66264.573 are complete. The
				  evaluation shall document the extent to which the drip pad meets each of the
				  design and operating standards of section
				  66264.573, except the standards
				  for liners and leak detection systems, specified in section
				  66264.573(b).
(b) The owner or operator shall develop a
				  written plan for upgrading, repairing, and modifying the drip pad to meet the
				  requirements of section
				  66264.573(b), and
				  submit the plan to the Department no later than two years before the date that
				  all repairs, upgrades, and modifications are complete. This written plan shall
				  describe all changes to be made to the drip pad in sufficient detail to
				  document compliance with all the requirements of section
				  66264.573. The plan shall be
				  reviewed and certified by an independent qualified registered professional
				  engineer.
(c) Upon completion of
				  all upgrades, repairs, and modifications, the owner or operator shall submit to
				  the Department, the as-built drawings for the drip pad together with a
				  certification by an independent, qualified professional engineer registered in
				  California attesting that the drip pad conforms to the drawings.
(d) If the drip pad is found to be leaking or
				  unfit for use, the owner or operator shall comply with the provisions of
				  section 66264.573(m) or
				  close the drip pad in accordance with section
				  66264.575.
1. New
					 section filed 7-29-94; operative 8-29-94 (Register 94, No.
					 30).
Note: Authority cited: Sections
						25150
						and
						25159,
						Health and Safety Code; and Section
						58012, Governor's Reorganization
						Plan Number 1 of 1991. Reference: Sections
						25150,
						25159
						and
						25159.5,
						Health and Safety Code; and 40 CFR Section
						264.571.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 15.7 - Drip Pads › Section 66264.572 - Design and Installation of New Drip Pads

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Owners and operators of new drip pads shall ensure that the
					 pads are designed, installed, and operated in accordance with one of the
					 following:
(a) All of the requirements
				  of sections
				  66264.573 (except 66264.573(b),
				  66264.574 and 66264.575, or
(b) All
				  of the requirements of sections
				  66264.573 (except section
				  66264.573(a)(4)(A) and
				  (B)), 66264.574 and 66264.575.
1. New
					 section filed 7-29-94; operative 8-29-94 (Register 94, No.
					 30).
Note: Authority cited: Sections
						25150,
						25159,
						25159.5
						and
						25245,
						Health and Safety Code; and Section
						58012, Governor's Reorganization
						Plan Number 1 of 1991. Reference: Sections
						25150,
						25159
						and
						25159.5,
						Health and Safety Code; and 40 CFR Section
						264.572.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 15.7 - Drip Pads › Section 66264.573 - Design and Operating Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Drip pads shall:
(1) be constructed of non-earthen materials,
				  excluding wood and nonstructurally supported asphalt;
(2) be sloped to free-drain treated wood
				  drippage, rain and other waters, or solutions of drippage and water or other
				  wastes to the associated collection system;
(3) have a curb or berm around the
				  perimeter;
(4)
(A) have a hydraulic conductivity of less
				  than or equal to 1x10-7 centimeters per second,
				  e.g., existing concrete drip pads shall be sealed, coated, or covered with a
				  surface material with a hydraulic conductivity of less than or equal to
				  1x10-7 centimeters per second such that the entire
				  surface where drippage occurs or may run across is capable of containing such
				  drippage and mixtures of drippage and precipitation, material, or other wastes
				  while being routed to an associated collection system. This surface material
				  shall be maintained free of cracks and gaps that could adversely affect its
				  hydraulic conductivity, and the materials shall be chemically compatible with
				  the preservatives that contact the drip pad. The requirements of this provision
				  apply only to existing drip pads and those drip pads for which the owner or
				  operator elects to comply with section
				  66264.572(a)
				  instead of Section
				  66264.572(b).
(4)
(B) the
				  owner or operator shall obtain and keep on file at the facility a written
				  assessment of the drip pad, reviewed and certified by an independent, qualified
				  registered professional engineer registered in California that attests to the
				  results of the evaluation. The assessment shall be reviewed, updated and
				  recertified annually. The evaluation shall document the extent to which the
				  drip pad meets the design and operating standards of this section, except for
				  paragraph (b) of this section.
(5) be of sufficient structural strength and
				  thickness to prevent failure due to physical contact, climatic conditions, the
				  stress of daily operations, e.g., variable and moving loads such as vehicle
				  traffic, movement of wood, etc.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 15.7 - Drip Pads › Section 66264.574 - Inspections

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) During
				  preconstruction, construction, and operating phases, liners and cover systems
				  (e.g., membranes, sheets, or coatings) shall be inspected for uniformity,
				  damage, and imperfections (e.g., holes, cracks, thin spots, or foreign
				  materials). Immediately after construction or installation, liners shall be
				  inspected and certified as meeting the requirements of section
				  66264.573 by an independent,
				  qualified professional engineer registered in California. The certification
				  shall be maintained at the facility as part of the facility operating record.
				  After installation, liners and covers shall be inspected to ensure tight seams
				  and joints and the absence of tears, punctures, or blisters.
(b) While a drip pad is in operation, it
				  shall be inspected weekly and after storms to detect evidence of any of the
				  following:
(1) deterioration, malfunctions or
				  improper operation of run-on and run-off control systems;
(2) the presence of leakage in and proper
				  functioning of leak detection system; or
(3) deterioration or cracking of the drip pad
				  surface.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 15.7 - Drip Pads › Section 66264.575 - Closure

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) At closure, the
				  owner or operator shall remove or decontaminate all waste residues,
				  contaminated containment system components (pad, liners, etc.), contaminated
				  subsoils, and structures and equipment contaminated with waste and leakage, and
				  manage them as hazardous waste.
(b)
				  If, after removing or decontaminating all residues and making all reasonable
				  efforts to effect removal or decontamination of contaminated components,
				  subsoils, structures, and equipment as required in subsection (a) of this
				  section, the owner or operator finds that not all contaminated subsoils can be
				  practically removed or decontaminated, the owner or operator shall close the
				  facility and perform post-closure care in accordance with closure and
				  post-closure care requirements that apply to landfills (section
				  66264.310). For permitted units,
				  the requirement to have a permit continues throughout the post-closure period.
				  In addition, for the purposes of closure, post-closure, and financial
				  responsibility, such a drip pad is then considered to be a landfill, and the
				  owner or operator shall meet all of the requirements for landfills specified in
				  articles 7 and 8 of this chapter.
(c)
(1) The
				  owner or operator of an existing drip pad, as defined in section
				  66264.570, that does not comply
				  with the liner requirements of section
				  66264.573(b)(1)
				  shall:
(A) include in the closure plan for
				  the drip pad under section
				  66264.112 both a plan for
				  complying with subsection (a) of this section and a contingent plan for
				  complying with subsection (b) of this section in case not all contaminated
				  subsoils can be practicably removed at closure; and
(B) prepare a contingent post-closure plan
				  under section
				  66264.118 for complying with
				  subsection (b) of this section in case not all contaminated subsoils can be
				  practicably removed at closure;
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 16 - Miscellaneous Units › Section 66264.600 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The requirements in this article apply to owners and
					 operators of facilities that transfer, treat, store, or dispose of hazardous
					 waste in miscellaneous units, except as section
					 66264.1 provides
					 otherwise.
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No.
					 22).
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25159
						and
						25159.5,
						Health and Safety Code; 40
						CFR Section
						264.600.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 16 - Miscellaneous Units › Section 66264.601 - Environmental Performance Standards

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A miscellaneous unit shall be located, designed,
					 constructed, operated, maintained, and closed in a manner that will ensure
					 protection of human health and the environment. Permits for miscellaneous units
					 shall contain such terms and provisions as necessary to protect human health
					 and the environment, including, but not limited to, as appropriate, design and
					 operating requirements, detection and monitoring requirements, and requirements
					 for responses to releases of hazardous waste or hazardous waste constituents
					 from the unit. Permit terms and provisions shall include those requirements of
					 articles 9 through 15 and articles 27, 28 and 28.5 of this chapter, chapter 20,
					 40 CFR Part 146 , and article 5.5 of chapter 6.5 of division 20 of the Health
					 and Safety Code (commencing with section
					 25100) that are appropriate for
					 the miscellaneous unit being permitted. Protection of human health and the
					 environment includes, but is not limited to:
(a) prevention of any releases that may have
				  adverse effects on human health or the environment due to migration of waste
				  constituents, hazardous constituents, or reaction products, in the ground water
				  or subsurface environment, considering:
(1)
				  the volume and physical and chemical characteristics of the waste in the unit,
				  including its potential for migration through soil, liners, or other containing
				  structures;
(2) the hydrologic and
				  geologic characteristics of the unit and the surrounding area;
(3) the existing quality of ground water and
				  soil-pore liquid and gas, including other sources of pollution and
				  contamination and their cumulative impact on the ground water and the normally
				  unsaturated zone;
(4) the quantity
				  and direction of groundwater flow;
(5) the proximity to and withdrawal rate of
				  current and potential groundwater users;
(6) the patterns of land use in the
				  region;
(7) the potential for
				  deposition or migration of waste constituents, hazardous constituents, or
				  reaction products, into subsurface physical structures, and into the root zone
				  of food-chain crops and other vegetation;
(8) the potential for health risks caused by
				  human exposure to constituents of concern; and
(9) the potential for damage to domestic
				  animals, wildlife, crops, vegetation, and physical structures caused by
				  exposure to constituents of concern;
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 16 - Miscellaneous Units › Section 66264.602 - Monitoring, Analysis, Inspection, Response, Reporting, and Corrective Action

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Monitoring, testing, analytical data, inspections,
					 response, and reporting procedures and frequency shall ensure compliance with
					 sections 66264.15,
					 66264.33,
					 66264.75,
					 66264.76,
					 66264.77,
					 66264.601 and
					 66264.801 as well as meet any
					 additional requirements needed to protect human health and the environment as
					 specified in the permit.
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No.
					 22).
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25159
						and
						25159.5,
						Health and Safety Code; 40
						CFR Section
						264.602.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 16 - Miscellaneous Units › Section 66264.603 - Post-Closure Care

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A miscellaneous unit that is a disposal unit shall be
					 maintained in a manner that complies with section
					 66264.601 during the post-closure
					 care period. In addition, if a transfer, treatment, or storage unit has
					 contaminated soils or ground water that cannot be completely removed or
					 decontaminated during closure, then that unit shall also meet the requirements
					 of section
					 66264.601 during post-closure
					 care. The post-closure plan under section
					 66264.118 shall specify the
					 procedures that will be used to satisfy this requirement.
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No.
					 22).
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25159
						and
						25159.5,
						Health and Safety Code; 40
						CFR Section
						264.603.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 17 - Environmental Monitoring and Response Programs for Air, Soil, and Soil-Pore Gas for Permitted Facilities › Section 66264.701 - Required Programs

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Owners and operators subject to this article shall conduct a monitoring and
				  response program as follows.
(1) Whenever
				  there is a statistically significant increase under section
				  66264.707(b) for
				  any hazardous constituents under section
				  66264.703 from a regulated unit at
				  any monitoring point under section
				  66264.705, or at another location
				  at which environmental monitoring is undertaken pursuant to state requirements,
				  the owner or operator shall institute a compliance monitoring program under
				  section 66264.708.
(2) Whenever the environmental protection
				  standard under section
				  66264.702 is exceeded, or when a
				  concentration specified for soil-pore gas or open-air downwind from the
				  hazardous waste facility, is exceeded, the owner or operator shall institute a
				  corrective action program under section
				  66264.708.
(3) In all other cases, the owner or operator
				  shall institute a detection monitoring program under section
				  66264.706.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 17 - Environmental Monitoring and Response Programs for Air, Soil, and Soil-Pore Gas for Permitted Facilities › Section 66264.702 - Environmental Protection Standard

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The owner or operator shall comply with
				  conditions specified in the facility permit that are designed to ensure that
				  hazardous constituents, under section
				  66264.703 entering soil or air
				  from a regulated unit, do not exceed the concentration limits under section
				  66264.704 cited by the Department
				  as maximum acceptable concentrations in soil, soil-pore gas, air, or on the
				  land surface.
(b) The owner or
				  operator shall not cause the concentration of a hazardous constituent in soil,
				  soil-pore gas or air outside the unit to exceed a concentration limit under
				  section 66264.704 specified in the
				  facility permit as maximum acceptable concentrations in soil, soil-pore gas,
				  air, or on the land surface.
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No.
					 22).
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25150(a),
						25159,
						25159.5
						and
						25245,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 17 - Environmental Monitoring and Response Programs for Air, Soil, and Soil-Pore Gas for Permitted Facilities › Section 66264.703 - Hazardous Constituents

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The Department will specify in the facility permit the hazardous constituents
				  to which the environmental protection standard of section
				  66264.702 applies. Constituents
				  specified in the permit will be limited to constituents reasonably expected to
				  be in or derived from waste contained in a regulated unit.
(b) The Department shall not specify in the
				  facility permit constituents the Department considers not capable of posing a
				  substantial present or potential hazard to human health or the environment and
				  that are not useful as an indicator of migration of hazardous waste. In
				  deciding which constituents to cite in the facility permit, the Department will
				  consider the following:
(1) potential effects
				  on human health or the environment that can result from migration of waste
				  constituents from a regulated unit considering:
(A) the volume, physical and chemical
				  characteristics of the waste in the regulated unit, including its potential for
				  migration;
(B) the hydrogeological
				  characteristics of the facility and surrounding land;
(C) the current and estimated future uses of
				  the area;
(D) any existing
				  contamination or pollution, including other sources and their cumulative
				  impact;
(E) the potential for
				  health risks caused by human exposure to waste constituents;
(F) the potential damage to wildlife, crops,
				  vegetation and physical structures caused by exposure to waste constituents;
				  and
(G) the persistence and
				  permanence of the potential adverse effects;
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 17 - Environmental Monitoring and Response Programs for Air, Soil, and Soil-Pore Gas for Permitted Facilities › Section 66264.704 - Concentration Limits

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  facility permit shall specify concentration limits for soil, soilpore gas, and
				  open-air downwind from the regulated unit, for hazardous constituents
				  established under section
				  66264.703.
(b) The concentration limit for a hazardous
				  constituent in soil outside the regulated unit shall not exceed the background
				  concentration of that constituent in the soil unless an alternate concentration
				  limit that is higher than background concentration for soil is established by
				  the Department under subsection (e) of this section.
(c) The concentration limit for a hazardous
				  constituent in open-air immediately downwind from the regulated unit:
(1) shall not exceed an ambient air quality
				  standard established by the California Air Resources Board; and
(2) shall not exceed a concentration limit
				  for a hazardous constituent established by the Department to protect human
				  health or the environment.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 17 - Environmental Monitoring and Response Programs for Air, Soil, and Soil-Pore Gas for Permitted Facilities › Section 66264.705 - Monitoring Points

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The Department will specify in the facility permit the
					 monitoring points at which monitoring must be conducted by the owner or
					 operator and at which the environmental protection standard of section
					 66264.702 applies. Monitoring
					 points shall be suitable for sampling any substance that may have migrated from
					 the regulated unit, and shall be located close enough to the regulated unit to
					 provide an early indication of contaminant migration.
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No.
					 22).
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25150(a),
						25159,
						25159.5
						and
						25245,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 17 - Environmental Monitoring and Response Programs for Air, Soil, and Soil-Pore Gas for Permitted Facilities › Section 66264.707 - Compliance Monitoring Program

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
An owner or operator required to establish a compliance
					 monitoring program under this article shall, at a minimum, discharge the
					 following responsibilities.
(a) The
				  owner or operator shall perform monitoring the Department specifies to
				  determine whether regulated units are in compliance with the environmental
				  protection standard under section
				  66264.702, or to determine the
				  vertical and horizontal extent to which a constituent of hazardous waste has
				  migrated from a regulated unit. The Department will specify the environmental
				  protection standard in the facility permit, including:
(1) a list of the hazardous constituents
				  identified under section
				  66264.703;
(2) concentration limits under section
				  66264.704 for each of those
				  hazardous constituents; and
(3) the
				  monitoring points under section
				  66264.705.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 17 - Environmental Monitoring and Response Programs for Air, Soil, and Soil-Pore Gas for Permitted Facilities › Section 66264.708 - Corrective Action Program

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
An owner or operator required to establish a corrective
					 action program under this article shall, at a minimum, discharge the following
					 responsibilities.
(a) The owner or
				  operator shall take corrective action to ensure that regulated units are in
				  compliance with the environmental protection standard under section
				  66264.702. The Department will
				  specify the environmental protection standard in the facility permit,
				  including:
(1) a list of the hazardous
				  constituents identified under section
				  66264.703;
(2) concentration limits under section
				  66264.704 for each of those
				  hazardous constituents; and
(3) the
				  monitoring points under section
				  66264.705.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 19 - Corrective Action for Solid Waste Management Units › Section 66264.800 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer of article 19 and section filed 12-23-93 as an emergency; operative
					 12-23-93 (Register 93, No. 52). A Certificate of Compliance must be transmitted
					 to OAL by 5-9-94 or emergency language will be repealed by operation of law on
					 the following day.
3. Repealer of article 19 and section refiled
					 4-25-94 as an emergency; operative 4-25-94 (Register 94, No. 17). A Certificate
					 of Compliance must be transmitted to OAL by 8-23-94 or emergency language will
					 be repealed by operation of law on the following day.
4. Repealer of
					 article 19 and section refiled 8-22-94 as an emergency; operative 8-22-94
					 (Register 94, No. 34). A Certificate of Compliance must be transmitted to OAL
					 by 12-20-94 or emergency language will be repealed by operation of law on the
					 following day.
5. Repealer of article 19 and section refiled
					 12-22-94 as an emergency; operative 12-22-94 (Register 94, No. 51). A
					 Certificate of Compliance must be transmitted to OAL 4-21-95 or emergency
					 language will be repealed by operation of law on the following
					 day.
6. Repealer of article 19 and section refiled 6-29-95 as an
					 emergency; operative 6-29-95 (Register 95, No. 26). A Certificate of Compliance
					 must be transmitted to OAL by 10-27-95 or emergency language will be repealed
					 by operation of law on the following day.
7. Editorial correction
					 inserting inadvertently deleted article 19 heading (Register 95, No.
					 43).
8. Repealer of article 19 and section refiled 10-26-95 as an
					 emergency; operative 10-26-95 (Register 95, No. 43). A Certificate of
					 Compliance must be transmitted to OAL by 2-23-96 or emergency language will be
					 repealed by operation of law on the following day.
9. Certificate of
					 Compliance as to 10-26-95 order transmitted to OAL 11-30-95 and filed 1-16-96
					 (Register 96, No. 3).
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25150,
						25159
						and
						25159.5,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 19 - Corrective Action for Solid Waste Management Units › Section 66264.801 - Corrective Action. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22)
2.
					 Repealer filed 12-23-93 as an emergency; operative 12-23-93 (Register 93, No.
					 52). A Certificate of Compliance must be transmitted to OAL by 5-9-94 or
					 emergency language will be repealed by operation of law on the following
					 day.
3. Repealer refiled 4-25-94 as an emergency; operative 4-25-94
					 (Register 94, No. 17). A Certificate of Compliance must be transmitted to OAL
					 by 8-23-94 or emergency language will be repealed by operation of law on the
					 following day.
4. Repealer refiled 8-22-94 as an emergency;
					 operative 8-22-94 (Register 94, No. 34). A Certificate of Compliance must be
					 transmitted to OAL by 12-20-94 or emergency language will be repealed by
					 operation of law on the following day.
5. Repealer of section
					 refiled 12-22-94 as an emergency; operative 12-22-94 (Register 94, No. 51). A
					 Certificate of Compliance must be transmitted to OAL 4-21-95 or emergency
					 language will be repealed by operation of law on the following
					 day.
6. Repealer refiled 6-29-95 as an emergency; operative 6-29-95
					 (Register 95, No. 26). A Certificate of Compliance must be transmitted to OAL
					 by 10-27-95 or emergency language will be repealed by operation of law on the
					 following day.
7. Repealer refiled 10-26-95 as an emergency;
					 operative 10-26-95 (Register 95, No. 43). A Certificate of Compliance must be
					 transmitted to OAL by 2-23-96 or emergency language will be repealed by
					 operation of law on the following day.
8. Certificate of Compliance
					 as to 10-26-95 order transmitted to OAL 11-30-95 and filed 1-16-96 (Register
					 96, No. 3).
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25150,
						25159
						and
						25159.5,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 27 - Air Emission Standards for Process Vents › Section 66264.1030 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  regulations in this article apply to owners and operators of facilities that
				  treat, store, or dispose of RCRA hazardous wastes (except as provided in
				  section 66264.1).
(b) Except for section
				  66264.1034, subsections (d) and
				  (e), this article applies to process vents associated with distillation,
				  fractionation, thin-film evaporation, solvent extraction, or air or steam
				  stripping operations that manage RCRA hazardous wastes with organic
				  concentrations of at least 10 ppmw, if these operations are conducted in one of
				  the following:
(1) a unit that is subject to
				  the permitting requirements of chapter 20, or
(2) a unit (including a hazardous waste
				  recycling unit) that is not exempt from permitting under the provisions of
				  section 66262.17 (i.e., a hazardous waste recycling unit that is not a 90-day
				  tank or container) and that is located at a hazardous waste management facility
				  otherwise subject to the permitting requirements of chapter 20, or
(3) A unit that is exempt from permitting
				  under the provisions of section 66262.17 (i.e., a "90-day" tank or container)
				  and is not a recycling unit under the provisions of section 66261.6.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 27 - Air Emission Standards for Process Vents › Section 66264.1032 - Standards: Process Vents

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The owner or operator of a facility with
				  process vents associated with distillation, fractionation, thin-film
				  evaporation, solvent extraction, or air or steam stripping operations managing
				  hazardous wastes organic concentrations of at least 10 ppmw shall either:
(1) reduce total organic emissions from all
				  affected process vents at the facility below 1.4 kg/h (3 lb/h) and 2.8 Mg/yr
				  (3.1 tons/yr); or
(2) reduce, by
				  use of a control device, total organic emissions from all affected process
				  vents at the facility by 95 weight percent.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 27 - Air Emission Standards for Process Vents › Section 66264.1034 - Test Methods and Procedures

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each owner or operator subject to the
				  provisions of this article shall comply with the test methods, procedures and
				  requirements provided in this section.
(b) When a closed-vent system is tested for
				  compliance with no detectable emissions, as required in Section
				  66264.1033 (
l
),
				  the test shall comply with the following requirements:
(1) monitoring shall comply with Reference
				  Method 21 in 40 CFR, part 60 ;
(2)
				  the detection instrument shall meet the performance criteria of Reference
				  Method 21 in 40 CFR, part 60 ;
(3)
				  the instrument shall be calibrated before use on each day of its use by the
				  procedures specified in Reference Method 21 in 40 CFR, part 60 ; and
(4) calibration gases shall be:
(A) zero air (less than 10 ppm of hydrocarbon
				  in air); and
(B) a mixture of
				  methane or n-hexane and air at a concentration of approximately, but less than,
				  10,000 ppm methane or n-hexane; and
(5) the background level shall be determined
				  as set forth in Reference Method 21 in 40 CFR, part 60 ;
(6) the instrument probe shall be traversed
				  around all potential leak interfaces as close to the interface as possible as
				  described in Reference Method 21 in 40 CFR, part 60 ; and
(7) the arithmetic difference between the
				  maximum concentration indicated by the instrument and the background level is
				  compared with 500 ppm for determining compliance.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 27 - Air Emission Standards for Process Vents › Section 66264.1035 - Recordkeeping Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
(1) Each owner or operator subject to the
				  provisions of this article shall comply with the recordkeeping requirements of
				  this section.
(2) An owner or
				  operator of more than one hazardous waste management unit subject to the
				  provisions of this article may comply with the recordkeeping requirements for
				  these hazardous waste management units in one recordkeeping system if the
				  system identifies each record by each hazardous waste management
				  unit.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 27 - Air Emission Standards for Process Vents › Section 66264.1036 - Reporting Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  A semiannual report shall be submitted to the Department by owners and
				  operators subject to the requirements of this article. The report shall be
				  submitted by first week of February and August of each year. The report shall
				  include the following information:
(1) the
				  identification number, name, and address of the facility; and
(2) for each month during the semiannual
				  reporting period:
(A) dates when any control
				  device exceeded or operated outside of the design specifications, as defined in
				  Section 66264.1035(c)(4)
				  and as indicated by the control device monitoring required by Section
				  66264.1033(f) for
				  more than 24 hours;
(B) dates when
				  any flares operated with visible emissions as defined in Section
				  66264.1033(d) and
				  as determined by Method 22 monitoring;
(C) the duration and cause of each exceedance
				  or visible emissions; and
(D) any
				  corrective measures taken.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emission Standards for Equipment Leaks › Section 66264.1050 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  regulations in this article apply to owners and operators of facilities that
				  treat, store, or dispose of RCRA hazardous wastes (except as provided in
				  section 66264.1).
(b) Except as provided in section
				  264.1064(k), this article applies to equipment that contains or contacts
				  hazardous wastes with organic concentrations of at least 10 percent by weight
				  that are managed in one of the following:
(1)
				  A unit that is subject to the permitting requirements of chapter 20,
				  or
(2) A unit (including a
				  hazardous waste recycling unit) that is not exempt from permitting under the
				  provisions of section 66262.17 (i.e., a hazardous waste recycling unit that is
				  not a "90-day" tank or container) and that is located at a hazardous waste
				  management facility otherwise subject to the permitting requirements of chapter
				  20, or
(3) A unit that is exempt
				  from permitting under the provisions of section 66262.17 (i.e., a "90-day" tank
				  or container) and is not a recycling unit under the provisions of section
				  66261.6.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emission Standards for Equipment Leaks › Section 66264.1052 - Standards: Pumps in Light Liquid Service

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
(1)
				  Each pump in light liquid service shall be monitored monthly to detect leaks by
				  the methods specified in Section
				  66264.1063(b),
				  except as provided in subsections (d), (e), and (f) of this section.
(2) Each pump in light liquid service shall
				  be checked by visual inspection each calendar week for indications of liquids
				  dripping from the pump seal.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emission Standards for Equipment Leaks › Section 66264.1053 - Standards: Compressors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each compressor shall be equipped with a seal system that includes a barrier
				  fluid system and that prevents leakage of total organic emissions to the
				  atmosphere, except as provided in subsections (h) and (i) of this
				  section.
(b) Each compressor seal
				  system as required in subsection (a) of this section shall be:
(1) operated with the barrier fluid at a
				  pressure that is at all times greater than the compressor stuffing box
				  pressure; or
(2) equipped with a
				  barrier fluid system that is connected by a closed-vent system to a control
				  device that complies with the requirements of Section
				  66264.1060; or
(3) equipped with a system that purges the
				  barrier fluid into a hazardous waste stream with no detectable emissions to the
				  atmosphere.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emission Standards for Equipment Leaks › Section 66264.1054 - Standards: Pressure Relief Devices in Gas/Vapor Service

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Except during pressure releases, each
				  pressure relief device in gas/vapor service shall be operated with no
				  detectable emissions, as indicated by an instrument reading of less than 500
				  ppm above background, as measured by the method specified in Section
				  66264.1063(c).
(b)
(1)
				  After each pressure release, the pressure relief device shall be returned to a
				  condition of no detectable emissions, as indicated by an instrument reading of
				  less than 500 ppm above background, as soon as practicable, but no later than
				  24 hours after each pressure release, except as provided in Section
				  66264.1059.
(2) No later than 24 hours after the pressure
				  release, the pressure relief device shall be monitored to confirm the condition
				  of no detectable emissions, as indicated by an instrument reading of less than
				  500 ppm above background, as measured by the method specified in Section
				  66264.1063(c).
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 14 - Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emission Standards for Equipment Leaks › Section 66264.1055 - Standards: Sampling Connecting Systems

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each sampling connection system shall be
				  equipped with a closed-purge, closed-loop, or closed-vent system. This system
				  shall collect the sample purge for return to the process or for routing to the
				  appropriate treatment system. Gases displaced during filling of the sample
				  container are not required to be collected or captured.
(b) Each closed-purge, closed-loop, or
				  closed-vent system as required in subsection (a) of this section shall meet one
				  of the following requirements:
(1) return the
				  purged process fluid directly to the process line;
(2) collect and recycle the purged process
				  fluid; or
(3) be designed and
				  operated to capture and transport all the purged process fluid to a waste
				  management unit that complies with the applicable requirements of sections
				  66264.1084 through
				  66264.1086 or a control device
				  that complies with the requirements of section
				  66264.1060.