reglab/statecodes huggingface dataset:
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 10 - Conduit › Section 2760 - General

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Types and
						Sizes. Rigid metallic conduit and rigid nonmetallic conduit are approved for
						general use. Flexible metal conduit shall be permitted to be used as permitted
						by Section 2881(c).
						Electrical metallic tubing is not approved for high-voltage installations.
(Title 24, Part 3, Section
						  3-710 -
						  10(a).)
(b) Circuit in a Conduit. The conductors in a
						conduit shall be only those of a single circuit or feeder with the associated
						neutral and grounding conductor(s) if used.
(Title 24, Part 3, Section
						  3-710 -
						  10(b).)
(c) Reaming. All ends of conduit shall be
						reamed to remove rough edges.
(Title 24, Part 3, Section
						  3-710 -
						  10(c).)
(d) Fittings.
(1) Conduit fittings shall be of a size and
						type which will permit at least the minimum radius cable bend as required by
						Section 2748 for the size, type, and
						voltage to be installed. No splices or taps shall be made within conduit
						fittings.
(2) The conduit shall be
						secured to each enclosure by locknuts on the inside and outside of the
						enclosure, by threaded hubs, or by other approved fittings.
EXCEPTION: Locknuts are not required where conduit is
						  stubbed through a concrete surface which forms a side of the
						  enclosure.
(3) A bushing
						shall be installed where cables enter a conduit unless the design of the
						equipment is such as to afford equal protection.
(Title 24, Part 3, Section
						  3-710 -
						  10(d).)
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 10 - Conduit › Section 2761 - Rigid Metal Conduit

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Use. Rigid metal conduit shall be permitted to be used under all atmospheric
						conditions and occupancies, provided conduits and fittings exposed to the
						weather or to severe corrosive influences are of corrosion-resistant material
						or have coatings inside and outside suitable for the conditions. Where
						dissimilar metals are used, they shall be joined by an approved device or
						method.
(Title 24, Part 3, Section
						  3-346 -
						  1.)
(b) Running Threads. Running threads shall
						not be used.
(Title 24, Part 3, Section
						  3-346 -
						  9(b).)
(c) Support. Conduit shall be supported at
						least every 10 feet. However, rigid metallic runs of conduit made up with
						approved threaded couplings and uninterrupted by pull boxes shall be permitted
						to be secured in accordance with Table 2, provided such fastening prevents
						transmission of stresses to terminus when conduit is deflected between
						supports.
Table 2761
Conduit
								  Size
Maximum Distance Between Conduit
								  Supports
½ inch
10 feet
¾ inch
10 feet
1 inch
12 feet
1 ¼ inch
14 feet
1 ½ inch
14 feet
2 inch
16 feet
2 ½ inch
16 feet
3 inch and larger
20 feet
(Title 24, Part 3, Section
						  3-346 -
						  12.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 12-10-87; operative 1-9-88 (Register 88, No.
						  1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 10 - Conduit › Section 2762 - Rigid Nonmetallic Conduit

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Description. Nonmetallic conduit shall be resistant to moisture, chemical
						atmospheres, impact and crushing, and distortion due to heat where such
						conditions are likely to be encountered in service. It shall be weather
						resistant where installed out of doors.
(Title 24, Part 3, Section
						  3-347 -
						  1.)
(b) Use. Rigid nonmetallic conduit and
						fittings approved for the purpose shall be permitted to be used for exposed
						work if properly protected where exposed to severe mechanical damage.
(Title 24, Part 3, Section
						  3-347 -
						  2(b).)
(c) Support. Conduit shall be supported
						within 4 feet of each box, cabinet, or other conduit termination and shall be
						adequately supported elsewhere as required in Table 2762.
Table 2762
Conduit
								  Size
Maximum Distance Between Conduit
								  Supports
½ inch
4 feet
¾ inch
4 feet
1 inch
5 feet
1 ¼ inch
5 feet
1 ½ inch
5 feet
2 inch
5 feet
2 ½ inch
6 feet
3 inch
6 feet
3 ½ inch
7 feet
4 inch
7 feet
5 inch
7 feet
6 inch
8 feet
Rigid nonmetallic conduit and fittings approved for the
						  purpose shall be permitted to be used underground if properly protected where
						  exposed to severe mechanical damage.
(Title 24, Part 3, Section
						  3-347 -
						  8.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 12-10-87; operative 1-9-88 (Register 88, No.
						  1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2764 - Grounding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Metal-enclosed bus shall be grounded in accordance with
						  Article 6.
(Title 24, Part 3, Section
						  364-22.)
1.
						  Editorial correction including renumbering of former Article 60 to Article 11
						  filed 11-2-83 (Register 83, No. 45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2765 - Adjacent and Supporting Structures

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Metal-enclosed busways shall be installed so that
						  temperature rise from induced circulating currents in any adjacent metallic
						  parts will not be hazardous to personnel or constitute a fire hazard.
(Title 24, Part 3, Section
						  364-23.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2766 - Neutral

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Neutral bus, where required, shall be sized to carry
						  neutral load current and shall have adequate momentary and short circuit rating
						  consistent with system requirements.
(Title 24, Part 3, Section
						  364-24.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2767 - Barriers and Seals

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Bus runs having sections located both inside and
						  outside of building shall provide a vapor seal at the building wall to prevent
						  interchange of air between indoor and outdoor sections unless forced cooled.
						  Fire barriers shall be provided at walls where fire separation is
						  required.
(Title 24, Part 3, Section
						  364-25.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2768 - Perforated Enclosures

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where perforated enclosures are used, bus shall be
						  installed in accordance with Article 9, Open Wiring.
(Title 24, Part 3, Section
						  3-364 -
						  27.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2769 - Terminations and Connections

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Flexible or expansion connections shall be provided in
						  long, straight runs of bus to allow for temperature expansion or contraction,
						  or where the bus run crosses building vibration insulation joints.
All conductor termination and connection hardware shall
						  be accessible for installation, connection, and maintenance.
Where bus enclosures terminate at machines cooled by
						  flammable atmospheres, seal-off bushings, baffles, or other means shall be
						  provided to prevent accumulation of flammable gas in the bus enclosure.
(Title 24, Part 3, Section
						  364-28.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2770 - Switches

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Switching devices or disconnecting links provided in
						  the bus run shall have the same momentary rating as the bus.
Disconnecting links shall be plainly marked to be
						  removable only when bus is de-energized. Switching devices which are not load
						  break shall be interlocked to prevent operation under load and disconnecting
						  link enclosures shall be interlocked to prevent access to energized
						  parts.
(Title 24, Part 3, Section
						  364-29.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2771 - Identification

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Each bus run shall be provided with a permanent
						  nameplate on which the following information shall be provided:
(a) Rated voltage.
(b) Rated continuous current; if bus is
						forced cooled, both the normal forced cooled rating and the self-cooled (not
						forced cooled) rating for the same temperature rise shall be given.
(c) Rated frequency.
(d) Rated impulse withstand
						voltage.
(e) Rated 60-cycle
						withstand voltage (dry).
(f) Rated
						momentary current.
(g)
						Manufacturer's name and address.
NOTE: Metal-enclosed buses shall be constructed and
						  tested in accordance with ANSI C37.20--1969.
(Title 24, Part 3, Section
						  364-21.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Editorial correction filed 11-3-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2772 - Drain Facilities

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Drain plugs, filter drains, or similar methods shall be
						  provided to remove condensed moisture from low points in bus run.
(Title 24, Part 3, Section
						  364-26.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 11 - Metal-Enclosed Bus › Section 2773 - Low-Voltage Wiring

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Secondary control devices and wiring which are provided
						  as part of the metal-enclosed bus run shall be isolated by grounded metal
						  barriers from all primary circuit elements with the exception of short lengths
						  of wire, such as at instrument transformer terminals.
(Title 24, Part 3, Section
						  364-30.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 12 - Continuous Rigid Cable Supports (Cable Trays) › Section 2775 - Definition

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A continuous rigid cable support is a unit or an
						  assembly of units or sections, and associated fittings, made of metal or other
						  fire-resistant materials forming a continuous rigid structure used to support
						  cables. Continuous rigid cable supports include ladders, troughs, trays,
						  channels, and other similar structures.
(Title 24, Part 3, Section
						  318-1.)
1.
						  Editorial correction including renumbering of former Article 61 to Article 12
						  filed 11-2-83 (Register 83, No. 45).
2. Amendment of article heading
						  filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing only pursuant
						  to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 12 - Continuous Rigid Cable Supports (Cable Trays) › Section 2776 - Use

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Continuous rigid cable supports shall be permitted to
						  be used as the mechanical support for metal-clad cables in fire-resistive
						  building constructions as permitted in Section
						  2783, but shall not be used in
						  hoistways, or where subjected to severe physical damage. Continuous rigid cable
						  supports shall be permitted to be used to support metal-clad cables in
						  flammable atmospheres as permitted in Article 34.
(Title 24, Part 3, Sections
						  3-318 -
						  2(a) and
						  318-3.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Editorial correction filed 11-3-83 (Register 83, No. 45).
3.
						  Amendment filed 12-10-87; operative 1-9-88 (Register 88, No.
						  1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 12 - Continuous Rigid Cable Supports (Cable Trays) › Section 2777 - Installation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Continuous
						rigid cable supports shall be installed as a complete support system.
(Title 24, Part 3, Section
						  3-318 -
						  5(a).)
(b) Each run of continuous rigid cable
						support shall be complete before the installation of cables.
(Title 24, Part 3, Section
						  318-5(b).)
(c) Where cables may be subjected to physical
						damage, noncombustible covers or enclosures providing the required protection
						shall be used.
(Title 24, Part 3, Section
						  3-318 -
						  5(d).)
(d) Continuous rigid cable supports shall be
						permitted to extend transversely through partitions or walls, other than fire
						walls, provided the section of the support within the wall is continuous and
						unventilated.
(Title 24, Part 3, Section
						  318-5(g).)
(e) Continuous rigid cable supports shall be
						permitted to extend vertically through floors and platforms, provided the
						continuous rigid cable support is totally enclosed where it passes through the
						floor or platform opening and for a distance of 6 feet above the floor or
						platform to provide protection from physical damage.
(Title 24, Part 3, Section
						  318-5(g).)
(f) Continuous rigid cable supports shall be
						permitted to extend vertically through floors and platforms in wet locations
						where there are curbs or other suitable means to prevent water flow through the
						floor or platform opening, and the continuous rigid cable support is totally
						enclosed where it passes through the floor or platform to provide protection
						from physical damage.
(Title 24, Part 3, Section
						  318-5(g).)
(g) In other than horizontal runs, the cables
						shall be fastened securely to transverse members of the continuous rigid cable
						support.
(Title 24, Part 3, Section
						  318-7(b).)
(h) A working space of 24 inches minimum
						shall be maintained on one side of each rigid cable support.
(Title 24, Part 3, Section
						  3-318 -
						  5(i).)
(i) A minimum vertical clearance of 6 inches
						shall be maintained from the top of the rigid cable support to all ceilings,
						beams, and other similar obstructions exceeding 24 inches, measured along the
						length of the cable support.
(Title 24, Part 3, Section
						  3-318 -
						  5(k).)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of subsections (c)-(g) filed 12-10-87; operative 1-9-88 (Register 88,
						  No. 1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 12 - Continuous Rigid Cable Supports (Cable Trays) › Section 2778 - Grounding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All metal sections of continuous rigid cable supports
						  and fittings shall be electrically continuous and effectively grounded to
						  provide a continuous circuit for fault current. A continuous rigid cable
						  support system shall not be used either as a grounded circuit conductor or as
						  an equipment grounding conductor.
(Title 24, Part 3, Section
						  3-318 -
						  6.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 12 - Continuous Rigid Cable Supports (Cable Trays) › Section 2779 - Construction

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Continuous rigid cable supports shall comply with the
						  following:
(a) Shall have suitable
						strength and rigidity to provide adequate support for all contained
						wiring.
(b) Shall not present sharp
						edges, burrs, or projections injurious to the insulation or jackets of the
						wiring.
(c) If made of metal, shall
						be adequately protected against corrosion or shall be made of
						corrosion-resistant material.
(d)
						Shall have side rails or equivalent structural members.
(e) Shall include fittings for changes in
						direction and elevation of runs.
(Title 24, Part 3, Section
						  318-4.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 12-10-87; operative 1-9-88 (Register 88, No.
						  1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2781 - Use

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Metal-clad
						cable shall be permitted to be used in dry locations.
(b) Metal-clad cable shall be permitted to be
						used in wet locations, provided the insulated conductors and grounding
						conductors under the metallic covering are suitable for use in wet locations,
						and
(1) The metallic covering is impervious to
						moisture, or
(2) A
						moisture-resistant jacket is provided over the metallic
						covering.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2782 - Grounding. Grounding Conductor

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
An internal grounding conductor or conductors, either
						  copper or aluminum, shall be provided in each cable and shall be grounded in
						  accordance with Article 6.
(Title 24, Part 3, Section
						  3-334 -
						  23.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2783 - Supports

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Metal-clad cable shall be permitted to be installed on
						  metal racks, trays, troughs, or continuous rigid cable supports which are
						  effectively grounded. Each cable shall be supported at intervals not exceeding
						  6 feet and within 2 feet of every box or fitting, and each cable shall be
						  attached to the support at intervals of not more than 10 feet horizontally and
						  2 feet vertically.
(Title 24, Part 3, Section
						  3-334 -
						  25.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 12-10-87; operative 1-9-88 (Register 88, No.
						  1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2784 - Bends

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All bends shall be so made that the cable will not be
						  injured. (See Section
						  2748.)
(Title 24, Part 3, Section
						  334-11.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 12-10-87; operative 1-9-88 (Register 88, No.
						  1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2785 - Fittings

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
At all points where metal-clad cable terminates,
						  suitable fittings for use with the particular type of cable and the conditions
						  of service shall be used.
(Title 24, Part 3, Section
						  3-334 -
						  12.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2786 - Elevation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Metal-clad cable shall not be installed below an
						  elevation of 8 fee above working platform or grade without additional
						  mechanical protection.
EXCEPTION: Where the cable terminates in the top of
						  metal-enclosed switchgear, transformers, rotating equipment, and other enclosed
						  equipment, the cable may be extended vertically down to the top of the
						  enclosure if adequate mechanical support is provided.
(Title 24, Part 3, Section
						  3-334 -
						  26.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2787 - Strength

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The flexible metal enclosure shall provide the
						  equivalent mechanical strength of not less than .025 inch of steel.
(Title 24, Part 3, Section
						  3-334 -
						  27.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 13 - Metal-Clad Cable › Section 2787.1 - Splices and Terminations of Metal-Clad Cable

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Metal-clad cable splices or terminations
						shall be electrically and mechanically suitable for the conditions.
(b) Bonding shall be provided across splices
						to maintain the electrical continuity of the metal sheath.
(Title 24, Part 3, Section
						  3-110 -
						  14(c).)
1. New
						  section filed 10-29-80; effective thirtieth day thereafter (Register 80, No.
						  44).
2. Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 14 - Portable (Flexible) Cable › Section 2789 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This article applies to multi-conductor portable
						  cables, size 8 AWG or larger.
1.
						  Editorial correction including renumbering of former Article 63 to Article 14
						  filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87;
						  operative 1-9-88 (Register 88, No. 1).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 14 - Portable (Flexible) Cable › Section 2790 - Conductor Construction

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Multiconductor portable cable for use in supplying
						  power to portable or mobile equipment at over 600 volts, nominal, shall consist
						  of No. 8 or larger conductors employing flexible stranding. However, the
						  minimum size of the insulated ground-check conductor of Type G-GC cables shall
						  be No. 10.
EXCEPTION: Portable-type cable is not required to
						  supply mobile equipment that is not frequently moved, provided the cable is
						  suitably protected and will not be moved while energized.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of section heading and section filed 4-1-2009; operative 4-1-2009.
						  Submitted to OAL for printing only pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 14 - Portable (Flexible) Cable › Section 2791 - Shielding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) All
						high-voltage portable cables shall be operated with grounded
						shielding.
(b) Cables operated at
						over 2,000 volts shall be shielded for the purpose of confining the voltage
						stresses to the insulation.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing
						  only pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 14 - Portable (Flexible) Cable › Section 2792 - Equipment Grounding Conductors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Grounding conductors shall be
						provided.
(b) Identification. A
						conductor of a flexible cord or cable that is used as a grounded conductor or
						an equipment grounding conductor shall be distinguishable from other
						conductors.
(c) Connection of
						grounding conductors shall be in accordance with Article 6.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of section heading and section filed 4-1-2009; operative 4-1-2009.
						  Submitted to OAL for printing only pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 14 - Portable (Flexible) Cable › Section 2793 - Minimum Bending Radii

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The minimum bending radii for portable cables during
						  installation and handling in service shall be adequate to prevent damage to the
						  cable.
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 14 - Portable (Flexible) Cable › Section 2794 - Fittings

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Connectors used to connect lengths of cable in a run
						  shall be of an approved type which lock firmly together. Provisions shall be
						  made to prevent opening or closing these connectors while energized. Suitable
						  means shall be used to eliminate tension at connectors and
						  terminations.
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 14 - Portable (Flexible) Cable › Section 2795 - Splices and Terminations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Portable (Flexible) cables shall not be
						operated with splices unless the splices are of the permanent molded,
						vulcanized, or other approved type.
(b) Terminations. Termination enclosures
						shall be suitably marked with a high voltage hazard warning, and terminations
						shall be accessible only to authorized and qualified personnel.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing
						  only pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2796 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Except as specifically modified in this Article, all
						  other requirements of these Safety Orders for permanent wiring shall also apply
						  to temporary wiring installations.
1. New
						  section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing only
						  pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2797 - Use

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Temporary electrical installations of more than 600
						  volts may be used only during periods of construction, test, experiment, or
						  emergencies.
1.
						  Editorial correction including renumbering of former Article 64 to Article 15
						  filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87;
						  operative 1-9-88 (Register 88, No. 1).
3. Amendment filed 4-1-2009;
						  operative 4-1-2009. Submitted to OAL for printing only pursuant to Labor Code
						  section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2798 - Guarding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Suitable fencing, barriers, or other means shall be
						  provided to prevent access of other than authorized and qualified personnel to
						  temporary wiring.
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2799 - Time Limit. [Renumbered]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Renumbering of former section
						  2799 to new section
						  2799.0 filed 4-1-2009; operative
						  4-1-2009. Submitted to OAL for printing only pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2799.0 - Time Limit

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Temporary wiring as permitted in this section shall not be used for a period
						exceeding 90 days, except for construction purpose in which case it may be used
						for not to exceed one year. If necessary to exceed the above time limitation,
						special permission shall be obtained from the enforcing authority.
(b) All temporary wiring shall be removed
						immediately upon the completion of the project or purpose for which the wiring
						was installed; or upon the expiration of the time limit specified
						above.
1.
						  Renumbering of former section
						  2799 to new section
						  2799.0, including amendment of
						  subsection (b), filed 4-1-2009; operative 4-1-2009. Submitted to OAL for
						  printing only pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2799.1 - Feeders

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The following requirements apply to feeders:
(a) Feeders shall originate in an approved
						distribution center.
(b) Conductors
						shall be run as multi-conductor cord or cable assemblies. However, if installed
						as permitted in Section
						2797, and if accessible only to
						qualified persons, feeders may be run as single insulated conductors.
1. New
						  section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing only
						  pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2799.2 - Branch Circuits

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The following requirements apply to branch
						  circuits:
(a) Branch circuits shall
						originate in an approved panelboard.
(b) Conductors shall be multiconductor cord
						or cable assemblies or open conductors.
(c) No branch-circuit conductor may be laid
						on the floor.
(d) Each branch
						circuit that supplies fixed equipment shall contain a separate equipment
						grounding conductor if run as open conductors.
1. New
						  section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing only
						  pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2799.3

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No bare conductors nor earth returns may be used for
						  the wiring of any temporary circuit.
1. New
						  section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing only
						  pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2799.4

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Suitable disconnecting switches shall be installed to
						  permit the disconnection of all ungrounded conductors of each temporary
						  circuit. Multiwire branch circuits shall be provided with a means to disconnect
						  simultaneously all ungrounded conductors at the power outlet or panelboard
						  where the branch circuit originated.
NOTE: Circuit breakers with their handles connected by
						  approved handle ties are considered a single disconnecting means for the
						  purpose of this requirement.
1. New
						  section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing only
						  pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 2 - High-Voltage Electrical Safety Orders › Article 15 - Temporary Wiring › Section 2799.5

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Flexible cords and cables shall be protected from
						  accidental damage, as might be caused, for example, by sharp corners,
						  projections, and doorways or other pinch points.
1. New
						  section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing only
						  pursuant to Labor Code section
						  142.3 (Register
						  2009, No. 14).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.