reglab/statecodes huggingface dataset:
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart E - LOCAL EDUCATIONAL AGENCY RESPONSIBILITIES AND STANDARDS FOR ABATEMENT › Section 855.510 - Enclosure Procedures for Schools

Current through Register Vol. 48, No. 28, July 12, 2024
The contractor shall enclose ACBM in accordance with the
				  following procedures:
a) The work area
				shall be cleaned and isolated in accordance with Sections
				855.400,
				855.410,
				855.420,
				855.425,
				855.430,
				855.440
				and
				855.450.
b) Areas that may be disturbed during the
				installation of hangers or other support/framing materials for the enclosure
				shall be sprayed with amended water. These areas shall be kept damp to reduce
				airborne fiber concentrations.
c)
				Loose and hanging ACBM shall be removed in accordance with the requirements of
				Section
				855.460.
d) After installation of hangers, brackets or
				other enclosure supports and before installation of enclosure, damaged areas of
				fireproofing/thermal insulation materials shall be repaired using a
				nonasbestos-containing replacement material. Surfaces shall be prepared and
				replacement material applied in accordance with manufacturer's
				recommendations.
e) Hand tools used
				to drill, cut into, or otherwise disturb ACBM during the installation of
				support systems for the enclosures shall be equipped with HEPA filtered local
				exhaust ventilation.
f) Enclosure
				materials shall be impact resistant and provide an airtight barrier once
				construction is complete (see Section
				855.390(i)
				 ).
g) Utilities shall be lowered as necessary
				and reinstalled in a manner which permits proper utilization and does not
				disturb the integrity of the enclosures. Utility maintenance shall not require
				the enclosures to be opened or disturbed.
h) Cleanup shall be in accordance with
				Section
				855.465.
i) Enclosed ACBM shall be designated (e.g.,
				sign, label or color code) in order to warn building maintenance personnel in
				the event that the enclosure must be disturbed.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart E - LOCAL EDUCATIONAL AGENCY RESPONSIBILITIES AND STANDARDS FOR ABATEMENT › Section 855.520 - Reestablishment of the Work Area and HVAC Systems in Schools

Current through Register Vol. 48, No. 28, July 12, 2024
The contractor shall reestablish the work area in accordance
				  with the following procedure:
a)
				Reestablishment of the work area shall only occur following the completion of
				the cleanup procedures and after clearance air monitoring has been performed
				and documented to the satisfaction of the school board or building
				owner.
b) The contractor and
				building owner shall visually inspect the work area for any remaining visible
				residue. Evidence of contamination shall necessitate additional cleaning in
				accordance with Section
				855.465.
c) Additional air monitoring shall be
				performed in accordance with Section
				855.470
				if additional cleanup is necessary.
d) Following completion of clearance air
				monitoring of the work area in accordance with Section 855.470, remaining
				polyethylene barriers and worker and equipment decontamination enclosure
				systems shall be removed and disposed of as asbestos-contaminated waste.
				Following removal, the entire area, including HVAC filter assembly and duct
				work, shall be wet cleaned or HEPA vacuumed to remove residual asbestos
				fibers.
e) Mounted objects removed
				from former positions during area preparation activities may be
				resecured.
f) Objects that were
				removed to temporary locations may be relocated to original
				positions.
g) New filters shall be
				installed in HVAC systems, and mechanical and electrical systems shall be
				reestablished in working order.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Section 855.600 - Adverse Licensure Action

Current through Register Vol. 48, No. 28, July 12, 2024
The Department shall provide written notice via certified
				  mail of its decision to deny, suspend or revoke a license. The applicant or
				  licensee shall have 15 days to submit a written request for an administrative
				  hearing to contest the Department's decision. The Department's decision to
				  deny, suspend or revoke a license shall be based upon one or more of the
				  following reasons:
a) The person has
				falsified information on the application for licensure.
b) The person has performed duties outside
				the areas for which he is licensed.
c) The person has conducted any asbestos
				abatement activities in a manner hazardous to the public health in Illinois or
				in any other state where the person has acted in a similar capacity.
d) The person has violated any provision of
				the Asbestos Abatement Act or the Commercial and Public Building Asbestos
				Abatement Act, as applicable, or this Part.
e) The person has violated the registration
				and licensing standards for Professional Engineers [225 ILCS 325 ], Structural
				Engineers [225 ILCS 340 ], Architects [225 ILCS 305 ] or Industrial Hygienists
				[225 ILCS 52 ], as applicable. The Department may use findings by the
				Department of Professional Regulation, Illinois EPA or adverse civil or
				criminal findings in a circuit court as a basis for its action.
f) The person has submitted fraudulent or
				altered documentation, license, or certificate to the Department, to a building
				owner or representative or agent thereof, or to a contractor.
g) The person has performed work requiring
				licensure at a job site without being in possession of the license and initial
				and current refresher certificates.
h) The person has permitted the duplication
				or use of his/her own license or training certificate by another.
i) The person has obtained training from a
				training provider which is not accredited by the Department.
j) The person has submitted an application
				fee which was returned for insufficient funds.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Section 855.610 - Fines and Penalties

Current through Register Vol. 48, No. 28, July 12, 2024
a) In
				addition to any other action authorized by the Asbestos Abatement Act, the
				Commercial and Public Building Asbestos Abatement Act, or this Part, the
				Department may assess fines and penalties against a person for violation of any
				provision of the Asbestos Abatement Act, the Commercial and Public Building
				Asbestos Abatement Act, or this Part. The Department shall review each
				inspection report and stop work order according to criteria provided by this
				Section to determine whether a fine will be assessed, the amount of any such
				fine, and whether each day of violation shall constitute a separate violation
				for purposes of fine assessment.
b)
				The Department shall consider the following criteria independently and
				aggregately to determine whether a fine shall be assessed:
1) Whether a stop work order has been issued
				by the Department, and whether such order was strictly obeyed by the
				person.
2) Whether the person has
				previously been cited for a violation of the Asbestos Abatement Act, the
				Commercial and Public Building Asbestos Abatement Act or this Part, except that
				any previously cited violation shall not be considered if such violation was
				held to be unfounded or unapproved by a final order of the Department or by a
				court of competent jurisdiction, or if any previous citations for violations
				occurred more than three years prior.
3) Whether the violation is of such nature as
				to result in the possibility of injury or other harm to the environment, to the
				person's agents or employees, to the building owner, users, or occupants, or to
				the general public.
4) Whether the
				violation appears to be the result of any degree of negligence by the person or
				by the person's agents or employees.
5) Whether the person demonstrated good faith
				efforts to correct the violation upon receipt of oral or written notice of the
				violation and whether such actions in fact corrected the violation.
6) Whether the person is in possession of any
				falsified asbestos abatement license or certificate or represents themselves as
				authorized to conduct work without a valid license in a fraudulent
				manner.
7) Whether the person
				falsified an inspection for asbestos containing building materials.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Section 855.620 - Administrative Hearings

Current through Register Vol. 48, No. 28, July 12, 2024
All hearings shall be conducted pursuant to the Commercial
				  and Public Building Asbestos Abatement Act, the Asbestos Abatement Act, and the
				  Department's Rules of Practice and Procedures in Administrative Hearings, 77
				  Ill. Adm. Code 100.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Section 855.630 - Emergency Stop Work Orders for Commercial and Public Buildings

Current through Register Vol. 48, No. 28, July 12, 2024
In circumstances of substantial danger to the environment or
				  to the public health of persons or to the welfare of persons, the Department
				  may direct an entity to cease and desist asbestos abatement activities, to halt
				  the activity causing or contributing to the danger, or to take such other
				  action as may be necessary. The contractor or contractors subject to the order
				  will be removed from the list provided for in Section 20 of the Commercial and
				  Public Building Asbestos Abatement Act. The Department shall authorize the
				  reinstatement of the asbestos abatement activities and reinstatement of the
				  contractor to the Department's list of contractors when the activities that are
				  the subject of the emergency stop work order have been brought into compliance
				  with the requirements of applicable State and federal requirements and this
				  Part.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Section 855.640 - Emergency Stop Work Orders for Schools

Current through Register Vol. 48, No. 28, July 12, 2024
Whenever the Department finds that an emergency exists which
				  requires action to protect the public health, it may, without notice or
				  hearing, issue an order reciting the existence of such an emergency and then
				  require that such action be taken as it may deem necessary to meet the
				  emergency, including but not limited to the issuance of a stop work order and
				  the immediate removal of a contractor or contractors from the list provided for
				  in Section 10 of the Asbestos Abatement Act [105 ILCS
				  105/10 ]. Notwithstanding any other provision in that
				  Act, such order shall be effective immediately. The State's Attorney and
				  sheriff of the county in which the school is located shall enforce the order
				  after receiving notice thereof. Any contractor affected by such an order is
				  entitled, upon request, to a hearing as provided for in rules and regulations
				  promulgated pursuant to the Asbestos Abatement Act. When such conditions are
				  abated, in the opinion of the Department, the Department may authorize the
				  reinstitution of the activities and inclusion on the list of contractors of
				  those activities and contractors which were the subject of a stop work order.
				  (Section 12a of the Asbestos Abatement Act)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix A - PROJECT FORM › ILLUSTRATION A - Worker and Equipment Decontamination Systems

Current through Register Vol. 48, No. 28, July 12, 2024
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION A - Building Inspection for Friable and Nonfriable Materials

Current through Register Vol. 48, No. 28, July 12, 2024
School Building I.D. #
_____________
Inspection Completion Date
________
School District Name
________________________________________________________
School Official Name
________________________________________________________
School Building Name
___________________________________________________
School Building Address
_________________________________________________
City
________
State
_________
Zip
_________
Phone
_________
Total Square Footage
___________
Total School Occupancy
_______________
Total Past Occupancy
___________
Total Man Hours for Inspection
___________
Total Man Hours for the Report Preparation
___________
Inspection Company
_________________________________
Phone
_______________
Company Address
_________________________________________________________
City
_________
State
___________
Zip
____________________
________________________________
______________
______________
School Inspector's
Signature
I.D. #
Date
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION B - Inspection Report Form

Current through Register Vol. 48, No. 28, July 12, 2024
Category
_________________________________________________________
Sample Area I.D.
______________
Inspection Date
__________
School I.D. #
_________________________________________
School Name
_______________________________________________________
School Address
_____________________________________________________
City
________________
State
_______________
Zip
_______
Room(s)
______________
Sample Numbers
______________________
Inspector Name(s) and I.D. #(s)
__________________________________
Location of Area:
________________________________________________
Description of Material Sampled:
_________________________________
__________________________________________________________________
Friability:
High
Moderate
Low
Area Estimate:
__
Ft.
Water Damage:
Yes
No
Pipe Diameter:
__
In.
Physical Damage:
Heavy
Moderate
Low
None
Type of Wall:
Smooth Concrete
Gypsum Board
Textured Concrete
Masonry
Other
Type of Floor:
Concrete
Carpet
Tile
Wood
Other
Type of Ceiling:
Acoustic Tile
Exposed Structure
Textured Plaster
Accessibility:
Height of friable material from floor:
________
Ft.
Existence of barriers:
Suspended Ceiling
Encapsulation
Other
Proximity to items requiring maintenance:
Electrical
_______
Ventilation
Plumbing
Other
Less than 1 Ft.
More than 1 Ft.-Less than 5 Ft.
More than 5 Ft.
Ventilation Systems:
Vents near friable material:
Yes
No
Distance
_______
Ft.
Return Grille
_______
Supply Grille
______
Air Movement:
Heavy
Moderate
Low
Activity and Movement:
Use of Room:
______________________________________________
Activity:
High
Moderate
Low
What is above the room?
_______________________________________
What is adjacent to the room?
__________________________________
Comments:
________________________________________________________
__________________________________________________________________
__________________________________________________________________
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION C - Sampling Area Diagram (Ceiling and Floor)

Current through Register Vol. 48, No. 28, July 12, 2024
DescriptionsSampling
					 Area I.D.#1
Classroom Annex (Constructed in 1962)
Friable Ceiling Material - First Floor
					 Classroom
Gray textured spray finish
Stuccoed in appearance
All ceiling areas sketched below comprise
					 sampling area (1),
with one exception noted.
Click here to view
					 image
(Measurements are
inside dimensions)
(1) Water Damage
(2) Ceiling broken and falling
(3) Stairwell ceiling not friable - not in
				  sampling area (1)
Note: Do not sample the above as one sample area
School I.D.#
__________________
School Name
__________________
Address
___________________
Phone Number
_________________
Inspector Name & I.D.#
_________________
Date of Inspection
________________
Diagram Prepared by
__________________
Date
__________________
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION D - Sampling Area Diagram (Boiler Room)

Current through Register Vol. 48, No. 28, July 12, 2024
Description of Boiler
					 RoomSampling
					 Area I.D.# A,B,C
Construction 1957
Damaged friable pipe and boiler
					 insulation
Grayish-white chalky material
Click here to view
					 image
Each should be a separate diagram and
					 sampling area
Sample Area "A" - Pipe Insulation
Sample Area "B" - Pipe Joints
Sample Area "C" - Boiler Insulation
Note: Do not sample the above as one sample area
School I.D.#
__________________
School Name
__________________
Address
__________________
Phone Number
__________________
Inspector Name & I.D.#
_________________
Date of Inspection
__________________
Diagram Prepared by
__________________
Date
__________________
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION E - Random Sampling Table

Current through Register Vol. 48, No. 28, July 12, 2024
For each sampling area, take the first sample from the
					 center of subarea marked 1, take the second sample from the center of subarea
					 marked 2, etc.
Sampling
Sampling
Sampling
Sampling
Sampling
Sampling
Area
Location
Area
Location
Area
Location
8
9
1
5
8
1
8
5
2
1
2
7
5
7
4
3
6
13
3
6
9
9
3
4
2
7
9
7
1
4
8
7
1
5
7
1
4
1
6
2
3
9
5
8
6
3
4
14
3
9
7
4
2
6
2
8
9
8
5
2
4
1
7
3
6
4
3
5
6
3
2
9
6
9
9
2
7
15
9
2
8
8
5
3
5
8
1
7
4
1
6
1
8
5
7
3
4
8
3
4
5
9
3
10
8
1
6
16
2
5
9
2
7
4
2
9
4
7
1
6
6
4
3
5
1
6
8
2
7
5
1
5
8
11
3
4
9
17
4
5
3
9
2
7
7
8
2
1
9
6
7
4
3
7
1
9
2
5
9
6
6
1
5
12
2
4
5
18
6
1
8
2
9
8
6
8
3
4
7
3
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION F - Irregularly Shaped Random Sampling Area

Current through Register Vol. 48, No. 28, July 12, 2024
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION G - Regular Shaped Random Sampling Area

Current through Register Vol. 48, No. 28, July 12, 2024
Description:Sampling
					 Area I.D.
Activity Center Annex (Construction in 1962)
Gray textured spray finish
Stuccoed in appearance
All ceiling areas sketched below comprise Sampling Area
					 (2)
Click here to view
					 image
(1) Water
				  Damage
(2) Ceiling broken and
				  falling
School:
____________________
School Official:
___________________
Address:
____________________
Telephone Number:
__________________
Inspector:
___________________
Diagram Prepared By:
_________________
Inspection Date:
__________________
Date:
___________________
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 855 - ASBESTOS ABATEMENT FOR PUBLIC AND PRIVATE SCHOOLS AND COMMERCIAL AND PUBLIC BUILDINGS IN ILLINOIS › Subpart F - FINES, PENALTIES, ADMINISTRATIVE HEARINGS AND EMERGENCY STOP WORK ORDERS › Appendix B - Illustrations - Inspection and Management Plan Forms › ILLUSTRATION H - Protocol for Asbestos Management Plan

Current through Register Vol. 48, No. 28, July 12, 2024
a) The name and
				  address of each school building and whether the school building contains
				  friable ACBM, and friable and nonfriable suspected ACBM assumed to be
				  ACBM.
b) For each inspection
				  conducted:
1) The date of the
				  inspection.
2) A blueprint,
				  diagram, or written description of each school building that identified clearly
				  each location and approximate square or linear feet of any homogeneous or
				  sampling area where material was sampled for ACBM, and, if possible, the exact
				  locations where each bulk sample was collected, date of collection, homogeneous
				  areas where nonfriable suspected ACBM is assumed to be ACBM.
3) A copy of the analyses of any bulk
				  samples, dates of analyses, and a copy of any other laboratory reports
				  pertaining to the analyses.
4) A
				  description of any response actions or preventive measures taken to reduce
				  asbestos exposure, including the names, addresses and IDPH license I.D. numbers
				  of all contractors involved, start and completion dates of the work, and
				  results of any air samples analyzed during and upon completion of the
				  work.
5) A description of
				  assessment, required to be made under
				  40
				  CFR 763.88, of material that was identified
				  as friable ACBM or friable suspected ACBM assumed to be ACBM, and the name,
				  IDPH license I.D. number, signature and copies of accreditation certificates of
				  the licensed inspector.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart A - DEFINITIONS AND INCORPORATED MATERIALS › Section 860.20 - Incorporated and Referenced Materials

Current through Register Vol. 48, No. 28, July 12, 2024
a) The following materials are incorporated
				by reference and include no later amendments or editions:
1) Standard Specifications for Water and
				Sewer Main Construction in Illinois, 2004 Edition. Illinois Society of
				Professional Engineers, 100 East Washington Street, Springfield IL
				62706
2) National Electrical Code,
				2014 Edition. National Fire Protection Association, 1 Batterymarch Park, Quincy
				MA 02269
3) Installation of Oil
				Burning Equipment, 2016 Edition. National Fire Protection Association, 1
				Batterymarch Park, Quincy MA 02269
4) National Fuel Gas Code, 2015 Edition.
				National Fire Protection Association, 1 Batterymarch Park, Quincy MA
				02269
5) Liquefied Petroleum Gas
				Code, 2014 Edition. National Fire Protection Association, 1 Batterymarch Park,
				Quincy MA 02269
6) ASTM
				International (formerly American Society of Testing and Materials, Standard
				Method for Test for Surface Burning Characteristics of Building Materials),
				Standard E84-1998, ASTM International, 100 Barr Harbor Drive, P.O. Box C 700,
				West Conshohocken PA 19248-2959
7)
				Transportation of Natural and Other Gas by Pipeline: Minimum Federal Safety
				Standards ( 49 CFR 192 ), February 1, 2017. United States Department of
				Transportation, Pipeline and Hazardous Materials Safety Administration, 1200
				New Jersey Avenue, SE, Washington DC 20590
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart B - PERMITS › Section 860.100 - Required Permits

Current through Register Vol. 48, No. 28, July 12, 2024
Section 4 of the Act specifies the information required to
				  obtain a permit for the construction of a new manufactured home community.
				  Section 4.2 of the Act contains the information required to obtain a permit for
				  the alteration of an existing manufactured home community. Permits shall expire
				  three years from the date of issuance. One three year extension may be granted
				  upon written request. Section
				  4.3 of the Act contains
				  the information required for a permit to reduce sites in an existing
				  manufactured home community. Alternations to an existing manufactured home site
				  or community must be performed in accordance with the Act and this Part. A
				  permit is not required for routine maintenance and repairs.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart B - PERMITS › Section 860.110 - Applications

Current through Register Vol. 48, No. 28, July 12, 2024
All permit applications shall be submitted to the Department
				  on a form furnished by the Department. The application shall indicate the
				  number and identification of existing sites, new sites to be constructed,
				  licensed sites to be altered or eliminated and the new total number of proposed
				  licensed sites.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart B - PERMITS › Section 860.120 - Plans

Current through Register Vol. 48, No. 28, July 12, 2024
Section 4(d) of the Act specifies that, for a new
				  manufactured home community, plans must be prepared and sealed by an architect
				  licensed under the authority of the Illinois Architectural Practice Act of 1989
				  or an engineer licensed under the authority of the Illinois Professional
				  Engineering Act. The plans shall be drawn to scale. Two copies of the plans
				  shall be submitted to the Department. The plans and application material shall
				  contain, at a minimum, an overall manufactured home community plan and a
				  typical site plan as follows:
a) The
				overall manufactured home community plan shall include the following details
				for all proposed construction:
1) The location
				and dimension of each proposed site;
2) The location, width, type of surface
				material and traffic flow of all streets;
3) The locations of all sidewalks and parking
				areas;
4) The existing and proposed
				contours of the area, including an indication of any area in a flood plain and
				drainage away from the homes;
5)
				The locations, types, sizes and identification numbers of all water pipes;
				details of any private or semi-private water sources, sufficient to indicate
				compliance, and if the manufactured home community is served by a community
				public water supply system, the name of the system;
6) The locations, types, sizes and
				identification numbers of all sewage pipes, details of all private sewage
				disposal systems sufficient to indicate compliance, and, if the manufactured
				home community is served by a public sewer system, the name of the
				system;
7) The locations, types and
				sizes of all electrical conductors and equipment;
8) The types, sizes, heights and locations of
				all proposed manufactured home community lighting;
9) The sizes, locations and types of all fuel
				pipes; the locations and sizes of all fuel storage tanks;
10) The locations of all recreational
				equipment, beaches, swimming pools, parks, and community buildings (Swimming
				pools and bathing beaches are subject to a separate construction permit as
				required by the Swimming Facility Act.);
11) The general locations of all existing
				manufactured home sites and a description of how proposed utility extensions
				for new sites will be connected;
12) The types, sizes and locations of all
				garbage containers and the frequency of garbage collection;
13) The types, sizes and locations of any
				storm drainage pipes;
14) The
				locations of fire hydrants and holding ponds and the name of the fire
				department that serves the manufactured home community; and
15) The locations of all easements.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart B - PERMITS › Section 860.130 - Flood Plain Requirements

Current through Register Vol. 48, No. 28, July 12, 2024
Prior to the issuance of a construction permit, the permit
				  applicant shall submit with the application a completed "Special Flood Hazard
				  Area Request Form" provided by the Department. If the site is within a Special
				  Flood Hazard Area, the applicant shall forward the plans for the project to the
				  Illinois Department of Natural Resources, Office of Water Resources. No project
				  to be located in a Special Flood Hazard Area shall be issued a permit without a
				  copy of a statement from the Office of Water Resources that the construction
				  complies with the requirements of Executive Order 79-4, effective May 31, 1979.
				  Construction of items such as water wells, septic tanks, underground utilities,
				  light poles, pavilions, playground equipment, sidewalks and driveways as
				  specified in Statewide Permit Number 6, issued by the Office of Water
				  Resources, are exempt from the requirements of this Section.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart B - PERMITS › Section 860.140 - Occupancy of New Sites

Current through Register Vol. 48, No. 28, July 12, 2024
No manufactured home shall be placed on a site that has not
				  been licensed by the Department. Upon the completion of the construction of new
				  sites, the Department's regional office shall be contacted (see Section 860.
				  Appendix A) to arrange for an inspection. After approval is granted by the
				  inspector, the fee for the license for the new site(s) shall be submitted
				  before the new site(s) shall be licensed or occupied. (Type A
				  Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart B - PERMITS › Section 860.150 - Immobilization

Current through Register Vol. 48, No. 28, July 12, 2024
Sites with immobilized manufactured homes are exempt from
				  licensure by the Department. In order for a home to be considered immobilized,
				  the following conditions must be met:
a) The home shall be provided with individual
				utilities as defined in Section 2.8 of the Act.
b) The wheels, tongue, and hitch shall be
				removed and the home shall be supported by a continuous perimeter foundation of
				material such as concrete, mortared concrete block, or mortared brick which
				extends below the established frost depth. The home shall be secured in
				accordance with the Manufactured Home Quality Assurance Act and Manufactured
				Home Installation Code. (Type A Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart B - PERMITS › Section 860.160 - Deletion of Sites

Current through Register Vol. 48, No. 28, July 12, 2024
Section
				  4.3 of the Act
				  specifies the requirements that must be followed to reduce the number of
				  licensed sites. In addition, the following conditions shall be met:
a) The utilities shall be disconnected as
				follows:
1) The water service shall be shut
				off and capped below the frost depth and the riser shall be removed (Type A
				Violation);
2) The sewer pipe shall
				be cut below the ground level and sealed to prevent sewer gas from escaping
				(Type A Violation);
3) The
				electrical supply to the site shall be disconnected and the service equipment
				shall be removed (Type A Violation);
4) Any natural gas to the site shall be
				disconnected below grade and sealed in accordance with the National Fuel Gas
				Code (Type A Violation); and
5) Any
				propane tanks and the piping thereto shall be removed. (Type A
				Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.200 - Layout of the Manufactured Home Community

Current through Register Vol. 48, No. 28, July 12, 2024
a) All areas of the manufactured home
				community shall be drained to prevent ponding of water. Sites shall be graded
				to prevent surface water or drainage from accumulating or going under the home.
				If necessary, a storm drainage system shall be installed. (Type A
				Violation)
b) Section 9.3 of the
				Act specifies the minimum square footage of each site and the location of the
				homes on the site. (See Section 860. Illustrations A and B.) There shall be a
				minimum street frontage of 25 linear feet for each site. (Type A
				Violation)
c)
No mobile
				home shall be parked closer than 5 feet to the side lot lines of a park, or
				closer than 10 feet to a public street, alley or building. Each individual site
				shall abut or face on a private or public street. All streets shall have
				unobstructed access to a public street. There shall be an open space of at
				least 10 feet adjacent to the sides of every mobile home and at least 5 feet
				adjacent to the ends of every mobile home
. [
				210 ILCS
				115/9.3 ] Homes located on these sites shall not be
				closer to a private street than the previous home on that site. (Type A
				Violation)
d) Manufactured homes
				located on sites constructed after July 1, 1998 shall be located at least 10
				feet from private streets or other manufactured homes, and shall not extend
				over a sidewalk. (Type A Violation)
e) All portions of sheds, carports, garages,
				porches and similar structures constructed after July 1, 1998 shall be at least
				3 feet from the manufactured home community property line, 5 feet from any
				other structure on adjacent sites, and 10 feet from all streets. For corner
				sites, sheds shall be at least 3 feet from all streets. Existing portions of
				sheds, carports, garages, porches, and similar structures may be replaced at
				the same location without complying with the requirements of this subsection
				(e). (Type A Violation)
f) If any
				portion of a home, porch or step is within 5 feet of a private street, a speed
				limit of 10 miles per hour or less shall be posted for that street. (Type A
				Violation)
g) When questions arise
				concerning the property lines of the manufactured home community, the licensee
				shall be responsible for identifying the legal location. (Type A
				Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.210 - Support Systems

Current through Register Vol. 48, No. 28, July 12, 2024
a) Sites on
				which homes were installed on or before July 1, 2005 shall have a support
				system in accordance with the requirements in effect at the time of the
				installation. (Type A Violation)
b)
				Manufactured home sites constructed after July 1, 2005 shall comply with the
				Manufactured Housing Quality Assurance Act and the Manufactured Home
				Installation Code. (Type B Violation)
c) The owner or operator of a licensed
				manufactured home community must keep on file copies of the Installation
				Compliance Certificate required by the Manufactured Home Installation Code.
				This information shall be made available by the owner or operator of the
				manufactured home community to the Department, the manufactured home owner and
				lessee, and the representative of the manufactured home owner and lessee. (Type
				A Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.220 - Streets and Parking

Current through Register Vol. 48, No. 28, July 12, 2024
a) All streets
				shall be maintained free of potholes, snow, and dust. Streets constructed after
				July 1, 1998 shall be constructed of rock and oil, asphalt or concrete. (Type A
				Violation)
b) The minimum road
				width shall comply with Section 860. Table A. (Type A Violation)
c) At least two parking spaces shall be
				provided for each site constructed after July 1, 1998. At least one space shall
				be available for all other sites. Parking spaces on streets must be a minimum
				of 18 feet in length. (Type A Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.230 - Water

Current through Register Vol. 48, No. 28, July 12, 2024
a) Potable water
				shall be provided at each site. The source of the water shall be either a
				community public water supply system regulated by the Illinois Environmental
				Protection Agency or a system regulated by the Department. Systems regulated by
				the Department shall comply with one of the following:
1) The construction and water quality
				requirements of the Drinking Water Systems Code shall be met. (Type B
				Violation)
2) Water wells shall be
				located and constructed in accordance with the Illinois Water Well Construction
				Code and water well pump installation shall comply with the Illinois Water Well
				Pump Installation Code. (Type B Violation)
3) Surface water supply systems shall be
				constructed and operated in accordance with the Surface Source Water Treatment
				Code. (Type B Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.240 - Sewage

Current through Register Vol. 48, No. 28, July 12, 2024
a) All sewage
				generated within a manufactured home community shall discharge into an approved
				sewage disposal system.
1) A sewage disposal
				system designed to discharge below ground, or to the ground surface with a flow
				of less than 1,500 gallons per day, shall be regulated by the Department and
				must meet the requirements of the Private Sewage Disposal Code. (Type A
				Violation)
2) A sewage disposal
				system or group of systems installed after July 1, 1998 designed to discharge
				1,500 or more gallons per day to the ground surface shall meet the requirements
				of the Illinois Pollution Control Board (35 Ill. Adm. Code
				309.102(a) and
				(b) ). (Type C Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.250 - Electrical

Current through Register Vol. 48, No. 28, July 12, 2024
a) New
				Installations
1) All electrical distribution
				systems constructed or replaced after July 1, 1998 and before July 1, 2005
				shall be designed and constructed to conform to the requirements of the
				National Electrical Code, 1996 Edition. Article 550-C of the National
				Electrical Code contains specific requirements for manufactured home
				communities. Design, construction, and replacement of electrical distribution
				systems shall be in accordance with the 2014 edition of the National Electrical
				Code. (Type C Violation)
2) For
				homes installed after July 1, 1998, the manufactured home community licensee
				shall be responsible for providing electrical service equipment at least
				equivalent to the amperage capacity of the home which it serves. (Type A
				Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.260 - Fuel Supply

Current through Register Vol. 48, No. 28, July 12, 2024
The distribution, storage, and use of natural gas, liquefied
				  petroleum gas, fuel oil, or other fuels shall be in accordance with the
				  following:
a) The National Fire
				Protection Association's Installation of Oil Burning Equipment, 2016 Edition.
				(Type A Violation)
b) The National
				Fire Protection Association's National Fuel Gas Code, 2015 Edition. (Type A
				Violation)
c) The National Fire
				Protection Association's Liquefied Petroleum Gas Code, 2014 Edition. (Type A
				Violation)
d) The United States
				Department of Transportation's Pipeline Safety Regulations.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.270 - Fire Safety

Current through Register Vol. 48, No. 28, July 12, 2024
a) Bales of
				straw or other flammable materials that do not meet the requirements of
				subsection (b) of this Section shall not be used for skirting or insulation of
				the manufactured home. (Type B Violation)
b) Garages, carports, porches, awnings,
				sheds, skirting and other similar appurtenances shall be constructed of
				material designed for exterior use that meets the flame spread rating of 200 or
				less in accordance with the American Society of Testing and Materials, Standard
				Method of Test for Surface Burning Characteristics of Building Materials
				(Standard E84). (Type B Violation)
c) Fire Hydrants
1) If a manufactured home community has fire
				hydrants, the fire hydrant valves shall be tested annually and the flow rates
				documented annually by the local fire department, water department or other
				entity capable of analyzing the available flow from the hydrants. Such test
				results shall be available to the Department upon request. (Type A
				Violation)
2) The licensee shall
				provide notification in writing to the local fire department of the hydrants
				that have been deemed unsatisfactory, which includes an agreement to either
				remove the hydrants, reverse the top of the hydrant or provide some other
				identification acceptable to the fire department to indicate that the hydrant
				is not acceptable, or install a system that meets the requirements of
				subsection (d). (Type A Violation)
3) The residents of the manufactured home
				community shall be advised in writing by the licensee within 30 days when a
				manufactured home community licensee becomes aware that one or more hydrants in
				the community is inadequate. The location of these fire hydrants shall be
				specified in writing, along with a plan to correct the situation and an
				anticipated date for completion. The hydrant shall be repaired or replaced
				within 30 days. A copy of the notification shall be provided to the
				Department's Springfield office. (Type A Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.280 - Lighting

Current through Register Vol. 48, No. 28, July 12, 2024
Communities constructed after July 1, 1998 shall have an
				  average illumination level of at least 0.6 foot candles and a minimum
				  illumination level of 0.3 foot candles maintained for all streets in the
				  manufactured home community. (Type A Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.290 - Pools and Beaches

Current through Register Vol. 48, No. 28, July 12, 2024
Swimming pools and bathing beaches, if provided, shall be
				  constructed and operated in accordance with the Swimming Facility Code.
				  Separate construction permits and licenses are required in accordance with the
				  Swimming Facility Act. (Type A Violation)
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 860 - MANUFACTURED HOME COMMUNITY CODE › Subpart C - REQUIREMENTS OF THE MANUFACTURED HOME COMMUNITY › Section 860.300 - Solid and Landscape Waste

Current through Register Vol. 48, No. 28, July 12, 2024
a) All
				garbage and refuse shall be stored and disposed of so as not to create a
				nuisance or a health threat.
1) Garbage must
				be stored in rust resistant, watertight and fly-proof containers with the lids
				closed. (Type A Violation)
2) Bulk
				garbage containers must be stored on a concrete or asphalt surface or on an
				impervious surface. (Type A Violation)
3) All containers intended for garbage must
				be emptied at least once a week. (Type A Violation)
4) A minimum capacity of 40 gallons per
				occupied site per week shall be provided, according to the manufactured home
				community rules in Section
				860.410.
				Sealed bags can be utilized to supplement the required containers on the day of
				garbage collection only. A single 20 gallon container is acceptable if emptied
				twice a week. (Type A Violation)
5)
				Individual containers shall be available at each site or bulk containers shall
				be located within 250 feet of any home. Upon request, the Department shall
				grant a variance, under the provisions of Section 850.500, to allow bulk
				containers to be located more than 250 feet from a home, provided that the
				Department receives written assurance that the location of the containers is
				acceptable to the residents whose homes will be more than 250 feet from the
				containers. There is no distance limitation for bulk containers used by the
				manufactured home community management to empty individual containers. (Type A
				Violation)
6) Garbage and refuse
				shall be disposed of in accordance with the requirements of the Illinois
				Pollution Control Board (35 Ill. Adm. Code Subtitle G). (Type A
				Violation)