reglab/statecodes huggingface dataset:
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2270 - Sanitation Station Specifications

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each recreational vehicle sanitation
				  station shall be provided with a drain inlet not less than four (4) inches in
				  diameter, discharging into a trap not more than twenty-four (24) inches below
				  the drain inlet. The drain inlet shall be equipped with a hinged cover, which
				  shall effectively close the drain inlet when not in use.
(b) Each drain inlet shall discharge into a
				  drainage lateral not less than four (4) inches in diameter connected to a
				  public sewer or private sewage disposal system.
(c) The drain inlet of each recreational
				  vehicle sanitation station shall be set in a concrete drain receptor not less
				  than three and one-half (3 ½ ) inches in thickness and not less than two
				  (2) feet horizontally from the drain inlet to the inside of the surrounding
				  curb. The surrounding curb shall be at least four (4) inches wide and two (2)
				  inches above the floor of the receptor. The inside surface of the drain
				  receptor shall be smooth finished concrete and shall slope a minimum of
				  one-fourth ( ¼ ) inch per foot from the bottom of the curb to the lip of
				  the drain inlet.
(d) A
				  three-quarter ( ¾ ) inch water hose connection shall be installed at
				  each recreational vehicle sanitation station to allow connection of a hose for
				  wash-down operation. A listed and approved backflow preventing vacuum breaker
				  shall be permanently installed in the water service pipe at least six (6)
				  inches above the highest point of usage. Provisions shall be made to store the
				  wash-down hose off the ground.
(e)
				  A sign providing operating instructions shall be posted at all recreational
				  vehicle sanitation stations.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865.1, Health and Safety
						Code. Reference: Sections 18865.1, 18871.3, 18871.4 and 18873.1, Health and
						Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2272 - Sanitation Station Warning Sign

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A warning sign shall be located
				  immediately adjacent to the hose connection of the recreational vehicle
				  sanitation station and shall read:
DANGER, UNSAFE WATER
Use this hose to flush holding tank and drain receptor
ONLY.
(b) The
				  warning sign shall be not less than eighteen (18) inches by twenty-four (24)
				  inches and lettered in minimum size of not less than one (1) inch lettering in
				  a color contrasting with the background.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865.1, Health and Safety
						Code. Reference: Sections 18865.1, 18871.3, 18871.4 and 18873.1, Health and
						Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2274 - Lot Water Service Outlet

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each lot provided with a lot drain inlet shall be provided with a lot water
				  service outlet delivering safe, pure, and potable water. The lot water service
				  outlet riser shall be not less than three-quarter ( ¾ ) inch nominal
				  pipe size. Lots may be provided with a lot water service outlet where no lot
				  drain inlet has been installed.
(b)
				  Each lot water service outlet shall be provided with an accessible water outlet
				  designed for connecting a three-fourths ( ¾ ) inch female swivel hose
				  connection for emergency use, in addition to the unit water
				  connection.
(c) Where lot water
				  service outlets are not provided, water pipe risers shall be installed
				  throughout the special park occupancy area for the supply of potable water and
				  fire suppression. Gravel, crushed rock, or other approved material shall be
				  provided at the base of each water pipe riser as necessary to prevent the
				  accumulation of standing water or muddy conditions. Water pipe risers shall be
				  installed within one hundred (100) feet of all lots not provided with lot water
				  service outlets.
(d) Potable water
				  need not be supplied in an incidental camping area if it is designated as a
				  "dry camp" and occupants are so notified by the operator. If water is supplied,
				  it shall be safe, pure, and potable and adequate for all the requirements of
				  the incidental camping area.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865.1, Health and Safety
						Code. Reference: Sections 18870.1 and 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2276 - Pressure

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Parks
				  constructed between July 11, 1979, and July 6, 2004, shall have water
				  distribution systems capable of providing a pressure not less than fifteen (15)
				  pounds per square inch at each lot at maximum operating conditions. Parks
				  constructed before and after the above dates must be capable of maintaining
				  twenty (20) pounds per square inch at maximum operating conditions.
(b) The testing of a water system in a park
				  to determine the maximum operating condition shall be either performed at the
				  reported time of maximum water pressure loss, if within normal business hours,
				  or measured with twenty-five (25) percent of the required lot water supply
				  outlets, as defined in section 2308 of this chapter, open with the pressure
				  metering device at the end of the tested line.
1. New
					 section filed 7-22-2005; operative 7-22-2005 pursuant to Government Code
					 section 11343.4 (Register 2005, No. 29).
2. Editorial correction of
					 HISTORY 1 (Register 2005, No. 33).
Note: Authority cited: Sections 18865 and 18873.1, Health
						and Safety Code. Reference: Sections 18865 and 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2278 - Water Pipe Size

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  quantity of water required to be supplied to each lot provided with a drain
				  inlet shall be as required for six (6) fixture units.
(b) Park water distribution systems shall be
				  designed and installed as set forth in the California Plumbing Code, Chapter 6,
				  and Appendix A.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.1, Health
						and Safety Code. Reference: Section 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2280 - Mechanical Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where subject to physical damage, all park water service
					 outlets shall be protected by posts, fencing, or other barriers approved by the
					 enforcement agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2284 - Water Conditioning Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A permit shall be obtained from the
				  enforcement agency prior to installing any regenerating water conditioning
				  equipment on a lot. Approval of the park operator is required on all
				  applications for a permit to install such equipment. Where the water
				  conditioning equipment is of the regenerating type, and the park drainage
				  system discharges into a public sewer, approval of the sanitary district or
				  agency having jurisdiction over the public sewer is required prior to issuance
				  of the permit.
(b) Regenerating
				  water conditioning equipment shall be listed and labeled by an approved listing
				  agency.
(c) Regenerating units
				  shall discharge the effluent of regeneration into a trap not less than one and
				  one-half (1 ½ ) inches in diameter connected to the park drainage
				  system. An approved air gap shall be installed on the discharge line a minimum
				  of twelve (12) inches above the ground. The trap need not be vented.
(d) Electrical supply connections to
				  regenerating water conditioning equipment shall comply with the requirements of
				  this chapter.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18873.1 and 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2300 - Application and Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  For parks with a permit to construct dated on or after July 7, 2004, fire
				  protection equipment meeting the requirements of the National Fire Protection
				  Association (N.F.P.A.) Standard No. 24, 1995 Edition, which is hereby
				  incorporated by reference, shall be installed and maintained in every park
				  consisting of fifteen (15) or more lots, or parks enlarged to consist of
				  fifteen (15) or more lots. Installation of fire protection equipment is
				  required only for the new lots added.
(b) For parks with a permit to construct
				  dated between September 1, 1968, and July 7, 2004, Fire protection equipment
				  meeting the requirements of the National Fire Protection Association (N.F.P.A.)
				  Standard No. 24,1977 Edition, which is hereby incorporated by reference, shall
				  be maintained in every park consisting of 15 or more lots.
(c) Testing of Private Fire Hydrants. Park
				  owners and operators shall be responsible for the operation and water flow
				  requirements of all private fire hydrants installed in any park, regardless of
				  its age or number of lots in the park, and responsible for compliance with
				  other applicable provisions of this article.
(d) Reciprocity of Enforcement Agencies. The
				  provisions of section 2302 and sections 2316 through 2318 of this article, do
				  not create any obligation for the enforcement agency to report violations to a
				  fire agency, or for the fire agency to report violations to the enforcement
				  agency. However, this subsection does not preclude either enforcement agencies
				  or fire agencies from sharing information related to fire prevention or
				  suppression in parks.
1. New
					 article 6 (sections 2300-2319) and section filed 7-6-2004; operative 7-6-2004
					 pursuant to Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Sections 18865 and 18873.5, Health
						and Safety Code. Reference: Section 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2302 - Local Fire Prevention Code Enforcement

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) When the department is the enforcement
				  agency, a fire agency, as defined in this chapter, may elect to assume
				  responsibility to enforce its fire prevention code in parks, within its
				  jurisdictional boundaries, by providing the department with a written thirty
				  (30)-day notice pursuant to Health and Safety Code section 18873.5
				  (d).
(b) The written notice
				  assuming enforcement responsibilities for fire prevention shall clearly
				  identify the geographical boundaries of the jurisdiction of the fire agency and
				  include the name and address of each park located within these geographical
				  boundaries.
(c) The fire agency
				  that has assumed responsibility to enforce its fire prevention code in parks
				  within its jurisdictional boundaries pursuant to this article, shall do all of
				  the following:
(1) Enforce its fire prevention
				  code as it applies to each of the following areas: fire hydrant systems, water
				  supply, fire equipment access, posting of fire equipment access, parking, lot
				  identification, weed abatement, debris abatement, combustible storage abatement
				  and burglar bars.
(2) Apply its
				  fire prevention code provisions only to conditions:
(A) that arise after the adoption of its fire
				  prevention code;
(B) not legally in
				  existence at the adoption of its fire prevention code; or
(C) that, in the opinion of the fire chief,
				  constitute a distinct hazard to life or property.
(3) Upon assuming responsibility to enforce
				  its fire prevention code in parks within its jurisdictional boundaries, the
				  fire agency shall notify all park operators within thirty (30) days of the
				  assumption of enforcement responsibility.
(A)
				  This notification shall include identification of the specific applicable codes
				  that will be enforced, where copies of the identified codes may be obtained,
				  and the scope and proposed time frame of any established or proposed inspection
				  program.
(B) The park operator
				  shall post a copy of the notification in the park as near as possible to the
				  location where the annual permit to operate is posted in order to advise the
				  occupants of the park of the change in enforcement
				  jurisdiction.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2304 - Local Regulations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The provisions of this article are not
				  applicable in parks located within a city, county, or city and county that is
				  the enforcement agency and has adopted and is enforcing a fire prevention code
				  imposing restrictions equal to or greater than the restrictions imposed by this
				  article.
(b) Any reporting
				  requirements imposed by the local agency fire prevention code shall be in
				  addition to, and shall not replace, the reporting requirements of this
				  article.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.5, Health
						and Safety Code. Reference: Sections 18865 and 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2305 - Fire Fighting Instructions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
In areas where fire department services are not available
					 the park operator shall be responsible for the instruction of park staff in the
					 use of private park fire protection equipment and their specific duties in the
					 event of fire.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.5, Health
						and Safety Code. Reference: Section 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2306 - Permits Required

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No person shall construct, reconstruct, modify, or alter
					 any installations relating to fire protection equipment within a park unless a
					 written permit has been obtained from the enforcement agency with written
					 evidence of approval from the fire agency responsible for fire suppression in
					 the park.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18870, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2308 - Lot Installations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
When water service is provided to a lot, each lot
					 constructed shall have installed an accessible three-fourths (3/4)-inch valved
					 water outlet with an approved vacuum breaker installed, designed for connecting
					 a three-fourths (3/4)-inch female swivel hose connection for fire suppression
					 use in addition to the water connection to the unit.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2310 - Alternate Systems

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where the required water supply is inadequate to comply
					 with the provisions of this article and either outside protection, or local
					 conditions justify reducing this requirement, other hydrant systems may be
					 installed provided the alternate system is approved by the fire agency
					 responsible for fire suppression in the park and by the enforcement
					 agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.5, Health
						and Safety Code. Reference: Section 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2312 - Private Systems

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) In
				  areas where fire department services are not available, as determined by the
				  enforcement agency, a private fire protection system shall be installed and
				  maintained consisting of hydrant or wet standpipe risers connected to the park
				  water main or a separate system capable of delivering seventy-five (75) gallons
				  per minute at thirty (30) psi with at least two lines open, in addition to the
				  normal requirements of the park, and with the hydrants or wet standpipes
				  located within seventy-five (75) feet of each lot. Each hydrant or wet
				  standpipe shall be provided with an approved one and one-half (1 ½ )
				  inch hose valve and connection with one (1) one and one-half (1 ½ ) inch
				  national standard male outlet and shall have connected thereto a minimum of
				  seventy-five (75) feet of one and one-half (1 ½ ) inch cotton or dacron
				  jacketed rubber lined fire hose with an approved cone type nozzle with a
				  minimum one-half ( ½ ) inch orifice. The fire hose shall be mounted on
				  an approved hose rack or reel enclosed in a weather resistant cabinet which
				  shall be painted red and marked "FIRE HOSE" in four (4) inch letters of
				  contrasting color.
(b) In parks
				  constructed prior to September 1, 1968 that have hydrants installed, the
				  hydrants shall be provided with not less than thirty-five (35) pounds water
				  pressure. These hydrants must meet the hose requirements contained in
				  subsection (a) of this section, but are not required to meet the water flow
				  requirements contained in subsection 2316(c) of this Article. In the event this
				  water pressure is not available, seventy-five (75) feet of three-quarter (
				  ¾ ) inch hose with attached cast brass adjustable spray stream, shut-off
				  nozzle, in a weather-protected cabinet which must deliver four and one-half
				  (4.5) gallons of water per minute at any given point within the park, may be
				  substituted for one and one-half (1 ½ ) inch diameter hose as specified
				  herein.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment filed 1-21-2009;
					 operative 1-21-2009 pursuant to Government Code section 11343.4 (Register 2009,
					 No. 4).
Note: Authority cited: Sections 18865, 18872, and
						18873.5, Health and Safety Code. Reference: Sections 18872 and 18873.5, Health
						and Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2314 - Care of Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All fire protection and suppression equipment shall be
					 protected against freezing in any areas subject to freezing.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2316 - Private Fire Hydrant Operation and Water Flow Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Private fire hydrants, as defined in this
				  article, shall meet the operational requirements as prescribed in subsection
				  (b) of this section, and meet the water flow standards prescribed by subsection
				  (c) of this section.
(b) Operation.
				  Private fire hydrants shall have at least the following characteristics in
				  order to be considered operational for the purposes of this article:
(1) valves that operate freely and are
				  properly lubricated;
(2) threads
				  and caps that are undamaged;
(3)
				  reasonable protection from vehicular damage;
(4) outlets on hydrants are fourteen (14)
				  inches to twenty-four (24) inches above grade. Standpipes outlets need not be a
				  specific height, but must be readily accessible.
(5) Thirty-six (36) inches of unobstructed
				  access around the hydrants;
(6)
				  locators or markings to clearly identify their location; and
(7) each one and one-half (1 ½ ) inch
				  hydrant meets the requirements for hoses, locations, storage and storage
				  cabinet marking as defined in section 2312 of this article.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2318 - Private Fire Hydrants with Violations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Correction of Violation. If, at any time,
				  a test undertaken pursuant to this article, or any other test or event,
				  indicates that a private fire hydrant is in violation of any provision of
				  section 2316, within sixty (60) days of the date of the event or the test of
				  the private fire hydrant, the park operator shall obtain a permit to construct
				  from the park enforcement agency, and shall promptly begin and maintain
				  activity to ensure the private fire hydrant meets the minimum requirements of
				  this article. This timeframe may be extended for extenuating circumstances
				  subject to approval by the enforcement agency.
(b) Approval to Use Existing Private Fire
				  Hydrant. Where the water flow test of a private fire hydrant reveals a water
				  flow less than that specified in subsection 2316(c) of this article, and it is
				  determined that the private fire hydrant cannot be repaired to meet the water
				  flow requirement, the park operator may request approval from the fire agency
				  responsible for fire suppression in that park to continue using the existing
				  private fire hydrant. Approval to use the existing private fire hydrant may be
				  granted by an authorized agent for the fire agency responsible for fire
				  suppression in the park, by signing Part VI on the form prescribed in
				  subsection 2317(a).
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.5, Health
						and Safety Code. Reference: Section 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 6 - Fire Protection Standards for Parks › Section 2319 - Private Fire Hydrant Compliance for Park Operation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Permits to operate shall not be issued
				  for parks with private fire hydrants that do not meet the requirements of this
				  article.
(b) When applying for or
				  renewing a permit to operate, the park operator shall submit the original form
				  prescribed in subsection 2317(a) to the enforcement agency, as defined in this
				  article, and a copy forwarded to the fire agency responsible for fire
				  suppression in the park.
(c)
				  Provided a park meets all other requirements for obtaining or renewing a permit
				  to operate, a permit to operate may be issued to a park where the form
				  prescribed in subsection 2317(a), has been submitted to the enforcement agency
				  and one of the following options exists:
(1)
				  the form shows no violations;
(2)
				  the water flow test reveals a water flow less than that specified in subsection
				  2316(c) of this article, and the park operator has obtained an approval for the
				  continued use of the existing private fire hydrant from the fire agency
				  responsible for fire suppression in that park, pursuant to subsection
				  2318(b);
(3) a construction permit
				  has been obtained and activity maintained to ensure the private fire hydrant
				  meets the minimum requirements of this article;
(4) all violations of section 2316 are
				  corrected, and a revised or final form as prescribed in section 2317(a),
				  verifying the correction, has been submitted to the enforcement agency;
				  or
(5) the system meets or exceeds
				  the requirements approved at the time of its construction.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2320 - Application and Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  When an MH-unit or commercial modular is installed in a special occupancy park
				  pursuant to section 2118(b), the installation shall comply with Chapter 2 of
				  this Division.
(b) Existing
				  construction, connections, and installations of units, made before the
				  effective date of the requirements of this chapter may continue in use so long
				  as they were in compliance with requirements in effect at the date of their
				  installation and are not found to be substandard.
1. New
					 article 7 (sections 2320-2360) and section filed 7-6-2004; operative 7-6-2004
					 pursuant to Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Sections 18865, Health and Safety
						Code. Reference: Section 18613, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2322 - Removal of Vehicle Towing Hitch and Wheels

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A recreational vehicle towing hitch shall not be removed
					 from the vehicle unless it is designed to be removed and reinstalled. When the
					 hitch has been removed from a unit, it shall be readily available for
					 reinstallation. The wheels, vehicle axles, and their assemblies shall not be
					 removed.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865.1, Health and Safety
						Code. Reference: Section 18871.10, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2324 - Installation Permits

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A
				  permit shall be obtained from the enforcement agency each time a camping cabin
				  is to be located or installed on any site in a park.
(b) A permit shall not be required for
				  locating or installing a recreational vehicle on a lot.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18870, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2327 - Camping Cabins

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Camping cabin design, construction and installation shall comply with the
				  requirements specified in sections 18862.5 and 18871.11 of the Health and
				  Safety Code.
(b) Camping cabins
				  shall meet the roof live load requirements for accessory structures in
				  accordance with section 2433 of this chapter.
(c) All sleeping rooms shall have smoke
				  alarms installed in accordance with Section 907.2.11 of the California Building
				  Code. Alarms may be battery powered only when electrical service is not
				  supplied to the cabin.
(d) Camping
				  cabins shall not exceed four hundred (400) square feet as measured by the
				  camping cabin's footprint, to include built-in porches or stairways contained
				  within the original cabin footprint.
(e) When a camping cabin is required to meet
				  accessibility requirements, it shall comply with the requirements specified in
				  Chapter 11B of the California Building Code.
(f) A camping cabin shall be readily
				  relocatable.
(g) Accessory
				  structures for camping cabins shall comply with provisions of section 2422 of
				  this chapter.
(h) Fuel burning
				  heating or cooking appliances shall not be operated in a camping
				  cabin.
(i) No plumbing of any kind
				  shall be installed in a camping cabin.
(j) Camping cabins installed in a State
				  Responsibility Area Fire Hazard Severity Zone or a local Very-High Fire Hazard
				  Severity Zone as indicated on the California Department of Forestry and Fire
				  Protection's Fire Hazard Severity Zone Maps shall comply with the materials,
				  systems, and methods of construction as defined in the California Building
				  Code, Title 24, Part 2, Chapter 7A.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment of subsection (c) and
					 new subsection (j) filed 1-21-2009; operative 1-21-2009 pursuant to Government
					 Code section 11343.4 (Register 2009, No. 4).
3. Amendment of
					 subsections (c) and (e) filed 2-19-2013; operative 4-1-2013 (Register 2013, No.
					 8).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18862.5, 18871.11 and 18873.5, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2328 - Utility Facilities

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) When utilities are supplied to a lot or
				  site in a park, all connections to those utilities shall comply with the
				  requirements of this chapter.
(b)
				  When utilities are shared between two adjacent lots, the units on those lots
				  must maintain the minimum setback and separation distances described in section
				  2330 of this chapter.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. New subsection (a) designator
					 and new subsection (b) filed 2-19-2013; operative 4-1-2013 (Register 2013, No.
					 8).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18872, 18873.1, 18873.3 and 18873.4, Health and
						Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2330 - Unit Separation and Setback Requirements Within Parks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) In parks, or portions of parks, units
				  shall not be located closer than six (6) feet from any permanent building or
				  another unit.
(b) A unit shall be
				  located a minimum of three (3) feet from all lot lines. However, a three (3)
				  foot setback is not required from a lot line bordering a roadway when the
				  roadway is located within the park.
(c) When a unit has projections, including
				  eave overhangs, a minimum six (6) foot separation shall be maintained between
				  the edge of any projection or eave overhang and an adjacent, unit, permanent
				  building, combustible accessory building or structure and its projection, or
				  eave overhang. A minimum of three (3) feet shall be maintained from the unit's
				  projection or eave overhang and the adjacent lot line or property line.
				  However, a unit may be installed up to a park roadway or common area provided
				  there is no combustible building or structure in the common area within six (6)
				  feet, and no building or structure of any kind within three (3) feet, of any
				  portion of the unit. The maximum seventy-five percent (75%) lot coverage
				  allowed by section 2110 of this chapter shall be maintained. Projections or
				  eave overhangs shall not extend beyond a lot line bordering a roadway or common
				  area.
(d) Lot lines shall be
				  identified as prescribed by section 2104.
(e) Setback and separation requirements for
				  accessory structures or buildings or building components installed prior to the
				  effective date of this chapter, are contained in section 2428 of article
				  9.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment of subsection (c) and
					 NOTE filed 12-26-2006; operative 1-2-2007 pursuant to Government Code section
					 11343.4 (Register 2006, No. 52).
Note: Authority cited: Sections 18865, 18865.05, 18872
						and 18873, Health and Safety Code. Reference: Sections 18865, 18872, 18873 and
						18873.5, Health and Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2333 - Foundations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A recreational vehicle or camping cabin shall not be
					 permanently affixed to a lot or installed on a foundation
					 system.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865.1, Health and Safety
						Code. Reference: Sections 18871 and 18871.10, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2334 - Accessory Structure Support Piers and Footings

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Load bearing piers shall be constructed
				  of rust resistant materials or treated to resist rust. The required load
				  bearing capacity of individual support piers and their footings shall be
				  calculated at not less than a combined live and dead load of seventy-five (75)
				  psf, based on roof live and dead load of twenty-five (25) psf and floor live
				  and dead load of fifty (50) psf of the accessory structure.
(b) Load bearing piers, other than concrete
				  block piers, shall be tested to determine the safe operating load. The tests
				  shall be conducted by testing agencies approved by the department. Testing
				  agencies shall provide a pier testing report to the department upon completion,
				  regardless of the testing results. A unique number provided by the testing
				  agency shall identify each test report. The following testing procedures shall
				  be used:
(1) A compression test shall be
				  performed on three (3) piers of the same height and construction, selected
				  randomly at the pier manufacturing facility by a representative of the testing
				  agency.
(A) The compression test shall be
				  performed on piers with all required design assemblies installed, such as
				  adjustable tops, clamps, securement devices or similar assemblies.
(B) The selected piers shall be subjected to
				  the compression test with each pier, fully assembled as will be installed,
				  placed squarely on a firm base, and tested to its failure point. The
				  compression test shall be measured in psf. Support pier failure will be
				  established when the support bends, cracks, buckles or deflects to an unsafe
				  level as determined by the approved testing agency.
(C) The safe operating load of a support pier
				  is one-third ( 1/3 ) the average of the three (3) failure
				  tests.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2337 - Support Inspection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
At the time of inspection, the installation of the
					 accessory structure on its support system shall be complete and the area under
					 the accessory structure shall be accessible for inspection.
(a) Skirting shall not be installed until all
				  underfloor installations have been approved by the enforcement
				  agency.
(b) Masonry walls shall not
				  be installed until all underfloor installations have been approved by the
				  enforcement agency, unless the installation of the masonry wall is required to
				  provide perimeter support to the accessory structure.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18871.3, Health and Safety
						Code
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2344 - Clearances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A minimum
				  clearance of twelve (12) inches shall be maintained under all horizontal
				  structural members of accessory structures.
(b) The finished floor of a camping cabin
				  shall not exceed eighteen (18) inches in height above the ground.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18865, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2346 - Skirting Design and Construction

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Where the space beneath an accessory
				  structure is enclosed, there shall be provided a removable access panel opening
				  a minimum of eighteen (18) inches by twenty-four (24) inches unobstructed by
				  pipes, ducts, or other equipment that may impede access. The access panel shall
				  not be fastened by any means requiring the use of a special tool or device to
				  remove the panel.
(b) Cross
				  ventilation shall be provided by openings having a net area of not less than
				  one and one-half (1 ½ ) square feet for each twenty-five (25) linear
				  feet of the accessory structure and including all skirted structures. The
				  openings shall be provided on at least the two (2) opposite sides along the
				  greatest length of the unit and shall be installed as close to all the corners
				  as practicable.
(c) When wood
				  siding or equivalent home siding products are used as skirting material, the
				  installation shall comply with the siding manufacturer installation
				  instructions. Where siding manufacturer installation instructions are not
				  available, the installation shall conform to the provisions of the California
				  Residential Code. All wood products used in skirting construction located
				  closer than six (6) inches to earth shall be treated wood or wood of natural
				  resistance to decay. Where located on concrete slabs placed on earth, wood
				  shall be treated wood or wood of natural resistance to decay.
(d) When skirting is installed on a unit or
				  accessory structure in a floodplain as designated by the local floodplain,
				  management agency, the skirting shall be either:
(1) a flexible material that will not impede
				  the water flow, or
(2) if
				  constructed of rigid materials, have openings totaling one (1) square inch of
				  opening for every one (1) square foot of enclosed area. The bottom of these
				  openings shall not be more than one (1) foot above grade. Openings may be
				  equipped with screens, louvers, valves, or other coverings or devices provided
				  that they permit the automatic entry and exit of
				  floodwaters.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2352 - Electrical Feeder Assembly

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A
				  recreational vehicle or camping cabin shall be connected to the lot service
				  equipment by one of the following means:
(1) A
				  listed power supply cord approved for mobilehome or recreational vehicle
				  use.
(2) A power supply cord
				  bearing the following markings: Type SO, ST, or STO. The cord shall not be
				  spliced.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2354 - Unit Gas Connector

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each unit connected to the lot outlet
				  shall be connected by an approved flexible gas connector, listed for its
				  intended use, not more than six (6) feet in length and of adequate size to
				  supply the unit's gas appliance demand, as evidenced by the label on the unit.
				  In the absence of a label, the unit's demand shall be determined by the
				  California Plumbing Code, Chapter 12.
(b) Only one (1) gas supply connection to a
				  unit shall be permitted.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18871 and 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 7 - Installations and Facilities › Section 2356 - Unit Water Connector

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A unit shall be connected to the lot water service outlet
					 by a flexible connector approved for potable water.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18871 and 18873.1, Health and Safety
						Code.