reglab/statecodes huggingface dataset:
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING ELECTRODES › Section 2395.81 - Water Pipe Electrode

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where available on the premises, a metal underground
							 water pipe shall always be used as the grounding electrode, regardless of its
							 length and whether supplied by a community or a local underground water piping
							 system or by a well on the premises. Where the buried portion of the water pipe
							 (including any metal well casing effectively bonded to the pipe) is less than
							 10 feet long or where the water pipe is or is likely to be isolated by
							 insulated sections or joints so that the effectively grounded portion is less
							 than 10 feet long, it shall be supplemented by the use of an additional
							 electrode of a type specified by Section
							 2395.82 or Section
							 2395.83. The interior metal cold
							 water piping system shall always be bonded to the service-equipment enclosure,
							 the grounded conductor at the service, the grounding electrode conductor where
							 of sufficient size, or to the one or more grounding electrodes used.
NOTE: Expanding use of nonmetallic piping for water
							 systems and insulating couplings on metal water systems makes it more important
							 that water piping within a building be adequately grounded without depending on
							 connections to an outside piping system.
(Title 24, Part 3, Section
							 250-81(a).)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING ELECTRODES › Section 2395.82 - Other Available Electrodes

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where a water system as described in Section
							 2395.81 is not available, the
							 grounding connection shall be made to any of the electrodes specified in (a)
							 through (d) below, where available.
(a) The metal frame of the building, where
						  effectively grounded.
(Title 24, Part 3, Section
							 250-81(b).)
(b) An electrode encased by at least 2 inches
						  of concrete, located within and near the bottom of a concrete foundation or
						  footing that is in direct contact with the earth, consisting of at least 20
						  feet of one or more steel reinforcing bars or rods of not less that ½
						  -inch diameter, or consisting of at least 20 feet of bare copper conductor not
						  smaller than No. 4 AWG.
(Title 24, Part 3, Section
							 250-81(c).)
(c) An electrically continuous metal
						  underground gas piping system that is uninterrupted with insulating sections or
						  joints and without an outer nonconductive coating, and then only if acceptable
						  to and expressly permitted by both the serving gas supplier and the authority
						  having jurisdiction.
(Title 24, Part 3, Section
							 250-83(a).)
(d) Other local metal underground systems or
						  structures, such as piping systems and underground tanks.
(Title 24, Part 3, Section
							 250-83(b).)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING ELECTRODES › Section 2395.83 - Made Electrodes

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where none of the electrodes specified in Sections
							 2395.81 and
							 2395.82 is available, one or more
							 of the electrodes specified in (a) or (b) below shall be used. Where
							 practicable, electrodes shall be embedded below permanent moisture level. Where
							 more than one electrode is used (including those used for signaling or
							 communication circuits, radio or television installations, or lightning rods),
							 each electrode shall not be less than 6 feet from any other electrodes. All
							 electrodes shall be free from nonconductive coatings, such as paint or
							 enamel.
NOTE: Two or more electrodes that are effectively
							 bonded together are to be treated as a single electrode in this sense.
(Title 24, Part 3, Section
							 250-83(a).)
(a) Rod and Pipe Electrodes. Rod and pipe
						  electrodes shall not be less than 8 feet in length and shall consist of the
						  following materials, and shall be installed in the following manner:
(1) Electrodes of pipe or conduit shall not
						  be smaller than ¾ -inch trade size and, where of iron or steel, shall
						  have the outer surface galvanized or otherwise metal-coated for corrosion
						  protection.
(2) Electrodes of rods
						  of steel or iron shall be at least 5/8 -inch in diameter. Nonferrous rods or
						  their equivalent shall be listed and shall be not less than ½ -inch in
						  diameter.
(3) The electrode shall
						  be installed such that at least 8 feet of length is in contact with the soil.
						  It shall be driven to a depth of not less than 8 feet except that where rock
						  bottom is encountered, the electrode shall be driven at an oblique angle not to
						  exceed 45 degrees from the vertical or shall be buried in a trench that is at
						  least 2 ½ feet deep. The upper end of the electrode shall be flush with
						  or below ground level unless the aboveground end and the grounding electrode
						  conductor attachment are protected against physical damage.
(Title 24, Part 3, Section
							 250-83(c).)
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING ELECTRODES › Section 2395.84 - Resistance of Made Electrodes

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A single electrode consisting of a rod, pipe, or
							 plate which does not have a resistance to ground of 25 ohms or less shall be
							 augmented by one additional electrode of any of the types specified in Sections
							 2395.82 or
							 2395.83.
(Title 24, Part 3, Section
							 250-84.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING ELECTRODES › Section 2395.86 - Use of Lightning Rods

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Lightning rod conductors and driven pipes, rods, or
							 other made electrodes used for grounding lightning rods shall not be used in
							 lieu of the made grounding electrodes required by Section
							 2395.83 for grounding wiring
							 systems and equipment. This provision shall not prohibit the bonding together
							 of grounding electrodes of different systems.
NOTE: Bonding together of all separate electrodes
							 will limit potential differences between them and between their associated
							 wiring systems.
(Title 24, Part 3, Section
							 250-86.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING CONDUCTORS › Section 2395.91 - Material. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Repealer filed 3-20-79; effective thirtieth day thereafter (Register 79, No.
							 12).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING CONDUCTORS › Section 2395.95 - Size of Equipment Grounding Conductors. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Repealer filed 3-20-79; effective thirtieth day thereafter (Register 79, No.
							 12).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING CONDUCTORS › Section 2395.113 - Connection Devices for Grounding Conductors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Connection devices or fittings that depend on solder
							 shall not be used.
(Title 24, Part 3, Section
							 250-113.)
1. New
							 section filed 3-20-79; effective thirtieth day thereafter (Register 79, No.
							 12).
2. Editorial correction filed 11-2-83 (Register 83, No.
							 45).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING CONDUCTORS › Section 2395.114 - Continuity and Attachment of Branch-Circuit Equipment Grounding Conductors to Boxes

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where more than one equipment grounding conductor of
							 a branch circuit enters a box, all such conductors shall be in good electrical
							 contact with each other and the arrangement shall be such that the
							 disconnection or removal of a receptacle, fixture, or other device fed from the
							 box will not interfere with or interrupt the grounding continuity.
(a) Metal Boxes. A connection shall be made
						  between the one or more equipment grounding conductors and a metal box by means
						  of a grounding screw which shall be used for no other purpose, or an approved
						  grounding device.
(b) Nonmetallic
						  Boxes. One or more equipment grounding conductors brought into a nonmetallic
						  outlet box shall be so arranged that a connection can be made to any fitting or
						  device in that box requiring grounding.
(Title 24, Part 3, Section
							 250-114.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No.
							 45).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING CONDUCTORS › Section 2395.115 - Connection to Electrodes. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Repealer filed 3-20-79; effective thirtieth day thereafter (Register 79, No.
							 12). For history of former section, see Register 75, No.
							 42.
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING CONDUCTORS › Section 2395.117 - Protection of Attachment. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Repealer filed 3-20-79; effective thirtieth day thereafter (Register 79, No.
							 12). For history of former Section, see Register 75, No.
							 42.
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 11 - Grounding › GROUNDING CONDUCTORS › Section 2395.118 - Clean Surfaces. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Repealer filed 3-20-79; effective thirtieth day thereafter (Register 79, No.
							 12). For history of former section, see Register 75, No.
							 42.
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 12 - Wiring Methods, Components, and Equipment for General Use › Section 2400.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The provisions of this Article do not apply to
						  conductors that are an integral part of factory-assembled
						  equipment.
1. New
						  article 12 (sections
						  2400.1-2400.2) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19). For prior history of article 12, see Register 79, No.
						  32.
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 12 - Wiring Methods, Components, and Equipment for General Use › Section 2400.2 - General Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Metal raceways, cable trays, cable armor,
						cable sheath, enclosures, frames, fittings, and other metal noncurrent-carrying
						parts that are to serve as grounding conductors, with or without the use of
						supplementary equipment grounding conductors, shall be effectively bonded where
						necessary to ensure electrical continuity and the capacity to conduct safely
						any fault current likely to be imposed on them. Any nonconductive paint,
						enamel, or similar coating shall be removed at threads, contact points, and
						contact surfaces or be connected by means of fittings designed so as to make
						such removal unnecessary.
(b) Where
						necessary for the reduction of electrical noise (electromagnetic interference)
						of the grounding circuit, an equipment enclosure supplied by a branch circuit
						may be isolated from a raceway containing circuits supplying only that
						equipment by one or more listed nonmetallic raceway fittings located at the
						point of attachment of the raceway to the equipment enclosure. The metal
						raceway shall be supplemented by an internal insulated equipment grounding
						conductor installed to ground the equipment enclosure.
(c) No wiring systems of any type may be
						installed in ducts used to transport dust, loose stock, or flammable vapors. No
						wiring system of any type may be installed in any duct used for vapor removal
						or for ventilation of commercial-type cooking equipment, or in any shaft
						containing only such ducts.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19). For prior history of article 12, see Register 79, No.
						  32.
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 13 - Temporary Wiring › Section 2405.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Except as specifically modified in this Article, all
						  other requirements of this Order for permanent wiring shall also apply to
						  temporary wiring installations.
(a)
						Temporary electrical power and lighting installations of 600 volts, nominal, or
						less may be used only as follows:
(1) During
						and for the period of construction, remodeling, maintenance, repairs, or
						demolition of buildings, structures, equipment or similar activities;
						or
(2) For a period not to exceed
						90 days for work associated with non-permanent work locations, such as
						carnivals, music festivals, Christmas decorative lighting, Christmas tree lots,
						and similar purposes; or
(3) For
						the period of work associated with experimental or developmental work and
						during emergencies.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 13 - Temporary Wiring › Section 2405.2 - General Requirements for Temporary Wiring

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Feeders. The following requirements apply
						to feeders:
(1) Feeders shall originate in an
						approved distribution center.
(2)
						Conductors shall be run as multi-conductor cord or cable assemblies. However,
						if installed as permitted in Section
						2405.1(a)(3), and
						if accessible only to qualified persons, feeders may be run as single insulated
						conductors.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 13 - Temporary Wiring › Section 2405.3 - Temporary Poles

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The minimum size of a temporary wood pole shall be 6
						  inches by 6 inches (nominal) if square, or have a top diameter of at least 5
						  inches if round, and be of sufficient length to maintain all required overhead
						  clearances specified in Section
						  2375.18, but not less than 20 feet
						  long. The lower end shall be embedded not less than 4 feet in the ground. A
						  pole of a material other than wood, if of equivalent strength, may be
						  used.
EXCEPTION: For distribution poles in areas accessible
						  to pedestrians only, a 4-inch x 4-inch (nominal) wood pole, or equivalent
						  (embedded 4 feet in the ground), shall be permitted, provided that a minimum
						  overhead conductor clearance of 10 feet is maintained.
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 14 - Conductors for General Wiring [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 14 (Sections
						2410.1-2410.15, not consecutive)
						filed 8-9-79; effective thirtieth day thereafter (Register 79, No. 32).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 15 - Cable Trays › Section 2418.2 - Wiring Methods

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Only the following wiring methods may be installed in
						  cable tray systems: armored cable; electrical metallic tubing; electrical
						  nonmetallic tubing; fire alarm cables; flexible metal conduit; flexible
						  metallic tubing; instrumentation tray cable; intermediate metal conduit;
						  liquidtight flexible metal conduit; liquidtight flexible nonmetallic conduit;
						  metal-clad cable; mineral-insulated, metal-sheathed cable; multiconductor
						  service-entrance cable; multiconductor underground feeder and branch-circuit
						  cable; multipurpose and communications cables; nonmetallic-sheathed cable;
						  power and control tray cable; power-limited tray cable; optical fiber cables;
						  and other factory-assembled, multiconductor control, signal, or power cables
						  that are specifically approved for installation in cable trays, rigid metal
						  conduit, and rigid nonmetallic conduit.
1. New
						  article 15 (sections
						  2418.2-2418.6) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19). For prior history of article 15, see Register 86, No.
						  37.
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 15 - Cable Trays › Section 2418.3 - Industrial Establishments

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
In industrial establishments where conditions of
						  maintenance and supervision assure that only qualified persons will service the
						  installed cable tray system, the following cables may also be installed in
						  ladder, ventilated-trough, or ventilated-channel cable trays:
(a) Single conductor cable.
(1) Single conductor cable shall be No. 1/0
						or larger and shall be of a type listed and marked on the surface for use in
						cable trays; where Nos. 1/0 through 4/0 single conductor cables are installed
						in ladder cable tray, the maximum allowable rung spacing for the ladder cable
						tray shall be 9 in. (229 mm); where exposed to direct rays of the sun, cables
						shall be identified as being sunlight resistant;
(2) Welding cables installed in dedicated
						cable trays;
(3) Single conductors
						used as equipment grounding conductors; these conductors, which may be
						insulated, covered, or bare, shall be No. 4 or larger; and
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 15 - Cable Trays › Section 2418.4 - Equipment Grounding Conductors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Metallic cable trays may be used as equipment grounding
						  conductors only where continuous maintenance and supervision ensure that
						  qualified persons will service the installed cable tray
						  system.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 15 - Cable Trays › Section 2418.5 - Hazardous (Classified) Locations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Cable trays in hazardous (classified) locations may
						  contain only the cable types permitted in such locations. (See Article
						  59.)
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 15 - Cable Trays › Section 2418.6 - Uses Not Permitted

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Cable tray systems may not be used in hoistways or
						  where subjected to severe physical damage.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 16 - Open Wiring on Insulators › Section 2420.3 - Exposed Wiring, Uses Permitted

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Scope. Open exposed wiring shall not be
						installed in any building or portion of a building except:
(1) In substations, transformer vaults,
						transformer enclosures, on the supply side of electric furnace electrodes, or
						in tunnels or similar locations, where such spaces are restricted to electrical
						use and are accessible to qualified and authorized persons only.
(2) For insulated conductors as permitted in
						Article 13; Temporary Wiring.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 16 - Open Wiring on Insulators › Section 2420.4 - Conductor Supports

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Conductors smaller than No. 8 shall be rigidly supported on noncombustible,
						nonabsorbent insulating materials and may not contact any other objects.
						Supports shall be installed as follows:
(1)
						Within 6 in. (152 mm) from a tap or splice;
(2) Within 12 in. (305 mm) of a dead-end
						connection to a lampholder or receptacle; and
(3) At intervals not exceeding 4.5 ft. (1.37
						m), and at closer intervals sufficient to provide adequate support where likely
						to be disturbed.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 16 - Open Wiring on Insulators › Section 2420.5 - Flexible Nonmetallic Tubing

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
In dry locations, where not exposed to severe physical
						  damage, conductors may be separately enclosed in flexible nonmetallic tubing.
						  The tubing shall be in continuous lengths not exceeding 15 feet (4.57 m) and
						  secured to the surface by straps at intervals not exceeding 4.5 feet (1.37
						  m).
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 16 - Open Wiring on Insulators › Section 2420.6 - Penetrations of Walls, Floors, Wood Cross Members, Etc

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Open conductors shall be separated from contact with
						  walls, floors, wood cross members, or partitions through which they pass by
						  tubes or bushings of noncombustible, nonabsorbent insulating material. If the
						  bushing is shorter than the hole, a waterproof sleeve of nonconductive material
						  shall be inserted in the hole and an insulating bushing slipped into the sleeve
						  at each end in such a manner as to keep the conductors absolutely out of
						  contact with the sleeve. Each conductor shall be carried through a separate
						  tube or sleeve.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 16 - Open Wiring on Insulators › Section 2420.7 - Protection from Physical Damage

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where open conductors cross ceiling joints or wall
						  studs and are exposed to physical damage (for example, located within 7 feet
						  (2.13 m) of the floor), they shall be protected.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 16 - Open Wiring on Insulators › Section 2420.17 - Exposed Wiring. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Renumbering and amendment of Section
						  2420.17 to Section
						  2420.3 filed 8-27-86; effective
						  thirtieth day thereafter (Register 86, No. 37). For prior history, see
						  Registers 83, No. 45 and 81, No. 41.
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 17 - Concealed Knob-and-Tube Wiring [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 17 (Sections
						2424.1-2424.6, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 18 - Mineral-Insulated Metal-Sheathed Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 18 (Sections
						2430.1-2430.4, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 19 - Aluminum-Sheathed Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 19 (Sections
						2431.1-2431.10, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 20 - Copper-Sheathed Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 20 (Sections
						2432.1-2432.10, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 21 - Metal-Clad Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 21 (Sections
						2434.1-2434.6, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 22 - Nonmetallic-Sheathed Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 22 (Sections
						2436.1-2436.3) filed 8-17-81;
						effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 23 - Shielded Nonmetallic-Sheathed Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 23 (Sections
						2437.1-2437.4, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 24 - Service-Entrance Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 24 (Sections
						2438.1-2438.3) filed 8-17-81;
						effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 25 - Underground Feeder and Branch Circuit Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 25 (Sections
						2439.1 and
						2439.3) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 26 - Power and Control Tray Cable [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
NOTE: See General Industry Safety Orders Article 59 for
						regulations applying to woodworking machines.
1.
						Repealer of article 26 (sections
						1680-1682) filed 8-15-86; effective
						thirtieth day thereafter (Register 86, No. 40).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 27 - Nonmetallic Extensions [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 27 (Sections
						2442.1-2442.6, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 28 - Underplaster Extensions [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 28 (Sections
						2444.1 and
						2444.2) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 29 - Intermediate Metal Conduit [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 29 (Sections
						2445.1-2445.4, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 30 - Rigid Metal Conduit [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 30 (Section
						2446.1) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 31 - Rigid Nonmetallic Conduit [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 31 (Sections
						2447.2 and
						2447.3) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 32 - Electrical Metallic Tubing [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 32 (Section
						2448.1) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 33 - Flexible Metal Conduit [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 33 (Sections
						2450.2 and
						2450.5) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 34 - Liquidtight Flexible Metal Conduit [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 34 (Sections
						2451.1-2451.7 not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 35 - Surface Raceways [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 35 (Sections
						2452.1-2452.27, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 36 - Multi-Outlet Assembly [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 36 (Sections
						2453.2 and
						2453.3) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 37 - Underfloor Raceways [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 37 (Sections
						2454.2-2454.7 not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 38 - Cellular Metal Floor Raceways [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 38 (Sections
						2456.1-2456.7, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 39 - Cellular Concrete Floor Raceways [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 39 (Sections
						2458.1 and
						2458.2) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 40 - Wireways [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 40 (Sections
						2462.1 and
						2462.2) filed 8-17-81; effective
						thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 41 - Flat Cable Assemblies [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer of Article 41 (Sections
						2463.1-2463.4, not consecutive)
						filed 8-17-81; effective thirtieth day thereafter (Register 81, No. 34).
Note: Authority and reference cited: Section
						  142.3, Labor
						  Code.