reglab/statecodes huggingface dataset:
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 5 - Inspection › Section 774 - Boilers Exempt from Inspection by Qualified Safety Engineers Employed by the Division

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
					 Boilers annually inspected internally and externally by qualified inspectors
					 employed by a company, city or county, may be exempt from annual inspections by
					 qualified safety engineers employed by the division providing:
(1) Reports of inspection are submitted on
					 prescribed forms to the Division within 21 days after the date of
					 inspection.
(2) The boiler and all
					 of its appurtenances complies with these orders as a minimum standard of
					 safety.
(3) The report of
					 inspection lists all repairs or changes ordered and the qualified inspector
					 notifies the division when such repairs or changes have been satisfactorily
					 completed.
(4) The permit to
					 operate is posted on or near the boiler to which it
					 applies.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 5 - Inspection › Section 775 - Operation of Unsafe Boilers

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) If the operation of any boiler, including
					 those exempt from annual inspection, constitutes a serious menace to the life
					 or safety of any person employed about it, the division or any of its safety
					 engineers, or any person affected thereby, may apply to the superior court of
					 the county in which the boiler is situated for an injunction restraining its
					 operation until the condition has been corrected.
(b) Whenever the condition of a boiler is
					 such as to make it unfit for any pressure, a qualified safety engineer,
					 employed by the division, may affix a rejection mark (o x) consisting of an "X"
					 at least one inch (1") high with a circle at least one-half inch (1/2")
					 diameter located between the upper arms of the "X." The rejection mark shall be
					 outlined in center punch marks and located immediately above the state serial
					 number.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 5 - Inspection › Section 776 - Special Inspection of Lap Seam Boilers

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Horizontal return tubular boilers over
					 thirty-six-inch (36") diameter with longitudinal lap-riveted seams shall not be
					 operated at a pressure in excess of fifty pounds (50 lbs.) per square inch
					 unless all of the following are done every five (5) years of operation:
(1) Sufficient tubes are removed to permit
					 the internal surfaces of the shell to be completely cleaned of scale.
(2) Sufficient brickwork is removed to permit
					 the external surfaces of the longitudinal seam to be cleaned.
(3) Before the tubes and brickwork are
					 replaced the boiler shall be thoroughly inspected internally and externally by
					 a qualified inspector. The tubes shall then be replaced and the boiler shall be
					 subject to a hydrostatic test of one and one-half (1 ½ ) times the
					 working pressure. This pressure shall be maintained for at least thirty (30)
					 minutes after which a qualified inspector shall examine all riveted joints for
					 leakage and/or cracks.
The term five (5) years used in this section shall mean
						five (5) years under steam, but in no case shall the time of service be taken
						as less than six (6) months per calendar year; a hydrostatic test of one and
						one-half (1 ½ ) times the allowed pressure on the boiler shall be made
						in the presence of a qualified inspector at least every five (5) calendar
						years. Each boiler shall be subject to any additional requirements found
						necessary by the qualified inspector.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 5 - Inspection › Section 777 - Boiler and Fired Pressure Vessel Inspection Fees

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
See the Division of Industrial Safety's regulations
						contained in Chapter 3.2, Group 2, Title 8, California Administrative Code. The
						shop inspection fees, permit fees, and inspection fees for boilers and fired
						pressure vessels are reprinted in Appendix 2 of these orders.
1. New
						section filed 3-28-78; effective thirtieth day thereafter (Register 78, No.
						13). For history of former section, see Register 77, No.
						49.
Note: Authority cited: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 5 - Inspection › Section 778 - Field Inspection Fees. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer filed 12-1-77; effective thirtieth day thereafter (Register 77, No.
						49). For prior history, see Register 76, No.
						33.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 5 - Inspection › Section 779 - Certification of Inspectors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Upon the written request of his employer,
					 a certificate of competency may be issued to a person who is employed as
					 provided in subsection (c) following and who obtains a passing grade in the
					 examination prescribed by the division. The prescribed examination may be that
					 of the National Board and shall determine the fitness and competency of any
					 candidate for this certificate. An average of at least seventy percent (70%)
					 shall be required for a passing grade.
(b) An applicant for a certificate of
					 competency shall be at least three (3) years experience in boiler or unfired
					 pressure vessel construction or repair or as an operating engineer in charge of
					 high-pressure boilers or as inspector of steam boilers or unfired pressure
					 vessels.
(1) bachelor of science degree in
					 engineering from an accredited school plus one year experience in design,
					 construction, operation or inspection of high pressure boilers and pressure
					 vessels.
(2) An associate degree in
					 mechanical technology plus two years experience in design, construction,
					 operation or inspection of high pressure boiler and pressure vessels.
(3) A high school education or the equivalent
					 plus three years experience:
(A) in high
					 pressure boiler and high pressure vessel construction or repair, or
(B) in charge of high pressure boiler and
					 pressure vessel operations, or
(C)
					 in the inspection of high pressure boilers and pressure
					 vessels.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 6 - Operation › Section 780 - Permit to Operate

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
					 Except during the time that a request for a permit remains unacted upon, no
					 boiler subject to annual inspection by these orders shall be placed in
					 operation until a permit to operate has been issued and posted on or near the
					 boiler.
(b) Upon the form supplied
					 by the division, a permit to operate shall be issued by the qualified inspector
					 making the inspection. The permit to operate shall indicate the date of
					 inspection, state serial number of the boiler, the pressure allowed at the time
					 of the internal inspection, the name of the inspector, and the name of the
					 inspection agency. No permit shall be issued until the boiler is in compliance
					 with these Safety Orders and satisfactory notice of compliance has been
					 transmitted to the division.
EXCEPTION: The division may issue and renew temporary
						permits not to exceed thirty (30) days each, to permit replacements or repairs
						to be made.
(c) Each permit
					 shall be posted under glass in a conspicuous place on or near the boiler. The
					 permit shall be available to any safety engineer employed by the division. The
					 permit to operate shall expire when a boiler changes both ownership and
					 location.
1.
						Editorial correction restoring inadvertently omitted article heading (Register
						97, No. 25).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 6 - Operation › Section 781 - Attendance on Boilers

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
					 All boilers subject to these orders shall be under the direct supervision of a
					 responsible person. Such person shall be responsible for:
(1) Safe operation of the boiler by a
					 competent attendant.
(2) Proper
					 maintenance of the boiler and its appurtenances.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 6 - Operation › Section 782 - Safe Practices

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The following Safety Orders from Title 8,
					 California Administrative Code are hereby made a part of these orders:
(1) General Industry Safety Order 3228(i):
					 Number of Exits, Boilers Furnace and Incinerator Rooms. See Appendix
					 1.
(2) General Industry Safety
					 Order 3274: Valves and Controls. See Appendix 1.
(3) General Industry Safety Order 3311:
					 Flarebacks. See Appendix 1.
(4)
					 General Industry Safety Order 3312: Entering Combustion Chambers, Flues,
					 Boilers or Unfired Steam Pressure Vessels. See Appendix 1.
(5) General Industry Safety Order 3310:
					 discharge Location. See Appendix 1.
(6) General Industry Safety Order 3514:
					 Tubular Gage Guard. See Appendix 1.
(7) General Industry Safety order 3515: Try
					 Cock Discharge Resceptable. See Appendix 1.
(8) General Industry Safety Order 3516: Steam
					 Gage and Water Gage Glass Location. See Appendix 1.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 783 - Renewals and Replacements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All renewals or replacement boiler drums, shells,
						headers, tubes or appurtenances shall comply with the requirements of the code
						for new construction.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 784 - Approval and Reporting of Repair

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) No repairs to drums, shells, stayed or
					 unstayed surface of a boiler shall be made until the contemplated repairs have
					 been approved by a qualified inspector. (This order shall not prohibit the
					 replacement of tubes, staybolts and/or appurtenances without inspection where
					 replacement is necessitated by normal usage and wear.)
(b) No repairs shall be made to any boiler
					 which has moved from its setting or foundation due to the failure of the boiler
					 or any part thereof until approved by the division.
(c) All repairs by fusion welding or riveting
					 to a damaged boiler or boiler support, where the safety of the boiler is
					 concerned, shall immediately be reported to the division by the qualified
					 inspector who authorized the repair. Complete details with sketches of all
					 repairs, including the identification number of the welder, if welding is used,
					 shall be submitted to the division by the qualified inspector.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 785 - Permissible Welded Patches and Welded Repair of Cracked Plates in Material of Known Weldable Quality

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The following welded repairs are permissible:
(a) Cracks in unstayed shells, drums, or
					 headers of boilers or fired pressure vessels may be repaired by welding
					 provided:
(1) The cracks do not extend between
					 rivet holes in a riveted longitudinal seam.
(2) The crack is not located within six
					 inches (6") of the calking edge of any longitudinal riveted seam.
(3) The total length of any one crack shall
					 not exceed sixteen (16) times the plate thickness or eight inches (8") unless
					 the completed repair is radiographed and stress-relieved.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 786 - Preparation for Welding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
					 All cracks permitted to be repaired by welding shall be chipped or ground to
					 form a clean welding groove with an included angle of not less than sixty
					 degrees (60) and extending to a depth equal to at least the plate thickness
					 less one-sixteenth inch (1/16"). The welding groove shall be extended until the
					 crack has been removed for its entire length. Whenever possible the root of the
					 weld shall be chipped out to clean metal and welded.
(b) Prior to repairing cracks by welding, all
					 tubes, rivets, and threaded staybolts within 6 inches of the crack shall be
					 removed. After welding is completed, such tube, rivet and/or staybolt holes
					 shall be reamed before installing new tubes, rivets, or staybolts. For threaded
					 staybolts the holes shall be tapped and new threaded staybolts installed. If a
					 crack originates or terminates at a welded staybolt, the staybolt shall be
					 removed prior to repairing the crack. After welding is completed, the hole
					 shall be properly prepared for installation of the new staybolt in accordance
					 with paragraph PW-19 of the Code.
1.
						Amendment filed 11-2-66; effective thirtieth day thereafter (Register 66, No.
						38). Approved by State Building Standards
						Commission.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 788 - Repair of Corroded Surfaces

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The following corroded surfaces may be built up by fusion
						welding:
(a) Corroded surfaces in
					 stayed sheets including tube sheets of fire-tube boilers, provided the
					 remaining thickness is at least fifty percent (50%) of the original thickness
					 and further provided the affected areas are not sufficiently extensive to
					 seriously impair the safety of the object; the qualified inspector shall decide
					 when such areas shall be repaired by other means.
(b) Corroded surfaces in plate around
					 handholes or manholes in unstayed sheets within three inches (6") of the
					 opening, provided the remaining thickness is not less than fifty percent (50%)
					 of the original thickness.
(c)
					 Calking edges of girth seams, provided the metal remaining between the rivet
					 and calking edge to be built up is at least fifty percent (50%) of the original
					 thickness and also provided the length of calking edge to be built up does not
					 exceed a length equal to the diameter of the boiler. Before any welding is
					 done, all rivets in the affected area and six inches (6") beyond each portion
					 to be built up shall be removed. After the welded repair has been completed the
					 rivet holes shall be reamed and new rivets driven.
(d) The building up or repair by welding of
					 rivet heads, staybolts, braces, or attachments to braces, or grooved areas is
					 not permitted.
(e) Scattered pits
					 and corrosion in unstayed shells may be built up by welding, provided the
					 largest dimension of such corroded area does not exceed the diameter of an
					 unreinforced opening in paragraph PG-32 of the Code and providing such areas
					 are not so located that they form a ligament in the longitudinal
					 direction.
1.
						Amendment filed 11-2-66; effective thirtieth day thereafter (Register 66, No.
						38). Approved by State Building Standards
						Commission.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 789 - Permissible Repair by Seal Welding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The ends of all tubes, suspension tubes,
					 and nipples of water-tube boilers and superheaters may be seal-welded in
					 accordance with the provisions of paragraph PWT-11 of the Code.
(b) Seal-welding of circumferential joints is
					 permissible, provided the seam is calked first and made tight under hydrostatic
					 pressure equal to the working pressure.
(c) The ends of fire tubes may be seal-welded
					 provided the thickness of the tube is at least seventy-five percent (75%) of
					 its original thickness, and the tubes are first rolled and beaded and found
					 tight under hydrostatic pressure at least equal to the working pressure. The
					 throat of the weld shall not exceed three-sixteenths inch (3/16").
1.
						Amendment filed 11-2-66; effective thirtieth day thereafter (Register 66, No.
						38). Approved by State Building Standards
						Commission.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 790 - Permissible Tube Repair

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
					 All the tubes in a firetube boiler may be retipped, provided the tube wall
					 thickness of the original tube is not less than ninety percent (90%) of the
					 original thickness and the retipped ends are from new material. The new end
					 shall be located in the tube sheet subject to the greatest heat. The
					 circumferential welds in such tubes shall not exceed four (4) in
					 number.
(b) Complete replacement of
					 sections of tubes or pipe in water-tube boilers is permitted, providing the
					 remaining tube is not less than the thickness required for the designed working
					 pressure and the requirements of paragraph PW-41 of the Code are complied
					 with.
(c) Bulges in tubes of
					 water-tube boilers may be repaired when:
(1)
					 The maximum dimension of the repaired area does not exceed the diameter of the
					 tube or two inches (2") whichever is the least.
(2) There are not more than three (3) such
					 repairs in any one (1) tube.
(3)
					 The tube wall adjacent to the bulge is not less than the thickness required for
					 the designed working pressure.
(4)
					 The requirements of paragraph PW-41 of the Code are complied
					 with.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 793 - Qualification of Welding Procedures and Operators

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No welded repair shall be made to any boiler or boiler
						appurtenance until the welding procedure and operator have been qualified in
						accordance with Section IX of the code in the overhead and horizontal
						positions. The certificate of competency number of the qualified inspector
						authorizing the repair shall be stamped adjacent to all welded repairs made to
						power boilers.
On welded repairs that are completely radiographed the
						operator qualification may be eliminated at the discretion of the division
						provided the welding procedure is properly qualified inspector indicates on his
						report the welding procedure used and the operator employed in making the
						repair.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 795 - Installation of Riveted Patches

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The following procedure shall be followed
					 when installing riveted patches:
(1)
					 Distorted sheets which require patching shall first be set back straight as
					 nearly as possible before proceeding with the cutting out of the plate so that
					 the patch may be kept as small as possible.
(2) All defective or deteriorated material
					 shall be removed and properly trimmed to provide for caulking and neat
					 workmanship in attaching the patch.
(3) The edges of a patch shall be beveled for
					 calking by planing, chipping, or gas cutting before applying it to the boiler.
					 Rivets should be driven by gun, if at all possible.
(4) All rivet holes shall be drilled full
					 size or the holes may be punched not to exceed one-fourth inch (1/4") less than
					 full size for plates over five-sixteenths inch (5/16"), and one-eighth inch
					 (1/8") less than full size for plates five-sixteenths inch (5/16") or less in
					 thickness, and then reamed to full size with patch in place. Rivet holes shall
					 be not more than one-sixteenth inch (1/16") greater in diameter than the
					 nominal diameter of the rivet.
(5)
					 Seal welding of the patch plate is permissible if a single bead is used with a
					 throat thickness not more than three-sixteenths inch (3/16"). The patch shall
					 be tight under a hydrostatic test pressure equal to the operating pressure
					 before seal welding. Rivets and patch bolts shall not be seal welded.
(6) When three (3) plates are lapped at the
					 corners of a patch, the middle plate shall be scarfed carefully to a feather
					 edge the entire width of the lap as shown in Figure 1.
(7) Upon the completion of repairs, a
					 hydrostatic test of one hundred fifty percent (150%) of the maximum allowable
					 operating pressure shall be applied. All seams shall be tight at this
					 pressure.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 2 - Boiler and Fired Pressure Vessel Safety Orders › Article 7 - Repairs › Section 796 - Riveted Patch Seam Calculations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Riveted patch seams are calculated as
					 follows:
(1) Determine the length, L, of the
					 patch from the area of the defect to be repaired (Figures 1, 2, 3, and 4). The
					 normal efficiency, e, of the single-riveted seam that is to be used in the
					 patch should then be determined from Table 1. This is governed by the thickness
					 of plate and diameter of rivet holes.
Table 1
EFFICIENCIES OF SINGLE-RIVETED
								  SEAMS
Plate Thickness,
								t
Rivet Hole Diameter,
								d
Pitch of Rivet,
								p
Efficiency of Seam, e
¼
11/16
1 7/8
63.6
9/32
¾
1 7/8
60.3
5/16
¾
1 7/8
60.0
11/32
13/16
1 
								15/16
58.0
3/8
13/16
1 
								15/16
57.0
13/32
7/8
2 
								1/16
57.5
7/16
15/16
2 ¼
56.0
15/32
15/16
2 1/8
55.5
½
1
2 ¼
55.7
9/16
1 
								1/16
2 3/8
53.0
19/32
1 
								1/16
2 ¼
52.8
5/8
1 
								1/16
2 ¼
50.5
21/32
1 1/8
2 
								5/16
51.4
11/16
1 1/8
2 
								5/16
51.4
Tensile strength assumed at 55,000 psi
								and shearing strength at 44,000 psi.
After determining the length, L, of a patch, determine
						its width girthwise, W. This is found by multiplying the length by the
						constant, C, as shown in Table 2 or 3, depending upon the type of boiler to be
						repaired. These tables give a constant, C, for a given efficiency, e, of patch
						and efficiency, E, of the longitudinal seam.
(2) To determine the longitudinal efficiency
					 of an existing patch, the length, L, and width, W, the pitch, P, and the
					 diameter, d, of rivet, should be measured. "W" divided by "L" will give the
					 constant, C. Table 1 will give "e." Then under "e" in Table 2 or 3, depending
					 upon the type of boiler to be repaired, find the constant, C. Whatever "E" is
					 in the first column is the longitudinal or allowed efficiency of the patch
					 seam.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 1 - Application [Repealed] › Section 1200 - Application of Orders. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Amended
						Subchapter 3 (Sections
						1200-1202,
						1204,
						1205,
						1210,
						1215-1217,
						1220,
						1225,
						1230,
						1240,
						1250,
						1270,
						1280 and Appendices A and B) filed
						7-18-66; effective thirtieth day thereafter (Register 66, No. 23). For former
						Subchapter 3, see Registers 3 and 55, No. 13.
2. Amendment filed
						7-6-79 as procedural and organizational; effective upon filing (Register 79,
						No. 27).
3. Amendment filed 8-7-85; effective thirtieth day
						thereafter (Register 85, No. 32).
4. Repealer of subchapter 3
						(articles 1-12, sections
						1200-1280), article 1 (section
						1200) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 1 - Application [Repealed] › Section 1201 - Permits for Variation from these Orders. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 1 - Application [Repealed] › Section 1202 - Posting of Application. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 2 - Definitions [Repealed] › Section 1204 - Definitions. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer of article 2 (section
						1204) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 3 - General Provisions [Repealed] › Section 1205 - General Provisions. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Amendment of subsection (b) filed 11-1-99; operative 12-1-99
						(Register 99, No. 45).
3. Repealer of article 3 (section
						1205) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 4 - Compression [Repealed] › Section 1210 - Compression Rate. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Amendment designating first paragraph as subsection (a) and
						new subsection (b) filed 11-1-99; operative 12-1-99 (Register 99, No.
						45).
3. Repealer of article 4 (section
						1210) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 5 - Decompression [Repealed] › Section 1215 - Normal Condition. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 8, No.
						32).
2. Repealer of article 5 (sections
						1215-1217) and section filed
						4-4-2006; operative 5-4-2006 (Register 2006, No.
						14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 5 - Decompression [Repealed] › Section 1216 - Repetitive Exposures. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
						NOTE filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer filed 4-4-2006; operative 5-4-2006 (Register 2006,
						No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 5 - Decompression [Repealed] › Section 1217 - Decanting. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer filed 4-4-2006; operative 5-4-2006 (Register 2006,
						No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 6 - Air Locks and Special Decompression Chamber [Repealed] › Section 1220 - Air Locks. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Amendment of subsections (c) and (g) and new subsection (p)
						filed 11-1-99; operative 12-1-99 (Register 99, No. 45).
3. Repealer
						of article 6 (sections
						1220-1225) and section filed
						4-4-2006; operative 5-4-2006 (Register 2006, No.
						14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 6 - Air Locks and Special Decompression Chamber [Repealed] › Section 1225 - Special Decompression Chamber. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer filed 4-4-2006; operative 5-4-2006 (Register 2006,
						No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 7 - Temperature, Illumination, Sanitation and Ventilation [Repealed] › Section 1230 - Temperature, Illumination, Sanitation and Ventilation. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Amendment of subsections (b) and (d) and new subsections (g)
						and (h) filed 11-1-99; operative 12-1-99 (Register 99, No. 45).
3.
						Change without regulatory effect amending subsection (e) filed 12-30-99
						pursuant to section
						100, title 1, California Code of
						Regulations (Register 99, No. 53).
4. Repealer of article 7 (section
						1230) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 8 - Compressor Plant, Air Supply, and Telephone Communication [Repealed] › Section 1240 - Compressor Plant, Air Supply and Telephone Communication. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer of article 8 (section
						1240) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 9 - Bulkheads and Screens [Repealed] › Section 1250 - Bulkheads and Screens. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer of article 9 (section
						1250) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 10 - Fire Prevention [Repealed] › Section 1270 - Fire Prevention. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer of article 10 (section
						1270) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 11 - Medical Attendance, Examination, and Regulations [Repealed] › Section 1280 - Medical Control. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment filed 8-7-85; effective thirtieth day thereafter (Register 85, No.
						32).
2. Repealer of article 11 (section
						1280) and section filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 12 - Suggestions for the Guidance of Compressed Air Workers [Repealed] › Appendix A

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment of Appendix A filed 8-7-85; effective thirtieth day thereafter
						(Register 85, No. 32).
2. Repealer of article 12 (Appendices A and
						B) and Appendix A filed 4-4-2006; operative 5-4-2006 (Register 2006, No. 14).
						For prior history of article 12, see Register 85, No.
						32).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 3 - Compressed Air Safety Orders (Governing Work in Compressed Air) [Repealed] › Article 12 - Suggestions for the Guidance of Compressed Air Workers [Repealed] › Appendix B

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Amendment of Appendix B filed 8-7-85; effective thirtieth day thereafter
						(Register 85, No. 32).
2. Repealer of Appendix B filed 4-4-2006;
						operative 5-4-2006 (Register 2006, No. 14).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 4 - Construction Safety Orders › Article 1 - Introduction › Section 1500 - Title. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Construction Safety Orders (§§
												1501 through
						1756) originally printed 4-20-45
						(Title 8).
2. Repealer and New Construction Safety Orders
						(Subchapter 4, §§
												1500 through
						1733) filed 8-29-57; effective
						thirtieth day thereafter (Register 57, No. 14). (For prior amendments, see
						Registers 3, 5, 9, and 14, No. 8).
3. Repealer of Subchapter 4 and
						new Subchapter 4 (§§
												1500 through
						1768) filed 7-9-65; effective
						thirtieth day thereafter (Register 65, No. 12).
4. Repealer of and
						new Introduction to Article 1 filed 4-27-79; effective thirtieth day thereafter
						(Register 79, No. 17).
5. Repealer of Preamble to Article 1 and
						Section 1500 filed 8-13-84; effective
						thirtieth day thereafter (Register 84, No. 33).
Note: Authority cited: Sections
						  142.3,
						  6312,
						  6500 and
						  6502, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 4 - Construction Safety Orders › Article 1 - Introduction › Section 1501 - Superseded Orders. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						Repealer filed 8-13-84; effective thirtieth day thereafter (Register 84, No.
						33).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 4 - Construction Safety Orders › Article 1 - Introduction › Section 1502 - Application

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) These Orders
					 establish minimum safety standards whenever employment exists in connection
					 with the construction, alteration, painting, repairing, construction
					 maintenance, renovation, removal, or wrecking of any fixed structure or its
					 parts. These Orders also apply to all excavations not covered by other safety
					 orders for a specific industry or operation.
(b) At construction projects, these Orders
					 take precedence over any other general orders that are inconsistent with them,
					 except for Tunnel Safety Orders or the Pressurized Worksite Standards in
					 Article 154 of the General Industry Safety Orders.
(c) Machines, equipment, processes, and
					 operations not specifically covered by these Orders shall be governed by other
					 applicable general Safety Orders.
1.
						Amendment of subsection (a) filed 7-6-79 as procedural and organizational;
						effective upon filing (Register 79, No. 27).
2. Amendment of
						subsection (a) filed 8-13-84; effective thirtieth day thereafter (Register 84,
						No. 33).
3. Change without regulatory effect amending subsection (b)
						filed 9-1-2010 pursuant to section
						100, title 1, California Code of
						Regulations (Register 2010, No. 36).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 4 - Construction Safety Orders › Article 1 - Introduction › Section 1502.1 - OSHA Standards. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
						section filed 2-14-73; effective thirtieth day thereafter (Register 73, No.
						7).
2. Repealer filed 8-13-84; effective thirtieth day thereafter
						(Register 84, No. 33).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 4 - Construction Safety Orders › Article 1 - Introduction › Section 1503 - Permits for Excavations, Trenches, Construction, (Building Structure, Scaffolding or Falsework), and Demolition. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
NOTE: Permit requirements of the Division of Occupational
						Safety and Health are contained in Chapter 3.2, Group 2, Title 8,
						CAC.
1. New
						section filed 4-30-75 as an emergency; effective upon filing (Register 75, No.
						18). For history of former section, see Register 75, No. 8.
2.
						Certificate of Compliance filed 6-20-75 (Register 75, No. 25).
3.
						Repealer and new section filed 5-12-83; effective thirtieth day thereafter
						(Register 83, No. 20).
Note: Authority cited: Section
						  142.3, Labor
						  Code. Reference: Section
						  142.3, Labor
						  Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 4 - Construction Safety Orders › Article 2 - Definitions › Section 1505 - Approvals

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Approvals.
(1) When the term "approved" is used in these
					 orders, it shall refer to products, materials, devices, systems, or
					 installations that have been approved, listed, labeled, or certified as
					 conforming to applicable governmental or other nationally recognized standards,
					 or applicable scientific principles. The approval, listing, labeling, or
					 certification of conformity, shall be based upon an evaluation performed by a
					 person, firm, or entity with appropriate registered engineering competence or
					 by a person, firm, or entity, independent of the manufacturer or supplier of
					 the product, with demonstrated competence in the field of such evaluation.
EXCEPTION: Where written approval by the Division is
						required in these orders.
(2) The term "approved" shall also refer to
					 products, materials, devices, systems, or installations that have been
					 approved, listed, labeled, or certified by a Nationally Recognized Testing
					 Laboratory (NRTL).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 4 - Construction Safety Orders › Article 3 - General › Section 1508 - Permits. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
						section filed 81-74 as an emergency; effective upon filing (Register 74, No.
						31).
2. Certificate of Compliance filed 11-22-74 (Register 74, No.
						48).
3. Certificate of Compliance refiled 11-27-74 (Register 74, No.
						48).
4. Repealer and new section filed 11-29-74; effective thirtieth
						day thereafter (Register 74, No. 48).
5. Repealer filed 9-27-85;
						effective thirtieth day thereafter (Register 85, No. 40).
6.
						Editorial correction of HISTORY 5 (Register 2010, No.
						50).
Note: Authority cited: Section
						  142.3, Labor
						  Code.