reglab/statecodes huggingface dataset:
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74.1 - Elevators, Dumbwaiters, Escalators, Moving Walks, Wheelchair Lifts, and Stairway Chair Lifts › Section 2562.3 - Identification and Signs

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
For installations built on or after May 5, 2008:
(a) Where there is more than one driving
						machine in a machine room, the disconnecting means shall be numbered to
						correspond to the identifying number of the driving machine that they
						control.
(b) The disconnecting
						means shall be provided with a sign to identify the location of the supply-side
						overcurrent protective device.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74.1 - Elevators, Dumbwaiters, Escalators, Moving Walks, Wheelchair Lifts, and Stairway Chair Lifts › Section 2562.4 - Single-Car and Multicar Installations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
For installations built on or after May 5, 2008 on
						  single-car and multicar installations, equipment receiving electrical power
						  from more than one source shall be provided with a disconnecting means for each
						  source of electrical power. The disconnecting means shall be within sight of
						  the equipment served.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74.1 - Elevators, Dumbwaiters, Escalators, Moving Walks, Wheelchair Lifts, and Stairway Chair Lifts › Section 2562.5 - Warning Sign for Multiple Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A warning sign shall be mounted on or next to the
						  disconnecting means where multiple disconnecting means are used and parts of
						  the controllers remain energized from a source other than the one disconnected.
						  The sign shall be clearly legible and shall read: "WARNING--PARTS OF THE
						  CONTROLLER ARE NOT DEENERGIZED BY THIS SWITCH."
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74.1 - Elevators, Dumbwaiters, Escalators, Moving Walks, Wheelchair Lifts, and Stairway Chair Lifts › Section 2562.6 - Interconnection Between Multicar Controllers

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A warning sign worded as required in Section
						  2562.5 shall be mounted on or next
						  to the disconnecting means where interconnections between controllers are
						  necessary for the operation of the system on multicar installations that remain
						  energized from a source other than the one disconnected.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74.1 - Elevators, Dumbwaiters, Escalators, Moving Walks, Wheelchair Lifts, and Stairway Chair Lifts › Section 2562.7 - Motor Controllers

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Motor controllers may be located outside the spaces
						  otherwise required by this Article, provided they are in enclosures with doors
						  or removable panels capable of being locked closed and the disconnecting means
						  is located adjacent to or is an integral part of the motor controller. Motor
						  controller enclosures for escalators or moving walks may be located in the
						  balustrade on the side located away from the moving steps or moving treadway.
						  If the disconnecting means is an integral part of the motor controller, it
						  shall be operable without opening the enclosure.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 75 - Electric Welders › Section 2563.22 - Overcurrent Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Overcurrent protection for motor generator arc welders
						  shall be as provided in (a) below. Where the nearest standard rating of the
						  overcurrent device used is under the value specified in this Section, or where
						  the rating or setting specified results in unnecessary opening of the
						  overcurrent device, the next higher rating or setting shall be
						  permitted.
(a) Each welder shall have
						overcurrent protection rated or set at not more than 200 percent of the rated
						primary current of the welder.
EXCEPTION: An overcurrent device shall not be required
						  for a welder having supply conductors protected by an overcurrent device rated
						  or set at not more than 200 percent of the rated primary current of the
						  welder.
(Title 24, Part 3, Section
						  630-22.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of subsection (a) filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 75 - Electric Welders › Section 2563.23 - Disconnecting Means-ARC Welders

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A disconnecting means shall be provided
						in the supply circuit for each arc welder that is not equipped with a
						disconnect mounted as an integral part of the welder. The disconnecting means
						shall be a switch or circuit breaker, and its rating shall not be less than
						that necessary to accommodate overcurrent protection.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Repealer and new section filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37).
3. Amendment of section and NOTE filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 75 - Electric Welders › Section 2563.33 - Disconnecting Means-Resistance Welders

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A switch or circuit breaker shall be
						provided by which each resistance welder and its control equipment can be
						disconnected from the supply circuit. The ampere rating of this disconnecting
						means may not be less than the supply conductor ampacity. The supply circuit
						switch may be used as the welder disconnecting means where the circuit supplies
						only one welder.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Repealer and new section filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37).
3. Amendment of section and NOTE filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 76 - Sound Recording and Similar Equipment › Section 2564.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article covers equipment and wiring for sound
						  recording and reproduction, centralized distribution of sound, public address,
						  speech-input systems, and electronic organs.
(Title 24, Part 3, Section
						  640-1.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment deleting subsection (a) designation only filed 8-27-86; effective
						  thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 76 - Sound Recording and Similar Equipment › Section 2564.6 - Grouping of Conductors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Conductors of different systems grouped in the same
						  conduit or other metal enclosure or in portable cords or cables shall comply
						  with (a) through (c) below.
(a)
						Power-Supply Conductors. Power-supply conductors shall be properly identified
						and shall be used solely for supplying power to the equipment to which the
						other conductors are connected.
(b)
						Leads to Motor Generator or Rotary Converter. Input leads to a motor generator
						or rotary converter shall be run separately from the output leads.
(c) Conductor Insulation. The conductors
						shall be insulated individually, or collectively in groups, by insulation at
						least equivalent to that on the power supply and other conductors.
EXCEPTION: Where the power supply and other conductors
						  are separated by a lead sheath or other continuous metallic covering.
(Title 24, Part 3, Section
						  640-6.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77 - Information Technology Equipment › Section 2565.1 - Disconnecting Means. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
						  section filed 2-1-83; effective thirtieth day thereafter (Register 83, No.
						  6).
2. Editorial correction of NOTE filed 11-2-83 (Register 83, No.
						  45).
3. Repealer filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37).
4. Amendment of article heading filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77 - Information Technology Equipment › Section 2565.2 - Supply Circuits and Interconnecting Cables

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Branch-Circuit Conductors. The
						branch-circuit conductors to which one or more units of a data processing
						system are connected to a source of supply shall have an ampacity not less than
						125 percent of the total connected load.
(b) Connecting Cables. The data processing
						system shall be permitted to be connected by means of computer or data
						processing cable or flexible cord and an attachment plug cap or cord-set
						assembly specifically approved as a part of the data processing system.
						Separate units shall be permitted to be interconnected by means of flexible
						cords and cables specifically approved as part of the data processing system.
						When run on the surface of the floor, they shall be protected against physical
						damage.
(c) Under Raised Floors.
						Power cables, communications cables and interconnecting cables associated with
						the data processing equipment shall be permitted under a raised floor provided:
(1) The raised floor is of suitable
						construction.
(2) The
						branch-circuit supply conductors to receptacles are in rigid metal conduit,
						intermediate metal conduit, electrical metallic tubing, metal wireway, metal
						surface raceway with metal cover, flexible metal conduit, liquidtight flexible
						metal conduit, mineral-insulated, metal-sheathed cable, metal-clad cable, or
						Type AC cable.
(3) Ventilation in
						the underfloor area is used for the data processing equipment and data
						processing area only.
(Title 24, Part 3, Section
						  645.2.)
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77 - Information Technology Equipment › Section 2565.3 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A
						disconnecting means shall be provided to disconnect the power to all electronic
						equipment in an information technology equipment room. There shall also be a
						similar means to disconnect the power to all dedicated heating, ventilating and
						air conditioning (HVAC) systems serving the room and to cause all required
						fire/smoke dampers to close.
EXCEPTION: Integrated electrical systems covered by
						  Article 89 need not have the disconnecting means required by this
						  section.
(b) Grouping. The
						control for these disconnecting means shall be grouped and identified and shall
						be readily accessible at the principal exit doors. A single means to control
						both the electronic equipment and HVAC system is permitted.
1. New
						  section filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
2. Amendment of section and NOTE filed 5-5-2008; operative
						  5-5-2008. Submitted to OAL for printing only pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77.1 - X-Ray Equipment › Section 2566.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article applies to X-ray
						  equipment.
1. New
						  article 77.1 (sections
						  2566.1-2566.3) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77.1 - X-Ray Equipment › Section 2566.2 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A
						disconnecting means shall be provided in the supply circuit. The disconnecting
						means shall be operable from a location readily accessible from the X-ray
						control. For equipment connected to a 120-volt branch circuit of 30 amperes or
						less, a grounding-type attachment plug cap and receptacle of proper rating may
						serve as a disconnecting means.
(b)
						If more than one piece of equipment is operated from the same high-voltage
						circuit, each piece or each group of equipment as a unit shall be provided with
						a high-voltage switch or equivalent disconnecting means. The disconnecting
						means shall be constructed, enclosed, or located so as to avoid contact by
						employees with its live parts.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77.1 - X-Ray Equipment › Section 2566.3 - Control

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The following requirements apply to industrial and
						  commercial laboratory equipment.
(a)
						Radiographic and fluoroscopic-type equipment shall be effectively enclosed or
						shall have interlocks that deenergize the equipment automatically to prevent
						ready access to live current-carrying parts.
(b) Diffraction- and irradiation-type
						equipment shall have a pilot light, readable meter deflection, or equivalent
						means to indicate when the equipment is energized, unless the equipment or
						installation is effectively enclosed or is provided with interlocks to prevent
						access to live current-carrying parts during operation.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77.2 - Induction and Dielectric Heating Equipment › Section 2567.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article applies to induction and dielectric
						  heating equipment and accessories for industrial and scientific applications,
						  but not for medical or dental applications or for appliances.
1. New
						  article 77.2 (sections
						  2567.1-2567.3) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77.2 - Induction and Dielectric Heating Equipment › Section 2567.2 - Guarding and Grounding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The converting apparatus (including the
						dc line) and high-frequency electric circuits (excluding the output circuits
						and remote-control circuits) shall be completely contained within enclosures of
						noncombustible material.
(b) All
						panel controls shall be of dead-front construction.
(c) Doors or detachable panels shall be
						employed for internal access. Where doors are used giving access to voltages
						from 500 to 600 volts ac or dc, either door locks shall be provided or
						interlocks shall be installed. Detachable panels not normally used for access
						to such parts shall be fastened in a manner that will make them difficult to
						remove (for example, by requiring the use of tools).
(d) Warning labels or signs that read
						"DANGER--HIGH VOLTAGE--KEEP OUT" shall be attached to the equipment and shall
						be plainly visible where persons might contact energized parts when doors are
						opened or closed or when panels are removed from compartments containing over
						250 volts ac or dc.
(e) Induction
						and dielectric heating equipment shall be protected as follows:
(1) Protective cages or adequate shielding
						shall be used to guard work applicators other than induction heating
						coils.
(2) Induction heating coils
						shall be protected by insulation or refractory materials or both.
(3) Interlock switches shall be used on all
						hinged access doors, sliding panels, or other such means of access to the
						applicator, unless the applicator is an induction heating coil at dc ground
						potential or operating at less than 150 volts ac.
(4) Interlock switches shall be connected in
						such a manner as to remove all power from the applicator when any one of the
						access doors or panels is open.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 77.2 - Induction and Dielectric Heating Equipment › Section 2567.3 - Remote Control

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						If remote controls are used for applying power, a selector switch shall be
						provided and interlocked to provide power from only one control point at a
						time.
(b) Switches operated by foot
						pressure shall be provided with a shield over the contact button to avoid
						accidental closing of the switch.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 78 - Electrically Driven or Controlled Irrigation Machines › GENERAL › Section 2568.2 - Definitions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Irrigation Machines. An irrigation machine is an
							 electrically driven or controlled machine, with one or more motors, not hand
							 portable, and used primarily to transport and distribute water for agricultural
							 purposes.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 78 - Electrically Driven or Controlled Irrigation Machines › GENERAL › Section 2568.4 - Irrigation Cable

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						  Supports. Irrigation cable shall be secured by approved straps, hangers or
						  similar fittings so designed and installed as not to injure the cable. Cable
						  shall be supported at intervals not exceeding 4 feet.
(b) Fittings. Fittings shall be used at all
						  points where irrigation cable terminates. The fittings shall be designed for
						  use with the cable and shall be suitable for the conditions of
						  service.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment of subsection (b) filed 8-27-86; effective thirtieth day thereafter
							 (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 78 - Electrically Driven or Controlled Irrigation Machines › GENERAL › Section 2568.8 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						  The main disconnecting means for a center pivot irrigation machine shall be
						  located at the point of connection of electrical power to the machine or shall
						  be visible and not more than 50 feet (15.2 m) from the machine.
(b) The disconnecting means shall be readily
						  accessible and capable of being locked in the open position.
(c) A disconnecting means shall be provided
						  for each motor and controller.
1.
							 Renumbering and amendment of former Section
							 2568.8 to Section
							 2568.12, and new Section
							 2568.8 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37). For prior history, see Register
							 83, No. 45.
2. Amendment of section and NOTE filed 5-5-2008;
							 operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 78 - Electrically Driven or Controlled Irrigation Machines › GENERAL › Section 2568.12 - Grounding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The following equipment shall be grounded:
(a) All electrical equipment on the
						  irrigation machine.
(b) All
						  electrical equipment associated with the irrigation machine.
(c) Metallic junction boxes and
						  enclosures.
(d) Control panels or
						  control equipment that supply or control electrical equipment to the irrigation
						  machine.
EXCEPTION: Grounding shall not be required on
							 machines where all of the following provisions are met:
(1) The machine is electrically controlled
						  but not electrically driven.
(2)
						  The control voltage is 30 volts or less.
(3) The control or signal circuits are
						  current limited.
(Title 24, Part 3, Section
							 675-12.)
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 78 - Electrically Driven or Controlled Irrigation Machines › GENERAL › Section 2568.15 - Lightning Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
If an irrigation machine has a stationary point, a
							 grounding electrode system shall be connected to the machine at the stationary
							 point for lightning protection.
1. New
							 section filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
2. Amendment of section and NOTE filed 5-5-2008; operative
							 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 78 - Electrically Driven or Controlled Irrigation Machines › GENERAL › Section 2568.16 - Energy from More Than One Source

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Equipment within an enclosure receiving electrical
							 energy from more than one source shall not be required to have a disconnecting
							 means for the additional source, provided that its voltage is 30 volts or
							 less.
(Title 24, Part 3, Section
							 675-16).
1.
							 Renumbering and amendment of former Section
							 2568.12 to Section
							 2568.16 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 78 - Electrically Driven or Controlled Irrigation Machines › GENERAL › Section 2568.23 - Disconnecting Means. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Repealer filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › GENERAL › Section 2569.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The provisions of this Article apply to electric
							 wiring for and equipment in or adjacent to all swimming, wading, therapeutic,
							 and decorative pools and fountains, and hydro-massage bathtubs, whether
							 permanently installed or storable, and to metallic auxiliary equipment, such as
							 pumps, filters, and similar equipment. Therapeutic pools in health care
							 facilities are exempt from these provisions.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Repealer and new section filed 8-27-86; effective thirtieth day thereafter
							 (Register 86, No. 37).
3. Amendment of section and NOTE filed
							 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
							 Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › GENERAL › Section 2569.5 - Receptacles

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Receptacles. A
						  single receptacle of the locking and grounding type that provides power for a
						  permanently installed swimming pool recirculating pump motor may be located not
						  less than 5 feet (1.52 m) from the inside walls of a pool. All other
						  receptacles on the property shall be located at least 10 feet (3.05 m) from the
						  inside walls of a pool.
(b)
						  Receptacles which are located within 15 feet (4.57 m) or 20 feet (6.08 m) if
						  the installation was built after May 5, 2008, of the inside walls of the pool
						  shall be protected by ground-fault circuit interrupters.
(c) For installations built on or after May
						  5, 2008 where a pool is installed permanently at a dwelling unit, at least one
						  125-volt, 15- or 20-ampere receptacle on a general-purpose branch circuit shall
						  be located a minimum of 10 feet (3.05 m) and not more than 20 feet (6.08 m)
						  from the inside wall of the pool. This receptacle shall be located not more
						  than 6.5 feet (1.98 m) above the floor, platform, or grade level serving the
						  pool.
NOTE: In determining these dimensions, the distance
							 to be measured is the shortest path the supply cord of an appliance connected
							 to the receptacle would follow without piercing a floor, wall, or ceiling of a
							 building or other effective permanent barrier.
1. New
							 section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
							 pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › GENERAL › Section 2569.6 - Lighting Fixtures, Lighting Outlets, and Ceiling Suspended (Paddle) Fans

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) In outdoor pool
						  areas, lighting fixtures, lighting outlets, and ceiling-suspended (paddle) fans
						  may not be installed over the pool or over the area extending 5 feet (1.52 m)
						  horizontally from the inside walls of a pool unless no part of the lighting
						  fixture of a ceiling-suspended (paddle) fan is less than 12 feet (3.66 m) above
						  the maximum water level. However, a lighting fixture or lighting outlet that
						  was installed before April 16, 1981, may be located less than 5 feet (1.52 m)
						  measured horizontally from the inside walls of a pool if it is at least 5 feet
						  (1.52 m) above the surface of the maximum water level and is rigidly attached
						  to the existing structure. It shall also be protected by a ground-fault circuit
						  interrupter installed in the branch circuit supplying the fixture.
(b) Lighting fixtures and lighting outlets
						  installed in the area extending between 5 feet (1.52 m) and 10 feet (3.05 m)
						  horizontally from the inside walls of a pool shall be protected by a
						  ground-fault circuit interrupter unless installed 5 feet (1.52 m) above the
						  maximum water level and rigidly attached to the structure adjacent to or
						  enclosing the pool.
1. New
							 section filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
2. Amendment of section heading, repealer and new section and
							 amendment of NOTE filed 5-5-2008; operative 5-5-2008. Submitted to OAL for
							 printing only pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › GENERAL › Section 2569.7 - Cord- and Plug-Connected Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Flexible cords used with the following
						  equipment may not exceed 3 feet (0.9 m) in length and shall have a copper
						  equipment grounding conductor with a grounding-type attachment plug.
(1) Cord- and plug-connected lighting
						  fixtures installed within 16 feet (4.88 m) of the water surface of permanently
						  installed pools.
(2) Other cord-
						  and plug-connected, fixed or stationary equipment used with permanently
						  installed pools.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › PERMANENTLY INSTALLED POOLS › Section 2569.20 - Underwater Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A ground-fault circuit interrupter shall
						  be installed in the branch circuit supplying underwater fixtures operating at
						  more than 15 volts. Equipment installed underwater shall be identified for the
						  purpose.
(b) No underwater lighting
						  fixtures may be installed for operation at over 150 volts between
						  conductors.
(c) A lighting fixture
						  facing upward shall have the lens adequately guarded to prevent contact by any
						  person.
1. New
							 section filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
2. Amendment of section heading, section and NOTE filed
							 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
							 Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › STORABLE POOLS › Section 2569.30 - Pumps

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A cord-connected swimming pool filter pump shall
							 incorporate an approved system of double insulation or its equivalent, and
							 shall be provided with means of grounding only the internal and nonaccessible
							 noncurrent-carrying metal parts of the appliance.
The means for grounding shall be an equipment
							 grounding conductor run with the power-supply conductors in the flexible cord
							 that is properly terminated in a grounding-type attachment plug having a fixed
							 grounding contact member.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › STORABLE POOLS › Section 2569.31 - Ground-Fault Circuit Interrupters Required

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All electric equipment, including power-supply cords,
							 used with storable swimming pools shall be protected by ground-fault circuit
							 interrupters. (Title 24, Part 3, Section
							 680-31.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 79 - Swimming Pools, Fountains and Similar Installations › FOUNTAINS › Section 2569.51 - Fountains

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All electric equipment, including power supply cords,
							 operating at more than 15 volts, and used with fountains shall be protected by
							 ground-fault circuit interrupters.
1. New
							 section filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
2. Amendment of section heading, section and NOTE filed
							 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
							 Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The provisions for emergency power systems apply to
						  circuits, systems, and equipment intended to supply power for illumination and
						  special loads, in the event of failure of the normal supply.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Repealer and new section filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37).
3. Amendment of article heading, section and
						  NOTE filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.4 - Tests and Maintenance

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Systems shall be tested periodically on a
						schedule acceptable to the authority having jurisdiction to assure their
						maintenance in proper operating condition.
(b) Where battery systems or unit equipments
						are involved, including batteries used for starting or ignition in auxiliary
						engines, the authority having jurisdiction shall require periodic
						maintenance.
(c) A written record
						shall be kept of such tests and maintenance.
(d) Means for testing all emergency lighting
						and power systems during maximum anticipated load conditions shall be
						provided.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of subsection (d) filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.9 - Wiring Methods

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Emergency circuit wiring shall be kept entirely
						  independent of all other wiring and equipment and may not enter the same
						  raceway, cable, box, or cabinet or other wiring except either where common
						  circuit elements suitable for the purpose are required, or for transferring
						  power from the normal to the emergency source.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.14 - Emergency Illumination. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Repealer filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.