reglab/statecodes huggingface dataset:
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-58 - Existing health care occupancies

Current through June,
				  2024
Section 13.3.2.10 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-59 - Existing Detention and Correctional facilities

Current through
				  June, 2024
Section 13.3.2.12 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-60 - Hotels and apartment occupancies

Current through June,
				  2024
Sections 13.3.2.13.1 and 13.3.2.15.1 are amended to read as
					 follows: "An automatic sprinkler system shall be installed throughout every
					 apartment house over one story and containing 17 or more dwelling units, every
					 congregate residence over one story and having an occupant load of 50 or more,
					 and every hotel over one story and containing 20 or more guest rooms.
					 Residential or quick-response sprinkler heads shall be used in the dwelling
					 unit and guest room portions of the building."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-61 - Existing hotels and dormitories

Current through June,
				  2024
Section 13.3.2.14 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-62 - Existing residential board and care facilities

Current through
				  June, 2024
Section 13.3.2.20 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-63 - Mercantile and storage occupancies

Current through June,
				  2024
Sections 13.3.2.21.1 and 13.3.2.25.1 are amended by adding
					 a second paragraph at the end of each section to read as follows: "In a
					 one-story building for Mercantile or Storage occupancies requiring an automatic
					 sprinkler system, a metal plate sign stating the maximum storage height
					 allowable for the installed sprinkler system shall be placed next to the main
					 shutoff valve of the automatic sprinkler riser."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-64 - Existing mercantile occupancies

Current through June,
				  2024
Section 13.3.2.22 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-65 - Existing high-rise buildings

Current through June,
				  2024
Section 13.3.2.24.2 is deleted in its
					 entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-66 - Positive alarm sequence

Current through June,
				  2024
Section 13.7.1.4.9.4 is amended to read as follows:
					 "13.7.1.4.9.4. When approved by the AHJ and where permitted by Chapter
					 11 through Chapter
					 42 of NFPA 101, a positive alarm
					 sequence shall be permitted, provided that it is in accordance with NFPA
					 72."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-68 - Audibility

Current through June, 2024
Section 13.7.1.4.9.8 is amended to read as follows: "The
					 alarm signal shall be a distinctive sound, which is not used for any other
					 purpose other than the fire alarm. Alarm signaling devices shall produce a
					 sound that exceeds the prevailing equivalent sound level in the room or space
					 by 15 decibels minimum, or exceeds any maximum sound level with a duration of
					 60 seconds minimum by 5 decibels minimum, whichever is louder. Sound levels for
					 alarm signals shall be 120 decibels maximum."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-69 - General

Current through June, 2024
Sections 13.7.2.3.1 and 13.7.2.4.1 are amended by adding a
					 second paragraph to each subsection to read as follows: "Fire alarm systems
					 shall be tested and logged monthly."
Sections 13.7.2.3.1 and 13.7.2.4.1 are also amended by
					 adding a paragraph to read: "An annunciator panel shall be provided in the
					 office of each school."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-70 - Existing apartment buildings

Current through June,
				  2024
Sections 13.7.2.12.1, 13.7.2.12.2, 13.7.2.13 and
					 13.7.2.13.1 are deleted in their entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-71 - Existing mercantile occupancies

Current through June,
				  2024
Section 13.7.2.18 is deleted in its
					 entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-72 - Existing business occupancies

Current through June,
				  2024
Section 13.7.2.20 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-73 - Fire department communication system

Current through June,
				  2024
Section 13.7.2.27.2.2 is amended to read as follows: "A
					 two-way, fire department communication system approved by the AHJ shall be
					 provided for fire department use. A jack or plug receptacle shall be located at
					 the following locations:
1. The
				  emergency command center/central location approved by the AHJ.
2. The designated fire service
				  elevator(s)
3. Each elevator lobby
				  on each floor of the building.
4.
				  Emergency and standby power rooms.
5. The stairwell side of each exit into each
				  required stairway.
The height of the jack or plug receptacle shall be not more
					 than 5 feet and not less than 3 feet above floor level. Portable hand sets in
					 compliance with the following provisions shall be provided by the building
					 owner or management for fire department use:
1. Not less than 10 approved-type portable
				  hand sets shall be stored and maintained in the central control
				  station.
2. Length of cord for
				  portable hand sets shall be provided as recommended and approved by the
				  AHJ.
3. Hand sets approved by the
				  AHJ shall be maintained in an operative condition at all times and shall be
				  replaced or repaired when found to be defective."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-74 - Manual fire alarm boxes

Current through June,
				  2024
Section 13.7.3.3.6 is amended to add a new sentence at the
					 end to read as follows: "The location of manual fire alarm boxes may be
					 modified by the AHJ."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-75 - Application

Current through June, 2024
Section 14.1 is amended to read as follows: "14.1
					 Application. Means of egress in existing buildings shall comply with this
Code.
The provisions of this chapter do not apply for new
					 construction. For new construction see the building code. Existing buildings
					 shall be maintained to meet the requirements of the building code at the time
					 the structure was built, unless specifically indicated for existing facilities.
					 Provisions in this chapter are provided for maintenance purposes.
Exception: Stairway marking requirements set forth in
					 Section 14.6.4.1 shall apply to new and existing
					 construction."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-76 - Additional doors

Current through June, 2024
Section 14.5.1.6 is amended by adding an exception at the
					 end to read as follows:
"EXCEPTION:
Double-acting screen doors
					 used in conjunction with exit doors having panic hardware in school cafetoriums
					 do not need to comply with this provision."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-77 - Latch

Current through June, 2024
Section 14.5.2 is amended by adding a new subsection to
					 read as follows: "14.5.2.12 In accordance with the building code, security
					 gates may be permitted across corridors or passageways in school buildings if
					 there is a readily visible durable sign on or adjacent to the gate, stating
					 'THIS GATE IS TO REMAIN SECURED IN THE OPEN POSITION WHENEVER THIS BUILDING IS
					 IN USE'. The sign shall be in letters not less than one inch high on a
					 contrasting background. The use of this exception may be revoked by the
					 building official for due cause."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-78 - Determination of occupant load

Current through June,
				  2024
Section 14.8.1 is amended by adding a new subsection to
					 read as follows: "14.8.1.7 The number of persons in a building or portion
					 thereof shall not exceed the amounts determined as specified in the building
					 code."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-79 - Occupant Load Factor

Current through June,
				  2024
Section 14.8.1.2 is amended to read as follows: "14.8.1.2*
					 Occupant Load Factor. The occupant load in any building or portion thereof
					 shall be not less than the number of persons determined by dividing the floor
					 area assigned to that use by the occupant load factor for that use as specified
					 in the building code."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-80 - Occupant load factor

Current through June,
				  2024
Table 14.8.1.2 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-81 - Mall building occupant load factors

Current through June,
				  2024
Figures 14.8.1.2 (a) and (b) are deleted in their
					 entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-82 - Occupant load increases

Current through June,
				  2024
Section 14.8.1.3.1 is amended to read as follows:
					 "14.8.1.3.1 When approved by the AHJ, the occupant load in any building or
					 portion thereof shall be permitted to be increased from the occupant load
					 established for the given use in accordance with Section 14.8.1.2 where all
					 other requirements of this
Code
are also met, based on such
					 increased occupant load."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-83 - Egress capacity

Current through June,
				  2024
Section 14.8.3.1 is amended to read as follows: "14.8.3.1
					 Egress capacity for approved components of means of egress shall be based on
					 the capacity factors shown in the building code."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-84 - Capacity factors

Current through June,
				  2024
Table 14.8.3.1 is deleted in its
					 entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-85 - Elevator identification

Current through June,
				  2024
Section 14.14.6.5.3 is amended by adding a new subsection
					 to read as follows: "14.14.6.5.3.3 At all elevator locations on each floor
					 level above and below the floor of exit discharge, there shall be displayed in
					 a conspicuous location a sign reading: TN CASE OF FIRE USE EXIT STAIRWAYS. DO
					 NOT USE ELEVATORS'. Lettering shall be not less than 5/8-inch high.
EXCEPTION:
Signs at least 2-3/4-inches X
					 2-1/4-inches in overall size with legible wording and approved by the AHJ, may
					 be used as an alternate and shall be affixed at each elevator call button
					 assembly.
Elevator service companies shall have their name and
					 telephone number in the elevator key box."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-86 - Outdoor fires

Current through June, 2024
Section 17.3.4.7.1 is amended to read as follows:
					 "17.3.4.7.1* Outdoor fires shall not be built, ignited, or maintained in or
					 upon hazardous fire areas, without approval from the AHJ."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-87 - Special hazards

Current through June,
				  2024
Section 18.1 is amended by adding a paragraph at the end of
					 the section to read as follows: "For occupancies of an especially hazardous
					 nature, or where special hazards exist in addition to the normal hazard of the
					 occupancy, or where access for fire apparatus is unduly difficult, or areas
					 where there is an inadequate fire flow, or inadequate fire hydrant spacing, the
					 AHJ may require additional safeguards including, but not limited to, additional
					 fire appliance units, more than one type of appliance, or special systems
					 suitable for the protection of the hazard involved."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-88 - Dimensions

Current through June, 2024
Sections 18.2.3.4.1.1 and 18.2.3.4.1.2 are amended to read
					 as follows: "The unobstructed width and unobstructed vertical clearance of a
					 fire apparatus access road shall meet county requirements."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-89 - Turning radius

Current through June, 2024
Section 18.2.3.4.3.1 is amended to read as follows: "The
					 turning radius of a fire apparatus access road shall meet county
					 requirements."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-90 - Bridges

Current through June, 2024
Section 18.2.3.4.5.1 is amended to read as follows: "When a
					 bridge is required to be used as part of a fire apparatus access road, it shall
					 be constructed and maintained in accordance with county
					 requirements."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-91 - Grade

Current through June, 2024
Section 18.2.3.4.6 is amended to read as follows: "The
					 gradient for a fire apparatus access road shall meet county
					 requirements."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-92 - Required water supply for fire protection

Current through June,
				  2024
Section 18.3.1 is amended to read as follows: "A water
					 supply approved by the county, capable of supplying the required fire flow for
					 fire protection shall be provided to all premises upon which facilities or
					 buildings, or portions thereof, are hereafter constructed, or moved into or
					 within the county. When any portion of the facility or building is in excess of
					 150 feet (45 720 mm) from a water supply on a fire apparatus access road, as
					 measured by an approved route around the exterior of the facility or building,
					 on-site fire hydrants and mains capable of supplying the required fire flow
					 shall be provided when required by the AHJ. For on-site fire hydrant
					 requirements see section 18.3.3.
EXCEPTIONS:
1. When facilities or buildings, or portions
				  thereof, are completely protected with an approved automatic fire sprinkler
				  system, the provisions of section 18.3.1 may be modified by the AHJ.
2. When water supply requirements cannot be
				  installed due to topography or other conditions, the AHJ may require additional
				  fire protection as specified in section 18.3.2, as amended in this
				  code.
3. When there are not more
				  than two dwellings, or two private garages, carports, sheds and agricultural
				  Occupancies, the requirements of section 18.3.1 may be modified by the
				  AHJ."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-93 - Required installations

Current through June,
				  2024
Section 18.3.3 is amended to read as follows: "The
					 location, number and type of fire hydrants connected to a water supply capable
					 of delivering the required fire flow shall be provided on a fire apparatus
					 access road or on the site of the premises or both, in accordance with the
					 appropriate county water requirements."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-94 - Testing

Current through June, 2024
Section 18.3.5 is amended to read as follows: "18.3.5
					 Private water supply systems shall be tested and maintained in accordance with
					 NFPA 25 or county requirements as determined by the AHJ."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-95 - Testing and maintenance

Current through June,
				  2024
Section 18.3 is amended by adding a new subsection to read
					 as follows: "18.3.7 The AHJ shall be notified whenever any fire hydrant is
					 placed out of service or returned to service. Owners of private property
					 required to have hydrants shall maintain hydrant records of approval, testing,
					 and maintenance, in accordance with the respective county water requirements.
					 Records shall be made available for review by the AHJ upon
					 request."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-96 - Nonmetallic containers

Current through June,
				  2024
Section 19.2.1.2.1 is amended by adding an exception at the
					 end to read as follows:
"EXCEPTION:
Containers used by private
					 residences for refuse pickup"
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-97 - Decorative materials

Current through June,
				  2024
Section 20.1.2.1 is amended by adding a new sentence at the
					 end to read as follows: "A record of fire-resistant treatment shall be kept on
					 the premises for review by the AHJ."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-98 - Amusement buildings

Current through June,
				  2024
Section 20.1.3.2 is amended to read as follows: "An
					 automatic sprinkler system shall be installed in all permanent and portable
					 amusement buildings. The main water-flow switch shall be electrically
					 supervised. The sprinkler main cutoff valve shall be supervised. When the
					 amusement building is portable, the sprinkler water-supply system may be a
					 temporary type, as approved by the AHJ.
EXCEPTION:
An automatic sprinkler system need
					 not be provided when the floor area of a portable amusement building is less
					 than 1,000 square feet and the exit travel distance from any point is less than
					 50 feet."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-99 - Plan of exit ways and aisles

Current through June,
				  2024
Section 20.1.4.1 is amended by adding a new subsection to
					 read as follows: "20.1.4.1.3 A floor plan indicating the seating arrangements,
					 location and width of exit ways and aisles shall be submitted to the AHJ for
					 review for places of assembly with an occupant load of 300 or more persons. A
					 copy of the plan shall be kept on display on the premises. An exit plan shall
					 also be posted in a conspicuous location near the main entrance and shall be
					 maintained in a legible condition by the owner or an authorized agent.
Management of the event or business shall be responsible
					 for the inspection before each show or event of all required means of egress
					 from each part of the building, including stairways, egress doors and any panic
					 hardware installed thereon, aisles and corridors. Passageways and similar
					 elements of the means of egress shall be available for immediate use and free
					 of all obstructions before each show or event. Management shall inform all
					 patrons of all required exit locations before each show or event in places of
					 assembly with an occupant load of 300 or more persons."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-100 - Overcrowding

Current through June, 2024
Section 20.1.4.1 is amended by adding a new subsection to
					 read as follows: "20.1.4.1.4 Overcrowding. Overcrowding and admittance of
					 persons beyond the approved capacity of a place of assembly are prohibited. The
					 AHJ, upon finding overcrowding conditions or obstructions in aisles,
					 passageways or other means of egress, or upon finding a condition which
					 constitutes a serious menace to life, is authorized to cause the performance,
					 presentation, spectacle or entertainment to be stopped until such conditions or
					 obstruction is corrected."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-101 - Open flame devices and pyrotechnics

Current through June,
				  2024
Section 20.1.4.3, Open Flame Devices and Pyrotechnics, is
					 amended by adding item (7) to read as follows: "(7) When approved by the AHJ,
					 open-flame devices may be used on stages or platforms, provided adequate
					 precautions are taken to prevent ignition of combustible materials. So-called
					 flaming sword or other like equipment shall not be used except in areas
					 protected by an automatic sprinkler system. This shall be construed to mean
					 that stages, platforms, dressing and storage rooms or areas used as places for
					 the performance of flaming sword or other dance performances using fire or
					 flame, shall be sprinklered. In addition, a suitable non-combustible net shall
					 be erected to prevent accidental release onto the viewing
					 audience."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-102 - Open flame devices and pyrotechnics

Current through June,
				  2024
Section 20.1.4.3, Open Flame Devices and Pyrotechnics, is
					 amended by adding a new subsection (8) to read as follows: "(8) Portable
					 heating equipment, not flue-connected, shall be permitted only as follows:
					 Equipment fueled by small heat sources which can be readily extinguished by
					 water, such as candles or alcohol-burning equipment (including solid alcohol)
					 may be used provided adequate precautions satisfactory to the AHJ are taken to
					 prevent ignition of any combustible materials."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-103 - Fire drills

Current through June, 2024
Section 20.2.3.2.2 is amended by adding a new exception at
					 the end to read as follows:
"EXCEPTION:
Fire drills at high
					 schools, middle schools and intermediate schools shall be conducted at least
					 quarterly during school sessions."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-104 - Use of school facilities for sleeping

Current through June,
				  2024
Section 20.2.3, Operating Features, is amended by adding a
					 new subsection to read as follows: "20.2.3.6 Use of School Facilities for
					 Sleeping. Educational occupancies that allow sleeping on a temporary basis
					 shall prohibit smoking or open flames and shall be provided with one of the
					 following:
1 Smoke alarms shall be
				  provided in the designated sleeping area. When the facility is provided with a
				  fire alarm system, the smoke alarms shall be connected to the fire alarm
				  system, or
2 An approved fire watch
				  shall be provided."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-106 - Emergency command center

Current through June,
				  2024
Section 20.16.1.1 is amended to read as follows: "An
					 emergency command center room for fire department operations shall be provided
					 in high-rise buildings. The location and accessibility of the emergency command
					 center room shall be approved by the AHJ. The room shall be accessible from the
					 exterior of the building. The central control station room shall be separated
					 from the remainder of the building by not less than a one-hour fire-resistive
					 occupancy separation. The room shall be a minimum of 96 (9 m2) square feet with
					 a minimum dimension of 8 feet (2438 mm). It shall contain the following as a
					 minimum:
1. The voice alarm and public
				  address system panels.
2. The fire
				  department communications panel.
3.
				  Fire-detection and alarm system annunciator panels.
4. Annunciator visually indicating the
				  location of the elevators and whether they are operational.
5. Status indicators and controls for air
				  handling systems.
6. Controls for
				  unlocking all stairway doors simultaneously.
7. Sprinkler valve and water-flow detector
				  display panels.
8. Emergency and
				  standby power status indicators.
9.
				  A telephone for fire department use with controlled access to the public
				  telephone system.
10. Fire pump
				  status indicators.
11. Schematic
				  building plans indicating the typical floor plan and detailing the building
				  core, means of egress, fire-protection systems, firefighting equipment and fire
				  department access.
12. Work
				  table.
Control panels in the emergency command center shall be
					 permanently identified as to function.
Alarm, supervisory and trouble signals as required by Items
					 3 and 7 above shall be annunciated in compliance with the fire code in the
					 emergency command center by means of an audible and visual
					 indicator."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-107 - Scope

Current through June, 2024
Section 25.1.1 is amended by adding an exception at the end
					 to read as follows: "Exception: The provisions of this chapter do not apply to
					 tents and temporary membrane structures having an area 200 square feet and
					 canopies having an area of 400 square feet or less."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-108 - Fireworks

Current through June, 2024
Section 25.1.5.5 is amended to read as follows: "25.1.5.5
					 Fireworks or unapproved open flames shall be prohibited in any tent or
					 temporary membrane structure.
Exception: Where permitted by Section 65.11."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-109 - Application

Current through June, 2024
Section 34.1.1 is amended by adding a new sentence at the
					 end to read as follows: "Automatic sprinkler systems shall be installed in
					 accordance with Section 13.3.2.25."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-110 - Permit authorizing individual

Current through June,
				  2024
Section 41.2.1.2 is amended to read as follows: "41.2.1.2
					 Management shall designate a permit authorizing individual (PAI), regardless of
					 whether a permit is required by the AHJ."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-111 - Permit authorizing individual

Current through June,
				  2024
Section 41.2.2 is amended to read as follows: "41.2.2
					 Permit Authorizing Individual (PAI). In conjunction with management, the PAI
					 shall be responsible for the safe operation of hot work activities regardless
					 of whether a permit is required by the AHJ."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-112 - Guard posts

Current through June, 2024
Section 42.2.3.8.2 is amended to read as follows:
					 "42.2.3.8.2* Guard posts or other approved means shall be provided to protect
					 tanks that are subject to vehicular damage in accordance with section
					 60.1.2.13.2 as amended."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-113 - Emergency electrical disconnects

Current through June,
				  2024
Section 42.2.5.7 is amended by adding new sentences at the
					 end to read as follows: "Such devices shall be distinctly labeled as EMERGENCY
					 FUEL SHUTOFF DEVICE. Signs shall be provided in approved locations. The signs
					 shall be in red letters on a white background, not less than two inches high,
					 with a 1/4 inch stroke."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-114 - Occupancy classification

Current through June,
				  2024
Section 42.2.6.1.1 is amended to read as follows:
					 "42.2.6.1.1 Occupancy Classification.
The occupancy classification of a motor fuel dispensing
					 facility that is located inside a building or structure shall be as defined in
					 the building
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-115 - Means of egress

Current through June, 2024
Section 42.2,6.1.2 is amended to read as follows:
					 "42.2.6.1.2 Means of Egress. In a motor fuel dispensing facility that is
					 located inside a building or structure, the required number, location, and
					 construction of means of egress shall meet all applicable requirements for
					 special purpose industrial occupancies, as set forth in the building code. For
					 the intent of this section, special purpose industrial occupancies are
					 equivalent to F-1 Occupancies as defined in the building
					 code."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-116 - Age limitation

Current through June,
				  2024
Section 42.2.7.1 is amended by adding a new subsection to
					 read as follows: "42.2.7.1.1 Age Limitation. Persons under the age of 15 years
					 are prohibited from dispensing fuel."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-117 - Foreign objects

Current through June,
				  2024
Section 42.2.7.1 is amended by adding a new subsection to
					 read as follows: "42.2.7.1.2 Foreign Objects. The placement of a foreign
					 object(s), that allows the fuel dispensing lever to remain in the open
					 position, is prohibited at all times."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-118 - Sources of ignition

Current through June,
				  2024
Section 42.2.7.2.5 is amended by adding a new sentence at
					 the end to read as follows: "42.2.7.2.5.1 Adequate grounding and bonding shall
					 be provided to prevent the accumulation of static electricity wherever Class I
					 or II liquids are transferred or dispensed."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-119 - Signs

Current through June, 2024
Section 42.2.7.2.5 is amended to read as follows:
					 "42.2.7.2.5.4* Signs. Warning signs shall be conspicuously posted in the
					 dispensing area and shall incorporate the following or equivalent
					 wording:
WARNING:
It is unlawful and dangerous to dispense gasoline into
					 unapproved containers.
No smoking.
Stop motor.
No filling of portable containers in or on a motor vehicle.
					 Place container on ground before filling.
Discharge your static electricity before fueling by
					 touching a metal surface away from the nozzle.
Do not re-enter your vehicle while gasoline is pumping. If
					 a fire starts,
do not
remove nozzle - back away immediately. Do
					 not allow individuals under the age of 15 years to use the pump.
The placement of a foreign object(s), that allows the fuel
					 dispensing lever to remain in the open position, is prohibited at all
					 times."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-120 - Latch-open device

Current through June, 2024
Section 42.2.7.4.3 is amended by adding a new subsection to
					 read as follows: "42.2.7.4.3.2 The hose nozzle valve shall not be equipped with
					 an integral latchopen device where dispensing of Class I, II or III-A liquids
					 is performed by someone other than a qualified attendant. The placement of a
					 foreign object(s), that allows the fuel dispensing lever to remain in the open
					 position, is prohibited at all times."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-121 - Latch-open device

Current through June, 2024
Section 42.2.7.5.4 is amended to read as follows:
					 "42.2.7.5. The hose nozzle valve shall not be equipped with an integral
					 latch-open device where dispensing of Class I, II or III-A liquids is performed
					 by someone other than a qualified attendant. The placement of a foreign
					 object(s), that allows the fuel dispensing lever to remain in the open
					 position, is prohibited at all times."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-122 - Materials

Current through June, 2024
Section 42.3.7.3 is amended to read as follows: "42.3.7.3
					 Materials shall not be placed on a pier in such a manner that they obstruct
					 access to fire-fighting equipment or important piping system control valves.
					 Where the pier is accessible to vehicular traffic, an unobstructed roadway to
					 the shore end of the wharf shall be maintained for access by fire-fighting
					 apparatus in accordance with county requirements."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-123 - Operations and maintenance

Current through June,
				  2024
Section 50,5.2.1 is amended to read as follows:
					 "Extinguishing systems shall be serviced at least every six months or after
					 activation of the system. Inspections shall be conducted by a qualified
					 individual as approved by the AHJ. A copy of the inspection test report shall
					 be kept on the premises and a copy of the inspection report shall be forwarded
					 to the AHJ within five (5) working days of completion of the required servicing
					 and testing.
The AHJ shall be notified a minimum of four (4) working
					 days prior to the service date by the company conducting the test. The AHJ
					 shall be informed of the name of the business being serviced, date and time of
					 servicing, and the company and the individual conducting the
					 servicing."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-125 - Facility-closure

Current through June, 2024
Section 60.1.2.4 is deleted in its entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-126 - Hazardous materials management plan

Current through June,
				  2024
Section 60.1.2.5.1 is amended to read as follows: "When
					 required by the AHJ, the owner of buildings or facilities shall have a
					 hazardous materials management plan (HMMP) posted on site. An example of a HMMP
					 can be found in Annex D."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-127 - Available

Current through June, 2024
Section 60.1.2.5.1.2 is amended to read as follows:
					 "Available. The HMMP shall be made available on site."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-128 - Hazardous materials inventory statement

Current through June,
				  2024
Section 60.1.2.5.2 is amended to read as follows: "When
					 required by the AHJ, a hazardous materials inventory statement (HMIS) shall be
					 made a part of the hazardous materials management plan. An example of a HMIS
					 can be found in Annex D."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-129 - Protection from vehicles

Current through June,
				  2024
The paragraph numbered 2 of Section 60.1.2.13.2 is amended
					 to read as follows: "2. Spaced not more than 3 feet (914 mm) between posts on
					 center,"
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-130 - Protection from vehicles

Current through June,
				  2024
The paragraph numbered 5 of section 60.1.2.13.2 is amended
					 to read as follows: "5. Located not less than 3 feet (914 mm) from the
					 tank."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-131 - Special information for permit application

Current through
				  June, 2024
Section 60.2.3 is deleted in its
					 entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-132 - Separation of occupancies of high hazard

Current through June,
				  2024
Section 60.3.2.3 and Table 60.3.2.3 are deleted in their
					 entirety.
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-133 - Mechanical exhaust

Current through June,
				  2024
Section 60.3.2.5.2 is amended to read as follows:
					 "60.3.2.5.2 Mechanical exhaust systems shall comply with the building
					 code."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-134 - Supply and exhaust openings

Current through June,
				  2024
Section 60.3.2.5.9 is amended to read as follows:
					 "60.3.2.5.9 The location of supply and exhaust openings shall be in accordance
					 with the building code."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-135 - Remote containment

Current through June,
				  2024
Section 60.3.2.8.3.12 is amended by revising the first
					 paragraph to read as follows: "60.3.2.8.3.12 Where remote containment systems
					 are provided, drainage systems shall be in accordance with the Plumbing Code,
					 and the following provisions also shall be met:"
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-137 - Tank vehicles

Current through June,
				  2024
Section 63.4.13.1.2 is amended to read as follows: "Tank
					 vehicles transporting cryogenic fluids shall not be left unattended on any
					 residential street or within 500 feet of any residential area, apartment or
					 hotel complex, educational, hospital or care facility at any time; or at any
					 other place or location that would present a hazard to persons or property from
					 fire loss.
EXCEPTION:
When unattendance is necessary in
					 connection with unloading the vehicle or servicing tanks; or when in case of
					 accident or other emergency, the operator must leave the vehicle to obtain
					 assistance."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-138 - Seizure of fireworks

Current through June,
				  2024
Section 65.1 is amended by adding a new subsection to read
					 as follows: "65.1.3 The AHJ is authorized to require the owner to remove at the
					 expense of the owner, all fireworks offered for sale, stored, or possessed in
					 violation of Chapter
					 65, or other applicable state or
					 county laws or rules."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-139 - Prohibition

Current through June, 2024
Section 65.1 is amended by adding a new subsection to read
					 as follows: "65.1.4 Importation, storage, possession, sale, purchase, transfer,
					 public displays and discharge of fireworks, shall be in accordance with chapter
					 132D,
					 HRS."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-141 - Minors

Current through June, 2024
Section 65.11.2 is amended by adding a new subsection to
					 read as follows: "65.11.2.8 It shall be unlawful for any minor to sell, handle
					 or give away for recompense any fireworks products."
Hawaii Administrative Rules › Title 12 - DEPARTMENT OF LABOR AND INDUSTRIAL RELATIONS › Chapter 45.2 - STATE FIR COUNCIL › STATE FIRE CODE › Subchapter 2 - AMENDMENTS TO THE NFPA 1, UFC › Section 12-45.2-142 - Plan

Current through June, 2024
Section 65.11.4.1 is amended to read as follows: "65.11.4.1
					 Plan. Where required, plans for CFRS facilities shall be submitted to the
					 AHJ."