Illinois Administrative Code › Title 41 - FIRE PROTECTION › Part 2120 - BOILER AND PRESSURE VESSEL SAFETY › Subpart A - DEFINITIONS AND ADMINISTRATION › Section 2120.40 - Administration

Current through Register Vol. 48, No. 28, July 12, 2024
a) Applying State
				Serial Number. The State serial number on boilers shall be not less than 
				5/16" in height
				and shall be preceded by the letter "B". The State serial number on pressure
				vessels shall be not less than 
				5/16" in height
				and shall be preceded by the letter "U". The inspector shall make certain that
				the correct Illinois State serial number is affixed to the boiler or pressure
				vessel at the time of inspection.
b) First Time Inspection. Effective January
				1, 1999, all first time inspections of boilers and pressure vessels shall be
				performed by the Chief or a Deputy Inspector employed by the
				Division.
c) Basis for Extending
				Certificate of Internal Inspection for Power Boilers. The Chief Inspector is
				authorized to extend, for a period not exceeding one year, or 2 years for power
				boilers having an output rated at or above 450,000 lbs/hr, the time within
				which power boilers are required to be internally inspected, subject to the
				following conditions and qualifications:
1)
				The analysis and treatment of feedwater for power boilers shall be under the
				supervision of a person qualified in the field of water chemistry.
2) The analysis and treatment of the boiler
				feedwater shall be for the purpose of controlling and limiting serious
				deteriorating, encrusting and sludging factors affecting the safety of the
				boiler.
3) The owner or user of
				power boilers must maintain, for examination by the inspector, accurate records
				of chemical and physical laboratory analyses of samples of the boiler water
				taken at regular intervals of not more than 24 hours operation and of the
				treatment applied. These records must specify dates and times of analyses, by
				whom analyzed, and the treatment applied at that time, and should be certified
				by the responsible authority. These records will adequately show the conditions
				of the water and any constituents or characteristics that are capable of
				producing corrosion or other deterioration of the boiler or its
				parts.
4) The Chief Inspector is
				authorized to review the qualifications of the supervisor and the acceptability
				of supervision in accordance with the requirements of subsections (c)(1)
				through (c)(3).
5) An internal
				inspection must have been performed during a pre-planned outage allowing
				appropriate time for a complete and comprehensive evaluation, including
				inspections of watersides, furnace area and all gas passages, with no
				deficiencies found that would preclude extending the internal inspection for
				one year, or 2 years for power boilers having an output rated at or above
				450,000 lbs/hr.
6) At no time shall
				the period between internal inspections for boilers having an output rated at
				or above 450,000 lbs/hr exceed a 36-month time interval.
7) Application for extension shall be by
				letter setting forth facts establishing compliance with the requirements of
				subsections (c)(1) through (c)(7) and shall be accompanied by the report of
				external inspection.