reglab/statecodes huggingface dataset:
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-2 - Automatic operation

Current through June, 2024
Elevator operation shall be automatic. Each car shall
						  be equipped with a self-leveling feature that will automatically bring the car
						  to floor landings within a tolerance of one-half (1/2) inch or thirteen (13)
						  millimeters under rated loading to zero loading conditions. This self-leveling
						  feature shall be automatic and independent of the operating device and shall
						  correct the overtravel or undertravel.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-3 - Hall call buttons

Current through June, 2024
Call buttons in elevator lobbies and halls shall be
						  centered at approximately forty-two (42) inches (1065 millimeters) above the
						  floor. When situations prohibit mounting at forty-two (42) inches, in
						  conjunction with ICC All7.l-2009, hall buttons maybe be mounted between fifteen
						  (15) inches and forty-eight (48) inches for unobstructed forward reach, and
						  between twenty-five (25) inches and forty-eight (48) inches for obstructed
						  forward reach. Such call buttons shall have visual signals to indicate when
						  each call is registered and when each call is answered. Call buttons shall be a
						  minimum of three-fourths (3/4) inch or nineteen (19) millimeters in the
						  smallest dimension. The button designating the up direction shall be on top as
						  shown in Figure
						  240-1,
						  titled, "Hoistway and Elevator Entrances", dated December 6, 1990, which is
						  made a part of this chapter, and located at the end of this chapter. Buttons
						  shall be raised or flush. Objects mounted or placed beneath hall call buttons
						  shall not project into the elevator lobby more than four (4) inches or 100
						  millimeters.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-4 - Hall lanterns

Current through June, 2024
A visible and audible signal shall be provided at each
						  hoistway entrance to indicate which car is answering a call. Audible signals
						  shall sound once for the up direction and twice for the down direction or shall
						  have verbal annunciators that say "up" or "down." Visible signals shall have
						  the following features:
(1) Hall
						lantern fixtures shall be mounted so that their centerline is at least
						seventy-two (72) inches or 1830 millimeters above the lobby floor;
(2) Visual elements shall be at least two and
						a half (2.5) inches or sixty-four (64) millimeters in the smallest dimension;
						and
(3) Signals shall be visible
						from the vicinity of the hall call button. In-car lanterns located in cars,
						visible from the vicinity of hall call buttons, and confirming to the above
						requirements, shall be acceptable as shown in Figure
						240-1,
						titled, "Hoistway and Elevator Entrances," dated December 6, 1990, which is
						made a part of this chapter, and located at the end of this chapter.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-5 - Raised characters on hoistway entrances

Current through June, 2024
All elevator hoistway entrances shall have raised floor
						  designations provided on both jambs. The centerline of the characters shall be
						  sixty (60) inches (1525 millimeters) from the floor. Such characters shall two
						  (2) inches or fifty (50) millimeters high and shall comply with ANSI
						  A117.1-1986 Rule 1.30. Permanently applied plates are acceptable if they are
						  permanently fixed to the jambs as shown in Figure
						  240-1,
						  titled, "Hoistway and Elevator Entrances", dated December 6, 1990, which is
						  made a part of this chapter, and located at the end of this
						  chapter.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-6 - Door protective and reopening device

Current through June, 2024
Elevator doors shall open and close automatically. They
						  shall be provided with a reopening device that will stop and reopen a car door
						  and hoistway door automatically if the door becomes obstructed by an object or
						  person. The device shall be capable of completing these operations without
						  requiring contact for an obstruction passing through the opening at heights of
						  five (5)inches and twenty-nine (29) inches or 125 and 735 millimeters,
						  respectively, from the floor as shown in Figure
						  240-1,
						  titled, "Hoistway and Elevator Entrances", dated December 6, 1990, which is
						  made a part of this chapter, and located at the end of this chapter. Door
						  reopening devices shall remain effective for at least twenty (20) seconds.
						  After such an interval, doors may close in accordance with the requirements of
						  ANSI A17.lb-1989.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-7 - Door and signal timing for hall calls

Current through June, 2024
The minimum acceptable time from notification that a
						  car is answering a call until the doors of that car start to close shall be
						  calculated from the following equation:
Click
						  here to view image
where T = total time in seconds and D = distance (in
						  feet or millimeters) from a point in the lobby or corridor sixty (60) inches or
						  1525 millimeters directly in front of the farthest call button controlling that
						  car to the centerline of its hoistway door as shown in Figure
						  240-2, titled
						  "Graph of Timing Equation", dated December 6, 1990, which is made a part of
						  this chapter, and located at the end of this chapter. For cars with in-car
						  lanterns, T begins when the lantern is visible from the vicinity of hall call
						  buttons and an audible signal is sounded. The minimum acceptable notification
						  time shall be five (5) seconds.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-8 - Door delay for car calls

Current through June, 2024
The minimum time for elevator doors to remain fully
						  open in response to a car call shall be three ( 3) seconds.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-9 - Floor plan of elevator cars

Current through June, 2024
The floor area of elevator cars shall provide space for
						  wheelchair users to enter the car, maneuver within reach of controls, and exit
						  from the car. Acceptable door opening and inside dimensions shall be as shown
						  in Figure 240-3, titled "Minimum Dimensions of Elevator Cars'', dated December
						  6, 1990, which is made a part of this chapter, and located at the end of this
						  chapter. The clearance between the car platform sill and the edge of any
						  hoistway landing shall be no greater than one and one-fourth inch or thirty-two
						  (32) millimeters.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-10 - Floor surfaces

Current through June, 2024
Floor surfaces shall comply with ANSI A117.1-1980 Rule
						  4.5.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-11 - Illumination levels

Current through June, 2024
The level of illumination at the car controls,
						  platform, and car threshold and landing sill shall be at least five (5)
						  footcandles ( 53. 8 lux) .
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-12 - Car controls

Current through June, 2024
Elevator control panels shall have the following
						  features:
(1) Buttons. All control
						buttons shall be at least three fourths (3/4) inch or nineteen (19) millimeters
						in their smallest dimension. They may be raised or flush;
(2) Tactile and visual control indicators.
						All control buttons shall be designated by raised standard alphabet characters
						for letters, Arabic characters for numerals, or standard symbols as shown in
						Figure 240-4(a), titled "Car Controls", dated December 6, 1990, which is made a
						part of this chapter, and located at the end of this chapter, and as required
						in ANSI Ai7.1-1989. Raised characters and symbols shall comply with ANSI
						A117.1-1986 Rule 4.30. The call button for the main entry floor shall be
						designated by a raised star at the left of the floor designation as shown in
						Figure 240-4(a), titled "Car Controls", dated December 6, 1990, which is made a
						part of this chapter, and located at the end of this chapter. All raised
						designations for control buttons shall be placed immediately to the left of the
						button to which they apply. Applied plates, permanently attached, are an
						acceptable means to provide raised control designations. Floor buttons shall be
						provided with visual indicators to show when each call is registered. The
						visual indicators shall be extinguished when each call is answered;
(3) Height. All floor buttons shall be no
						higher than fifty-four (54) inches or 1220 millimeters, above the finish floor
						for side approach and forty-eight (48) inches for front approach. Emergency
						controls, including the emergency alarm and emergency stop, shall be grouped at
						the bottom of the panel and shall have their centerlines no less than
						thirty-five (35) inches or 890 millimeters above the floor as shown in Figures
						240-4(a) and (b), entitled "Car Controls", dated December 6, 1990, which is
						made a part of this chapter, and located at the end of this chapter. The
						emergency alarm bell shall be operable under normal power as well as for a
						minimum of one (1) hour on auxiliary power in the event of the loss of normal
						power; and
(4) Location. Controls
						shall be located on a front wall if cars have center opening doors, and at the
						side wall or at the front wall next to the door if cars have side opening doors
						as shown in Figures 240-4(c) and (d), entitled "Car Controls", dated December
						6, 1990, which is made a part of this chapter, and located at the end of this
						chapter.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-13 - Car position indicators

Current through June, 2024
In elevator cars, a visual car position indicator shall
						  be provided above the car control panel or over the door to show the position
						  of the elevator in the hoistway. As the car passes or stops at a floor served
						  by the elevators, the corresponding numerals shall illuminate, and an audible
						  signal shall sound. Numerals shall be a minimum of one-half (1/2) inch or
						  thirteen (13) millimeters high. The audible signal shall be no less than twenty
						  (20) decibels with a frequency no higher than 1500 Hertz. An automatic verbal
						  announcement of the floor number at which a car stops or which a car passes may
						  be substituted for the audible signal.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 240 - ELEVATOR REQUIREMENTS FOR INDIVIDUALS WITH DISABILITIES › Section 12-240-14 - Emergency communications

Current through June, 2024
If provided, emergency two-way communication systems
						  between the elevator and a point outside the hoistway shall comply with ANSI
						  A17.1-1989. The highest operable part of a two-way communication system shall
						  be a maximum of forty-eight (48) inches or 1220 millimeters from the floor of
						  the car. It shall be identified by a raised or recessed symbol and lettering
						  complying with ANSI A117-1986 Rule 4.30 and located adjacent to the device. If
						  the system uses a handset, then the length of the cord from the panel to the
						  handset shall be at least twenty-nine (29) inches or 735 millimeters. If the
						  system is located in a closed compartment, the compartment door hardware shall
						  conform to ANSI A117.1-1980 Rule 4.27, Controls and Operating Mechanisms. The
						  emergency intercommunication system shall not require voice
						  communication.
Figure
						  240-1
Holstway and Elevator Entrances
December 6, 1990
Click here to view
						  image
Figure
						  240-2
Graph of Timing Equation
December 6, 1990
Click here to view
						  image
Figure 240-3
Minimum Dimensions of Elevator Cars
December 6, 1990
Click here to view
						  image
Figure 240-4
Car Controls December 6, 1990
Click here to view
						  image
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-1 - Application

Current through June, 2024
This chapter shall apply to amusement rides installed
						  on a temporary or permanent basis at carnivals, circuses, fairs, amusement
						  parks, or other locations available to the public. It shall not apply to small
						  rides such as a single animal figure or three-car carousel, usually coin
						  operated, which are designed for use by small children.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-2 - Definitions

Current through June, 2024
As used in this chapter:
"Accident" means an unexpected happening causing loss
						  or injury which is not due to any fault or misconduct on the part of the person
						  injured but from consequences of which the person has no control of and may be
						  entitled to some legal relief.
"Amusement ride" means a mechanically or electrically
						  operated device designed to carry passengers in various modes and used for
						  entertainment and amusement.
"Manager" means a person having possession, custody, or
						  managerial control of an amusement ride or its temporary structure at any
						  location available to the public whether as owner, lessee, agent, or otherwise.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-3 - Design and construction requirements

Current through June, 2024
(a) All amusement
						rides and their structures shall be designed, constructed, and installed so as
						to carry safely all loads and withstand any normal stresses to which they may
						be subjected.
(b) All amusement
						rides shall be so placed or secured with blocking, cribbing, outriggers, guys,
						or other means as to be stable under all operating condition.
(c) The interior and exterior parts of all
						amusement rides with which a passenger may come in contact shall be smooth and
						rounded, free from sharp, rough, or splintered edges and corners with no
						protruding studs, bolts, screws, or other projections which might cause injury.
						Interior parts on or against which a person may be forcibly thrown by the
						action of the ride shall be adequately padded. Any ride which is self-powered
						and which is operated by a passenger shall have the driving mechanism guarded
						and locked in place to prevent the passengers from gaining access into the
						mechanism. Belts, bars, foot rests, and other equipment shall be provided when
						necessary for safe entrance, exit, and for support while the device is in
						operation. Equipment and fastenings shall be of sufficient strength to retain
						the passengers. The fastenings shall be of a type which cannot be inadvertently
						or accidentally released.
(d) An
						amusement ride shall be provided with an automatic maximum speed limiting
						device if capable of exceeding its maximum safe operating speed.
(e) If cars or other components of an
						amusement ride may collide in such a way as to cause personal injuries upon
						failure of normal controls, emergency brakes sufficient to prevent the
						collision shall be provided.
(f) On
						rides which make use of inclined tracks, automatic antirollback devices shall
						be installed to prevent backward movement of the passenger carrying unit in
						case of power loss or failure of the propelling mechanism.
(g) Machinery used in or with an amusement
						ride shall be enclosed, barricaded, or otherwise effectively guarded against
						contact. Guards removed for maintenance purposes shall be replaced before
						normal operation is resumed.
(h)
						Areas in which persons may be endangered by the movement or operation of an
						amusement ride shall be fenced, barricaded, or otherwise guarded against public
						intrusion.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-4 - Access to and egress from amusement rides

Current through June, 2024
(a) Safe and
						adequate means of access to and egress from amusement rides shall be provided.
						The means of access and egress shall have:
(1) Protection of users from adjacent hazards
						or from falling by the use of rails, enclosures, barriers, or similar
						means;
(2) Secure treading and
						supporting surface free from debris, obstruction, projection and slipping,
						tripping, and other hazards;
(3)
						Adequate clearance;
(4) Stairways
						or ramps provided when the difference between two levels exceeds 8 inches (20
						cm); and
(5) Sufficient
						illumination by natural or artificial means to prevent tripping or exposure to
						other hazards.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-5 - Load test

Current through June, 2024
(a) Amusement rides having suspended
						passenger seats or spaces, amusement rides normally operated at speeds or with
						movements creating severe centrifugal force, and amusement rides so elevated
						that a structural failure will likely cause injury shall be required to undergo
						and withstand the following load test without failure in any material respect:
						Each passenger seat or space shall be weighted with at least 150 pounds dead
						weight except that in a ride intended only for small children each seat or
						space shall be weighted with at least 100 pounds (45.4 kg); and while so
						loaded, the ride shall be operated at a maximum normal speed to test the full
						operation of all control devices, speed limiting devices, brakes, and other
						equipment provided for safety.
(b)
						A ride is unsafe if it fails to withstand the load test. If the ride has
						withstood a load test without failure in any material respect, it shall be
						required to be so tested again only if rebuilt, modified, or if there are
						reasonable grounds to believe that a further test is necessary to ensure safety
						and the department orders such test to be made.
(c) The load test shall be made in the
						presence of and under the supervision of an inspector from the department. Load
						test results witnessed and certified by a professional engineer or by a safety
						specialist approved by the department may be accepted in lieu of a test
						witnessed by an inspected from the department.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-6 - Identification and rating plates

Current through June, 2024
Every amusement ride shall be identified by a trade or
						  descriptive name and an identification number and there shall be firmly
						  attached in a readily visible location a metal plate upon which there is
						  legibly impressed the name and number of the ride, its model number if any, and
						  the name and address of its manufacturer. Upon the same or another attached
						  metal plate there shall be legibly impressed the maximum safe number of
						  passengers and the maximum safe speed.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-7 - Rebuilt and modified rides

Current through June, 2024
If an amusement ride has undergone and passed the
						  required load test and is rebuilt or modified changing its original action, the
						  ride shall be:
(1) Re-identified by a
						different name, identification number, or both; and
(2) Subjected to all other provisions of this
						chapter as if it were a new ride not previously used, including a load
						test.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-8 - Assembly and disassembly

Current through June, 2024
(a) Parts of
						amusement rides and their structures shall be properly aligned and shall not be
						bent, distorted, cut, or otherwise injured to force a fit.
(b) Parts which are excessively worn or which
						have been materially damaged shall not be used.
(c) An inspection of all fastening and
						locking devices shall be made after assembly to ensure that they have been
						properly installed.
(d) Broken,
						damaged, and unsuitable tools and equipment shall not be used. Electrically
						operated tools shall be grounded during use unless their construction is such
						that special grounding is not required for safety.
(e) Assembly and disassembly of amusement
						rides and temporary structures shall be carried on under illumination
						sufficient to permit the work to be safely performed and inspected.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-9 - Location notice

Current through June, 2024
If any person intends to use or operate an amusement
						  ride at any location available to the public, the department shall be notified
						  in writing at least 5 days prior to the use or operation of the ride. The
						  written notification shall state, at a minimum, the following:
(1) The specific dates when the ride is to be
						used or operated;
(2) The location
						where the ride is to be used or operated; and
(3) The identification type and number of the
						ride.
If an unscheduled or emergency use or operation of a
						  ride makes it not possible to give a 5-day notice, the notice shall be given to
						  the department immediately by telephone.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-11 - Air compressors and equipment

Current through June, 2024
Air compressor tanks and equipment used in connection
						  therewith shall be constructed, equipped, operated, maintained, inspected, and
						  tested as required by part 10 of this title.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-12 - Fire prevention and protection

Current through June, 2024
(a) Approved fire
						extinguishers shall be provided when necessary to secure reasonable and
						adequate protection from fire hazards.
(b) Flammable waste such as oily rags and
						other flammable materials shall be placed in covered metal containers which
						shall be kept in easily accessible locations. The containers shall not be kept
						at or near exits or under amusement rides.
(c) Gasoline and other volatile liquids and
						flammable gases shall be stored and handled in compliance with chapters
						12-74 and 12-75.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-13 - Operation of amusement rides

Current through June, 2024
(a) It shall be the
						responsibility of the manager to ensure that the operator of each amusement
						ride is a responsible person at least 18 years of age who has been properly
						instructed in the safe operation of the amusement ride.
(b) It shall be the responsibility of the
						manager to post all necessary warning and danger signs. Such signs shall be
						conspicuously located where they will render the most effective protection,
						shall be of sufficient size to be legible at a distance of not less than 6 feet
						(1.8 m), and shall be illuminated as required for good visibility. On those
						amusement rides where there is a greater than normal possibility of passengers
						being thrown from the ride, permanent notices shall be posted in locations
						visible to all passengers warning them that restraining devices are required to
						be tight.
(c) It shall be the
						responsibility of the operator to ensure that the restraining devices for all
						passengers have been properly fastened and adjusted prior to placing the ride
						in motion.
(d) The operator shall
						remain in the immediate vicinity of the operating controls at all times while
						the amusement ride is in motion.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Elevator Code › Subtitle 8 - DIVISION OF OCCUPATIONAL SAFETY AND HEALTH › Part 11 - ELEVATORS AND RELATED SYSTEMS › Chapter 250 - AMUSEMENT RIDES › Section 12-250-14 - Availability of standards

Current through June, 2024
(a) ANSI/ASME A12.1
						is available from the American National Standards Institute, 1430 Broadway, New
						York, N.Y. 10018.
(b) ANSI/NFPA 70
						is available from National Fire Protection Association, Batterymarch Park,
						Quincy, MA 02269.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 1 - RULES OF GENERAL APPLICABILITY › 2 - Scope

Current through June, 2024
This chapter sets forth minimum requirements for the design
					 and construction of buildings for the effective use of energy and is intended
					 to provide flexibility to allow the use of innovative approaches and techniques
					 to achieve the effective use of energy.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 1 - RULES OF GENERAL APPLICABILITY › 3 - Definitions

Current through June, 2024
In this chapter, unless the context otherwise
					 requires:
"ICC" means the International Code Council.
"IECC Section" means a section of a chapter of the
International Energy Conservation Code.
"IECC" means the ICC,
International Energy
					 Conservation Code,
2018 edition, as copyrighted by the International
					 Code Council.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 1 - RULES OF GENERAL APPLICABILITY › 4 - Adoption of the International Energy Conservation Code

Current through June, 2024
The
International Energy Conservation
					 Code,
2018
Edition
as copyrighted and published in
					 2017 by International Code Council, Incorporated, 500 New Jersey Avenue,
					 6th Floor, Washington, DC 20001, is adopted by
					 reference and made a part of this chapter. This incorporation by reference
					 includes all parts of the
International Energy Conservation
					 Code
subject to the amendments hereinafter set
					 forth.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 6 - Title

Current through June, 2024
IECC Section 101.1 is amended to read as follows:
101.1 Title.
This code shall be known as the
					 Energy Conservation Code of the State of Hawai'i and shall be cited as such. It
					 is referred to herein as "this code."
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 8 - INSULATION COMPONENT R-Value method

Current through June, 2024
IECC TABLE C402.1.3, OPAQUE THERMAL ENVELOPE INSULATION
					 COMPONENT REQUIREMENTS, R-VALUE METHOD is amended to read as follows:
CLIMATE ZONE 1,
Mass walls, R-5.7 ci (footnote j)
j. Mass walls 6" and greater in thickness are
				  excepted from ci requirement
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 9 - Above-grade walls

Current through June, 2024
IECC Section C402.2.2 is amended to read as follows:
C402.2.2 Above Grade Walls
.
The
					 minimum thermal resistance (R-value) of materials installed in the wall cavity
					 between framing members and continuously on the walls shall be as specified in
					 Table C402.1.3, based on framing type and construction materials used in the
					 wall assembly.
Exceptions:
Continuous insulation for above grade walls and mass walls
					 are not required when one of the following conditions are met:
1. Walls have a covering with a reflectance
				  of = 0.64; or
2. Walls have
				  overhangs with a projection factor equal to or greater than 0.3. The projection
				  factor is the horizontal distance from the surface of the wall to the farthest
				  most point of the overhang divided by the vertical distance from the
				  first-floor level to the bottom most point of the overhang.
3. Concrete, CMU and similar mass walls are 6
				  inches or greater in thickness.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 10 - Table C402.4

Current through June, 2024
Building Envelope Fenestration Maximum U-Factor and
					 SHGC Requirements
b is added to the IECC to read as
					 follows:
b. Jalousie windows are excepted
					 from SHGC requirements.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 11 - Area-weighted SHGC

Current through June, 2024
Section C402.4.3.5 is added to the IECC to read as
					 follows:
C402.4.3.5 Area-weighted SHGC.
In commercial
					 buildings, an area-weighted average of fenestration products shall be permitted
					 to satisfy SHGC requirements.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 12 - Door switches

Current through June, 2024
Section C403.2.3 is added to the IECC to read as
					 follows:
C403.2.3 Door switches.
Opaque and glass doors
					 opening to the outdoors in hotel and motel sleeping units, guest suites and
					 time-share condominiums, shall be provided with controls that disable the
					 mechanical cooling, or reset the cooling setpoint to 90°F or greater within
					 five minutes of the door opening. Mechanical cooling may remain enabled if the
					 outdoor air temperature is below the space temperature.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 13 - Sub-metering

Current through June, 2024
Section C405.10 is added to the IECC to read as
					 follows:
C405.10 Sub-metering.
In new buildings with
					 tenants, metering shall be collected for the entire building and individually
					 for each tenant occupying 1,000 ft 
					 2 (total enclosed and unenclosed)
					 (93 m 
					 2) or more. Tenants shal l have
					 access to data collected for their space. A tenant is defined as " one who
					 rents or leases from a landlord."
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 14 - Compliance

Current through June, 2024
IECC Section C501.4 is amended to read as follows:
C501.4 Compliance.
Alterations,
					 repairs, additions
and changes of occupancy to, or relocation of,
					 existing buildings and structures shall comply with the provisions and
					 regulations for
alterations, repairs, additions
and changes of
					 occupancy or relocation, as adopted by the authorities having
					 jurisdiction.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 15 - Roof replacement

Current through June, 2024
IECC Section C503.3.1 is amended to read as follows (note
					 that options are provided for this amendment):
C503.3.1 Roof replacement.
Roof replacement
					 shall comply with Section C402.1.3, C402.1.4, C402.1.5 or C407 where the
					 existing roof assembly is part of the building thermal envelope and contains
					 insulation entirely above the roof deck. Replacement of uninsulated roofs shall
					 include either initial reflectance [GREATER THAN OR EQUAL TO] 85% and aged
					 reflectance [GREATER THAN OR EQUAL TO] 75% 63% or at least two one of the
					 following:
1. EnergyStar compliant
				  covering
2. Radiant barrier,
				  or
3. Attic ventilation via solar
				  fan(s), ridge ventilation or gable vents
4. One or more exceptions in Section
				  C402.3
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 17 - Compliance

Current through June, 2024
IECC Section R401.2 is amended to read as follows:
R401.2 Compliance.
Projects shall comply with
					 one of the following:
1. Sections
				  R401.3 through R404
2. Sections
				  R405 and the provisions of Section R401 through R404 labeled
				  "Mandatory."
3. An energy rating
				  index (ERI) approach in Section R406.
4. The Tropical zone requirements in Section
				  R401.2.l.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 18 - Tropical zone

Current through June, 2024
IECC Section R401.2.1 is amended to read as follows:
R401.2.1 Tropical zone.
Residential
					 buildings
in the tropical zone at elevations below 2,400 feet (731.5
					 m) above sea level shall be deemed to comply with this chapter where the
					 following conditions are met:
1. Not
				  more than one-half of the dwelling unit is air conditioned
2. The dwelling unit is not heated.
3. Solar, wind or other renewable energy
				  source supplies not less than 90 percent of the energy for service water
				  heating.
4. Glazing in
dwelling units
shall have a maximum
solar heat gain
coefficient as specified in Table R402.1.2.
5. Skylights in dwelling units shall have a
				  max imum U-factor as specified in Table R402.l.4.
6. Permanently installed lighting is in
				  accordance with Section R404.
7.
				  The roof/ceiling complies with one of the following options:
a. Comply with one of the roof surface
				  options in Table C402.3 and install R-13 insulation or greater.
b. Install R-19 insulation or
				  greater.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 19 - General

Current through June, 2024
Section R401.3.1 is added to the IECC to read as
					 follows:
R401.3.1 Sampling
. For builders of multiple
					 single family and multi-family units of similar construction type and envelope
					 systems (i.e. production home building), air infiltration/duct testing may be
					 completed by following Chapter
					 6 ("standard for Sampled Ratings"), of
					 the current Residential Energy Service Network (RESNET) National Home Energy
					 Rating System Standards.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 20 - INSULATION AND FENESTRATION REQUIREMENTS BY COMPONENT

Current through June, 2024
IECC Table R402.1.2 is added to the table:
Window SHGC Requirements
Projection Factor of overhang from base of
								average window sill
SHGC
.25
<30 - .50
.40
[GREATER THAN OR EQUAL TO].50
N/A
Exception: North-facing windows with pf [GREATER THAN] .20
					 are exempt from the SHGC requirement. Overhangs shall extend 2 feet on each
					 side of window or to nearest wall, whichever is less.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 21 - INSULATION AND FENESTRATION REQUIREMENTS BY COMPONENTS

Current through June, 2024
IECC Table R402.1.2 is amended to read as follows:
Climate Zone 1
Mass Wall R-Value: ¾ or
					 NRj
.
j Exception: R-value for mass
					 walls are not required if mass walls meet one of the following
					 requirements:
1. have a reflectance
				  =0.64.
2. have overhangs with a
				  projection factor =0.3.
3. are =6
				  inches in thickness.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 22 - Specific insulation requirements (Prescriptive

Current through June, 2024
IECC Section R402.2 is amended to read as follows:
R402.2 Specific insulation requirements
					 (Prescriptive).
In addition to the requirements of Section R402.1,
					 insulation shall meet the specified requirements of Sections R402.2.1 through
					 R402.2.13.
Exception:
Above-grade walls and roof/ceilings shall be permitted to
					 comply with Section R407.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 23 - Mass walls

Current through June, 2024
IECC Section R402.2.5 Mass walls is amended to read as
					 follows:
1. Above-ground walls of
				  concrete block, (concrete masonry units) CMU, concrete, insulated concrete
				  form, masonry cavity, brick but not brick veneer, adobe, compressed earth
				  block, rammed earth, solid timber or solid logs.
2. Any wall having a heat capacity greater
				  than or equal to 6 Btu/ft2·°F (123
				  kJ/m2·K).
3. Concrete, CMU and similar mass walls are 6
				  inches or greater in thickness.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 24 - Glazed Fenestration SHGC

Current through June, 2024
IECC Section R402.3.2 Glazed fenestration SHGC is added to
					 the IECC to read as follows:
Exceptions:
2. Jalousie windows are excepted from SHGC
				  requirements.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 25 - Solar water heating

Current through June, 2024
Section R403.5.5 is added to the IECC to read as
					 follows:
R403.5.5 Solar water heating.
Solar water
					 heating systems are required for new single-family residential construction
					 pursuant to section
					 196-6.5,
					 HRS.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 26 - Ceiling fans

Current through June, 2024
Section R403.6.2 is added to the IECC to read as
					 follows:
R403.6.2 Ceiling fans.
A ceiling fan, rough-in
					 or whole house fan is provided for bedrooms and the largest space that is not
					 used as a bedroom, provided that the whole house mechanical ventilation system
					 complies with the requirements of Table R403.6.1.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 28 - Compliance

Current through June, 2024
IECC Section R501.4 is amended to read as follows:
R501.4 Compliance.
Alterations,
					 repairs, additions
and changes of occupancy to, or relocation of,
					 existing buildings and structures shall comply with the provisions and
					 regulations for
alterations, repairs, additions
and changes of
					 occupancy or relocation, as adopted by the authorities having
					 jurisdiction.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Energy Conservation Code › Subchapter 2 - AMENDMENTS TO THE 2018 ICC INTERNATIONAL ENERGY CONSERVATION CODE › 29 - Building envelope

Current through June, 2024
IECC Section R503.1.1 is amended to read as follows:
R503.1.1 Building envelope.
Exception:
The following alterations shall not
					 be required to comply with the requirements for new construction provided that
					 the energy use of the building is not increased:
5. Roofs without insulation in the cavity and
				  where the sheathing or insulation is exposed during a roof replacement shall
				  meet one of the following:
1. R-30 cavity
				  insulation or the cool roof requirements in Section C402.3 for residential
				  buildings.
2. R-19 cavity insulation
				  or the cool roof requirements in Section C402.3 for Tropical Zone residential
				  buildings.
3. When uninsulated roof
				  sheathing is exposed during alteration, at least two of the following must be
				  installed:
a. Energy Star compliant roof
				  covering;
b. Radiant
				  barrier;
c. Attic ventilation via
				  solar attic fans or ridge ventilation of gable ventilation; or
d. A minimum of one two exceptions listed in
				  C402.3.
Footnote to exception: Shake roofs on battens must be
					 replaced with materials that result in equal or improved energy
					 efficiency.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Fire Code › 3 - Definitions

Current through June, 2024
In this chapter, unless the context otherwise
				  requires:
"Annex" means the explanatory material attached to the NFPA
				  1, Fire Code.
"Authority having jurisdiction" or "AHJ" means an
				  organization, office, or individual responsible for enforcing the requirements
				  of a code or standard, or for approving equipment, materials, an installation,
				  or a procedure.
"NFPA" means the National Fire Protection
				  Association.
Hawaii Administrative Rules › Title 3 - DEPARTMENT OF ACCOUNTING AND GENERAL SERVICES › Building Code Council › State Fire Code › 4 - Adoption of the 2018 NFPA 1, Fire Code

Current through June, 2024
The NFPA 1, Fire Code, 2018 edition is made a part of this
				  chapter, subject to the amendments provided in this chapter. The annexes to the
				  NFPA 1, Fire Code are not adopted except as provided in this
				  chapter.