reglab/statecodes huggingface dataset:
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.193 - Containment and detection of releases

Current through June, 2024
(a) Secondary
					 containment systems must be:
(1) Designed,
					 installed, and operated to prevent any migration of materials or accumulated
					 liquid out of the system to the soil, ground water, or surface water at any
					 time during the use of the tank system; and
(2) Capable of detecting and collecting
					 releases and accumulated liquids until the collected material is removed.
Note to paragraph (a): If the collected material is a
						hazardous waste under part 261 of this chapter, it is subject to management as
						a hazardous waste in accordance with all applicable requirements of parts 262
						through 265, 266, and 268 of this chapter. If the collected material is
						discharged through a point source to waters of the United States, it is subject
						to the requirements of sections 301, 304, and 402 of the Clean Water Act, as
						amended. If discharged to a Publicly Owned Treatment Works (POTW), it is
						subject to the requirements of section 307 of the Clean Water Act, as amended.
						If the collected material is released to the environment, it may be subject to
						the reporting requirements of 40 CFR part 302 .
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.194 - General operating requirements

Current through June, 2024
(a) Hazardous
					 secondary materials or treatment reagents must not be placed in a tank system
					 if they could cause the tank, its ancillary equipment, or the containment
					 system to rupture, leak, corrode, or otherwise fail.
(b) The remanufacturer or other person that
					 stores or treats the hazardous secondary material must use appropriate controls
					 and practices to prevent spills and overflows from tank or containment systems.
					 These include at a minimum:
(1) Spill
					 prevention controls (e.g., check valves, dry disconnect couplings);
(2) Overfill prevention controls (e.g., level
					 sensing devices, high level alarms, automatic feed cutoff, or bypass to a
					 standby tank); and
(3) Maintenance
					 of sufficient freeboard in uncovered tanks to prevent overtopping by wave or
					 wind action or by precipitation.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.195 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.196 - Response to leaks or spills and disposition of leaking or unfit-for-use tank systems

Current through June, 2024
A tank system or secondary containment system from which
						there has been a leak or spill, or which is unfit for use, must be removed from
						service immediately, and the remanufacturer or other person that stores or
						treats the hazardous secondary material must satisfy the following
						requirements:
(a) Cessation of use;
					 prevent flow or addition of materials. The remanufacturer or other person that
					 stores or treats the hazardous secondary material must immediately stop the
					 flow of hazardous secondary material into the tank system or secondary
					 containment system and inspect the system to determine the cause of the
					 release.
(b) Removal of material
					 from tank system or secondary containment system.
(1) If the release was from the tank system,
					 the remanufacturer or other person that stores or treats the hazardous
					 secondary material must, within 24 hours after detection of the leak or, if the
					 remanufacturer or other person that stores or treats the hazardous secondary
					 material demonstrates that it is not possible, at the earliest practicable
					 time, remove as much of the material as is necessary to prevent further release
					 of hazardous secondary material to the environment and to allow inspection and
					 repair of the tank system to be performed.
(2) If the material released was to a
					 secondary containment system, all released materials must be removed within 24
					 hours or in as timely a manner as is possible to prevent harm to human health
					 and the environment.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.197 - Termination of remanufacturing exclusion

Current through June, 2024
Hazardous secondary material stored in units more than 90
						days after the unit ceases to operate under the remanufacturing exclusion at
						40
						CFR 261.4(a)(27) or
						otherwise ceases to be operated for manufacturing, or for storage of a product
						or a raw material, then becomes subject to regulation as hazardous waste under
						parts 261 through 266, 268, 270, and 124 of this chapter, as
						applicable.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.198 - Special requirements for ignitable or reactive materials

Current through June, 2024
(a) Ignitable or reactive material must not
					 be placed in tank systems, unless the material is stored or treated in such a
					 way that it is protected from any material or conditions that may cause the
					 material to ignite or react.
(b)
					 The remanufacturer or other person that stores or treats hazardous secondary
					 material which is ignitable or reactive must store or treat the hazardous
					 secondary material in a tank that is in compliance with the requirements for
					 the maintenance of protective distances between the material management area
					 and any public ways, streets, alleys, or an adjoining property line that can be
					 built upon as required in Tables 2-1 through 2-6 of the National Fire
					 Protection Association's "Flammable and Combustible Liquids Code," (1977 or
					 1981), (incorporated by reference, see § 260.11).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.199 - Special requirements for incompatible materials

Current through June, 2024
(a)
					 Incompatible materials must not be placed in the same tank system.
(b) Hazardous secondary material must not be
					 placed in a tank system that has not been decontaminated and that previously
					 held an incompatible material.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart J - Tank Systems › Section 11-261.200 - Air emission standards

Current through June, 2024
The remanufacturer or other person that stores or treats
						the hazardous secondary material shall manage all hazardous secondary material
						placed in a tank in accordance with the applicable requirements of subparts AA,
						BB, and CC of this part.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart M - Emergency Preparedness and Response for Management of Excluded Hazardous Secondary Materials › Section 11-261.400 - Applicability

Current through June, 2024
The requirements of this subpart apply to those areas of
						an entity managing hazardous secondary materials excluded under §
						261.4(a)(23) and/or (24) where hazardous secondary materials are generated or
						accumulated on site.
(a) A generator
					 of hazardous secondary material, or an intermediate or reclamation facility
					 operating under a verified recycler variance under § 260.31(d), that
					 accumulates 6000 kg or less of hazardous secondary material at any time must
					 comply with §§ 261.410 and 261.411.
(b) A generator of hazardous secondary
					 material, or an intermediate or reclamation facility operating under a verified
					 recycler variance under § 260.31(d) that accumulates more than 6000 kg of
					 hazardous secondary material at any time must comply with §§ 261.410
					 and 261.420.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart M - Emergency Preparedness and Response for Management of Excluded Hazardous Secondary Materials › Section 11-261.410 - Preparedness and prevention

Current through June, 2024
(a) Maintenance and
					 operation of facility. Facilities generating or accumulating hazardous
					 secondary material must be maintained and operated to minimize the possibility
					 of a fire, explosion, or any unplanned sudden or non-sudden release of
					 hazardous secondary materials or hazardous secondary material constituents to
					 air, soil, or surface water which could threaten human health or the
					 environment.
(b) Required
					 equipment. All facilities generating or accumulating hazardous secondary
					 material must be equipped with the following, unless none of the hazards posed
					 by hazardous secondary material handled at the facility could require a
					 particular kind of equipment specified below:
(1) An internal communications or alarm
					 system capable of providing immediate emergency instruction (voice or signal)
					 to facility personnel;
(2) A
					 device, such as a telephone (immediately available at the scene of operations)
					 or a hand-held two-way radio, capable of summoning emergency assistance from
					 local police departments, fire departments, or state or local emergency
					 response teams;
(3) Portable fire
					 extinguishers, fire control equipment (including special extinguishing
					 equipment, such as that using foam, inert gas, or dry chemicals), spill control
					 equipment, and decontamination equipment; and
(4) Water at adequate volume and pressure to
					 supply water hose streams, or foam producing equipment, or automatic
					 sprinklers, or water spray systems.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart M - Emergency Preparedness and Response for Management of Excluded Hazardous Secondary Materials › Section 11-261.411 - Emergency procedures for facilities generating or accumulating 6000 kg or less of hazardous secondary material

Current through June, 2024
A generator or an intermediate or reclamation facility
						operating under a verified recycler variance under § 260.31(d) that
						generates or accumulates 6000 kg or less of hazardous secondary material must
						comply with the following requirements:
(a) At all times there must be at least one
					 employee either on the premises or on call (i.e., available to respond to an
					 emergency by reaching the facility within a short period of time) with the
					 responsibility for coordinating all emergency response measures specified in
					 paragraph (d) of this section. This employee is the emergency
					 coordinator.
(b) The generator or
					 intermediate or reclamation facility operating under a verified recycler
					 variance under §260.31(d) must post the following information next to the
					 telephone:
(1) The name and telephone number
					 of the emergency coordinator;
(2)
					 Location of fire extinguishers and spill control material, and, if present,
					 fire alarm; and
(3) The telephone
					 number of the fire department, unless the facility has a direct
					 alarm.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart M - Emergency Preparedness and Response for Management of Excluded Hazardous Secondary Materials › Section 11-261.420 - Contingency planning and emergency procedures for facilities generating or accumulating more than 6000 kg of hazardous secondary material

Current through June, 2024
A generator or an intermediate or reclamation facility
						operating under a verified recycler variance under § 260.31(d) that
						generates or accumulates more than 6000 kg of hazardous secondary material must
						comply with the following requirements:
(a) Purpose and implementation of contingency
					 plan.
(1) Each generator or an intermediate or
					 reclamation facility operating under a verified recycler variance under §
					 260.31(d) that accumulates more than 6000 kg of hazardous secondary material
					 must have a contingency plan for his facility. The contingency plan must be
					 designed to minimize hazards to human health or the environment from fires,
					 explosions, or any unplanned sudden or non-sudden release of hazardous
					 secondary material or hazardous secondary material constituents to air, soil,
					 or surface water.
(2) The
					 provisions of the plan must be carried out immediately whenever there is a
					 fire, explosion, or release of hazardous secondary material or hazardous
					 secondary material constituents which could threaten human health or the
					 environment.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart AA - Air Emission Standards for Process Vents › Section 11-261.1030 - Applicability

Current through June, 2024
The regulations in this subpart apply to process vents
						associated with distillation, fractionation, thin-film evaporation, solvent
						extraction, or air or stream stripping operations that manage hazardous
						secondary materials excluded under the remanufacturing exclusion at §
						261.4(a)(27) with concentrations of at least 10 ppmw, unless the process vents
						are equipped with operating air emission controls in accordance with the
						requirements of an applicable Clean Air Act regulation codified under 40 CFR
						part 60, part 61, or part 63.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart AA - Air Emission Standards for Process Vents › Section 11-261.1032 - Standards: Process vents

Current through June, 2024
(a) The
					 remanufacturer or other person that stores or treats hazardous secondary
					 materials in hazardous secondary material management units with process vents
					 associated with distillation, fractionation, thin-film evaporation, solvent
					 extraction, or air or steam stripping operations managing hazardous secondary
					 material with organic concentrations of at least 10 ppmw shall either:
(1) Reduce total organic emissions from all
					 affected process vents at the facility below 1.4 kg/h (3 lb/h) and 2.8 Mg/yr
					 (3.1 tons/yr), or
(2) Reduce, by
					 use of a control device, total organic emissions from all affected process
					 vents at the facility by 95 weight percent.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart AA - Air Emission Standards for Process Vents › Section 11-261.1033 - Standards: Closed-vent systems and control devices

Current through June, 2024
(a)
(1) The remanufacturer or other person that
					 stores or treats the hazardous secondary materials in hazardous secondary
					 material management units using closed-vent systems and control devices used to
					 comply with provisions of this part shall comply with the provisions of this
					 section.
(2) [Reserved]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart AA - Air Emission Standards for Process Vents › Section 11-261.1034 - Test methods and procedures

Current through June, 2024
(a) Each
					 remanufacturer or other person that stores or treats the hazardous secondary
					 material subject to the provisions of this subpart shall comply with the test
					 methods and procedural requirements provided in this section.
(b) When a closed-vent system is tested for
					 compliance with no detectable emissions, as required in § 261.1033(l) of
					 this subpart, the test shall comply with the following requirements:
(1) Monitoring shall comply with Reference
					 Method 21 in 40 CFR part 60 .
(2)
					 The detection instrument shall meet the performance criteria of Reference
					 Method 21.
(3) The instrument shall
					 be calibrated before use on each day of its use by the procedures specified in
					 Reference Method 21.
(4)
					 Calibration gases shall be:
(i) Zero air
					 (less than 10 ppm of hydrocarbon in air).
(ii) A mixture of methane or n-hexane and air
					 at a concentration of approximately, but less than, 10,000 ppm methane or
					 n-hexane.
(5) The
					 background level shall be determined as set forth in Reference Method
					 21.
(6) The instrument probe shall
					 be traversed around all potential leak interfaces as close to the interface as
					 possible as described in Reference Method 21.
(7) The arithmetic difference between the
					 maximum concentration indicated by the instrument and the background level is
					 compared with 500 ppm for determining compliance.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart AA - Air Emission Standards for Process Vents › Section 11-261.1035 - Recordkeeping requirements

Current through June, 2024
(a)
(1) Each remanufacturer or other person that
					 stores or treats the hazardous secondary material subject to the provisions of
					 this subpart shall comply with the recordkeeping requirements of this section.
(2) A remanufacturer or other
					 person that stores or treats the hazardous secondary material of more than one
					 hazardous secondary material management unit subject to the provisions of this
					 subpart may comply with the recordkeeping requirements for these hazardous
					 secondary material management units in one recordkeeping system if the system
					 identifies each record by each hazardous secondary material management
					 unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart AA - Air Emission Standards for Process Vents › Section 11-261.1036-11-261.1049 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1050 - Applicability

Current through June, 2024
(a) The regulations in this subpart apply to
					 equipment that contains hazardous secondary materials excluded under the
					 remanufacturing exclusion at § 261.4(a)(27), unless the equipment
					 operations are subject to the requirements of an applicable Clean Air Act
					 regulation codified under 40 CFR part 60, part 61, or part 63.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1051 - Definitions

Current through June, 2024
As used in this subpart, all terms shall have the meaning
						given them in § 261.1031, the Resource Conservation and Recovery Act, and
						40 CFR parts 260-266.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1052 - Standards: Pumps in light liquid service

Current through June, 2024
(a)
(1) Each pump in light liquid service shall
					 be monitored monthly to detect leaks by the methods specified in §
					 261.1063(b), except as provided in paragraphs (d), (e), and (f) of this
					 section.
(2) Each pump in light
					 liquid service shall be checked by visual inspection each calendar week for
					 indications of liquids dripping from the pump seal.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1053 - Standards: Compressors

Current through June, 2024
(a) Each compressor
					 shall be equipped with a seal system that includes a barrier fluid system and
					 that prevents leakage of total organic emissions to the atmosphere, except as
					 provided in paragraphs (h) and (i) of this section.
(b) Each compressor seal system as required
					 in paragraph (a) of this section shall be:
(1)
					 Operated with the barrier fluid at a pressure that is at all times greater than
					 the compressor stuffing box pressure, or
(2) Equipped with a barrier fluid system that
					 is connected by a closed-vent system to a control device that complies with the
					 requirements of § 261.1060, or
(3) Equipped with a system that purges the
					 barrier fluid into a hazardous secondary material stream with no detectable
					 emissions to atmosphere.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1054 - Standards: Pressure relief devices in gas/vapor service

Current through June, 2024
(a)
					 Except during pressure releases, each pressure relief device in gas/vapor
					 service shall be operated with no detectable emissions, as indicated by an
					 instrument reading of less than 500 ppm above background, as measured by the
					 method specified in § 261.1063(c).
(b)
(1)
					 After each pressure release, the pressure relief device shall be returned to a
					 condition of no detectable emissions, as indicated by an instrument reading of
					 less than 500 ppm above background, as soon as practicable, but no later than 5
					 calendar days after each pressure release, except as provided in §
					 261.1059.
(2) No later than 5
					 calendar days after the pressure release, the pressure relief device shall be
					 monitored to confirm the condition of no detectable emissions, as indicated by
					 an instrument reading of less than 500 ppm above background, as measured by the
					 method specified in § 261.1063(c).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1055 - Standards: Sampling connection systems

Current through June, 2024
(a) Each sampling
					 connection system shall be equipped with a closed-purge, closed-loop, or
					 closed-vent system. This system shall collect the sample purge for return to
					 the process or for routing to the appropriate treatment system. Gases displaced
					 during filling of the sample container are not required to be collected or
					 captured.
(b) Each closed-purge,
					 closed-loop, or closed-vent system as required in paragraph (a) of this section
					 shall meet one of the following requirements:
(1) Return the purged process fluid directly
					 to the process line;
(2) Collect
					 and recycle the purged process fluid; or
(3) Be designed and operated to capture and
					 transport all the purged process fluid to a material management unit that
					 complies with the applicable requirements of §§ 261.1084 through
					 264.1086 of this subpart or a control device that complies with the
					 requirements of § 261.1060 of this subpart.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1056 - Standards: Open-ended valves or lines

Current through June, 2024
(a)
(1) Each open-ended valve or line shall be
					 equipped with a cap, blind flange, plug, or a second valve.
(2) The cap, blind flange, plug, or second
					 valve shall seal the open end at all times except during operations requiring
					 hazardous secondary material stream flow through the open-ended valve or
					 line.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1057 - Standards: Valves in gas/vapor service or in light liquid service

Current through June, 2024
(a) Each valve in gas/vapor or light liquid
					 service shall be monitored monthly to detect leaks by the methods specified in
					 2611063(b) and shall comply with paragraphs (b) through (e) of this section,
					 except as provided in paragraphs (f), (g), and (h) of this section and 2611061
					 and 2611062.
(b) If an instrument
					 reading of 10,000 ppm or greater is measured, a leak is detected.
(c)
(1) Any
					 valve for which a leak is not detected for two successive months may be
					 monitored the first month of every succeeding quarter, beginning with the next
					 quarter, until a leak is detected.
(2) If a leak is detected, the valve shall be
					 monitored monthly until a leak is not detected for two successive
					 months,
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1058 - Standards: Pumps and valves in heavy liquid service, pressure relief devices in light liquid or heavy liquid service, and flanges and other connectors

Current through June, 2024
(a) Pumps and
					 valves in heavy liquid service, pressure relief devices in light liquid or
					 heavy liquid service, and flanges and other connectors shall be monitored
					 within five days by the method specified in § 261.1063(b) if evidence of a
					 potential leak is found by visual, audible, olfactory, or any other detection
					 method.
(b) If an instrument
					 reading of 10,000 ppm or greater is measured, a leak is detected.
(c)
(1)
					 When a leak is detected, it shall be repaired as soon as practicable, but not
					 later than 15 calendar days after it is detected, except as provided in §
					 261.1059.
(2) The first attempt at
					 repair shall be made no later than 5 calendar days after each leak is detected.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1059 - Standards: Delay of repair

Current through June, 2024
(a) Delay of repair
					 of equipment for which leaks have been detected will be allowed if the repair
					 is technically infeasible without a hazardous secondary material management
					 unit shutdown. In such a case, repair of this equipment shall occur before the
					 end of the next hazardous secondary material management unit
					 shutdown.
(b) Delay of repair of
					 equipment for which leaks have been detected will be allowed for equipment that
					 is isolated from the hazardous secondary material management unit and that does
					 not continue to contain or contact hazardous secondary material with organic
					 concentrations at least 10 percent by weight.
(c) Delay of repair for valves will be
					 allowed if:
(1) The remanufacturer or other
					 person that stores or treats the hazardous secondary material determines that
					 emissions of purged material resulting from immediate repair are greater than
					 the emissions likely to result from delay of repair.
(2) When repair procedures are effected, the
					 purged material is collected and destroyed or recovered in a control device
					 complying with § 261.1060.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1061 - Alternative standards for valves in gas/vapor service or in light liquid service: percentage of valves allowed to leak

Current through June, 2024
(a) A
					 remanufacturer or other person that stores or treats the hazardous secondary
					 material subject to the requirements of § 261.1057 may elect to have all
					 valves within a hazardous secondary material management unit comply with an
					 alternative standard that allows no greater than 2 percent of the valves to
					 leak.
(b) The following
					 requirements shall be met if a remanufacturer or other person that stores or
					 treats the hazardous secondary material decides to comply with the alternative
					 standard of allowing 2 percent of valves to leak:
(1) A performance test as specified in
					 paragraph (c) of this section shall be conducted initially upon designation,
					 annually, and at other times requested by the director.
(2) If a valve leak is detected, it shall be
					 repaired in accordance with § 261.1057(d) and (e).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1062 - Alternative standards for valves in gas/vapor service or in light liquid service: skip period leak detection and repair

Current through June, 2024
(a) A
					 remanufacturer or other person that stores or treats the hazardous secondary
					 material subject to the requirements of § 261.1057 may elect for all
					 valves within a hazardous secondary material management unit to comply with one
					 of the alternative work practices specified in paragraphs (b)(2) and (3) of
					 this section.
(b)
(1) A remanufacturer or other person that
					 stores or treats the hazardous secondary material shall comply with the
					 requirements for valves, as described in § 261.1057, except as described
					 in paragraphs (b)(2) and (3) of this section.
(2) After two consecutive quarterly leak
					 detection periods with the percentage of valves leaking equal to or less than
					 two percent, a remanufacturer or other person that stores or treats the
					 hazardous secondary material may begin to skip one of the quarterly leak
					 detection periods (i.e., monitor for leaks once every six months) for the
					 valves subject to the requirements in § 261.1057 of this
					 subpart.
(3) After five consecutive
					 quarterly leak detection periods with the percentage of valves leaking equal to
					 or less than two percent, a remanufacturer or other person that stores or
					 treats the hazardous secondary material may begin to skip three of the
					 quarterly leak detection periods (i.e., monitor for leaks once every year) for
					 the valves subject to the requirements in § 261.1057 of this
					 subpart.
(4) If the percentage of
					 valves leaking is greater than two percent, the remanufacturer or other person
					 that stores or treats the hazardous secondary material shall monitor monthly in
					 compliance with the requirements in § 261.1057, but may again elect to use
					 this section after meeting the requirements of § 261.1057(c)(1).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1063 - Test methods and procedures

Current through June, 2024
(a) Each
					 remanufacturer or other person that stores or treats the hazardous secondary
					 material subject to the provisions of this subpart shall comply with the test
					 methods and procedures requirements provided in this section.
(b) Leak detection monitoring, as required in
					 §§ 261.1052-261.1062, shall comply with the following requirements:
(1) Monitoring shall comply with Reference
					 Method 21 in 40 CFR part 60 .
(2)
					 The detection instrument shall meet the performance criteria of Reference
					 Method 21.
(3) The instrument shall
					 be calibrated before use on each day of its use by the procedures specified in
					 Reference Method 21.
(4)
					 Calibration gases shall be:
(i) Zero air
					 (less than 10 ppm of hydrocarbon in air).
(ii) A mixture of methane or n-hexane and air
					 at a concentration of approximately, but less than, 10,000 ppm methane or
					 n-hexane.
(5) The
					 instrument probe shall be traversed around all potential leak interfaces as
					 close to the interface as possible as described in Reference Method
					 21.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1064 - Recordkeeping requirements

Current through June, 2024
(a)
(1) Each remanufacturer or other person that
					 stores or treats the hazardous secondary material subject to the provisions of
					 this subpart shall comply with the recordkeeping requirements of this section.
(2) A remanufacturer or other
					 person that stores or treats the hazardous secondary material in more than one
					 hazardous secondary material management unit subject to the provisions of this
					 subpart may comply with the recordkeeping requirements for these hazardous
					 secondary material management units in one recordkeeping system if the system
					 identifies each record by each hazardous secondary material management
					 unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-261.1065-11-261.1079 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart CC - Air Emission Standards for Tanks and Containers › Section 11-261.1080 - Applicability

Current through June, 2024
(a) The regulations in this subpart apply to
					 tanks and containers that contain hazardous secondary materials excluded under
					 the remanufacturing exclusion at § 261.4(a)(27), unless the tanks and
					 containers are equipped with and operating air emission controls in accordance
					 with the requirements of an applicable Clean Air Act regulations codified under
					 40 CFR part 60, part 61, or part 63.
(b) [Reserved]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart CC - Air Emission Standards for Tanks and Containers › Section 11-261.1082 - Standards: General

Current through June, 2024
(a) This section
					 applies to the management of hazardous secondary material in tanks and
					 containers subject to this subpart.
(b) The remanufacturer or other person that
					 stores or treats the hazardous secondary material shall control air pollutant
					 emissions from each hazardous secondary material management unit in accordance
					 with standards specified in §§ 261.1084 through 261.1087 of this
					 subpart, as applicable to the hazardous secondary material management unit,
					 except as provided for in paragraph (c) of this section.
(c) A tank or container is exempt from
					 standards specified in §§ 261.1084 through 261.1087 of this subpart,
					 as applicable, provided that the hazardous secondary material management unit
					 is a tank or container for which all hazardous secondary material entering the
					 unit has an average VO concentration at the point of material origination of
					 less than 500 parts per million by weight (ppmw). The average VO concentration
					 shall be determined using the procedures specified in § 261.1083(a) of
					 this subpart. The remanufacturer or other person that stores or treats the
					 hazardous secondary material shall review and update, as necessary, this
					 determination at least once every 12 months following the date of the initial
					 determination for the hazardous secondary material streams entering the
					 unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart CC - Air Emission Standards for Tanks and Containers › Section 11-261.1083 - Material determination procedures

Current through June, 2024
(a) Material
					 determination procedure to determine average volatile organic (VO)
					 concentration of a hazardous secondary material at the point of material
					 origination.
(1) Determining average VO
					 concentration at the point of material origination. A remanufacturer or other
					 person that stores or treats the hazardous secondary material shall determine
					 the average VO concentration at the point of material origination for each
					 hazardous secondary material placed in a hazardous secondary material
					 management unit exempted under the provisions of §261.1082(c) of this
					 subpart from using air emission controls in accordance with standards specified
					 in §§ 261.1084 through 261.1087 of this subpart, as applicable to the
					 hazardous secondary material management unit.
(i) An initial determination of the average
					 VO concentration of the material stream shall be made before the first time any
					 portion of the material in the hazardous secondary material stream is placed in
					 a hazardous secondary material management unit exempted under the provisions of
					 §261.1082(c) of this subpart from using air emission controls, and
					 thereafter an initial determination of the average VO concentration of the
					 material stream shall be made for each averaging period that a hazardous
					 secondary material is managed in the unit; and
(ii) Perform a new material determination
					 whenever changes to the source generating the material stream are reasonably
					 likely to cause the average VO concentration of the hazardous secondary
					 material to increase to a level that is equal to or greater than the applicable
					 VO concentration limits specified in § 261.1082 of this subpart.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart CC - Air Emission Standards for Tanks and Containers › Section 11-261.1084 - Standards: tanks

Current through June, 2024
(a) The provisions of this section apply to
					 the control of air pollutant emissions from tanks for which § 261.1082(b)
					 of this subpart references the use of this section for such air emission
					 control.
(b) The remanufacturer or
					 other person that stores or treats the hazardous secondary material shall
					 control air pollutant emissions from each tank subject to this section in
					 accordance with the following requirements as applicable:
(1) For a tank that manages hazardous
					 secondary material that meets all of the conditions specified in paragraphs
					 (b)(1)(i) through (iii) of this section, the remanufacturer or other person
					 that stores or treats the hazardous secondary material shall control air
					 pollutant emissions from the tank in accordance with the Tank Level 1 controls
					 specified in paragraph (c) of this section or the Tank Level 2 controls
					 specified in paragraph (d) of this section.
(i) The hazardous secondary material in the
					 tank has a maximum organic vapor pressure which is less than the maximum
					 organic vapor pressure limit for the tank's design capacity category as
					 follows:
(A) For a tank design capacity equal
					 to or greater than 151 m3, the maximum organic vapor
					 pressure limit for the tank is 5.2 kPa.
(B) For a tank design capacity equal to or
					 greater than 75 m3 but less than 151
					 m3, the maximum organic vapor pressure limit for the
					 tank is 27.6 kPa.
(C) For a tank
					 design capacity less than 75 m3, the maximum organic
					 vapor pressure limit for the tank is 76.6 kPa.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart CC - Air Emission Standards for Tanks and Containers › Section 11-261.1085 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart CC - Air Emission Standards for Tanks and Containers › Section 11-261.1086 - Standards: containers

Current through June, 2024
(a) Applicability.
					 The provisions of this section apply to the control of air pollutant emissions
					 from containers for which § 261.1082(b) of this subpart references the use
					 of this section for such air emission control.
(b) General requirements.
(1) The remanufacturer or other person that
					 stores or treats the hazardous secondary material shall control air pollutant
					 emissions from each container subject to this section in accordance with the
					 following requirements, as applicable to the container.
(i) For a container having a design capacity
					 greater than 0.1 m3 and less than or equal to 0.46
					 m3, the remanufacturer or other person that stores
					 or treats the hazardous secondary material shall control air pollutant
					 emissions from the container in accordance with the Container Level 1 standards
					 specified in paragraph (c) of this section.
(ii) For a container having a design capacity
					 greater than 0.46 m3 that is not in light material
					 service, the remanufacturer or other person that stores or treats the hazardous
					 secondary material shall control air pollutant emissions from the container in
					 accordance with the Container Level 1 standards specified in paragraph (c) of
					 this section.
(iii) For a container
					 having a design capacity greater than 0.46 m3 that
					 is in light material service, the remanufacturer or other person that stores or
					 treats the hazardous secondary material shall control air pollutant emissions
					 from the container in accordance with the Container Level 2 standards specified
					 in paragraph (d) of this section.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 261.1 - HAZARDOUS WASTE MANAGEMENT: IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Part 261 - IDENTIFICATION AND LISTING OF HAZARDOUS WASTE › Subpart CC - Air Emission Standards for Tanks and Containers › Section 11-261.1088 - Inspection and monitoring requirements

Current through June, 2024
(a) The
					 remanufacturer or other person that stores or treats the hazardous secondary
					 material shall inspect and monitor air emission control equipment used to
					 comply with this subpart in accordance with the applicable requirements
					 specified in §§ 261.1084 through 261.1087 of this subpart.
(b) The remanufacture or other person that
					 stores or treats the hazardous secondary material shall develop and implement a
					 written plan and schedule to perform the inspections and monitoring required by
					 paragraph (a) of this section. The remanufacturer or other person that stores
					 or treats the hazardous secondary material shall keep the plan and schedule at
					 the facility.