reglab/statecodes huggingface dataset:
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1142 - Design and Plan Requirements-Electrical

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Electrical plans shall include a single
				  line diagram of the electrical equipment to be installed, altered or changed.
				  Complete load calculations of the electrical system shall be provided with
				  plans.
(b) Complete engineering
				  plans, specifications, calculations and supporting data, stamped and signed by
				  an electrical engineer, shall be submitted when the park's electrical main
				  service or any of the electrical wiring system exceeds the voltage of the
				  secondary system.
(c) Any person
				  applying for a permit to install additional electrical equipment in a park
				  shall submit the following information with the application for a permit to
				  construct:
(1) The size of the feeder circuit
				  and overcurrent protection of that feeder circuit; and
(2) The number of lots and the load of any
				  other electrical equipment supplied by the feeder circuit.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1144 - Electric Heating. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1146 - Voltage Drop

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The voltage drop shall not exceed five (5) percent on the
					 park electrical wiring system from the park service to the most remote outlet
					 on the system, except that taps to compensate for below normal full capacity
					 voltage may be used on the primary side of secondary distribution transformers
					 to correct for voltage drop on the primary feeders. The voltage of secondary
					 systems shall not exceed a nominal 240 volts.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1148 - Overcurrent Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Conductors shall be protected by
				  overcurrent protective devices. A fuse or circuit breaker rating shall not be
				  greater than the allowable ampacity of the conductors to be protected as
				  specified in Tables 310-16 through 310-19 found in the California Electrical
				  Code, except as provided in Articles 210, 240, and 430.
(b) All electrical equipment and devices,
				  including service equipment, transformers and receptacles, shall be protected
				  by overcurrent protective devices rated at not more than the rating of the
				  equipment or device, except as provided in Articles 210, 240, 430, and 450 of
				  the California Electrical Code.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1150 - Park Electrical Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each service equipment enclosure for the
				  park shall be provided with a single main disconnect switch or circuit breaker
				  lockable in the open position for disconnecting the electrical wiring system or
				  systems of the park.
(b) A
				  disconnecting means shall be provided for disconnecting each distribution
				  transformer. When the disconnecting means is not installed immediately adjacent
				  to the distribution transformer, it shall be identified as to its usage and
				  shall be arranged to be locked in the open position.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1151 - Lot Electrical Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A single disconnecting switch or circuit breaker shall be
					 provided in the lot service equipment for disconnecting the power supply to the
					 unit. The disconnecting switch, circuit breaker or its individual enclosure
					 shall be clearly marked to identify the lot serviced.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1152 - Ground-Fault Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Ground-fault protection of park service equipment shall be
					 provided for solidly grounded wye electrical services of more than 150 volts to
					 ground, but not exceeding 600 volts phase-to-phase for each service
					 disconnecting means rated at 1,000 amperes or more. Each service disconnecting
					 means rated 1000-amperes or more shall be performance tested when first
					 installed, as required by the California Electrical Code, section 230-95. The
					 test shall be conducted in accordance with approved instructions, which shall
					 be provided with the equipment. A written record of this test shall be made and
					 shall be available to the enforcement agency.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
2. Amendment filed 7-22-2005; operative
					 7-22-2005 pursuant to Government Code section 11343.4 (Register 2005, No.
					 29).
3. Editorial correction of section and HISTORY 2 (Register
					 2005, No. 33).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1153 - Equipment Grounding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Exposed noncurrent-carrying metal parts of fixed electrical
					 equipment shall be grounded as required by the California Electrical Code,
					 Article 250.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1154 - Primary System Grounding-600 Volts or Less

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) When the park electrical service is
				  supplied by a grounded system operated at 600 volts or less, an equipment
				  grounding conductor shall be run with the feeders of the park primary
				  electrical system to all equipment supplied by the primary electrical
				  system.
(b) Park primary electrical
				  systems within the park operated at 600 volts or less supplied by an ungrounded
				  system shall not be grounded.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1156 - Primary System Grounding-Over 600 Volts

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Park primary electrical systems within
				  the park operated at more than 600 volts supplied by a grounded system shall be
				  grounded at the park service.
(b)
				  Park primary electrical systems within the park operated at more than 600 volts
				  supplied by an ungrounded system shall not be grounded.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1158 - Secondary Systems-Lot Service Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The neutral conductor of all secondary systems supplying
					 lot service equipment shall be grounded at both the secondary system source and
					 the lot service equipment.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1160 - Secondary Systems-Other than Lot Service Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The neutral conductor of all secondary systems supplying
					 equipment other than lot service equipment shall be grounded as required by the
					 California Electrical Code, article 250.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1162 - Grounding Connections

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
System grounding conductors and equipment grounding
					 conductors shall be connected as required by the California Electrical Code,
					 article 250. The connection of a grounding conductor to a grounding electrode
					 shall be exposed and readily accessible.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1163 - Grounding of Units

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All exposed, noncurrent-carrying metal parts of a unit,
					 when connected to the lot service equipment, shall be grounded by means of a
					 grounding conductor run with the circuit conductors or in a listed power supply
					 cord provided with an approved polarized multi-prong plug. One prong of the
					 plug shall be for the sole purpose of connecting that grounding conductor, by
					 means of a listed and approved grounding receptacle, to the grounded terminal
					 at the lot service. The conductor shall be insulated and identified by a green
					 color.
1.
					 Renumbering of former section 1648 to new section 1163, including amendment of
					 section heading and section, filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18550 and 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1164 - Feeder Assembly

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The neutral conductor and the equipment grounding conductor
					 of the feeder assembly supplying service equipment, shall be connected to the
					 grounding electrode at each lot service enclosure.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1166 - Grounding Conductors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Only copper grounding conductors shall be used to connect
					 electrical systems to a grounding electrode. Grounding conductors shall be
					 protected from physical damage by cabinet enclosures, raceways, or cable
					 armor.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1170 - Protection of Outdoor Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) All electrical equipment, including
				  switches, circuit breakers, receptacles, lighting fixtures, control equipment,
				  and metering devices located in either damp or wet locations or outside of a
				  unit, accessory building or structure, or a building component designed as a
				  weatherproof structure, shall be constructed of, or installed in, equipment
				  approved for damp or wet locations.
(b) Meter sockets, without meters installed,
				  shall be blanked off with an approved blanking plate before the service is
				  energized.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1172 - High-Voltage Conductors. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1176 - Aluminum Conductors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Connections of aluminum conductors shall
				  be made only inside boxes or equipment enclosures which are designed and
				  installed to prevent the entry or accumulation of moisture within the
				  enclosure.
(b) Only connectors
				  which are listed for use with aluminum conductors shall be used to connect
				  aluminum conductors. If more than one conductor is connected to a connector,
				  the connector shall be provided with a terminal fitting for each
				  conductor.
(c) Prior to inserting
				  an aluminum conductor into the connector, the conductor from which the
				  insulation has been removed shall be wire-brushed and sealed with an approved
				  oxide-inhibiting joint compound.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1178 - Mechanical Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where subject to physical damage from vehicular traffic or
					 other causes, the lot service equipment shall be protected by posts, fencing or
					 other barriers approved by the enforcement agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1182 - Installation of Lot Service Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Approved lot service equipment supplied
				  by underground feeders may be of the self-supporting type and shall be
				  stabilized by concrete not less than three and one-half (3 ½ ) inches
				  thick and surrounding the equipment base by not less than six (6) inches beyond
				  the equipment base in all directions.
(b) Approved lot service equipment supplied
				  by underground feeders requiring installation on a mounting post shall be
				  securely fastened to a nominal four (4) inches by four (4) inches redwood or
				  pressure treated post or equivalent. The post shall be installed not less than
				  twenty-four (24) inches in the earth and stabilized by a concrete pad. The
				  concrete pad shall be not less than three and one-half (3 ½ ) inches
				  thick, surrounding the post base by not less than six (6) inches beyond the
				  post base in all directions. The equipment shall be mounted with the bottom of
				  the equipment not less than twelve (12) inches above the stabilizing concrete
				  pad.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1183 - Access to Electrical Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All park or lot service equipment shall be accessible by an
					 unobstructed entrance or passageway not less than twenty-four (24) inches in
					 width and seventy-eight (78) inches high and shall have a working space not
					 less than thirty (30) inches wide and thirty-six (36) inches deep in front of
					 any panel opening on the service equipment used for examination, servicing,
					 adjustment, or maintenance. The lot service equipment shall be located and
					 maintained not less than twelve (12) inches nor more than seventy-eight (78)
					 inches above the stabilizing pad.
EXCEPTION: parks constructed prior to July 1, 1979, shall
					 have a working space not less than thirty (30) inches wide and thirty (30)
					 inches deep in front of and centered on the service
					 equipment.
1.
					 Renumbering of former section 1646 to new section 1183, including amendment of
					 section, filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment filed 7-22-2005;
					 operative 7-22-2005 pursuant to Government Code section 11343.4 (Register 2005,
					 No. 29).
3. Editorial correction of HISTORY 2 (Register 2005, No.
					 33).
4. Amendment filed 1-21-2009; operative 1-21-2009 pursuant to
					 Government Code section 11343.4 (Register 2009, No.
					 4).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18550 and 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1184 - Lot Location

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Equipment to supply electrical power to a unit shall be
					 located within four (4) feet of the unit or the proposed location of the
					 unit.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Amendment filed 7-6-2004;
					 operative 7-6-2004 pursuant to Government Code section 11343.4 (Register 2004,
					 No. 28).
Note: Authority cited: Sections 18300 and 18670, Health
						and Safety Code. Reference: Section 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1185 - Electrical Appliances, Equipment, and Air Conditioning

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) When electrical equipment or fixed
				  appliances are installed to serve a unit, an accessory building or structure,
				  or building component, the installation shall be supplied by one of the
				  following methods:
(1) By an individual branch
				  circuit from the unit terminating in a single outlet or junction box, provided
				  a permit is obtained from the department for the alteration to the unit. An
				  alteration permit shall be obtained from the department pursuant to the
				  requirements of Title 25, California Code of Regulations, Chapter 3, section
				  4042.
(2) By means of a permanent
				  wiring method to the lot electrical service equipment, provided the lot service
				  equipment is designed and listed for the additional load.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1186 - Lot Receptacles

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A receptacle used to supply electrical
				  energy to a unit shall conform with the American National Standards
				  Institute-National Electrical Manufacturers Association (ANSI-NEMA) Standard,
				  WD-6, 1997 for one of the following configurations:
(1) 125/250 volts, 50-amperes, 3 pole, 4
				  wire, grounding type for 120/240 volt systems.
(2) 125 volts, 30-amperes, 2 pole, 3 wire,
				  grounding type for 120 volt systems.
(3) 125 volts, 20-amperes, 2 pole, 3 wire,
				  grounding type for supplying units having only one 15 or 20-ampere branch
				  circuit.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1188 - Existing Electrical Installations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Lot service equipment shall have the
				  capacity to supply the unit, appliance, accessory building or structure, and
				  building component located on the lot. The park operator may prohibit the
				  installation of a unit, appliance, accessory building or structure, or building
				  component that exceeds the rated capacity of the lot electrical service, unless
				  the load in the unit, appliance, accessory building or structure, or building
				  component is reduced. If the unit or electrical appliance is allowed to be
				  installed by the park and the connected load on the lot exceeds the rated
				  capacity of the lot electrical service equipment, the lot electrical service
				  equipment and feeders shall be replaced with equipment and conductors properly
				  rated to supply the unit, appliance, or accessory building or structure.
				  Notwithstanding the provisions of this subsection, park approval is required
				  when an alteration or addition to the existing electrical system of the unit,
				  appliance, accessory building or structure, or building component will exceed
				  the rated capacity of the lot service equipment.
(b) The enforcement agency may order unsafe
				  installations of existing electrical systems or portions thereof to be
				  reconstructed or altered, if necessary for the protection of life and
				  property.
(c) The use of electrical
				  equipment and installations in existence prior to the effective date of
				  applicable amendments to this chapter may be continued, provided such equipment
				  and installations are maintained in safe operating condition and the calculated
				  connected loads do not exceed the rated ampacity of such equipment and
				  installations.
(d) Lot electrical
				  service equipment may continue supplying accessory buildings or structures or
				  building components or other electrical equipment located outside the unit,
				  provided the lot electrical service has the capacity to serve them and the
				  equipment is maintained in a safe operating condition.
1.
					 Renumbering of former section 1644 to new section 1188, including amendment of
					 section, filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18550, 18605, 18610 and 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 3 - Electrical Requirements › Section 1190 - Authority to Order Disconnect-Electrical

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The enforcement agency is authorized to
				  require any electrical installation or equipment found to be defective, and in
				  such condition as to endanger life or property, to be disconnected.
(b) Installations which have been
				  disconnected shall not be re-energized until a permit has been obtained to
				  repair the electrical installation or equipment, and the work has been
				  inspected and approved by the enforcement agency.
1.
					 Renumbering of former section 1654 to new section 1190, including amendment of
					 section, filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18550 and 18670, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1200 - Application and Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The requirements of this article shall apply to the construction, installation,
				  arrangement, alteration, use, maintenance, and repair of fuel gas and oil
				  equipment and installations for supplying fuel gas and oil to parks, units, and
				  accessory building or structures in all parts of the state.
(b) Existing construction, connections, and
				  installations of fuel gas or oil made before the effective date of the
				  requirements of this chapter may continue in use so long as they were in
				  compliance with requirements in effect at the date of their installation and
				  are not found to be substandard.
1. Repealer
					 and new section filed 8-22-85; effective upon filing pursuant to Government
					 Code Section 11346.2(d) (Register 85, No. 36).
2. Amendment of
					 article heading, section and NOTE filed 7-6-2004; operative 7-6-2004 pursuant
					 to Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Sections 18300, 18610 and 18690,
						Health and Safety Code. Reference: Sections 18610 and 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1202 - Application and Scope. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18300, 18610, 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1204 - Permit Required. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18500, 18501, 18502 and 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1208 - Basic Fuel Gas Regulations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Except as otherwise permitted or required
				  by this article, all fuel gas equipment and installations for supplying fuel
				  gas to units or accessory buildings or structures, and fuel gas piping systems
				  outside of permanent buildings in parks, shall comply with the requirements
				  found in the California Plumbing Code, Chapter 12.
(b) The requirements for fuel gas equipment
				  and installations within permanent buildings in parks are located in the
				  California Mechanical Code and the California Plumbing Code unless otherwise
				  provided by this chapter. However, in a city, county, or city and county, which
				  has assumed responsibility for enforcement of the Mobilehome Parks Act and
				  Special Occupancy Parks Act, pursuant to sections 18300 and 18865 of the Health
				  and Safety Code, and has adopted and is enforcing a plumbing and mechanical
				  code equal to or greater than the requirements of the California Plumbing Code
				  and the California Mechanical Code, may enforce its code as it pertains to
				  permanent buildings.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36)
2. Amendment filed 5-26-87;
					 operative 6-25-87 (Register 87, No. 23).
3. Amendment filed
					 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Sections 18300 and 18690, Health
						and Safety Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1210 - Liquefied Petroleum Gas (LPG)

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All LPG equipment and installations of tanks one hundred
					 twenty-five (125) US gallons or larger shall comply with the applicable
					 provisions of the Unfired Pressure Vessel Safety Orders, California Code of
					 Regulations, Title 8, Division 1, Chapter 4, Subchapter 1, unless otherwise
					 provided by this chapter.
1. Amendment
					 filed 8-22-85; effective upon filing pursuant to Government Code Section
					 11346.2(d) (Register 85, No. 36).
2. Amendment of section heading
					 and section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code
					 section 11343.4 (Register 2004, No. 28).
3. Amendment filed
					 1-21-2009; operative 1-21-2009 pursuant to Government Code section 11343.4
					 (Register 2009, No. 4).
Note: Authority cited: Sections 18300 and 18690, Health
						and Safety Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1211 - LPG Tanks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  LPG tank installations in parks must conform to the provisions related to LPG
				  tanks contained in Chapter 38 of the California Fire Code, which is hereby
				  incorporated by reference.
(b)
				  MH-Units designed and constructed with securely mounted tanks, may be served by
				  either the lot or mounted tanks, but not by both at the same time.
(c) A permit from the enforcement agency is
				  required to install fuel tanks exceeding sixty (60) U. S. gallons within a
				  park.
(d) LPG tanks shall be
				  designed and constructed in accordance with nationally recognized standards for
				  unfired pressure vessels.
(e) LPG
				  tanks shall be securely, but not permanently, fastened to the mobilehome or
				  recreational vehicle hitch or a substantial post to prevent accidental
				  overturning.
(f) All LPG tanks
				  located in a floodplain as designated by the local floodplain management agency
				  shall be securely anchored to prevent flotation.
1.
					 Renumbering of former section 1664 to new section 1211, including amendment of
					 section heading and section, filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No. 28).
2.
					 Amendment of subsection (a) filed 1-21-2009; operative 1-21-2009 pursuant to
					 Government Code section 11343.4 (Register 2009, No. 4).
3. New
					 subsections (e) and (f) filed 2-18-2011; operative 2-18-2011 pursuant to
					 Government Code section 11343.4 (Register 2011, No.
					 7).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1212 - Location of LPG Tanks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Except for tanks on personal, portable LPG fueled appliances, no LPG tank shall
				  be stored or located in any of the following locations:
(1) within five (5) feet of any source of
				  ignition (lot electrical service is not a source of ignition);
(2) within five (5) feet of any mechanical
				  ventilation air intake;
(3) under
				  any unit or habitable accessory building;
(4) within any structure or area where three
				  (3) or more sides are more than fifty (50) percent closed; or
(5) Within five (5) feet of property lines
				  and lot lines of adjacent lots that can be built upon.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1214 - Material. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1216 - Installation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) All main line
				  gas piping installed below ground shall have a minimum earth cover of:
(1) twenty-four (24) inches or,
(2) eighteen (18) inches when installed in
				  the same trench as other utilities; and covered with clean fill free from
				  stones, boulders, cinderfill, construction debris or other material that may
				  damage the piping.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1218 - Park Gas System Shutoff Valve

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A readily accessible and identified shutoff valve
					 controlling the flow of gas to the entire park-owned gas piping system shall be
					 installed at the point of connection to the service piping or supply
					 connection.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1220 - Lot Gas Shutoff Valve

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each lot shall have a gas shutoff valve, listed for its intended use by a
				  department-approved listing agency, installed in a readily accessible location
				  upstream of the lot gas outlet.
(b)
				  The valve shall be located on the lot gas riser outlet at a height of not less
				  than six (6) inches above grade.
(c) The lot gas shutoff valve shall not be
				  located under or within any unit, or accessory building or structure.
EXCEPTION: gas shut-off valves may be located under an
					 awning or carport that is not enclosed complying with Article 9 of this
					 chapter.
(d) Whenever the
				  lot gas riser outlet is not in use, it shall be closed with an approved cap or
				  plug to prevent accidental discharge of gas.
1. Amendment
					 of section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1222 - Lot Gas Outlet

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The gas riser outlet shall terminate within four (4) feet of the unit, or
				  proposed location of the unit on the lot.
(b) Each unit connected to the gas riser
				  outlet shall be connected by a listed flexible gas connector in accordance with
				  section 1354 of this chapter.
1. Amendment
					 of subsection (b) filed 8-22-85; effective upon filing pursuant to Government
					 Code Section 11346.2(d) (Register 85, No. 36).
2. Amendment of
					 section heading and section filed 7-6-2004; operative 7-6-2004 pursuant to
					 Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Sections 18300 and 18690, Health
						and Safety Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1224 - Mobilehome Gas Connector. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
2. Editorial correction of section heading
					 (Register 2005, No. 33).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Sections 18550, 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1226 - Gas Meters

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  When gas meters are installed, they shall not depend on the gas riser outlet
				  for support. Gas meters shall be adequately supported by a post and bracket or
				  by other means approved by the enforcement agency.
(b) Meters shall not be installed beneath
				  units, in unventilated or inaccessible locations, or closer than three (3) feet
				  from sources of ignition. The unit electrical service equipment shall not be
				  considered a source of ignition when not enclosed in the same compartment with
				  a gas meter.
(c) All gas meter
				  installations shall be provided with a shutoff valve or cock located adjacent
				  to and on the inlet side of the meter. In the case of a single meter
				  installation utilizing a LPG tank, the tank service valve may be used in lieu
				  of the shutoff valve or cock.
(d)
				  Each meter installed shall be in a readily accessible location and shall be
				  provided with unions or other fittings so as to be easily removed and replaced
				  while maintaining an upright position.
(e) Parks constructed after January 1, 1997,
				  shall have individual gas meters for each lot and shall be served by gas
				  distribution facilities owned, operated, and maintained by the gas corporation,
				  as defined in section 222 of the Public Utilities Code, providing gas service
				  in the area.
1. Amendment
					 of subsection (c) filed 8-22-85; effective upon filing pursuant to Government
					 Code Section 11346.2(d) (Register 85, No. 36).
2. Amendment of
					 section and NOTE filed 7-6-2004; operative 7-6-2004 pursuant to Government Code
					 section 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18300 and 18690, Health
						and Safety Code. Reference: Section 18690, Health and Safety Code; and Section
						2791, Public Utilities Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1228 - Mechanical Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where subject to physical damage from vehicular traffic or
					 other causes, all gas riser outlets, regulators, meters, valves, tanks or other
					 exposed equipment shall be protected by posts, fencing, or other barriers
					 approved by the enforcement agency.
1. Amendment
					 filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1229 - Regulator and Relief Vents

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Atmospherically controlled regulators shall be installed in
					 such a manner that moisture cannot enter the regulator vent and accumulate
					 above the diaphragm. Where the regulator vent may be obstructed because of snow
					 or icing conditions, a shield, hood, or other device approved by the
					 enforcement agency shall be provided to guard against closing the vent
					 opening.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2 - Mobilehome Parks and Installations › Article 4 - Fuel Gas and Oil Requirements › Section 1230 - Required Gas Supply

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The minimum hourly volume of gas required at each lot outlet, or any section of
				  a park gas piping system shall be calculated as shown in Table
				  1230-1.
(b) Required gas supply for
				  other fuel gas consuming appliances connected to the park gas piping system
				  shall be calculated as provided in the California Plumbing Code, Chapter 12.
Table 1230-1 Demand Factors for Use
								in Calculating Gas Piping Systems in Parks
Number of
								Lots
BTU Per Hours Per
								Lot
1
125,000
2
117,000
3
104,000
4
96,000
5
92,000
6
87,000
7
83,000
8
81,000
9
79,000
10
77,000
11-20
66,000
21-30
62,000
31-40
58,000
41-60
55,000
Over 60
50,000
1. Amendment
					 of subsection (b) filed 8-22-85; effective upon filing pursuant to Government
					 Code Section 11346.2(d) (Register 85, No. 36).
2. Amendment filed
					 7-6-2004; operative 7-6-2004 pursuant to Government Code section 11343.4
					 (Register 2004, No. 28).
Note: Authority cited: Section 18300, Health and Safety
						Code. Reference: Section 18690, Health and Safety
						Code.