reglab/statecodes huggingface dataset:
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Section 611.1359 - Analytical Methods

Current through Register Vol. 48, No. 28, July 12, 2024
The supplier must conduct analyses for lead, copper, pH,
				  conductivity, calcium, alkalinity, orthophosphate, silica, and temperature
				  using the methods in Section
				  611.611(a).
a) Only a certified laboratory in one of the
				categories in Section
				611.490(a) may
				conduct analyses for lead and copper to demonstrate that a supplier complies
				with this Subpart AG. To obtain certification for conducting analyses for lead
				and copper, a laboratory must fulfill specific conditions:
1) The laboratory must analyze lead- and
				copper-containing performance evaluation samples provided by USEPA or the
				Agency;
2) The laboratory must
				achieve certain quantitative acceptance limits:
A) For lead: ±30 percent of the actual
				amount in the performance evaluation sample when the actual amount is greater
				than or equal to 0.005 mg/L (the PQL for lead is
				0.005 mg/L);
B) For copper: ±10 percent of the
				actual amount in the performance evaluation sample when the actual amount is
				greater than or equal to
				0.050 mg/L (the PQL for copper
				is 0.050 mg/L);
3) The laboratory must achieve the
				method detection limit (MDL) for lead of
				0.001 mg/L using the procedures
				in 35 Ill. Adm. Code 186 and appendix B to
				40 CFR
				136: "Definition and Procedure for the
				Determination of the Method Detection Limit-Revision
				1.11", incorporated by reference
				in Section 611.102(c). The
				laboratory needs only accomplish this if the laboratory will process source
				water composite samples under Section
				611.1358(a)(1)(D);
				and
4) The laboratory must have
				current certification to perform analyses under the specifications this
				subsection (a)(1) describes.
BOARD NOTE: This subsection (a) corresponds with Section
				  611.359(a) and
				  derives from 40 CFR
				  141.89(a) and (a)(1)
				  (2020).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Section 611.1360 - Reporting

Current through Register Vol. 48, No. 28, July 12, 2024
A supplier must report specific information to the Agency as
				  this Section provides.
a) Reporting
				for Tap, Lead, and Copper, and Water Quality Parameter Monitoring
1) Except as subsection (a)(1)(H) provides
				otherwise, a supplier must report certain information for all samples Section
				611.1356 specifies and for all
				water quality parameter samples Section
				611.1357 specifies within ten
				days after the end of each applicable sampling period Sections
				611.1356 and
				611.1357 specify (i.e., every
				six months, annually, triennially, or every nine years). For a monitoring
				period shorter than six months, the end of the monitoring period is the last
				date on which the supplier may collect samples during that period, as Sections
				611.1356 and
				611.1357 specify.
A) The results of all tap samples for lead
				and copper, including the location of each site and the criteria under Section
				611.1356(a)(3) through
				(a)(7) under which the supplier selected the
				site for the supplier's sampling pool;
B) Supporting documents for each tap water
				lead or copper sample the supplier requests the Agency invalidate under Section
				611.1356(f)(2);
C) This subsection (a)(1)(C) corresponds with
				40 CFR
				141.90(a)(1)(iii) (2020), a
				provision that USEPA removed and marked "reserved". This statement preserves
				structural parity with the federal rules;
D) The 90th percentile lead and copper
				concentrations the supplier measures from among all lead and copper tap samples
				the supplier collects during each sampling period (calculated under Section
				611.1350(c)(3)),
				unless the Agency calculates the system's 90th percentile lead and copper
				levels under subsection (h);
E)
				With the exception of initial tap sampling under Section
				611.1356(d)(1),
				the supplier must designate any site it did not sample during previous sampling
				periods and explain why sampling sites have changed;
F) The results of all tap samples for pH and
				the applicable of alkalinity, calcium, conductivity, temperature, and
				orthophosphate, and silica the supplier collects under Section
				611.1357(b) through
				(e);
G) The results of all samples the supplier
				collects at entry points for applicable water quality parameters under Section
				611.1357(b) through
				(e); and
H) A supplier must report the results of all
				water quality parameter samples the supplier collects under Section
				611.1357(c) through
				(f) during each six-month monitoring period
				Section 611.1357(d) 
				specifies within the first ten days following the end of the monitoring period,
				unless the Agency specifies a more frequent reporting requirement in a
				SEP.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Section 611.1361 - Recordkeeping

Current through Register Vol. 48, No. 28, July 12, 2024
Any supplier subject to this Subpart AG must retain original
				  records of all sampling data and analyses, reports, surveys, letters,
				  evaluations, schedules, Agency determinations, and any other information
				  Sections 611.1351 through Section
				  611.1360 require. Each supplier
				  must retain the records this Section requires on its premises for at least 12
				  years.
BOARD NOTE: This Section corresponds with Section
					 611.361 and derives from
					 40 CFR
					 141.91
					 (2020).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Appendix C - Common Names of Organic Chemicals

Current through Register Vol. 48, No. 28, July 12, 2024
The following common names are used for certain organic
				  chemicals:
Common Name
CAS No.
CAS Name
Aldrin
309-00-2
1,4,5,8-Dimethanonaphthalene,
							 1,2,3,4,10,10-hexachloro-1,4,4a,5,8,8a-hexahydro-, (1alpha, 4alpha, 4abeta,
							 5alpha, 8alpha, 8abeta)-
Bromoform
75-25-2
Methane, tribromo-
Chlordane
57-74-9
4,7-Methano-1H-indene,
							 1,2,4,5,6,7,8,8-octachloro-2,3,3a,4,7,7a-hexahydro-
Chloroform
67-66-3
Methane, trichloro-
2,4-D
94-75-7
Acetic acid, 2,4-dichlorophenoxy-
DDT
50-29-3
Benzene,
							 1,1'-(2,2,2-trichloroethylidene)bis(4-chloro-
Dieldrin
60-57-1
2,7:3,6-Dimethanonaphth(2,3-b)oxirene,
							 3,4,5,6,9,9-hexachloro-1a,2,2a,3,6,6a,7,7a-octahydro-,(1aalpha, 2beta, 2aalpha,
							 3beta, 6beta, 6aalpha, 7beta, 7aalpha)-
Endrin
72-20-8
2,7:3,6-Dimethanonaphth(2,3-b)oxirene,
							 3,4,5,6,9,9-hexachloro-1a,2,2a,3,6,6a,7,7a-octahydro-, (1aalpha, 2beta, 2abeta,
							 3alpha, 6alpha, 6abeta, 7beta, 7aalpha)-,
Heptachlor
76-44-8
4,7-Methano-1H-indene,1,4,5,6,7,8,8-heptachloro-3a,4,7,7a-tetrahydro-
Heptachlor epoxide
1024-57-3
2,5-Methano-2H-indeno(1,2b) oxirene,
							 2,3,4,5,6,7,7-heptachloro-1a,1b,5,5a,6,6a-hexahydro-, (1a alpha, 1b beta, 2
							 alpha, 5 alpha, 5a beta, 6 beta, 6a alpha)-
Lindane
58-89-9
Cyclohexane, 1,2,3,4,5,6-hexachloro-, (1alpha,
							 2alpha, 3beta, 4alpha, 5alpha, 6beta)-
Methoxychlor
72-43-5
Benzene,
							 1,1'-(2,2,2-trichloroethylidene)bis(4-methoxy-
Silvex (2,4,5-TP)
93-72-1
Propanoic acid, 2-(2,4,5-trichlorophenoxy)-
Toxaphene
8001-35-2
Toxaphene
TTHM
Total trihalomethanes (See Section
							 611.101
							 )
BOARD NOTE: Derived from 40 CFR 141.30 and 261, appendix
					 VIII (2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Appendix D - Defined Substrate Method for the Simultaneous Detection of Total Coliforms and Escherichia Coli from Drinking Water (Repealed)

Current through Register Vol. 48, No. 28, July 12, 2024
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Appendix I - Acronyms Used in Public Notification Regulation

Current through Register Vol. 48, No. 28, July 12, 2024
CCR
Consumer Confidence Report
CWS
Community Water System
DBP
Disinfection Byproduct
GWR
Groundwater Rule
HPC
Heterotrophic Plate Count
IESWTR
Interim Enhanced Surface Water Treatment Rule
IOC
Inorganic Chemical
LCR
Lead and Copper Rule
MCL
Maximum Contaminant Level
MCLG
Maximum Contaminant Level Goal
MRDL
Maximum Residual Disinfectant Level
MRDLG
Maximum Residual Disinfectant Level Goal
NCWS
Non-Community Water System
NPDWR
National Primary Drinking Water Regulation
NTNCWS
Non-Transient Non-Community Water System
NTU
Nephelometric Turbidity Unit
OGWDW
USEPA, Office of Ground Water and Drinking
							 Water
OW
USEPA, Office of Water
PN
Public Notification
PWS
Public Water System
SDWA
Safe Drinking Water Act
SMCL
Secondary Maximum Contaminant Level
SOC
Synthetic Organic Chemical
SWTR
Surface Water Treatment Rule
TCR
Total Coliform Rule
TT
Treatment Technique
TWS
Transient Non-Community Water System
USEPA
United States Environmental Protection Agency
VOC
Volatile Organic Chemical
BOARD NOTE: Derived from Appendix C to Subpart Q to 40 CFR
					 141(2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table B - Fecal or Total Coliform Density Measurements

Current through Register Vol. 48, No. 28, July 12, 2024
System Size (Persons Served)
Samples per Week
500
or fewer
1
501
to
3300
2
3301
to
10,000
3
10,001
to
25,000
4
More than
25,000
5
Samples must be taken on separate days.
BOARD NOTE: Derived from
					 40 CFR
					 141.74(b)(1) (2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table C - Frequency of RDC Measurement

Current through Register Vol. 48, No. 28, July 12, 2024
System Size (Persons Served)
Samples per Day
500
or
fewer
1
501
to
1,000
2
1001
to
2,500
3
2501
to
3,300
4
The day's samples cannot be taken at the same time. The
				  sampling intervals are subject to Agency review and approval by a SEP.
BOARD NOTE: Derived from
					 40 CFR
					 141.74(b)(5) and (c)(2)
					 (2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table D - Number of Lead and Copper Monitoring Sites

Current through Register Vol. 48, No. 28, July 12, 2024
System Size (Persons Served)
Number of Sites
(Standard Monitoring)
Number of Sites
(Reduced Monitoring)
More than 100,000
100
50
10,001-100,000
60
30
3,301 to 10,000
40
20
501 to 3,300
20
10
101 to 500
10
5
100 or fewer
5
5
BOARD NOTE: Derived from
					 40 CFR
					 141.86(c) (2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table F - Number of Water Quality Parameter Sampling Sites

Current through Register Vol. 48, No. 28, July 12, 2024
System Size
Minimum Number of Sites
(Number of Persons Served)
(Standard Monitoring)
(Reduced Monitoring)
more than 100,000
25
10
10,001 to 100,000
10
7
3,301 to 10,000
3
3
501 to 3,300
2
2
101 to 500
1
1
100 or fewer
1
1
BOARD NOTE: This Table F derives from
					 40 CFR
					 141.87(a)(2)(i) and
					 (e)(1).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table G - Summary of Section 611.357 Monitoring Requirements for Water Quality Parameters (Repealed)

Current through Register Vol. 48, No. 28, July 12, 2024
See end note 1 below.
BOARD NOTE: Derived from the table to
					 40 CFR
					 141.87(2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table H - CT Values (mg·min/l) for Cryptosporidium Inactivation by Chlorine Dioxide

Current through Register Vol. 48, No. 28, July 12, 2024
Log Credit
Water Temperature (°C)
[LESS THAN OR EQUAL TO] 0.5
1
2
3
5
7
10
15
20
25
30
0.25
159
153
140
128
107
90
69
45
29
19
12
0.5
319
305
279
256
214
180
138
89
58
38
24
1.0
637
610
558
511
429
360
277
179
116
75
49
1.5
956
915
838
767
643
539
415
268
174
113
73
2.0
1275
1220
1117
1023
858
719
553
357
232
150
98
2.5
1594
1525
1396
1278
1072
899
691
447
289
188
122
3.0
1912
1830
1675
1534
1286
1079
830
536
347
226
147
A supplier may use the following equation to determine log
				  credit between the indicated values:
Log credit = (0.001506 a ? (1.09116
				  )Temp(in °C)) a ? CT
BOARD NOTE: Derived from the table at
					 40 CFR
					 141.720(b)(1) (2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table I - CT Values (mg·min/l) for Cryptosporidium Inactivation by Ozone

Current through Register Vol. 48, No. 28, July 12, 2024
Log Credit
Water Temperature (°C)
[LESS THAN OR EQUAL TO] 0.5
1
2
3
5
7
10
15
20
25
30
0.25
6.0
5.8
5.2
4.8
4.0
3.3
2.5
1.6
1.0
0.6
0.39
0.5
12
12
10
9.5
7.9
6.5
4.9
3.1
2.0
1.2
0.78
1.0
24
23
21
19
16
13
9.9
6.2
3.9
2.5
1.6
1.5
36
35
31
29
24
20
15
9.3
5.9
3.7
2.4
2.0
48
46
42
38
32
26
20
12
7.8
4.9
3.1
2.5
60
58
52
48
40
33
25
16
9.8
6.2
3.9
3.0
72
69
63
57
47
39
30
19
12
7.4
4.7
A supplier may use the following equation to determine log
				  credit between the indicated values:
Log credit = (0.0397 a ? (1.09757
				  )Temp(in °C)) a ? ? CT
BOARD NOTE: Derived from the table at
					 40 CFR
					 141.720(b)(2) (2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table J - UV Dose Table for Cryptosporidium, Giardia lamblia, and Virus Inactivation Credit

Current through Register Vol. 48, No. 28, July 12, 2024
Log Credit
UV dose
							 (mJ/cm2)
Cryptosporidium
Giardia lamblia
Virus
0.5
1.6
1.5
39
1.0
2.5
2.1
58
1.5
3.9
3.0
79
2.0
5.8
5.2
100
2.5
8.5
7.7
121
3.0
12
11
143
3.5
15
15
163
4.0
22
22
186
BOARD NOTE: Derived from the table at
					 40 CFR
					 141.720(d)(1) (2012).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 611 - PRIMARY DRINKING WATER STANDARDS › Subpart AG - INTERIM LEAD AND COPPER RULES › Table R - Radionuclide Conversion Factors

Current through Register Vol. 48, No. 28, July 12, 2024
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Click
				  here to view image
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart A - GENERAL › Section 615.101 - Purpose

Current through Register Vol. 48, No. 28, July 12, 2024
This Part specifies the requirements and standards for the
				  protection of groundwater for certain types of existing facilities or units
				  located wholly or partially within a setback zone regulated by the Act or
				  within a regulated recharge area under Section
				  17.4 of the Act and 35 Ill. Adm.
				  Code 617.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart A - GENERAL › Section 615.103 - Incorporations by Reference

Current through Register Vol. 48, No. 28, July 12, 2024
a) The
				Board incorporates the following material by reference:
CFR (Code of Federal Regulations). Available from the
				  Superintendent of Documents, U.S. Government Printing Office, Washington, D.C.
				  20402, 202-783-3238.
Method Detection Limit Definition, appendix B to Part 136,
				  40 CFR
				  136 (2017).
49 CFR
				  173 (2017).
NTIS. National Technical Information Service, 5301 Shawnee
				  Road, Alexandria VA 22312.
"Test Methods for Evaluating Solid Wastes, Physical/Chemical
				  Methods", EPA Publication No. SW-846, as amended by Updates I, II, IIA, IIB,
				  III, IIIA, and IIIB I, (Third Edition, 1986, as amended by Revision I (December
				  1987), Doc. No. 55-001-00000-1) (available online).
b) This Section incorporates no later
				amendments or editions.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart A - GENERAL › Section 615.104 - Prohibitions

Current through Register Vol. 48, No. 28, July 12, 2024
A person must not cause or allow the construction or
				  operation of any facility or unit in violation of the Act or regulations
				  adopted by the Board thereunder, including this Part.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart A - GENERAL › Section 615.105 - General Exceptions

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				This Part does not apply to any facility or unit, or to the owner or operator
				of any facility or unit:
1) For which the
				owner or operator obtains certification of minimal hazard under Section
				14.5 of the Act; or
2) For which alternate requirements are
				imposed in an adjusted standard proceeding or as part of a site-specific
				rulemaking, under Title VII of the Act; or
3) For which alternate requirements are
				imposed in a regulated recharge area proceeding under Section
				17.4 of the Act; or
4) That is
located on the same site
				as a non-community water system well and for which the owner is the same for
				both the
facility or unit
and the well.
(Section
				14.4(b) of the
				Act); or
5) That is located
within a regulated recharge area as delineated
in 35 Ill. Adm.
				Code 617 if
:
A)
The
				boundary of the lateral area of influence of a community water supply well
				located within the regulated recharge area
does not
include
				such
facility or unit
therein;
B)
The distance from the wellhead of
				the community water supply to the
facility or unit
exceeds
				2500 feet; and
C)
The community water supply well was
not
in existence
				prior to January 1, 1988.
[415 ILCS
				5/14.4(b) ]; or
6) For which the owner or operator of the
				facility for storage and related handling of pesticides or fertilizers for the
				purpose of commercial application or at a central location for the purpose of
				distribution to retail sales outlets that has filed a written notice of intent
				under Section 14.6 of the Act
with the
				Department of Agriculture by January 1, 1993, or within 6 months after the date
				on which a maximum setback zone is established or a regulated recharge area
				regulation is adopted that affects such a facility
; or has filed a
				written certification of intent under Section
				14.6 of the Act
on the
				appropriate license or renewal application form submitted to the Department of
				Agriculture or other appropriate agency.
[415 ILCS
				5/14.6(a) ] This exception does not
				apply to those facilities that are not in compliance with the program
				requirements of subsections
				14.6(b) and
				14.6(c) of the
				Act.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.201 - Applicability

Current through Register Vol. 48, No. 28, July 12, 2024
This Subpart applies to:
a) Surface impoundments subject to Subpart
				F;
b) Pesticide storage and
				handling units subject to Subpart I;
c) Fertilizer storage and handling units
				subject to Subpart J;
d) Road oil
				storage and handling units subject to Subpart K; and
e) De-icing agent storage and handling units
				subject to Subpart L.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.202 - Compliance Period

Current through Register Vol. 48, No. 28, July 12, 2024
The compliance period is the active life of the unit,
				  including closure and post-closure care periods.
a) The active life begins when the unit first
				begins operation or one year after the date of first applicability, whichever
				occurs later, and ends when the post-closure care period ends.
b) The post-closure care period for units
				other than pesticide storage and handling units subject to Subpart I and
				fertilizer storage and handling units subject to Subpart J is five years after
				closure, except as provided in subsection (d) or Section
				615.211(e).
c) The post-closure care period for pesticide
				storage and handling units subject to Subpart I and for fertilizer storage and
				handling units subject to Subpart J is three years after closure, except as
				provided in Section 615.211(e).
d) Despite subsections (a), (b), and (c), no
				post-closure care period is required if all waste, waste residues, contaminated
				containment system components, and contaminated subsoils are removed or
				decontaminated at closure, and no ongoing corrective action is required under
				Section 615.211.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.203 - Compliance with Groundwater Standards

Current through Register Vol. 48, No. 28, July 12, 2024
The owner or operator must comply with the groundwater
				  standards.
a) The term of compliance
				is the compliance period.
b)
				Compliance must be measured at the compliance point, or compliance points if
				more than one such point exists.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.204 - Groundwater Monitoring System

Current through Register Vol. 48, No. 28, July 12, 2024
a) Except as provided otherwise in subsection
				(b), the groundwater monitoring system must consist of a sufficient number of
				wells, installed at appropriate locations and depths to yield groundwater
				samples, that:
1) Represent the quality of
				background water that has not been affected by contamination from the facility
				or unit; and
2) Represent the
				quality of groundwater at the compliance point or points.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.205 - Groundwater Monitoring Program

Current through Register Vol. 48, No. 28, July 12, 2024
The owner or operator must develop a groundwater monitoring
				  program that consists of:
a)
				Consistent sampling and analysis procedures that are designed to ensure
				monitoring results that provide a reliable indication of groundwater quality
				below the unit. At a minimum, the program must include procedures and
				techniques for:
1) Sample
				collection;
2) Sample preservation
				and shipment;
3) Analytical
				procedures; and
4) Chain of custody
				control.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.206 - Contaminants to be Monitored

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				The owner or operator must monitor for all constituents that meet the following
				criteria, except as provided in subsections (b) and (c):
1) Material containing the constituents is
				stored, disposed of, or otherwise handled at the site; and
2) There is a groundwater standard for the
				constituents.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.207 - Sampling Frequency

Current through Register Vol. 48, No. 28, July 12, 2024
a) The
				owner or operator must determine whether groundwater standards have been
				exceeded at each monitoring well at least quarterly during the compliance
				period, except as provided otherwise in subsection (b) or (c) or Section
				615.209(b).
b) The owner or operator of a unit subject to
				Subpart I for the storage and handling of pesticides or Subpart J for the
				storage and handling of fertilizer may substitute the quarterly determination
				of subsection (a) with a determination at least semi-annually if all of the
				following conditions are met:
1) The unit is
				in compliance with the containment requirements of 8 Ill. Adm. Code
				255;
2) There have been no
				detections within the preceding two years in any of the monitoring wells of any
				contaminant stored or handled at the facility or of any contaminant
				attributable to operation of the unit; and
3) No reportable agrichemical spills, as
				defined in 8 Ill. Adm. Code 255, have occurred at the facility within the
				previous two years.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.208 - Reporting

Current through Register Vol. 48, No. 28, July 12, 2024
The owner or operator must submit results of all monitoring
				  required under this Subpart to the Agency within 60 days after completion of
				  sampling.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.209 - Non-Compliance Response Program

Current through Register Vol. 48, No. 28, July 12, 2024
If monitoring results collected under Sections
				  615.206 and
				  615.207 show that a groundwater
				  standard has been exceeded, the owner or operator must:
a) Notify the Agency of this finding when
				submitting the groundwater monitoring results required under Section
				615.208. The notification must
				indicate which groundwater standards have been exceeded.
b) Resample the groundwater within 3 days in
				all monitoring wells where a groundwater standard has been exceeded and
				redetermine the presence and concentration of each parameter required under
				Section 615.206, except that:
1) If the unit
				is subject to Subpart I for the storage and related handling of pesticides,
				resample the groundwater within 3 days in all monitoring wells where a
				groundwater standard has been exceeded and determine the presence and
				concentration in each such sample of each pesticide previously and presently
				stored or handled at the unit.
2)
				If the unit is subject to Subpart J for the storage and related handling of
				fertilizers, monitor monthly for the parameters set forth in Section
				615.206(c)
				until the groundwater standard is no longer exceeded.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.210 - Alternate Non-Compliance Response Program

Current through Register Vol. 48, No. 28, July 12, 2024
If the groundwater sampling required under Section
				  615.207 shows that a groundwater
				  standard has been exceeded, it is presumed that contamination from the facility
				  or unit that is being monitored is responsible for the standard being exceeded.
				  An owner or operator may overcome that presumption by making a demonstration
				  that a source other than the facility or unit that is being monitored caused
				  the exceedance or that the exceedance resulted from error in sampling,
				  analysis, or evaluation. In making the demonstration, the owner or operator
				  must:
a) Notify the Agency that the
				owner or operator intends to make a demonstration under this Section when
				submitting the groundwater monitoring results required under Section
				615.208.
b) Submit a report to the Agency that
				demonstrates that a source other than a facility or unit owned or operated by
				the owner or operator caused the groundwater standard to be exceeded, or that
				the groundwater standard was exceeded due to an error in sampling, analysis or
				evaluation. Such report must be included with the next submission of
				groundwater monitoring results required under Section 615.208; and
c) Continue to monitor in compliance with the
				groundwater monitoring program established under Sections
				615.205,
				615.206, and 615.207.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart B - GROUNDWATER MONITORING REQUIREMENTS › Section 615.211 - Corrective Action Program

Current through Register Vol. 48, No. 28, July 12, 2024
An owner or operator required to conduct a corrective action
				  program under this Subpart must:
a)
				Begin corrective action within 120 days after the date on which the sample
				results are submitted to the Agency under Section
				615.209(c).
b) Take corrective action that results in
				compliance with the groundwater standards at the compliance point or
				points.
c) Establish and implement
				a groundwater monitoring program to demonstrate the effectiveness of the
				corrective action program.
d) Take
				corrective action that maintains compliance with the groundwater standards:
1) At all compliance points; and
2) Beyond the unit boundary, where necessary
				to protect human health and the environment, unless the owner or operator
				demonstrates to the Agency that, despite the owner's or operator's best
				efforts, the owner or operator was unable to obtain the necessary permission to
				undertake such action. The owner or operator is not relieved of responsibility
				to clean up a release that has migrated beyond the unit boundary where off-site
				access is denied.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart C - GENERAL CLOSURE AND POST-CLOSURE REQUIREMENTS › Section 615.301 - Applicability

Current through Register Vol. 48, No. 28, July 12, 2024
This Subpart applies to:
a) Land treatment units subject to Subpart
				E;
b) Surface impoundments subject
				to Subpart F;
c) Pesticide storage
				and handling units subject to Subpart I; and
d) Fertilizer storage and handling units
				subject to Subpart J.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart C - GENERAL CLOSURE AND POST-CLOSURE REQUIREMENTS › Section 615.302 - Closure Performance Standard

Current through Register Vol. 48, No. 28, July 12, 2024
The owner or operator must close the unit in a manner
				  that:
a) Controls, minimizes, or
				eliminates, to the extent necessary to protect human health and the
				environment, post-closure escape of waste, waste constituents, leachate,
				contaminated runoff, or waste decomposition products to soils, groundwaters,
				surface waters, and the atmosphere;
b) Minimizes the need for maintenance during
				and beyond the post-closure care period; and
c) Complies with the closure requirements of
				35 Ill. Adm. Code: Subtitles C and G.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart C - GENERAL CLOSURE AND POST-CLOSURE REQUIREMENTS › Section 615.303 - Certification of Closure

Current through Register Vol. 48, No. 28, July 12, 2024
Within 60 days after the closure is complete, the owner or
				  operator must submit to the Agency, by registered or certified mail, a
				  certification that the unit has been closed in compliance with the closure
				  requirements. The certification must be signed by the owner or operator and by
				  an independent registered professional engineer. Documentation supporting the
				  independent registered professional engineer's certification must be furnished
				  to the Agency upon request.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart C - GENERAL CLOSURE AND POST-CLOSURE REQUIREMENTS › Section 615.304 - Survey Plat

Current through Register Vol. 48, No. 28, July 12, 2024
a) Before the
				submission of the certification of closure of each unit, the owner or operator
				must record with land titles and submit to the Agency and any local zoning
				authority, or authority with jurisdiction over local land use, a survey plat
				indicating the location and dimensions of any waste disposal units and any
				pesticide or fertilizer storage and handling units with respect to permanently
				surveyed benchmarks. This plat must be prepared and certified by a registered
				land surveyor.
b) For pesticide
				storage and handling units or fertilizer storage and handling units, records or
				reports required under any other State or federal regulatory program and that
				contain the information required above may be used to satisfy this reporting
				requirement.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart C - GENERAL CLOSURE AND POST-CLOSURE REQUIREMENTS › Section 615.305 - Post-Closure Notice for Waste Disposal Units

Current through Register Vol. 48, No. 28, July 12, 2024
Within 60 days after certification of closure of the unit,
				  the owner or operator of a unit subject to Subpart D or F must submit to the
				  Agency, the County Recorder, and any local zoning authority, or authority with
				  jurisdiction over local land use, a record of the type, location and quantity
				  of wastes disposed of within each cell or other area of the
				  unit.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart C - GENERAL CLOSURE AND POST-CLOSURE REQUIREMENTS › Section 615.306 - Certification of Completion of Post-Closure Care

Current through Register Vol. 48, No. 28, July 12, 2024
Within 60 days after completion of the established
				  post-closure care period, the owner or operator must submit to the Agency, by
				  registered or certified mail, a certification that the post-closure care period
				  for the unit was performed in compliance with the specifications in the
				  approved post-closure plan. The certification must be signed by the owner or
				  operator and an independent registered professional engineer. Documentation
				  supporting the independent registered professional engineer's certification
				  must be furnished to the Agency upon request.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart C - GENERAL CLOSURE AND POST-CLOSURE REQUIREMENTS › Section 615.307 - Post-Closure Care Period

Current through Register Vol. 48, No. 28, July 12, 2024
The post-closure care period is as defined at Section
				  615.202.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart D - ON-SITE LANDFILLS › Section 615.401 - Applicability

Current through Register Vol. 48, No. 28, July 12, 2024
This Subpart applies to existing landfill units that are
				  located wholly or partially within a setback zone or regulated recharge area
				  and that contain special waste or other waste generated on-site, except that
				  this Subpart does not apply to any existing landfill unit that:
a) Contains solely one or more of the
				following: hazardous waste, livestock waste, landscape waste, or construction
				and demolition debris; or
b) Is
				exempt from this Part under Section
				615.105.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart D - ON-SITE LANDFILLS › Section 615.402 - Required Closure of Units Located Within Minimum Setback Zones

Current through Register Vol. 48, No. 28, July 12, 2024
A person must not cause or allow the operation within a
				  minimum setback zone of any landfill unit after January 10, 1994. Closure of a
				  landfill unit must be completed within three years.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart D - ON-SITE LANDFILLS › Section 615.403 - Required Closure of Units Located Within Maximum Setback Zones

Current through Register Vol. 48, No. 28, July 12, 2024
Starting two years after the effective date of the ordinance
				  or regulation that establishes a maximum setback zone, a person must not cause
				  or allow the operation within the maximum setback zone of any landfill unit at
				  which special waste is disposed of. Closure must be completed within three
				  years after the effective date of the ordinance or regulation that establishes
				  the maximum setback zone.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart D - ON-SITE LANDFILLS › Section 615.404 - Required Closure of Units Located Within Regulated Recharge Areas

Current through Register Vol. 48, No. 28, July 12, 2024
A person must not cause or allow the operation within a
				  regulated recharge area of any landfill unit that contains special waste and
				  for which the distance from the wellhead of the community water supply well to
				  any part of the landfill unit is 2500 feet or less. This provision becomes
				  effective four years after the date on which the Board establishes the
				  regulated recharge area. Closure must be completed within five years after the
				  date on which the Board establishes the regulated recharge
				  area.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart E - ON-SITE LAND TREATMENT UNITS › Section 615.421 - Applicability

Current through Register Vol. 48, No. 28, July 12, 2024
This Subpart applies to existing land treatment units that
				  are located wholly or partially within a setback zone or regulated recharge
				  area and that treat or dispose of special waste or other waste generated
				  on-site, except that this Subpart does not apply to any existing land treatment
				  unit that:
a) Contains solely one or
				more of the following: hazardous waste, livestock waste, landscape waste, or
				construction and demolition debris; or
b) Is exempt from this Part under Section
				615.105.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart E - ON-SITE LAND TREATMENT UNITS › Section 615.422 - Required Closure of Units Located Within Minimum Setback Zones

Current through Register Vol. 48, No. 28, July 12, 2024
A person must not cause or allow the operation within a
				  minimum setback zone of any land treatment unit after January 10, 1994. Closure
				  must be completed by January 10, 1995.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart E - ON-SITE LAND TREATMENT UNITS › Section 615.423 - Required Closure of Units Located Within Maximum Setback Zones

Current through Register Vol. 48, No. 28, July 12, 2024
Starting two years after the effective date of the ordinance
				  or regulation that establishes a maximum setback zone, a person must not cause
				  or allow the operation within the maximum setback zone of any land treatment
				  unit at which special waste is treated or disposed of. Closure must be
				  completed within three years after the effective date of the ordinance or
				  regulation that establishes the maximum setback zone.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart E - ON-SITE LAND TREATMENT UNITS › Section 615.424 - Land Treatment of Sludges in Maximum Setback Zones

Current through Register Vol. 48, No. 28, July 12, 2024
Nothing in this Subpart prohibits land treatment within a
				  maximum setback zone of sludge resulting from the treatment of domestic
				  wastewater or of sludge resulting from the treatment of water to produce
				  potable water, if such activities are conducted in compliance with the Act and
				  35 Ill. Adm. Code: Subtitle C.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart E - ON-SITE LAND TREATMENT UNITS › Section 615.425 - Closure and Post-Closure Care

Current through Register Vol. 48, No. 28, July 12, 2024
The owner or operator must comply with the requirements of
				  Sections 615.302 and
				  615.303.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart F - ON-SITE SURFACE IMPOUNDMENTS › Section 615.441 - Applicability

Current through Register Vol. 48, No. 28, July 12, 2024
This Subpart applies to existing surface impoundment units
				  that are located wholly or partially within a setback zone or regulated
				  recharge area and that contain special waste or other waste generated on-site,
				  except that this Subpart does not apply to any existing surface impoundment
				  unit that:
a) Contains solely one or
				more of the following: hazardous waste, livestock waste, landscape waste, or
				construction and demolition debris; or
b) Is exempt from this Part under Section
				615.105.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart F - ON-SITE SURFACE IMPOUNDMENTS › Section 615.442 - Required Closure of Units Located Within Minimum Setback Zones

Current through Register Vol. 48, No. 28, July 12, 2024
A person must not cause or allow the operation within a
				  minimum setback zone of any surface impoundment unit after January 10, 1994.
				  Closure must be completed by January 10, 1995.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart F - ON-SITE SURFACE IMPOUNDMENTS › Section 615.443 - Required Closure of Units Located Within Maximum Setback Zones

Current through Register Vol. 48, No. 28, July 12, 2024
Starting two years after the effective date of the ordinance
				  or regulation that establishes a maximum setback zone, a person must not cause
				  or allow the operation within the maximum setback zone of any surface
				  impoundment unit at which special waste is stored, treated or disposed of.
				  Closure must be completed within three years after the effective date of the
				  ordinance or regulation that establishes the maximum setback
				  zone.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart F - ON-SITE SURFACE IMPOUNDMENTS › Section 615.444 - Groundwater Monitoring

Current through Register Vol. 48, No. 28, July 12, 2024
The owner or operator of an existing on-site surface
				  impoundment must comply with the requirements of Subpart B.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart F - ON-SITE SURFACE IMPOUNDMENTS › Section 615.445 - Inspection Requirements

Current through Register Vol. 48, No. 28, July 12, 2024
During operation, a surface impoundment must be inspected
				  weekly and after storms to detect evidence of any of the following:
a) Deterioration, malfunctions or improper
				operation of overtopping control systems;
b) Sudden drops in the level of the
				impoundment's contents;
c) Severe
				erosion or other signs of deterioration in dikes or other containment devices;
				or
d) A leaking dike.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart F - ON-SITE SURFACE IMPOUNDMENTS › Section 615.446 - Operating Requirements

Current through Register Vol. 48, No. 28, July 12, 2024
a) A
				person must not cause or allow incompatible materials to be placed in the same
				surface impoundment unit.
b) A
				surface impoundment unit must be removed from service in compliance with
				subsection (c) when:
1) The level of liquids
				in the unit suddenly drops and the drop is not known to be caused by changes in
				the flows into or out of the unit; or
2) The dike leaks.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart F - ON-SITE SURFACE IMPOUNDMENTS › Section 615.447 - Closure and Post-Closure Care

Current through Register Vol. 48, No. 28, July 12, 2024
a) If closure is to be by removal, the owner
				or operator must remove all waste, all waste residues, contaminated containment
				system components (e.g., liners), contaminated subsoils and structures, and
				equipment contaminated with waste and leachate; and, if disposed of in the
				State of Illinois, dispose of them at a disposal site permitted by the Agency
				under the Act.
b) If closure is not
				to be by removal, the owner or operator must comply with the requirements of
				Subpart C and must:
1) Eliminate free liquids
				by removing liquid wastes or solidifying the remaining wastes and waste
				residues.
2) Stabilize remaining
				wastes to a bearing capacity sufficient to support final cover.
3) Cover the surface impoundment unit with a
				final cover consisting of at least a 2-foot-thick layer of compacted clay with
				a permeability of no more than 1x10-7 centimeters
				per second and designed and constructed to:
A)
				Provide long-term minimization of the migration of liquids through the closed
				impoundment unit;
B) Function with
				minimum maintenance;
C) Promote
				drainage and minimize erosion or abrasion of the final cover; and
D) Accommodate settling and subsidence so
				that the cover's integrity is maintained.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 615 - EXISTING ACTIVITIES IN A SETBACK ZONE OR REGULATED RECHARGE AREA › Subpart G - ON-SITE WASTE PILES › Section 615.461 - Applicability

Current through Register Vol. 48, No. 28, July 12, 2024
This Subpart applies to existing waste piles that are located
				  wholly or partially within a setback zone or regulated recharge area and that
				  contain special waste or other waste generated on-site, except that this
				  Subpart does not apply to any existing waste pile that:
a) Contains solely one or more of the
				following: hazardous waste, livestock waste, landscape waste, or construction
				and demolition debris;
b) Consists
				of sludge resulting from the treatment of wastewater from a Publicly Owned
				Treatment Works (POTW) and the sludge pile is situated on an underdrained
				pavement and operated in compliance with the Act, 35 Ill. Adm. Code: Subtitle C
				and 35 Ill. Adm. Code: Subtitle G; or
c) Is exempt from this Part under Section
				615.105.