reglab/statecodes huggingface dataset:
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emissions Standards for Equipment Leaks › Section 66265.1057 - Standards: Valves in Gas/Vapor Service or in Light Liquid Service

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each valve in
				  gas/vapor or light liquid service shall be monitored monthly to detect leaks by
				  the methods specified in Section
				  66265.1063(b)
				  except when in compliance with subsections (c) and shall comply with (d) and
				  (e) of this section, except as provided in subsections (f), (g), and (h) of
				  this section and Sections
				  66265.1061 and
				  66265.1062.
(b) If an instrument reading of 10,000 ppm or
				  greater is measured, a leak is detected.
(c)
(1) Any
				  valve for which a leak is not detected for two successive months shall be
				  monitored the first month of every succeeding quarter, beginning with the next
				  quarter, until a leak is detected.
(2) If a leak is detected, the valve shall be
				  monitored monthly until a leak is not detected for two successive
				  months.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emissions Standards for Equipment Leaks › Section 66265.1058 - Standards: Pumps and Valves in Heavy Liquid Service, Pressure Relief Devices in Light Liquid or Heavy Liquid Service, and Flanges and Other Connectors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Pumps and valves in heavy liquid service, pressure relief devices in light
				  liquid or heavy liquid service, and flanges and other connectors shall be
				  monitored within five days by the method specified in Section
				  66265.1063(b) if
				  evidence of a potential leak is found by visual, audible, olfactory, or any
				  other detection method.
(b) If an
				  instrument reading of 10,000 ppm or greater is measured, a leak is
				  detected.
(c)
(1) When a leak is detected, it shall be
				  repaired as soon as practicable, but not later than fifteen (15) calendar days
				  after it is detected, except as provided in Section
				  66265.1059.
(2) The first attempt at repair shall be made
				  as soon as possible, to minimize escape of hazardous constituents to the
				  environment, but no later than 24 hours after each leak is
				  detected.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emissions Standards for Equipment Leaks › Section 66265.1059 - Standards: Delay of Repair

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Delay of repair of equipment for which
				  leaks have been detected will be allowed if the repair is technically
				  infeasible without a hazardous waste management unit shutdown. In such a case,
				  repair of this equipment shall occur before the end of the next hazardous waste
				  management unit shutdown.
(b) Delay
				  of repair of equipment for which leaks have been detected will be allowed for
				  equipment that is isolated from the hazardous waste management unit and that
				  does not continue to contain or contact hazardous waste with organic
				  concentrations at least ten percent by weight.
(c) Delay of repair for valves will be
				  allowed if:
(1) The owner or operator
				  determines that emissions of purged material resulting from immediate repair
				  are greater than the emissions likely to result from delay of repair;
				  and
(2) When repair procedures are
				  effected, the purged material is collected and destroyed or recovered in a
				  control device complying with Section
				  66265.1060.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emissions Standards for Equipment Leaks › Section 66265.1061 - Alternative Standards for Valves in Gas/Vapor Service or in Light Liquid Service: Percentage of Valves Allowed to Leak

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) An owner or operator subject to the
				  requirements of Section
				  66265.1057 may elect to have all
				  valves within a hazardous waste management unit comply with an alternative
				  standard which allows no greater than two percent of the valves to
				  leak.
(b) The following
				  requirements shall be met if an owner or operator decides to comply with an
				  alternative standard which allows two percent of the valves to leak:
(1) the owner or operator shall notify the
				  Department that the owner or operator has elected to comply with the
				  requirements of this section;
(2) a
				  performance test as specified in subsection (c) of this section shall be
				  conducted initially upon designation, annually, and at any other time required
				  by the Department upon a determination by the Department that a performance
				  test is necessary to protect human health or the environment; and
(3) if a valve leak is detected, it shall be
				  repaired in accordance with Sections
				  66265.1057(d) and
				  (e).
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emissions Standards for Equipment Leaks › Section 66265.1062 - Alternative Standards for Valves in Gas/Vapor Service or in Light Liquid Service: Skip Period Leak Detection and Repair

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
(1) An
				  owner or operator subject to the requirements of Section
				  66265.1057 shall elect for all
				  valves within a hazardous waste management unit to comply with one of the
				  alternative work practices specified in subsection (b)(2) and (3) of this
				  section.
(2) An owner or operator
				  shall notify the Department before implementing one of the alternative work
				  practices.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emissions Standards for Equipment Leaks › Section 66265.1063 - Test Methods and Procedures

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each owner or operator subject to the
				  provisions of this article shall comply with the test methods and procedures
				  requirements provided in this section.
(b) Leak detection monitoring, as required in
				  Sections 66265.1052 through
				  66265.1062, shall comply with the
				  following requirements:
(1) monitoring shall
				  comply with Reference Method 21 in 40 CFR, part 60 , incorporated by reference
				  in Section
				  66260.11 of this
				  chapter.
(2) the detection
				  instrument shall meet the performance criteria of Reference Method
				  21.
(3) the instrument shall be
				  calibrated before use on each day of its use by the procedures specified in
				  Reference Method 21;
(4)
				  Calibration gases shall be:
(A) zero air
				  (less than 10 ppm of hydrocarbon in air);
(B) a mixture of methane or n-hexane and air
				  at a concentration of approximately, but less than, 10,000 ppm methane or
				  n-hexane.
(5) the
				  instrument probe shall be traversed around all potential leak interfaces as
				  close to the interface as possible as described in Reference Method
				  21.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28 - Air Emissions Standards for Equipment Leaks › Section 66265.1064 - Recordkeeping Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
(1) Each owner or operator subject to the
				  provisions of this article shall comply with the recordkeeping requirements of
				  this section.
(2) An owner or
				  operator of more than one hazardous waste management unit subject to the
				  provisions of this article may comply with the recordkeeping requirements for
				  these hazardous waste management units in one recordkeeping system if the
				  system identifies each record by each hazardous waste management
				  unit.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1080 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  requirements of this article apply to owners and operators of all facilities
				  that treat, store, or dispose of RCRA hazardous waste in tanks, surface
				  impoundments, or containers subject to either articles 9, 10, or 11 except as
				  section 66265.1 and subsection (b) of this
				  section provide otherwise.
(b) The
				  requirements of this article do not apply to the following waste management
				  units at the facility:
(1) A waste management
				  unit that holds hazardous waste placed in the unit before December 6, 1996, and
				  in which no hazardous waste is added to the unit on or after December 6,
				  1996.
(2) A container that has a
				  design capacity less than or equal to 0.1
				  m3.
(3)
				  A tank in which an owner or operator has stopped adding hazardous waste and the
				  owner or operator has begun implementing or completed closure pursuant to an
				  approved closure plan.
(4) A
				  surface impoundment in which an owner or operator has stopped adding hazardous
				  waste (except to implement an approved closure plan) and the owner or operator
				  has begun implementing or completed closure pursuant to an approved closure
				  plan.
(5) A waste management unit
				  that is used solely for on-site treatment or storage of hazardous waste that is
				  placed in the unit as a result of implementing remedial activities required
				  under the corrective action authorities of RCRA sections
				  3004(u),
				  3004(v), or
				  3008(h); CERCLA
				  authorities; or similar Federal or State authorities.
(6) A waste management unit that is used
				  solely for the management of radioactive mixed waste in accordance with all
				  applicable regulations under the authority of the Atomic Energy Act and the
				  Nuclear Waste Policy Act.
(7) A
				  hazardous waste management unit that the owner or operator certifies is
				  equipped with and operating air emission controls in accordance with the
				  requirements of an applicable Clean Air Act regulation codified under 40 CFR
				  part 60 , part 61, or part 63. For the purpose of complying with this
				  subsection, a tank for which the air emission control includes an enclosure, as
				  opposed to a cover, must be in compliance with the enclosure and control device
				  requirements of section
				  66265.1085(i),
				  except as provided in section
				  66265.1083(c)(5).
(8) A tank that has a process vent as defined
				  in section
				  66260.10.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1082 - Schedule for Implementation of Air Emission Standards

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Owners or operators of facilities
				  existing on December 6, 1996 and subject to articles 9, 10, and 11 shall meet
				  the following requirements:
(1) Install and
				  begin operation of all control equipment or waste management units required to
				  comply with this article and complete modifications of production or treatment
				  processes to satisfy exemption criteria in accordance with section
				  66265.1083(c) by
				  December 6, 1996, except as provided for in subsection (a)(2) of this
				  section.
(2) When control equipment
				  or waste management units required to comply with this article cannot be
				  installed and in operation or modifications of production or treatment
				  processes to satisfy exemption criteria in accordance with section
				  66265.1083(c)
				  cannot be completed by December 6, 1996, the owner or operator shall:
(A) Install and begin operation of the
				  control equipment and waste management units, and complete modifications of
				  production or treatment processes as soon as possible but no later than
				  December 8, 1997.
(B) Prepare an
				  implementation schedule that includes the following information: specific
				  calendar dates for award of contracts or issuance of purchase orders for
				  control equipment, waste management units, and production or treatment process
				  modifications; initiation of on-site installation of control equipment or waste
				  management units, and modifications of production or treatment processes;
				  completion of control equipment or waste management unit installation, and
				  production or treatment process modifications; and performance of testing to
				  demonstrate that the installed equipment or waste management units, and
				  modified production or treatment processes meet the applicable standards of
				  this article.
(C) For facilities
				  subject to the recordkeeping requirements of section
				  66265.73, the owner or operator
				  shall enter the implementation schedule specified in subsection (a)(2)(B) of
				  this section in the operating record no later than December 6, 1996.
(D) For facilities not subject to section
				  66265.73, the owner or operator
				  shall enter the implementation schedule specified in subsection (a)(2)(B) of
				  this section in a permanent, readily available file located at the facility no
				  later than December 6, 1996.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1084 - Waste Determination Procedures

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Waste determination procedure to
				  determine average volatile organic (VO) concentration of a hazardous waste at
				  the point of waste origination.
(1) An owner
				  or operator shall determine the average VO concentration at the point of waste
				  origination for each hazardous waste placed in a waste management unit exempted
				  under the provisions of section
				  66265.1083(c)(1)
				  from using air emission controls in accordance with standards specified in
				  sections 66265.1085 through
				  66265.1088, as applicable to the
				  waste management unit.
(A) An initial
				  determination of the average VO concentration of the waste stream shall be made
				  before the first time any portion of the material in the hazardous waste stream
				  is placed in a waste management unit exempted under the provisions of section
				  66265.1083(c)(1)
				  from using air emission controls, and thereafter an initial determination of
				  the average VO concentration of the waste stream shall be made for each
				  averaging period that a hazardous waste is managed in the unit; and
(B) Perform a new waste determination
				  whenever changes to the source generating the waste stream are reasonably
				  likely to cause the average VO concentration of the hazardous waste to increase
				  to a level that is equal to or greater than the VO concentration limit
				  specified in section
				  66265.1083(c)(1).
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1085 - Standards: Tanks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
				  provisions of this section apply to the control of air pollutant emissions from
				  tanks for which section
				  66265.1083(b)
				  references the use of this section for such air emission control.
(b) The owner or operator shall control air
				  pollutant emissions from each tank subject to this section in accordance with
				  the following requirements, as applicable:
(1) For a tank that manages hazardous waste
				  that meets all of the conditions specified in subsections (b)(1)(A) through
				  (b)(1)(C) of this section, the owner or operator shall control air pollutant
				  emissions from the tank in accordance with the Tank Level 1 controls specified
				  in subsection (c) of this section or the Tank Level 2 controls specified in
				  subsection (d) of this section.
(A) The
				  hazardous waste in the tank has a maximum organic vapor pressure which is less
				  than the maximum organic vapor pressure limit for the tank's design capacity
				  category as follows:
1. For a tank design
				  capacity equal to or greater than 151 m3, the
				  maximum organic vapor pressure limit for the tank is 5.2 kPa.
2. For a tank design capacity equal to or
				  greater than 75 m3 but less than 151
				  m3, the maximum organic vapor pressure limit for the
				  tank is 27.6 kPa.
3. For a tank
				  design capacity less than 75 m3, the maximum organic
				  vapor pressure limit for the tank is 76.6 kPa.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1086 - Standards: Surface Impoundments

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The provisions of this section apply to
				  the control of air pollutant emissions from surface impoundments for which
				  section 66265.1083(b)
				  references the use of this section for such air emission control.
(b) The owner or operator shall control air
				  pollutant emissions from the surface impoundment by installing and operating
				  either of the following:
(1) A floating
				  membrane cover in accordance with the provisions specified in subsection (c) of
				  this section; or
(2) A cover that
				  is vented through a closed-vent system to a control device in accordance with
				  the requirements specified in subsection (d) of this
				  section.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1087 - Standards: Containers

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The provisions of this section apply to the control of air pollutant emissions
				  from containers for which section
				  66265.1083(b)
				  references the use of this section for such air emission control.
(b) General requirements.
(1) The owner or operator shall control air
				  pollutant emissions from each container subject to this section in accordance
				  with the following requirements, as applicable to the container, except when
				  the special provisions for waste stabilization processes specified in
				  subsection (b)(2) of this section apply to the container.
(A) For a container having a design capacity
				  greater than 0.1 m3 and less than or equal to 0.46
				  m3, the owner or operator shall control air
				  pollutant emissions from the container in accordance with the Container Level 1
				  standards specified in subsection (c) of this section.
(B) For a container having a design capacity
				  greater than 0.46 m3 that is not in light material
				  service, the owner or operator shall control air pollutant emissions from the
				  container in accordance with the Container Level 1 standards specified in
				  subsection (c) of this section.
(C)
				  For a container having a design capacity greater than 0.46
				  m3 that is in light material service, the owner or
				  operator shall control air pollutant emissions from the container in accordance
				  with the Container Level 2 standards specified in subsection (d) of this
				  section.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1088 - Standards: Closed-Vent Systems and Control Devices

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) This section applies to each closed-vent
				  system and control device installed and operated by the owner or operator to
				  control air emissions in accordance with standards of this article.
(b) The closed-vent system shall meet the
				  following requirements:
(1) The closed-vent
				  system shall route the gases, vapors, and fumes emitted from the hazardous
				  waste in the waste management unit to a control device that meets the
				  requirements specified in subsection (c) of this section.
(2) The closed-vent system shall be designed
				  and operated in accordance with the requirements specified in section
				  66265.1033(j).
(3) In the case when the closed-vent system
				  includes bypass devices that could be used to divert the gas or vapor stream to
				  the atmosphere before entering the control device, each bypass device shall be
				  equipped with either a flow indicator as specified in subsection (b)(3)(A) of
				  this section or a seal or locking device as specified in subsection (b)(3)(B)
				  of this section. For the purpose of complying with this subsection, low leg
				  drains, high point bleeds, analyzer vents, open-ended valves or lines,
				  spring-loaded pressure relief valves, and other fittings used for safety
				  purposes are not considered to be bypass devices.
(A) If a flow indicator is used to comply
				  with subsection (b)(3) of this section, the indicator shall be installed at the
				  inlet to the bypass line used to divert gases and vapors from the closed-vent
				  system to the atmosphere at a point upstream of the control device inlet. For
				  this subsection, a flow indicator means a device which indicates the presence
				  of either gas or vapor flow in the bypass line.
(B) If a seal or locking device is used to
				  comply with subsection (b)(3) of this section, the device shall be placed on
				  the mechanism by which the bypass device position is controlled (e.g., valve
				  handle, damper lever) when the bypass device is in the closed position such
				  that the bypass device cannot be opened without breaking the seal or removing
				  the lock. Examples of such devices include, but are not limited to, a car-seal
				  or a lock-and-key configuration valve. The owner or operator shall visually
				  inspect the seal or closure mechanism at least once every month to verify that
				  the bypass mechanism is maintained in the closed position.
(4) The closed-vent system shall be inspected
				  and monitored by the owner or operator in accordance with the procedure
				  specified in section
				  66265.1033(k).
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1089 - Inspection and Monitoring Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The owner or operator shall inspect and
				  monitor air emission control equipment used to comply with this article in
				  accordance with the applicable requirements specified in sections
				  66265.1085 through
				  66265.1088.
(b) The owner or operator shall develop and
				  implement a written plan and schedule to perform the inspections and monitoring
				  required by subsection (a) of this section. The owner or operator shall
				  incorporate this plan and schedule into the facility inspection plan required
				  under section
				  66265.15.
1. Change
					 without regulatory effect adding new section filed 6-11-99 pursuant to Health
					 and Safety Code section
					 25159.1
					 (Register 99, No. 24).
Note: Authority cited: Sections
						25150,
						25159,
						25159.5,
						25245
						and
						58012,
						Health and Safety Code. Reference: Sections
						25150,
						25159
						and
						25159.5,
						Health and Safety Code; and 40 CFR section
						265.1089.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 28.5 - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 66265.1090 - Recordkeeping Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each owner or operator of a facility subject to requirements in this article
				  shall record and maintain the information specified in subsections (b) through
				  (j) of this section, as applicable to the facility. Except for air emission
				  control equipment design documentation and information required by subsections
				  (i) and (j) of this section, records required by this section shall be
				  maintained in the operating record for a minimum of 3 years. Air emission
				  control equipment design documentation shall be maintained in the operating
				  record until the air emission control equipment is replaced or otherwise no
				  longer in service. Information required by subsections (i) and (j) of this
				  section shall be maintained in the operating record for as long as the waste
				  management unit is not using air emission controls specified in sections
				  66265.1085 through
				  66265.1088 in accordance with the
				  conditions specified in section
				  66265.1080(d) or
				  section 66265.1080(b)(7)
				  of this article, respectively.
(b)
				  The owner or operator of a tank using air emission controls in accordance with
				  the requirements of section
				  66265.1085 shall prepare and
				  maintain records for the tank that include the following information:
(1) For each tank using air emission controls
				  in accordance with the requirements of section
				  66265.1085, the owner or operator
				  shall record:
(A) A tank identification number
				  (or other unique identification description as selected by the owner or
				  operator).
(B) A record for each
				  inspection required by section
				  66265.1085 that includes the
				  following information:
1. Date inspection was
				  conducted.
2. For each defect
				  detected during the inspection: The location of the defect, a description of
				  the defect, the date of detection, and corrective action taken to repair the
				  defect. In the event that repair of the defect is delayed in accordance with
				  the provisions of section
				  66265.1085 the owner or operator
				  shall also record the reason for the delay and the date that completion of
				  repair of the defect is expected.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 29 - Containment Buildings › Section 66265.1100 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The requirements of this article apply to owners or
					 operators who store or treat hazardous waste in units designed and operated
					 under section
					 66265.1101. These provisions will
					 become effective on February 18, 1993, although the owner or operator may
					 notify the Department of the owner or operator's intent to be bound by this
					 article at an earlier time. The owner or operator is not subject to the
					 definition of land disposal in section
					 66260.10 provided that the
					 unit:
(a) Is a completely enclosed,
				  self-supporting structure that is designed and constructed of manmade materials
				  of sufficient strength and thickness to support themselves, the waste contents,
				  and any personnel and heavy equipment that operate within the unit, and to
				  prevent failure due to pressure gradients, settlement, compression, or uplift,
				  physical contact with the hazardous wastes to which they are exposed; climatic
				  conditions; and the stresses of daily operation, including the movement of
				  heavy equipment within the unit and contact of such equipment with containment
				  walls;
(b) Has a primary barrier
				  that is designed to be sufficiently durable to withstand the movement of
				  personnel, wastes, and handling equipment within the unit;
(c) If the unit is used to manage liquids,
				  has:
(1) A primary barrier designed and
				  constructed of materials to prevent migration of hazardous constituents into
				  the barrier;
(2) A liquid
				  collection system designed and constructed of materials to minimize the
				  accumulation of liquid on the primary barrier; and
(3) A secondary containment system designed
				  and constructed of materials to prevent migration of hazardous constituents
				  into the barrier, with a leak detection and liquid collection system capable of
				  detecting, collecting, and removing leaks of hazardous constituents at the
				  earliest possible time, unless the unit has been granted a variance from the
				  secondary containment system requirements of section
				  66265.1101(b)(4);
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 29 - Containment Buildings › Section 66265.1101 - Design and Operating Standards

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) All containment buildings shall comply
				  with the following design standards:
(1) The
				  containment buildings shall be completely enclosed with a floor, walls, and a
				  roof to prevent exposure to the elements, (e.g., precipitation, wind, runon),
				  and to assure containment of managed wastes.
(2) The floor and containment walls of the
				  unit, including the secondary containment system, if required under subsection
				  (b) of this section, shall be designed and constructed of materials of
				  sufficient strength and thickness to support themselves, the waste contents,
				  and any personnel and heavy equipment that operate within the unit, and to
				  prevent failure due to pressure gradients, settlement, compression, or uplift,
				  physical contact with the hazardous wastes to which they are exposed; climatic
				  conditions; and the stresses of daily operation, including the movement of
				  heavy equipment within the unit and contact of such equipment with containment
				  walls. The unit shall be designed so that it has sufficient structural strength
				  to prevent collapse or other failure. All surfaces to be in contact with
				  hazardous wastes shall be chemically compatible with those wastes. The
				  Department will consider standards established by professional organizations
				  generally recognized by the industry such as the American Concrete Institute
				  (ACI) and the American Society of Testing Materials (ASTM) in judging the
				  structural integrity requirements of this subsection. If appropriate to the
				  nature of the waste management operation to take place in the unit, an
				  exception to the structural strength requirement may be made for light-weight
				  doors and windows that meet these criteria:
(A) They provide an effective barrier against
				  fugitive dust emissions under subsection (c)(1)(D); and
(B) The unit is designed and operated in a
				  fashion that assures that wastes will not actually come in contact with these
				  openings.
(3)
				  Incompatible hazardous wastes or treatment reagents shall not be placed in the
				  unit or its secondary containment system if they could cause the unit or
				  secondary containment system to leak, corrode, or otherwise fail.
(4) A containment building shall have a
				  primary barrier designed to withstand the movement of personnel, waste, and
				  handling equipment in the unit during the operating life of the unit and
				  appropriate for the physical and chemical characteristics of the waste to be
				  managed.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 15 - Interim Status Standards for Owners and Operators of Hazardous Waste Transfer, Treatment, Storage, and Disposal Facilities › Article 29 - Containment Buildings › Section 66265.1103-66265.1110 - Reserved

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Note: Authority cited: Sections
						25150,
						25159,
						25159.5,
						25179.6
						and
						58012,
						Health and Safety Code. Reference: Sections
						25159,
						25159.5
						and
						58012,
						Health and Safety Code and 40 CFR Sections 265.1102 and
						265.1103-265.1110.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 1 - General › Section 66266.2 - List of Recyclable Hazardous Wastes

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Wastes on the list of Recyclable
				  Hazardous Wastes in subdivision (b) are wastes which the Department finds to be
				  both economically and technologically feasible to recycle.
(b) List of Recyclable Hazardous Wastes
acetone
benzene
butanol
carbon tetrachloride
chloroform
ethanol
ethyl acetate
ethylene glycol (used antifreeze)
Freons
hexanes
lead-acid batteries
methanol
methylene dichloride
methyl ethyl ketone
mixed hydrocarbon solvents
paint thinner
perchloroethylene
trichloroethane
toluene
xylenes
used oil
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Amendment of section heading, section and NOTE filed 6-12-2003; operative
					 7-12-2003 (Register 2003, No. 24).
Note: Authority cited: Sections
						25150
						and
						25175,
						Health and Safety Code. Reference: Sections
						25159.5
						and
						25175,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.3 - Requirements for Generator of Recyclable Material. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer filed 9-20-96; operative 10-20-96 (Register 96, No.
					 38).
Note: Authority cited: Sections
						208
						and
						25150,
						Health and Safety Code. Reference: Sections
						25143.2,
						25153,
						25154,
						25159.5
						and
						25170,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.4 - Requirements for Transporter of Recyclable Material. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer filed 9-20-96; operative 10-20-96 (Register 96, No.
					 38).
Note: Authority cited: Sections
						208
						and
						25150,
						Health and Safety Code. Reference: Sections
						25143.2,
						25154,
						25159.5
						and
						25170,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.5 - Requirements for Operator of a Resource Recovery Facility. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Editorial correction of printing error in subsection (a) (Register 92, No.
					 49).
3. Amendment of subsection (a)(5) and NOTE filed 7-1-96;
					 operative 7-31-96 (Register 96, No. 27).
4. Repealer filed 9-20-96;
					 operative 10-20-96 (Register 96, No. 38).
Note: Authority cited: Sections
						25150,
						25159,
						58004
						and
						58012,
						Health and Safety Code. Reference: Sections
						25143.2,
						25154,
						25170,
						25200
						and
						25201,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.6 - Exclusions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The following
				  materials are not regulated under this division:
(1) a product for use in agriculture that was
				  processed from a non-RCRA hazardous waste at a facility which is authorized by
				  the Department pursuant to this division and which is licensed by the
				  California Department of Food and Agriculture pursuant to Food and Agricultural
				  Code sections
				  14551 or
				  15051, and that meets the
				  requirements of that Department for such use;
(2) surplus material as defined in section
				  66260.10.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.7 - Series a Resource Recovery Facility Permit. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer filed 9-20-96; operative 10-20-96 (Register 96, No.
					 38).
Note: Authority cited: Sections
						208
						and
						25150,
						Health and Safety Code. Reference: Sections
						25159.5,
						25170,
						25200
						and
						25201,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.8 - Series B Resource Recovery Facility Permit. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer filed 9-20-96; operative 10-20-96 (Register 96, No.
					 38).
Note: Authority cited: Sections
						208
						and
						25150,
						Health and Safety Code. Reference: Sections
						25159.5,
						25170,
						25200
						and
						25201,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.9 - Series C Resource Recovery Facility Permit. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer filed 9-20-96; operative 10-20-96 (Register 96, No.
					 38).
Note: Authority cited: Sections
						208
						and
						25150,
						Health and Safety Code. Reference: Sections
						25159.5,
						25170,
						25200
						and
						25201,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.10 - Criteria for Compliance. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer filed 9-20-96; operative 10-20-96 (Register 96, No.
					 38).
Note: Authority cited: Sections
						208
						and
						25150,
						Health and Safety Code. Reference: Sections
						25159.5,
						25170,
						25200
						and
						25201,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.11 - General Provisions for Resource Recovery Facilities

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) No person shall create, manufacture, or
				  produce from a hazardous waste, a product which poses a hazard to health,
				  safety or the environment under the circumstances of its intended
				  use.
1. New
					 section filed 5-24-91; operative 7-1-91 (Register 91, No. 22).
2.
					 Repealer of subsection (a) and subsection relettering filed 9-20-96; operative
					 10-20-96 (Register 96, No. 38).
Note: Authority cited: Sections
						208
						and
						25150,
						Health and Safety Code. Reference: Sections
						25159.5,
						25170,
						25200
						and
						25201,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.12 - Requirements for Persons Who Store and/or Recycle Recyclable Materials. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. New
					 section filed 12-23-92; operative 1-22-93 (Register 93, No. 2).
2.
					 Repealer filed 9-20-96; operative 10-20-96 (Register 96, No. 38). Article 3.
					 Requirements for Recyclable Materials That Are Placed on the Land (Used in a
					 Manner That Constitutes Disposal)
Note: Authority cited: Sections
						208,
						25150
						and
						25159,
						Health and Safety Code. Reference: Sections
						25159
						and
						25159.5,
						Health and Safety Code; 40
						CFR Section
						261.6.
California Code of Regulations › Title 22 - Social Security › Division 4.5 - Environmental Health Standards for the Management of Hazardous Waste › Chapter 16 - Recyclable Materials (Recyclable Hazardous Wastes) › Article 2 - Generator, Transporter and Facility Operator Requirements › Section 66266.20 - Applicability

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This article applies to recyclable materials that, in the
					 course of being recycled, are placed on the land, either without mixing with
					 other materials or after mixing with other materials. These recyclable
					 materials are considered to be: "used in a manner constituting disposal"
					 pursuant to subdivisions (e)(1) and (e)(2) of section
					 25143.2
					 of the Health and Safety Code.
1. Amendment
					 of article heading, new article 3 (sections
					 66266.20-66266.21) and section
					 filed 6-9-97; operative 1-1-98 (Register 97, No.
					 24).
Note: Authority cited: Sections
						25143.2(e)(2)
						and
						25150(e),
						Health and Safety Code. Reference: Sections
						25143.2(f),
						25150(e),
						25170(i)
						and
						25244.1,
						Health and Safety Code.