reglab/statecodes huggingface dataset:
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2170 - Protection of Outdoor Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) All electrical equipment, including
				  switches, circuit breakers, receptacles, lighting fixtures, control equipment,
				  and metering devices located in either damp or wet locations or outside of a
				  unit, accessory building or structure, or a building component designed as a
				  weatherproof structure shall be constructed of, or installed in, equipment
				  approved for damp or wet locations.
(b) Meter sockets, without meters installed,
				  shall be blanked off with an approved blanking plate before the service is
				  energized.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2176 - Aluminum Conductors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Connections of aluminum conductors shall
				  be made only inside boxes or equipment enclosures which are designed and
				  installed to prevent the entry or accumulation of moisture within the
				  enclosure.
(b) Only connectors
				  which are listed for use with aluminum conductors shall be used to connect
				  aluminum conductors. If more than one conductor is connected to a connector,
				  the connector shall be provided with a terminal fitting for each
				  conductor.
(c) Prior to inserting
				  an aluminum conductor into the connector, the conductor from which the
				  insulation has been removed shall be wire-brushed and sealed with an approved
				  oxide-inhibiting joint compound.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2178 - Mechanical Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where subject to physical damage from vehicular traffic or
					 other causes, the lot service equipment shall be protected by posts, fencing or
					 other barriers approved by the enforcement agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2180 - Lot Service Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The rating of the overcurrent protection
				  in the lot service equipment shall not exceed the rating of the connected
				  feeder assembly. Lot service equipment may contain any or all of the approved
				  receptacles conforming with section 2186 of this chapter.
(b) Lot service equipment may also contain
				  the means for supplying accessory structures or other electrical equipment
				  located on the lot, provided the lot service equipment is designed and listed
				  for such application.
(c) Only one
				  (1) power supply connection shall be made to a unit.
(d) Lot service equipment may also contain
				  additional receptacles for supplying portable electrical equipment, provided
				  that such receptacles are listed grounding-type receptacles. All 120-volt,
				  single-phase, 15- and 20-ampere receptacle outlets in lot service equipment
				  shall be protected by ground-fault circuit protection. The requirement for
				  ground-fault circuit protection shall not apply to equipment or installations
				  constructed, installed, or approved for construction or installation prior to
				  September 1, 1975.
(e) When an
				  electrical meter is installed as an integral component of the lot service
				  equipment, it shall be of a class or rating that will accurately measure all
				  loads up to the rated ampacity of the lot service equipment.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18871.10,
						Health and Safety Code. Reference: Sections 18871, 18871.10 and 18873.3, Health
						and Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2182 - Installation of Lot Service Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Approved lot service equipment supplied
				  by underground feeders may be of the self-supporting type and shall be
				  stabilized by concrete not less than three and one-half (3 ½ ) inches
				  thick and surrounding the equipment base by not less than six (6) inches beyond
				  the equipment base in all directions.
(b) Approved lot service equipment supplied
				  by underground feeders requiring installation on a mounting post shall be
				  securely fastened to a nominal four (4) inches by four (4) inches redwood or
				  pressure treated post or equivalent. The post shall be installed not less than
				  24 inches in the earth and stabilized by a concrete pad. The concrete pad shall
				  be not less than three and one-half (3 ½ ) inches thick, surrounding the
				  post base by not less than six (6) inches beyond the post base in all
				  directions. The equipment shall be mounted with the bottom of the equipment not
				  less than twelve (12) inches above the stabilizing concrete pad.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2183 - Access to Electrical Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All park or lot service equipment shall be accessible by an
					 unobstructed entrance or passageway not less than twenty-four (24) inches in
					 width and seventy-eight (78) inches high, and shall have a working space not
					 less than thirty (30) inches wide and thirty-six (36) inches deep in front of
					 any panel opening on the service equipment used for examination, servicing,
					 adjustment, or maintenance. The lot service equipment shall be located and
					 maintained not less than twelve (12) inches nor more than seventy-eight (78)
					 inches above the stabilizing pad.
EXCEPTION: parks constructed prior to July 1, 1979, shall
					 have a working space not less than 30 inches wide and 30 inches deep in front
					 of and centered on the service equipment.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment filed 7-22-2005;
					 operative 7-22-2005 pursuant to Government Code section 11343.4 (Register 2005,
					 No. 29).
3. Editorial correction of HISTORY 2 (Register 2005, No.
					 33).
4. Amendment filed 1-21-2009; operative 1-21-2009 pursuant to
					 Government Code section 11343.4 (Register 2009, No.
					 4).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18871 and 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2185 - Electrical Appliances and Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) When electrical equipment or fixed
				  appliances are installed to serve an accessory structure, the installation
				  shall be supplied by means of a permanent wiring method to the lot service
				  equipment, provided the lot service equipment is designed and listed for the
				  additional load.
(b) If the park
				  electrical system or the feeder supplying the lot electrical service equipment
				  does not have the ampacity to supply the equipment in addition to its connected
				  load, a permit to construct, as required in section 2018 of this chapter, shall
				  be obtained for alteration of the required service supply and
				  equipment.
(c) All electrical
				  appliances and equipment not located within enclosed weatherproof structures
				  must be approved for use in wet locations.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. New subsection (c) filed
					 7-22-2005; operative 7-22-2005 pursuant to Government Code section 11343.4
					 (Register 2005, No. 29).
3. Editorial correction of HISTORY 2
					 (Register 2005, No. 33).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2186 - Lot Receptacles

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A receptacle used to supply electrical
				  energy to a unit shall conform with the American National Standards
				  Institute-National Electrical Manufacturers Association (ANSI-NEMA) Standard,
				  WD-6, 1997 for one of the following configurations:
(1) 125/250 volts, 50-amperes, 3 pole, 4
				  wire, grounding type for 120/240 volt systems.
(2) 125 volts, 30-amperes, 2 pole, 3 wire,
				  grounding type for 120 volt systems.
(3) 125 volts, 20-amperes, 2 pole, 3 wire,
				  grounding type for supplying units having only one 15 or 20-ampere branch
				  circuit.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2188 - Existing Electrical Installations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Lot service equipment shall have the
				  capacity to supply the unit, appliance, accessory building or structure, and
				  building component located on the lot. The park operator may prohibit the
				  installation of a unit, appliance, accessory building or structure, or building
				  component that exceeds the rated capacity of the lot electrical service, unless
				  the load in the unit, appliance, accessory building or structure, or building
				  component is reduced. If the unit or electrical appliance is allowed to be
				  installed by the park and the connected load on the lot exceeds the rated
				  capacity of the lot electrical service equipment, the lot electrical service
				  equipment and feeders shall be replaced with equipment and conductors properly
				  rated to supply the unit, appliance, or accessory building or structure.
				  Notwithstanding the provisions of this subsection, park approval is required
				  when an alteration or addition to the existing electrical system of the unit,
				  appliance, accessory building or structure, or building component will exceed
				  the rated capacity of the lot service equipment.
(b) The enforcement agency may order unsafe
				  installations of existing electrical systems or portions thereof to be
				  reconstructed or altered, if necessary for the protection of life and
				  property.
(c) The use of electrical
				  equipment and installations in existence prior to the effective date of
				  applicable amendments to this chapter may be continued, provided such equipment
				  and installations are maintained in safe operating condition and the calculated
				  connected loads do not exceed the rated ampacity of such equipment and
				  installations.
(d) Lot electrical
				  service equipment may continue supplying accessory buildings or structures or
				  building components or other electrical equipment located outside the unit,
				  provided the lot electrical service has the capacity to serve them and the
				  equipment is maintained in a safe operating condition.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18871, 18871.10, 18872 and 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 3 - Electrical Requirements › Section 2190 - Authority to Order Disconnect - Electrical

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The enforcement agency is authorized to require any
					 electrical installation or equipment found to be defective, and in such
					 condition as to endanger life or property, to be disconnected. Installations
					 which have been disconnected shall not be re-energized until a permit has been
					 obtained to repair the electrical installation or equipment and the work has
					 been inspected and approved by the enforcement agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18871 and 18873.3, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2200 - Application and Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The requirements of this article shall apply to the construction, installation,
				  arrangement, alteration, use, maintenance, and repair of fuel gas equipment and
				  installations for supplying fuel gas to parks, and units in all parts of the
				  state.
(b) Existing construction,
				  connections, and installations of fuel gas made before the effective date of
				  the requirements of this chapter may continue in use so long as they were in
				  compliance with requirements in effect at the date of their installation and
				  are not found to be substandard.
1. New
					 article 4 (sections 2200-2236) and section filed 7-6-2004; operative 7-6-2004
					 pursuant to Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Sections 18865, 18872 and 18873.4,
						Health and Safety Code. Reference: Sections 18872 and 18873.4, Health and
						Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2208 - Basic Fuel Gas Regulations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Except as otherwise permitted or required
				  by this article, all fuel gas equipment and installations for supplying fuel
				  gas to units or accessory buildings or structures, and fuel gas piping systems
				  outside of permanent buildings in parks, shall comply with the requirements
				  found in the California Plumbing Code, Chapter 12.
(b) The requirements for fuel gas equipment
				  and installations within permanent buildings in parks are located in the
				  California Mechanical Code, and the California Plumbing Code unless provided
				  otherwise in this chapter. However, in a city, county, or city and county,
				  which has assumed responsibility for enforcement of the Mobilehome Parks Act
				  and Special Occupancy Parks Act, pursuant to sections 18300 and 18865 of the
				  Health and Safety Code, and has adopted and is enforcing a plumbing and
				  mechanical code equal to or greater than the requirements of The California
				  Plumbing Code and California Mechanical Code, may enforce its code as it
				  pertains to permanent buildings.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.4, Health
						and Safety Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2210 - Liquefied Petroleum Gas (LPG)

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All LPG equipment and installations of tanks one hundred
					 twenty-five (125) US gallons or larger shall comply with the applicable
					 provisions of the Unfired Pressure Vessel Safety Orders, California Code of
					 Regulations, Title 8, Division 1, Chapter 4, Subchapter 1, unless otherwise
					 provided by this chapter.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment filed 1-21-2009;
					 operative 1-21-2009 pursuant to Government Code section 11343.4 (Register 2009,
					 No. 4).
Note: Authority cited: Sections 18865 and 18873.4, Health
						and Safety Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2211 - LPG Tanks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  LPG tank installations in parks must conform to the provisions related to LPG
				  tanks contained in Chapter 38 of the California Fire Code.
(b) Units designed and constructed with
				  securely mounted tanks may be served by either the lot or mounted tanks, but
				  not by both at the same time.
(c) A
				  permit from the enforcement agency is required to install any LPG fuel tank
				  exceeding sixty 60 U. S. gallons.
(d) LPG tanks shall be designed and
				  constructed in accordance with nationally recognized standards for unfired
				  pressure vessels.
(e) LPG tanks
				  shall be securely, but not permanently, fastened to the mobilehome or
				  recreational vehicle hitch or a substantial post to prevent accidental
				  overturning.
(f) All LPG tanks
				  located in a floodplain as designated by the local floodplain management
				  agency, shall be securely anchored to prevent flotation.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment of subsection (a)
					 filed 1-21-2009; operative 1-21-2009 pursuant to Government Code section
					 11343.4 (Register 2009, No. 4).
3. New subsections (e) and (f) filed
					 2-18-2011; operative 2-18-2011 pursuant to Government Code section 11343.4
					 (Register 2011, No. 7).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2212 - Location of LPG Tanks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Except for tanks on personal, portable LPG fueled appliances, no LPG tank shall
				  be stored or located in any of the following locations:
(1) within five (5) feet of any source of
				  ignition (lot electrical service is not a source of ignition);
(2) within five (5) feet of any mechanical
				  ventilation air intake;
(3) under
				  any unit or habitable accessory building;
(4) within any structure or area where three
				  (3) or more sides are more than fifty (50) percent closed; or
(5) Within five (5) feet of property lines
				  and lot lines of adjacent lots that can be built upon.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2216 - Installation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) All main line
				  gas piping installed below ground shall have a minimum earth cover of:
(1) twenty-four (24) inches or,
(2) eighteen (18) inches when installed in
				  the same trench as other utilities; and covered with clean fill free from
				  stones, boulders, cinderfill, construction debris or other material that may
				  damage the piping.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2218 - Park Gas System Shutoff Valve

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A readily accessible and identified shutoff valve
					 controlling the flow of gas to the entire park-owned gas piping system shall be
					 installed at the point of connection to the service piping or supply
					 connection.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2220 - Lot Gas Shutoff Valve

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each lot shall have a gas shutoff valve, listed for its intended use by a
				  department-approved listing agency, installed in a readily accessible location
				  upstream of the lot gas outlet.
(b)
				  The valve shall be located on the lot gas riser outlet at a height of not less
				  than six (6) inches above grade.
(c) The lot gas shutoff valve shall not be
				  located under or within any unit, or accessory building or structure.
EXCEPTION: gas shut-off valves may be located under an
					 awning or carport that is not enclosed complying with Article 9 of this
					 chapter.
(d) Whenever the
				  lot gas riser outlet is not in use, it shall be closed with an approved cap or
				  plug to prevent accidental discharge of gas.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2222 - Lot Gas Outlet

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The gas riser outlet shall terminate within four (4) feet of the unit, or
				  proposed location of the unit on the lot.
(b) Each unit connected to the gas riser
				  outlet shall be connected by a listed flexible gas connector in accordance with
				  section 2354 of this chapter.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2226 - Gas Meters

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  When gas meters are installed, they shall not depend on the gas riser outlet
				  for support. Gas meters shall be adequately supported by a post and bracket or
				  by other means approved by the enforcement agency.
(b) Meters shall not be installed beneath
				  units, in unventilated or inaccessible locations, or closer than three (3) feet
				  from sources of ignition. The unit electrical service equipment shall not be
				  considered a source of ignition when not enclosed in the same compartment with
				  a gas meter.
(c) All gas meter
				  installations shall be provided with a shutoff valve or cock located adjacent
				  to and on the inlet side of the meter. In the case of a single meter
				  installation utilizing an LPG tank, the tank service valve may be used in lieu
				  of the shutoff valve or cock.
(d)
				  Each meter installed shall be in a readily accessible location and shall be
				  provided with unions or other fittings so as to be easily removed and replaced
				  while maintaining an upright position.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment of subsection (c) and
					 repealer of subsection (e) filed 7-22-2005; operative 7-22-2005 pursuant to
					 Government Code section 11343.4 (Register 2005, No. 29).
3.
					 Editorial correction of HISTORY 2 (Register 2005, No.
					 33).
Note: Authority cited: Sections 18865 and 18873.4, Health
						and Safety Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2228 - Mechanical Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where subject to physical damage from vehicular traffic or
					 other causes, all gas riser outlets, regulators, meters, valves, tanks, or
					 other exposed equipment shall be protected by posts, fencing, or other barriers
					 approved by the enforcement agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2229 - Regulator and Relief Vents

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Atmospherically controlled regulators shall be installed in
					 such a manner that moisture cannot enter the regulator vent and accumulate
					 above the diaphragm. Where the regulator vent may be obstructed because of snow
					 or icing conditions, a shield, hood, or other device approved by the
					 enforcement agency shall be provided to guard against closing the vent
					 opening.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2230 - Required Gas Supply

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The minimum hourly volume of gas required at each lot outlet, or any section of
				  a park gas piping system shall be calculated as shown in Table
				  2230-1.
(b) Required gas supply for
				  other fuel gas consuming appliances connected to the park gas piping system
				  shall be calculated as provided in the California Plumbing Code, Chapter 12.
Table 2230-1
Demand Factors for Use in
								Calculating Gas Piping Systems in Parks
Number of Lots
BTU Per Hours Per Lot
1
125,000
2
117,000
3
104,000
4
96,000
5
92,000
6
87,000
7
83,000
8
81,000
9
79,000
10
77,000
11-20
62,000
21-30
62,000
31-40
58,000
41-60
55,000
Over 60
50,000
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2232 - Gas Pipe Size

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The size of each section of a gas piping system shall be
					 calculated as provided in the California Plumbing Code, Chapter 12 or by other
					 standard engineering methods acceptable to the enforcement
					 agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 4 - Fuel Gas Requirements › Section 2236 - Authority to Order Disconnect of Fuel Gas Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The enforcement agency shall require the
				  gas utility or person supplying gas to a park to disconnect any gas piping or
				  equipment found to be defective and in such condition as to endanger life or
				  property.
(b) Gas piping or
				  equipment which has been ordered disconnected by the enforcement agency shall
				  not be reconnected to a gas supply until a permit has been obtained to repair,
				  alter or reconstruct the gas piping and the work has been inspected and
				  approved by the enforcement agency.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18871 and 18873.4, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2240 - Application and Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  The requirements of this article shall apply to the construction, installation,
				  arrangement, alteration, use, maintenance, and repair of all plumbing equipment
				  and installations to supply water to, and dispose of sewage from, units,
				  accessory buildings or structures and permanent buildings in all parts of the
				  state.
(b) Existing plumbing
				  construction, connections, and installations made before the effective date of
				  the requirements of this chapter may continue in use so long as they were in
				  compliance with requirements in effect at the date of their installation and
				  are not found to be substandard.
1. New
					 article 5 (sections 2240-2284) and section filed 7-6-2004; operative 7-6-2004
					 pursuant to Government Code section 11343.4 (Register 2004, No.
					 28).
Note: Authority cited: Sections 18865, 18871.4, 18872 and
						18873.1, Health and Safety Code. Reference: Section 18871.4, 18872 and 18873.1,
						Health and Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2246 - Basic Plumbing Regulations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Except as otherwise permitted or required
				  by this article, all requirements for plumbing equipment and installations
				  outside of permanent buildings in parks shall comply with the California
				  Plumbing Code, with the exception of Chapter 1.
If there is any conflict between the provisions of this
					 chapter and the California Plumbing Code, the provisions of this chapter shall
					 prevail.
(b) All
				  requirements for plumbing equipment and installations within permanent
				  buildings in parks shall comply with the California Plumbing Code, except in a
				  city, county, or city and county, which has assumed enforcement responsibility
				  and has adopted, and is enforcing, a plumbing code equal to or greater than the
				  requirements of this article.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.1, Health
						and Safety Code. Reference: Sections 18865 and 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2248 - Sewage Disposal

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  All park drainage systems shall discharge into a public sewer or a private
				  sewage disposal system approved by the local health department.
(b) Septic tanks shall not be located within
				  five (5) feet of any unit, accessory building or structure, or permanent
				  building. Leach or disposal fields shall not be located within eight (8) feet
				  of any unit, accessory building or structure, or permanent building.
(c) Recreational vehicle drain outlets shall
				  discharge into the park drainage system, or a closed, vented container approved
				  by the local health department.
(d)
				  Recreational vehicles occupying lots without drain inlets, or approved
				  containers, shall have the drain outlets of the vehicles capped with a
				  gas-tight cover.
(e) Any
				  alternative means of sewage removal and disposal in a park shall be approved by
				  the local health department.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Sections 18871.4 and 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2252 - Installation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Listed nonmetallic pipe and fittings installed in park
					 drainage systems shall be installed in accordance with their listing and
					 applicable standards. When installed under roadways, minimum depth of cover for
					 nonmetallic drain pipe shall be thirty-six (36) inches. The pipe shall be
					 bedded on a minimum of three (3) inches of clean sand and shall be backfilled
					 with a minimum cover depth of six (6) inches of clean sand, granulated earth or
					 similar material. The trench shall then be backfilled in thin layers to a
					 minimum of twelve (12) inches above the top of the nonmetallic pipe with clean
					 earth, which shall not contain stones, boulders or other materials, which would
					 damage or break the pipe.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Sections 18865 and 18873.1, Health
						and Safety Code. Reference: Sections 18872 and 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2254 - Drain Inlet

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) On
				  lots provided with a drain inlet for a unit, the drain inlet shall be not less
				  than three (3) inches in diameter and shall be connected to an approved sewage
				  disposal system.
(b) When drain
				  inlets are provided, they shall accommodate a threaded or clamp-type fitting
				  for connecting drain connectors at proper grade. The drain inlet shall be
				  accessible at ground level. The vertical riser of a drain inlet shall not
				  exceed three (3) inches in height above the concrete supporting slab. Drain
				  inlets shall be gas-tight when not in use.
(c) Each drain inlet shall be protected from
				  movement by being encased in a concrete slab not less than three and one-half
				  (3 ½ ) inches thick and which surrounds the inlet by not less than six
				  (6) inches on any side.
(d) In
				  parks constructed after July 7, 2004, that contain lot drain inlets, the
				  opening of the drain inlet shall not extend above the surrounding concrete. The
				  surface of the concrete surrounding the drain inlet shall be smooth finished
				  concrete and shall slope a minimum of one-quarter ( ¼ ) inch per foot
				  from the outer edge to the inner edge of the drain inlet.
(e) Drain inlets and extensions to grade
				  shall be of material approved for use under or within a building.
(f) The lot drain inlet shall be located
				  within four (4) feet of the outside of the unit.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
2. Amendment of subsection (e)
					 filed 12-26-2006; operative 1-2-2007 pursuant to Government Code section
					 11343.4 (Register 2006, No. 52).
Note: Authority cited: Sections 18865 and 18873.1, Health
						and Safety Code. Reference: Section 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2258 - Trap

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A lot drain
				  inlet shall be provided with a trap except where:
(1) a recreational vehicle manufactured prior
				  to January 1, 1999, is bearing an insignia of approval issued by the
				  department, or
(2) a recreational
				  vehicle manufactured on or after January 1,1999, bearing a label or insignia
				  indicating that the recreational vehicles manufacturer's construction and
				  designs comply with either the American National Standards Institute (ANSI)
				  Standard on recreational vehicles, A119.2, or the ANSI Standard on recreational
				  vehicle park trailers, A119.5, is connected to the lot drain
				  inlet.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2260 - Venting

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Where a drain inlet trap is provided, it shall be
					 individually vented with a vent pipe of not less than two (2) inches interior
					 diameter unless the system is a wet vented system as provided in section 2264
					 of this article.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2262 - Vent Location and Support

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All vent pipes in outdoor locations shall be located at
					 least ten (10) feet from an adjoining property line and shall extend at least
					 ten (10) feet above ground level. All vent pipes shall be supported by at least
					 the equivalent of a four (4) inch by four (4) inch nominal dimension redwood
					 post securely anchored in the ground. One-piece galvanized iron vent pipes may
					 be self-supporting if securely anchored at their base in concrete at least,
					 twelve (12) inches in depth and extending a minimum four (4) inches out from
					 the pipe.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2264 - Wet Vented Systems

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) In
				  lieu of the individual vents, the park drainage system may be wet vented by
				  means of a combination drain, waste, and vent system. Wet vented systems in
				  which the trap for one or more lots is not individually vented shall be of
				  sufficient size and provided with an adequate vent or vents to assure free
				  circulation of air. Wet vented drainage systems may be permitted only when each
				  such system conforms to Table 2268-1 and Table 2268-2 and all of the following
				  requirements for such systems:
(1) A wet
				  vented drainage system shall have a terminal vent installed not more than
				  fifteen (15) feet downstream from the uppermost trap on any branch line and
				  shall be relief vented at intervals of not more than one hundred (100) feet or
				  portion thereof.
(2) Wet vented
				  drainage laterals shall be not more than six (6) feet in length for three (3)
				  inch diameter pipe and not more than fifteen (15) feet in length for four (4)
				  inch diameter pipe.
(3) No vertical
				  drain pipe shall be permitted in any wet vented drainage system, except the
				  tail pipe of the trap or riser of the drain inlet. Tail pipes shall be as short
				  as possible, and in no case shall exceed two (2) feet in
				  length.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2266 - Systems Without Traps

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Terminal or relief vents are not required for drainage
					 systems without traps.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2268 - Pipe Size

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each
				  lot drain inlet shall be assigned a waste loading value of six (6) fixture
				  units and each park drainage system shall be sized according to Table 2268-1 or
				  as provided herein. Drainage laterals shall be not less than three (3) inches
				  in diameter.
(b) A park drainage
				  system in which the grade, slope, or sizing of drainage pipe does not meet the
				  minimums specified in Tables 2268-1 or 2268-2 shall be designed by a registered
				  engineer for a minimum velocity flow of two (2) feet per second.
(c) Park drainage systems installed without
				  P-traps or vents may be sized for individually vented systems in accordance
				  with Table 2268-1 for individually vented systems.
(d) A park drainage system which exceeds the
				  fixture unit loading of Table 2268-1 shall be designed by a registered
				  engineer.
Table 2268-1
Drainage Pipe Diameter and Number of
								Fixture Units on Drainage System
Maximum
							 No.
Maximum No.
Terminal
							 &
of Fixture
							 Units
of Fixture Units
Relief
							 Vent
Size of
							 Drainage
Individually
Wet
							 Vented
Wet Vented
Pipe (Inches)
Vented
							 System
System
System
							 (Inches)
3
35
14
2
4
180
35
3
5
356
180
4
6
600
356
4
Table 2268-2
Minimum Grade and Slope of Drainage
								Pipe
Slope
Slope
Pipe
							 Size
per 100 ft.
Pipe
							 Size
per 100 ft.
(inches)
(inches)
(inches)
(inches)
2
25
6
8
3
20
8
4
4
15
10
3 ½
5
11
12
3
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865, Health and Safety
						Code. Reference: Section 18873.1, Health and Safety
						Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 2.2 - Special Occupancy Parks › Article 5 - Plumbing Requirements › Section 2269 - Recreational Vehicle Sanitation Stations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Recreational vehicle sanitation stations
				  shall be provided in an accessible location.
(b) One recreational vehicle sanitation
				  station shall be provided for each one hundred (100) lots or portion thereof
				  not provided with three (3) inch drain inlets.
(c) Recreational vehicle sanitation stations
				  are not required in tent camps, incidental camping areas, or dry camps, but if
				  provided, they shall comply with the requirements of this Article.
1. New
					 section filed 7-6-2004; operative 7-6-2004 pursuant to Government Code section
					 11343.4 (Register 2004, No. 28).
Note: Authority cited: Section 18865.1, Health and Safety
						Code. Reference: Sections 18865.1, 18871.3, 18871.4 and 18873.1, Health and
						Safety Code.