reglab/statecodes huggingface dataset:
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › Section 2553.19 - Sizing of Feeder Conductors for Television Studio Sets

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) General. It shall be permissible to apply
						the demand factors listed in Table 2553.19(a) to that portion of the maximum
						possible connected load for studio or stage set lighting for all permanently
						installed feeders between substations and stages and to all permanently
						installed subfeeders between the main stage switchboard and stage distribution
						centers or location boards.
TABLE 2553.19(a) DEMAND FACTORS FOR STAGE SET
						  LIGHTING
Total Stage Set
								  Lighting
Feeder Demand
Load
								  (Wattage)
Factors
First 50,000 or less
								  at..........................
..........................100%
Next 50,001 to 100,000
								  at..........................
..........................75%
Next 100,001 to 200,000
								  at..........................
..........................60%
All over
								  200,000..........................
..........................50%
(b) Portable Feeders. A demand factor of 50
						percent of maximum possible connected load shall be permitted for all portable
						feeders.
(Title 24, Part 3, Section
						  530-19.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of Table 2553.19(a) filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › Section 2553.20 - Grounding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Metal-clad cable, metal raceways, and all
						  noncurrent-carrying metal parts of appliances, devices, and equipment shall be
						  grounded as specified in Article 11. This shall not apply to pendant and
						  portable lamps, to stage lighting and stage sound equipment, nor to other
						  portable or semi-portable special stage equipment operating at not over 150
						  volts to ground.
(Title 24, Part 3, Section
						  530-20.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › VIEWING, CUTTING, AND PATCHING TABLES › Section 2553.41 - Lamps at Tables

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Only composition or metal-sheathed, porcelain,
							 keyless lampholders equipped with suitable means to guard lamps from physical
							 damage and from film and film scrap shall be used at patching, viewing, and
							 cutting tables.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › FILM STORAGE VAULTS › Section 2553.51 - Lamps in Cellulose Nitrate Film Storage Vaults

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Lamps in cellulose nitrate film storage vaults shall
							 be rigid fixtures of the glass enclosed and gasketed type. Lamps shall be
							 controlled by a switch having a pole in each ungrounded conductor. This switch
							 shall be located outside of the vault and provided with a pilot light to
							 indicate whether the switch is on or off. This switch shall disconnect from all
							 sources of supply all ungrounded conductors terminating in any outlet in the
							 vault.
(Title 24, Part 3, Section
							 530-51.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › FILM STORAGE VAULTS › Section 2553.52 - Motors and Other Equipment in Cellulose Nitrate Film Storage Vaults

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No receptacles, outlets, electric motors, heaters,
							 portable lights, or other portable electric equipment shall be located in film
							 storage vaults.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › SUBSTATIONS › Section 2553.64 - Working Space and Guarding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Working space and guarding in permanent fixed
							 substations shall comply with Section
							 2340.16 and
							 2340.17.
EXCEPTION: Switchboards of not over 250 volts DC
							 between conductors, when located in substations or switchboard rooms accessible
							 to qualified persons only, shall not be required to be dead-front.
(Title 24, Part 3, Section
							 530-64.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › SUBSTATIONS › Section 2553.65 - Portable Substations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Wiring and equipment in portable substations shall
							 conform to the sections applying to installations in permanent fixed
							 substations; but, due to the limited space available, the working spaces shall
							 be permitted to be reduced, provided that the equipment shall be so arranged
							 that the operator can do his work safely, and so that other persons in the
							 vicinity cannot accidentally come into contact with current-carrying parts or
							 bring conducting objects into contact with them while they are
							 energized.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c), Health
								and Safety Cod.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 71 - Motion-Picture Studios and Similar Locations › SUBSTATIONS › Section 2553.66 - Grounding at Substations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Noncurrent-carrying metal parts shall be
							 grounded.
EXCEPTION: Frames of DC circuit breakers installed on
							 switchboards. (Title 24, Part 3, Section
							 530-66.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › GENERAL › Section 2554.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This article covers motion picture projectors and
							 associated equipment of the professional and nonprofessional types.
For further information, see Storage and Handling of
							 Cellulose Nitrate Motion Picture Film (NFPA No. 40-1982).
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.2 - Professional Projector-Definition

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The professional projector is a type employing 35- or
							 70-millimeter film which has a minimum width of 1 3/8 inches (35 mm) and has on
							 each edge 5.4 perforations per inch, or a type using carbon arc, Xenon, or
							 other light source equipment which develops hazardous gases, dust, or
							 radiation.
1.
							 Renumbering and amendment of former Section
							 2554.10 to Section
							 2554.2 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37). For history of former section,
							 see Register 83, No. 45.
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.10 - Location of Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Motor generator sets, transformers, rectifiers,
							 rheostats, and similar equipment for the supply or control of current to arc
							 lamps on projectors shall, if practicable, be located in separate rooms. Where
							 placed in the projector room, they shall be so located or guarded that arcs or
							 sparks cannot come in contact with film, and motor generator sets shall have
							 the commutator end or ends protected.
1.
							 Renumbering and amendment of former Section
							 2554.10 to Section
							 2554.2, and renumbering and
							 amendment of former Section
							 2554.17 to Section
							 2554.10 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37). For history of former section,
							 see Register 83, No. 45.
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.11 - Equipment Prohibited

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Switches, overcurrent devices, or other equipment not
							 normally required or used for projectors, sound reproduction, flood, or other
							 special effect lamps or other equipment shall not be installed in such booths
							 or rooms.
EXCEPTION: Remote control switches for the control of
							 auditorium lights or a switch for the motor operating the curtain at the motion
							 picture screen.
(Title 24, Part 3, Section
							 540-11(b) without
							 Exception 2.)
1.
							 Renumbering and amendment of former Section
							 2554.19 to Section
							 2554.11 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37). For history of former section,
							 see Register 83, No. 45.
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.12 - Motor-Driven Projectors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Motor-driven projectors shall be approved for the
							 purpose as an assembly or shall comply with all of the following
							 conditions:
(a) A listed projector
						  shall be used.
(b) A listed
						  projector lamp shall be used.
(c)
						  Motors shall be so designed or guarded as to prevent ignition of film by sparks
						  or arcs.
(d) Projectors shall be in
						  charge of a qualified operator.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment of subsection (c) filed 8-27-86; effective thirtieth day thereafter
							 (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code, and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.13 - Conductors Size

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Conductors supplying outlets for arc projectors of
							 the professional type shall not be smaller than No. 8 and shall be of
							 sufficient size for the projector employed.
(Title 24, Part 3, Section
							 540-13.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.14 - Conductors on Lamps and Hot Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Insulated conductors having a maximum operating
							 temperature of 200°C (392°F) shall be used on all lamps or other
							 equipment where the ambient temperature at the conductors as installed will
							 exceed 50°C (122°F).
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.15 - Flexible Cords

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Cords approved for hard service shall be used on
							 portable equipment.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.16 - Lamp Guards

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Incandescent lamps in projection rooms or booths
							 shall be provided with an approved lamp guard unless otherwise protected by
							 noncombustible shades or other enclosures.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.17 - Location of Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Renumbering and amendment of Section
							 2554.17 to Section
							 2554.10 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.19 - Equipment Prohibited

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Renumbering and amendment of Section
							 2554.19 to Section
							 2554.11 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.20 - Approval

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Projectors and enclosures for arc, Xenon and
							 incandescent lamps and rectifiers, transformers, rheostats and similar
							 equipment shall be approved.
(Title 24, Part 3, Section
							 540-20.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Repealer and new section filed 8-27-86; effective thirtieth day thereafter
							 (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE PROFESSIONAL TYPE › Section 2554.21 - Marking

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Projectors and other equipment as set forth in
							 Section 2554.20 shall be marked with the
							 name or trademark of the maker and with the voltage and current for which they
							 are designed.
(Title 24, Part 3, Section
							 540-21.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE NONPROFESSIONAL TYPE › Section 2554.30 - Nonprofessional Projector-Definition

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The nonprofessional projector is a type employing
							 film other than that used on professional-type projectors.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE NONPROFESSIONAL TYPE › Section 2554.31 - Booth Not Required

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Projectors of the nonprofessional or miniature type,
							 when employing only approved slow-burning (cellulose acetate or equivalent)
							 film, shall be permitted to be operated without a booth.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE NONPROFESSIONAL TYPE › Section 2554.32 - Approval

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Projectors, lamp enclosures, and current-controlling
							 devices and similar devices shall be listed as component parts of the projector
							 equipment.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE NONPROFESSIONAL TYPE › Section 2554.33 - Source of Illumination

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The source of illumination shall be a lamp or a type
							 listed for stereopticon use or for motion picture projection.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE NONPROFESSIONAL TYPE › Section 2554.34 - Marking

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Projectors
						  shall be marked with:
(1) The name or
						  trademark of the maker;
(2) The
						  current and voltage for which they are designed; and
(3) For projectors of this type using the
						  standard 35-millimeter film, the wording "For use with slow-burning films
						  only."
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › EQUIPMENT AND PROJECTORS OF THE NONPROFESSIONAL TYPE › Section 2554.35 - Nonprofessional Film Marking

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The slow-burning (cellulose acetate or equivalent)
							 film shall have a permanent distinctive marker for its entire length
							 identifying the manufacturer and the slow-burning character of the film
							 stock.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Editorial correction filed 11-3-83 (Register 83, No. 45).
3.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 72 - Motion Picture Projectors › SOUND RECORDING AND REPRODUCTION › Section 2554.50 - Sound Recording and Reproduction

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Sound recording and reproduction equipment shall
							 comply with Article 76.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 73 - Electric Signs and Outline Lighting › Section 2560.2 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Each sign and outline lighting system, or feeder circuit or branch circuit
						supplying a sign or outline lighting system, shall be controlled by an
						externally operable switch or circuit breaker that will open all ungrounded
						conductors.
EXCEPTIONS:
1.
						A disconnecting means is not required for an exit directional sign located
						within a building.
2. A
						disconnecting means is not required for cord-connected signs with an attachment
						plug.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 73 - Electric Signs and Outline Lighting › Section 2560.3 - Location

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The
						disconnecting means shall be within sight of the sign or outline lighting
						system that it controls. Where the disconnecting means is out of the line of
						sight from any section that may be energized, the disconnecting means shall be
						capable of being locked in the open position.
(b) Signs or outline lighting systems
						operated by electronic or electromechanical controllers located external to the
						sign or outline lighting system may have a disconnecting means located within
						sight of the controller or in the same enclosure with the controller. The
						disconnecting means shall disconnect the sign or outline lighting system and
						the controller from all ungrounded supply conductors. It shall be designed so
						no pole can be operated independently and shall be capable of being locked in
						the open position.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 73 - Electric Signs and Outline Lighting › Section 2560.10 - Clearances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Vertical and
						Horizontal. Signs and outline system enclosures shall have not less than the
						vertical and horizontal clearances from open conductors specified in the
						following table:
TABLE 2560.10
CLEARANCES
Vertical clearance above all signs upon which
								  persons can walk..........................
8 feet
Vertical clearance above all signs upon which
								  persons cannot walk..........................
3 feet
Vertical clearance under
								  signs..........................
3 feet
Horizontal clearance from
								  signs..........................
3 feet
(Title 24, Part 3, Section
						  3-600 -
						  10(a).)
(b) Elevation. The bottom of sign and outline
						lighting enclosures shall not be less than 16 feet above areas accessible to
						vehicles.
EXCEPTION: The bottom of such enclosures may be less
						  than 16 feet above areas accessible to vehicles where such enclosures are
						  protected from physical damage.
(Title 24, Part 3, Section
						  600-10(b).)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Editorial correction of subsection (a) filed 11-3-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article applies to the installation of electric
						  equipment and wiring used in connection with cranes, monorail hoists, hoists,
						  and all runways.
1.
						  Repealer of Article 74 (Sections
						  2561.1-2561.55 not consecutive) and
						  new Article 74 (Sections
						  2561.1-2561.55, not consecutive)
						  filed 11-16-79; effective thirtieth day thereafter (Register 79, No.
						  46).
2. Amendment filed 5-5-2008; operative 5-5-2008. Submitted to
						  OAL for printing only pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.2 - Special Requirements for Particular Locations

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Combustible Materials. Where a crane or hoist operates
						  over readily combustible material, the resistors shall be placed in a well
						  ventilated cabinet composed of noncombustible material so constructed that it
						  will not emit flames or molten metal.
EXCEPTION: Resistors shall be permitted to be located
						  in a cage or cab constructed of noncombustible material which encloses the
						  sides of the cage or cab from the floor to a point at least 6 inches above the
						  top of the resistors.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.3 - Clearance

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) On every new
						installation, major replacement, modification or repair made after March 15,
						1972, the dimension of the working space in the direction of access to
						energized parts which may require examination, adjustment, servicing, or
						maintenance while energized shall be a minimum of 2.5 feet (762 mm). Where
						controls are enclosed in cabinets, the doors shall either open at least 90
						degrees or be removable.
NOTE: For the purpose of this section, a major
						  replacement, modification, or repair shall mean 50 percent or more of the
						  current replacement value of the crane or hoist.
(b) On floor operated overhead cranes a
						suitable work platform with means of access shall be provided, attached to the
						building structure, or on the overhead crane bridge, giving ready and safe
						access to electrical control cabinets for service, maintenance or repair.
EXCEPTION: Floor operated porta-lift type platforms,
						  rolling scaffolds or similar type platforms may be used.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment deleting Title 24 cross reference filed 8-27-86; effective thirtieth
						  day thereafter (Register 86, No. 37).
3. Amendment of section and
						  NOTE filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.7 - Lifting Magnets

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All cranes using a lifting magnet shall have a magnet
						  circuit switch of the enclosed type with provision for locking in the "open"
						  position. A separate means for discharging the inductive load of the magnet
						  shall be provided.
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.8 - Remote Control Circuits

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Switching devices shall not be placed in the grounded
						  conductor of remote control circuits.
(Title 24, Part 3, Section
						  3-610 -
						  16.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.11 - Wiring Method

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Conductors shall be enclosed in a raceway or shall be
						  Type MC or MI cable.
EXCEPTION: No. 1: Contact conductors so located or
						  arranged that persons cannot inadvertently touch energized parts or bring
						  conducting material into contact with them.
EXCEPTION: No. 2: Short lengths of open conductors at
						  resistors, collectors, DC motors and other equipment so located or arranged
						  that persons cannot inadvertently touch energized parts or bring conducting
						  material into contact with them.
EXCEPTION: No. 3: Where flexibility is necessary,
						  multi-conductor cable may be used.
EXCEPTION: No. 4: Where multi-conductor cable is used
						  with a suspended push button station, the station shall be supported in some
						  suitable manner that protects the electrical connections against strain.
(Title 24, Part 3, Section
						  610-11.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.31 - Runway Conductor Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A disconnecting means shall be provided
						between the runway contact conductors and the power supply. Such disconnecting
						means shall consist of a motor-circuit switch, circuit breaker, or molded case
						switch.
The disconnecting means shall open all ungrounded
						  conductors simultaneously and shall be:
(1) Readily accessible and operable from the
						ground or floor level;
(2) Arranged
						to be locked in the open position; and
(3) Placed within view of the runway contact
						conductors.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.32 - Disconnecting Means for Cranes and Monorail Hoists

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A motor-circuit switch, molded case
						switch, or circuit breaker shall be provided in the leads from the runway
						contact conductors or other power supply on all cranes and monorail hoists.
EXCEPTION: The disconnecting means may be omitted where
						  a monorail hoist or hand-propelled crane bridge installation meets all of the
						  following conditions:
(1) The unit is
						controlled from the ground or floor level;
(2) The unit is within view of the power
						supply disconnecting means; and
(3)
						No fixed work platform has been provided for servicing the
						unit.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.50 - Controls. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of subsections (h) and (i) filed 8-27-86; effective thirtieth day
						  thereafter (Register 86, No. 37).
3. Repealer of section and
						  amendment of NOTE filed 5-5-2008; operative 5-5-2008. Submitted to OAL for
						  printing only pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.51 - Separate Controls

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Each motor shall be provided with an individual
						  controller.
EXCEPTION: No. 1: Where two or more motors drive a
						  single hoist, carriage, truck, or bridge, they shall be permitted to be
						  controlled by a single controller.
EXCEPTION: No. 2: One controller shall be permitted to
						  be switched between motors provided:
(a) The controller's horsepower rating is not
						lower than the horsepower rating of the largest motor.
(b) Only one motor is operated at one time.
(Title 24, Part 3, Section
						  610-51.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74 - Cranes and Hoists › Section 2561.55 - Limit Switch

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A limit switch or other device shall be provided to
						  prevent the load block from passing the safe upper limit of travel of any
						  hoisting mechanism.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 74.1 - Elevators, Dumbwaiters, Escalators, Moving Walks, Wheelchair Lifts, and Stairway Chair Lifts › Section 2562.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The following requirements apply to elevators,
						  dumbwaiters, escalators, moving walks, wheelchair lifts, and stairway chair
						  lifts.
1. New
						  article 74.1 (sections
						  2562.1-2562.7) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.