reglab/statecodes huggingface dataset:
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart AA - Air Emission Standards for Process Vents › Section 11-264.1032 - Standards: Process vents

Current through June, 2024
(a) The owner or
					 operator of a facility with process vents associated with distillation,
					 fractionation, thin-film evaporation, solvent extraction, or air or steam
					 stripping operations managing hazardous wastes with organic concentrations of
					 at least 10 ppmw shall either:
(1) Reduce
					 total organic emissions from all affected process vents at the facility below
					 1.4 kg/h (3 lb/h) and 2.8 Mg/yr (3.1 tons/yr), or
(2) Reduce, by use of a control device, total
					 organic emissions from all affected process vents at the facility by 95 weight
					 percent.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart AA - Air Emission Standards for Process Vents › Section 11-264.1034 - Test methods and procedures

Current through June, 2024
(a) Each owner or
					 operator subject to the provisions of this subpart shall comply with the test
					 methods and procedures requirements provided in this section.
(b) When a closed-vent system is tested for
					 compliance with no detectable emissions, as required in § 264.1033(l) of
					 this subpart, the test shall comply with the following requirements:
(1) Monitoring shall comply with Reference
					 Method 21 in 40 CFR part 60 .
(2)
					 The detection instrument shall meet the performance criteria of Reference
					 Method 21.
(3) The instrument shall
					 be calibrated before use on each day of its use by the procedures specified in
					 Reference Method 21.
(4)
					 Calibration gases shall be:
(i) Zero air
					 (less than 10 ppm of hydrocarbon in air).
(ii) A mixture of methane or n-hexane and air
					 at a concentration of approximately, but less than, 10,000 ppm methane or
					 n-hexane.
(5) The
					 background level shall be determined as set forth in Reference Method
					 21.
(6) The instrument probe shall
					 be traversed around all potential leak in-ter-faces as close to the interface
					 as -possible as described in Reference -Method 21.
(7) The arithmetic difference between the
					 maximum concentration indicated by the instrument and the background level is
					 compared with 500 ppm for determining compliance.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart AA - Air Emission Standards for Process Vents › Section 11-264.1035 - Recordkeeping requirements

Current through June, 2024
(a)
(1) Each owner or operator subject to the
					 provisions of this subpart shall comply with the recordkeeping requirements of
					 this section.
(2) An owner or
					 operator of more than one hazardous waste management unit subject to the
					 provisions of this subpart may comply with the recordkeeping requirements for
					 these hazardous waste management units in one recordkeeping system if the
					 system identifies each record by each hazardous waste management
					 unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart AA - Air Emission Standards for Process Vents › Section 11-264.1036 - Reporting requirements

Current through June, 2024
(a) A semiannual
					 report shall be submitted by owners and operators subject to the requirements
					 of this subpart to the director by dates specified by the director. The report
					 shall include the following information:
(1)
					 The Environmental Protection Agency identification number, name, and address of
					 the facility.
(2) For each month
					 during the semiannual reporting period, dates when the control device exceeded
					 or operated outside of the design specifications as defined in §
					 264.1035(c)(4) and as indicated by the control device monitoring required by
					 § 264.1033(f) and such exceedances were not corrected within 24 hours, or
					 that a flare operated with visible emissions as defined in § 264.1033(d)
					 and as determined by Method 22 monitoring, the duration and cause of each
					 exceedance or visible emissions, and any corrective measures taken.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart AA - Air Emission Standards for Process Vents › Section 11-264.1037-11.264.1049 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1050 - Applicability

Current through June, 2024
(a) The regulations in this subpart apply to
					 owners and operators of facilities that treat, store, or dispose of hazardous
					 wastes (except as provided in § 264.1).
(b) Except as provided in § 264.1064(k),
					 this subpart applies to equipment that contains or contacts hazardous wastes
					 with organic concentrations of at least 10 percent by weight that are managed
					 in one of the following:
(1) A unit that is
					 subject to the permitting requirements of 40 CFR part 270 , or
(2) A unit (including a hazardous waste
					 recycling unit) that is not exempt from permitting under the provisions of
					 40
					 CFR 262.17 (i.e., a hazardous waste recycling
					 unit that is not a "90-day" tank or container) and that is located at a
					 hazardous waste management facility otherwise subject to the permitting
					 requirements of 40 CFR part 270 , or
(3) A unit that is exempt from permitting
					 under the provisions of
					 40
					 CFR 262.17 (i.e., a "90-day" tank or
					 container) and is not a recycling unit under the provisions of
					 40 CFR
					 261.6.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1051 - Definitions

Current through June, 2024
As used in this subpart, all terms shall have the meaning
						given them in § 264.1031, the Act, and parts 260-266.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1052 - Standards: Pumps in light liquid service

Current through June, 2024
(a)
(1) Each pump in light liquid service shall
					 be monitored monthly to detect leaks by the methods specified in §
					 264.1063(b), except as provided in paragraphs (d), (e), and (f) of this
					 section.
(2) Each pump in light
					 liquid service shall be checked by visual inspection each calendar week for
					 indications of liquids dripping from the pump seal.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1053 - Standards: Compressors

Current through June, 2024
(a) Each compressor
					 shall be equipped with a seal system that includes a barrier fluid system and
					 that prevents leakage of total organic emissions to the atmosphere, except as
					 provided in paragraphs (h) and (i) of this section.
(b) Each compressor seal system as required
					 in paragraph (a) of this section shall be:
(1) Operated with the barrier fluid at a
					 pressure that is at all times greater than the compressor stuffing box
					 pressure, or
(2) Equipped with a
					 barrier fluid system that is connected by a closed-vent system to a control
					 device that complies with the requirements of § 264.1060, or
(3) Equipped with a system that purges the
					 barrier fluid into a hazardous waste stream with no detectable emissions to
					 atmosphere.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1054 - Standards: Pressure relief devices in gas/vapor service

Current through June, 2024
(a)
					 Except during pressure releases, each pressure relief device in gas/vapor
					 service shall be operated with no detectable emissions, as indicated by an
					 instrument reading of less than 500 ppm above background, as measured by the
					 method specified in § 264.1063(c).
(b)
(1)
					 After each pressure release, the pressure relief device shall be returned to a
					 condition of no detectable emissions, as indicated by an instrument reading of
					 less than 500 ppm above background, as soon as practicable, but no later than 5
					 calendar days after each pressure release, except as provided in §
					 264.1059.
(2) No later than 5
					 calendar days after the pressure release, the pressure relief device shall be
					 monitored to confirm the condition of no detectable emissions, as indicated by
					 an instrument reading of less than 500 ppm above background, as measured by the
					 method specified in § 264.1063(c).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1055 - Standards: Sampling connection systems

Current through June, 2024
(a) Each sampling
					 connection system shall be equipped with a closed-purge, closed-loop, or
					 closed-vent system. This system shall collect the sample purge for return to
					 the process or for routing to the appropriate treatment system. Gases displaced
					 during filling of the sample container are not required to be collected or
					 captured.
(b) Each closed-purge,
					 closed-loop, or closed-vent system as required in paragraph (a) of this section
					 shall meet one of the following requirements:
(1) Return the purged process fluid directly
					 to the process line;
(2) Collect
					 and recycle the purged process fluid; or
(3) Be designed and operated to capture and
					 transport all the purged process fluid to a waste management unit that complies
					 with the applicable requirements of § 264.1084 through § 264.1086 of
					 this subpart or a control device that complies with the requirements of §
					 264.1060 of this subpart.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1056 - Standards: Open-ended valves or lines

Current through June, 2024
(a)
(1) Each open-ended valve or line shall be
					 equipped with a cap, blind flange, plug, or a second valve.
(2) The cap, blind flange, plug, or second
					 valve shall seal the open end at all times except during operations requiring
					 hazardous waste stream flow through the open-ended valve or line.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1057 - Standards: Valves in gas/vapor service or in light liquid service

Current through June, 2024
(a) Each valve in gas/vapor or light liquid
					 service shall be monitored monthly to detect leaks by the methods specified in
					 2651063(b) and shall comply with paragraphs (b) through (e) of this section,
					 except as provided in paragraphs (f), (g), and (h) of this section, and 2651061
					 and 2651062.
(b) If an instrument
					 reading of 10,000 ppm or greater is measured, a leak is detected.
(c)
(1) Any
					 valve for which a leak is not detected for two successive months may be
					 monitored the first month of every succeeding quarter, beginning with the next
					 quarter, until a leak is detected.
(2) If a leak is detected, the valve shall be
					 monitored monthly until a leak is not detected for 2 successive
					 months.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1058 - Standards: Pumps and valves in heavy liquid service, pressure relief devices in light liquid or heavy liquid service, and flanges and other connectors

Current through June, 2024
(a) Pumps and
					 valves in heavy liquid service, pressure relief devices in light liquid or
					 heavy liquid service, and flanges and other connectors shall be monitored
					 within 5 days by the method specified in § 264.1063(b) if evidence of a
					 potential leak is found by visual, audible, olfactory, or any other detection
					 method.
(b) If an instrument
					 reading of 10,000 ppm or greater is measured, a leak is detected.
(c)
(1)
					 When a leak is detected, it shall be repaired as soon as practicable, but not
					 later than 15 calendar days after it is detected, except as provided in §
					 264.1059.
(2) The first attempt at
					 repair shall be made no later than 5 calendar days after each leak is
					 detected.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1059 - Standards: Delay of repair

Current through June, 2024
(a) Delay of repair
					 of equipment for which leaks have been detected will be allowed if the repair
					 is technically infeasible without a hazardous waste management unit shutdown.
					 In such a case, repair of this equipment shall occur before the end of the next
					 hazardous waste management unit shutdown.
(b) Delay of repair of equipment for which
					 leaks have been detected will be allowed for equipment that is isolated from
					 the hazardous waste management unit and that does not continue to contain or
					 contact hazardous waste with organic concentrations at least 10 percent by
					 weight.
(c) Delay of repair for
					 valves will be allowed if:
(1) The owner or
					 operator determines that emissions of purged material resulting from immediate
					 repair are greater than the emissions likely to result from delay of
					 repair.
(2) When repair procedures
					 are effected, the purged material is collected and destroyed or recovered in a
					 control device complying with § 264.1060.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1061 - Alternative standards for valves in gas/vapor service or in light liquid service: percentage of valves allowed to leak

Current through June, 2024
(a) An owner
					 or operator subject to the requirements of § 264.1057 may elect to have
					 all valves within a hazardous waste management unit comply with an alternative
					 standard that allows no greater than 2 percent of the valves to leak.
(b) The following requirements shall be met
					 if an owner or operator decides to comply with the alternative standard of
					 allowing 2 percent of valves to leak:
(1) A
					 performance test as specified in paragraph (c) of this section shall be
					 conducted initially upon designation, annually, and at other times requested by
					 the director.
(2) If a valve leak
					 is detected, it shall be repaired in accordance with § 264.1057(d) and
					 (e).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1062 - Alternative standards for valves in gas/vapor service or in light liquid service: skip period leak detection and repair

Current through June, 2024
(a) An owner
					 or operator subject to the requirements of § 264.1057 may elect for all
					 valves within a hazardous waste management unit to comply with one of the
					 alternative work practices specified in paragraphs (b) (2) and (3) of this
					 section.
(b)
(1) An owner or operator shall comply with
					 the requirements for valves, as described in § 264.1057, except as
					 described in paragraphs (b)(2) and (b)(3) of this section.
(2) After two consecutive quarterly leak
					 detection periods with the percentage of valves leaking equal to or less than 2
					 percent, an owner or operator may begin to skip one of the quarterly leak
					 detection periods (i.e., monitor for leaks once every six months) for the
					 valves subject to the requirements in § 264.1057 of this
					 subpart.
(3) After five consecutive
					 quarterly leak detection periods with the percentage of valves leaking equal to
					 or less than 2 percent, an owner or operator may begin to skip three of the
					 quarterly leak detection periods (i.e., monitor for leaks once every year) for
					 the valves subject to the requirements in § 264.1057 of this
					 subpart.
(4) If the percentage of
					 valves leaking is greater than 2 percent, the owner or operator shall monitor
					 monthly in compliance with the requirements in § 264.1057, but may again
					 elect to use this section after meeting the requirements of §
					 264.1057(c)(1).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1063 - Test methods and procedures

Current through June, 2024
(a) Each owner or
					 operator subject to the provisions of this subpart shall comply with the test
					 methods and procedures requirements provided in this section.
(b) Leak detection monitoring, as required in
					 §§ 264.1052-264.1062, shall comply with the following requirements:
(1) Monitoring shall comply with Reference
					 Method 21 in 40 CFR part 60 .
(2)
					 The detection instrument shall meet the performance criteria of Reference
					 Method 21.
(3) The instrument shall
					 be calibrated before use on each day of its use by the procedures specified in
					 Reference Method 21.
(4)
					 Calibration gases shall be:
(i) Zero air
					 (less than 10 ppm of hydrocarbon in air).
(ii) A mixture of methane or n-hexane and air
					 at a concentration of approximately, but less than, 10,000 ppm methane or
					 n-hexane.
(5) The
					 instrument probe shall be traversed around all potential leak interfaces as
					 close to the interface as -possible as described in Reference Method
					 21.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1064 - Recordkeeping requirements

Current through June, 2024
(a)
(1) Each owner or operator subject to the
					 provisions of this subpart shall comply with the recordkeeping requirements of
					 this section.
(2) An owner or
					 operator of more than one hazardous waste management unit subject to the
					 provisions of this subpart may comply with the recordkeeping requirements for
					 these hazardous waste management units in one recordkeeping system if the
					 system identifies each record by each hazardous waste management
					 unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1065 - Reporting requirements

Current through June, 2024
(a) A semiannual
					 report shall be submitted by owners and operators subject to the requirements
					 of this subpart to the director by dates specified by the director. The report
					 shall include the following information:
(1)
					 The Environmental Protection Agency identification number, name, and address of
					 the facility.
(2) For each month
					 during the semiannual reporting period:
(i)
					 The equipment identification number of each valve for which a leak was not
					 repaired as required in § 264.1057(d).
(ii) The equipment identification number of
					 each pump for which a leak was not repaired as required in § 264.1052 (c)
					 and (d)(6).
(iii) The equipment
					 identification number of each compressor for which a leak was not repaired as
					 required in § 264.1053(g).
(3) Dates of hazardous waste management unit
					 shutdowns that occurred within the semiannual reporting period.
(4) For each month during the semiannual
					 reporting period, dates when the control device installed as required by §
					 264.1052, 264.1053, 264.1054, or 264.1055 exceeded or operated outside of the
					 design specifications as defined in § 264.1064(e) and as indicated by the
					 control device monitoring required by § 264.1060 and was not corrected
					 within 24 hours, the duration and cause of each exceedance, and any corrective
					 measures taken.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart BB - Air Emission Standards for Equipment Leaks › Section 11-264.1066-11.264.1079 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1080 - Applicability

Current through June, 2024
(a) The requirements of this subpart apply to
					 owners and operators of all facilities that treat, store, or dispose of
					 hazardous waste in tanks, surface impoundments, or containers subject to either
					 subpart I, J, or K of this part except as § 264.1 and paragraph (b) of
					 this section provide otherwise.
(b)
					 The requirements of this subpart do not apply to the following waste management
					 units at the facility:
(1) A waste management
					 unit that holds hazardous waste placed in the unit before December 6, 1996, and
					 in which no hazardous waste is added to the unit on or after December 6,
					 1996.
(2) A container that has a
					 design capacity less than or equal to 0.1
					 m3.
(3)
					 A tank in which an owner or operator has stopped adding hazardous waste and the
					 owner or operator has begun implementing or completed closure pursuant to an
					 approved closure plan.
(4) A
					 surface impoundment in which an owner or operator has stopped adding hazardous
					 waste (except to implement an approved closure plan) and the owner or operator
					 has begun implementing or completed closure pursuant to an approved closure
					 plan.
(5) A waste management unit
					 that is used solely for on-site treatment or storage of hazardous waste that is
					 placed in the unit as a result of implementing remedial activities required
					 under the corrective action authorities of RCRA sections 3004(u), 3004(v), or
					 3008(h); CERCLA authorities; section
					 342J-36,
					 HRS; or similar Federal or State authorities.
(6) A waste management unit that is used
					 solely for the management of radioactive mixed waste in accordance with all
					 applicable regulations under the authority of the Atomic Energy Act and the
					 Nuclear Waste Policy Act.
(7) A
					 hazardous waste management unit that the owner or operator certifies is
					 equipped with and operating air emission controls in accordance with the
					 requirements of an applicable Clean Air Act regulation codified under 40 CFR
					 part 60, part 61, or part 63. For the purpose of complying with this paragraph,
					 a tank for which the air emission control includes an enclosure, as opposed to
					 a cover, must be in compliance with the enclosure and control device
					 requirements of § 264.1084(i), except as provided in §
					 264.1082(c)(5).
(8) A tank that has
					 a process vent as defined in
					 40
					 CFR 264.1031.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1081 - Definitions

Current through June, 2024
As used in this subpart, all terms shall have the meaning
						given to them in
						40
						CFR 265.1081, the Act, and parts 260 through
						266 of this chapter.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1083 - Waste determination procedures

Current through June, 2024
(a) Waste
					 determination procedure to determine average volatile organic (VO)
					 concentration of a hazardous waste at the point of waste origination.
(1) An owner or operator shall determine the
					 average VO concentration at the point of waste origination for each hazardous
					 waste placed in a waste management unit exempted under the provisions of §
					 264.1082(c)(1) of this subpart from using air emission controls in accordance
					 with standards specified in § 264.1084 through § 264.1087 of this
					 subpart, as applicable to the waste management unit.
(i) An initial determination of the average
					 VO concentration of the waste stream shall be made before the first time any
					 portion of the material in the hazardous waste stream is placed in a waste
					 management unit exempted under the provisions of § 264.1082(c)(1) of this
					 subpart from using air emission controls, and thereafter an initial
					 determination of the average VO concentration of the waste stream shall be made
					 for each averaging period that a hazardous waste is managed in the unit;
					 and
(ii) Perform a new waste
					 determination whenever changes to the source generating the waste stream are
					 reasonably likely to cause the average VO concentration of the hazardous waste
					 to increase to a level that is equal to or greater than the applicable VO
					 concentration limits specified in § 264.1082 of this subpart.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1084 - Standards: Tanks

Current through June, 2024
(a) The provisions of this section apply to
					 the control of air pollutant emissions from tanks for which § 264.1082(b)
					 of this subpart references the use of this section for such air emission
					 control.
(b) The owner or operator
					 shall control air pollutant emissions from each tank subject to this section in
					 accordance with the following requirements as applicable:
(1) For a tank that manages hazardous waste
					 that meets all of the conditions specified in paragraphs (b)(1)(i) through
					 (b)(1)(iii) of this section, the owner or operator shall control air pollutant
					 emissions from the tank in accordance with the Tank Level 1 controls specified
					 in paragraph (c) of this section or the Tank Level 2 controls specified in
					 paragraph (d) of this section.
(i) The
					 hazardous waste in the tank has a maximum organic vapor pressure which is less
					 than the maximum organic vapor pressure limit for the tank's design capacity
					 category as follows:
(A) For a tank design
					 capacity equal to or greater than 151 m3, the
					 maximum organic vapor pressure limit for the tank is 5.2 kPa.
(B) For a tank design capacity equal to or
					 greater than 75 m3 but less than 151
					 m3, the maximum organic vapor pressure limit for the
					 tank is 27.6 kPa.
(C) For a tank
					 design capacity less than 75 m3, the maximum organic
					 vapor pressure limit for the tank is 76.6 kPa.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1085 - Standards: Surface impoundments

Current through June, 2024
(a) The provisions
					 of this section apply to the control of air pollutant emissions from surface
					 impoundments for which § 264.1082(b) of this subpart references the use of
					 this section for such air emission control.
(b) The owner or operator shall control air
					 pollutant emissions from the surface impoundment by installing and operating
					 either of the following:
(1) A floating
					 membrane cover in accordance with the provisions specified in paragraph (c) of
					 this section; or
(2) A cover that
					 is vented through a closed-vent system to a control device in accordance with
					 the provisions specified in paragraph (d) of this section.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1086 - Standards: Containers

Current through June, 2024
(a) The provisions
					 of this section apply to the control of air pollutant emissions from containers
					 for which § 264.1082(b) of this subpart references the use of this section
					 for such air emission control.
(b)
					 General requirements.
(1) The owner or
					 operator shall control air pollutant emissions from each container subject to
					 this section in accordance with the following requirements, as applicable to
					 the container, except when the special provisions for waste stabilization
					 processes specified in paragraph (b)(2) of this section apply to the container.
(i) For a container having a design capacity
					 greater than 0.1 m3 and less than or equal to 0.46
					 m3, the owner or operator shall control air
					 pollutant emissions from the container in accordance with the Container Level 1
					 standards specified in paragraph (c) of this section.
(ii) For a container having a design capacity
					 greater than 0.46 m3 that is not in light material
					 service, the owner or operator shall control air pollutant emissions from the
					 container in accordance with the Container Level 1 standards specified in
					 paragraph (c) of this section.
(iii) For a container having a design
					 capacity greater than 0.46 m3 that is in light
					 material service, the owner or operator shall control air pollutant emissions
					 from the container in accordance with the Container Level 2 standards specified
					 in paragraph (d) of this section.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1087 - Standards: Closed-vent systems and control devices

Current through June, 2024
(a)
					 This section applies to each closed-vent system and control device installed
					 and operated by the owner or operator to control air emissions in accordance
					 with standards of this subpart.
(b)
					 The closed-vent system shall meet the following requirements:
(1) The closed-vent system shall route the
					 gases, vapors, and fumes emitted from the hazardous waste in the waste
					 management unit to a control device that meets the requirements specified in
					 paragraph (c) of this section.
(2)
					 The closed-vent system shall be designed and operated in accordance with the
					 requirements specified in § 264.1033(k) of this part.
(3) In the case when the closed-vent system
					 includes bypass devices that could be used to divert the gas or vapor stream to
					 the atmosphere before entering the control device, each bypass device shall be
					 equipped with either a flow indicator as specified in paragraph (b)(3)(i) of
					 this section or a seal or locking device as specified in paragraph (b)(3)(ii)
					 of this section. For the purpose of complying with this paragraph, low leg
					 drains, high point bleeds, analyzer vents, open-ended valves or lines, spring
					 loaded pressure relief valves, and other fittings used for safety purposes are
					 not considered to be bypass devices.
(i) If a
					 flow indicator is used to comply with paragraph (b)(3) of this section, the
					 indicator shall be installed at the inlet to the bypass line used to divert
					 gases and vapors from the closed-vent system to the atmosphere at a point
					 upstream of the control device inlet. For this paragraph, a flow indicator
					 means a device which indicates the presence of either gas or vapor flow in the
					 bypass line.
(ii) If a seal or
					 locking device is used to comply with paragraph (b)(3) of this section, the
					 device shall be placed on the mechanism by which the bypass device position is
					 controlled (e.g., valve handle, damper lever) when the bypass device is in the
					 closed position such that the bypass device cannot be opened without breaking
					 the seal or removing the lock. Examples of such devices include, but are not
					 limited to, a car-seal or a lock-and-key configuration valve. The owner or
					 operator shall visually inspect the seal or closure mechanism at least once
					 every month to verify that the bypass mechanism is maintained in the closed
					 position.
(4) The
					 closed-vent system shall be inspected and monitored by the owner or operator in
					 accordance with the procedure specified in § 264.1033(l).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1088 - Inspection and monitoring requirements

Current through June, 2024
(a) The owner or
					 operator shall inspect and monitor air emission control equipment used to
					 comply with this subpart in accordance with the applicable requirements
					 specified in § 264.1084 through § 264.1087 of this subpart.
(b) The owner or operator shall develop and
					 implement a written plan and schedule to perform the inspections and monitoring
					 required by paragraph (a) of this section. The owner or operator shall
					 incorporate this plan and schedule into the facility inspection plan required
					 under
					 40 CFR
					 264.15.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1089 - Recordkeeping requirements

Current through June, 2024
(a) Each owner or
					 operator of a facility subject to requirements of this subpart shall record and
					 maintain the information specified in paragraphs (b) through (j) of this
					 section, as applicable to the facility. Except for air emission control
					 equipment design documentation and information required by paragraphs (i) and
					 (j) of this section, records required by this section shall be maintained in
					 the operating record for a minimum of 3 years. Air emission control equipment
					 design documentation shall be maintained in the operating record until the air
					 emission control equipment is replaced or otherwise no longer in service.
					 Information required by paragraphs (i) and (j) of this section shall be
					 maintained in the operating record for as long as the waste management unit is
					 not using air emission controls specified in §§ 264.1084 through
					 264.1087 of this subpart in accordance with the conditions specified in §
					 264.1080(d) or § 264.1080(b)(7) of this subpart, respectively.
(b) The owner or operator of a tank using air
					 emission controls in accordance with the requirements of § 264.1084 of
					 this subpart shall prepare and maintain records for the tank that include the
					 following information:
(1) For each tank using
					 air emission controls in accordance with the requirements of § 264.1084 of
					 this subpart, the owner or operator shall record:
(i) A tank identification number (or other
					 unique identification description as selected by the owner or
					 operator).
(ii) A record for each
					 inspection required by § 264.1084 of this subpart that includes the
					 following information:
(A) Date inspection was
					 conducted.
(B) For each defect
					 detected during the inspection: The location of the defect, a description of
					 the defect, the date of detection, and corrective action taken to repair the
					 defect. In the event that repair of the defect is delayed in accordance with
					 the requirements of § 264.1084 of this subpart, the owner or operator
					 shall also record the reason for the delay and the date that completion of
					 repair of the defect is expected.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart CC - Air Emission Standards for Tanks, Surface Impoundments, and Containers › Section 11-264.1091 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 264.1 - HAZARDOUS WASTE MANAGEMENT: STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 264 - STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart DD - Containment Buildings › Section 11-264.1100 - Applicability

Current through June, 2024
The requirements of this subpart apply to owners or
						operators who store or treat hazardous waste in units designed and operated
						under § 264.1101 of this subpart. The owner or operator is not subject to
						the definition of land disposal in
						40 C.F.R. section
						268.2(c), as incorporated
						and amended in section 11-268.1-1 provided that the unit:
(a) Is a completely enclosed, self-supporting
					 structure that is designed and constructed of manmade materials of sufficient
					 strength and thickness to support themselves, the waste contents, and any
					 personnel and heavy equipment that operate within the unit, and to prevent
					 failure due to pressure gradients, settlement, compression, or uplift, physical
					 contact with the hazardous wastes to which they are exposed; climatic
					 conditions; and the stresses of daily operation, including the movement of
					 heavy equipment within the unit and contact of such equipment with containment
					 walls;
(b) Has a primary barrier
					 that is designed to be sufficiently durable to withstand the movement of
					 personnel, wastes, and handling equipment within the unit;
(c) If the unit is used to manage liquids,
					 has:
(1) A primary barrier designed and
					 constructed of materials to prevent migration of hazardous constituents into
					 the barrier;
(2) A liquid
					 collection system designed and constructed of materials to minimize the
					 accumulation of liquid on the primary barrier; and
(3) A secondary containment system designed
					 and constructed of materials to prevent migration of hazardous constituents
					 into the barrier, with a leak detection and liquid collection system capable of
					 detecting, collecting, and removing leaks of hazardous constituents at the
					 earliest practicable time, unless the unit has been granted a variance from the
					 secondary containment system requirements under §
					 264.1101(b)(4);