reglab/statecodes huggingface dataset:
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 4 - Materials and Installation of Water Mains and Appurtenances › Section 64575 - Flushing

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A flushing
				  valve or blowoff shall be provided at the end of each newly installed dead-end
				  water main. Fire hydrants meeting the criteria of this section may be
				  considered flushing valves.
(b)
				  Flushing valves and blowoffs shall not discharge to a sanitary sewer without an
				  air gap separation between the sewer and the valve or blowoff.
(c) The flushing velocity in the main shall
				  not be less than 2.5 ft/s unless it is determined that conditions do not permit
				  the required flow to be discharged to waste.
(d) Newly installed flushing valves and
				  blowoffs shall be designed to maintain the minimum continuous flushing flows as
				  indicated below to produce a minimum velocity of 2.5ft/s in commonly used sizes
				  of pipe.
Table 64575-A. Minimum Flushing Flows for Different
					 Size Water Mains.
Nominal Main Size Diameter
							 (inches)
Minimum Flushing Flow (gallons
							 per minute)
2
25
3
50
4
100
6
225
8
400
10
600
12
900
14
1200
16
1600
1. New
					 section filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
2. Change without regulatory effect amending subsection (a)
					 filed 4-21-2011 pursuant to section
					 100, title 1, California Code of
					 Regulations (Register 2011, No. 16).
Note: Authority cited: Sections
						116350,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116275,
						116375,
						116535
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 4 - Materials and Installation of Water Mains and Appurtenances › Section 64576 - Air-Release, Air Vacuum, and Combination Valves

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Each new air-release, air vacuum, or combination valve, and
					 any such valve installed to replace an existing valve shall be:
(a) Installed such that its vent opening is
				  above grade, above the calculated 100-year flood water level, and, if recorded
				  data are available, above the highest recorded water level;
(b) Readily accessible for inspection,
				  maintenance and replacement;
(c)
				  Constructed and designed to prevent exposure to rainwater or runoff, vandalism,
				  and birds, insects, rodents, or other animals;
(d) Fitted with a downward-facing screened
				  vent or a domed and screened cap; and
(e) Installed pursuant to American Water
				  Works Association Standard C512-04 and Manual M51 (2001), which are hereby
				  incorporated by reference.
1. New
					 section filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						116350,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116275,
						116375,
						116535
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 4 - Materials and Installation of Water Mains and Appurtenances › Section 64577 - Isolation Valves

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
As a minimum, isolation valves shall be installed on all
					 new water mains within the distribution system as follows:
(a) No farther than 1,320 linear feet apart
				  on all mains having a diameter of 12 inches or less.
(b) At each tee or crossing connection
				  between mains that have a diameter of 12 inches or less, within 100 feet of the
				  tee or crossing connection with the primary main.
(c) Between the water main and each fire
				  hydrant served by the main.
1. New
					 section filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						116350,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116275,
						116375,
						116535
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 4 - Materials and Installation of Water Mains and Appurtenances › Section 64578 - Water Main Valve Construction

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Newly installed valves constructed on water mains shall
					 comply with the following:
(a) A valve
				  box shall be installed over each buried valve stem to aid in locating and
				  operating the valve.
(b) For valves
				  buried in trenches greater than five feet below the finished grade, either a
				  valve stem riser to permit the use of a normal key or a notation on valve
				  records indicating that a long key will be required shall be
				  provided.
1. New
					 section filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						116350,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116275,
						116375,
						116535
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 5 - Disinfection Requirements › Section 64580 - Disinfection of New or Repaired Mains

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Prior to use, newly installed water mains, or water mains
					 that have been taken out of service for maintenance or repair, shall be
					 disinfected and sampled for bacteriological quality in accordance with American
					 Water Works Association Standard C651-05, which is hereby incorporated by
					 reference. Samples from new mains shall be negative for coliform bacteria prior
					 to the new main(s) being placed into service.
1. New
					 article 5 (sections
					 64580-64583) and section filed
					 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						116350,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116275,
						116375,
						116535
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 5 - Disinfection Requirements › Section 64582 - Disinfection of Reservoirs

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A newly-installed distribution reservoir or distribution
					 reservoir that has been taken out of service for repair or inspection shall be
					 disinfected and sampled for bacteriological quality in accordance with the
					 American Water Works Association Standard C652-02, which is hereby incorporated
					 by reference. If the results of the bacteriological sampling are positive for
					 coliform bacteria, the reservoir shall be resampled for bacteriological quality
					 and the test results shall be submitted to the State Board for review and
					 approval before the reservoir is placed into service.
1. New
					 section filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
2. Change without regulatory effect amending section and NOTE
					 filed 6-2-2015 pursuant to section
					 100, title 1, California Code of
					 Regulations (Register 2015, No. 23).
Note: Authority cited: Sections
						116271,
						116350
						and
						116375,
						Health and Safety Code. Reference: Sections
						116275,
						116375
						and
						116535,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 5 - Disinfection Requirements › Section 64583 - Disinfection of Wells

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A new or repaired well, or a well that has not been in
					 operation for more than three months shall be sampled for bacteriological
					 quality prior to use. If the results of the bacteriological sampling are
					 positive for coliform bacteria, the well shall be disinfected in accordance
					 with the American Water Works Association C654-03, which is hereby incorporated
					 by reference, and resampled for bacteriological quality and the test results
					 shall be submitted to the State Board for review and approval before the well
					 is placed into service.
1. New
					 section filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
2. Change without regulatory effect amending section and NOTE
					 filed 6-2-2015 pursuant to section
					 100, title 1, California Code of
					 Regulations (Register 2015, No. 23).
Note: Authority cited: Sections
						116271,
						116350
						and
						116375,
						Health and Safety Code. Reference: Sections
						116275,
						116375
						and
						116535,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 6 - Distribution Reservoirs › Section 64585 - Design and Construction

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each distribution reservoir shall meet the following:
(1) Any reservoir coatings or linings shall
				  be installed in accordance with manufacturer's instructions;
(2) Vents and other openings shall be
				  constructed and designed to prevent the entry of rainwater or runoff, and
				  birds, insects, rodents, or other animals;
(3) At least one sampling tap shall be
				  available to enable representative sampling of the water in the reservoir that
				  will be entering the distribution system; the tap shall be protected against
				  freezing, if necessary; and
(4) A
				  reservoir shall not be designed, constructed, or used for any activity that
				  creates a contamination hazard.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 7 - Additives › Section 64590 - Direct Additives

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No chemical or product shall be added to drinking water by
					 a water supplier unless the chemical or product is certified as meeting the
					 specifications of NSF International/American National Standard Institute
					 (NSF/ANSI) 60-2005 (Drinking Water Treatment Chemicals--Health Effects), which
					 is hereby incorporated by reference. Certification shall be from an ANSI
					 accredited product certification organization whose certification system
					 includes, as a minimum, the following criteria for ensuring the chemical or
					 product meets NSF/ANSI Standard 60.
(a) Annual product testing,
(b) Annual facility inspections,
(c) Annual quality assurance and quality
				  control review,
(d) Annual
				  manufacturing practice reviews, and
(e) Annual chemical stock
				  inspections.
1. New
					 article 7 (sections
					 64590-64593) and renumbering of
					 former section
					 64700 to new section
					 64590, including amendment of
					 section and NOTE, filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Section
						116350,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116275,
						116375,
						116550
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 7 - Additives › Section 64591 - Indirect Additives

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Except as provided in Section
				  64593 or where a more stringent
				  statutory requirement exists, after March 9, 2008, a water system shall not use
				  any chemical, material, lubricant, or product in the production, treatment or
				  distribution of drinking water that will result in its contact with the
				  drinking water including process media (carbon, sand), protective materials
				  (coatings, linings, liners), joining and sealing materials (solvent cements,
				  welding materials, gaskets, lubricating oils), pipes and related products
				  (pipes, tanks, fittings), and mechanical devices used in
				  treatment/transmission/distribution systems (valves, chlorinators, separation
				  membranes) that has not been tested and certified as meeting the specifications
				  of NSF International/American National Standard Institute (NSF/ANSI) 61-2005 /
				  Addendum 1.0-2005 (Drinking Water System Components--Health Effects), which is
				  hereby incorporated by reference. This requirement shall be met under testing
				  conducted by a product certification organization accredited for this purpose
				  by the American National Standards Institute.
(b) If a treatment chemical is generated on
				  site,
(1) No equipment used in the generation
				  process shall be in contact with a drinking water, or a chemical to be applied
				  to drinking water, after March 9, 2008, unless the equipment has been tested
				  and certified as meeting the specifications of NSF International/American
				  National Standard Institute (NSF/ANSI) Standard 61-2005/Addendum 1.0-2005
				  (Drinking Water System Components--Health Effects). This requirement shall be
				  met under testing conducted by a product certification organization accredited
				  for this purpose by the American National Standards Institute; and
(2) No input chemical used in the generation
				  process shall be in contact with a drinking water after March 9, 2008 unless
				  the chemical meets the requirements of section
				  64590.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 7 - Additives › Section 64593 - Use of Uncertified Chemicals, Materials or Products

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A water supplier may use a chemical,
				  material or product that has not been certified pursuant to sections
				  64590 or
				  64591 if the chemical, material or
				  product is in the process of being tested and certified and there are no
				  certified alternatives.
(b) Prior
				  to use of an uncertified chemical, material or product, the water supplier
				  shall provide the State Board with an explanation of the need for the chemical,
				  material or product; the date that the chemical, material or product was
				  submitted for testing; the name of the accredited product certification
				  organization conducting the testing; and a statement that certified
				  alternatives are not available.
(c)
				  Unless directed otherwise by the State Board to ensure a pure and wholesome
				  drinking water supply, a water supplier may use the following chemicals,
				  materials, or products that have not been and are not in the process of being
				  certified pursuant to section
				  64590 or
				  64591:
(1) a material or product previously approved
				  by the State Board for use or installation on or before March 9,
				  2008;
(2) a material or product
				  constructed of components meeting the requirements of sections
				  64590 and
				  64591;
(3) chemical by-products necessary for
				  meeting drinking water standards, such as sodium hypochlorite for disinfection,
				  generated by chemicals certified pursuant to section
				  64590 or
				  64591; and
(4) atmospheric air and small parts, such as
				  probes, sensors, wires, nuts, bolts, and tubing for which there are no
				  certified alternatives.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64600 - Water System Operations and Maintenance Plan

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) If directed by the State Board to do so
				  based on an identified deficiency in the system's operations, a water system
				  shall develop and submit a Water System Operations and Maintenance Plan (Plan);
				  the water system shall include those elements in the following list that are
				  deemed by the State Board to be relevant to the deficiency:
(1) The operations and maintenance schedule
				  for each unit process for each treatment plant that treats an approved surface
				  water;
(2) The operations and
				  maintenance schedule for each groundwater source and unit process;
(3) The schedule and procedure for flushing
				  dead end mains, and the procedures for disposal of the flushed water including
				  dechlorination;
(4) The schedule
				  for routine inspection of reservoirs, and the procedures for cleaning
				  reservoirs;
(5) The schedule and
				  procedures for inspecting, repairing, and replacing water mains;
(6) The plan and procedures for responding to
				  water supply emergencies;
(7) The
				  plan and procedures for responding to consumer complaints;
(8) The schedule and procedures for testing
				  backflow prevention assemblies;
(9)
				  The schedule and procedures for routine exercising of water main
				  valves;
(10) The schedule and
				  program for maintenance and calibration of source flow meters and other online
				  instruments used to determine the quality or quantity of water;
(11) The qualifications and training of
				  operating personnel;
(12) The
				  program for control of biological organisms on the interior walls of water
				  mains; and
(13) For an underground
				  reservoir with a buried roof designed for a function in addition to covering
				  the reservoir, a comprehensive routine inspection and monitoring plan to ensure
				  that there is no contamination of the reservoir as a result of that additional
				  function.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64602 - Minimum Pressure

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
				  Each distribution system shall be operated in a manner to assure that the
				  minimum operating pressure in the water main at the user service line
				  connection throughout the distribution system is not less than 20 pounds per
				  square inch at all times.
(b) Each
				  new distribution system that expands the existing system service connections by
				  more than 20 percent or that may otherwise adversely affect the distribution
				  system pressure shall be designed to provide a minimum operating pressure
				  throughout the new distribution system of not less than 40 pounds per square
				  inch at all times excluding fire flow.
1. Repealer
					 of subsection (c) filed 10-9-85; effective thirtieth day thereafter (Register
					 85, No. 42).
2. Repealer and new section filed 2-8-2008; operative
					 3-9-2008 (Register 2008, No. 6).
Note: Authority cited: Sections
						116350,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116275,
						116375,
						116535,
						116555
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64604 - Preparation and Maintenance of Records

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each public water system subject to this
				  chapter shall prepare:
(1) "As built" plans,
				  maps, and drawings of all new water system facilities including updated
				  information for all existing facilities in the same location or connected to
				  the new facilities. The plans, maps, and drawings shall be clear and legible
				  and shall include the location, size, construction material, and year of
				  installation of each new water main or other facility.
(2) A schematic drawing or map showing the
				  location of each water source, treatment facility, pumping plant, reservoir,
				  water main and isolation valve.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64610 - Basic Design of Pumping Stations. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 10-9-85; effective thirtieth day thereafter (Register 85, No.
					 42).
2. Repeal and deletion of former article 4 heading and repealer
					 of article 4 (sections
					 64610-64612) filed 2-8-2008;
					 operative 3-9-2008 (Register 2008, No. 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64612 - Water Sealed Pumps. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Amendment
					 filed 10-9-85; effective thirtieth day thereafter (Register 85, No.
					 42).
2. Repealer filed 2-8-2008; operative 3-9-2008 (Register 2008,
					 No. 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64622 - Water Main Materials. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Amendment
					 filed 10-9-85; effective thirtieth day thereafter (Register 85, No.
					 42).
2. Repeal and deletion of former article 5 heading and repealer
					 of article 5 (sections
					 64622-64644) and section filed
					 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64624 - Water Main Selection and Installation. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Amendment
					 filed 10-9-85; effective thirtieth day thereafter (Register 85, No.
					 42).
2. Repealer filed 2-8-2008; operative 3-9-2008 (Register 2008,
					 No. 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64626 - Layout of Water Mains. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64628 - Minimum Water Main Diameter and Length of Run. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Amendment
					 of subsection (d)(2) filed 10-9-85; effective thirtieth day thereafter
					 (Register 85, No. 42).
2. Repealer filed 2-8-2008; operative
					 3-9-2008 (Register 2008, No. 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64630 - Water Main Installation. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Amendment
					 filed 10-9-85; effective thirtieth day thereafter (Register 85, No.
					 42).
2. Repealer filed 2-8-2008; operative 3-9-2008 (Register 2008,
					 No. 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64632 - Water Main Valve Locations. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64634 - Water Main Valve Construction Standards. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Amendment
					 filed 10-9-85; effective thirtieth day thereafter (Register 85, No.
					 42).
2. Repealer filed 2-8-2008; operative 3-9-2008 (Register 2008,
					 No. 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64636 - Air and Vacuum Relief and Air Release Valves. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64638 - Water Main Joints. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64640 - Fire Hydrants. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64642 - Flushing Valves and Blowoffs. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 16 - California Waterworks Standards › Article 8 - 8. Distribution System Operation › Section 64644 - Service Connection Pipe. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1. Repealer
					 filed 2-8-2008; operative 3-9-2008 (Register 2008, No.
					 6).
Note: Authority cited: Sections
						208
						and
						4010.1(h),
						Health and Safety Code. Reference: Sections
						4010.1(h),
						4012,
						4013
						and
						4019,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.10 - Approved Surface Water

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Approved surface water" means a surface water or
					 groundwater under the direct influence of surface water that has received
					 permit approval from the State Board in accordance with sections
					 116525
					 through
					 116550
					 of the Health and Safety Code.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No. 25).
2.
					 Amendment of section and NOTE filed 12-13-2007; operative 1-12-2008 (Register
					 2007, No. 50).
3. Change without regulatory effect amending section
					 and NOTE filed 6-2-2015 pursuant to section
					 100, title 1, California Code of
					 Regulations (Register 2015, No. 23).
Note: Authority cited: Sections
						116271
						and
						116375,
						Health and Safety Code. Reference: Sections
						116270,
						116275,
						116365,
						116375,
						116385,
						116390,
						116400,
						116525,
						116530,
						116535,
						116540,
						116550
						and
						116625,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.12 - Bag Filters

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Bag filters" mean pressure-driven separation devices that
					 remove particulate matter larger than 1 micrometer using an engineered porous
					 filtration media. They are typically constructed of a non-rigid, fabric
					 filtration media housed in a pressure vessel in which the direction of flow is
					 from the inside of the bag to outside.
1. New
					 section filed 5-22-2013; operative 7-1-2013 (Register 2013, No.
					 21).
Note: Authority cited: Sections
						116350,
						116375,
						131052
						and
						131200,
						Health and Safety Code. Reference: Sections
						116350
						and
						116375,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.13 - Bank Filtration

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Bank filtration" means a water treatment process that uses
					 a well to recover surface water that has naturally infiltrated into ground
					 water through a river bed or bank(s). Infiltration is typically enhanced by the
					 hydraulic gradient imposed by a nearby pumping water supply or other
					 well(s).
1. New
					 section filed 5-22-2013; operative 7-1-2013 (Register 2013, No.
					 21).
Note: Authority cited: Sections
						116350,
						116375,
						131052
						and
						131200,
						Health and Safety Code. Reference: Sections
						116350
						and
						116375,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.15 - Cartridge Filters

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Cartridge filters" mean pressure-driven separation devices
					 that remove particulate matter larger than 1 micrometer using an engineered
					 porous filtration media. They are typically constructed as rigid or semi-rigid,
					 self-supporting filter elements housed in pressure vessels in which flow is
					 from the outside of the cartridge to the inside.
1. New
					 section filed 5-22-2013; operative 7-1-2013 (Register 2013, No.
					 21).
Note: Authority cited: Sections
						116350,
						116375,
						131052
						and
						131200,
						Health and Safety Code. Reference: Sections
						116350
						and
						116375,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.16 - Coagulant Chemical

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Coagulant chemical" means a floc-forming agent that has
					 been demonstrated to provide coagulation.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.20 - Coagulation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Coagulation" means a process using coagulant chemicals and
					 rapid mixing, by which colloidal and suspended material are destabilized and
					 agglomerated into settleable and/or filterable flocs.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.21 - Comprehensive Performance Evaluation (CPE)

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Comprehensive performance evaluation (CPE)" means a review
					 and analysis of a treatment plant's performance-based capabilities and
					 associated administrative, operation, and maintenance
					 practices.
1. New
					 section filed 12-13-2007; operative 1-12-2008 (Register 2007, No.
					 50).
Note: Authority cited: Sections
						100275,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116270,
						116275,
						116365,
						116375,
						116385,
						116390,
						116400,
						116525,
						116530,
						116535,
						116540,
						116550,
						116625
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.23 - Conventional Filtration Treatment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Conventional filtration treatment" means a series of
					 treatment processes which includes coagulation, flocculation, sedimentation,
					 and filtration resulting in substantial particulate removal.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.26 - Diatomaceous Earth Filtration

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Diatomaceous earth filtration" means a process resulting
					 in particulate removal in which a precoat cake of graded diatomaceous earth
					 filter media is deposited on a support membrane (septum) and, while the water
					 is being filtered by passing through the cake on the septum, additional filter
					 media known as body feed is continuously added to the feed water to maintain
					 the permeability of the filter cake.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.30 - Direct Filtration Treatment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Direct filtration treatment" means a series of processes
					 including coagulation, flocculation, and filtration but excluding
					 sedimentation.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1. 4023.3, 4024, 4025,
						4026.4, and 4031, Health and Safety
						Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.32 - Disinfectant Contact Time

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Disinfectant contact time" means the time in minutes that
					 it takes for water to move from the point of disinfectant application or a
					 previous point of disinfectant residual measurement to a point before or at the
					 point where residual disinfectant concentration is measured. Disinfectant
					 contact time in pipelines is calculated by dividing the internal volume of the
					 pipe by the flow rate through the pipe. Disinfectant contact time within mixing
					 basins and storage reservoirs is determined by tracer studies or an equivalent
					 demonstration to the State Board.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No. 25).
2.
					 Change without regulatory effect amending section and NOTE filed 6-2-2015
					 pursuant to section
					 100, title 1, California Code of
					 Regulations (Register 2015, No. 23).
Note: Authority cited: Sections
						116271
						and
						116375,
						Health and Safety Code. Reference: Sections
						116275,
						116365,
						116375,
						116385,
						116390,
						116400,
						116530,
						116535
						and
						116550,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.33 - Disinfection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Disinfection" means a process which inactivates pathogenic
					 organisms in water by chemical oxidants or equivalent agents.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.34 - Disinfection Profile

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Disinfection profile" means a summary of
Giardia
					 lamblia
or virus inactivation through the treatment
					 plant.
1. New
					 section filed 12-13-2007; operative 1-12-2008 (Register 2007, No.
					 50).
Note: Authority cited: Sections
						100275,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116270,
						116275,
						116365,
						116375,
						116385,
						116390,
						116400,
						116525,
						116530,
						116535,
						116540,
						116550,
						116625
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.36 - Engineering Report

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Engineering report" means a water treatment technical
					 report prepared by a qualified engineer.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1. 4023.3, 4024, 4025,
						4026.4, and 4031, Health and Safety
						Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.38 - Filter Profile

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Filter profile" means a graphical representation of
					 individual filter performance, based on continuous turbidity measurements or
					 total particle counts versus time for an entire filter run, from startup to
					 backwash inclusively, that includes data collected while another filter is
					 being backwashed.
1. New
					 section filed 12-13-2007; operative 1-12-2008 (Register 2007, No.
					 50).
Note: Authority cited: Sections
						100275,
						116375
						and
						131200,
						Health and Safety Code. Reference: Sections
						116270,
						116275,
						116365,
						116375,
						116385,
						116390,
						116400,
						116525,
						116530,
						116535,
						116540,
						116550,
						116625
						and
						131051,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.40 - Filter-to-Waste

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Filter-to-waste" means a provision in a filtration process
					 to allow the first filtered water, after backwashing a filter, to be wasted or
					 reclaimed.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.43 - Filtration

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Filtration" means a process for removing particulate
					 matter from water by passage through porous media.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.46 - Flocculation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Flocculation" means a process to enhance agglomeration or
					 collection of smaller floc particles into larger, more easily settleable or
					 filterable particles through gentle stirring by hydraulic or mechanical
					 means.
1. New
					 section filed 5-6-91; operative 6-5-91 (Register 91, No.
					 25).
Note: Authority cited: Sections
						208
						and
						4023.3,
						Health and Safety Code. Reference: Sections
						4010,
						4010.1,
						4011,
						4012,
						4013,
						4014,
						4016,
						4023.1,
						4023.3,
						4024,
						4025,
						4026.4,
						and
						4031,
						Health and Safety Code.
California Code of Regulations › Title 22 - Social Security › Division 4 - Environmental Health › Chapter 17 - Surface Water Treatment › Article 1 - General Requirements and Definitions › Section 64651.48 - Flowing Stream

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
"Flowing stream" means a course of running water flowing in
					 a definite channel.
1. New
					 section filed 5-22-2013; operative 7-1-2013 (Register 2013, No.
					 21).
Note: Authority cited: Sections
						116350,
						116375,
						131052
						and
						131200,
						Health and Safety Code. Reference: Sections
						116350
						and
						116375,
						Health and Safety Code.