reglab/statecodes huggingface dataset:
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 6 - Mechanical Systems › Section 806 - Location of Liquefied Petroleum Gas Tanks

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) No tank or cylinder shall be maintained
						within an enclosed housing accommodation, nor within five (5) feet (1.5 meters)
						of a source of ignition, nor with the outlet less than five (5) feet (1.5
						meters) away from any building opening which is below the level of such
						outlet.
(b) No tank or cylinder
						shall be maintained or stored beneath any shed, structure, mobile home,
						recreational vehicle, commercial coach, or other housing accommodation in a
						labor camp.
(c) Tanks shall be
						maintained to be separated from the nearest building, structure, mobile home,
						recreational vehicle, commercial coach or other housing accommodations with a
						minimum clearance of ten (10) feet (3 meters) for tanks with a capacity of 61
						to 576 gallons (230.5 to 2177.2 liters) and twenty-five (25) feet (7.5 meters)
						minimum clearance for tanks with a capacity of 576 to 2000 gallons (2177.2 to
						7560 liters).
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 6 - Mechanical Systems › Section 808 - Tank Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
L.P. Gas tanks located adjacent to driveways and
						  parking areas shall be maintained to prevent mechanical damage.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 6 - Mechanical Systems › Section 810 - Warning Signs

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No smoking warning sign(s) shall be maintained at all
						  L.P. Gas tank locations.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 6 - Mechanical Systems › Section 812 - Tank Support

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All L.P. Gas tanks shall be maintained on a firm pad or
						  foundation.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 6 - Mechanical Systems › Section 814 - Prohibited Use of Connectors

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Existing gas supply tubing and connectors shall be
						  maintained and not extended through walls or partitions.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 6 - Mechanical Systems › Section 816 - Outlets to Be Capped

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Gas supply outlets shall be maintained capped when not
						  in use.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 818 - Use of Fuel

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All existing fuel burning appliances and equipment
						  shall be maintained and approved by the enforcing agency for the type of fuel
						  supplied.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 820 - Unvented Heaters

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
No unvented fuel burning heater shall be permitted to
						  be used in a labor camp.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 822 - Prohibited Use

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Gas hot plates, cook stoves and ranges shall not be
						  used as room heaters in a labor camp.
1.
						  Amendment filed 12-31-79 as an emergency; designated effective 1-1-80 (Register
						  80, No. 1). A Certificate of Compliance must be filed within 120 days or
						  emergency language will be repealed on 5-1-80.
2. Amendment filed
						  4-28-80 as an emergency; effective upon filing (Register 80, No. 18).
						  Certificate of Compliance included.
3. Editorial correction of NOTE
						  filed 11-18-82 (Register 82, No. 47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 824 - Appliance Installation Instructions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All heating and air conditioning equipment shall be
						  maintained according to the manufacturers installation
						  instructions.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 826 - Clearances for Existing Appliances Without Instructions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Clearances shall be maintained between the appliance
						  and combustible materials as follows:
1. 36 inches (91.4 centimeters) for solid or
						liquid fuel fired Radiant Heaters, 12 inches (30.4 centimeters) for solid or
						liquid fuel fired circulating heaters, and six inches (15.2 centimeters) for
						gas fired circulating space heaters. Separations will be measured from the
						appliance jacket, sides, rear and from the single wall connector vent
						piping.
2. Space or room heaters
						burning gas, solid or liquid fuel when mounted on combustible flooring shall
						have at least four (4) inches (10.1 centimeters) of open space under the base
						of the appliance.
3. The
						combustible flooring under the appliance shall be protected with sheet metal of
						not less than 24 U.S. Gauge, extending six inches (15.2 centimeters) beyond the
						appliance on all sides, and where solid fuel is used shall extend not less than
						18 inches (45.7 centimeters) at the front or side where the ashes are
						removed.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 828 - Shut-Off Valve

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All heating appliances supplied with gas or liquid fuel
						  shall be maintained with a shut-off valve installed in the supply line
						  immediately adjacent to the appliance.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 830 - Clean Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All heating and cooking appliances shall be clean and
						  grease free. It is the employer/manager's responsibility to see that the
						  appliances in dwelling units are clean and grease free before occupancy by a
						  new tenant.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 832 - Appliance Vent Installation

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Appliance vent piping shall be
						maintained, connected to the appliance hood collar or draft diverter and
						extended without openings through protective flashing to a point above the
						roof.
(b) Appliance vent piping
						shall be maintained to be secured at each joint, properly graded and adequately
						supported.
(c) Appliances shall be
						maintained to be properly vented and shall not be vented into a fireplace or
						into a chimney serving a fireplace.
1.
						  Editorial correction filed 11-18-82 (Register 82, No. 47).
2.
						  Amendment filed 3-15-83; effective thirtieth day thereafter (Register 83, No.
						  12).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 834 - Water Heater Relief Valves

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Water heaters equipped with pressure-temperature relief
						  valves shall be maintained with metal piping installed, undiminished in size,
						  extending from the valve outlet to a point outside of the building not more
						  than two feet (60.9 centimeters) nor less than six inches (15.2 centimeters)
						  above the ground and pointing downward.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 836 - Appliance Compartments

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Fuel burning heating appliance
						compartments shall be maintained structurally sound, and provide adequate
						combustion air through screened openings.
(b) Heating appliance compartments shall be
						maintained in a clean condition and not used for storage.
(c) Heating appliance compartments outside of
						buildings shall be maintained to protect the appliance from the
						weather.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 7 - Heating Appliances › Section 838 - Secured Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All heating appliances shall be maintained rigidly
						  secured in place.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 850 - Electrical Systems Use

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Electrical fixtures, equipment and other devices may
						  have their existing use, maintenance or repair continued if the use,
						  maintenance or repair is in accordance with the original design and location
						  and is not a hazard to life, health, or property.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 852 - Safeguards

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All electrical equipment, devices, and safeguards shall
						  be maintained in good working order.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 854 - Wiring Methods and Materials

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Electrical materials, devices, appliances fittings and
						  equipment maintained in labor camps shall be approved for the purpose and shall
						  be maintained to be connected and secured in an approved manner when in
						  service.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 858 - Overcurrent Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Electrical conductors shall be maintained
						and protected by means of fuses or circuit breakers rated at not more than the
						allowable capacity of the conductors.
(b) Tampering. Overcurrent protection shall
						not be altered or tampered with.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 860 - Weather Proof

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The service equipment which is not rain tight shall be
						  maintained and protected from the weather.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 862 - Vertical Clearances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The minimum vertical clearance to be maintained for
						  open electrical conductors are as follows:
(a) Above roofs--eight feet (2.4
						meters).
(b) Above walkways and at
						attachment point of buildings--10 feet (3.0 meters).
(c) Above driveways and parking areas--15
						feet (4.5 meters).
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 864 - Conductors on Poles

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Overhead electrical conductors located on poles and
						  bracket supports shall be maintained and properly supported, secured, and
						  routed to clear sharp objects, other conductors and tree
						  branches.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 866 - Grounding Fixed Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Non-current carrying metal parts of fixed electrical
						  equipment shall be maintained effectively grounded.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 868 - Grounding of Cord Connected Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Cord connected appliances, such as washing machines,
						  dishwashers, garbage disposals, electrical system of gas ranges and furnaces
						  and other equipment required to be grounded, shall be maintained to be grounded
						  by means of an approved cord with a grounding conductor and a grounded type
						  attachment plug.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 870 - Grounded Convenience Outlet

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Grounding type outlets located at the following
						  locations shall be maintained in good working order:
(a) Adjacent to fixed appliances.
(b) For appliances located adjacent to
						lavatories, sinks, laundry tubs, or within reach of a grounded
						surface.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 872 - Outlets in Habitable Rooms

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
At least one convenience outlet and one supplied
						  electric light fixture shall be maintained in good working order in all
						  habitable rooms.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 874 - Lighting in Bath and Toilet Room

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
At least one supplied light fixture in good working
						  order shall be maintained in all bathrooms and toilet rooms.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 878 - Enclosed Light Fixture

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The light fixtures located over a bathtub or in a
						  shower compartment shall be maintained to be moisture proof and equipped with
						  enclosure and enclosure gaskets in good condition.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 880 - Shower Light Switch

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The switch for shower lighting fixtures or an exhaust
						  fan which have been located over a tub or in a shower compartment shall be
						  maintained outside of the tub space or the shower compartment in a dry
						  location.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 882 - Range Hood Light

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The light fixtures located in or under a range hood
						  shall be maintained to be grease and moisture proof with enclosure and
						  enclosure gaskets maintained in good condition.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 884 - Pullchain Switch

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A pullchain switch shall not be maintained in a damp
						  location, and not over or within reach of a plumbing fixture, cookstove, range,
						  furnace, and other grounded surfaces.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 886 - Exposed Nonmetallic Sheathed Cable

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Exposed nonmetallic sheathed cable shall be maintained
						  to be protected from physical and mechanical damage by running boards,
						  guardstrips or installed in conduit.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 888 - Cable Clamps

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All loose nonmetallic sheathed cable shall be
						  maintained to be secured in place by staples and straps at intervals which will
						  not exceed 4 ½ feet (1.3 meters) and within 12 inches (30.4 centimeters)
						  from every cabinet, box, or fitting.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 890 - Outlet Boxes

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All electrical conductors shall be maintained to
						  terminate in an approved outlet box or a junction box rigidly secured to the
						  building or structure.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 892 - Covers

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Open outlet boxes, fittings and enclosures shall be
						  maintained with covers. Openings not in use will be closed.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 894 - Extension Cords

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Extension cords shall not be maintained as a connection
						  to electric light fixture sockets in order to energize
						  appliances.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 8 - Electrical Systems › Section 896 - Cord Wiring

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Flexible cords shall not be maintained as a fixed
						  wiring method or run through walls and partitions.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Section 17040, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 9 - Use of Mobile Homes, Recreational Vehicles, Commercial Coaches, Mobile Home Accessory Buildings, Structures, Tents and Camp Grounds › Section 900 - Facilities

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The facilities to accommodate tent campers, mobile
						  homes, recreational vehicles, and commercial coaches shall be maintained in
						  conformance with the applicable requirements of Title 25, California
						  Administrative Code, Part 1, Chapter 2, Subchapters 1 and 2.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Sections 17040 and 17041, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 9 - Use of Mobile Homes, Recreational Vehicles, Commercial Coaches, Mobile Home Accessory Buildings, Structures, Tents and Camp Grounds › Section 902 - Installation Requirements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All mobile homes in a labor camp shall be maintained in
						  accordance with the provisions of Title 25, California Administrative Code,
						  Part 1, Chapter 2, Subchapters 1 and 2, as applicable.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Sections 17040 and 17041, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 9 - Use of Mobile Homes, Recreational Vehicles, Commercial Coaches, Mobile Home Accessory Buildings, Structures, Tents and Camp Grounds › Section 904 - Insignia and/or Label Required

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The mobile homes constructed prior to June 15, 1976,
						  recreational vehicles, and commercial coaches provided by the employer shall
						  bear an insignia of approval issued by the Department of Housing and Community
						  Development. The mobile homes constructed on or after June 15, 1976, shall bear
						  a label indicating compliance to the Federal Mobile home Construction and
						  Safety Standards.
1.
						  Editorial correction adding NOTE filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Sections 17040 and 17041, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 9 - Use of Mobile Homes, Recreational Vehicles, Commercial Coaches, Mobile Home Accessory Buildings, Structures, Tents and Camp Grounds › Section 908 - Alterations and Conversions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All mobile homes required to bear a department insignia
						  of approval and/or a Federal label shall be maintained in compliance with Title
						  25, California Administrative Code, Chapter 3, Subchapters 1 and 2. Prior to
						  making any alteration or conversion, a permit shall be obtained from the
						  department.
1.
						  Editorial correction filed 11-18-82 (Register 82, No.
						  47).
Note: Authority cited: Sections 17003.5 and 17040,
							 Health and Safety Code. Reference: Sections 17040 and 17041, Health and Safety
							 Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 6 - Maintenance, Use and Occupancy › Subarticle 9 - Use of Mobile Homes, Recreational Vehicles, Commercial Coaches, Mobile Home Accessory Buildings, Structures, Tents and Camp Grounds › Section 910 - Tents

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The tents
						provided by the operator shall not be used to house occupants unless such tents
						are maintained with tight wooden floors raised at least four inches (10.1
						centimeters) above the ground level and are equipped with baseboards on all
						sides to a height of at least six inches (15.2 centimeters) or maintained with
						concrete slabs with the finished surface at least four inches (10.1
						centimeters) above grade and equipped with curbs on all sides at least six
						inches (15.2 centimeters) high.
(b)
						A tent shall not be considered a suitable sleeping place when it is found
						necessary to provide heating facilities in order to maintain a minimum
						temperature of 50° Fahrenheit (10° Celsius) within such tent during the
						period of occupancy.
1.
						  Editorial correction filed 11-18-82 (Register 82, No. 47).
2.
						  Amendment of subsection (a) filed 3-6-85; effective thirtieth day thereafter
						  (Register 85, No. 10).
3. Amendment of subsection (b) and NOTE filed
						  8-20-92 as an emergency; operative 8-20-92 (Register 92, No. 34). A Certificate
						  of Compliance must be filed with OAL 12-18-92 or emergency language will be
						  repealed by operation of law on the following day.
4. Repealer of
						  emergency amendment filed 8-20-92 and reinstatement of prior text filed 3-15-93
						  by operation of Government Code section 11346.1(f) (Register 93, No.
						  12).
Note: Authority cited: Sections 17040, 17041 and
							 17050, Health and Safety Code. Reference: Sections 17040 and 17041, Health and
							 Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 7 - Actions and Proceedings › Section 920 - Actions and Proceedings

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Actions and proceedings of this
					 subchapter shall be in accordance with Chapters 5 and 6 (commencing with
					 Section 17050) of the Health and Safety Code.
(b) The enforcement agency may revoke without
					 additional hearing the permit to operate or exemption of a labor camp whenever
					 any judgment is rendered against the operator thereof concerning the operation
					 of the labor camp.
(c) The
					 enforcement agency may revoke without additional hearing the exemption of
					 employee community housing whenever any judgment is rendered against the owner
					 or operator thereof for not maintaining or operating such employee community
					 housing in substantial compliance with relevant portions of these
					 regulations.
1.
						Amendment filed 12-31-79 as an emergency; designated effective 1-1-80 (Register
						80, No. 1). A Certificate of Compliance must be filed within 120 days or
						emergency language will be repealed on 5-1-80.
2. Amendment filed
						4-28-80 as an emergency; effective upon filing (Register 80, No. 18).
						Certificate of Compliance included.
3. Editorial correction filed
						11-18-82 (Register 82, No. 47).
4. Repealer of subsection (d) filed
						3-6-85; effective thirtieth day thereafter (Register 85, No.
						10).
Note: Authority cited: Sections 17003.5, 17040 and
						  17050, Health and Safety Code. Reference: Sections 17040, 17051, 17060.5 and
						  17061, Health and Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 7 - Actions and Proceedings › Section 922 - Permit or Exemption Suspension

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
If any labor camp or employee community housing is not in
						substantial compliance with relevant use, occupancy, or maintenance provisions
						of the Employee Housing Act, this subchapter, or the conditions of the permit
						to operate, or exemption, the permit to operate or exemption may be suspended
						by the enforcement agency pursuant to the procedures in this
						article.
1.
						Amendment filed 12-31-79 as an emergency; designated effective 1-1-80 (Register
						80, No. 1). A Certificate of Compliance must be filed within 120 days or
						emergency language will be repealed on 5-1-80.
2. Amendment filed
						4-28-80 as an emergency; effective upon filing (Register 80, No. 18).
						Certificate of Compliance included.
3. Editorial correction filed
						11-18-82 (Register 82, No. 47).
Note: Authority cited: Sections 17003.5 and 17036,
						  Health and Safety Code. Reference: Section 17036, Health and Safety
						  Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 7 - Actions and Proceedings › Section 923 - Authority to Serve Notices

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Authority to serve notices required by this subchapter is
						provided in Section 17051 of the Health and Safety Code.
1.
						Amendment filed 12-31-79 as an emergency; designated effective 1-1-80 (Register
						80, No. 1). A Certificate of Compliance must be filed within 120 days or
						emergency language will be repealed on 5-1-80.
2. Editorial
						correction of NOTE filed 11-18-82 (Register 82, No.
						47).
Note: Authority cited: Sections 17003.5, 17036, 17040
						  and 17050, Health and Safety Code. Reference: Section 17051, Health and Safety
						  Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 7 - Actions and Proceedings › Section 924 - Notice

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The enforcement agency shall issue and serve upon the
						permittee or exemptee a notice setting forth in what respects the provisions of
						the Health and Safety Code, this subchapter or the conditions of the permit to
						operate or exemption have been violated, and shall notify him that unless these
						provisions have been complied with within five days, or within such longer
						period of time, not to exceed 30 days, which may be allowed by the enforcement
						agency from the date of notice, the permit to operate or exemption shall be
						suspended.
1.
						Amendment filed 12-31-79 as an emergency; designated effective 1-1-80 (Register
						80, No. 1). A Certificate of Compliance must be filed within 120 days or
						emergency language will be repealed on 5-1-80.
2. Editorial
						correction of NOTE filed 11-18-82 (Register 82, No.
						47).
Note: Authority cited: Sections 17003.5 and 17036,
						  Health and Safety Code. Reference: Sections 17036, 17051 and 17060, Health and
						  Safety Code.
California Code of Regulations › Title 25 - Housing and Community Development › Division 1 - Housing and Community Development › Chapter 1 - State Housing Law Regulations and Earthquake Protection Law Regulations › Subchapter 3 - Employee Housing › Article 7 - Actions and Proceedings › Section 926 - Service

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The notice shall be served by posting at least one copy
						in a conspicuous place on the premises described in said permit or exemption,
						and by sending another copy by certified mail, postage prepaid, return receipt
						requested, to the person to whom the permit or exemption was issued at the
						permittee's or exemptee's address of record, or as otherwise designated on the
						permit or exemption. The notice may also be served by personal service at the
						discretion of the enforcement agency.
1.
						Amendment filed 12-31-79 as an emergency; designated effective 1-1-80 (Register
						80, No. 1). A Certificate of Compliance must be filed within 120 days or
						emergency language will be repealed on 5-1-80.
2. Editorial
						correction of NOTE filed 11-18-82 (Register 82, No.
						47).
Note: Authority cited: Sections 17003.5 and 17036,
						  Health and Safety Code. Reference: Sections 17036 and 17051, Health and Safety
						  Code.