reglab/statecodes huggingface dataset:
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.16 - Emergency Illumination

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Emergency illumination shall include all
						required means of egress lighting, illuminated exit signs, and all other lights
						necessary to provide illumination.
(b) Where emergency lighting is necessary,
						the system shall be so arranged that the failure of any individual lighting
						element, such as the burning out of a light bulb, cannot leave any space in
						total darkness.
1. New
						  section filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
2. Amendment of section and NOTE filed 5-5-2008; operative
						  5-5-2008. Submitted to OAL for printing only pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.19 - Switch Location. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Renumbering and amendment of Section
						  2571.19 to Section
						  2571.21 filed 8-27-86; effective
						  thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.21 - Switch Location

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						All manual switches for controlling emergency circuits shall be in locations
						convenient to authorized persons responsible for their actuation. In places of
						assembly, such as theaters, a switch for controlling emergency lighting systems
						shall be located in the lobby or at a place conveniently accessible
						thereto.
(b) In no case shall a
						control switch for emergency lighting in a theater or motion picture theater or
						place of assembly be placed in a motion picture projection booth or on a stage.
EXCEPTION: Where multiple switches are provided, one
						  such switch shall be permitted in such locations where so arranged that it can
						  energize but not disconnect the circuit.
(Title 24, Part 3, Section
						  700-21.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Renumbering and amendment of former Section
						  2571.21 to Section
						  2571.25, and renumbering and
						  amendment of former Section
						  2571.19 to Section
						  2571.21 filed 8-27-86; effective
						  thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.25 - Accessibility

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The branch circuit overcurrent devices in emergency
						  circuits shall be accessible to authorized persons only.
(Title 24, Part 3, Section
						  700-25.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Renumbering and amendment of former Section
						  2571.21 to Section
						  2571.25 filed 8-27-86; effective
						  thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 80 - Emergency Power Systems › Section 2571.30 - Signs

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
For installations built on or after May 5, 2008:
(a) A sign shall be placed at the service
						entrance equipment indicating the type and location of on-site emergency power
						sources. However, a sign is not required for individual unit
						equipment.
(b) Where the grounded
						circuit conductor connected to the emergency source is connected to a grounding
						electrode conductor at a location remote from the emergency source, there shall
						be a sign at the grounding location that shall identify all emergency and
						normal sources connected at that location.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 81 - Stand-by Power Generation Systems › Section 2575.1 - Scope. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Repealer filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 81 - Stand-by Power Generation Systems › Section 2575.10 - Legally Required Stand-by Power Generation Systems. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Repealer filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
						  37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 82 - Electrolytic Systems › Section 2580.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The provisions of this article shall apply to
						  electroplating and electrostripping processes.
(Title 24, Part 3, Section
						  3-669 -
						  1.)
1.
						  Editorial correction filed 11-2-83 (Register 83, No.
						  45).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 82 - Electrolytic Systems › Section 2580.2 - Wiring Methods. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Renumbering of Section
						  2580.2 to Section
						  2580.6 filed 8-27-86; effective
						  thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code; and Section
							 18943(c),
							 Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 82 - Electrolytic Systems › Section 2580.6 - Wiring Methods

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Systems not exceeding 50 volts DC. Insulated open conductors on insulators or
						bare busbars shall be permitted for the supply of electrolytic installations
						not exceeding 50 volts DC.
(b)
						Systems exceeding 50 volts DC.
(1) Insulated
						open conductors on insulators or bare busbars shall be permitted for the supply
						of electrolytic installations exceeding 50 volts DC, when guarded as required
						in Section 2340.17.
EXCEPTION: Unguarded bare conductors or busbars shall
						  be permitted at the tanks.
(2) When access to the process while
						energized is necessary, the entrance door guarding the electrolytic process
						shall be electrically interlocked so that access by employees will be prevented
						when the voltage exceeds 50 volts DC.
(Title 24, Part 3, Section
						  3-669 -
						  6.)
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 82 - Electrolytic Systems › Section 2599 - General. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
						  Amendment filed 2-9-55; effective thirtieth day thereafter (Register 55, No.
						  3).
2. Amendment filed 11-27-62; effective thirtieth day thereafter
						  (Register 62, No. 24).
3. Renumbering of Article 36 to Article 83
						  (Section 2599) filed 10-14-75; effective
						  thirtieth day thereafter (Register 75, No. 42).
4. Repealer of
						  Article 83 (Section
						  2599) filed 11-14-75; effective
						  thirtieth day thereafter (Register 75, No.
						  46).
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article applies to the installation of the
						  electrical components and accessory equipment of electrolytic cells,
						  electrolytic cell lines, and process power supply for the production of
						  aluminum, cadmium, chlorine, copper, fluorine, hydrogen peroxide, magnesium,
						  sodium, sodium chlorate, and zinc. Cells used as a source of electric energy
						  and for electroplating processes and cells used for production of hydrogen are
						  not covered by this Article.
1. New
						  article 83 (sections
						  2583.1-2583.8) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.2 - Application

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Installations covered by this Article shall comply with
						  all applicable provisions of these Safety Orders, except as follows:
(a) Overcurrent protection of electrolytic
						cell dc process power circuits need not comply with the requirements of Article
						10, Overcurrent Protection;
(b)
						Equipment located or used within the cell line working zone or associated with
						the cell line dc power circuits need not comply with the provisions of Article
						11, Grounding; and
(c) Electrolytic
						cells, cell line conductors, cell line attachments, and the wiring of auxiliary
						equipment and devices within the cell line working zone need not comply with
						the provisions of Article 2. Administration, Article 6, Branch Circuits, or
						Article 8, Outdoor Wiring.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.3 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
If more than one dc cell line process power supply
						  serves the same cell line, a disconnecting means shall be provided on the cell
						  line circuit side of each power supply to disconnect it from the cell line
						  circuit. Removable links or removable conductors may be used as the
						  disconnecting means.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.4 - Portable Electric Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The frames and enclosures of portable
						electric equipment used within the cell line working zone may not be grounded,
						unless the cell line circuit voltage does not exceed 200 volts DC or the frames
						are guarded.
(b) Ungrounded
						portable electric equipment shall be distinctively marked and shall employ
						plugs and receptacles of a configuration that prevents connection of this
						equipment to grounding receptacles and that prevents inadvertent interchange of
						ungrounded and grounded portable electric equipment.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.5 - Power Supply Circuits and Receptacles for Portable Electric Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Circuits
						supplying power to ungrounded receptacles for hand-held, cord- and
						plug-connected equipment shall meet the following requirements:
(1) The circuits shall be electrically
						isolated from any distribution system supplying areas other than the cell line
						working zone and shall be ungrounded;
(2) The circuits shall be supplied through
						isolating transformers with primaries operating at not more than 600 volts
						between conductors and protected with proper overcurrent protection;
(3) The secondary voltage of the isolating
						transformers may not exceed 300 volts between conductors; and
(4) All circuits supplied from the
						secondaries shall be ungrounded and shall have an approved overcurrent device
						of proper rating in each conductor.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.6 - Fixed and Portable Electric Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) The following need not be grounded:
(1) AC systems supplying fixed and portable
						electric equipment within the cell line working zone; and
(2) Exposed conductive surfaces, such as
						electric equipment housings, cabinets, boxes, motors, raceways and the like
						that are within the cell line working zone.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.7 - Auxiliary Nonelectrical Connections

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Auxiliary nonelectrical connections such as air hoses,
						  water hoses, and the like, to an electrolytic cell, its attachments, or
						  auxiliary equipment may not have continuous conductive reinforcing wire, armor,
						  braids, or the like.
Hoses shall be of a nonconductive
						  material.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 83 - Electrolytic Cells › Section 2583.8 - Cranes and Hoists

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						The conductive surfaces of cranes and hoists that enter the cell line working
						zone need not be grounded. The portion of an overhead crane or hoist that
						contacts an energized electrolytic cell or energized attachments shall be
						insulated from ground.
(b) Remote
						crane or hoist controls that may introduce hazardous electrical conditions into
						the cell line working zone shall employ one or more of the following systems:
(1) Isolated and ungrounded control
						circuit;
(2) Nonconductive rope
						operator;
(3) Pendant pushbutton
						with nonconductive supporting means and with nonconductive surfaces or
						ungrounded exposed conductive surfaces; or
(4) Radio.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article covers the installation of portable wiring
						  and equipment, including wiring in or on all structures, for carnivals,
						  circuses, exhibitions, fairs, traveling attractions, and similar events
						  installed on or after May 5, 2008.
1. New
						  article 84 (sections
						  2584.1-2584.8) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.2 - Protection of Electric Equipment

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Electric equipment and wiring methods in or on rides,
						  concessions, or other units shall be provided with mechanical protection where
						  such equipment or wiring methods are subject to physical
						  damage.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.3 - Services

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Services shall
						be installed in accordance with applicable requirements of these Safety Orders,
						and, in addition, shall comply with the following:
(1) Service equipment shall not be installed
						in a location that is accessible to unqualified persons, unless the equipment
						is lockable; and
(2) Service
						equipment shall be mounted on solid backing and installed so as to be protected
						from the weather, unless the equipment is of weatherproof
						construction.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.4 - Overhead Conductor Clearances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Amusement rides and amusement attractions shall be
						  maintained not less than 15 feet (4.57 m) in any direction from overhead
						  conductors operating at 600 volts or less, except for the conductors supplying
						  the amusement ride or attraction. Amusement rides or attractions may not be
						  located under or within 15 feet (4.57 m) horizontally of conductors operating
						  in excess of 600 volts.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.5 - Wiring Methods

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Flexible cords and cables shall be listed for extra-hard usage. When used
						outdoors, flexible cords and cables shall also be listed for wet locations and
						shall be sunlight resistant.
(b)
						Single conductor cable shall be size No. 2 or larger.
(c) Open conductors are prohibited except as
						part of a listed assembly or festoon lighting installed in accordance with
						Article 8, Outdoor Wiring.
(d)
						Flexible cords and cables shall be continuous without splice or tap between
						boxes or fittings. Cord connectors shall not be laid on the ground unless
						listed for wet locations. Connectors and cable connections shall not be placed
						in audience traffic paths or within areas accessible to the public unless
						guarded.
(e) Wiring for an
						amusement ride, attraction, tent, or similar structure shall not be supported
						by another ride or structure unless specifically identified for the
						purpose.
(f) Flexible cords and
						cables run on the ground, where accessible to the public, shall be covered with
						approved nonconductive mats. Cables and mats shall be arranged so as not to
						present a tripping hazard.
(g) A
						box or fitting shall be installed at each connection point, outlet, switch
						point, or junction point.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.6 - Inside Tents and Concessions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Electrical wiring for temporary lighting, where
						  installed inside of tents and concessions, shall be securely installed, and,
						  where subject to physical damage, shall be provided with mechanical protection.
						  All temporary lamps for general illumination shall be protected from accidental
						  breakage by a suitable fixture or lampholder with a guard.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.7 - Portable Distribution and Termination Boxes

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Employers shall only use portable distribution and
						  termination boxes that meet the following requirements:
(a) Boxes shall be designed so that no live
						parts are exposed to accidental contact. Where installed outdoors, the box
						shall be of weatherproof construction and mounted so that the bottom of the
						enclosure is not less than 6 in. (152 mm) above the ground;
(b) Busbars shall have an ampere rating not
						less than the overcurrent device supplying the feeder supplying the box. Busbar
						connectors shall be provided where conductors terminate directly on
						busbars;
(c) Receptacles shall have
						overcurrent protection installed within the box. The overcurrent protection
						shall not exceed the ampere rating of the receptacle, except as permitted in
						Article 56 for motor loads;
(d)
						Where single-pole connectors are used, they shall comply with the following:
(1) Where ac single-pole portable cable
						connectors are used, they shall be listed and of the locking type. Where
						paralleled sets of current-carrying single-pole separable connectors are
						provided as input devices, they shall be prominently labeled with a warning
						indicating the presence of internal parallel connections. The use of
						single-pole separable connectors shall comply with at least one of the
						following conditions:
(A) Connection and
						disconnection of connectors are only possible where the supply connectors are
						interlocked to the source and it is not possible to connect or disconnect
						connectors when the supply is energized; or
(B) Line connectors are of the listed
						sequential-interlocking type so that load connectors are connected in the
						following sequence:
1. Equipment grounding
						conductor connection;
2. Grounded
						circuit-conductor connection, if provided; and
3. Ungrounded conductor connection; and so
						that disconnection is in the reverse order; or
(C) A caution notice is provided adjacent to
						the line connectors indicating that plug connection must be in the following
						sequence:
1. Equipment grounding conductor
						connection;
2. Grounded
						circuit-conductor connection, if provided; and
3. Ungrounded conductor connection; and
						indicating that disconnection is in the reverse order;
						and
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 84 - Carnivals, Circuses, Fairs, and Similar Events › Section 2584.8 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Each ride and concession shall be provided with a fused disconnect switch or
						circuit breaker located within sight and within 6 feet (1.83 m) of the
						operator's station.
(b) The
						disconnecting means shall be readily accessible to the operator, including when
						the ride is in operation.
(c) Where
						accessible to unqualified persons, the enclosure for the switch or circuit
						breaker shall be of the lockable type.
(d) A shunt trip device that opens the fused
						disconnect or circuit breaker when a switch located in the ride operator's
						console is closed is a permissible method of opening the circuit.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 85 - Class 1, Class 2, and Class 3 Remote Control, Signaling, and Power-Limited Circuits › Section 2585.1 - Classification

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Class 1, Class 2, and Class 3 remote control,
						  signaling, or power-limited circuits are characterized by their usage and
						  electrical power limitation that differentiates them from light and power
						  circuits. These circuits are classified in accordance with their respective
						  voltage and power limitations as summarized in subsections (a)-(c)
						  below:
(a) A Class 1 power-limited
						circuit shall be supplied from a source having a rated output of not more than
						30 volts and 1000 volt-amperes.
(b)
						A Class 1 remote control circuit or a Class 1 signaling circuit shall have a
						voltage not exceeding 600 volts; however, the power output of the source need
						not be limited.
(c) The power
						source for a Class 2 or Class 3 circuit shall be listed equipment marked as a
						Class 2 or Class 3 power source, except as follows:
(1) Thermocouples do not require listing as a
						Class 2 power source.
(2) A dry
						cell battery is considered an inherently limited Class 2 power source, provided
						the voltage is 30 volts or less and the capacity is less than or equal to that
						available from series-connected No. 6 carbon zinc cells.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 85 - Class 1, Class 2, and Class 3 Remote Control, Signaling, and Power-Limited Circuits › Section 2585.2 - Marking

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
A Class 2 or Class 3 power supply unit shall be durably
						  marked where plainly visible to indicate the class of supply and its electrical
						  rating.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 85 - Class 1, Class 2, and Class 3 Remote Control, Signaling, and Power-Limited Circuits › Section 2585.3 - Separation from Conductors of Other Circuits

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
For installations built on or after May 5, 2008 cables
						  and conductors of Class 2 and Class 3 circuits may not be placed in any cable,
						  cable tray, compartment, enclosure, manhole, outlet box, device box, raceway,
						  or similar fitting with conductors of electric light, power, Class 1,
						  nonpower-limited fire alarm circuits, and medium power network-powered
						  broadband communications cables unless a barrier or other equivalent form of
						  protection against contact is employed.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 86 - Fire Alarm Systems › Section 2586.1 - Classifications

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Fire alarm circuits shall be classified either as
						  nonpower limited or power limited.
1. New
						  article 86 (sections
						  2586.1-2586.4) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 86 - Fire Alarm Systems › Section 2586.2 - Power Sources

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The power sources for use with fire alarm circuits
						  shall be either power limited or nonpower limited as follows:
(a) The power source of nonpower-limited fire
						alarm (NPLFA) circuits shall have an output voltage of not more than 600 volts,
						nominal; and
(b) The power source
						for a power-limited fire alarm (PLFA) circuit shall be listed equipment marked
						as a PLFA power source.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.6
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 86 - Fire Alarm Systems › Section 2586.3 - Separation from Conductors of Other Circuits

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Nonpower-limited fire alarm circuits and
						Class 1 circuits may occupy the same enclosure, cable, or raceway provided all
						conductors are insulated for maximum voltage of any conductor within the
						enclosure, cable, or raceway. Power supply and fire alarm circuit conductors
						are permitted in the same enclosure, cable, or raceway only if connected to the
						same equipment.
(b) Power-limited
						circuit cables and conductors may not be placed in any cable, cable tray,
						compartment, enclosure, outlet box, raceway, or similar fitting with conductors
						of electric light, power, Class 1, non-power-limited fire alarm circuit
						conductors, or medium power network-powered broadband communications
						circuits.
(c) Power-limited fire
						alarm circuit conductors shall be separated at least 2 in. (50.8 mm) from
						conductors of any electric light, power, Class 1, nonpower-limited fire alarm,
						or medium power network-powered broadband communications circuits unless a
						special and equally protective method of conductor separation is
						employed.
(d) Conductors of one or
						more Class 2 circuits are permitted within the same cable, enclosure, or
						raceway with conductors of power-limited fire alarm circuits provided that the
						insulation of Class 2 circuit conductors in the cable, enclosure, or raceway is
						at least that needed for the power-limited fire alarm circuits.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 86 - Fire Alarm Systems › Section 2586.4 - Identification

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Fire alarm circuits shall be identified at terminal and
						  junction locations in a manner that will prevent unintentional interference
						  with the signaling circuit during testing and servicing. Power-limited fire
						  alarm circuits shall be durably marked as such where plainly visible at
						  terminations.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 87 - Communications Systems › Section 2587.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article applies to central-station-connected and
						  non-central-station-connected telephone circuits, radio and television
						  receiving and transmitting equipment, including community antenna television
						  and radio distribution systems, telegraph, district messenger, and outside
						  wiring for fire and burglar alarm, and similar central station systems. These
						  installations need not comply with the provisions of Article 2 through Article
						  86 of these Low-Voltage Electrical Safety Orders, except for Section
						  2375.7 and Article
						  59.
1. New
						  article 87 (sections
						  2587.1-2586.5) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 87 - Communications Systems › Section 2587.2 - Protective Devices

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A
						listed primary protector shall be provided on each circuit run partly or
						entirely in aerial wire or aerial cable not confined within a block.
(b) A listed primary protector shall be also
						provided on each aerial or underground circuit when the location of the circuit
						within the block containing the building served allows the circuit to be
						exposed to accidental contact with electric light or power conductors operating
						at over 300 volts to ground.
(c) In
						addition, where there exists a lightning exposure, each interbuilding circuit
						on premises shall be protected by a listed primary protector at each end of the
						interbuilding circuit.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 87 - Communications Systems › Section 2587.3 - Conductor Location

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Lead-in or aerial-drop cables from a pole or other support, including the point
						of initial attachment to a building or structure, shall be kept away from
						electric light, power, Class 1, or nonpower-limited fire alarm circuit
						conductors so as to avoid the possibility of accidental contact.
(b) A separation of at least 6 feet (1.83 m)
						shall be maintained between communications wires and cables on buildings and
						lightning conductors.
(c) Where
						communications wires and cables and electric light or power conductors are
						supported by the same pole or run parallel to each other in-span, the following
						conditions shall be met:
(1) Where
						practicable, communication wires and cables on poles shall be located below the
						electric light or power conductors; and
(2) Communications wires and cables shall not
						be attached to a crossarm that carries electric light or power
						conductors.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 87 - Communications Systems › Section 2587.4 - Equipment Location

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Outdoor metal structures supporting antennas, as well
						  as self-supporting antennas such as vertical rods or dipole structures, shall
						  be located as far away from overhead conductors of electric light and power
						  circuits of over 150 volts to ground as necessary to prevent the antenna or
						  structure from falling into or making accidental contact with such
						  circuits.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 87 - Communications Systems › Section 2587.5 - Grounding

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) If exposed to
						contact with electric light and power conductors, the metal sheath of aerial
						cables entering buildings shall be grounded or shall be interrupted close to
						the entrance to the building by an insulating joint or equivalent device. Where
						protective devices are used, they shall be grounded in an approved
						manner.
(b) Masts and metal
						structures supporting antennas shall be permanently and effectively grounded
						without splice or connection in the grounding conductor.
(c) Transmitters shall be enclosed in a metal
						frame or grill or separated from the operating space by a barrier, all metallic
						parts of which are effectively connected to ground. All external metal handles
						and controls accessible to the operating personnel shall be effectively
						grounded. Unpowered equipment and enclosures are considered to be grounded
						where connected to an attached coaxial cable with an effectively grounded
						metallic shield.
1. New
						  section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 88 - Solar Photovoltaic Systems › Section 2588.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Article covers solar photovoltaic systems
						  constructed or installed on or after May 5, 2008 that can be interactive with
						  other electric power production sources or can stand alone with or without
						  electrical energy storage such as batteries. These systems may have ac or dc
						  output for utilization.
1. New
						  article 88 (sections
						  2588.1-2588.3) and section filed
						  5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to
						  Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.