Florida Administrative Code › 25 - PUBLIC SERVICE COMMISSION › 25 - Departmental › Chapter 25-6 - ELECTRIC SERVICE BY ELECTRIC PUBLIC UTILITIES › Part IV - GENERAL SERVICE PROVISIONS › Section 25-6.0455 - Annual Distribution Service Reliability Report

Current through Reg. 50, No. 138; July 16, 2024
(1) Each utility shall file a Distribution
				  Service Reliability Report with the Commission Clerk on or before March 1 of
				  each year, for the preceding calendar year.
(2) The Distribution Service Reliability
				  Report will exclude the impact of all service interruptions associated with
				  generation and transmission disturbances governed by subsections
				   25-6.018(2) and
				  (3), F.A.C.
(3) The report shall contain the following
				  information on an actual and adjusted basis:
(a) The utility's total number of Outage
				  Events (N), categorized by cause for the highest ten causes of Outage Events,
				  the Average Duration of Outage Events (L-Bar), and Average Service Restoration
				  Time (CAIDI). The utility shall record these data and analyses on Form PSC/ENG
				  102-1(a) (8/06) and Form PSC/ENG 102-1(b) (8/06), entitled "Causes of Outage
				  Events - Actual" and "Causes of Outage Events - Adjusted", respectively, which
				  may be obtained from the Division of Engineering, 2540 Shumard Oak Boulevard,
				  Tallahassee, Florida 32399-0850, (850)413-6910, and which are incorporated
				  herein by reference;
(b)
				  Identification of the three percent of the utility's Primary Circuits (feeders)
				  with the highest number of feeder breaker interruptions. For each primary
				  circuit so identified the utility shall report the primary circuit
				  identification number or name, substation origin, general location, number of
				  affected customers by service class served, Number of Outage Events (N),
				  Average Duration of Outage Events (L-Bar), Average Service Restoration Time
				  (CAIDI), whether the same circuit is being reported for the second consecutive
				  year, the number of years the primary circuit was reported on the "Three
				  Percent Feeder List" in the past five years, and the corrective action date of
				  completion. The utility shall record these data and analyses on Form PSC/ENG
				  102-2(a) (8/06) and Form PSC/ENG 102-2(b) (8/06), entitled "Three Percent
				  Feeder List - Actual" and "Three Percent Feeder List - Adjusted", respectively,
				  which may be obtained from the Division of Engineering, 2540 Shumard Oak
				  Boulevard, Tallahassee, Florida 32399-0850, (850)413-6910, and which are
				  incorporated herein by reference;
(c) The reliability indices SAIDI, CAIDI,
				  SAIFI, MAIFIe, and CEMI5 for its system and for each district or region into
				  which its system may be divided. The utility shall report these data and
				  analyses on Form PSC/ENG 102-3(a) (8/06) and Form PSC/ENG 102-3(b) (8/06),
				  entitles "System Reliability Indices - Annual" and "System Reliability Indices
				  - Adjusted", respectively, which may be obtained from the Division of
				  Engineering, 2540 Shumard Oak Boulevard, Tallahassee, Florida 32399-0850,
				  (850)413-6910, and which are incorporated herein by reference. Any utility
				  furnishing electric service to fewer than 50, 000 retail customers shall not be
				  required to report the reliability indices MAIFIe or CEMI5; and
(d) The calculations for each of the required
				  indices and measures of distribution reliability.