reglab/statecodes huggingface dataset:
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1720 - Water Closets

Current through Register Vol. 48, No. 28, July 12, 2024
a) All water
				closets shall either be of stainless steel (Type 304) construction, including
				framework, reinforcing and interior piping, or be vitreous china complying with
				ASME A112.19.2/CSA B45.1.
b) If
				stainless steel water closets are used, they shall comply with the following:
1) The bowl and flushing rim shall not be
				less than 14 gauge.
2) The water
				closet shall have a minimum of a 3-inch diameter, fully enclosed stainless
				steel P-trap and shall pass a 21/8-inch diameter ball.
3) All welds shall be ground smooth, and
				exterior surfaces polished.
4)
				Integral contoured seats that are self-draining and crevice freeshall be a part
				of the water closet.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1730 - Urinals

Current through Register Vol. 48, No. 28, July 12, 2024
a) All urinals
				shall be either Type 304 stainless steel or vitreous china complying with ASME
				A112.19.2/CSA B45.1.
b) All
				stainless steel urinals shall comply with the following:
1) The urinal shall be fabricated of Type 304
				stainless steel with exposed edges polished.
2) All exposed welds are to be ground
				smooth.
3) All construction is to
				be free from visible voids, seams or crevices.
4) The trap shall provide a 2-inch seal and
				pass a 1.9 -inch diameter ball.
5)
				The urinal shall be fitted with an integrally welded steel beehive dome
				strainer.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1740 - Combination Lavatory/Toilet

Current through Register Vol. 48, No. 28, July 12, 2024
a) The
				cabinet shall be of stainless steel (Type 304) with a minimum of 12 gauge for
				the cabinet and 14 gauge for the top.
b) The cabinet top shall have a
				backsplash.
c) The lavatory shall
				include adjustable control valves on the hot and cold, self-closing filler
				valve with a maximum ½ gpm flow control and a combination penal
				filler/bubbler spout. A maximum of 115F temperature is allowed.
d) The lavatory drain shall not have a
				mechanical air vent attached.
e)
				Supply inlets to the lavatory shall have screw driver stops, gate or globe
				valves.
f) The water closet shall
				have no less than a 3 inch diameter, fully enclosed stainless steel toilet
				P-trap and shall pass a 21/8 inch diameter ball.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1750 - Service Sinks/Lavatory

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Service sinks/lavatories shall be either stainless steel, cast iron complying
				with ASME A112.19.1/CSA B45.2, or vitreous china complying with ASME
				A112.19.2/CSA B45.1. Stainless steel service sinks/lavatories shall be
				fabricated of Type 304 stainless steel with the exterior surfaces polished; all
				exposed welds are to be ground smooth, and there shall be no visible voids,
				seams or crevices.
b) Security
				sink/lavatory shall include a self-closing valve set with integral stops, gate
				or globe valves, reversible union inlets and plain-end filler spout, or a grid
				strainer drain, elbow waste with a 2-inch female connection. Timing of control
				valves shall be field adjustable from five to 40 seconds and shall not require
				shutting off the supply lines.
c)
				The waste assembly shall comply with Section
				890.410(g)(1)
				 and be of brass, copper or bronze
				construction.
d) Drains with
				mechanical air vents are prohibited.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1760 - Sinks

Current through Register Vol. 48, No. 28, July 12, 2024
a) All sinks for
				food preparation or cleansing of utensils used to prepare food shall be of
				stainless steel (Type 304) construction, including framework and
				reinforcing.
b) All welds shall be
				ground smooth, and exterior surfaces polished.
c) All sinks shall be provided with waste
				outlets at least one and one-half (1 1/2) inches in diameter. A crossbar,
				strainer, or other means shall be provided to restrict the clear opening of the
				waste outlet. No kitchen sink basket shall be less than three and one-half (3
				½) inches in diameter.
d)
				Waste lines and water supply lines shall conform with Sections
				890.130
				through
				890.1600.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1770 - Cabinet Showers

Current through Register Vol. 48, No. 28, July 12, 2024
a) All cabinet
				showers shall be unitized one-piece fixtures of stainless steel with the
				exposed surfaces polished, except the receptor which shall have a non-skid
				surface. All exposed welds shall be ground smooth and all construction is to be
				free of visible voids, seams or crevices.
b) Shower compartments shall have at least
				1,296 square inches outside dimensions and shall be at least 32 inches in
				shortest dimension outside dimensions.
c) The valve shall be an adjustable type with
				a maximum of two and one-half (2 1/2) gpm flow control, integral screwdriver
				stop valve.
d) The shower shall
				include a stainless steel soap dish, shower head and clothes hook, designed for
				correctional facility use.
e) The
				shower head within shower cabinets or site constructed showers shall be located
				in such a manner as not to pose an insanitary or nuisance condition outside the
				shower area. The shower heads are to be on a side wall or overhead so as not to
				spray water out of the shower cabinet or area and create a slipping hazard on
				the tile floor or cause water to pond in areas other than the shower
				area.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1780 - Flush Valves

Current through Register Vol. 48, No. 28, July 12, 2024
a) All flush
				valves for water closets or urinals shall conform with Sections
				890.650(e)
				and
				890.660(b)
				of this Part.
b) All flush valves
				shall feature rubber diaphragm operation, non-hold-open push buttons (and
				handles), union check stops and vacuum breakers as approved in this Part. (See
				Sections
				890.1130(c)
				and
				890.1140(a)
				and (b).)
c) Flush valves shall be concealed wherever
				possible.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart L - PLUMBING SYSTEMS/CORRECTIONAL FACILITIES › Section 890.1800 - Floor Drains

Current through Register Vol. 48, No. 28, July 12, 2024
a) Location.
				Floor drains can be located either within a cell or outside the cell.
b) Drain Cover. Each drain cover shall be
				securely anchored by means of vandal resistant screws.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Section 890.1910 - Inspections

Current through Register Vol. 48, No. 28, July 12, 2024
A plumbing system or any part thereof shall not be enclosed,
				  covered up or used until the system has been inspected and approved by a
				  plumbing inspector. It is the responsibility of the licensed plumber or
				  plumbing contractor on the job to arrange for inspection by the Department or a
				  local plumbing inspector. The plumbing inspector may require tests as listed in
				  Section
				  890.1930 to
				  determine whether or not the system as installed is in compliance with this
				  Part. Plumbing found not to be in compliance with this Part shall not be
				  approved. A plumbing system not complying with the provisions of this Part
				  shall not be used until such time as it is brought into compliance with this
				  Part. After the plumbing corrections have been made, the plumbing contractor
				  shall arrange for reinspection.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Section 890.1920 - Testing of Plumbing Systems

Current through Register Vol. 48, No. 28, July 12, 2024
Defective Plumbing. Where there is reason to believe that the
				  plumbing system fails to comply with this Part, the Department or local
				  plumbing inspector may require such tests (see Section
				  890.1930 ) and
				  inspections as may be necessary to assure that any defects are found and
				  corrected.
a) Exposure of Work. When
				plumbing work has been covered or concealed prior to being tested and approved,
				it shall be exposed for testing. It is the responsibility of the licensed
				plumber or plumbing contractor to expose plumbing for inspection
				purposes.
b) Equipment, Material
				and Labor for Tests. All equipment, material and labor required for inspection
				and testing a plumbing system or any part thereof is the responsibility of the
				licensed plumber or plumbing contractor.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Section 890.1940 - General Administration

Current through Register Vol. 48, No. 28, July 12, 2024
The plans and specifications for a plumbing system whose
				  design does not comply with this Part must be submitted to the Department for
				  approval prior to installation of such a plumbing system. Such approval shall
				  be in writing from the Department and shall be based on a determination that
				  the system is expected to perform and exhibit durability as if meeting the
				  requirements of this Part.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Section 890.1950 - Violations

Current through Register Vol. 48, No. 28, July 12, 2024
a) Notice of
				Violation
1) Violators of this Part shall be
				informed of any violation at the time of inspection, followed by a formal
				notice in writing, including a deadline date for correction of the
				violation(s).
2) Factors to be
				considered in establishing deadline dates for correction shall include the
				nature and complexity of the violation, the stage of construction, the type of
				violation involved, the weather, and whether or not the violation represents a
				potential or immediate health hazard.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table C - Minimum Air Gaps for Plumbing Fixtures

Current through Register Vol. 48, No. 28, July 12, 2024
Minimum Air Gap (Inches)
When
Not
Affected by Near
								Wall1
When Affected by Near
								Wall2
Lavoratories and other fixtures with effective
								opening not greater than 1/2 inch diameter.
1
1½
Drinking water fountains, single orifice not
								greater than 
								7/16
								(0.437 ) inch diameter or multiple orifices having total area of 0.150 square
								inches (area of circle 
								7/16
								inch diameter).
1
1½
Sink, laundry trays, goose neck bath faucets and
								other fixtures with effective opening not greater than one inch
								diameter.
1½
2¼
Stills, sterilizers and other appliances, fixtures,
								devices and water and waste connections used for preparation of sterile
								material.
2
3
Over rim bath fillers and other fixtures with
								effective openings not greater than one inch diameter.
2
3
Effective openings greater than one inch.
2 X Diameter of
effective opening
3 X Diameter of
effective opening
1 Side walls, ribs or other
					 similar obstructions do not affect air gaps when spaced from inside edge of
					 spout opening a distance greater than three times the diameter of the effective
					 opening for a single wall, or a distance greater than four times the diameter
					 of the effective opening for two intersecting walls.
2 Vertical walls, ribs or
					 similar obstructions extending from the water surface or to above the
					 horizontal plane of the spout opening require a greater air gap when spaced
					 closer to the nearest inside edge of spout opening than specified in Footnote 1
					 above. The effect of three or more such vertical walls or ribs has not been
					 determined. In such cases, the air gap shall be measured from the top of the
					 wall.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table D - Minimum Water Distribution Pipe Size

Current through Register Vol. 48, No. 28, July 12, 2024
Type of Fixture or Device (See
								Footnotes 1 & 2)
Pipe Size (inches)
Bathtubs
½
Combination sink and tray
½
Drinking fountain
3/8
Dishwasher (domestic)
½
Dishwasher (commercial)
¾
Kitchen sink (residential)
½
Kitchen sink (commercial) 1 Faucet
½
Kitchen sink (commercial) 2 Faucets
¾
Lavatory
3/8
Laundry tray (1, 2 or 3 compartment)
½
Shower (single head)
½
Sinks (service/slop)
½
Sinks (flushing rim)
¾
Urinal (flush tank)
½
Urinal (direct flush valve)
¾
Urinal (siphon jet)
1
Washing machine (automatic)
½
Water closet (tank type)
3/8
Water closet (flush valve type)
1
Hose bibbs
½
Wall hydrant
½
1 For fixtures not listed, the
					 minimum supply branch shall be installed in the diameters required for similar
					 type fixtures.
2 The fixture supply pipe shall
					 be extended to within 12 inches of the point of connection to fixture and be
					 within the same area and physical space as the point of connection to the
					 fixture.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table E - Drainage Fixture Units (D.F.U.) Per Fixture Group

Current through Register Vol. 48, No. 28, July 12, 2024
Type of Fixture
D.F.U./Fixture (Load)
Minimum Size of
								Trap2 (inches)
Bathroom groups:
1 tank water closet, 1 lavatory
with 1¼ inch trap and 1
bathtub1 or shower
								stall
7
11/4
1 water closet with flush valve, 1
lavatory with 1¼ inch trap and 1
bathtub or
								shower1
11
Bathtub (with or without overhead
								shower)1
2
1½
Bathtub1
3
2
Bidet
2
1½
Clothes washer, automatic
3
2
Dental unit or cuspidor
1
1¼
Drinking fountain
½
1
Dishwasher2,
								domestic
2
1½
Floor drains
See Appendix A, Table F
2
Lavatories:
Lavatory
1
1¼
Lavatory
2
1½
Lavatory, barber, beauty parlor
2
1½
Lavatory, dental
1
1¼
Lavatory, surgeon's
2
1½
Laundry tray (1 or 2 compartments)
2
1½
Type of Fixture
D.F.U./Fixture (Load)
Minimum Size of
								Trap2 (inches)
Shower stall
3
2
Showers (group) per
								head2
3
2
Sinks:
Combination sink and tray
3
1½
Combination sink and tray with
food-disposal unit
4 Separate Traps
1½
Flushing rim (with valve)
8
3
Kitchen sink, domestic
2
1½
Kitchen sink, domestic, with food-waste
grinder
3 Separate Traps
1½
Pot, scullery,
								etc.2
4
1½
Service (P trap)
3
3
Service (P trap)
2
2
Surgeon's
3
1½
Wash sink2 (circular or
								multiple),
each set of faucets
2
1½
Urinals:
Urinal, pedestal, siphon jet, blowout
8
2
Urinal stall
3
2
Urinal, wall integral trap
3
2
Urinal, wall P trap, exposed
2
1½
Water closets:
Tank operated
4
3
Valve-operated
8
3
1A shower head over a bathtub
					 does not increase the fixture value.
2See Appendix A: Table F and
					 Section
					 890.1330(b)
					 for method of determining unit values of fixtures not listed in this Table or
					 for rating of devices with intermittent flows.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table F - Fixtures Not Listed in Table E

Current through Register Vol. 48, No. 28, July 12, 2024
Fixture Drain or Trap Size
Drainage Fixture Unit Valve (D.F.U.)
11/4 inches and smaller
1
11/2 inches
2
2 inches
3
21/2 inches
4
3 inches
5
4 inches
6
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table G - Building Drains

Current through Register Vol. 48, No. 28, July 12, 2024
Diameter of Pipe (inches)
Maximum Number of Drainage Fixture
								Units (D.F.U.) That May be Connected to Any Portion of the Building
								Drain
Grade per Foot
1/16
								Inch
1/8 Inch
1/4 Inch
1/2 Inch
4
-
180
216
250
5
-
390
480
575
6
-
700
840
1,000
8
1,400
1,600
1,920
2,300
10
2,500
2,900
3,500
4,200
12
3,900
4,600
5,600
6,700
15
7,000
8,300
10,000
12,000
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table H - Horizontal Fixture Branches and Stacks

Current through Register Vol. 48, No. 28, July 12, 2024
Maximum Number of Drainage Fixture
								Units (D.F.U.)
That May be Connected to:
More than 3 Stories in Height
Diameter of Pipe (inches)
Any Horizontal Fixture Branch
One Stack of 3 Stories in Height or 3
								Intervals
Total for Stack
Total at One Story or Branch Interval
11/4
1
2
2
1
11/2
3
4
8
2
2
6
10
24
6
21/2
12
20
42
9
3
201
302
602
161
4
100
240
500
90
5
360
540
1,100
200
6
620
960
1,900
350
8
1,400
2,200
3,600
600
10
2,500
3,800
5,600
1,500
12
3,900
6,000
8,400
1,500
15
7,000
-
-
-
1 Not over two water
					 closets.
2 Not over six water closets, or
					 more than two per branch interval or per floor.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table I - Allowed Distance from Fixture Trap to Vent

Current through Register Vol. 48, No. 28, July 12, 2024
Size of Fixture Drains
								(Inches)
Maximum Allowed Distance from Trap
								to Vent
11/4
2 ft. 6 in.
11/2
3 ft. 6 in.
2
4 ft. 0 in.
3
5 ft. 0 in.
4 and larger
6 ft. 0 in.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table J - Size of Vent Stacks

Current through Register Vol. 48, No. 28, July 12, 2024
Number of Bathroom Groups
Diameter of Vent Stacks
								(Inches)
1 or 2
2
3 to 9
3
10 to 16
4
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table K - Size and Length of Vents

Current through Register Vol. 48, No. 28, July 12, 2024
Size of Soil or Waste Stack
Fixture Units Connected
Diameter of Vent Required
								(Inches)
11/4
11/2
2
21/2
3
4
5
6
8
Maximum Length of Vent (Feet)
11/4
2
30
11/2
8
50
150
11/2
10
30
100
2
12
30
75
200
2
20
26
50
150
21/2
42
30
100
300
3
10
30
100
200
600
3
30
60
200
500
3
60
50
60
400
4
100
35
100
260
1,000
4
200
30
90
250
900
4
500
20
70
180
700
5
200
35
80
350
1,000
5
500
30
70
300
900
5
1,100
20
50
200
700
6
350
25
50
200
400
1,300
6
620
15
30
125
300
1,100
6
960
24
100
250
1,000
6
1,900
20
70
200
700
8
600
50
150
500
1,300
8
1,400
40
100
400
1,200
8
2,200
30
80
350
1,100
9
3,600
25
60
250
800
10
1,000
75
125
1,000
10
2,500
50
100
500
10
3,800
30
80
350
10
5,600
25
60
250
Agency Note: Per Section
						890.1580(e),
						no more than 20 percent of the maximum developed length may be installed in the
						horizontal position. Vent piping serving floor drains shall be installed in
						such a manner as to minimize horizontal vent
						distances.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table L - Horizontal Circuit and Loop Vent Sizing Table

Current through Register Vol. 48, No. 28, July 12, 2024
Line
Soil or waste pipe diam.
								(in.)
Fixture Units (max. number
Diameter of circuit or loop vent
								(in.)
11/2
2
21/2
3
4
5
Maximum Horizontal Length
								(ft.)
1
11/2
10
20
2
2
12
15
40
3
2
20
10
30
4
3
10
20
40
100
5
3
30
40
100
6
3
60
16
80
7
4
100
7
20
52
200
8
4
200
6
18
50
180
9
4
500
14
36
140
10
5
200
16
70
200
11
5
1,100
10
40
140
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table M - Load Values Assigned to Fixtures

Current through Register Vol. 48, No. 28, July 12, 2024
Fixture
Occupancy
Type of
Supply Control
Load Values in Water (Supply Fixture Units)
Cold
Hot
Total
Water Closet
Public/Private
Flush Valve
10
-
10
Water Closet
Public/Private
Flush Tank
3
-
3
Urinal
Public
1" Flush Valve
10
-
10
Urinal
Public
¾" Flush Valve
5
-
5
Urinal
Public
Flush Tank
3
-
3
Lavatory
Public
Faucet
1
1
2
Bathtub
Public
Faucet
3
3
4
Shower Head
Public
Mixing Valve
2
2
3
Service Sink
Offices, etc.
Faucet
2
2
3
Kitchen Sink
Hotel/Restaur.
Faucet
3
3
4
Drinking Fountain
Office, etc.
3/8" Valve
0.25
-
0.25
Lavatory
Private
Faucet
0.75
0.75
1
Bathtub
Private
Faucet
1.5
1.5
2
Shower Stall
Private
Mixing Valve
1
1
2
Kitchen Sink
Private
Faucet
1.5
1.5
2
Laundry Trays (1 to 3)
Private
Faucet
2
2
3
Dishwashing Machine
Private
Automatic
-1
1
Laundry Machine (8 lb)
Private
Automatic
1.5
1.5
2
Laundry Machine (16 lb)
Public/ General
Automatic
3
3
4
Agency Notes: For fixtures not listed, loads shall be
						assumed by comparing the fixtures to one listed using water in similar
						quantities and at similar rates. The assigned loads for fixtures with both cold
						and hot water supplies are given for separate cold and hot water loads and for
						total load.
Where a unit of local government or the community public
						water supply does not require separate water service lines for irrigation or
						similar systems that are likely to impose continuous demands (e.g., lawn
						sprinkler or air conditioning systems), the following rule applies: estimate
						the continuous demand (in gallons per minute) for outlets/systems separately
						from the intermittent demand from the fixtures listed in this table, and add
						this amount to the demand of the fixtures (in gallons per minute).
Fire sprinkler systems are exempt from this
						table.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table N - Water Supply Fixture Units (WSFU) for a Supply System with Flush Tanks Water Closets

Current through Register Vol. 48, No. 28, July 12, 2024
WSFU
Demand
(GPM)
Pipe Size
(Inches)
Pressure
Loss
(PSI/100'
of Pipe)
Velocity
(Ft./Sec.)
Meter Size
(Inches)
2
2
½"
4.2
2.7
5/8"
4
3
½"
8.7
4.2
5/8"
6
5
½"
22.5
7.0
5/8"
8
6.5
¾"
6.3
4.3
5/8"
10
8
¾"
9.0
5.4
¾"
12
9.2
¾"
11.5
6.1
¾"
14
10.4
¾"
15.0
6.9
¾"
16
11.6
¾"
18.0
7.7
¾"
20
14
1"
7.2
5.6
¾"
25
17
1"
10.0
6.6
¾"
30
20
1"
13.6
8.0
1"
35
22.5
1¼"
5.8
5.7
1"
40
25
1¼"
7.0
6.3
1"
45
27
1¼"
8.2
6.9
1"
50
29
1¼"
9.5
7.4
1"
60
32
1½"
5.0
5.8
1½"
70
35
1½"
6.2
6.4
1½"
80
38
1½"
7.0
7.2
1½"
90
41
1½"
8.0
7.5
1½"
100
43.5
1½"
8.7
7.8
2"
120
48
2"
2.7
5.0
2"
140
52.5
2"
3.1
5.4
2"
160
57
2"
3.6
5.8
2"
180
61
2"
3.9
6.1
2"
200
65
2"
4.5
6.6
2"
225
70
2"
5.2
7.1
2"
250
75
2"
6.0
7.7
3"
275
80
2½"
2.6
5.5
3"
300
85
2½"
2.9
5.8
3"
350
95
2½"
3.5
6.5
3"
400
105
2½"
4.2
7.1
3"
450
115
2½"
5.0
8.0
3"
500
125
3"
2.3
5.9
3"
600
145
3"
3.1
6.8
4"
750
170
3"
4.0
8.0
4"
1000
208
4"
1.5
5.7
4"
1250
240
4"
1.9
6.4
4"
1500
267
4"
2.3
7.0
4"
1750
294
4"
2.8
7.8
4"
2000
320
6"
0.36
3.7
6"
Agency Notes:
Where a unit of local government or the
						community public water supply does not require separate water service lines for
						irrigation or similar systems that are likely to impose continuous demands
						(e.g., lawn sprinkler or air conditioning systems), the following rule applies:
						estimate the continuous demand (in gallons per minute) for outlets/systems
						separately from the intermittent demand from the above fixtures, and add this
						amount to the demand of the fixtures (in gallons per minute).
Meter and meter yoke sizes shown in this table
						shall apply only to those jurisdictions or governmental units where local
						ordinances or community public water supply requirements do not prescribe
						specific sizes of meters or meter yokes. Where local ordinances or community
						public water supply requirements cover sizing, those requirements shall be
						followed.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table O - Water Supply Fixture Units (WSFU) for a Supply System with Flushometer Water Closets

Current through Register Vol. 48, No. 28, July 12, 2024
WSFU
Demand (GPM)
Pipe Size (Inches)
Pressure Loss (PSI/100'
of Pipe)
Velocity (Ft./Sec.)
Meter Size (Inches)
10
27
1¼"
8.3
6.8
¾"
12
28.6
1¼"
9.2
7.2
¾"
14
30.2
1¼"
10
7.9
¾"
16
31.8
1¼"
11
8.0
¾"
20
35
1½"
6.0
6.4
¾"
25
38
1½"
7.0
6.9
1"
30
41
1½"
8.0
7.4
1"
35
43.8
1½"
8.8
8.0
1"
40
46.5
2"
2.5
4.7
1"
45
49
2"
2.7
5.1
1"
50
51.5
2"
2.9
5.4
1½"
60
55
2"
3.4
5.8
1½"
70
58.5
2"
3.7
6.0
1½"
80
62
2"
4.0
6.2
1½"
90
64.8
2"
4.6
6.5
1½"
100
67.5
2"
5.0
6.8
1½"
120
72.5
2"
5.6
7.2
2"
140
77.5
2"
6.3
8.0
2"
160
82.5
2½"
2.7
5.7
2"
180
87
2½"
3.0
6.1
2"
200
91.5
2½"
3.4
6.4
2"
225
97
2½"
3.7
6.8
2"
250
101
2½"
4.0
7.1
3"
275
106
2½"
4.2
7.3
3"
300
110
2½"
4.6
7.6
3"
350
119
3"
2.1
5.5
3"
400
126
3"
2.3
5.9
3"
450
138
3"
2.7
6.3
3"
500
145
3"
3.0
6.8
3"
600
160
3"
3.6
7.4
4"
750
178
4"
1.1
4.7
4"
1000
208
4"
1.5
5.6
4"
1250
240
4"
1.9
6.4
4"
1500
267
4"
2.3
7.0
4"
1750
294
4"
2.8
7.8
4"
2000
321
6"
0.4
3.7
6"
Agency Notes:
Where a unit of local government or the
						community public water supply does not require separate water service lines for
						irrigation or similar systems that are likely to impose continuous demands
						(e.g., lawn sprinkler or air conditioning systems), the following rule applies:
						estimate the continuous demand (in gallons per minute) for outlets/systems
						separately from the intermittent demand from the above fixtures, and add this
						amount to the demand of the fixtures (in gallons per minute).
Meter and meter yoke sizes shown in this table
						shall apply only to those jurisdictions or governmental units where local
						ordinances or community public water supply requirements do not prescribe
						specific sizes of meters or meter yokes. Where local ordinances or community
						public water supply requirements cover such sizing, those requirements shall be
						followed.
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table P - Demand at Individual Water Outlets

Current through Register Vol. 48, No. 28, July 12, 2024
Demand at Individual Water
								Outlets
Type of Outlet
Demand (g.p.m.)
Ordinary Lavatory Faucet
2.0
Self Closing Lavatory Faucet
2.5
Sink Faucet, 3/8" or 1/2"
4.5
Sink Faucet, 3/4"
6.0
Bath Faucet, 1/2"
5.0
Shower Head, 1/2"
5.0
Laundry Faucet, 1/2"
5.0
Ballcock in Water Closet Flush Tank
3.0
1" Flush Valve (25 psi flow pressure)
35.0
1" Flush Valve (15 psi flow pressure)
27.0
3/4" Flush Valve (15 psi flow pressure)
15.0
Drinking Fountain Jet
0.75
Dishwashing Machine (domestic)
4.0
Laundry Machine (8 to 16 pounds)
4.0
Aspirator (operating room or laboratory)
2.5
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix A - Plumbing Materials, Equipment, Use Restrictions and Applicable Standards › Table Q - Allowance in Equivalent Length of Pipe for Friction Loss in Valves and Fittings

Current through Register Vol. 48, No. 28, July 12, 2024
The following applies to all types of material approved for
					 potable water distribution:
Equivalent Feet of Pipe for Various
								Pipe Sizes
Valve or Fitting
1/2"
3/4"
1"
11/4"
1 1/2"
2"
2 1/2"
3"
45° ell (wrought)
0.5
0.5
1.0
1.0
2.0
2.0
3.0
4.0
90° ell (wrought)
0.5
1.0
1.0
2.0
2.0
2.0
2.0
3.0
Tee, Run (wrought)
0.5
0.5
0.5
0.5
1.0
1.0
2.0
-
Tee, Branch (wrought)
1.0
2.0
3.0
4.0
5.0
7.0
9.0
-
45° ell (cast)
0.5
1.0
2.0
2.0
3.0
5.0
8.0
11.0
90° ell (cast)
1.0
2.0
4.0
5.0
8.0
11.0
14.0
18.0
Tee, Run (cast)
0.5
0.5
0.5
1.5
1.0
2.0
2.0
2.0
Tee, Branch (cast)
2.0
3.0
5.0
7.0
9.0
12.0
16.0
20.0
Compression Stop
13.0
21.0
30.0
-
-
-
-
-
Globe Valve
-
-
-
53.0
66.0
90.0
-
-
Gate Valve
-
-
1.0
1.0
2.0
2.0
2.0
2.0
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION A - Air Gap Drawing #1

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Air
					 Gap.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION B - Air Gap Drawing #2

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Air
					 Gap.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION C - Battery of Fixtures

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Battery of
					 Fixtures.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION D - Branch

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of
					 "Branch.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION E - Branch Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Branch
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION F - Building Drain

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Building
					 Drain.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION G - Building Sub-Drain

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Building
					 Sub-Drain.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION H - Circuit Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Circuit
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION I - Common Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Common
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION J - Continuous Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Continuous
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION K - Dead End

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Dead
					 End.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION L - Drain

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of
					 "Drain.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION M - Fixture Drain

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Fixture
					 Drain.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION O - Grade

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of
					 "Grade.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION P - Horizontal Branch

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Horizontal
					 Branch.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION Q - Main Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Main
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION S - Relief Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Relief
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION U - Revent Pipe

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Revent
					 Pipe.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION V - Stack Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Stack
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION W - Trap

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of
					 "Trap.")
(Referenced in Section 890.120, Definition of "Trap
					 Seal.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION Y - Wet Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Wet
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION Z - Yoke Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.120, Definition of "Yoke
					 Vent.")
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION AA - Sleeves

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.180(c) and (d))
Click here to
					 view image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION BB - Buried Piping Parallel to Footing

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section
					 890.180(e) and
					 (f) )
Click here to
					 view image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix B - Illustrations for Subpart A › ILLUSTRATION CC - Individual Dry Vent

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section
					 890.120, Definition
					 of "Individual Dry Vent.")
Click here to
					 view image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix C - Illustrations for Subpart C › ILLUSTRATION A - Caulked Joints

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.320(a))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix C - Illustrations for Subpart C › ILLUSTRATION B - Flared Joints

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.320(e))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix C - Illustrations for Subpart C › ILLUSTRATION C - Positions of Application for Compression Type Joints

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.320(o)(1))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION A - Fixture Traps

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.410(a))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION B - Distance of Trap to Fixture

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.410(b))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION C - Types of Traps

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.410(d))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION D - Trap Cleanouts

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.410(g))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION E - Prohibited Traps

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.410(k))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION F - Underground Drainage

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.420(c))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION G - Concealed Piping

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.420(d))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix D - Illustrations for Subpart D › ILLUSTRATION H - Cleanout Clearance

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.420(j))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix E - Illustrations for Subpart E › ILLUSTRATION A - Grease Interceptor

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.510)
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix E - Illustrations for Subpart E › ILLUSTRATION B - Typical Grease Interceptor/Catch Basin

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.510)
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix E - Illustrations for Subpart E › ILLUSTRATION C - Interceptor/Separator Vents

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.510(a)(6))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix F - Illustrations for Subpart F › ILLUSTRATION A - Prohibited Fixtures

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.650(j)
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix F - Illustrations for Subpart F › ILLUSTRATION B - Circular Wash Sinks

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.680(d))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix F - Illustrations for Subpart F › ILLUSTRATION D - Commercial-Type Grinder

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.710(b))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix F - Illustrations for Subpart F › ILLUSTRATION E - Protective Guard

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.720(a))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix F - Illustrations for Subpart F › ILLUSTRATION F - Trap and Strainer

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.730)
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix G - Illustrations for Subpart G › ILLUSTRATION A - Cast Iron Soil Pipe Support #1

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.920)
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix G - Illustrations for Subpart G › ILLUSTRATION B - Cast Iron Soil Pipe Support #2

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.920)
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix H - Illustrations for Subpart H › ILLUSTRATION A - Indirect Waste Piping #1

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.1010(a))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix H - Illustrations for Subpart H › ILLUSTRATION B - Indirect Waste Piping #2

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.1010(a))
Click here to view
					 image
Illinois Administrative Code › Title 77 - PUBLIC HEALTH › Part 890 - ILLINOIS PLUMBING CODE › Subpart M - INSPECTIONS, TESTS, MAINTENANCE AND ADMINISTRATION › Appendix H - Illustrations for Subpart H › ILLUSTRATION C - Indirect Waste Piping #3

Current through Register Vol. 48, No. 28, July 12, 2024
(Referenced in Section 890.1010(a))
Click here to view
					 image