reglab/statecodes huggingface dataset:
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.304 - Monitoring and inspection

Current through June, 2024
(a) An owner or
					 operator required to have a leak detection system under § 265.301(a) must
					 record the amount of liquids removed from each leak detection system sump at
					 least once each week during the active life and closure period.
(b) After the final cover is installed, the
					 amount of liquids removed from each leak detection system sump must be recorded
					 at least monthly. If the liquid level in the sump stays below the pump
					 operating level for two consecutive months, the amount of liquids in the sumps
					 must be recorded at least quarterly. If the liquid level in the sump stays
					 below the pump operating level for two consecutive quarters, the amount of
					 liquids in the sumps must be recorded at least semi-annually. If at any time
					 during the postclosure care period the pump operating level is exceeded at
					 units on quarterly or semiannual recording schedules, the owner or operator
					 must return to monthly recording of amounts of liquids removed from each sump
					 until the liquid level again stays below the pump operating level for two
					 consecutive months.
(c) "Pump
					 operating level" is a liquid level proposed by the owner or operator and
					 approved by the director based on pump activation level, sump dimensions, and
					 level that avoids backup into the drainage layer and minimizes head in the
					 sump. The timing for submission and approval of the proposed "pump operating
					 level" will be in accordance with § 265.302(a).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.305-11-265.308 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.309 - Surveying and recordkeeping

Current through June, 2024
The owner or operator of a landfill must maintain the
						following items in the operating record required in § 265.73:
(a) On a map, the exact location and
					 dimensions, including depth, of each cell with respect to permanently surveyed
					 benchmarks; and
(b) The contents of
					 each cell and the approximate location of each hazardous waste type within each
					 cell.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.310 - Closure and post-closure care

Current through June, 2024
(a) At final
					 closure of the landfill or upon closure of any cell, the owner or operator must
					 cover the landfill or cell with a final cover designed and constructed to:
(1) Provide long-term minimization of
					 migration of liquids through the closed landfill;
(2) Function with minimum
					 maintenance;
(3) Promote drainage
					 and minimize erosion or abrasion of the cover;
(4) Accommodate settling and subsidence so
					 that the cover's integrity is maintained; and
(5) Have a permeability less than or equal to
					 the permeability of any bottom liner system or natural subsoils
					 present.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.311 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.312 - Special requirements for ignitable or reactive waste

Current through June, 2024
(a)
					 Except as provided in paragraph (b) of this section, and in § 265.316,
					 ignitable or reactive waste must not be placed in a landfill, unless the waste
					 and landfill meets all applicable requirements of 40 CFR part 268 , and:
(1) The resulting waste, mixture, or
					 dissolution of material no longer meets the definition of ignitable or reactive
					 waste under § 261.21 or § 261.23 of this chapter; and
(2) Section 265.17(b) is complied
					 with.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.313 - Special requirements for incompatible wastes

Current through June, 2024
Incompatible wastes, or incompatible wastes and
						materials, (see appendix V for examples) must not be placed in the same
						landfill cell, unless § 265.17(b) is complied with.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.314 - Special requirements for bulk and containerized liquids

Current through June, 2024
(a) The placement of bulk or
					 non-containerized liquid hazardous waste or hazardous waste containing free
					 liquids (whether or not sorbents have been added) in any landfill is
					 prohibited.
(b) Containers holding
					 free liquids must not be placed in a landfill unless:
(1) All free-standing liquid,
(i) has been removed by decanting, or other
					 methods,
(ii) has been mixed with
					 sorbent or solidified so that free-standing liquid is no longer observed;
					 or
(iii) had been otherwise
					 eliminated; or
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.315 - Special requirements for containers

Current through June, 2024
Unless they are very small, such as an ampule, containers
						must be either:
(a) At least 90
					 percent full when placed in the landfill; or
(b) Crushed, shredded, or similarly reduced
					 in volume to the maximum practical extent before burial in the
					 landfill.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart N - Landfills › Section 11-265.316 - Disposal of small containers of hazardous waste in overpacked drums (lab packs)

Current through June, 2024
Small containers of hazardous waste in overpacked drums
						(lab packs) may be placed in a landfill if the following requirements are
						met:
(a) Hazardous waste must be
					 packaged in non-leaking inside containers. The inside containers must be of a
					 design and constructed of a material that will not react dangerously with, be
					 decomposed by, or be ignited by the waste held therein. Inside containers must
					 be tightly and securely sealed. The inside containers must be of the size and
					 type specified in the Department of Transportation (DOT) hazardous materials
					 regulations (49 CFR parts 173, 178 and 179) , if those regulations specify a
					 particular inside container for the waste.
(b) The inside containers must be overpacked
					 in an open head DOT-specification metal shipping container (49 CFR parts 178
					 and 179) of no more than 416-liter (110 gallon) capacity and surrounded by, at
					 a minimum, a sufficient quantity of sorbent material, determined to be
					 nonbiodegradable in accordance with § 265.314(e), to completely sorb all
					 of the liquid contents of the inside containers. The metal outer container must
					 be full after it has been packed with inside containers and sorbent
					 material.
(c) The sorbent material
					 used must not be capable of reacting dangerously with, being decomposed by, or
					 being ignited by the contents of the inside containers in accordance with
					 § 265.17(b).
(d) Incompatible
					 wastes, as defined in § 260.10 of this chapter, must not be placed in the
					 same outside container.
(e)
					 Reactive waste, other than cyanide- or sulfide-bearing waste as defined in
					 § 261.23(a)(5) of this chapter, must be treated or rendered non-reactive
					 prior to packaging in accordance with paragraphs (a) through (d) of this
					 section. Cyanide- and sulfide-bearing reactive waste may be packaged in
					 accordance with paragraphs (a) through (d) of this section without first being
					 treated or rendered non-reactive.
(f) Such disposal is in compliance with the
					 requirements of 40 CFR part 268 . Persons who incinerate lab packs according to
					 the requirements in
					 40 CFR
					 268.42(c)(1) may use fiber
					 drums in place of metal outer containers. Such fiber drums must meet the DOT
					 specifications in
					 49 CFR
					 173.12 and be overpacked according to the
					 requirements in paragraph (b) of this section.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.340 - Applicability

Current through June, 2024
(a) The regulations of this subpart apply to
					 owners and operators of hazardous waste incinerators (as defined in §
					 260.10 of this chapter), except as § 265.1 provides otherwise.
(b) Integration of the MACT standards.
(1) Except as provided by paragraphs (b)(2)
					 and (b)(3) of this section, the standards of this part no longer apply when an
					 owner or operator demonstrates compliance with the maximum achievable control
					 technology (MACT) requirements of part 63, subpart EEE, of this chapter by
					 conducting a comprehensive performance test and submitting to the director a
					 Notification of Compliance under §§ 63.1207(j) and 63.1210(d) of this
					 chapter documenting compliance with the requirements of part 63, subpart EEE,
					 of this chapter.
(2) The following
					 requirements continue to apply even when the owner or operator has demonstrated
					 compliance with the MACT requirements of 40 C.F.R. part 63 , subpart EEE:
					 40
					 C.F.R. section 265.351 (closure), as
					 incorporated and amended in this chapter, and the applicable requirements of 40
					 C.F.R. part 265 , subparts A to H, BB, and CC, as incorporated and amended in
					 this chapter.
(3) Section 265.345
					 generally prohibiting burning of hazardous waste during startup and shutdown
					 remains in effect if you elect to comply with § 270.235(b)(1)(i) of this
					 chapter to minimize emissions of toxic compounds from startup and
					 shutdown.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.341 - Waste analysis

Current through June, 2024
In addition to the waste analyses required by §
						265.13, the owner or operator must sufficiently analyze any waste which he has
						not previously burned in his incinerator to enable him to establish steady
						state (normal) operating conditions (including waste and auxiliary fuel feed
						and air flow) and to determine the type of pollutants which might be emitted.
						At a minimum, the analysis must determine:
(a) Heating value of the waste;
(b) Halogen content and sulfur content in the
					 waste; and
(c) Concentrations in
					 the waste of lead and mercury, unless the owner or operator has written,
					 documented data that show that the element is not present.
[Comment: As required by § 265.73, the owner or
						operator must place the results from each waste analysis, or the documented
						information, in the operating record of the facility.]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.342-11-265.344 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.345 - General operating requirements

Current through June, 2024
During start-up and shut-down of an incinerator, the
						owner or operator must not feed hazardous waste unless the incinerator is at
						steady state (normal) conditions of operation, including steady state operating
						temperature and air flow.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.346 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.347 - Monitoring and inspections

Current through June, 2024
The owner or operator must conduct, as a minimum, the
						following monitoring and inspections when incinerating hazardous waste:
(a) Existing instruments which relate to
					 combustion and emission control must be monitored at least every 15 minutes.
					 Appropriate corrections to maintain steady state combustion conditions must be
					 made immediately either automatically or by the operator. Instruments which
					 relate to combustion and emission control would normally include those
					 measuring waste feed, auxiliary fuel feed, air flow, in-ciner-a-tor
					 temperature, scrubber flow, scrubber pH, and relevant level
					 -controls.
(b) The complete
					 incinerator and associated equipment (pumps, valves, conveyors, pipes, etc.)
					 must be inspected at least daily for leaks, spills, and fugitive emissions, and
					 all emergency shutdown controls and system alarms must be checked to assure
					 proper operation.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.348-11-265.350 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.351 - Closure

Current through June, 2024
At closure, the owner or operator must remove all
						hazardous waste and hazardous waste residues (including but not limited to ash,
						scrubber -waters, and scrubber sludges) from the incinerator.
[Comment: At closure, as throughout the operating period,
						unless the owner or operator can demonstrate, in accordance with §
						261.3(d) of this chapter, that the residue removed from his incinerator is not
						a hazardous waste, the owner or operator becomes a generator of hazardous waste
						and must manage it in accordance with all applicable requirements of parts 262
						through 266 of this chapter.]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.352 - Interim status incinerators burning particular hazardous wastes

Current through June, 2024
(a) Owners or operators of incinerators
					 subject to this subpart may burn EPA Hazardous Wastes F020, F021, F022, F023,
					 F026, or F027 if they receive a certification from the director that they can
					 meet the performance standards of subpart O of part 264 when they burn these
					 wastes.
(b) The following standards
					 and procedures will be used in determining whether to certify an incinerator:
(1) The owner or operator will submit an
					 application to the director containing applicable information in §§
					 270.19 and 270.62 demonstrating that the incinerator can meet the performance
					 standards in subpart O of part 264 when they burn these wastes.
(2) The director will issue a tentative
					 decision as to whether the incinerator can meet the performance standards in
					 subpart O of part 264. Notification of this tentative decision will be provided
					 by newspaper advertisement and radio broadcast in the jurisdiction where the
					 incinerator is located. The director will accept comment on the tentative
					 decision for 60 days. The director also may hold a public hearing upon request
					 or at his discretion.
(3) After the
					 close of the public comment period, the director will issue a decision whether
					 or not to certify the incinerator.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart O - Incinerators › Section 11-265.353-11-265.369 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.370 - Other thermal treatment

Current through June, 2024
The regulations in this subpart apply to owners or
						operators of facilities that thermally treat hazardous waste in devices other
						than enclosed devices using controlled flame combustion, except as § 265.1
						provides otherwise. Thermal treatment in enclosed devices using controlled
						flame combustion is subject to the requirements of subpart O if the unit is an
						incinerator, and subpart H of part 266, if the unit is a boiler or an
						industrial furnace as defined in § 260.10.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.371-11-265.372 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.373 - General operating requirements

Current through June, 2024
Before adding hazardous waste, the owner or operator must
						bring his thermal treatment process to steady state (normal) conditions of
						operation-including steady state operating temperature-using auxiliary fuel or
						other means, unless the process is a non-continuous (batch) thermal treatment
						process which requires a complete thermal cycle to treat a discrete quantity of
						hazardous waste.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.374 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.375 - Waste analysis

Current through June, 2024
In addition to the waste analyses required by §
						265.13, the owner or operator must sufficiently analyze any waste which he has
						not previously treated in his thermal process to enable him to establish steady
						state (normal) or other appropriate (for a non-continuous process) operating
						conditions (including waste and auxiliary fuel feed) and to determine the type
						of pollutants which might be emitted. At a minimum, the analysis must
						determine:
(a) Heating value of the
					 waste;
(b) Halogen content and
					 sulfur content in the waste; and
(c) Concentrations in the waste of lead and
					 mercury, unless the owner or operator has written, documented data that show
					 that the element is not present.
[Comment: As required by § 265.73, the owner or
						operator must place the results from each waste analysis, or the documented
						information, in the operating record of the facility.]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.376 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.377 - Monitoring and inspections

Current through June, 2024
(a) The owner or
					 operator must conduct, as a minimum, the following monitoring and inspections
					 when thermally treating hazardous waste:
(1)
					 Existing instruments which relate to temperature and emission control (if an
					 emission control device is present) must be monitored at least every 15
					 minutes. Appropriate corrections to maintain steady state or other appropriate
					 thermal treatment conditions must be made immediately either automatically or
					 by the operator. Instruments which relate to temperature and emission control
					 would normally include those measuring waste feed, auxiliary fuel feed,
					 treatment process temperature, and relevant process flow and level
					 controls.
(2) The stack plume
					 (emissions), where present, must be observed visually at least hourly for
					 normal appearance (color and opacity). The operator must immediately make any
					 indicated operating corrections necessary to return any visible emissions to
					 their normal appearance.
(3) The
					 complete thermal treatment process and associated equipment (pumps, valves,
					 conveyors, pipes, etc.) must be inspected at least daily for leaks, spills, and
					 fugitive emissions, and all emergency shutdown controls and system alarms must
					 be checked to assure proper operation.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.378-11-265.380 - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.381 - Closure

Current through June, 2024
At closure, the owner or operator must remove all
						hazardous waste and hazardous waste residues (including, but not limited to,
						ash) from the thermal treatment process or equipment.
[Comment: At closure, as throughout the operating period,
						unless the owner or operator can demonstrate, in accordance with § 261.3
						(c) or (d) of this chapter, that any solid waste removed from his thermal
						treatment process or equipment is not a hazardous waste, the owner or operator
						becomes a -generator of hazardous waste and must manage it in accordance with
						all applicable requirements of parts 262, 263, and 265 of this
						chapter.]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.382 - Open burning; waste explosives

Current through June, 2024
Open burning of hazardous waste is prohibited except for
						the open burning and detonation of waste explosives. Waste explosives include
						waste which has the potential to detonate and bulk military propellants which
						cannot safely be disposed of through other modes of treatment. Detonation is an
						explosion in which chemical transformation passes through the material faster
						than the speed of sound (0.33 kilometers/second at sea level). Owners or
						operators choosing to open burn or detonate waste explosives must do so in
						accordance with the following table and in a manner that does not threaten
						human health or the environment.
Pounds of waste explosives or propellants
Minimum distance from open burning or detonation
								  to the property of others
0 to 100
204 meters (670 feet).
101 to 1,000
380 meters (1,250 feet).
1,001 to 10,000
530 meters (1,730 feet).
10,001 to 30,000
690 meters (2,260 feet).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart P - Thermal Treatment › Section 11-265.383 - Interim status thermal treatment devices burning particular hazardous waste

Current through June, 2024
(a) Owners or
					 operators of thermal treatment devices subject to this subpart may burn EPA
					 Hazardous Wastes F020, F021, F022, F023, F026, or F027 if they receive a
					 certification from the director that they can meet the performance standards of
					 subpart O of part 264 when they burn these wastes.
(b) The following standards and procedures
					 will be used in determining whether to certify a thermal treatment unit:
(1) The owner or operator will submit an
					 application to the director containing the applicable information in
					 §§ 270.19 and 270.62 demonstrating that the thermal treatment unit
					 can meet the performance standard in subpart O of part 264 when they burn these
					 wastes.
(2) The director will issue
					 a tentative decision as to whether the thermal treatment unit can meet the
					 performance standards in subpart O of part 264. Notification of this tentative
					 decision will be provided by newspaper advertisement and radio broadcast in the
					 jurisdiction where -the thermal treatment device is located. The director will
					 accept comment on the tentative decision for 60 days. The director also may
					 hold a public hearing upon request or at his discretion.
(3) After the close of the public comment
					 period, the director will issue a decision whether or not to certify the
					 thermal treatment unit.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart Q - Chemical, Physical, and Biological Treatment › Section 11-265.400 - Applicability

Current through June, 2024
The regulations in this subpart apply to owners and
						operators of facilities which treat hazardous wastes by chemical, physical, or
						biological methods in other than tanks, surface impoundments, and land
						treatment facilities, except as § 265.1 provides otherwise. Chemical,
						physical, and biological treatment of hazardous waste in tanks, surface
						impoundments, and land treatment facilities must be conducted in accordance
						with subparts J, K, and M, respectively.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart Q - Chemical, Physical, and Biological Treatment › Section 11-265.401 - General operating requirements

Current through June, 2024
(a) Chemical,
					 physical, or biological treatment of hazardous waste must comply with §
					 265.17(b).
(b) Hazardous wastes or
					 treatment reagents must not be placed in the treatment process or equipment if
					 they could cause the treatment process or equipment to rupture, leak, corrode,
					 or otherwise fail before the end of its intended life.
(c) Where hazardous waste is continuously fed
					 into a treatment process or equipment, the process or equipment must be
					 equipped with a means to stop this inflow (e.g., a waste feed cut-off system or
					 by-pass system to a standby containment device).
[Comment: These systems are intended to be used in the
						event of a malfunction in the treatment process or equipment.]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart Q - Chemical, Physical, and Biological Treatment › Section 11-265.402 - Waste analysis and trial tests

Current through June, 2024
(a) In addition to
					 the waste analysis required by § 265.13, whenever:
(1) A hazardous waste which is substantially
					 different from waste previously treated in a treatment process or equipment at
					 the facility is to be treated in that process or equipment, or
(2) A substantially different process than
					 any previously used at the facility is to be used to chemically treat hazardous
					 waste;
the owner or operator must, before treating the different
						waste or using the different process or equipment:
(i) Conduct waste analyses and trial
					 treatment tests (e.g., bench scale or pilot plant scale tests); or
(ii) Obtain written, documented information
					 on similar treatment of similar waste under similar operating conditions;
to show that this proposed treatment will meet all
						applicable requirements of § 265.401 (a) and (b).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart Q - Chemical, Physical, and Biological Treatment › Section 11-265.403 - Inspections

Current through June, 2024
(a) The owner or operator of a treatment
					 facility must inspect, where present:
(1)
					 Discharge control and safety equipment (e.g., waste feed cut-off systems,
					 bypass systems, drainage systems, and pressure relief systems) at least once
					 each operating day, to ensure that it is in good working order;
(2) Data gathered from monitoring equipment
					 (e.g., pressure and temperature gauges), at least once each operating day, to
					 ensure that the treatment process or equipment is being operated according to
					 its design;
(3) The construction
					 materials of the treatment process or equipment, at least weekly, to detect
					 corrosion or leaking of fixtures or seams; and
(4) The construction materials of, and the
					 area immediately surrounding, discharge confinement structures (e.g., dikes),
					 at least weekly, to detect erosion or obvious signs of leakage (e.g., wet spots
					 or dead vegetation).
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart Q - Chemical, Physical, and Biological Treatment › Section 11-265.404 - Closure

Current through June, 2024
At closure, all hazardous waste and hazardous waste
						residues must be removed from treatment processes or equipment, discharge
						control equipment, and discharge confinement structures.
[Comment: At closure, as throughout the operating period,
						unless the owner or operator can demonstrate, in accordance with § 261.3
						(c) or (d) of this chapter, that any solid waste removed from his treatment
						process or equipment is not a hazardous waste, the owner or operator becomes a
						generator of hazardous waste and must manage it in accordance with all
						applicable requirements of parts 262, 263, and 265 of this
						chapter.]
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart Q - Chemical, Physical, and Biological Treatment › Section 11-265.405 - Special requirements for ignitable or reactive waste

Current through June, 2024
(a)
					 Ignitable or reactive waste must not be placed in a treatment process or
					 equipment unless:
(1) The waste is treated,
					 rendered, or mixed before or immediately after placement in the treatment
					 process or equipment so that (i) the resulting waste, mixture, or dissolution
					 of material no longer meets the definition of ignitable or reactive waste under
					 § 261.21 or 261.23 of this chapter, and (ii) § 265.17(b) is complied
					 with; or
(2) The waste is treated
					 in such a way that it is protected from any material or conditions which may
					 cause the waste to ignite or react.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart Q - Chemical, Physical, and Biological Treatment › Section 11-265.406 - Special requirements for incompatible wastes

Current through June, 2024
(a)
					 Incompatible wastes, or incompatible wastes and materials, (see appendix V for
					 examples) must not be placed in the same treatment process or equipment, unless
					 § 265.17(b) is complied with.
(b) Hazardous waste must not be placed in
					 unwashed treatment equipment which previously held an incompatible waste or
					 material, unless § 265.17(b) is complied with.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart R - Underground Injection › Section 11-265.430 - Applicability

Current through June, 2024
Underground injection of hazardous waste is prohibited in
						the State of Hawaii.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart S-V - Reserved

Current through June, 2024
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart W - Drip Pads › Section 11-265.440 - Applicability

Current through June, 2024
(a) The requirements of this subpart apply to
					 owners and operators of facilities that use new or existing drip pads to convey
					 treated wood drippage, precipitation, and/or surface water run-off to an
					 associated collection system. Existing drip pads are those constructed before
					 December 6, 1990 for HSWA drip pads and June 18, 1994 for non-HSWA drip pads
					 and those for which the owner or operator has a design and has entered into
					 binding financial or other agreements for construction prior to December 6,
					 1990 for HSWA drip pads and June 18, 1994 for non-HSWA drip pads. All other
					 drip pads are new drip pads. The requirement at § 265.443(b)(3) to install
					 a leak collection system applies only to those drip pads that are constructed
					 after December 24, 1992 for HSWA drip pads and June 18, 1994 for non-HSWA drip
					 pads except for those constructed after December 24, 1992 for HSWA drip pads
					 and June 18, 1994 for non-HSWA drip pads for which the owner or operator has a
					 design and has entered into binding financial or other agreements for
					 construction prior to December 24, 1992 for HSWA drip pads and June 18, 1994
					 for non-HSWA drip pads.
(b) The
					 owner or operator of any drip pad that is inside or under a structure that
					 provides protection from precipitation so that neither run-off nor run-on is
					 generated is not subject to regulation under § 265.443(e) or §
					 265.443(f), as appropriate.
(c) The
					 requirements of this subpart are not applicable to the management of infrequent
					 and incidental drippage in storage yards provided that:
(1) The owner or operator maintains and
					 complies with a written contingency plan that describes how the owner or
					 operator will respond immediately to the discharge of such infrequent and
					 incidental drippage. At a minimum, the contingency plan must describe how the
					 facility will do the following:
(i) Clean up
					 the drippage;
(ii) Document the
					 cleanup of the drippage;
(iii)
					 Retain documents regarding cleanup for three years; and
(iv) Manage the contaminated media in a
					 manner consistent with Federal regulations.
Hawaii Administrative Rules › Title 11 - DEPARTMENT OF HEALTH › Subtitle 1 - GENERAL DEPARTMENTAL PROVISIONS › Chapter 265.1 - HAZARDOUS WASTE MANAGEMENT: INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Part 265 - INTERIM STATUS STANDARDS FOR OWNERS AND OPERATORS OF HAZARDOUS WASTE TREATMENT, STORAGE, AND DISPOSAL FACILITIES › Subpart W - Drip Pads › Section 11-265.441 - Assessment of existing drip pad integrity

Current through June, 2024
(a) For each
					 existing drip pad as defined in § 265.440, the owner or operator must
					 evaluate the drip pad and determine that it meets all of the requirements of
					 this subpart, except the requirements for liners and leak detection systems of
					 § 265.443(b). No later than the effective date of this rule, the owner or
					 operator must obtain and keep on file at the facility a written assessment of
					 the drip pad, reviewed and certified by a qualified Professional Engineer that
					 attests to the results of the evaluation. The assessment must be reviewed,
					 updated, and re-certified annually until all upgrades, repairs, or
					 modifications necessary to achieve compliance with all the standards of §
					 265.443 are complete. The evaluation must document the extent to which the drip
					 pad meets each of the design and operating standards of § 265.443, except
					 the standards for liners and leak detection systems, specified in §
					 265.443(b).
(b) The owner or
					 operator must develop a written plan for upgrading, repairing, and modifying
					 the drip pad to meet the requirements of § 265.443(b), and submit the plan
					 to the director no later than 2 years before the date that all repairs,
					 upgrades, and modifications are complete. This written plan must describe all
					 changes to be made to the drip pad in sufficient detail to document compliance
					 with all the requirements of § 265.443. The plan must be reviewed and
					 certified by a qualified Professional Engineer.
(c) Upon completion of all repairs and
					 modifications, the owner or operator must submit to the director, the as-built
					 drawings for the drip pad together with a certification by a qualified
					 Professional Engineer attesting that the drip pad conforms to the
					 drawings.
(d) If the drip pad is
					 found to be leaking or unfit for use, the owner or operator must comply with
					 the provisions of § 265.443(m) of this subpart or close the drip pad in
					 accordance with § 265.445 of this subpart.