reglab/statecodes huggingface dataset:
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Section 570.204 - Component Design Criteria

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Settling Basin
1) Basin volume shall be 4.5
				cubic feet per 100 square feet of area contributing runoff plus an additional
				10% volume safety factor.
2) Ramp
				slope shall not be steeper than 12:1 (H:V), with 15:1 being
				preferred.
3) Basin depth shall be
				2 to 4 feet.
4) Settling basins
				located where groundwater tables rise to within 2 feet of the surface shall be
				provided with foundation drainage.
5) The settling basin riser pipe should be 18
				to 24 inches in diameter with vertical slots 1 inch by 4 inches high spaced at
				120° intervals around the pipe. There should be 6 slots per foot of height
				with the bottom row of slots even with the settling basin floor. To avoid
				excess clogging, offset or locate the riser pipe as far as practicable from the
				inlet of the settling basin and attach 3/4 inch mesh expanded metal screen
				cover over the top of the riser pipe. Provide a 3/4 inch mesh expanded metal
				screen ahead of the riser pipe so that all runoff entering the riser pipe must
				first cross the screen. Refer to Appendix I for a diagram.
6) The settling basin ramp, floor, end-wall,
				and side-walls should be designed, constructed, and maintained to withstand
				normal operation practices involving power machinery.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Section 570.205 - Specifications for Vegetation Establishment

Current through Register Vol. 48, No. 28, July 12, 2024
The following specifications shall apply to all runoff field
				  application systems:
a) All trees,
				stumps, brush, rocks, and similar materials that can interfere with installing
				the field application area shall be removed. The materials shall be disposed of
				in a manner that is consistent with standards for maintaining and improving the
				quality of the environment and with proper functioning of the field application
				area.
b) The field application area
				shall be shaped to the grade and dimensions shown in the plan or as staked in
				the field. If necessary, topsoil shall be stockpiled and spread to the required
				grade and thickness. Excess spoil shall be disposed of in areas where it does
				not interfere with the required flow characteristics of the field application
				area.
c) All areas disturbed during
				construction shall be vegetated.
d)
				To aid in the establishment of vegetation, feedlot runoff shall be prevented
				from entering the field application area through the use of temporary
				diversions until vegetation is established to a minimum height of 4 inches and
				90 percent ground cover.
e)
				Immediately prior to seedbed preparation, apply the following minimum amounts
				of starter fertilizer per acre:
Nitrogen (N) - 120 pounds of actual nitrogen
Phosphorus (P) - 120 pounds of
				  P2O5
Potassium (K) - 120 pounds K2O
f) Apply limestone, if necessary,
				for the species to be grown.
g)
				Incorporate the required lime and fertilizer and prepare a firm seedbed to a
				depth of 3 inches. The seedbed shall be free from clods, stones, or other
				debris that might hamper proper seeding.
h) Select one of the following mixtures and
				seed according to the rate shown:
1) Reed
				canarygrass - 25 lbs./acre
2)
				Mixture reed canarygrass and tall fescue - 15 lbs./acre of each
				species.
3) Use of species other
				than canarygrass or tall fescue shall be considered an innovative
				design.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Section 570.206 - Operation and Maintenance Criteria

Current through Register Vol. 48, No. 28, July 12, 2024
The following operation and maintenance criteria shall apply
				  as best management practices to all runoff field application systems:
a) Protect the field application area from
				damage by farm equipment, traffic and livestock. LIVESTOCK MUST BE FENCED OUT
				OF THE RUNOFF FIELD APPLICATION AREA.
b) Avoid damaging the field application area
				with herbicides.
c) Fertilize the
				field application area when necessary to establish growth.
d) Harvest when the forage is at the proper
				state of maturity for maximum quality feed. No harvesting shall occur after
				September 15. Use the following guide for cutting stages and minimum cutting
				height for the species seeded:
1) Reed
				canarygrass - cut at early boot stage to heading - minimum cutting height 6
				inches.
2) Reed canarygrass - tall
				fescue mixture - cut at early boot to heading - minimum cutting height 6
				inches.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Section 570.207 - Innovative Designs

Current through Register Vol. 48, No. 28, July 12, 2024
It is strongly suggested that any operator contemplating use
				  of runoff field application systems not designed, constructed or maintained in
				  accordance with the design criteria contained herein receive PRIOR approval
				  from the Agency for such system. The Agency will approve innovative designs
				  should the operator present clear, cogent and convincing proof that the
				  technique has a reasonable and substantial chance for meeting the requirements
				  of the Act and Regulations, based upon conservative engineering principles. For
				  further information contact the Division of Water Pollution Control - Permit
				  Section in Springfield (217/782-0610), or the Agency regional office in your
				  area. Examples of innovative designs are:
a) Settling basin designed at less than 4.5
				cubic feet per 100 square feet of drainage area.
b) Settling channel used instead of settling
				basin.
c) Use of terraces for field
				application area.
d) Riser pipe
				designed differently than provided herein.
e) Use of vegetation other than tall fescue
				or reed canarygrass.
f) Greater
				than 300 animal units on feedlot.
g) Distribution manifold designed for full
				pipe flow driven by gravity.
h) Not
				providing a junction box.
i)
				Application of materials other than feedlot runoff, rainfall, or milking parlor
				washwaters to the runoff field application system (for example silage leachate,
				sewage, pesticides, oil, refuse).
j) Use of field application area smaller than
				provided herein or with less than 2 hours contact time.
k) Use of soils on runoff field application
				area with infiltration rates outside the range of 1.0 to 6.0 inches per
				hour.
l) Use of field application
				area widths greater than 100 feet.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Appendix A - Design Procedure Outlined

Current through Register Vol. 48, No. 28, July 12, 2024
DESIGN PROCEDURE OUTLINED
1. Collect Site Specific Data
a. Types and Areas (sft) contributing
				  drainage
b. Slope of Field Application Area (FAA) -
				  Appendix D
c. Soil Infiltration Rate (SI) of FAA - Appendix
				  C
2. Calculate Runoff Volume and Total Drainage Area
Working Table in Appendix B
3. Settling Basin Design
4.5 cft/100 sft of drainage area + 10% extra
				  volume
Dimensions from Appendix I
4. Field Application Area Design
FAA = (VR x 12)/((2 x SI) - 1.69 ) (square
				  feet)
Dimensions from Appendix E
5. Calculate Flow onto Field Application Area
Flows from Appendix G
or
Qf = (.0026) (FAA) (gpm)
6. Effluent Transport System Design
Recommended Designs from Appendix F
7. Junction Box Design
Recommended Design from Appendix H
8. Distribution Manifold Design
Recommended Designs from Appendix H
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Appendix B - Procedure to Estimate Volume of Feedlot Runoff*

Current through Register Vol. 48, No. 28, July 12, 2024
Procedure to Estimate Volume of Feedlot
				  Runoff*
(A)
X
(B)
=
(C)
Type of Drainage Area
Area
(Square feet)
Multiplication Factor
(feet)
Runoff Volume
(Cubic feet)
Roof
0.1408
Feedlot
a.
Paved or Concrete
0.0991
b.
Earthen
0.0748
1. Feedlot Runoff Volume = Total of Column (C)
				  (cubic feet).
2.
Click here to view
				  image
3. Design Runoff Volume (VR) = 1 + 2 (cubic feet).
Use VR (cubic feet) for designing field
				  application area.
4. Total area (sum of column A in square feet)
				  divided by 100 is used to design settling basin.
5. To convert Runoff Volume (VR) from units of
				  cubic feet into equivalent units of gallons, multiply cubic feet by 7.481
				  gallons/cubic feet.
* Multiplication factor corresponds to Q of the
				  U.S.D.A. - S.C.S. runoff equation.
Storm event (I) is 1-year, 2-hour storm of 1.69
				  inches.
Curve numbers (CN) are 100-roof; 95-paved;
				  91-earthen.
S = (1000/CN) - 10
Click here to view
				  image
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Appendix D - Procedure to Determine Slopes

Current through Register Vol. 48, No. 28, July 12, 2024
Slope must be determined at the site of the runoff field
				  application area to use Appendix E. Many methods are available to determine
				  slope but all methods are based on the fact:
Click here to view
				  image
where [DELTA] means "the change in."
The following procedure can be used to determine
				  slope.
1. Obtain a 40 foot length of string or wire with
				  a 25 foot section marked off (if you use nylon, measure the 25 feet with a
				  steel tape because nylon stretches when pulled taut); carpenter's line level
				  from a hardware store; a stake; a rod about 8 feet long (an 8 ft. 2 x 4 works
				  well); a tape measure; a notebook and an assistant.
2. Set up your notes as follows:
Site
run (ft)
rise (ft)
1
0
0
1-2
25
2-3
25
3-4
25
etc.
Refer to Figure 1.
3. Stake one end of the string at point 1 and
				  attach the other end to the rod so that there is 25 feet between the stake and
				  rod, and the string can slide up and down the rod. With the string taut, level
				  the string in the center using the line level and record the rise at point 2 in
				  your notes by measuring the string height at the rod.
4. Repeat step 3 all the way down the field and
				  calculate the slope by:
Click here to view
				  image
5. Use the % slope for Appendix E.
Figure 1:
Field set-up for determining
				  slope
Click here to view
				  image
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Appendix E - Tables to Determine Dimensions of Field Application Areas

Current through Register Vol. 48, No. 28, July 12, 2024
Tables to Determine Dimensions of Field
				  Application Areas
Table 1: How to Use Table 2
Click here to view
				  image
1. Enter at slope of field application area from Appendix
				  D.
2. Read down column and find corresponding length of field
				  application area.
3. Continue down column stopping at area closest to that
				  previously calculated for your site.
4. Read left to find width of field application area.
Table 2:
Runoff Field Application Areas (square feet)
Slope (%) Length (ft)
0.5
300
0.7
375
1.0
425
1.5
525
2.0
600
3.0
750
4.0
800
Width (ft)
20
6,000
7,500
8,500
10,500
12,000
15,000
17,000
25
7,500
9,375
10,625
13,125
15,000
18,750
21,250
30
9,000
11,250
12,750
15,750
18,000
22,500
25,500
35
10,500
13,125
14,875
18,375
21,000
26,250
29,750
40
12,000
15,000
17,000
21,000
24,000
30,000
34,000
45
13,500
16,875
19,125
23,625
27,000
33,750
38,250
50
15,000
18,750
21,250
26,350
30,000
37,500
42,500
55
16,500
20,625
23,375
28,875
33,000
41,250
46,750
60
18,000
22,500
25,500
31,500
36,000
45,000
51,000
65
19,500
24,375
27,625
34,125
39,000
48,750
55,250
70
21,000
26,250
29,750
36,750
42,000
52,500
59,500
75
22,500
28,125
31,875
39,375
45,000
56,250
63,750
80
24,000
30,000
34,000
42,000
48,000
60,000
68,000
85
25,500
31,875
36,125
44,625
51,000
63,750
72,250
90
27,000
33,750
38,250
47,250
54,000
67,500
76,500
95
28,500
35,625
40,375
49,875
57,000
71,250
80,750
100
30,000
37,500
42,500
52,500
60,000
75,000
85,000
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Appendix F - Recommend Effluent Transport Systems Designs

Current through Register Vol. 48, No. 28, July 12, 2024
Type
Maximum Flow* Qf (gpm)
Minimum Slope (%)
Design Velocity (fps)
Materials
Dimensions
Pipe
179
0.5
2
PVC
6" diam
332
0.4
2
PVC
8" diam
Open Channel
Rectangular
224
0.33
2
Concrete, Wood, Asphalt,
							 Aluminum
6" x 6"
Trapazoidal
224
0.37
2
Concrete, Wood, Asphalt,
							 Aluminum
b = 6"
S = 2:1
d = 3'
Mannings Equation with n = 0.013
Click here to view
				  image
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Appendix H - Recommended Distribution Manifold Designs

Current through Register Vol. 48, No. 28, July 12, 2024
Type1
Maximum Flow Qf
							 (gpm)
Slope
Dimensions
Materials2
Weirs3
Diagram
1/2 Pipe
150
level
8" diam.
PVC
30° V-notch
A
225
level
10"
PVC
30° V-notch
B
Box Trough
225
level
6" x 6"
2" x 8" dimension lumber
30° V-notch
C
Aluminum Guttering
(Size with the Box Trough Criteria Above)
Click here to view
				  image
Click here to view
				  image
CROSS-SECTION
				  VIEW
Click here to view
				  image
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 570 - DESIGN AND MAINTENANCE CRITERIA REGARDING RUNOFF FIELD APPLICATION SYSTEMS › Subpart B - DESIGN CRITERIA › Appendix I - Diagram of Setting Basin Components

Current through Register Vol. 48, No. 28, July 12, 2024
Click here to view
				  image
SETTLING BASIS DIMENSIONS
				  (feet)
Total Volume = V1 +
							 V2 (cubic feet)
Total Length = L1 +
							 L2
V1 = 1/2
							 bhL1
Pick: h - 2 to 4 feet
V2 = Total Volume -
							 V1
b - 8 to 15 feet recommended
slope - 12 to 15 recommended
Click here to view
				  image
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.100 - Introduction

Current through Register Vol. 48, No. 28, July 12, 2024
This Part 580 contains Illinois Environmental Protection Agency
				(Illinois EPA or Agency) rules for the procedure that owners or operators of
				livestock waste handling facilities that release livestock waste from the
				livestock waste handling facility or transportation equipment must follow to
				satisfy their obligation under Section 18(a) of the Livestock Management
				Facilities Act [510 ILCS
				77/18(a) ] and Section 4(h) of the
				Environmental Protection Act [415
				ILCS 5/4(h) ], and the procedure that
				the Illinois EPA will follow to distribute or provide access to that
				information.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.101 - Scope

Current through Register Vol. 48, No. 28, July 12, 2024
This Part 580 contains the procedures for reporting releases
				and the procedures for distribution of that information. These regulations are
				cumulative with conditions, effluent limitations and other requirements
				established under the Illinois Environmental Protection Act [415 ILCS 5 ],
				regulations of the Illinois Pollution Control Board, the federal Water
				Pollution Control Act (
				33 U.S.C.
				1251 ), as now or hereafter amended, and
				regulations pursuant thereto, including terms and conditions of National
				Pollutant Discharge Elimination System (NPDES) permits issued by the Agency and
				penalties under Title XII of the Environmental Protection Act [415 ILCS 5/Title
				XII].
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.102 - Applicability

Current through Register Vol. 48, No. 28, July 12, 2024
The regulations in this Part 580 apply to the owners or
				operators of livestock waste handling facilities that release livestock waste
				from the livestock waste handling facility or transportation equipment as those
				terms are defined in Section
				580.104,
				subject to the provisions of Section
				580.105(b).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.103 - Purpose

Current through Register Vol. 48, No. 28, July 12, 2024
The purpose of this Part 580 is to promote the prompt and
				effective notification of releases of livestock waste to minimize damage to the
				environment and to protect the health of our citizens.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.105 - Method of Reporting a Release of Livestock Waste

Current through Register Vol. 48, No. 28, July 12, 2024
a) An owner or operator of a livestock waste
			 handling facility shall report any release of livestock waste from the
			 livestock waste handling facility or from the transport of livestock waste by
			 means of transportation equipment within 24 hours after the discovery of the
			 release. Reports of releases to surface waters, including to sinkholes, drain
			 inlets, broken subsurface drains or other conduits to groundwater or surface
			 waters, shall be made upon discovery of the release, except when such immediate
			 notification will impede the owner's or operator's response to correct the
			 cause of the release or to contain the livestock waste, in which case the
			 report shall be made as soon as possible but no later than 24 hours after
			 discovery.
b) Reporting shall not
			 be required in the case of a release of less than 25 gallons that is not
			 released to the waters of the State or from a controlled and recovered release
			 during field application. [510 ILCS
			 77/18(a) ]
c) The report required under subsection (a)
			 shall be given to the Illinois Environmental Protection Agency through the
			 Illinois Emergency Management Agency by calling:
1-800-782-7860
1-217-782-7860
(if calling from outside Illinois).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.106 - Contents of Report

Current through Register Vol. 48, No. 28, July 12, 2024
The report required under Section
				580.105(a)
				must include, as a minimum, each of the following to the extent that it is
				known at the time of the report:
a)
			 name and telephone number of the person reporting the release;
b) county, distance and direction from
			 nearest town, village or municipality of the release;
c) an estimate of the quantity in gallons
			 that was released, and an estimate of the flow rate if the release is
			 ongoing;
d) area into which the
			 release occurred (field, ditch, stream, or other description) and apparent
			 environmental impacts of the release;
e) time and duration of the
			 release;
f) the names and telephone
			 numbers of persons who may be contacted for further information;
g) dangers to health or the environment
			 resulting from the release;
h)
			 actions taken to respond to, contain and mitigate the release; and
i) name of facility and mailing
			 address.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.107 - Reporting of Releases to Groundwater

Current through Register Vol. 48, No. 28, July 12, 2024
If an owner or operator of a lagoon required to implement
				groundwater monitoring under 35 Ill. Adm. Code
				506.204(d)
				submits a report to the Department of a proposed response action required under
				8 Ill. Adm. Code
				900.611,
				the owner or operator shall submit that report to the Agency at the same
				time.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.200 - Distribution of Information

Current through Register Vol. 48, No. 28, July 12, 2024
a)
			 Reports under this Part are required by Section 18(a) of the Livestock
			 Management Facilities Act [
			 510 ILCS
			 77/18(a) ] and Section 4(h) of the
			 Environmental Protection Act [
			 415
			 ILCS 5/4(h) ].
b) All reports under Sections
			 580.105
			 and
			 580.300
			 will be forwarded to the Department by the Agency.
c) All reports under this Part indicating, or
			 with respect to which subsequent investigations reveal, releases to surface
			 waters will be forwarded by the Agency to the Illinois Department of Natural
			 Resources and to the health department of the county in which the release
			 occurred.
d) All reports under this
			 Part indicating, or with respect to which subsequent investigations reveal,
			 releases to groundwater will be forwarded by the Agency to the health
			 department of the county in which the release occurred.
e) All reports under this Part are accessible
			 from the Agency through the Freedom of Information Act [ 5 ILCS 140 ] and
			 Agency regulations at 2 Ill. Adm. Code 1828.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 580 - PROCEDURES FOR REPORTING RELEASES OF LIVESTOCK WASTE › Section 580.300 - Follow-up Written Report

Current through Register Vol. 48, No. 28, July 12, 2024
An owner or operator of a livestock waste handling facility who
				reports by telephone any release of livestock waste shall provide a follow-up
				written report of the release within 5 days after the discovery of the release.
				The report shall confirm and update the information provided by telephone
				pursuant to Section
				580.106.
				Written reports shall be addressed to:
Illinois Environmental Protection Agency
Bureau of Water
Compliance Assurance Section
1021 North Grand Avenue East
P. O. Box 19276
Springfield, Illinois 62794-9276
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 601 - INTRODUCTION › Section 601.101 - General Requirements

Current through Register Vol. 48, No. 28, July 12, 2024
a)
			 Owners and official custodians of a public water supply in the State of
			 Illinois must provide, under the Act, Board Rules, and the Safe Drinking Water
			 Act (42 U.S.C.
			 300f et seq.), continuous operation and
			 maintenance of public water supply facilities to assure that the water is safe
			 in quality, clean, adequate in quantity, and of satisfactory mineral
			 characteristics for ordinary domestic consumption.
b) Finished Water Quality
1) The finished water delivered to any user
			 at any point in the distribution system must contain no impurity at a
			 concentration that may be hazardous to the health of the consumer or that would
			 be excessively corrosive or otherwise deleterious to the water supply. Drinking
			 water delivered to any user at any point in the distribution system must
			 contain no impurity that could reasonably be expected to cause offense to the
			 sense of sight, taste, or smell.
2)
			 Any substance used in treatment must not remain in the water at a concentration
			 greater than that required by good practice. A substance that may have a
			 deleterious physiological effect, or one for which physiological effects are
			 not known, must not be used in a manner that would permit it to reach the
			 consumer.
3) Concentrations of
			 constituents listed in the following chart should not be exceeded in the
			 finished water.
Contaminant
Secondary
						  MCL
Noticeable Effects above the
						  Secondary MCL
Aluminum
0.2 mg/L
colored water
Chloride
250 mg/L
salty taste
Color
15 color units
visible tint
Copper
1 mg/L
metallic taste; blue-green staining
Fluoride
2.0 mg/L
tooth discoloration
Foaming Agents
0.5 mg/L
frothy, cloudy; bitter taste; odor
Iron
0.3 mg/L
rusty color; sediment; metallic taste; reddish or
						  orange staining
Manganese
0.05 mg/L
black to brown color; black staining; bitter metallic
						  taste
Odor
3 T.O.N. (Threshold Odor Number)
"rotten-egg", musty or chemical smell
Silver
0.1 mg/L
skin discoloration; graying of the white part of the
						  eye
Sulfate
250 mg/L
salty taste
Total Dissolved Solids
500 mg/L
hardness; deposits; colored water; staining; salty
						  taste
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 601 - INTRODUCTION › Section 601.102 - Applicability and Organization of this Chapter

Current through Register Vol. 48, No. 28, July 12, 2024
a) This Chapter applies to groundwater and
			 public water supplies, except for those designated as non-community water
			 supplies. A public water supply ends at each service connection.
b) The rules in this Chapter are organized as
			 follows:
1) Part 601 contains definitions,
			 analytical testing requirements, and incorporations by reference applicable to
			 Parts 601, 602, 603, and 604.
2)
			 Part 602 contains permitting requirements and standards for community water
			 supplies and technical, financial, and managerial capacity requirements for new
			 community water supplies.
3) Part
			 603 contains ownership and responsible personnel requirements for community
			 water supplies.
4) Part 604
			 contains design, operation, and maintenance criteria for community water
			 supplies.
5) Part 611 contains
			 rules identical in substance to federal regulations promulgated by the United
			 States Environmental Protection Agency (USEPA) under sections 1412(b), 1414(c),
			 1417(a), and 1445(a) of the Safe Drinking Water Act (SDWA) (42 U.S.C.
			 300g-1(b),
			 300g-3(c),
			 300g-6(a), and
			 300j-4(a)). Part
			 611 establishes primary drinking water rules and includes definitions and
			 incorporations by reference applicable to Part 611.
6) Part 615 contains requirements and
			 standards for the protection of groundwater for certain types of existing
			 facilities or units located wholly or partially within a setback zone or a
			 regulated recharge area. Part 615 includes definitions and incorporations by
			 reference applicable to Part 615.
7) Part 616 contains requirements and
			 standards for the protection of groundwater for certain types of new facilities
			 or units located wholly or partially within a setback zone or a regulated
			 recharge area. Part 616 includes definitions applicable to Part 616.
8) Part 617 contains the requirements and
			 standards for regulated recharge areas. Part 617 includes definitions and an
			 incorporation by reference applicable to Part 617.
9) Part 618 contains requirements and
			 standards for maximum setback zones. Part 618 includes definitions applicable
			 to Part 618.
10) Part 620 contains
			 the method of classification of groundwater, nondegradation provisions, the
			 groundwater quality standards, and procedures and protocols for the management
			 and protection of groundwater. Part 620 includes definitions and incorporations
			 by reference applicable to Part 620.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 601 - INTRODUCTION › Section 601.103 - Severability

Current through Register Vol. 48, No. 28, July 12, 2024
If any provision of this Chapter or its application to any
				person or in any circumstance is adjudged invalid, that adjudication will not
				affect the validity of this Chapter as a whole or any portion not adjudged
				invalid.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 601 - INTRODUCTION › Section 601.104 - Analytical Testing

Current through Register Vol. 48, No. 28, July 12, 2024
a) To
			 determine compliance with the community water supplies rules in this Subtitle
			 F, all sampling, monitoring, and testing must be made according to the methods
			 described in 35 Ill. Adm. Code 611, the National Primary Drinking Water
			 Regulations (40 CFR
			 141), or any other method specifically
			 approved by the Agency.
b) All
			 analyses for substances other than those listed in 35 Ill. Adm. Code 611 must
			 be performed by methods acceptable to the Agency.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.101 - Purpose

Current through Register Vol. 48, No. 28, July 12, 2024
The purpose of this Part is to establish minimum standards
				  for the permitting of community water supplies. The definitions in 35 Ill. Adm.
				  Code 601.105 apply to this
				  Part.
a) A person must not
construct, install, or operate a community water supply without a
				permit granted by the Agency
. [415 ILCS
				5/18(a)(3) ]
b)
Owners are required to submit
				plans and specifications to the Agency and obtain written approval before
				construction, installation, changes, or additions to a community water
				supply,
except as provided in Section
				602.104
.
[415 ILCS
				5/15(a) ]
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.102 - Community Water Supply Permits

Current through Register Vol. 48, No. 28, July 12, 2024
A community water supply may seek the following types of
				  permits issued by the Agency:
a)
				Construction Permit, under Subpart B;
b) Operating Permit, under Subpart
				C;
c) Algicide Permit, under
				Subpart D;
d) Aquatic Pesticide
				Permit, under Subpart E; or
e) A
				special exception permit, under Subpart F.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.103 - Public Water Supply Capacity Development

Current through Register Vol. 48, No. 28, July 12, 2024
All new community water supplies must demonstrate
				  technical, financial, and managerial capacity as a condition for issuance of
				  construction
and
operating
permits
by the
				  Agency. The demonstration must be consistent with the technical, financial and
				  managerial provisions of the federal Safe Drinking Water Act
(
				  42
				  USC 300f ), and regulations adopted by the
				  Agency. [415
				  ILCS 5/15(b) ]
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.104 - Emergency Permits

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Whenever emergency conditions require immediate action, the Agency may issue
				construction and operating permits by telephone to the owner, official
				custodian, or Responsible Operator in Charge, with whatever special conditions
				the Agency considers necessary for the proper safeguarding of the health of the
				water consumers.
b) Emergency
				conditions are hazards or threats to public health caused by:
1) accidents;
2) equipment failures;
3) human error; or
4) natural disasters.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.106 - Restricted Status

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Restricted status is defined as the Agency determination, under Section 39(a)
				of the Act and Section
				602.105, that all or part of a
				community water supply facility may no longer be issued a construction permit
				without causing a violation of the Act or Board or Agency rules. Board rules
				whose violation can result in a restricted status determination include rules
				establishing maximum contaminant levels, treatment techniques, source water
				quantity requirements, treatment unit loading rates, storage volume
				requirements, and minimum pressure for a distribution system.
1) When the Agency cannot issue a
				construction permit to a community water supply because that issuance would
				extend an existing violation of the Act or Board or Agency rules, the Agency
				must place the community water supply on restricted status.
2) Except as specified in Section
				602.105(a)(6),
				the Agency must not issue a permit for water main extension construction when
				the water main would extend an existing violation of the Act or Board or Agency
				rules.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.107 - Critical Review

Current through Register Vol. 48, No. 28, July 12, 2024
a) The
				Agency must publish in the Environmental Register and on its webpage, at the
				same frequency as the Restricted Status List under Section
				602.106(b), a
				list of community water supplies that according to Agency records exceed 80
				percent of the rate of any of the quantity requirements in the Board's or
				Agency's rules. This list will be entitled the "Critical Review
				List".
b) The Critical Review List
				must include a description of the cause of the community water supply's
				inclusion on the list.
c) The
				Agency must notify the owner or official custodian and the Responsible Operator
				in Charge of the community water supply when the community water supply is
				initially placed on critical review status by the Agency.
d) Owners or official custodians of community
				water supplies that have been placed on critical review status must notify of
				this status any person requesting construction of a water main
				extension.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.108 - Right of Inspection

Current through Register Vol. 48, No. 28, July 12, 2024
The permittee must allow the Agency and its duly authorized
				  representatives to perform inspections as authorized by the Act,
				  including:
a) entering at reasonable
				times the permittee's premises where treatment or distribution facilities are
				located or where any activity is to be conducted under a permit;
b) having access to and copying at reasonable
				times any records required to be kept under the terms and conditions of a
				permit;
c) inspecting at reasonable
				times, including during any hours of operation:
1) equipment constructed or operated under
				the permit;
2) equipment or
				monitoring methodology; or
3)
				equipment required to be kept, used, operated, calibrated, and maintained under
				the permit;
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.109 - Fees

Current through Register Vol. 48, No. 28, July 12, 2024
a)
Each
				applicant required to pay a fee must submit the fee to the Agency along with
				the permit application or as-built plans. The Agency must deny any construction
				permit application for which a fee is required that does not contain the
				appropriate fee
. [415 ILCS
				5/16.1(a) ]
b) The following fees are required by the
				Act:
1)
$240 if the construction
				permit application is to install or extend water main that is more than 200
				feet, but not more than 1,000 feet in length.
[415 ILCS
				5/16.1(d)(1) ]
2)
$720 if the construction permit
				application is to install or extend water main that is more than 1,000 feet but
				not more than 5,000 feet in length
. [415 ILCS
				5/16.1(d)(2) ]
3)
$1200 if the construction permit
				application is to install or extend water main that is more than 5,000 feet in
				length.
[415 ILCS
				5/16.1(d)(3) ]
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.110 - Signatory Requirement for Permit Applications

Current through Register Vol. 48, No. 28, July 12, 2024
All permit applications must be signed by the owner or
				  official custodian of the
community
water supply, or
				  by the owner's duly authorized agent, and must be accompanied by evidence of
				  authority to sign the application.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.111 - Application Forms and Additional Information

Current through Register Vol. 48, No. 28, July 12, 2024
The Agency may prescribe the form in which all information
				  required under this Part must be submitted and may require such additional
				  information as is necessary to determine whether the community water supply
				  will meet the requirements of the Act and this Chapter.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.112 - Filing and Final Action by Agency on Permit Applications

Current through Register Vol. 48, No. 28, July 12, 2024
a) For permits without a fee under Section
				602.109:
1) An application for a permit is considered
				to be filed on the date of initial receipt by the Agency of the application
				documents. The Agency must send the applicant written notification of the
				receipt of the complete application.
2) Except for emergency permits, applications
				for construction permits must be filed at least 90 days before the expected
				start of construction.
3) If the
				Agency fails to take final action, by granting or denying the permit as
				requested or with conditions, within 90 days from the filing of the completed
				application, the applicant may consider the permit granted for one
				year.
4) Any applicant for a permit
				may waive in writing the requirement that the Agency must take final action
				within 90 days from the filing of the application.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.113 - Duration

Current through Register Vol. 48, No. 28, July 12, 2024
a) Construction
				Permits
1) Construction permits for community
				water supply facilities expire one year after the date issued or renewed,
				unless construction has started. If construction does not start within one year
				after the issuance or renewal, the permit may be renewed for additional one
				year periods at the discretion of the Agency, upon written request of the
				applicant.
2) If construction
				starts within one year after the construction permit was issued or renewed, the
				permit expires five years from the date issued or renewed. Afterward, the
				permit may be renewed for periods specified by the Agency at its discretion,
				upon written request of the applicant.
3) For the purposes of this Section,
				construction is considered to have started when work at the site has been
				initiated and proceeds in a reasonably continuous manner to
				completion.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.114 - Conditions

Current through Register Vol. 48, No. 28, July 12, 2024
In addition to specific conditions authorized under this
				  Part, the Agency may impose conditions in a permit necessary to accomplish the
				  purposes of the Act and that are not inconsistent with regulations promulgated
				  by the Board.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.116 - Requirement for As-Built Plans

Current through Register Vol. 48, No. 28, July 12, 2024
If any portion of a community water supply has been
				  constructed without a construction permit as required by Section
				  602.101, or an emergency permit
				  issued under Section 602.104, the community water
				  supply must submit to the Agency as-built plans and specifications and a
				  construction permit application. As-built plans and specifications must be
				  prepared by a qualified person as described in Section
				  602.105(a)(4).
				  All plans and specifications submitted to the Agency under this Section must be
				  clearly marked "as-built" or "record drawings". Any deficiencies requiring
				  correction, as determined by the Agency, must be corrected within a time limit
				  set by the Agency. Submission of as-built plans and the correction of any
				  deficiencies does not relieve the owner or official custodian from any
				  liability for construction without a permit.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.117 - Existence of Permit No Defense

Current through Register Vol. 48, No. 28, July 12, 2024
The existence of a permit under this Chapter is not a defense
				  to a violation of the Act or a Board or Agency rule except for the requirements
				  to secure construction, operating, algicide, aquatic pesticide, or emergency
				  permits.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.118 - Appeal of Final Agency Action on a Permit Application

Current through Register Vol. 48, No. 28, July 12, 2024
a) If the Agency denies a permit required
				under this Part, the applicant may petition the Board to appeal the Agency's
				final decision under Section 40 of the Act.
b) An applicant may consider any condition
				imposed by the Agency in a permit as the Agency's refusal to grant a permit,
				which entitles the applicant to appeal the Agency's decision to the Board under
				Section 40 of the Act.
c) All
				appeals must be filed with the Board within 35 days after the date on which the
				Agency served its decision on the applicant.
However, the 35-day
				period
to appeal
may be extended for an additional period not
				to exceed 90 days by written notice provided to the Board from the applicant
				and the Agency within the initial appeal period.
[415 ILCS
				5/40(a)(1) ]
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.119 - Revocations

Current through Register Vol. 48, No. 28, July 12, 2024
Failure to comply with a permit condition, the Act, or a
				  Board or Agency rule is grounds for enforcement action as provided in the Act,
				  including revocation of a permit. Revocation of a permit must be sought by
				  filing a complaint with the Board under Title VIII of the
				  Act.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart A - GENERAL PERMIT PROVISIONS › Section 602.120 - Limitations

Current through Register Vol. 48, No. 28, July 12, 2024
Issuance of a permit under this Part does not relieve the
				  applicant of the obligation to obtain other permits required from other State
				  entities, the Agency, or local governing bodies.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart B - CONSTRUCTION PERMITS › Section 602.200 - Construction Permit Requirement

Current through Register Vol. 48, No. 28, July 12, 2024
a) A person must not cause or allow the
				construction of any new community water supply installation, or cause or allow
				the change of or addition to any existing community water supply, without a
				construction permit issued by the Agency.
b) Construction permits must be obtained by
				the owner or official custodian of a community water supply:
1) prior to beginning construction of any
				proposed community water supply;
2)
				prior to all alterations, changes or additions to an existing community water
				supply that may affect the sanitary quality, mineral quality or adequacy of the
				community water supply;
3) prior to
				adding new chemicals to the treatment process or changing the points of
				chemical application; and
4) prior
				to rehabilitating a water main using a liner.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart B - CONSTRUCTION PERMITS › Section 602.205 - Preliminary Plans

Current through Register Vol. 48, No. 28, July 12, 2024
a) To
				expedite the review of subsequent construction permit application plan
				documents, preliminary plans may be submitted prior to the submission of a
				construction permit application. No construction permit may be issued until the
				completed application, required fee, plans, and specifications have been
				submitted.
b) If preliminary plans
				are submitted, as directed under the Illinois Drinking Water Revolving Loan
				Funding Process (see 35 Ill. Adm. Code 664), the documents must include a
				description of alternate solutions, a discussion of the alternatives, and
				reasons for selecting the alternative recommended.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart B - CONSTRUCTION PERMITS › Section 602.210 - Construction Permit Applications

Current through Register Vol. 48, No. 28, July 12, 2024
All applications for construction permits required under this
				  Part must contain, when appropriate, the following information and
				  documents:
a) General information,
				including:
1) name of the community water
				supply;
2) community water supply
				identification number;
3) the name
				and mailing address of the owner or official custodian of the community water
				supply; and
4) name, scope and
				location of the project;
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart B - CONSTRUCTION PERMITS › Section 602.215 - Submission of Applications, Plans and Specifications

Current through Register Vol. 48, No. 28, July 12, 2024
a) Two copies of the completed application
				and of any required plans, specifications and supplemental schedules must be
				submitted to the Agency for review and approval.
b) All permit applications must be mailed or
				delivered to the appropriate address designated by the Agency.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 602 - PERMITS › Subpart B - CONSTRUCTION PERMITS › Section 602.220 - Alterations

Current through Register Vol. 48, No. 28, July 12, 2024
a) Before any
				deviations from plans and specifications approved by the Agency are made, the
				owner or official custodian, or an authorized delegate, must make a written
				request for a supplemental permit. The written request must document all of the
				changes made to the previously approved plans and specifications. Only those
				changes identified will be considered for a supplemental permit.
b) Revised plans or specifications must be
				submitted to and approved by the Agency with the supplemental permit
				request.
c) The Agency must approve
				supplemental permit requests if those requests comply with Section
				602.105
				and this Subpart.
d) A supplemental
				permit is not required for minor changes that will not affect the location,
				capacity, hydraulic conditions, water treatment processes or sanitary or
				mineral quality of the water to be delivered.
e) A supplemental permit will not be granted
				to add water main after construction has begun, except for additional water
				main necessary due to a change in the connection point to the existing water
				distribution system or due to a change in route or alignment. A new application
				for construction permit must be submitted for water main to serve additional
				users.