reglab/statecodes huggingface dataset:
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 51 - Lighting Fixtures, Lampholders, Lamps and Receptacles › Section 2510.56 - Receptacles, Cord Connectors and Attachment Plugs (Caps)

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Attachment Plugs. All new or replacement
						15- and 20-ampere attachment plugs and connectors shall be constructed so that
						there are no exposed current-carrying parts except the prongs, blades or pins.
						The cover for wire terminations shall be a part that is essential for the
						operation of an attachment plug or connector (dead-front construction).
						Attachment plugs shall be installed so that their prongs, blades, or pins are
						not energized unless inserted into an energized receptacle. No receptacles may
						be installed so as to require an energized attachment plug as its source of
						supply.
(b) Non-interchangeability.
						Receptacles, cord connectors and attachment plugs shall be constructed so that
						the receptacle or cord connectors will not accept an attachment plug with a
						different voltage or current rating than that for which the device is intended.
EXCEPTION: A 20-ampere T-slot receptacle or cord
						  connector shall be permitted to accept a 15-ampere attachment plug of the same
						  voltage rating.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Editorial correction of Section heading filed 11-3-83 (Register 83, o.
						  45).
3. Amendment filed 8-27-86; effective thirtieth day thereafter
						  (Register 86, No. 37.)
4. Amendment of section heading, section and
						  NOTE filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
						  pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 51 - Lighting Fixtures, Lampholders, Lamps and Receptacles › Section 2510.58 - Non-Grounding-Type Receptacles, Adapters, Cord Connectors, and Attachment Plugs

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						Nongrounding-type receptacles and connectors shall not be used for
						grounding-type attachment plugs.
(b) Adapters. Two-pole to three-pole adapters
						shall not be used. Adapters permitting change to different rated (amperes or
						volts) configurations shall not be used.
1.
						  Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
						  Amendment of subsections (b) and (d) filed 8-27-86; effective thirtieth day
						  thereafter (Register 86, No. 37).
3. Amendment of section heading,
						  section and NOTE filed 5-5-2008; operative 5-5-2008. Submitted to OAL for
						  printing only pursuant to Labor Code
						  142.3(a)(3)
						  (Register 2008, No. 19).
Note: Authority cited: Section
							 142.3, Labor
							 Code. Reference: Section
							 142.3, Labor
							 Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › GENERAL › Section 2522.2 - Energized Parts

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						  Appliances shall have no live parts normally exposed to contact.
EXCEPTION: Toasters, grills, or other appliances in
							 which the current-carrying parts at high temperatures are necessarily
							 exposed.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
3. Amendment of section and NOTE filed 5-5-2008; operative
							 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.7 - General

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All appliances shall be installed in an approved
							 manner.
(Title 24, Part 3, Section
							 422-7.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.8 - Flexible Cords. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Repealer of section and amendment of NOTE filed 5-5-2008; operative 5-5-2008.
							 Submitted to OAL for printing only pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.9 - Portable Immersion Heaters

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Electric heaters of the portable immersion type shall
							 be so constructed and installed that current-carrying parts are effectively
							 insulated from electrical contact with the substance in which they are
							 immersed. The authority having jurisdiction may make exceptions for special
							 applications of apparatus if suitable precautions are taken.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.10 - Protection of Combustible Material

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Each electrically heated appliance that is intended
							 by size, weight, and service to be located in a fixed position shall be so
							 placed as to provide ample protection between the appliance and adjacent
							 combustible material.
(Title 24, Part 3, Section
							 422-10.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.11 - Stands for Portable Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Each smoothing iron and other portable electrically
							 heated appliance intended to be applied to combustible material shall be
							 equipped with an approved stand, which shall be permitted to be a separate
							 piece of equipment or a part of the appliance.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.12 - Signals for Heated Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Electrically heated appliance or group of appliances
							 intended to be applied to combustible material shall be provided with a
							 signal.
EXCEPTION: If an appliance is provided with an
							 integral temperature-limiting device.
(Title 24, Part 3, Section
							 422-12.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.15 - Infrared Lamp Industrial Heating Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Infrared heating lamps rated at 300 watts
						  or less shall be permitted with lampholders of the medium-base, unswitched
						  porcelain type or other types approved for the purpose.
(b) Screw shell lampholders shall not be used
						  with infrared lamps over 300 watts rating.
EXCEPTION: Lampholders approved for the
							 purpose.
(c) Lampholders
						  shall be permitted to be connected to any of the branch circuits supplying
						  lighting and/or appliance loads and, in industrial occupancies, shall be
						  permitted to be operated in series on circuits of over 150 volts to ground
						  provided the voltage rating of the lampholders is not less than the circuit
						  voltage.
Each section, panel, or strip carrying a number of
							 infrared lampholders (including the internal wiring of such section, panel, or
							 strip) shall be considered an appliance. The terminal connection block of each
							 such assembly shall be considered an individual outlet.
(Title 24, Part 3, Section
							 422-15.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment of subsection (c) filed 8-27-86; effective thirtieth day thereafter
							 (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › INSTALLATION OF APPLIANCES › Section 2522.17 - Wall-Mounted Ovens and Counter-Mounted Cooking Units

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Wall-mounted ovens and counter-mounted
						  cooking units complete with provisions for mounting and for making electrical
						  connections shall be considered as fixed appliances.
(b) A separable connector or a plug and
						  receptacle combination in the supply line to an oven or cooking unit used only
						  for ease in servicing or for installation shall:
(1) Not be installed as the disconnecting
						  means.
(2) Be approved for the
						  temperature of the space in which it is located.
(Title 24, Part 3, Section
							 422-17.)
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › CONTROL AND PROTECTION OF APPLIANCES › Section 2522.20 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Each appliance shall have a means to disconnect it
							 from all ungrounded conductors. If an appliance is supplied by more than one
							 source, the disconnecting means shall be grouped and
							 identified.
1. New
							 section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only
							 pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › CONTROL AND PROTECTION OF APPLIANCES › Section 2522.21 - Disconnection of Fixed Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) For fixed appliances rated at not over
						  300 volt amperes or 1/8 hp., the branch circuit overcurrent device shall be
						  permitted to serve as the disconnecting means.
(b) For fixed appliances of greater rating
						  the branch circuit switch or circuit breaker shall be permitted to serve as the
						  disconnecting means where readily accessible to the user of the appliance.
(Title 24, Part 3, Section
							 422-21.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment of subsection (b) filed 8-27-86; effective thirtieth day thereafter
							 (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › CONTROL AND PROTECTION OF APPLIANCES › Section 2522.22 - Disconnection of Portable Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) For portable appliances, a separable
						  connector or an attachment plug and receptacle shall be permitted to serve as
						  the disconnecting means.
(b) The
						  rating of a receptacle or of a separable connector shall not be less than the
						  rating of any appliance connected thereto.
EXCEPTION: Demand factors authorized elsewhere in
							 these Orders shall be permitted to be applied.
(c) Attachment plugs and connectors shall
						  conform to the following:
(1) Energized Parts.
						  They shall be so constructed and installed as to guard against inadvertent
						  contact with energized parts.
(2)
						  Interrupting Capacity. They shall be capable of interrupting their rated
						  current without hazard to the operator.
(3) Interchange ability. They shall be so
						  designed that they will not fit into receptacles of lesser
						  rating.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › CONTROL AND PROTECTION OF APPLIANCES › Section 2522.23 - Disconnection of Stationary Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) For stationary appliances rated at not
						  over 300 volt amperes or 1/8 horsepower, the branch circuit overcurrent device
						  shall be permitted to serve as the disconnecting means.
(Title 24, Part 3, Section
							 422-21(a).)
(b) For stationary appliances of greater
						  rating, the branch circuit switch or circuit breaker shall be permitted to
						  serve as the disconnecting means where readily accessible to the user of the
						  appliance.
(Title 24, Part 3, Section
							 422-21(b).)
(c) For cord-connected appliances, such as
						  free-standing household-type ranges and clothes dryers, a separable connector
						  or an attachment plug and receptacle shall be permitted to serve as the
						  disconnecting means. Attachment plugs and connectors shall comply with Section
						  2522.22(c).
For household electric ranges, an attachment plug and
							 receptacle connection at the rear base of a range, if it is accessible from the
							 front by removal of a drawer, shall be considered as meeting the intent of this
							 rule.
(Title 24, Part 3, Section
							 422-22(a) and
							 (b).)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › CONTROL AND PROTECTION OF APPLIANCES › Section 2522.26 - Disconnecting Means for Motor-Driven Appliances

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
If a switch or circuit breaker serves as the
							 disconnecting means for a stationary or fixed motor-driven appliance of more
							 than 1/8 horsepower, it shall be located within sight from the motor controller
							 and shall comply with the disconnecting means specified in Article 56.
(Title 24, Part 3, Section
							 422-26.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › MARKING OF APPLIANCES › Section 2522.30 - Nameplate

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) Each electric
						  appliance shall be provided with a nameplate, giving the identifying name and
						  the rating in volts and amperes, or in volts and watts. If the appliance is to
						  be used on a specific frequency or frequencies, it shall be so marked.
When motor overload protection external to the
							 appliance is required, the appliance shall be so marked.
(b) Marking shall be located so as to be
						  visible or easily accessible after installation.
(Title 24, Part 3, Section
							 422-30.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No.
							 45).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › MARKING OF APPLIANCES › Section 2522.31 - Marking of Heating Elements

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All heating elements that are rated over one ampere,
							 replaceable in the field, and a part of an appliance shall be legibly marked
							 with the ratings in volts and amperes, or in volts and watts, or with the
							 manufacturer's part number.
(Title 24, Part 3, Section
							 422-31.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 52 - APPLIANCES › MARKING OF APPLIANCES › Section 2522.32 - Appliances Consisting of Motors and Other Loads

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Appliances shall be marked in accordance with (a) or
							 (b) below.
(a) In addition to the
						  marking required in Section
						  2522.30, the marking on an
						  appliance consisting of a motor with other load(s) or motors with or without
						  other load(s) shall specify the minimum circuit size and the maximum rating of
						  the circuit overcurrent protective device.
EXCEPTION: No. 1: Portable appliances and other
							 appliances, factory-equipped with cords and attachment plugs, complying with
							 Section 2522.30.
EXCEPTION: No. 2: An appliance where both the minimum
							 circuit size and maximum rating of the circuit overcurrent protective device
							 are not more than 15 amperes and complies with Section
							 2522.30.
(b) An alternate marking method shall be
						  permitted to specify the rating of the largest motor in volts and amperes, and
						  the additional load(s) in volts and amperes or volts and watts in addition to
						  the marking required in Section
						  2522.30.
EXCEPTION: No. 1: Portable appliances and other
							 appliances, factory-equipped with cords and attachment plugs, complying with
							 Section 2522.30.
EXCEPTION: No. 2: The ampere rating of a motor 1/8
							 hp. or less or a nonmotor load one ampere or less shall be permitted to be
							 omitted unless such loads constitute the principal load.
(Title 24, Part 3, Section
							 422-32.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No.
							 45).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 53 - FIXED ELECTRIC SPACE HEATING EQUIPMENT › GENERAL › Section 2524.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This article covers fixed electric equipment used for
							 space heating. Equipment shall be of a type approved for the purpose and
							 location where installed. For the purpose of this article, heating equipment
							 shall include heating cable, unit heaters, boilers, central systems, or other
							 approved fixed electric space heating equipment. This article shall not apply
							 to process heating and room air conditioning.
(Title 24, Part 3, Section
							 424-1.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 53 - FIXED ELECTRIC SPACE HEATING EQUIPMENT › GENERAL › Section 2524.19 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Means shall be provided to disconnect the heater,
							 controller(s), and overcurrent protective device(s) of all fixed electric space
							 heating equipment from all ungrounded conductors.
(Title 24, Part 3, Section
							 424-19.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 53 - FIXED ELECTRIC SPACE HEATING EQUIPMENT › GENERAL › Section 2524.21 - Switch and Circuit Breaker to Be Indicating

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Switches and circuit breakers used as disconnecting
							 means shall be of the indicating type.
(Title 24, Part 3, Section
							 424-21.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 53 - FIXED ELECTRIC SPACE HEATING EQUIPMENT › GENERAL › Section 2524.65 - Location of Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Duct heater controller equipment shall be accessible
							 with the disconnecting means installed at or within sight from the
							 controller.
EXCEPTION: The disconnecting means shall be arranged
							 to be locked in the "open" position if it is not within sight of the
							 controller. A distance of 50 feet shall be considered as equivalent to being
							 out of sight.
(Title 24, Part 3, Section
							 424-65.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 54 - FIXED OUTDOOR ELECTRIC DE-ICING AND SNOW MELTING EQUIPMENT › GENERAL › Section 2526.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This article covers electrically energized heating
							 units, panels, and cables where embedded in driveways, walks, steps, and other
							 areas.
(Title 24, Part 3, Section
							 426-1(a).)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 54 - FIXED OUTDOOR ELECTRIC DE-ICING AND SNOW MELTING EQUIPMENT › CONTROL AND PROTECTION › Section 2526.20 - Disconnecting Means. [Renumbered]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Renumbering and amendment of Section
							 2526.20 to Section
							 2526.50 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 54 - FIXED OUTDOOR ELECTRIC DE-ICING AND SNOW MELTING EQUIPMENT › CONTROL AND PROTECTION › Section 2526.50 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
All fixed outdoor electric de-icing and snow melting
							 equipment shall be provided with a means for disconnection from all ungrounded
							 conductors. Where readily accessible to the user of the equipment, the branch
							 circuit switch or circuit breaker shall be permitted to serve as the
							 disconnecting means. Switches used as disconnecting means shall be of the
							 indicating type.
(Title 24, Part 3, Section
							 426-50.)
1.
							 Renumbering and amendment of former Section
							 2526.20 to Section
							 2526.50 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37). For history of former section,
							 see Register 83, No. 45.
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › GENERAL › Section 2527.1 - Scope

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The requirements of this article shall apply to
							 electrically energized heating systems and the installation of these systems
							 used with pipelines and/or vessels. This article covers electrical heating of
							 pipelines and/or vessels by separate external heating elements, other than the
							 skin electric current tracing or impedance methods.
(Title 24, Part 3, Section
							 427-1.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › GENERAL › Section 2527.2 - Definitions

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
For the purpose of this article:
(a) A pipeline is a length of pipe including
						  pumps, valves, flanges, control devices, strainers and/or similar equipment for
						  conveying fluids.
(b) A vessel is a
						  container such as a barrel, drum, or tank for holding fluids or other
						  material.
1.
							 Editorial correction filed 11-2-83 (Register 83, No.
							 45).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › INSTALLATION › Section 2527.10 - General

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Equipment for pipeline and vessel electrical heating
							 shall be of a type compatible with the chemical, thermal and physical
							 environment.
(Title 24, Part 3, Section
							 427-10.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › INSTALLATION › Section 2527.11 - Use

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Electric heating equipment shall be installed in such
							 a manner as to be afforded protection from physical damage.
(Title 24, Part 3, Section
							 427-11.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › INSTALLATION › Section 2527.12 - Marking. [Renumbered]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Renumbering and amendment of Section
							 2527.12 to Section
							 2527.13 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › INSTALLATION › Section 2527.13 - Identification

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
The presence of electric pipeline and vessel heating
							 equipment shall be evident by the posting of appropriate signs or other
							 markings at frequent intervals in the area involved.
(Title 24, Part 3, Section
							 427-13.)
1.
							 Renumbering and amendment of former Section
							 2527.12 to Section
							 2527.13 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › CONTROL AND PROTECTION › Section 2527.20 - Disconnecting Means. [Renumbered]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Renumbering of Section
							 2527.20 to Section
							 2527.55 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › CONTROL AND PROTECTION › Section 2527.22 - Overcurrent Protection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
Heaters shall be protected against
							 overcurrent.
(Title 24, Part 3, Section
							 3-427 -
							 22.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 55 - FIXED ELECTRIC HEATING EQUIPMENT FOR PIPELINES AND VESSELS › CONTROL AND PROTECTION › Section 2527.55 - Disconnecting Means

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a)
						  Means shall be provided to disconnect all fixed electric pipeline or vessel
						  heating equipment from all ungrounded conductors. The branch circuit switch or
						  circuit breaker, where readily accessible to the user of the equipment, shall
						  be permitted to serve as the disconnecting means. Switches used as
						  disconnecting means shall be of the indicating type, and shall be provided with
						  a positive lockout in the "off" position.
(b) The factory-installed attachment plug of
						  cord-connected equipment, rated 20 amperes or less and 150 volts or less to
						  ground is an acceptable means of disconnection.
(Title 24, Part 3, Section
							 427-55.)
1.
							 Renumbering of former Section
							 2527.20 to Section
							 2527.55 filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 56 - MOTORS, MOTOR CIRCUITS AND CONTROLLERS › GENERAL › Section 2530.4 - In Sight From

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
If specified that one equipment shall be "in sight
							 from" another piece of equipment, one shall be visible and not more than 50
							 feet from the other.
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Repealer and new section filed 8-27-86; effective thirtieth day thereafter
							 (Register 86, No. 37).
3. Amendment of NOTE filed 5-5-2008;
							 operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code
							 142.3(a)(3)
							 (Register 2008, No. 19).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 56 - MOTORS, MOTOR CIRCUITS AND CONTROLLERS › GENERAL › Section 2530.36 - Fuses - In Which Conductor. [Repealed]

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Repealer filed 8-27-86; effective thirtieth day thereafter (Register 86, No.
							 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 56 - MOTORS, MOTOR CIRCUITS AND CONTROLLERS › GENERAL › Section 2530.43 - Automatic Restarting

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) A motor-running overload device that can
						  restart a motor automatically after overload tripping shall not be installed
						  unless approved for use with the motor it protects.
(b) A motor that can restart automatically
						  after shutdown shall not be installed if its automatic restarting can result in
						  injury to persons.
(Title 24, Part 3, Section
							 430-43.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Amendment deleting subsection (a) designation only filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
3. Change without
							 regulatory effect amending section filed 11-15-99 pursuant to section
							 100, title 1, California Code of
							 Regulations (Register 99, No. 47).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 56 - MOTORS, MOTOR CIRCUITS AND CONTROLLERS › GENERAL › Section 2530.74 - Disconnection

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
(a) General.
						  Control circuits shall be so arranged that they will be disconnected from all
						  sources of supply when the disconnecting means is in the "Open" position. The
						  disconnecting means shall be permitted to consist of two or more separate
						  devices, one of which disconnects the motor and the controller from the
						  source(s) of power supply for the motor, and the other(s), the control
						  circuit(s) from its power supply. Where separate devices are used, they shall
						  be located immediately adjacent to each other.
(Title 24, Part 3, Section
							 430-74(a) without
							 exceptions.)
(b) Control
						  Transformer in Controller. Where a transformer or other device is used to
						  obtain a reduced voltage for the control circuit and is located in the
						  controller, such transformer or other device shall be connected to the load
						  side of the disconnecting means for the control circuit.
(Title 24, Part 3, Section
							 430-74(b).)
1.
							 Editorial correction filed 11-2-83 (Register 83, No. 45).
2.
							 Editorial correction of subsection (a) filed 11-3-83 (Register 83, No.
							 45).
3. Amendment of subsection (a) filed 8-27-86; effective
							 thirtieth day thereafter (Register 86, No. 37).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.
California Code of Regulations › Title 8 - Industrial Relations › Division 1 - Department of Industrial Relations › Chapter 4 - Division of Industrial Safety › Subchapter 5 - Electrical Safety Orders › Group 1 - Low-Voltage Electrical Safety Orders › Article 56 - MOTORS, MOTOR CIRCUITS AND CONTROLLERS › MOTOR CONTROLLERS › Section 2530.81 - General

Current through Register 2024 Notice Reg. No. 28, July 12, 2024
This Section, "Motor Controllers," is intended to
							 require suitable controllers for all motors.
(a) Definition. For definition of
						  "Controller," see Article 1. For the purpose of this Article, the term
						  "Controller" includes any switch or device normally used to start and stop a
						  motor.
(b) Stationary Motor of 1/8
						  Horsepower or Less. For a stationary motor rated at 1/8 horsepower or less that
						  is normally left running and is so constructed that it cannot be damaged by
						  overload or failure to start, such as clock motors and the like, the branch
						  circuit protective device shall be permitted to serve as the
						  controller.
(c) Portable Motor of
						  1/3 Horsepower or Less. For a portable motor rated at 1/3 horsepower or less,
						  the controller shall be permitted to be an attachment plug and receptacle.
(Title 24, Part 3, Section
							 430-81.)
1.
							 Editorial correction filed 11-2-83 (Register 83, No.
							 45).
Note: Authority cited: Section
								142.3, Labor
								Code. Reference: Section
								142.3, Labor
								Code; and Section
								18943(c),
								Health and Safety Code.