Arizona Administrative Code › Title 20 - COMMERCE, FINANCIAL INSTITUTIONS, AND INSURANCE › Chapter 05 - INDUSTRIAL COMMISSION OF ARIZONA › Article 4 - ARIZONA BOILERS AND LINED HOT WATER HEATERS › Section R20-5-407 - Inspection of Boilers, Lined Hot Water Storage Heaters, Direct Fired Jacketed Steam Kettles and Issuance of Inspection Certificates

Current through Register Vol. 30, No. 28, July 12, 2024
A. An Authorized
				Inspector shall comply with the guidelines set forth in The National Board
				Inspection Code, ANSI/NB-23- 2019 Edition , incorporated by reference. This
				incorporation does not include any later amendments or editions of the
				incorporated material. A copy of this referenced material is available for
				review at the Industrial Commission of Arizona, 800 W. Washington Street,
				Phoenix, AZ 85007 and may be obtained from the National Board of Boiler and
				Pressure Vessel Inspectors, 1055 Crupper Avenue, Columbus, OH 43229-1183 or at
http://www.nationalboard.org/
.
B. If an Owner, Operator, or User fails to
				comply with the requirements for an inspection or pressure test under this
				Article, the Division shall withhold the Inspection Certificate until the
				Owner, Operator, or User complies with the requirements.
C. An Authorized Inspector shall not engage
				in the sale of any object or device relating to , or equipment associated with,
				Boilers, Lined Hot Water Heaters, or Direct Fired Jacketed Steam
				Kettles.
D. Under A.R.S. §
									23-485(D), the
				Special Inspector shall file an inspection report within 30 days of an
				inspection by entering data into the Division's Web-based inspection entry
				form, by submitting a paper inspection report issued by the Division , or by
				electronic transfer of data. Whatever form of data transfer a Special Inspector
				chooses, there shall be no cost to the Division. The inspection report shall
				contain the following:
1. Whether it is a
				Certificate or non-Certificate Inspection;
2. Whether it is an Internal Inspection,
				External Inspection, or both;
3.
				Name of location, address and phone number of the object;
4. Name, address and phone number of owner or
				responsible party;
5. Contact
				person's name and phone number at the inspection location;
6. State Identification Number;
7. Inspection Certificate due date;
8. Inspection Certificate duration;
9. Install/reinstall date, if
				known;
10. Whether the object is active, inactive,
				Out-of-Service, standby, or scrapped;
11. MAWP permitted or
				allowed;
12. National Board registration number;
13.
				Name of the manufacturer and the year the object was built;
14.
				Special location in plant, if applicable;
15. Boiler
				type;
16. Purpose of the Boiler;
17. Specify type of
				fuel used;
18. Whether the firing method is automatic, manual ,
				or unknown;
19. Whether the fuel train is in compliance with
				CSD-1, NFPA 85, Z21.10.3 or other;
20. Whether the Boiler
				is fully attended as per
				R20-5-408(C);
21.
				Size/ input rate, as applicable;
22. Size classification
				(HS/BTU/Kw);
23. Whether the heating surface type is stamped,
				computed , or unknown;
24. Minimum Safety
				Valve relief capacity required;
25. Whether the
				minimum Safety Valve relief capacity type is BTU/Hr, lbs/Hr or
				unknown;
26. Number of temperature/pressure controls, as
				applicable;
27. Owner number assigned by the Owner to specifically
				identify object's location;
28. Inspection
				date;
29. Whether the Inspection Certificate is
				posted;
30. Safety Valve total capacity;
31. Safety Valve total capacity type (PPH/Hr
				or BTU/Hr);
32. Safety Valve #1 set pressure;
33.
				Safety Valve #2 set pressure;
34. Safety Valve #3
				set pressure;
35. Safety Valve code
				stamping (Example: V,HV,UV,UV3.TV,TD, OR NV);
36. Whether the object
				has been hydro tested;
37. Hydro Test (psi),
				if applicable;
38. Whether Pressure/Altitude Gage was
				tested;
39. Whether the condition of the object is okay to
				issue an Inspection Certificate;
40. Inspection
				comments, condition of Boiler;
41. Violations
				noted;
42. Inspector name and Special Inspector number;
				and
43. National Board Commission number
				.