reglab/statecodes huggingface dataset:
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart A - DESIGN REQUIREMENTS › Section 653.120 - Piping Identification

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Piping in a water treatment facility shall be identified clearly by legends and
				color coding as described in the Standards or American National Standards
				Institute (ANSI) Standard A-13.1. A consistant standard shall be used
				throughout the system.
b) Potable
				water lines shall be clearly and permanently identified where dual water lines
				or pressure sewer systems exist.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart B - OPERATION AND MAINTENANCE › Section 653.201 - Required Supervision

Current through Register Vol. 48, No. 28, July 12, 2024
Specific information required by 35 Ill. Adm. Code 603 shall
				  be furnished by completing a Notification of Ownership or Responsible Personnel
				  form available from the Agency.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart B - OPERATION AND MAINTENANCE › Section 653.202 - Chemical Addition

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Chemicals added to drinking water and passed to the distribution system shall
				be approved by the United States Environmental Protection Agency (USEPA)
				(pursuant to provisions of the Safe Drinking Water Act (
				42
				U.S.C. 300f et seq. (1980)), the Toxic
				Substance Control Act (
				15 U.S.C.
				2604 et seq. (1982)), or the Federal
				Insecticide, Fungicide, and Rodenticide Act (
				7
				U.S.C. 136 et seq. (1980)) or the United
				States Food and Drug Administration (USFDA) (pursuant to the Federal Food, Drug
				and Cosmetic Act (
				21
				U.S.C. 301 et seq. (1983)) and meet the
				purity requirements of Water Chemicals Codex, National Research Council of the
				National Science Foundation. All chemical containers shall bear the name,
				address and telephone number of the supplier, along with a functional name or
				identification and strength of the chemical. Chemicals shall not be fed in
				excess of the maximum dosage approved by USEPA or USFDA.
b) Chemicals added for raw water treatment
				including but not limited to clarification, softening and constituent removal
				not intended to pass to the distribution system shall meet American Water Works
				Association Standards purity requirements of Water Chemicals Codex, National
				Research Council of the National Science Foundation. The chemical shall be
				specifically approved for use by the USEPA (pursuant to provisions of the Safe
				Drinking Water Act, the Toxic Substance Control Act, the Federal Insecticide,
				Fungicide, and Rodenticide Act) or the USFDA (pursuant to the Federal Food,
				Drug and Cosmetic Act). Chemicals shall not be fed in excess of the maximum
				dosage approved by USEPA or USFDA.
c) A free chlorine residual of 10 mg/l shall
				be maintained at all times in stock solutions used for iron and/or manganese
				sequestration. This chlorine residual shall not replace the chlorination
				requirement of 35 Ill. Adm. Code 604.401.
d) Protective paints and coatings, concrete
				coatings and admixtures, grouts and liners used in a community water supply
				shall be approved by the USEPA (pursuant to provisions of the Safe Drinking
				Water Act, the Toxic Substance Control Act, or the Federal Insecticide,
				Fungicide and Rodenticide Act).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart B - OPERATION AND MAINTENANCE › Section 653.203 - Exceptions for Community Water Supplies

Current through Register Vol. 48, No. 28, July 12, 2024
a) Replacement in existing community water
				supplies of components such as pressure tanks, water mains, pressure filters or
				ion exchange softeners that do not meet the Standards or these Technical Policy
				Statements shall not be required if:
1) the
				finished water meets the water quality standards of 35 Ill. Adm. Code 604;
				and
2) water pressure meets the
				standards of Section
				653.106;
				and either
3) the components were
				permitted by the State Agency, other than this Agency, having administrative
				program authority at the time of construction; or
4) no permits were required from any State
				Agency at the time of construction.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart C - REPAIR WORK AND EMERGENCY OPERATION › Section 653.301 - Protection During Repair Work

Current through Register Vol. 48, No. 28, July 12, 2024
Official custodians of community water supplies shall protect
				  the water supply from contamination when any part of the system is out of
				  service for repair, construction, alteration or replacement.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart C - REPAIR WORK AND EMERGENCY OPERATION › Section 653.302 - Disinfection Following Repair or Replacement

Current through Register Vol. 48, No. 28, July 12, 2024
Any part of a community water system which has direct contact
				  with finished water and has been out of service for repair, alteration or
				  replacement shall be disinfected as required by Section
				  652.203
				  before being returned to service. Equipment which does not come in contact with
				  finished water such as raw surface water pumps, raw surface water transmission
				  lines, chemical mixing tanks and clarifiers need only be flushed before being
				  returned to service. Filters shall be disinfected. Wells, water storage tanks
				  and water mains shall be disinfected in accordance with AWWA Standards A100,
				  D105 and C601, respectively.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart C - REPAIR WORK AND EMERGENCY OPERATION › Section 653.303 - Emergency Operation

Current through Register Vol. 48, No. 28, July 12, 2024
a) A
				boil order shall be issued when bacteriological analyses show persistent low
				level contamination or gross contamination. The boil order shall remain in
				effect until requirements of 35 Ill. Adm. Code 604.102 are met. Issuance of a
				boil order does not relieve the water supply from making public notification in
				accordance with 35 Ill. Adm. Code 606: Subpart B.
b) Owners and operators of community water
				supplies shall immediately notify the Agency at the appropriate Regional Office
				in accordance with Section
				652.301(b)
				when there is knowledge or suspicion that a water supply has become
				contaminated. On weekends, holidays and after office hours, the Agency may be
				reached through the Agency Emergency Response Unit at 217/782-3637.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart D - PUBLIC NOTIFICATION › Section 653.401 - Purpose

Current through Register Vol. 48, No. 28, July 12, 2024
a) Public
				notification is used to inform water users of problems within a water supply
				and to enlist support to obtain resources to correct the problems.
b) Public notice in no way relieves operators
				and official custodians from issuing a boil order or other rapid notice of
				health advisory if an emergency exists. A boil order or emergency notice does
				not relieve the water supply from making public notification.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart D - PUBLIC NOTIFICATION › Section 653.403 - Public Notification Required

Current through Register Vol. 48, No. 28, July 12, 2024
Public notification shall be made when:
a) finished water distributed to the consumer
				is not in compliance with any Maximum Allowable Concentration (MAC) as
				specified in 35 Ill. Adm. Code 604: Subparts A, B or C;
b) finished water samples required by 35 Ill.
				Adm. Code 605 are not analyzed by a certified laboratory;
c) turbidity samples are not analyzed by a
				person approved by the Agency as specified in Section
				654.402;
d) a variance from any Maximum Allowable
				Concentration specified in 35 Ill. Adm. Code 604: Subpart A, B, or C has been
				granted by the Illinois Pollution Control Board; or
e) the compliance schedule included as
				condition of variance has not been met.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart D - PUBLIC NOTIFICATION › Section 653.404 - Persons to Be Notified

Current through Register Vol. 48, No. 28, July 12, 2024
a) All
				water customers shall be notified in writing by direct mail or other means of
				direct delivery. Notices in institutions shall be posted in conspicuous places
				so that notice can be read by residents.
b) Supplies which furnish water to satellite
				supplies shall notify the official custodian of those supplies when conditions
				require public notification. That official custodian of the satellite supply
				shall be responsible for notifying the customers of that satellite
				supply.
c) A copy of the written
				notice and copies of all other materials provided for notification purposes
				shall be sent to the Division of Public Water Supplies at the same time the
				customers are notified.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart E - OPERATIONAL TESTING EQUIPMENT › Section 653.501 - Operational Testing Equipment

Current through Register Vol. 48, No. 28, July 12, 2024
a) Smooth-nosed sampling taps shall be
				provided for collecting representative samples of treated and untreated
				water.
b) All community water
				supplies shall have DPD test equipment or other approved means as approved in
				"Standard Methods for the Examination of Water and Wastewater", 15th edition
				for measuring disinfectant used.
c)
				Testing equipment shall be available to plants with specific treatment
				processes which include, but are not limited to:
1) fluoride adjustment - test equipment for
				measuring levels of fluoride ion;
2) iron removal - test equipment for
				measuring iron levels;
3) ion
				exchange softening - equipment for measuring hardness;
4) coagulation and filtration - jar test
				equipment for determining chemical dosages and equipment for measuring pH,
				hardness, alkalinity and nitrate;
5) lime softening - equipment for measuring
				pH, hardness and alkalinity;
6)
				reverse osmosis - equipment for measuring total dissolved solids, chlorides and
				monitoring sulfates; and
7)
				polyphosphate addition - equipment for measuring both ortho- and total
				phosphates.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart F - CHLORINATION › Section 653.601 - Chlorination - Engineering Design Criteria

Current through Register Vol. 48, No. 28, July 12, 2024
a) Procedure for Submitting Plans and
				Specifications - Design documents for chlorination shall be prepared and
				submitted in accordance with 35 Ill. Adm. Code 602.
b) Chlorinator equipment shall be:
1) capable of maintaining a minimum free
				chlorine residual of 0.2 mg/l or a minimum combined residual of 0.5 mg/l in all
				active parts of the distribution system at all times;
2) large enough to satisfy the immediate
				chlorine demand and give a measurable residual of at least 2.0 mg/l under all
				operating conditions after contact; and
3) capable of feeding chlorine to the water
				being treated at a dosage rate of at least 5.0 mg/l except when the water has a
				high chlorine demand. Factors in determining chlorine demand are:
A) pH;
B) water temperature;
C) contact time;
D) presence in the water of substances having
				chlorine demand such as hydrogen sulfide, iron, manganese and nitrogenous
				compounds including ammonia; and
E)
				supplemental treatment such as aeration which reduces chlorine
				demand.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart F - CHLORINATION › Section 653.602 - Testing Equipment for Residual Chlorine

Current through Register Vol. 48, No. 28, July 12, 2024
a) Residual chlorine shall be determined by
				methods in "Standard Methods for the Examination of Water and Wastewater", 15th
				edition.
b) Colorimetric
				determinations of chlorine residuals shall be made using the DPD
				methods.
c) The test equipment used
				shall be capable of indicating values of 0.1, 0.2, 0.3, 0.4, 0.5, 0.7, 1.0,
				2.0, mg/l and higher if chlorine is applied for taste and odor
				control.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart F - CHLORINATION › Section 653.603 - Minimum Contact Time

Current through Register Vol. 48, No. 28, July 12, 2024
a) A
				minimum chlorine contact time of 60 minutes shall be provided for all surface
				water supplies and for ground water supplies using surface water-type
				treatment, springs or infiltration lines, or water obtained from creviced rock
				aquifers with less than 50 feet of cover.
b) Contact time is measured as the time
				following filtration of surface or ground water, or chlorination of well water
				when there is no other treatment, and the time when the water reaches the first
				user.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart F - CHLORINATION › Section 653.604 - Distribution System Residuals

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				A minimum free chlorine residual of 0.2 mg/l or a minimum combined residual of
				0.5 mg/l shall be maintained in all active parts of the distribution system at
				all times.
b) Chlorine residual
				test shall be made at frequent and regular intervals to determine the amount
				and type of residuals existing at different points in the distribution
				system.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart F - CHLORINATION › Section 653.605 - Chlorination Operating Records

Current through Register Vol. 48, No. 28, July 12, 2024
a) A copy of the daily operating report
				records signed by the certified operator or registered person in responsible
				charge shall be submitted to the Illinois Environmental Protection Agency each
				month as required by 35 Ill. Adm. Code 606.101. These operating reports shall
				show:
1) amount of water pumped;
2) chlorine chemical used;
3) amount of chlorine chemical fed;
4) calculated chlorine dosage; and
5) residual chlorine test results.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart F - CHLORINATION › Section 653.606 - Exemptions From Chlorination - Satellite Supplies

Current through Register Vol. 48, No. 28, July 12, 2024
a) Satellite community water supplies are
				exempt from chlorination provided the requirements of Section
				653.604
				are met.
b) Chlorination facilities
				shall be installed and used:
1) whenever the
				chlorine residual in any active part of the distribution system drops below 0.2
				mg/l free or 0.5 mg/l combined; or
2) if daily operating report records of
				chlorine residuals are not kept and submitted to the Agency.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart F - CHLORINATION › Section 653.608 - Chlorination Exemption Revocation

Current through Register Vol. 48, No. 28, July 12, 2024
a) Chlorination exemptions are valid until
				revoked.
b) A chlorination
				exemption shall be revoked immediately without prior notice if a supply fails
				to meet any of the exemption requirements. An application for a Construction
				Permit for the installation of chlorination equipment shall be made within 60
				days following revocation. Chlorination equipment shall be installed and a
				properly certified operator shall be retained or an appeal filed with the
				Illinois Pollution Control Board within 90 days following revocation.
c) One or more of the following conditions
				will result in revocation:
1) increase in
				population to greater than 5000;
2)
				addition of a new source subject to contamination, or finding that an existing
				source is subject to contamination based on raw water bacteriological analyses
				records;
3) development of a
				history of recurring or persistent contamination as indicated by sampling
				results;
4) addition of treatment
				other than fluoridation (although a certified operator will not be required if
				the additional treatment consists of that designated in Ill. Rev. Stat. ch. 111
				1/2, par 509.1(f)(e) );
5) failure
				to maintain an active program of educating water consumers on prevention of
				contamination;
6) failure to have a
				certified operator or registered person for more than 15 days; or
7) failure to submit bacteriological samples
				twice a month during more than three months of the past 12 months or for two
				consecutive sampling periods. A supply which fails to monitor for
				bacteriological quality on a semi-monthly basis but does have one set of
				samples analyzed for each monthly sampling period will not be required to make
				public notice for the monitoring violation.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart G - FLUORIDATION › Section 653.701 - Fluoridation - Engineering Design Criteria

Current through Register Vol. 48, No. 28, July 12, 2024
a) Procedure for Submitting Plans and
				Specifications - Design documents for fluoridation shall be prepared and
				submitted in accordance with 35 Ill. Adm. Code 602.
b) Basis of Design - Equipment shall have the
				capacity to maintain the fluoride content in the finished water between 0.9 and
				1.2 mg/l.
c) Selection of Chemical
				- Fluoride compounds shall meet requirements of Section
				653.202 and the
				AWWA Standards.
d) Chemical Feed
				Equipment - Feeders shall be accessible for repair and maintenance, protected
				against dust hazard and be accessible to the chemical storage area.
1) Weighing scales for measuring the daily
				amount of chemicals shall be provided for dry feeders.
2) Scales or a volumetric device shall be
				provided for determining the amount of solution fed.
3) Dust collection equipment and ventilation
				shall be provided where loading operations may create dust hazards.
4) Corrosion-resistant containers with
				non-corrodible covers and over-hanging edges shall be provided for solution
				feeders. Openings shall be constructed to prevent contamination.
5) A free chlorine residual of 10 mg/l shall
				be maintained in solutions prepared from dry chemicals. This chlorine residual
				shall not replace the chlorination requirement of 35 Ill. Adm. Code
				604.401.
6) Chlorine shall not be
				added to hydrofluosilicic acid solutions.
7) Corrosion-resistant parts shall be used in
				the pump headers when hydrofluosilicic acid is fed.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart G - FLUORIDATION › Section 653.702 - Fluoridation Treatment Equipment Start-up

Current through Register Vol. 48, No. 28, July 12, 2024
a) Operating personnel shall be provided
				instructions for the use of the fluoridation equipment.
b) An Operating Permit shall be obtained
				prior to initiating operation of the fluoridation equipment. The Illinois
				Department of Public Health shall be notified as soon as fluoridation has been
				started.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart G - FLUORIDATION › Section 653.703 - Fluoride Sampling

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Samples shall be submitted monthly to the Illinois Environmental Protection
				Agency laboratory.
b) Sample
				containers will be furnished by the Illinois Environmental Protection
				Agency.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart G - FLUORIDATION › Section 653.704 - Fluoride Operating Records

Current through Register Vol. 48, No. 28, July 12, 2024
a) A copy of the daily operating report
				record signed by the certified operator or registered person in responsible
				charge shall be submitted to the Illinois Environmental Protection Agency each
				month as required by 35 Ill. Adm. Code 606.101. These operating reports shall
				show:
1) amount of water pumped;
2) fluoride chemical used;
3) amount of fluoride chemical fed;
4) gallons of dilution water used;
5) calculated fluoride dosage; and
6) fluoride ion test results.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart H - CROSS-CONNECTIONS › Section 653.801 - Cross-Connection Control Program

Current through Register Vol. 48, No. 28, July 12, 2024
An active cross-connection control program shall be adopted
				  and shall include the following:
a) A
				cross-connection control survey of the distribution system shall be conducted
				at least every two years by the official custodian or an authorized delegate.
1) The purpose of this survey is to compile
				and update an inventory of devices; the survey must consist of a pencil and
				paper collection of information, conducted by telephone, mail or personal visit
				to the manager or owner of a specific property.
2) This survey is not intended to include an
				actual visual inspection of piping or plumbing systems.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart H - CROSS-CONNECTIONS › Section 653.803 - Cross-Connection Control Devices

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				A fixed proper air gap shall be used whenever technically possible.
b) Atmospheric Vacuum Breakers may be
				installed subject to the following conditions:
1) An atmospheric vacuum breaker shall not be
				installed where back pressure may occur.
2) An atmospheric vacuum breaker shall be
				installed at the highest point in the waterline and after the last control
				valve before the point of discharge and a minimum of six inches above the flood
				level rim of the receptacle.
3) An
				atmospheric vacuum breaker shall not be used for installations where the
				substance in the container receiving water is lethal or toxic. Examples of
				acceptable installations include:
A) surface
				wash piping for a gravity filter;
B) solution tanks of gravimetric dry chemical
				feeders;
C) outlets with hose
				attachments; and
D) receptacles
				with a low level inlet where the substance contained is non-toxic such as food
				or beverages.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart H - CROSS-CONNECTIONS › Section 653.804 - Heat Exchange Cross-Connections

Current through Register Vol. 48, No. 28, July 12, 2024
a) Instantaneous water heaters or water
				storage heaters using shell and tube design steam-fired heat exhangers shall be
				acceptable for heating water for domestic use under the following conditions:
1) The purity of the steam supplied to the
				heat exchangers shall meet United States Food and Drug Administration (USFDA)
				requirements for steam that may contact food. Boiler water and steam condensate
				additivies shall meet requirements of USFDA regulation
				21 CFR
				173.310(1983).
2) Double check-valve assembly meeting
				requirements of Section
				653.801(d)
				 shall be installed in the cold water inlet
				piping of the heat exchanger. The unit shall be tested annually and required
				service performed within 15 days.
3) A maintenance log shall be maintained and
				include the information specified in Section
				653.802(e)(4).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 653 - DESIGN, OPERATION AND MAINTENANCE CRITERIA › Subpart H - CROSS-CONNECTIONS › Section 653.805 - Fire Protection Systems

Current through Register Vol. 48, No. 28, July 12, 2024
A reduced pressure principle backflow preventers shall be
				  installed to protect the community water supply against backflow and
				  backsiphonage when:
a) the fire safety
				system contains antifreeze, fire retardant or other chemicals;
b) water is pumped into the fire safety
				system from another source; or
c)
				water flows into the fire safety system by gravity from a non-potable source;
				or
d) there is a connection whereby
				water can be pumped into the fire safety system from any other
				source.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart A - RAW WATER QUALITY › Section 654.101 - Surface Water Quality

Current through Register Vol. 48, No. 28, July 12, 2024
Surface water shall be approved as a community water supply
				  source only if treatment to produce a finished water which meets the standards
				  of 35 Ill. Adm. Code 604 is provided.
a) Sampling shall be performed to determine
				treatment requirements. Representative samples shall be collected at least once
				a month over 12 consecutive periods to determine raw water quality.
b) More frequent sampling shall be required
				to obtain a true representation of raw surface water quality. Raw water
				characterisitics shall be determined after heavy rainfall and runoff, low
				stream flow and at other times when unusual factors pertaining to physical and
				chemical quality, treatability, tastes, and odors exist.
c) A 12 month running geometeric mean shall
				be used to calculate raw water bacteriological quality.
d) Complete treatment including coagulation,
				clarification, rapid sand filtration or its equivalent, and continuous
				post-chlorination shall be provided for all surface waters.
e) Auxiliary treatment shall be provided for
				waters containing coliform bacteria exceeding 5,000 per 100 milliters in more
				than 20% of the samples examined during any one month. Examples of auxiliary
				treatment are presedimentation, prechlorination and storage of raw water for 30
				days or more.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart A - RAW WATER QUALITY › Section 654.102 - Ground Water Quality

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Treatment equivalent to that described in Section
				654.101
				shall be provided for ground water sources subject to bacteriological
				contamination.
b) Ground waters
				which exceed the standards in 35 Ill. Adm. Code 604 shall be treated to comply
				with those standards.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart B - RAW WATER QUANTITY › Section 654.201 - Surface Water Quantity

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Determination of surface water source adequacy shall be based on:
1) catchment areas, stream flows and weather
				records;
2) safe yield;
3) maximum flood flows;
4) required water releases; and
5) evaporation, seepage and siltation
				losses.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart B - RAW WATER QUANTITY › Section 654.202 - Ground Water Quantity

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Ground water source adequacy shall be determined by the amount of water
				produced by each well pumping within its calculated safe yield.
b) Where multiple wells are used the combined
				delivery shall:
1) exceed the record maximum
				daily demand; and
2) equal or
				exceed the calculated average daily demand with the largest producing well out
				of service.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart B - RAW WATER QUANTITY › Section 654.203 - Combination of Ground and Surface Water

Current through Register Vol. 48, No. 28, July 12, 2024
a) Water sources consisting of a combination
				of ground water and surface water shall be evaluated according to Section
				654.201
				and
				654.202.
b) The adequacy of each source shall be
				calculated. The combined delivery shall exceed the record maximum daily
				demand.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart C - BACTERIOLOGICAL SAMPLES › Section 654.301 - Monthly Sampling Period

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				The term "monthly" refers to the designated sampling schedule which the Agency
				provides to each community water supply and does not necessarily correspond to
				a calendar month.
b) Samples
				collected before the designated beginning date shall be counted in the previous
				time period. Samples collected after the designated ending date shall be
				counted in the following time period.
c) Check samples, emergency samples and
				special purpose samples such as those taken to determine adequate disinfection
				after new construction or repair shall not be counted as part of the monthly
				total required by 35 Ill. Adm. Code 605.102.
d) Samples which cannot be analyzed (too old,
				no collection date, or other similar reasons) shall be replaced during the
				scheduled sampling period and the replacement samples shall be counted as part
				of the monthly total required by 35 Ill. Adm. Code 605.102.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart C - BACTERIOLOGICAL SAMPLES › Section 654.302 - Sampling Schedule

Current through Register Vol. 48, No. 28, July 12, 2024
a) A
				schedule for samples and sampling points shall be established jointly by the
				community water supply and the Agency. A minimum of 95% of the treated water
				samples shall be collected at representative points throughout all sections of
				the distribution system.
b) Samples
				submitted to certified laboratories shall be analyzed within the established
				sampling schedule and results submitted to the Agency within ten days of the
				close of the sampling period.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart C - BACTERIOLOGICAL SAMPLES › Section 654.303 - Finished Water Bacteriological Quality

Current through Register Vol. 48, No. 28, July 12, 2024
a) Compliance with 35 Ill. Adm. Code 604.102
				shall be determined using the following:
1)
				Confirmed negative sample results (no coliform present) shall be counted as
				zero when computing the monthly average.
2) Confirmed positive excessive growths shall
				be counted as 80 when computing the monthly average.
3) Confirmed positives shall be counted as
				the number recorded by the laboratory.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart C - BACTERIOLOGICAL SAMPLES › Section 654.304 - Additional Required Samples

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Check samples are required to verify an analysis showing
				contamination.
b) Check samples are
				required under the following conditions when the membrane filter technique is
				used:
1) four or more confirmed coliform
				colonies in a single sample;
2)
				excessive growth (confluent growth or too numerous to count) confirmed either
				positive or negative for coliform; or
3) one, two or three colonies of coliform in
				25% or more of the samples analyzed.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart D - CHEMICAL AND TURBIDITY SAMPLES › Section 654.401 - Chemical Samples

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Chemical samples shall be submitted to an Agency laboratory within ten days
				following receipt of the sample containers. The Agency shall be notified and an
				agreement reached to establish a more appropriate sampling time if submission
				within ten days is not possible.
b)
				Chemical samples shall be collected during normal water plant operation.
				Finished water chemical samples shall be collected from a free-flowing tap at a
				representative point in the distribution system.
c) A new sample will be required if
				analytical results do not balance chemically. This resample shall be indicated
				by an "R" on the report sheet and must be submitted to the laboratory within
				ten days.
d) Public notice shall be
				made in accordance with 35 Ill. Adm. Code Part 606: Subpart B if required
				samples are not submitted.
e)
				Chemical sampling requirements, other than for trihalomethanes, shall not be
				required for satellite community water supplies, unless they provide additional
				treatment, other than chlorination.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart D - CHEMICAL AND TURBIDITY SAMPLES › Section 654.402 - Turbidity Samples

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Owners and operators of community water supplies utilizing surface water
				sources shall sample at representative entry points to the distribution system
				at least once per day, and make an immediate turbidity analysis of each sample.
1) Samples shall be tested by a specific
				individual approved by the Agency to conduct turbidity analyses.
2) A turbidity monitoring report shall be
				submitted to the Agency within ten days after the close of the month.
3) Daily turbidity records shall be
				maintained in accordance with 35 Ill. Adm. Code
				607.106.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart D - CHEMICAL AND TURBIDITY SAMPLES › Section 654.403 - Recommended Finished Water Contaminant Concentrations

Current through Register Vol. 48, No. 28, July 12, 2024
It is recommended that concentrations of constituents listed
				  in Table A not be exceeded in the finished water.
Table A - SECONDARY MAXIMUM CONTAMINANT LEVELS
FOR FINISHED WATER
Contaminant
Reported As
Level
mg/l*
Chloride
Cl
250.
Color
Color Units
15. C.U.
Copper
Cu
1.
Foaming Agents
MBAS
0.5
Hydrogen Sulfide
H2S
0.05
Iron
Fe
0.3
Manganese
Mn
0.05
Odor
Threshold Odor Number
3. T.O.N.
Sulfate
SO4
250.
Total Dissolved Solids
TDS
500.
Zinc
Zn
5.
* Unless otherwise indicated.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 654 - RAW AND FINISHED WATER QUALITY AND QUANTITY › Subpart E - RADIOLOGICAL SAMPLES › Section 654.501 - Samples for New Sources and Supplies

Current through Register Vol. 48, No. 28, July 12, 2024
Monitoring of the Distribution system in accordance with 35
				  Ill. Adm. Code 604: Subpart C, shall begin one year after:
a) a new community water supply is developed;
				or
b) a community water supply
				begins using an additional source.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 660 - PROCEDURES FOR ISSUING GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart A - INTRODUCTION › Section 660.101 - Purpose

Current through Register Vol. 48, No. 28, July 12, 2024
a) Section 4(v) of
				the Environmental Protection Act (Ill. Rev. Stat. 1986 Supp., ch. 1111/2, par.
				1004(v), as added by P.A. 85-288, effective September 8, 1987) authorizes the
				Illinois Environmental Protection Agency ("Agency") to distribute grants
				subject to appropriation by the general assembly, to units of local government
				for financing and construction of public water supply facilities. With respect
				to all monies appropriated from the build Illinois bond fund or the build
				Illinois purposes fund for public water supply grants, such grants shall be
				made in accordance with rules promulgated by the agency.
b) The rules forth in this Part constitute
				the procedures which apply to any grant to units of local government for
				financing and construction of public water supply facilities.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 660 - PROCEDURES FOR ISSUING GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart A - INTRODUCTION › Section 660.102 - Definitions

Current through Register Vol. 48, No. 28, July 12, 2024
Unless specified otherwise, all terms shall have the meanings
				  set forth in the Environmental Protection Act (Ill. Rev. Stat. 1985, ch. 111
				  1/2, pars. 1001 et seq., as amended) ("the Act"), 35 Ill. Adm. Code
				  661.102,
				  and 35 Ill. Adm. Code 601.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 660 - PROCEDURES FOR ISSUING GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart A - INTRODUCTION › Section 660.103 - Severability

Current through Register Vol. 48, No. 28, July 12, 2024
If any provision of this Part or the application thereof to
				  any person or in any circumstances is adjudged invalid, such adjudication shall
				  not affect the validity of this Part as a whole or any provision thereof not
				  adjudged invalid.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 660 - PROCEDURES FOR ISSUING GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - PROCEDURES › Section 660.201 - General

Current through Register Vol. 48, No. 28, July 12, 2024
a) The Agency will
				not award a grant unless an appropriation has been made for the project by the
				General Assembly and approved by the Governor.
b) The Agency will award grants to fund only
				allowable, eligible project costs as described in 35 Ill. Adm. Code
				661.701.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 660 - PROCEDURES FOR ISSUING GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - PROCEDURES › Section 660.202 - Applications for Grants Under Section 4(v) of the Act

Current through Register Vol. 48, No. 28, July 12, 2024
a) Applicants shall apply for grants on forms
				prescribed by the Agency.
b) Except
				as provided otherwise in Section
				660.203,
				the Agency will not award a grant unless the applicant:
1) Applies for the grant on forms prescribed
				by the Agency; and
2) Provides the
				documents described in subsection (c).
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 660 - PROCEDURES FOR ISSUING GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - PROCEDURES › Section 660.203 - Deferral of Document Submission

Current through Register Vol. 48, No. 28, July 12, 2024
a) Upon written request of the applicant, the
				Director will defer the submission of any or all of the documents described
				Section
				660.201(c)(2) through
				(c)(7) if the Director finds in writing that
				such documents are not needed for purposes of awarding the grant.
b) As a special condition of the grant, the
				Director shall establish a schedule consistent with 35 Ill. Adm. Code
				661.401 for
				the submission by the grantee of any document deferred under subsection
				(a).
c) The Agency shall not grant
				approval of formal advertising under 35 Ill. Adm. Code
				661.302(e)
				 until all documents deferred under
				subsection (a) have been submitted to the Agency.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 661 - GENERAL CONDITIONS OF GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart A - INTRODUCTION › Section 661.101 - Purposes

Current through Register Vol. 48, No. 28, July 12, 2024
a) Sections 4(k),
				4(x)(1), and 4(x)(2) 4 of the Environmental Protection Act [
				415
				ILCS 5/4(k), 415 ILCS 5/4(x)(1),
				415
				ILCS 5/4(x)(2) ] authorize the
				Illinois Environmental Protection Agency ("Agency")
to distribute
				grants, subject to appropriation by the general assembly, to units of local
				government for financing and construction of public water supply facilities.
				With respect to all monies appropriated from the
Build
Illinois Bond Fund or the Build Illinois Purposes Fund for public water
				supply grants, such grants shall be made in accordance with rules promulgated
				by the Agency
.
b) The
				rules set forth in this Part constitute conditions that apply to any grant to
				units of local government for financing and construction of public water supply
				facilities.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 661 - GENERAL CONDITIONS OF GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart A - INTRODUCTION › Section 661.103 - Severability

Current through Register Vol. 48, No. 28, July 12, 2024
If any provision of this Part or the application thereof to
				  any person or in any circumstance is adjudged invalid, such adjudication shall
				  not affect the validity of this Part as a whole or any provision thereof not
				  adjudged invalid.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 661 - GENERAL CONDITIONS OF GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - LIABILITIES AND REMEDIES FOR FAILURE TO COMPLY WITH GRANT CONDITIONS › Section 661.201 - Noncompliance with Grant Conditions

Current through Register Vol. 48, No. 28, July 12, 2024
a) In the event of noncompliance with any
				condition imposed pursuant to a grant, the Director shall take one or more of
				the following actions:
1) Commence legal
				action in a court of competent jurisdiction (e.g., to obtain an injunction or
				to recover in fraud);
2) Annul the
				grant and recover all grant funds pursuant to the Illinois Grant Funds Recovery
				Act [ 30 ILCS 705 ];
3) Terminate
				the grant pursuant to Section
				661.203;
4) Suspend all or part of the project work
				pursuant to Section
				661.202;
				or
5) Take other action as provided
				by law, including, but not limited to, reducing the amount of the grant by the
				amount of misused funds or disallow costs in accordance with Section
				661.701.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 661 - GENERAL CONDITIONS OF GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - LIABILITIES AND REMEDIES FOR FAILURE TO COMPLY WITH GRANT CONDITIONS › Section 661.202 - Stop-Work Order

Current through Register Vol. 48, No. 28, July 12, 2024
a) The
				Agency may, for any violation of this Part or for any violation of a special
				condition set forth in the grant, by written order to the grantee, require the
				grantee to stop all or any part of the project work for a period of not more
				than 30 days after the date of the order, and for any further period to which
				the parties may agree. Any such order shall be specifically identified as a
				stop-work order issued pursuant to this clause. Any such order shall include a
				list of the project activities to which the stop-work order shall apply. Upon
				receipt of such an order, the grantee shall forthwith comply with its terms and
				take all reasonable steps to minimize the incurrence of costs allocable to the
				work covered by the order during the period of work stoppage. Within a period
				of not more than 30 days of the date of the stop-work order, or within any
				extension of that period to which the parties shall have agreed, the Agency
				shall either:
1) Cancel the stop-work order
				upon the resolution of the violations leading to the stop-work order;
				or
2) Terminate the work covered by
				such order as provided in Section
				661.203 if
				the violations are not resolved.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 661 - GENERAL CONDITIONS OF GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - LIABILITIES AND REMEDIES FOR FAILURE TO COMPLY WITH GRANT CONDITIONS › Section 661.203 - Termination

Current through Register Vol. 48, No. 28, July 12, 2024
a) Grant
				Termination by Agency
The Agency, by written notice and after consultation with the
				  grantee, may terminate the grant. Cause for termination shall include, but not
				  be limited to: default (inability or unwillingness to perform under this Part)
				  by the grantee, failure by the grantee to comply with the terms and conditions
				  of the grant, lack of adequate funding, or advancements in the state of the
				  art. Upon termination, the grantee shall refund to the State of Illinois any
				  unexpended grant funds, except that portion required by the grantee to make
				  payment for materials and equipment furnished or services rendered under an
				  enforceable contract prior to the effective date of the termination and further
				  provided that those costs are otherwise allowable under Section
				  661.701
				  and under the conditions of the grant.
b) Project Termination by Grantee
The grantee may not terminate a project for which the grant
				  has been awarded, except for good cause. Good cause for termination shall
				  include, but not be limited to, realignment of programs, change in program
				  requirements or priorities, lack of adequate funding, or advancement in the
				  state of the art. If the Agency finds that there is good cause for the
				  termination of all or any portion of a project for which the grant has been
				  awarded, it shall enter into a termination agreement or unilaterally terminate
				  the grant, effective with the date of termination of the project by the
				  grantee. Any termination agreement shall include special conditions for the
				  termination of the grant. If the Agency finds that the grantee has terminated
				  the project without good cause, then the grant shall be annulled and all grant
				  funds previously paid or owing to the grantee shall be returned to the State of
				  Illinois.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 661 - GENERAL CONDITIONS OF GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - LIABILITIES AND REMEDIES FOR FAILURE TO COMPLY WITH GRANT CONDITIONS › Section 661.204 - Waiver of Conditions

Current through Register Vol. 48, No. 28, July 12, 2024
a)
				Except as provided otherwise in subsection (b), if the requirement waived is
				not considered by the Director to be necessary to insure the integrity of the
				project, upon written request of the grantee, the Director shall waive any or
				all of the conditions required by this Part, either in whole or in part, with
				respect to any grant offer, by a statement made in writing to the grantee as a
				special condition of the grant offer and the waiver made subject to such
				additional conditions as the Director may deem necessary based upon the
				waiver.
b) The Director may not
				waive any conditions set forth in Section
				661.407
				and Section
				661.705.
Illinois Administrative Code › Title 35 - ENVIRONMENTAL PROTECTION › Part 661 - GENERAL CONDITIONS OF GRANTS FOR THE FINANCING AND CONSTRUCTION OF PUBLIC WATER SUPPLY FACILITIES › Subpart B - LIABILITIES AND REMEDIES FOR FAILURE TO COMPLY WITH GRANT CONDITIONS › Section 661.205 - Covenant Against Contingent Fees

Current through Register Vol. 48, No. 28, July 12, 2024
The grantee must warrant that no person or agency has been
				  employed or retained to solicit or secure this grant upon an agreement or
				  understanding for a commission, percentage, brokerage, or contingent
				  fee.