reglab/statecodes huggingface dataset:
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.013 - Emergency Lighting

Current through Reg. 50, No. 138; July 16, 2024
(1) Emergency
				lighting shall be provided in all residential child care facilities, except
				wilderness programs campsites.
(2)
				Residential child care facilities in which the total number of resident
				children is fewer than 9 need not comply with subsection (1). However, this
				exception does not apply to emergency shelter care, or to runaway and transient
				youth shelters.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206(1)(b)
					 FS.
New 7-2-84, Formerly 4A-41.13, Amended 9-24-90, 7-11-01,
					 Formerly 4A-41.013.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.014 - Segregation and Protection from Hazards

Current through Reg. 50, No. 138; July 16, 2024
(1) Commercial cooking equipment shall have
				hood systems installed in accordance with NFPA 96, Standard for Ventilation
				Control and Fire Protection of Commercial Cooking Equipment as adopted in Rule
				 69A-3.012, F.A.C.
(2) Flammable/combustible liquids.
(a) Flammable and/or combustible liquids
				shall be limited to that required for maintenance and for any equipment
				necessary to the operation of the facility and shall be stored in approved,
				closed and appropriately marked containers.
(b) If either flammable or combustible
				liquids in excess of 10 gallons in the aggregate are stored or dispensed on the
				premises of the facility, the facility shall comply with Chapter 4 of NFPA 30
				Flammable and Combustible Liquids Code, the edition as adopted in Rule
				 69A-3.012, F.A.C.
(c) Notwithstanding the foregoing provisions,
				any hazardous operation or process may be conducted without protection in a
				detached structure sufficiently remote from the main building to avoid any
				danger to the occupants of the main building except that any protection
				necessary for the safety of the occupants of the detached structure must be
				provided. The detached structure shall be a minimum of 10 feet from any other
				occupied structures.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.016 - Furnishings and Decorations

Current through Reg. 50, No. 138; July 16, 2024
(1) All
				residential child care facilities in which security is required shall use only
				mattresses having a fire retardant cotton core with a retardant outer
				cover.
(2) Polyurethane mattresses
				are prohibited in all residential child care facilities.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206(1)(b)
					 FS.
New 7-2-84, Formerly 4A-41.16, Amended 9-24-90, 7-11-01,
					 Formerly 4A-41.016.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.017 - Portable Fire Extinguishers

Current through Reg. 50, No. 138; July 16, 2024
Residential child care facilities shall have at least one
				  general purpose Class A, B, and C portable fire extinguisher for each floor.
				  All required extinguishers shall have a minimum rating of 2A-10B:C and shall be
				  placed so that the nearest extinguisher is not more than 75 feet from any other
				  point in the facility.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206(1)(b)
					 FS.
New 7-2-84, Formerly 4A-41.17, Amended 9-24-90, 7-11-01,
					 Formerly 4A-41.017.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.019 - Alarm and Detection Requirements

Current through Reg. 50, No. 138; July 16, 2024
(1)
				Smoke Detectors installed in existing residential child care facilities having
				16 or fewer residents may continue to be battery powered, single station, UL217
				detectors.
(2) Fire Alarms
				installed in existing residential child care facilities with 16 or fewer
				residents may continue to be manually operated, powered by the building
				electrical service, but it is not required to be electrically
				supervised.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206(1)(b)
					 FS.
New 7-2-84, Formerly 4A-41.19, Amended 9-24-90, 7-11-01,
					 Formerly 4A-41.019.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.020 - Building Services and Equipment

Current through Reg. 50, No. 138; July 16, 2024
(1)
				Unvented fuel-fired room heaters shall not be used in residential child care
				facilities.
(2) Other heating
				equipment shall be of an approved type and shall be installed in accordance
				with the terms of its approval and with the manufacturer's instructions, and
				meet the requirements of NFPA 101, 2000 edition, Section 9-2, as adopted in
				rule Chapter 69A-60, F.A.C.
(3) No
				stove or combustion heater shall be so located as to block escape in case of
				malfunctioning of the stove or heater.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206(1)(b)
					 FS.
New 7-2-84, Formerly 4A-41.20, Amended 9-24-90, 7-11-01,
					 Formerly 4A-41.020.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.022 - Storage, Trash, or Debris Underneath Structures

Current through Reg. 50, No. 138; July 16, 2024
Any structure situated above the ground level shall not have
				  an accumulation of combustible storage, trash, or debris underneath the
				  structure. Any area between the ground and the bottom of the structure shall be
				  covered, shielded, skirted, or otherwise protected to preclude this
				  occurrence.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206
					 FS.
New 7-2-84, Formerly 4A-41.22, Amended 9-24-90, Formerly
					 4A-41.022.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.023 - Tents

Current through Reg. 50, No. 138; July 16, 2024
Tents shall be erected only outside of buildings or
				  structures. All tents shall be fire retardant whether used for living, shade,
				  recreation, education or any other purpose. It is the proprietor's
				  responsibility to produce proof of the fire retardant properties of the tent
				  material upon request.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206
					 FS.
New 7-2-84, Formerly 4A-41.23, Amended 9-24-90, Formerly
					 4A-41.023.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.024 - Fire Exit Drills

Current through Reg. 50, No. 138; July 16, 2024
Unless otherwise authorized by the authority having
				  jurisdiction, as defined in Section
				   633.118, F.S., fire exit drills
				  shall be held with sufficient frequency to familiarize all occupants with the
				  drill procedure and to have the conduct of the drill a matter of established
				  routine. They shall be conducted no less frequently than once per month and
				  shall be properly documented.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206(1)(b)
					 FS.
New 7-2-84, Formerly 4A-41.24, Amended 9-24-90, 7-11-01,
					 Formerly 4A-41.024.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.025 - Fire and Emergency Plan

Current through Reg. 50, No. 138; July 16, 2024
Each residential child care facility shall develop a written
				  fire and emergency evacuation plan which may include input from the authority
				  having jurisdiction as described in Section
				   633.118, F.S.
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104(1),
					 633.206(1)(b)
					 FS.
New 7-2-84, Formerly 4A-41.25, Amended 9-24-90, 7-11-01,
					 Formerly 4A-41.025.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.101 - Scope

Current through Reg. 50, No. 138; July 16, 2024
(1) These rules apply to any residential
				child care facility required to be licensed by the Florida Department of
				Children and Families, pursuant to Section
				 409.175, F.S., in which
				full-time residence is provided to five or fewer children who are unrelated to
				the proprietor and who are under age 18. Programs which use such a facility
				include, for example, group homes which are administered by an agency,
				wilderness camps, maternity homes, emergency shelters, and runaway
				shelters.
(2) These rules address
				life safety during fires and similar emergencies. They address particular
				matters of construction, protection, and occupancy of buildings to minimize
				danger to life from fire, smoke, fumes or panic before buildings are
				vacated.
Rulemaking Authority
					 633.104(1) FS.
					 Law Implemented 633.206(1)(b)
					 FS.
New 9-17-03, Formerly
					 4A-41.101.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.102 - Definitions

Current through Reg. 50, No. 138; July 16, 2024
As used in this part of these rules:
(1) "Facility" means a residential child
				caring agency, a child placing agency, or a "Family Foster Home," as defined in
				Section  409.175(2),
				F.S.
(2) "Agency" means a
				residential child caring agency or a child-placing agency.
(3) "AHJ" means the local authority having
				firesafety and fire prevention jurisdiction which employs or contracts with at
				least one firesafety inspector certified under Chapter 633, F.S.
(4) "Division" means the Division of State
				Fire Marshal of the Department of Financial Services.
(5) "NFPA" means the National Fire Protection
				Association.
(6) "Child" means any
				unmarried person under the age of 18 years.
(7) "Owner" means the person who is licensed
				to operate the child-placing agency, family foster home, or residential
				child-caring agency.
Rulemaking Authority
					 633.104(1) FS.
					 Law Implemented 633.206
					 FS.
New 9-17-03, Formerly
					 4A-41.102.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.103 - Standards of the National Fire Protection Association Adopted

Current through Reg. 50, No. 138; July 16, 2024
(1) The following portions of NFPA 101, known
				as the Life Safety Code, current edition, adopted in rule Chapter 69A-60,
				F.A.C., are hereby adopted and incorporated herein by reference:
(a) Section 24.2.1;
(b) Section 24.2.2, except that an approved
				means of escape shall be equivalent to an outside window or door which shall be
				openable from the inside, without the use of tools or a key and shall provide a
				clear opening of not less than 22 inches in the least dimension and a minimum
				of 5 square feet in area. The bottom of the opening shall be not more than 48''
				above the finished floor;
(c)
				24.2.3, 24.2.4, 24.3.4, 24.3.4.1, and 24.3.4.3.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.104 - Occupancy Capacity of Each Facility

Current through Reg. 50, No. 138; July 16, 2024
The total number of children shall be as determined in
				  accordance with Section
				   409.175(3)(a),
				  F.S.
Rulemaking Authority
					 633.104(1) FS.
					 Law Implemented 633.206(1)(b)
					 FS.
New 9-17-03, Formerly
					 4A-41.104.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.105 - Emergency Egress and Relocation Drills

Current through Reg. 50, No. 138; July 16, 2024
(1) An emergency egress and relocation drill
				shall be conducted by each owner at each facility at least three (3) times per
				year. Each emergency egress and relocation drill shall be conducted at least 90
				days after the previous emergency egress and relocation drill. The AHJ is
				permitted to require an additional emergency egress and relocation drill in
				conjunction with an annual firesafety inspection.
(2) The purpose of each emergency egress and
				relocation drill is to familiarize each occupant with the procedures required
				for the safe, orderly, and expeditious exiting of the building or structure.
				All occupants shall exit the building or structure to a predetermined area of
				safety. The climate and weather conditions shall be taken into consideration
				when scheduling any emergency egress and relocation drill.
(3) Each emergency egress and relocation
				drill shall be conducted at an unexpected time and under varying conditions
				that may occur in the case of fires.
(4) During each emergency egress and
				relocation drill, all occupants shall evacuate the building independently or
				with staff assistance or any other available assistance, as needed.
(5) Each emergency egress and relocation
				drill shall be applicable to all occupants of the facility with emphasis on the
				safe, orderly, and expeditious exiting under proper discipline.
(6) Any occupant subject to an emergency
				egress and relocation drill shall proceed to a predetermined location outside
				the building and remain there until all occupants are accounted for. Occupants
				are permitted to return to the building only when allowed by the person
				conducting the emergency egress and relocation drill.
(7) The owner shall keep a record of each
				emergency egress and relocation drill on Form DFS-K3-1557, (rev. 3/20/03),
				Record of Emergency Egress and Relocation Drills, which is hereby adopted and
				incorporated into these rules by reference. Copies of the form may be obtained
				by writing to the Department of Financial Services, Division of State Fire
				Marshal, Bureau of Fire Prevention, 200 East Gaines Street, Tallahassee,
				Florida 32399-0342. The record shall list as a minimum:
(a) The date the drill was
				conducted.
(b) The time of day the
				drill was conducted.
(c) The amount
				of time, in minutes and seconds, that were required for all occupants to safely
				exit the building.
(d) Any unusual
				circumstance, in narrative or outline form, affecting the safe, orderly and
				expeditious exit from the building.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.106 - Inspections

Current through Reg. 50, No. 138; July 16, 2024
(1) The appropriate firesafety inspector
				shall conduct a firesafety inspection, which must be determined to be
				satisfactory for each facility prior to its initial licensure and prior to the
				annual renewal of its license.
(2)
				The owner shall request from the AHJ a firesafety inspection at least 30 days
				in advance of license expiration.
(3) The AHJ or the Division is permitted to
				require additional firesafety inspections.
(4) The owner shall be responsible for
				requesting all required firesafety inspections in writing or electronic format,
				except for any additional firesafety inspections which may be required as
				provided in subsection (3). All verbal inspection requests shall be followed by
				a written or electronic verification.
(5) Each required firesafety inspection shall
				be completed by the AHJ, where available.
(6) Any time there is no AHJ to perform a
				firesafety inspection, the owner shall notify the Division in writing or in an
				electronic format. The Division shall inspect or cause the facility to be
				inspected in accordance with Section
				 633.206, F.S.
(7) A local firesafety inspector, or if no
				local firesafety inspector is available, a special state firesafety inspector,
				certified in accordance with Chapter 633, F.S., shall complete each required
				firesafety inspection.
(8) The
				inspecting authority shall provide a copy of each inspection report to the
				licensing agency within thirty days after completing the inspection.
(9) For the purpose of meeting the fire
				safety inspection requirements of this subsection, a family foster home shall
				comply with the following:
(a) Install smoke
				detectors in accordance with Section 24.3.4.1 of NFPA 101, current edition,
				adopted in rule chapter 69A-60, F.A.C.;
(b) Fireplaces, heaters, radiators and other
				hot surfaces shall be shielded against accidental contact;
(c) Sleeping rooms shall have a primary and
				secondary means of escape in accordance with paragraph
				 69A-41.103(1)(b),
				F.A.C.;
(d) All heating appliances
				and other heating devices shall be properly vented;
(e) Emergency evacuation instructions must be
				posted in a conspicuous location;
(f) Conduct emergency egress and relocation
				drills in accordance with Rule
				 69A-41.105, F.A.C.;
(g) Be free of improperly stored combustible
				materials;
(h) All exits and stairs
				shall be free of storage or obstructions affecting its use;
(i) Be free of temporary electrical
				wiring;
(j) Have at least one
				working flashlight for each sleeping room;
(k) Comply with Rules
				 69A-41.107 and
				 69A-41.108,
				F.A.C.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.107 - Cooking Equipment; Exception

Current through Reg. 50, No. 138; July 16, 2024
Notwithstanding any previous construction or interpretation
				  of any law, rule, or code provision, any time a single domestic range or stove
				  is used in an arrangement similar to that of a single family residence, the
				  facility shall not be required to comply with NFPA 96, Standard for Ventilation
				  Control and Fire Protection of Commercial Cooking Operations, the edition as
				  adopted in Rule  69A-3.012,
				  F.A.C.
Rulemaking Authority
					 633.104(1) FS.
					 Law Implemented 633.206(1)(b)
					 FS.
New 9-17-03, Formerly
					 4A-41.107.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-41 - UNIFORM FIRE SAFETY STANDARDS FOR RESIDENTIAL CHILD CARE FACILITIES › Section 69A-41.108 - Special Requirements

Current through Reg. 50, No. 138; July 16, 2024
(1) Each
				facility shall have installed at least one portable fire extinguisher with a
				minimum rating of 2A-10BC.
(2) No
				unvented fuel-fired heaters shall be permitted unless the heater is listed and
				approved for such use.
Rulemaking Authority
					 633.104(1) FS.
					 Law Implemented 633.206(1)(b)
					 FS.
New 9-17-03, Formerly
					 4A-41.108.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-42 - UNIFORM FIRE SAFETY STANDARDS FOR MOBILE HOME PARKS AND RECREATIONAL VEHICLE PARKS › Section 69A-42.001 - Title

Current through Reg. 50, No. 138; July 16, 2024
The rules comprising rule chapter 69A-42, F.A.C., shall be
				  known as the "Uniform Fire Safety Standards for Mobile Home Parks and
				  Recreational Vehicle Parks."
Rulemaking Authority
					 633.104 FS. Law Implemented
					 633.104,
					 633.206
					 FS.
New 5-1-84, Formerly 4A-42.01, Repromulgated 8-1-90,
					 Formerly 4A-42.001.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-42 - UNIFORM FIRE SAFETY STANDARDS FOR MOBILE HOME PARKS AND RECREATIONAL VEHICLE PARKS › Section 69A-42.002 - Purpose

Current through Reg. 50, No. 138; July 16, 2024
The purpose of these rules is to establish uniform
				  requirements that will provide a reasonable degree of safety from fire in
				  mobile home parks and recreational vehicle parks. These rules apply to both
				  existing and new mobile home parks and recreational vehicle parks, except that
				  the provisions of section
				   633.104(4),
				  F.S., are specifically applicable to existing mobile home parks. These rules
				  try to avoid requirements that might result in unreasonable hardships or
				  unnecessary inconveniences or interference with the normal use of the
				  facilities.
Rulemaking Authority
					 633.206(1)(b)
					 FS. Law Implemented 633.104(1),
					 633.206
					 FS.
New 5-1-84, Formerly 4A-42.02, Amended 8-1-90, 9-6-01,
					 Formerly 4A-42.002.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-42 - UNIFORM FIRE SAFETY STANDARDS FOR MOBILE HOME PARKS AND RECREATIONAL VEHICLE PARKS › Section 69A-42.003 - Definitions

Current through Reg. 50, No. 138; July 16, 2024
As used in this rule chapter, unless the context clearly
				  requires otherwise.
(1) "Authority
				Having Jurisdiction" shall mean a duly authorized representative of an agency
				or agencies having legal enforcement authority, as described in section
				 633.118, F.S.
(2) "Approved" shall mean materials, devices,
				construction, and/or installations accepted by the authority having
				jurisdiction under the provisions of these rules by reason of tests or
				investigations conducted by it or by an agency satisfactory to the authority,
				based upon nationally accepted test standards or principles.
(3) "Mobile Home" shall have the same meaning
				as "Manufactured Home" set forth in NFPA 501A, adopted by reference in rule
				 69A-3.012, F.A.C.
(4) "Mobile Home Park" shall mean a place set
				aside and offered by a person or public body for the parking or accommodation
				of six or more mobile homes utilized for sleeping or eating for either direct
				or indirect remuneration to the owner, lessor, or operator of such
				place.
(5) "Recreational Vehicle
				Park" shall mean a place set aside and offered by a person or public body for
				the parking and accommodation of six or more recreational vehicles utilized for
				sleeping or eating for either direct or indirect remuneration to the owner,
				lessor, or operator of such place, and also includes buildings and sites set
				aside for group camping and similar recreational
				facilities.
Rulemaking Authority
					 633.104(1),
					 633.206(1)(b)
					 FS. Law Implemented 633.206
					 FS.
New 5-1-84, Formerly 4A-42.03, Amended 8-1-90, 9-6-01,
					 Formerly 4A-42.003, Amended 10-19-09.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-42 - UNIFORM FIRE SAFETY STANDARDS FOR MOBILE HOME PARKS AND RECREATIONAL VEHICLE PARKS › Section 69A-42.004 - Discretionary Powers of the Authority Having Jurisdiction

Current through Reg. 50, No. 138; July 16, 2024
The authority having jurisdiction may modify these rules
				  under the following conditions:
(1)
				Any modification to this rule chapter must be in strict conformance with this
				section. No currently placed mobile home shall be displaced unless it is
				clearly evident in the opinion of the authority having jurisdiction that there
				is a threat of imminent danger to the health, safety or welfare of the general
				public.
(2) The authority having
				jurisdiction may allow alternative arrangements to accomplish this degree of
				safety, but in no case shall the modification afford less safety to life than
				compliance with the corresponding provisions contained in these rules for
				existing buildings.
(3) Nothing in
				these rules is intended to prevent the use of systems, methods, or devices of
				equivalent or superior quality, strength, fire resistance, effectiveness,
				durability, and safety to those prescribed by the authority having jurisdiction
				so long as the system, method, or device is of demonstrated equivalency and is
				approved for the intended purpose.
Rulemaking Authority
					 633.104(1),
					 633.206(1)(b)
					 FS. Law Implemented 633.104(4),
					 633.206
					 FS.
New 5-1-84, Formerly 4A-42.04, Repromulgated 8-1-90,
					 Formerly 4A-42.004, Amended 10-19-09.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-42 - UNIFORM FIRE SAFETY STANDARDS FOR MOBILE HOME PARKS AND RECREATIONAL VEHICLE PARKS › Section 69A-42.0041 - Fire Separation Requirements

Current through Reg. 50, No. 138; July 16, 2024
No portion of a mobile home, excluding the tongue, shall be
				  located closer than 10 ft. (3m) side to side, 8 ft. (2.4m) end to side, or 6
				  ft. (1.8m) end to end horizontally from any other mobile home or community
				  building unless the exposed composite walls and roof of either structure are
				  without opening and constructed of materials that will provide a one-hour fire
				  resistance rating or the structures are separated by a one-hour fire-rated
				  barrier.
Rulemaking Authority
					 633.104(1),
					 633.206(1)(b)
					 FS. Law Implemented 633.104(4),
					 633.206
					 FS.
New 10-19-09.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-42 - UNIFORM FIRE SAFETY STANDARDS FOR MOBILE HOME PARKS AND RECREATIONAL VEHICLE PARKS › Section 69A-42.005 - Standards of the National Fire Protection Association Adopted

Current through Reg. 50, No. 138; July 16, 2024
(1) National Fire Protection Association
				501A, "Standard for Fire Safety Criteria for Manufactured Home Installations,
				Sites, and Communities," and 1194, "Standard for Fire Safety Criteria for
				Recreational Vehicle Parks and Campgrounds," adopted in rule
				 69A-3.012, F.A.C., shall be the
				governing standards, except as modified in this rule chapter.
(2) The codes and standards published by the
				National Fire Protection Association may be obtained by writing to the NFPA at:
				1 Batterymarch Park, Quincy, Massachusetts 02169-7471. All standards adopted
				and incorporated by reference in this rule are also available for public
				inspection during regular business hours at the Bureau of Fire Prevention,
				Division of State Fire Marshal, Department of Financial Services, 325 John Knox
				Road, The Atrium, Third Floor, Tallahassee, Florida 32303.
Rulemaking Authority
					 633.104(1),
					 633.206(1)(b)
					 FS. Law Implemented 633.206
					 FS.
New 5-1-84, Formerly 4A-42.05, Amended 8-1-90, 9-6-01,
					 Formerly 4A-42.005, Amended 10-19-09.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.001 - Title

Current through Reg. 50, No. 138; July 16, 2024
These rules, comprising rule Chapter 69A-43, F.A.C., shall be
				  known as "The Uniform Fire Safety Standards for Transient Public Lodging
				  Establishments, Timeshare Plans, or Timeshare Unit
				  Facilities."
Rulemaking Authority
					  509.215,
					 633.104,
					 633.206(1)(b),
					 721.24(5) FS.
					 Law Implemented 509.215,
					  633.104(1),
					  633.206(1)(b),
					  721.24(5) 
					 FS.
New 11-12-85, Formerly 4A-43.01, Amended 5-14-91, 9-6-01,
					 Formerly 4A-43.001.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.002 - Purpose

Current through Reg. 50, No. 138; July 16, 2024
The purpose of this rule chapter is to specify measures to be
				  used in conjunction with Sections
				   509.215 and
				   721.24, F.S., to provide a
				  reasonable degree of public safety from fire in transient public lodging
				  establishments, or any transient facility or accommodation of a "time-share
				  plan" or "time share unit." These rules try to avoid requirements which might
				  result in unreasonable hardships, or unnecessary inconvenience, or interference
				  with the normal use and occupancy of a building, but at the same time insist
				  upon compliance with a uniform standard for life safety necessary in the public
				  interest.
Rulemaking Authority
					 509.215,
					 633.104,
					 721.24(5) FS.
					 Law Implemented 509.215,
					 633.206,
					 721.24
					 FS.
New 11-12-85, Formerly 4A-43.02, Amended 5-14-91, Formerly
					 4A-43.002.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.003 - Scope

Current through Reg. 50, No. 138; July 16, 2024
These rules apply to any transient public lodging
				  establishment as defined and licensed by the Department of Business and
				  Professional Regulation under Sections
				   509.013(4) and
				  (11), F.S., and any time-share unit or
				  time-share plan as defined in Sections
				   721.05(39) and
				  (41), F.S.
Rulemaking Authority
					  509.215,
					 633.104,
					 633.206(1)(b),
					 721.24(5) FS.
					 Law Implemented 509.215,
					  633.104(1),
					  633.206(1)(b),
					  721.24(5) 
					 FS.
New 11-12-85, Formerly 4A-43.03, Amended 8-24-87, 5-14-91,
					 5-23-94, 9-6-01, Formerly 4A-43.003.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.004 - Definitions

Current through Reg. 50, No. 138; July 16, 2024
As used in this rule chapter, the following definitions shall
				  apply:
(1) "Approved" shall refer
				either to:
(a) Materials, devices,
				construction, and installation accepted by the authority having jurisdiction
				under the provisions of these rules by reason of tests or investigations
				conducted by it or by an agency satisfactory to the authority, based upon
				nationally accepted test standards or principles; or to:
(b) Occupancy or use accepted by the
				authority having jurisdiction under the provisions of these rules by reason of
				the submission of adequate proof of conformity with the basic requirements of
				the State Fire Marshal's Rules.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.005 - Interpretation of this Rule Chapter

Current through Reg. 50, No. 138; July 16, 2024
The State Fire Marshal shall be the final administrative
				  interpreting authority regarding the rules in this rule
				  chapter.
Rulemaking Authority
					 509.215,
					 633.104 FS. Law Implemented
					 509.215,
					 633.104,
					 633.206,
					 721.24
					 FS.
New 11-12-85, Formerly 4A-43.05,
					 4A-43.005.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.009 - Automatic Smoke Detection Requirements

Current through Reg. 50, No. 138; July 16, 2024
(1) The single station smoke detectors
				specified for construction contracts before October 1, 1983, by Section
				 509.215, F.S., for transient
				public lodging establishments which are less than 3 stories in height and by
				Section  721.24, F.S., for a time-share
				plan which is less than 3 stories in height shall be approved UL 217, listed
				single station smoke detector. Existing facilities may continue to use battery
				powered smoke detectors provided they are tested on a regular basis in
				accordance with paragraph (1)(b), and replaced in accordance with the
				manufacturer's recommendations, as required in Section 2-6 of NFPA 72, the
				edition as adopted in Rule
				 69A-3.012, F.A.C., but not less
				than once every twelve (12) months. New facilities shall have the detectors
				powered by the building electrical service with a rechargeable battery as a
				secondary power supply in compliance with NFPA 72, Section 1-5.2.6, the edition
				as adopted in Rule  69A-3.012, F.A.C.
(a) All such smoke detectors shall comply
				with NFPA 72, Section 2-3, the edition as adopted in rule Chapter 69A-3,
				F.A.C.
(b) Battery powered, single
				station smoke detectors, where used, shall be tested and inspected not less
				frequently than once per week. A log of the required tests and inspections
				shall be kept and available to the authority having jurisdiction at any time.
				This log shall include, but not be limited to, the following information and
				any other information as may be required by the authority having jurisdiction.
1. A list, clearly identifying each
				individual detector by its physical location.
2. The date of each required test &
				inspection.
3. The identity and
				signature of the inspector.
4. The
				result of each test & inspection.
5. The completion date and form of any
				maintenance performed.
6. The
				completion date and form of any corrective measures taken for each improperly
				functioning device.
7. A copy of
				the manufacturer's recommended maintenance schedule and
				procedures.
(c) At such
				time that the authority having jurisdiction finds cause to believe that the
				requirements of paragraph (1)(a) or (b), are not being fulfilled, detectors
				powered by the building electrical system shall be
				required.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.0095 - Individually Annunciated at Panel

Current through Reg. 50, No. 138; July 16, 2024
Single station smoke detectors which annunciate at a panel at
				  a supervised location, where used, shall meet the following:
(1) All means of interconnecting equipment,
				devices and/or appliances shall be monitored for the integrity of the
				conductors or equivalent so that the occurrence of a single open or a single
				ground trouble condition in the installation conductors and their restoration
				to normal shall be automatically signaled as "trouble" at the panel in the
				supervised location.
(2) Trouble
				signals shall be audible and distinctive from alarm signals, and shall comply
				with NFPA 72, Section 1-5.4.6, the edition as adopted in rule Chapter 69A-3,
				F.A.C.
(3) The annunciator system
				shall have primary power supplied in accordance with NFPA 72, Section 1-5.2.4,
				the edition as adopted in rule Chapter 69A-3, F.A.C., and secondary power
				supplied in accordance with NFPA 72, Section 1-5.2.5, the edition as adopted in
				rule Chapter 69A-3, F.A.C.
Rulemaking Authority
					  509.215,
					 633.104,
					 633.206(1)(b),
					 721.24(5) FS.
					 Law Implemented 509.215,
					  633.104(1),
					  633.206(1)(b),
					  721.24(5) 
					 FS.
New 5-14-91, Amended 9-6-01, Formerly
					 4A-43.0095.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.011 - Standpipe and Hose Systems

Current through Reg. 50, No. 138; July 16, 2024
Standpipe and hose systems are required for all transient
				  public lodging establishments, timeshare units or timeshare plans which are
				  located in buildings exceeding 50 feet in height or in buildings over six
				  stories high which have a complete automatic sprinkler system. The standpipe
				  and hose systems shall comply with the provisions of NFPA 14, the edition as
				  adopted in Rule  69A-3.012, F.A.C. Both standpipe
				  and hose are required for those buildings which do not have sprinkler systems.
				  A standpipe with no hose, but hose connections, is required for those buildings
				  that do have sprinkler systems.
Rulemaking Authority
					  509.215,
					 633.104,
					 633.206(1)(b),
					 721.24(5) FS.
					 Law Implemented 509.215,
					  633.104(1),
					  633.206(1)(b),
					  721.24(5) 
					 FS.
New 11-12-85, Formerly 4A-43.11, Amended 8-24-87, 5-14-91,
					 9-6-01, Formerly 4A-43.011.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.014 - Special Compliance Schedule

Current through Reg. 50, No. 138; July 16, 2024
All required public lodging establishments, time share plans
				  or time share units shall be sprinklered in accordance with Sections
				   509.215 and
				   721.24, F.S. All systems must
				  have been installed and operational by October 1, 1994, and the Division of the
				  State Fire Marshal will no longer grant any extensions for delayed
				  installations.
Rulemaking Authority
					  509.215,
					 633.104,
					 633.206(1)(b),
					 721.24(5) FS.
					 Law Implemented 509.215,
					  633.104(1),
					  633.206(1)(b),
					  721.24(5) 
					 FS.
New 11-12-85, Formerly 4A-43.14, Amended 8-24-87, 5-14-91,
					 9-6-01, Formerly 4A-43.014.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.015 - Historic Hotel Structures

Current through Reg. 50, No. 138; July 16, 2024
(1) Any
				request to utilize the special provisions of Section
				 509.215(4),
				F.S., shall be made in writing to the Director of the Division of State Fire
				Marshal.
(2) The special historical
				review task force, as designated in Section
				 509.215(4)(b),
				F.S., shall review the application of fire safety standards required by Section
				 509.215, F.S., and shall address
				other fire safety provisions pursuant to the authority of Section
				 633.104,
				F.S.
Rulemaking Authority
					  509.215,
					 633.104,
					 633.206(1)(b),
					 721.24(5) FS.
					 Law Implemented 509.215,
					  633.104(1),
					  633.206(1)(b),
					  721.24(5) 
					 FS.
New 11-12-85, Formerly 4A-43.15, Amended 8-24-87, 5-14-91,
					 9-6-01, Formerly 4A-43.015.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.018 - One and Two Family Dwellings, Recreational Vehicles and Mobile Homes Licensed as Public Lodging Establishments

Current through Reg. 50, No. 138; July 16, 2024
(1)
				This section applies to one and two family dwellings, recreational vehicles and
				mobile homes licensed as public lodging establishments as defined in Section
				 509.013(4)(a),
				F.S. Except as modified by this rule, one and two family dwellings used by more
				than one party per living unit shall comply with Chapter 24, One-Family and
				Two-Family Dwellings, of NFPA 101, Life Safety Code, as adopted in Chapter
				69A-3, F.A.C., and incorporated by reference therein.
(2) Three family and four family dwellings
				licensed as public lodging establishments shall comply with Chapter 28, New
				Hotels and Dormitories or Chapter 29, Existing Hotels and Dormitories, of NFPA
				101, Life Safety Code, as adopted in Chapter 69A-3, F.A.C., and incorporated by
				reference therein.
(3) Smoke
				detectors.
(a) One and two family dwellings
				and mobile homes shall have an approved single station or multiple station
				smoke detectors continuously powered by the house electrical system.
(b) Recreational vehicles shall have an
				approved single station smoke detector continuously powered by 120 volt
				electrical service.
(c) In addition
				to paragraph (3)(a) or (b), above, an approved single station smoke detector
				powered by the building electrical system, and 120 volt AC electrical service
				for recreational vehicles, shall be provided in each sleeping room.
(d) To qualify as "approved," smoke detectors
				shall be installed in accordance with NFPA 72, National Fire Alarm Code, the
				edition as adopted in Chapter 69A-3, F.A.C., and incorporated by reference
				therein.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-43 - UNIFORM FIRE SAFETY STANDARDS FOR TRANSIENT PUBLIC LODGING ESTABLISHMENTS, TIMESHARE PLANS, AND TIMESHARE UNIT FACILITIES' › Section 69A-43.019 - Standards of the National Fire Protection Association Adopted

Current through Reg. 50, No. 138; July 16, 2024
(1) Except as modified by Section
				 509.215, F.S., the standards of
				the National Fire Protection Association, NFPA 101, the Life Safety Code, the
				edition as adopted and incorporated in Rule
				 69A-3.012, F.A.C., shall be the
				uniform firesafety standards for "public lodging establishments," as defined in
				Section  509.013(4)(a),
				F.S., which are "transient establishments," as defined in Section
				 509.013(11),
				F.S.
(2) The codes and standards
				published by the National Fire Protection Association may be obtained by
				writing to the National Fire Protection Association at 1 Batterymarch Park,
				Quincy, Massachusetts 02169-7471. All codes and standards referenced in this
				rule are also available for public inspection during regular business hours at
				the Bureau of Fire Prevention, Division of State Fire Marshal, 325 John Knox
				Road, The Atrium, Third Floor, Tallahassee, Florida 32303.
Rulemaking Authority
					 509.215(5) FS.
					 Law Implemented 509.215
					 FS.
New 9-15-02, Formerly
					 4A-43.019.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-44 - MINIMUM FIRE SAFETY STANDARDS FOR RESIDENTIAL ALCOHOL AND DRUG ABUSE TREATMENT AND PREVENTION PROGRAMS, MENTAL HEALTH RESIDENTIAL TREATMENT FACILITIES AND CRISIS STABILIZATION UNITS › Section 69A-44.001 - Title

Current through Reg. 50, No. 138; July 16, 2024
This rule chapter shall be known as "Minimum Fire Safety
				  Standards for Residential Alcohol and Drug Abuse Treatment and Prevention
				  Programs, Mental Health Residential Treatment Facilities and Crisis
				  Stabilization Units."
Rulemaking Authority
					 394.879(2),
					 633.104,
					 633.206 FS. Law Implemented
					 394.879(2),
					 633.104,
					 633.206,
					 633.216
					 FS.
New 7-12-87, Amended 9-1-91, Formerly
					 4A-44.001.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-44 - MINIMUM FIRE SAFETY STANDARDS FOR RESIDENTIAL ALCOHOL AND DRUG ABUSE TREATMENT AND PREVENTION PROGRAMS, MENTAL HEALTH RESIDENTIAL TREATMENT FACILITIES AND CRISIS STABILIZATION UNITS › Section 69A-44.002 - Purpose

Current through Reg. 50, No. 138; July 16, 2024
The purpose of this rule chapter is to specify measures to
				  provide a reasonable degree of public safety from fire in programs and
				  facilities subject to this rule chapter.
Rulemaking Authority
					 394.879(2),
					 633.104,
					 633.206 FS. Law Implemented
					 394.879(2),
					 633.104,
					 633.206,
					 633.216
					 FS.
New 7-12-87, Amended 9-1-91, Formerly
					 4A-44.002.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-44 - MINIMUM FIRE SAFETY STANDARDS FOR RESIDENTIAL ALCOHOL AND DRUG ABUSE TREATMENT AND PREVENTION PROGRAMS, MENTAL HEALTH RESIDENTIAL TREATMENT FACILITIES AND CRISIS STABILIZATION UNITS › Section 69A-44.003 - Application

Current through Reg. 50, No. 138; July 16, 2024
(1) Except as provided in subsection (2),
				below, these rules apply as statewide minimum standards for facilities used as
				Residential Alcohol and Drug Abuse Treatment and Prevention Programs or Mental
				Health Residential Treatment Facilities and Crisis Stabilization
				Units.
(2) These rules shall be
				applied as Uniform Fire Safety Standards as required by chapter 633, F.S., for
				state-owned or state-leased facilities whose purpose is the same as those
				described in subsection
				 69A-44.003(1),
				F.A.C.
(3) Documentation of
				client's status is determined by the facilities' administration. Facilities
				shall maintain documentation for each client, which shall specify whether the
				client is capable or incapable of self-preservation in the event of a fire or
				other emergency. Documentation shall be completed and maintained as specified
				by the Florida Department of Children and Families. Health care facilities are
				exempt from this requirement.
Rulemaking Authority
					 394.879(2),
					 633.104,
					 633.206 FS. Law Implemented
					 394.879(2),
					 633.104,
					 633.206,
					 633.216
					 FS.
New 7-12-87, Amended 9-1-91, Formerly
					 4A-44.003.
Florida Administrative Code › 69 - DEPARTMENT OF FINANCIAL SERVICES › 69A - Division of State Fire Marshal › Chapter 69A-44 - MINIMUM FIRE SAFETY STANDARDS FOR RESIDENTIAL ALCOHOL AND DRUG ABUSE TREATMENT AND PREVENTION PROGRAMS, MENTAL HEALTH RESIDENTIAL TREATMENT FACILITIES AND CRISIS STABILIZATION UNITS › Section 69A-44.006 - Definitions

Current through Reg. 50, No. 138; July 16, 2024
(1) "Crisis Stabilization Unit" shall mean a
				mental health program housed in a facility providing an alternative to
				inpatient hospitalization and which provides brief, intensive services 24 hours
				a day, 7 days a week, for mentally ill individuals who are in an acutely
				disturbed state. Persons who reside in these units are considered to be
				incapable of self-preservation for the purpose of these rules.
(2) "Mental Health Residential Treatment
				Facility" shall mean a facility, other than a Crisis Stabilization Unit,
				providing residential care and treatment to individuals exhibiting symptoms of
				mental illness who are in need of a 24-hour, 7-day-a-week structured living
				environment, respite care, or long term community placement. "Residential
				treatment facility" shall also include short term residential treatment
				facilities for treatment of mental illness.
Rulemaking Authority
					 394.879(2),
					 633.104,
					 633.206 FS. Law Implemented
					 394.879(2),
					 633.104,
					 663.206,
					 633.216
					 FS.
New 7-12-87, Amended 9-1-91, Formerly
					 4A-44.006.