reglab/statecodes huggingface dataset:
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 1. General Provisions › 50-74-105. Purchaser to notify department of purchase

50-74-105. Purchaser to notify department of purchase.
(1) Any person purchasing any boiler, whether traction or stationary, not exempted by the provisions of 50-74-103 shall, within 10 days after such purchase, report the fact of such purchase to the department and shall notify the department as to where the boiler will be installed and operated.
(2) Any person failing to comply with the provisions of this section shall be deemed guilty of a misdemeanor.
History: En. Sec. 5, Ch. 32, L. 1905; re-en. Sec. 1655, Rev. C. 1907; amd. Sec. 13, Ch. 30, L. 1913; amd. Sec. 4, Ch. 32, L. 1919; re-en. Sec. 2726, R.C.M. 1921; amd. Sec. 1, Ch. 140, L. 1923; re-en. Sec. 2726, R.C.M. 1935; amd. Sec. 4, Ch. 77, L. 1967; amd. Sec. 14, Ch. 225, L. 1971; amd. Sec. 33, Ch. 182, L. 1975; R.C.M. 1947, 69-1515(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 1. General Provisions › 50-74-106. Certificate and license to be conspicuously displayed

50-74-106. Certificate and license to be conspicuously displayed.
All certificates of inspection, operating certificates, and engineer's licenses must be displayed in a conspicuous place in the boiler room.
History: En. Sec. 562, Pol. C. 1895; re-en. Sec. 1651, Rev. C. 1907; amd. Sec. 11, Ch. 30, L. 1913; re-en. Sec. 2722, R.C.M. 1921; re-en. Sec. 2722, R.C.M. 1935; amd. Sec. 10, Ch. 225, L. 1971; amd. Sec. 20, Ch. 513, L. 1973; R.C.M. 1947, 69-1511(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 1. General Provisions › 50-74-107. Wrongful certification or granting of a license a misdemeanor

50-74-107. Wrongful certification or granting of a license a misdemeanor.
Any inspector or assistant inspector who willfully certifies regarding any boilers or their attachments or grants a license to any person to act as engineer contrary to the provisions of this chapter is guilty of a misdemeanor.
History: En. Sec. 562, Pol. C. 1895; re-en. Sec. 1651, Rev. C. 1907; amd. Sec. 11, Ch. 30, L. 1913; re-en. Sec. 2722, R.C.M. 1921; re-en. Sec. 2722, R.C.M. 1935; amd. Sec. 10, Ch. 225, L. 1971; amd. Sec. 20, Ch. 513, L. 1973; R.C.M. 1947, 69-1511(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 1. General Provisions › 50-74-108. Tampering with safety valve a misdemeanor

50-74-108. Tampering with safety valve a misdemeanor.
A renter, user, or owner of a boiler or a person who tampers with the safety valve to allow the boiler to carry greater pressure than is allowed by the inspection certificate is guilty of a misdemeanor.
History: En. Sec. 555, Pol. C. 1895; re-en. Sec. 1644, Rev. C. 1907; amd. Sec. 6, Ch. 30, L. 1913; re-en. Sec. 2715, R.C.M. 1921; re-en. Sec. 2715, R.C.M. 1935; amd. Sec. 4, Ch. 225, L. 1971; amd. Sec. 9, Ch. 187, L. 1977; R.C.M. 1947, 69-1504(2).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-201. State boiler inspectors

50-74-201. State boiler inspectors.
The department shall appoint state inspectors of boilers and shall prescribe their duties and term of office and fix their compensation.
History: En. Sec. 550, Pol. C. 1895; re-en. Sec. 1639, Rev. C. 1907; amd. Sec. 1, Ch. 30, L. 1913; amd. Sec. 1, Ch. 12, L. 1921; re-en. Sec. 2712, R.C.M. 1921; re-en. Sec. 2712, R.C.M. 1935; amd. Sec. 1, Ch. 77, L. 1967; amd. Sec. 1, Ch. 225, L. 1971; amd. Sec. 25, Ch. 182, L. 1975; amd. Sec. 1, Ch. 152, L. 1977; R.C.M. 1947, 69-1501(2); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-202. Special boiler inspectors

50-74-202. Special boiler inspectors.
(1) In addition to the state boiler inspectors, the department shall issue to the inspectors of boiler insurance companies authorized to do business in the state commissions, certificates, or other recognition as special boiler inspectors and may accept the inspection reports of such special inspectors as equivalent to those of the state inspectors.
(2) Each such special inspector shall hold a certificate as boiler inspector issued by the national board of boiler and pressure vessels inspectors.
(3) Such special inspectors shall receive no salary or expenses from the state, nor shall the state collect inspection fees for inspections made by such special inspectors.
History: En. Sec. 550, Pol. C. 1895; re-en. Sec. 1639, Rev. C. 1907; amd. Sec. 1, Ch. 30, L. 1913; amd. Sec. 1, Ch. 12, L. 1921; re-en. Sec. 2712, R.C.M. 1921; re-en. Sec. 2712, R.C.M. 1935; amd. Sec. 1, Ch. 77, L. 1967; amd. Sec. 1, Ch. 225, L. 1971; amd. Sec. 25, Ch. 182, L. 1975; amd. Sec. 1, Ch. 152, L. 1977; R.C.M. 1947, 69-1501(3); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-203. Repealed

50-74-203. Repealed.
Sec. 4, Ch. 440, L. 2021.
History: En. Sec. 2, p. 102, L. 1889; amd. Sec. 551, Pol. C. 1895; re-en. Sec. 1640, Rev. C. 1907; amd. Sec. 2, Ch. 30, L. 1913; re-en. Sec. 2713, R.C.M. 1921; amd. Sec. 2, Ch. 225, L. 1971; R.C.M. 1947, 69-1502; amd. Sec. 1887, Ch. 56, L. 2009.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-204. Joint or separate inspection authorized -- inspectors to certify inspection under seal

50-74-204. Joint or separate inspection authorized -- inspectors to certify inspection under seal.
In making an inspection of the boilers and machinery herein provided for, the inspectors may act jointly or separately, but the inspector or assistant inspector making such inspection must in all cases certify the same under the seal of the inspector of boilers and safety.
History: En. Sec. 562, Pol. C. 1895; re-en. Sec. 1651, Rev. C. 1907; amd. Sec. 11, Ch. 30, L. 1913; re-en. Sec. 2722, R.C.M. 1921; re-en. Sec. 2722, R.C.M. 1935; amd. Sec. 10, Ch. 225, L. 1971; amd. Sec. 20, Ch. 513, L. 1973; R.C.M. 1947, 69-1511(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-205. Purchaser to receive certificate of inspection

50-74-205. Purchaser to receive certificate of inspection.
(1) Any person purchasing any boiler, whether traction or stationary, shall be entitled to receive from the seller the certificates of inspection issued on such boiler.
(2) Any person failing to comply with the provisions of this section shall be deemed guilty of a misdemeanor.
History: En. Sec. 5, Ch. 32, L. 1905; re-en. Sec. 1655, Rev. C. 1907; amd. Sec. 13, Ch. 30, L. 1913; amd. Sec. 4, Ch. 32, L. 1919; re-en. Sec. 2726, R.C.M. 1921; amd. Sec. 1, Ch. 140, L. 1923; re-en. Sec. 2726, R.C.M. 1935; amd. Sec. 4, Ch. 77, L. 1967; amd. Sec. 14, Ch. 225, L. 1971; amd. Sec. 33, Ch. 182, L. 1975; R.C.M. 1947, 69-1515(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-206. Boiler to be inspected prior to use -- duty of notification

50-74-206. Boiler to be inspected prior to use -- duty of notification.
(1) The inspector of boilers must inspect all boilers and steam generators before the same are used.
(2) All persons who bring into this state for operation in this state any boiler or boilers must notify the department stating the number and kind of boilers and where they are to be located and operated in this state and must secure from the department a certificate of inspection before boilers are placed in operation except in the case of new boilers, which must be inspected within 90 days after they are put in use.
History: En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; R.C.M. 1947, 69-1503(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-207. Boiler opened for repair subject to inspection -- duty of notification

50-74-207. Boiler opened for repair subject to inspection -- duty of notification.
Any owner, operator, or user who opens a boiler or boilers between inspections for repair or other reasons must notify the department of such action, and such boiler or boilers shall at the discretion of the department be inspected by the state or special boiler inspector before the boiler or boilers may be placed back in operation.
History: En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; R.C.M. 1947, 69-1503(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-208. Penalty for operation without certificate or failure to give notice

50-74-208. Penalty for operation without certificate or failure to give notice.
Any person failing to give notice to the department as provided in 50-74-206 or 50-74-207 or who operates such boilers without a certificate from the department shall be punished by a fine of not less than $100 or more than $500 for each offense, by imprisonment in the county jail for not less than 30 or more than 90 days, or by both such fine and imprisonment.
History: En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; R.C.M. 1947, 69-1503(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-209. Required inspection intervals -- failure to comply with safety standards -- inspections through other states

50-74-209. Required inspection intervals -- failure to comply with safety standards -- inspections through other states.
(1) (a) All manually fired boilers and all boilers and banks of boilers rated with a total input of 400,000 Btu's an hour or greater must be inspected at least once each year.
(b) All automatically fired boilers rated with an input of less than 400,000 Btu's an hour must be inspected at least once every 2 years, except that an automatically fired boiler in a school, day-care center, hospital, rest home, retirement center, or place of assembly with a capacity for more than 100 persons must be inspected once a year.
(c) Boilers exempt under the provisions of 50-74-103 do not require inspections.
(d) Upon written application, longer inspection intervals may be authorized by the department.
(2) In addition to the inspection required by subsection (1), it is the duty of each inspector to examine at proper times, when in the inspector's opinion an examination is necessary, all boilers that have become unsafe from any cause and to notify the owner or the person using the boilers of any defect and what repairs are necessary to render them safe.
(3) If a boiler is found, upon inspection, to violate safety standards set forth in rules referred to in 50-74-101, the department shall order the owner of the boiler to comply with the standards. An owner who negligently or knowingly fails to comply with an order is guilty of a misdemeanor and upon conviction is punishable by a fine of not less than $50 or more than $100, imprisonment for not more than 60 days in a county detention center, or both.
(4) The department may accept valid inspections for traction engines that have been performed by other states.
History: (1)En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; Sec. 69-1503, R.C.M. 1947; (2)En. Sec. 557, Pol. C. 1895; re-en. Sec. 1646, Rev. C. 1907; re-en. Sec. 2717, R.C.M. 1921; re-en. Sec. 2717, R.C.M. 1935; Sec. 69-1506, R.C.M. 1947; R.C.M. 1947, 69-1503(part), 69-1506; amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 1, Ch. 499, L. 2001; amd. Sec. 2, Ch. 322, L. 2019.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-210. Duty to permit inspection

50-74-210. Duty to permit inspection.
It is the duty of the owners, engineers, or managers of steam or water boilers to allow the inspector free access to the same.
History: En. Sec. 558, Pol. C. 1895; re-en. Sec. 1647, Rev. C. 1907; amd. Sec. 7, Ch. 30, L. 1913; re-en. Sec. 2718, R.C.M. 1921; re-en. Sec. 2718, R.C.M. 1935; amd. Sec. 6, Ch. 225, L. 1971; amd. Sec. 27, Ch. 182, L. 1975; R.C.M. 1947, 69-1507(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-211. Inspector to notify department of refused access

50-74-211. Inspector to notify department of refused access.
In case the owner, operators, or manager of any boiler is notified by the inspector to have the boiler ready for inspection on a certain day and fails to have such boiler ready for inspection at such time, the inspector shall notify the department to gain access to the boiler.
History: En. Sec. 558, Pol. C. 1895; re-en. Sec. 1647, Rev. C. 1907; amd. Sec. 7, Ch. 30, L. 1913; re-en. Sec. 2718, R.C.M. 1921; re-en. Sec. 2718, R.C.M. 1935; amd. Sec. 6, Ch. 225, L. 1971; amd. Sec. 27, Ch. 182, L. 1975; R.C.M. 1947, 69-1507(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-212. Payment of costs resulting from refused access

50-74-212. Payment of costs resulting from refused access.
The owner, engineer, or manager of any boiler who has refused access resulting in a department order must pay all transportation and hotel expenses of the inspector who makes the inspection directed by such order in addition to the inspection fee provided by law.
History: En. Sec. 558, Pol. C. 1895; re-en. Sec. 1647, Rev. C. 1907; amd. Sec. 7, Ch. 30, L. 1913; re-en. Sec. 2718, R.C.M. 1921; re-en. Sec. 2718, R.C.M. 1935; amd. Sec. 6, Ch. 225, L. 1971; amd. Sec. 27, Ch. 182, L. 1975; R.C.M. 1947, 69-1507(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-213. Failure to comply with department directed access a misdemeanor

50-74-213. Failure to comply with department directed access a misdemeanor.
Any person failing to immediately comply with department directed access to the boiler shall be deemed guilty of a misdemeanor and upon conviction thereof shall be punished by a fine of not less than $100 or more than $500, by imprisonment in the county jail for not less than 2 months or more than 6 months, or by both such fine and imprisonment.
History: En. Sec. 558, Pol. C. 1895; re-en. Sec. 1647, Rev. C. 1907; amd. Sec. 7, Ch. 30, L. 1913; re-en. Sec. 2718, R.C.M. 1921; re-en. Sec. 2718, R.C.M. 1935; amd. Sec. 6, Ch. 225, L. 1971; amd. Sec. 27, Ch. 182, L. 1975; R.C.M. 1947, 69-1507(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-214. Engineer to assist in inspection

50-74-214. Engineer to assist in inspection.
It is the duty of the engineer operating any boiler or boilers to assist the inspectors in their examination of the boilers and point out any defects known to the engineer in the boilers or machinery under the engineer's charge. If an engineer does not comply with this section, the engineer's license must be revoked or suspended.
History: En. Sec. 558, Pol. C. 1895; re-en. Sec. 1647, Rev. C. 1907; amd. Sec. 7, Ch. 30, L. 1913; re-en. Sec. 2718, R.C.M. 1921; re-en. Sec. 2718, R.C.M. 1935; amd. Sec. 6, Ch. 225, L. 1971; amd. Sec. 27, Ch. 182, L. 1975; R.C.M. 1947, 69-1507(part); amd. Sec. 1888, Ch. 56, L. 2009.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-215. Interior and exterior examination of boiler

50-74-215. Interior and exterior examination of boiler.
(1) The inspector must be satisfied by a thorough interior and exterior examination that the:
(a) boilers are well-made and of good and suitable material;
(b) openings for the passage of water and steam, respectively, and all pipes and tubes exposed to heat are of the proper dimensions and free from obstructions;
(c) flues are circular in shape;
(d) fire line of the furnace is at least 2 inches below prescribed minimum waterline of the boilers;
(e) arrangements for delivering the feed water are such that the boilers cannot be injured by the feed water; and
(f) boilers and the steam connections may be safely employed without danger to life.
(2) A boiler or steam pipe or any of the connections to a boiler or steam pipe that are made in whole or in part of bad material or are unsafe from any cause may not be approved. Nothing in this section may be construed to prevent the use of any boiler or steam generator, that is not constructed of riveted iron or steel plates, when the inspector has satisfactory evidence that the boiler or steam generator is equal in strength to and as safe from explosion as boilers of the best quality, constructed of iron or steel plates.
History: (1)En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; Sec. 69-1503, R.C.M. 1947; (2)En. Sec. 556, Pol. C. 1895; re-en. Sec. 1645, Rev. C. 1907; re-en. Sec. 2716, R.C.M. 1921; re-en. Sec. 2716, R.C.M. 1935; amd. Sec. 5, Ch. 225, L. 1971; Sec. 69-1505, R.C.M. 1947; R.C.M. 1947, 69-1503(part), 69-1505; amd. Sec. 1889, Ch. 56, L. 2009.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-216. Hydrostatic pressure test

50-74-216. Hydrostatic pressure test.
When necessary, the boiler inspector shall subject boilers, except those exempted by 50-74-103, to hydrostatic pressure, which hydrostatic pressure shall not exceed 150% of the steam pressure allowed on the boilers, providing there are no such leaks on such boilers which prevent the inspector from applying such hydrostatic pressure.
History: En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; R.C.M. 1947, 69-1503(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-217. Other inspection requirements

50-74-217. Other inspection requirements.
The inspector must be satisfied that:
(1) the safety valves are of suitable relieving capacity ratings, sufficient in number and area, and properly arranged and properly adjusted so as not to allow a greater pressure in a boiler than the amount prescribed by the inspection certificate;
(2) there are a sufficient number of gauge cocks properly inserted to indicate the amount of water and suitable gauges that will correctly record the pressure of steam; and
(3) adequate and certain provisions for an ample supply of water to feed the boiler at all times and suitable means for blowing out are provided so as to thoroughly remove mud and sediment from all parts of the boiler when it is under pressure of steam.
History: En. Sec. 555, Pol. C. 1895; re-en. Sec. 1644, Rev. C. 1907; amd. Sec. 6, Ch. 30, L. 1913; re-en. Sec. 2715, R.C.M. 1921; re-en. Sec. 2715, R.C.M. 1935; amd. Sec. 4, Ch. 225, L. 1971; amd. Sec. 9, Ch. 187, L. 1977; R.C.M. 1947, 69-1504(1); amd. Sec. 1890, Ch. 56, L. 2009.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-218. Safe working pressure

50-74-218. Safe working pressure.
(1) If a boiler is constructed with lap horizontal seams on the boiler, dome, or drum, a factor of 4 1/2 must be used in determining the safe working pressure allowed on the boiler.
(2) If a boiler is constructed with butt strap horizontal seams, a factor of four may be used in determining the safe working pressure.
(3) If a boiler is a historical boiler, as defined by the department by rule, on stayed sections, a safety factor of four must be used in determining the safe working pressure.
(4) If a boiler rests on a side wall on lugs, is hung by I-beams, or is in any way set up so that the weight of the boiler is pulling against the horizontal seam of rivets, a factor of five must be used in determining the safe working pressure.
(5) If the horizontal lap seams of a boiler are exposed to the fire, a factor of five must be used in determining the safe working pressure.
(6) On new stay bolts, 7,500 pounds pressure per square inch is allowed. If the stay bolts are corroded or defective, the inspector must determine the pressure to be allowed on the stay bolts.
(7) On braces made of solid material, 8,000 pounds pressure per square inch is allowed. On welded braces or braces with only one crowfoot, 6,000 pounds pressure per square inch is allowed.
(8) Cast iron may not be used in the construction or reinforcements of a boiler if the pressure allowed on the boiler is more than 100 pounds per square inch.
History: En. Sec. 555, Pol. C. 1895; re-en. Sec. 1644, Rev. C. 1907; amd. Sec. 6, Ch. 30, L. 1913; re-en. Sec. 2715, R.C.M. 1921; re-en. Sec. 2715, R.C.M. 1935; amd. Sec. 4, Ch. 225, L. 1971; amd. Sec. 9, Ch. 187, L. 1977; R.C.M. 1947, 69-1504(3); amd. Sec. 1, Ch. 160, L. 2011.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 2. Inspections › 50-74-219. Repealed

50-74-219. Repealed.
Sec. 4, Ch. 440, L. 2021.
History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(1); amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 13, Ch. 514, L. 1995; amd. Sec. 3, Ch. 385, L. 1997; amd. Sec. 2, Ch. 499, L. 2001; amd. Sec. 5, Ch. 68, L. 2005; amd. Sec. 1, Ch. 46, L. 2015; amd. Sec. 3, Ch. 322, L. 2019.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-301. License required to operate boilers and steam engines

50-74-301. License required to operate boilers and steam engines.
All boilers and steam engines, except as exempted in 50-74-103, come under the provisions of this chapter, and persons operating same are required to hold the proper grade of license.
History: En. Sec. 5, Ch. 32, L. 1905; re-en. Sec. 1655, Rev. C. 1907; amd. Sec. 13, Ch. 30, L. 1913; amd. Sec. 4, Ch. 32, L. 1919; re-en. Sec. 2726, R.C.M. 1921; amd. Sec. 1, Ch. 140, L. 1923; re-en. Sec. 2726, R.C.M. 1935; amd. Sec. 4, Ch. 77, L. 1967; amd. Sec. 14, Ch. 225, L. 1971; amd. Sec. 33, Ch. 182, L. 1975; R.C.M. 1947, 69-1515(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-302. General requirements for licensure

50-74-302. General requirements for licensure.
No person may be granted a license to operate steam or water boilers and steam machinery under the provisions of this chapter who has not met the qualifications for licensing and been found to be competent by examination to perform the duties of an engineer.
History: En. Sec. 559, Pol. C. 1895; re-en. Sec. 1648, Rev. C. 1907; amd. Sec. 8, Ch. 30, L. 1913; re-en. Sec. 2719, R.C.M. 1921; re-en. Sec. 2719, R.C.M. 1935; amd. Sec. 7, Ch. 225, L. 1971; amd. Sec. 10, Ch. 187, L. 1977; R.C.M. 1947, 69-1508(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-303. Engineer's license classifications

50-74-303. Engineer's license classifications.
(1) Engineers entrusted with the operation, care, and management of steam or water boilers and steam machinery, as specified in 50-74-302, are divided into six classes, including first-class engineers, second-class engineers, third-class engineers, agricultural-class engineers, low-pressure engineers, and limited low-pressure engineers.
(2) Licenses for the operation of steam or water boilers and steam machinery are divided into six classifications in accordance with the following schedule:
(a) First-class engineers are licensed to operate all classes, pressures, and temperatures of steam and water boilers and steam-driven machinery with the exception of traction and hoisting engines.
(b) Second-class engineers are licensed to operate steam boilers operating not in excess of 250 pounds per square inch gauge saturated steam pressure, water boilers operating not in excess of 375 pounds per square inch gauge pressure and 450 degrees F temperature, and steam-driven machinery not to exceed 100 horsepower per unit, with the exception of traction and hoisting engines.
(c) Third-class engineers are licensed to operate steam boilers operating not in excess of 150 pounds per square inch gauge saturated steam pressure or not in excess of 150 horsepower per hour and water boilers operating not in excess of 160 pounds per square inch gauge pressure and 350 degrees F temperature.
(d) Agricultural-class engineers are licensed to operate steam boilers that operate not in excess of 150 pounds per square inch saturated steam pressure and that:
(i) are not operated for more than 6 months of the year; and
(ii) are not operated for purposes other than the harvesting or processing of agricultural products.
(e) Low-pressure engineers are licensed to operate steam boilers operating not in excess of 15 pounds per square inch gauge pressure and water boilers operating not in excess of 50 pounds per square inch gauge pressure and 250 degrees F temperature.
(f) Limited low-pressure engineers are licensed to operate hot water heating boilers not in excess of 30 pounds per square inch gauge pressure and 210 degrees F temperature and hot water supply boilers not in excess of 160 pounds per square inch gauge pressure and 210 degrees F temperature.
History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(1), (2); amd. Sec. 14, Ch. 514, L. 1995; amd. Sec. 1, Ch. 392, L. 2003; amd. Sec. 2, Ch. 440, L. 2021.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-305. Exceptions to requirements for engineer's license

50-74-305. Exceptions to requirements for engineer's license.
Allowable exceptions or variances to the minimum requirements set out in 50-74-304 are as follows:
(1) An applicant for an engineer's license in any classification who holds a valid license in that classification from another state having licensing requirements equal to or exceeding the minimum requirements set out in 50-74-304, who successfully passes a written examination prescribed by the department, and who is found competent to operate a boiler and steam-driven machinery in that classification by the department must be granted a license in that classification.
(2) Operating experience in a classification accumulated in the United States military services or the merchant marine service satisfactory to the department may be accepted in lieu of the operating experience required for licensing of engineers in each of the license classifications.
(3) An applicant who has training in the operation of steam or water boilers and steam machinery and who has been certified as having satisfactorily completed a prescribed training course from a department-approved institution or training program in the classification for which the applicant is applying may, pursuant to department rule, be credited with experience toward a first-, second-, or third-class or low-pressure engineer's license.
History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(4); amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 33, Ch. 308, L. 1995; amd. Sec. 16, Ch. 514, L. 1995.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-306. Traction licenses -- application without examination from other states

50-74-306. Traction licenses -- application without examination from other states.
(1) The licenses named in 50-74-303 do not entitle the holder to operate a traction engine.
(2) A person who is entrusted with the care and management of traction engines or boilers on wheels is required to pass an examination testing the person's competency to operate that class of machinery and procure a traction license.
(3) A person who is entrusted with the care, management, and operation of steam locomotives not addressed by federal regulations is required to pass an examination testing the person's competency to operate that class of machinery and procure a traction license.
(4) The department may issue a license to an individual holding a valid license from another state upon application without examination if the requirements of 50-74-307(2) are met.
(5) A traction license does not entitle its holder to operate any other class of steam machinery.
History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(part); amd. Sec. 1, Ch. 65, L. 2001; amd. Sec. 4, Ch. 322, L. 2019.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-307. Requirements for traction licenses

50-74-307. Requirements for traction licenses.
(1) An applicant for a traction engineer's license:
(a) must be 18 years of age or older;
(b) shall attend a steam school approved by the department by rule and may apply steam school hours to the hour requirement established in subsection (3);
(c) must have at least 50 hours total experience in the operation of steam traction engines; and
(d) shall successfully pass a written examination prescribed by the department.
(2) The department may issue a license to an individual holding a valid license from another state under 50-74-306 if the individual is from a state that has standards greater than or equal to the state of Montana.
History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(part); amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 17, Ch. 514, L. 1995; amd. Sec. 2, Ch. 65, L. 2001; amd. Sec. 2, Ch. 160, L. 2011; amd. Sec. 5, Ch. 322, L. 2019.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-308. Waiver of experience requirement for traction licenses

50-74-308. Waiver of experience requirement for traction licenses.
The department, at its discretion, may waive the experience requirement for operators of traction engines which are maintained and operated as a hobby for the restoration and show purposes of antique equipment.
History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(part); amd. Sec. 64, Ch. 613, L. 1989.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-309. Repealed

50-74-309. Repealed.
Sec. 127, Ch. 467, L. 2005.
History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(2); amd. Sec. 18, Ch. 514, L. 1995.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-310. Repealed

50-74-310. Repealed.
Sec. 28, Ch. 196, L. 2003.
History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(3).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-311. Waiting period before reexamination permitted

50-74-311. Waiting period before reexamination permitted.
In case of the failure of any applicant to successfully pass an examination, 45 days must elapse before the applicant may again be examined for license.
History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(4); amd. Sec. 1891, Ch. 56, L. 2009.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-312. Review of license rejection -- waiting period

50-74-312. Review of license rejection -- waiting period.
(1) An applicant for a license under the provisions of this chapter whose application has been rejected may, within 45 days after the date of the rejection, set forth in writing any arguments opposing the rejection and request a review by the department. The request must be addressed to the department and must be signed by the applicant.
(2) Within 2 days after receiving the request, the department shall notify the applicant in writing that on a certain day, not less than 5 days or more than 30 days after receipt of the written request, the department shall review and evaluate the application and any arguments opposing the rejection of the license application.
(3) The applicant may appear in person at the review. At least 2 days before the day set for the review, the applicant may designate in writing to the department the name of an engineer holding a valid license of equal or higher grade than the one applied for, and the engineer may testify on behalf of the applicant at the review.
(4) After the review, if the department determines that the applicant is entitled to the license, the department shall issue the license. If the department affirms the decision to not issue the license, the applicant may reapply to take the license examination, as provided in 50-74-311, and may not take the examination within 45 days of the final decision to not issue the license.
History: (1) thru (3)En. Sec. 564, Pol. C. 1895; re-en. Sec. 1653, Rev. C. 1907; re-en. Sec. 2724, R.C.M. 1921; re-en. Sec. 2724, R.C.M. 1935; amd. Sec. 12, Ch. 225, L. 1971; amd. Sec. 31, Ch. 182, L. 1975; Sec. 69-1513, R.C.M. 1947; (4)En. Sec. 565, Pol. C. 1895; re-en. Sec. 1654, Rev. C. 1907; re-en. Sec. 2725, R.C.M. 1921; re-en. Sec. 2725, R.C.M. 1935; amd. Sec. 13, Ch. 225, L. 1971; amd. Sec. 32, Ch. 182, L. 1975; Sec. 69-1514, R.C.M. 1947; R.C.M. 1947, 69-1513, 69-1514; amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 19, Ch. 514, L. 1995; amd. Sec. 186, Ch. 483, L. 2001; amd. Sec. 26, Ch. 196, L. 2003; amd. Sec. 125, Ch. 467, L. 2005.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-313. Repealed

50-74-313. Repealed.
Sec. 127, Ch. 467, L. 2005.
History: En. Sec. 6, Ch. 32, L. 1905; re-en. Sec. 1656, Rev. C. 1907; amd. Sec. 14, Ch. 30, L. 1913; amd. Sec. 1, Ch. 54, L. 1919; re-en. Sec. 2727, R.C.M. 1921; amd. Sec. 2, Ch. 54, L. 1959; amd. Sec. 167, Ch. 147, L. 1963; amd. Sec. 15, Ch. 225, L. 1971; R.C.M. 1947, 69-1516; amd. Sec. 54, Ch. 492, L. 1997.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-314. Repealed

50-74-314. Repealed.
Sec. 46, Ch. 481, L. 1997.
History: En. Sec. 561, Pol. C. 1895; re-en. Sec. 1650, Rev. C. 1907; amd. Sec. 10, Ch. 30, L. 1913; re-en. Sec. 2721, R.C.M. 1921; amd. Sec. 9, Ch. 225, L. 1971; amd. Sec. 29, Ch. 182, L. 1975; R.C.M. 1947, 69-1510; amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 20, Ch. 514, L. 1995.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-315. Unlawful to operate boiler or steam engine without license

50-74-315. Unlawful to operate boiler or steam engine without license.
(1) It is unlawful for any person in this state to operate a stationary boiler or steam engine or any boiler or steam engine other than engines and boilers exempted by the provisions of 50-74-103 without a license granted under the provisions of this chapter. The owner, renter, or user of any engine or boiler is equally liable for the violation of this section.
(2) A person who operates a boiler or steam engine without first obtaining a license is guilty of a misdemeanor and, upon conviction, shall be fined no less than $50 or more than $100 or be imprisoned in the county jail for any term not to exceed 60 days, or both.
History: (1)En. Sec. 568, Pol. C. 1895; re-en. Sec. 1657, Rev. C. 1907; amd. Sec. 15, Ch. 30, L. 1913; re-en. Sec. 2728, R.C.M. 1921; re-en. Sec. 2728, R.C.M. 1935; amd. Sec. 16, Ch. 225, L. 1971; amd. Sec. 34, Ch. 182, L. 1975; Sec. 69-1517, R.C.M. 1947; (2)En. Sec. 559, Pol. C. 1895; re-en. Sec. 1648, Rev. C. 1907; amd. Sec. 8, Ch. 30, L. 1913; re-en. Sec. 2719, R.C.M. 1921; re-en. Sec. 2719, R.C.M. 1935; amd. Sec. 7, Ch. 225, L. 1971; amd. Sec. 10, Ch. 187, L. 1977; Sec. 69-1508, R.C.M. 1947; R.C.M. 1947, 69-1508(part), 69-1517(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-316. Unlawful to employ unlicensed operator

50-74-316. Unlawful to employ unlicensed operator.
It shall be unlawful, except as stated in 50-74-317, for any person, firm, or corporation to employ any person not duly licensed as an engineer within the meaning of this chapter to run or operate any of the boilers or engines subject to the provisions of this chapter.
History: En. Sec. 568, Pol. C. 1895; re-en. Sec. 1657, Rev. C. 1907; amd. Sec. 15, Ch. 30, L. 1913; re-en. Sec. 2728, R.C.M. 1921; re-en. Sec. 2728, R.C.M. 1935; amd. Sec. 16, Ch. 225, L. 1971; amd. Sec. 34, Ch. 182, L. 1975; R.C.M. 1947, 69-1517(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-317. When unlicensed person may operate

50-74-317. When unlicensed person may operate.
(1) In case of accident, sickness, or any unforeseen event that prevents a licensed engineer, employed by an owner, renter, or user of an engine or boiler, from performing required duties, the owner, renter, or user may for 15 days employ any person 18 years of age or older whom the owner, renter, or user considers competent to run the engine or boiler.
(2) Although the person employed may not be the holder of an engineer's license, the person must have reasonable qualifications acceptable to the department.
(3) A person employing an unlicensed engineer shall immediately notify the department.
(4) An owner, renter, or user of boilers or steam machinery may not employ unlicensed engineers for more than 15 days in any 1 calendar year.
History: En. Sec. 568, Pol. C. 1895; re-en. Sec. 1657, Rev. C. 1907; amd. Sec. 15, Ch. 30, L. 1913; re-en. Sec. 2728, R.C.M. 1921; re-en. Sec. 2728, R.C.M. 1935; amd. Sec. 16, Ch. 225, L. 1971; amd. Sec. 34, Ch. 182, L. 1975; R.C.M. 1947, 69-1517(part); amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 21, Ch. 514, L. 1995.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-318. Qualifications of boiler inspectors -- fees for inspections

50-74-318. Qualifications of boiler inspectors -- fees for inspections.
(1) A person employed by the department to enter premises and inspect boilers or machinery subject to this chapter must:
(a) have 5 years of actual experience in the operation or inspection of boilers or steam-driven equipment; and
(b) hold or possess the necessary qualifications to obtain either a stationary engineer's license or a commission issued by the national board of boiler and pressure vessel inspectors.
(2) The department shall establish a schedule of fees and may collect fees for the inspection of boilers prior to the issuance of a boiler operating certificate. The fees must be commensurate with the cost of the inspections and with appropriations for other purposes.
History: En. Sec. 1, Ch. 440, L. 2021.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 74. Boilers and Steam Engines › Part 3. Licenses › 50-74-320. Examinations -- fees -- third parties

50-74-320. Examinations -- fees -- third parties.
(1) The department shall administer the engineer examinations at least once every 3 months at places within the state as determined by the department.
(2) The department shall determine the fees to be charged an applicant for each examination and reexamination. The fees must be commensurate with costs.
(3) The department may use a third party to provide examination and grading services.
History: En. Sec. 25, Ch. 196, L. 2003.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 75. Consolidation of Boiler, Mine, and Coal Mine Inspectors (Repealed) › Part 1. General Provisions (Repealed) › 50-75-101. Repealed

50-75-101. Repealed.
Sec. 10, Ch. 21, L. 1981.
History: En. Sec. 1, Ch. 92, L. 1917; amd. Sec. 1, Ch. 47, L. 1921; re-en. Sec. 3034, R.C.M. 1921; re-en. Sec. 3034, R.C.M. 1935; R.C.M. 1947, 50-901.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 75. Consolidation of Boiler, Mine, and Coal Mine Inspectors (Repealed) › Part 1. General Provisions (Repealed) › 50-75-102. Repealed

50-75-102. Repealed.
Sec. 10, Ch. 21, L. 1981.
History: En. Sec. 2, Ch. 92, L. 1917; amd. Sec. 2, Ch. 47, L. 1921; re-en. Sec. 3035, R.C.M. 1921; re-en. Sec. 3035, R.C.M. 1935; R.C.M. 1947, 50-902.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 75. Consolidation of Boiler, Mine, and Coal Mine Inspectors (Repealed) › Part 1. General Provisions (Repealed) › 50-75-103. Repealed

50-75-103. Repealed.
Sec. 10, Ch. 21, L. 1981.
History: En. Sec. 3, Ch. 92, L. 1917; re-en. Sec. 3036, R.C.M. 1921; re-en. Sec. 3036, R.C.M. 1935; R.C.M. 1947, 50-903.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 75. Consolidation of Boiler, Mine, and Coal Mine Inspectors (Repealed) › Part 1. General Provisions (Repealed) › 50-75-104. Repealed

50-75-104. Repealed.
Sec. 10, Ch. 21, L. 1981.
History: En. Sec. 4, Ch. 92, L. 1917; re-en. Sec. 3037, R.C.M. 1921; re-en. Sec. 3037, R.C.M. 1935; R.C.M. 1947, 50-904(part).
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 75. Consolidation of Boiler, Mine, and Coal Mine Inspectors (Repealed) › Part 1. General Provisions (Repealed) › 50-75-105. Repealed

50-75-105. Repealed.
Sec. 10, Ch. 21, L. 1981.
History: En. Sec. 4, Ch. 92, L. 1917; re-en. Sec. 3037, R.C.M. 1921; re-en. Sec. 3037, R.C.M. 1935; R.C.M. 1947, 50-904(part); amd. Sec. 24, Ch. 37, L. 1979.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 75. Consolidation of Boiler, Mine, and Coal Mine Inspectors (Repealed) › Part 1. General Provisions (Repealed) › 50-75-106. Repealed

50-75-106. Repealed.
Sec. 10, Ch. 21, L. 1981.
History: En. Sec. 5, Ch. 92, L. 1917; re-en. Sec. 3038, R.C.M. 1921; re-en. Sec. 3038, R.C.M. 1935; R.C.M. 1947, 50-905.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 75. Consolidation of Boiler, Mine, and Coal Mine Inspectors (Repealed) › Part 1. General Provisions (Repealed) › 50-75-107. Repealed

50-75-107. Repealed.
Sec. 10, Ch. 21, L. 1981.
History: En. Sec. 55, Ch. 96, L. 1915; amd. Sec. 6, Ch. 92, L. 1917; re-en. Sec. 3039, R.C.M. 1921; re-en. Sec. 3039, R.C.M. 1935; R.C.M. 1947, 50-906(part); amd. Sec. 25, Ch. 37, L. 1979.
2023 Montana Code Annotated › Title 50. Health and Safety › Chapter 76. Hoisting Engines › Part 1. General Provisions › 50-76-101. When chapter not to apply

50-76-101. When chapter not to apply.
(1) This chapter does not apply to hoisting engines, air compressors, or elevators under federal control or to operating elevators in completed private or public buildings.
(2) The provisions of this chapter do not apply to forklifts and front-end and rear-end loaders or line trucks and bucket trucks.
(3) For the purposes of this section, "line trucks" are hoisting and digging devices mounted on a standard manufacturer's truck chassis with an all-weather cab capable of transporting a driver and two or more crew members. Line trucks are equipped with a hydraulically operated, telescoping boom that uses a nonmetallic cable for hoisting. Line trucks may be equipped with a rotary digging device and are capable of attaining maximum allowable highway speeds. "Bucket trucks" are personnel-lifting devices designed to lift personnel to work stations above ground. Bucket trucks are not designed for the purposes intended for a line truck.
History: (1)En. Sec. 3, Ch. 104, L. 1915; amd. Sec. 2, Ch. 31, L. 1919; re-en. Sec. 2732, R.C.M. 1921; re-en. Sec. 2732, R.C.M. 1947; amd. Sec. 19, Ch. 225, L. 1971; amd. Sec. 4, Ch. 456, L. 1975; Sec. 69-1603, R.C.M. 1947; (2)En. Sec. 1, Ch. 104, L. 1915; amd. Sec. 1, Ch. 31, L. 1919; re-en. Sec. 2730, R.C.M. 1921; re-en. Sec. 2730, R.C.M. 1935; amd. Sec. 17, Ch. 225, L. 1971; amd. Sec. 35, Ch. 182, L. 1975; amd. Sec. 1, Ch. 456, L. 1975; Sec. 69-1601, R.C.M. 1947; R.C.M. 1947, 69-1601(5), 69-1603(2); amd. Sec. 1, Ch. 288, L. 1983; amd. Sec. 1, Ch. 247, L. 1987; amd. Sec. 1892, Ch. 56, L. 2009.