reglab/housing_qa huggingface dataset:
UT Code § 15A-3-313 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 3 - Statewide Amendments to International Plumbing Code|Section 313 - Amendments to Chapter 13 of IPC.

 Effective 5/12/2020  15A-3-313. Amendments to Chapter 13 of IPC.    (1) A new IPC, Section 1301.4.1, is added as follows:"1301.4.1 Recording.The existence of a nonpotable water system shall be recorded on the deed of ownership for the property. The certificate of occupancy shall not be issued until the documentation for the recording required under this section is completed by the property owner."     (2) IPC, Section 1301.5, is deleted and replaced with the following:"1301.5 Potable water connections.Where a potable water system is connected to a nonpotable water system, the potable water supply shall be protected against backflow by a reduced pressure backflow prevention assembly or an air gap installed in accordance with Section 608."     (3) IPC, Section 1301.9.4, is deleted and replaced with the following:" 1301.9.4 Makeup water.Where an uninterrupted supply is required for the intended application, potable or reclaimed water shall be provided as a source of makeup water for the storage tank. The makeup water supply shall be protected against backflow by a reduced pressure backflow prevention assembly or an air gap installed in accordance with Section 608. A full-open valve located on the makeup water supply line to the storage tank shall be provided. Inlets to the storage tank shall be controlled by fill valves or other automatic supply valves installed to prevent the tank from overflowing and to prevent the water level from dropping below a predetermined point. Where makeup water is provided, the water level shall not be permitted to drop below the source water inlet or the intake of any attached pump."     (4) IPC, Section 1302.12.4, is deleted and replaced with the following:"1302.12.4 Inspection and testing of backflow prevention assemblies.Testing of a backflow preventer shall be conducted in accordance with Sections 312.10.1, 312.10.2, and 312.10.3."     (5) IPC, Section 1303.15.6, is deleted and replaced with the following:"1303.15.6 Inspection and testing of backflow prevention assemblies.Testing of a backflow prevention assembly shall be conducted in accordance with Sections 312.10.1, 312.10.2, and 312.10.3."     (6) IPC, Section 1304.4.2, is deleted and replaced with the following:"1304.4.2 Inspection and testing of backflow prevention assemblies.Testing of a backflow preventer or backwater valve shall be conducted in accordance with Sections 312.10.1, 312.10.2, and 312.10.3."    Amended by Chapter 441, 2020 General Session
UT Code § 15A-3-314 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 3 - Statewide Amendments to International Plumbing Code|Section 314 - Amendments to Chapter 14 of IPC.

 Effective 7/1/2019  15A-3-314. Amendments to Chapter 14 of IPC.  IPC, Chapter 14, is deleted and replaced with the following:"1401. Subsurface Landscape Irrigation Systems.Graywater recycling systems utilized for subsurface irrigation for single-family residences shall comply with the requirements of UAC R317-401, Graywater Systems. Graywater recycling systems utilized for subsurface irrigation for other occupancies shall comply with UAC R317-3, Design Requirements for Wastewater Collection, Treatment, and Disposal Systems, and UAC R317-4, Onsite Wastewater Systems." Amended by Chapter 20, 2019 General Session
UT Code § 15A-3-315 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 3 - Statewide Amendments to International Plumbing Code|Section 315 - Amendments to Chapter 15 of IPC.

 Effective 7/1/2016  15A-3-315. Amendments to Chapter 15 of IPC.  In IPC, Chapter 15, the following referenced standard is added:    "Standard reference numberTitleReferenced in code section number   USC-FCCCHR 10th Edition Manual of Cross Connection ControlFoundation for Cross-Connection Control and Hydraulic Research University of Southern California Kaprielian Hall 300 Los Angeles CA 90089-2531Table 608.1"    Enacted by Chapter 249, 2016 General Session
UT Code § 15A-3-401 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 4 - Statewide Amendments to International Mechanical Code|Section 401 - General provisions.

 Effective 7/1/2019  15A-3-401. General provisions.    (1) The amendments in this part are adopted as amendments to the IMC to be applicable statewide.     (2) In IMC, Section 1004.2, the first sentence is deleted and replaced with the following: " In accordance with Title 34A, Chapter 7, Safety, and requirements made by rule by the Labor Commission, boilers and pressure vessels in Utah are regulated by the Utah Labor Commission, Division of Boiler, Elevator and Coal Mine Safety, except those located in private residences or in apartment houses of less than five family units. Boilers shall be installed in accordance with their listing and labeling, with minimum clearances as prescribed by the manufacturer's installation instructions and the state boiler code, whichever is greater."     (3) In IMC, Section 1004.3.1, the word "unlisted" is inserted before the word "boilers".     (4) In IMC, Section 1209.3, the following words are added at the end of the section: "or other methods approved for the application."    Amended by Chapter 20, 2019 General Session
UT Code § 15A-3-402 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 4 - Statewide Amendments to International Mechanical Code|Section 402 - Amendments to Chapters 1 through 5 of IMC.

 Effective 5/12/2020  15A-3-402. Amendments to Chapters 1 through 5 of IMC.    (1) In IMC, Table 403.3.1.1, note h is deleted and replaced with the following: "h. 1. A nail salon shall provide each manicure station where a nail technician files or shapes an acrylic nail, as defined by rule by the Division of Occupational and Professional Licensing, in accordance with Title 63G, Chapter 3, Utah Administrative Rulemaking Act, with: a. a source capture system equipped with, at minimum, a MERV 8 particulate filter and an activated carbon filter that is capable of filtering and recirculating air to inside space at a rate not less than 50 cfm per station; or b. a source capture system capable of exhausting not less than 50 cfm per station. c. A nail salon that complies with Note h. la or h. lb is not required to comply with the labeling, listing, or testing requirements described in International Mechanical Code sections 301.7 or 301.8. 2. For a source capture system described in paragraph 1, the source capture system inlets for exhausting or recirculating air shall be located in accordance with Section 502.20. 3. Where one or more exhausting source capture systems described in paragraph 1 operate continuously during occupancy, the source capture system exhaust rate shall be permitted to be applied to the exhaust flow rate required by Table 403.3.1.1 for the nail salon. 4. The requirements of this note apply to: a. an existing nail salon that remodels the nail salon after July 1, 2017; b. a new nail salon that begins construction after July 1, 2017; and c. all nail salons beginning on July 1, 2020."     (2) In IMC, Section 502.20 is deleted and rewritten as follows: "502.20 Manicure stations. A nail salon that files or shapes an acrylic nail shall provide each manicure station with a source capture system in accordance with Table 403.3.1.1, note h. For a manicure table that does not have factory-installed source capture system inlets for recirculating or exhausting air, a nail salon shall provide the manicure table with inlets for recirculating or exhausting air located not more than 12 inches (305 mm) horizontally and vertically from the point of any acrylic chemical application. Exception: Section 502.20 applies to a manicure station in: a. an existing nail salon that remodels the nail salon after July 1, 2017; b. a new nail salon that begins construction after July 1, 2017; and c. all nail salons beginning on July 1, 2020."    Amended by Chapter 441, 2020 General Session
UT Code § 15A-3-501 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 5 - Statewide Amendments to International Fuel Gas Code|Section 501 - General provisions.

 Effective 7/1/2019  15A-3-501. General provisions.  The following are adopted as an amendment to the IFGC to be applicable statewide:  (1) In IFGC, Section 404.9, a new Section 404.9.1, is added as follows: "404.9.1 Meter protection. Fuel gas services shall be in an approved location and/or provided with structures designed to protect the fuel gas meter and surrounding piping from physical damage, including falling, moving, or migrating ice and snow. If an added structure is used, it must still provide access for service and comply with the IBC or the IRC."     (2) IFGC, Section 409.5.3, is deleted.     (3) In IFGC, Section 502.1, the last sentence is deleted and replaced with "Plastic vents for Category IV appliances shall not be required to be listed and labeled where such vents comply with all of the following:1. specified by the appliance manufacturer;2. installed in accordance with the appliance manufacturer's instructions; and3. the vent gas temperatures do not exceed 140 degrees Fahrenheit."     (4) In IFGC, Section 503.4.1, in the last sentence after "appliance manufacturer" insert: "where the appliance vent gas temperatures do not exceed 140 degrees Fahrenheit,".     (5) In IFGC, Section 503.6.11.1, the following exception is added:"Exception: Existing and replacement Category I appliances may be located in rooms within the occupiable space provided all the following are met:1. The original installation was compliant with existing codes at the time of installation.2. The dwelling is equipped with a current, operable carbon monoxide detector, installed in accordance with Section 915 of the International Building Code.3. The AHJ has approved a replacement based on the extreme difficulty of an installing individual Category I vent system or a direct vent Category IV appliance.4. The room or space is used for no other purpose.5. Combustion air is provided in accordance with Section 304. Where outdoor combustion air is provided, the room has a solid weather-stripped door equipped with an approved self-closure device.6. Common vents terminate with a listed cap."     (6) In IFGC, Section 631.2, the following sentence is inserted before the first sentence: " In accordance with Title 34A, Chapter 7, Safety, and requirements made by rule by the Labor Commission, boilers and pressure vessels in Utah are regulated by the Utah Labor Commission, Division of Boiler, Elevator and Coal Mine Safety, except those located in private residences or in apartment houses of less than five family units. Boilers shall be installed in accordance with their listing and labeling, with minimum clearances as prescribed by the manufacturer's installation instructions and the state boiler code, whichever is greater."    Amended by Chapter 20, 2019 General Session
UT Code § 15A-3-601 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 6 - Statewide Amendments to National Electrical Code|Section 601 - General provisions.

 Effective 7/1/2021  15A-3-601. General provisions.  The following are adopted as amendments to the NEC to be applicable statewide:  (1) The IRC provisions are adopted as the residential electrical standards applicable to residential installations under the IRC. All other installations shall comply with the adopted NEC.     (2) In NEC, Section 210.8(A), the words "through 250-volt" are deleted.     (3) In NEC, Section 210.8(A)(5), the word "Basements" is deleted and replaced with "Unfinished portions or areas of the basement not intended as habitable rooms."     (4) In NEC, Section 210.8(F), is deleted.     (5) NEC, Section 210.65, is deleted.     (6) In NEC, Section 230.67, is deleted.     (7) In NEC, Section 314.27(C), is deleted and replaced with the following: "314.27(C) Boxes at Ceiling-Suspended (Paddle) Fan Outlets. Outlet boxes or outlet box systems used as the sole support of a ceiling-suspended (paddle) fan shall be listed, shall be marked by their manufacturer as suitable for this purpose, and shall not support ceiling-suspended (paddle) fans that weigh more than 32 kg (70 lb). For outlet boxes or outlet box systems designed to support ceiling-suspended (paddle) fans that weigh more than 16 kg (35 lb), the required marking shall include the maximum weight to be supported."     (8) In NEC, Section 406.9(C), is deleted and replaced with the following: "406.9(C) Bathtub and Shower Space. Receptacles shall not be installed within or directly over a bathtub or shower stall."    Amended by Chapter 199, 2021 General Session
UT Code § 15A-3-1001 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 9 - Installation and Safety Requirements for Mobile Homes Built Before June 15, 1976|Section 1001 - General provisions.

 Effective 5/12/2020  15A-3-1001. General provisions.    (1) In ISPSC, Section 202, the following definition is added for private residential swimming pool: "PRIVATE RESIDENTIAL SWIMMING POOL. A swimming pool, spa pool, or wading pool used only by an individual, family, or living unit members and guests, but not serving any type of multiple unit housing complex of four or more living units."     (2) In ISPSC, Section 320.1, the following changes are made:   (a) the words "or storm" are deleted;     (b) the words "onsite waste water" are added before the word "disposal"; and     (c) the words "or shall be disposed of by other means approved by the state or local authority" are deleted.      Enacted by Chapter 441, 2020 General Session
UT Code § 15A-3-1001 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 3 - Statewide Amendments Incorporated as Part of State Construction Code|Part 10 - Statewide Amendments to International Swimming Pool and Spa Code|Section 1001 - General provisions.

 Effective 5/12/2020  15A-3-1001. General provisions.    (1) In ISPSC, Section 202, the following definition is added for private residential swimming pool: "PRIVATE RESIDENTIAL SWIMMING POOL. A swimming pool, spa pool, or wading pool used only by an individual, family, or living unit members and guests, but not serving any type of multiple unit housing complex of four or more living units."     (2) In ISPSC, Section 320.1, the following changes are made:   (a) the words "or storm" are deleted;     (b) the words "onsite waste water" are added before the word "disposal"; and     (c) the words "or shall be disposed of by other means approved by the state or local authority" are deleted.      Enacted by Chapter 441, 2020 General Session
UT Code § 15A-4-101 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 4 - Local Amendments Incorporated as Part of State Construction Code|Part 1 - Local Amendments to International Building Code|Section 101 - General provision.

15A-4-101. General provision.  The amendments in this part are adopted as amendments to the IBC to be applicable to the specified jurisdiction.  Enacted by Chapter 14, 2011 General Session
UT Code § 15A-4-105 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 4 - Local Amendments Incorporated as Part of State Construction Code|Part 1 - Local Amendments to International Building Code|Section 105 - Amendments to IBC applicable to Park City Corporation or Park City Fire District.

 Effective 5/9/2017  15A-4-105. Amendments to IBC applicable to Park City Corporation or Park City Fire District.    (1) The following amendment is adopted as an amendment to the IBC for the Park City Corporation, in IBC, Section 3409.2, exception 3, is modified to read as follows: "3. Designated as historic under a state or local historic preservation program."     (2) The following amendments are adopted as amendments to the IBC for the Park City Corporation and Park City Fire District:   (a) IBC, Section (F)903.2, is deleted and replaced with the following: "(F)903.2 Where required. Approved automatic sprinkler systems in new buildings and structures shall be provided in the location described in this section.1. All new construction having more than 6,000 square feet on any one floor, except R-3 occupancy.2. All new construction having more than two (2) stories, except R-3 occupancy.3. All new construction in the Historic Commercial Business zone district, regardless of occupancy.4. All new construction and buildings in the General Commercial zone district where there are side yard setbacks or where one or more side yard setbacks is less than two and one half (2.5) feet per story of height.5. All existing building within the Historic District Commercial Business zone."; and     (b) In IBC, Table 1505.1, new footnotes d and e are added as follows: "d. Wood roof covering assemblies are prohibited in R-3 occupancies in areas with a combined rating of more than 11 using Tables 1505.1.1 and 1505.1.2 with a score of 9 for weather factors.e. Wood roof covering assemblies shall have a Class A rating in occupancies other than R-3 in areas with a combined rating of more than 11 using Tables 1505.1.1 and 1505.1.2 with a score of 9 for weather factors. The owner of the building shall enter into a written and recorded agreement that the Class A rating of the roof covering assembly will not be altered through any type of maintenance process.     TABLE 1505.1.1     WILDFIRE HAZARD SEVERITY SCALE    RATINGSLOPEVEGETATION   1less than or equal to 10%Pinion-juniper   210.1 - 20%Grass-sagebrush   3greater than 20%Mountain brush or softwoods        TABLE 1505.1.2     PROHIBITION/ALLOWANCE OF WOOD ROOFING    RatingR-3 OccupancyAll Other Occupancies   Less than or equal to 11Wood roof covering assemblies per Table 1505.1 are allowedWood roof covering assemblies per Table 1505.1 are allowed   Greater than or equal to 12Wood roof covering is prohibitedWood roof covering assemblies with a Class A rating are allowed"        Amended by Chapter 341, 2017 General Session
UT Code § 15A-4-106 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 4 - Local Amendments Incorporated as Part of State Construction Code|Part 1 - Local Amendments to International Building Code|Section 106 - Amendments to IBC applicable to Salt Lake City.

15A-4-106. Amendments to IBC applicable to Salt Lake City.  The following amendment is adopted as an amendment to the IBC for Salt Lake City, in IBC, Section 1008.1.9.7, a new exception is added as follows: "Exception: In International Airport areas designated as Group "A" Occupancies where national security interests are present, the use of panic hardware with delayed egress is allowed when all provisions of Section 1008.1.9.7 are met and under item #4 1 second is changed to 2 seconds."  Enacted by Chapter 14, 2011 General Session
UT Code § 15A-4-107 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 4 - Local Amendments Incorporated as Part of State Construction Code|Part 1 - Local Amendments to International Building Code|Section 107 - Amendments to IBC applicable to Sandy City.

 Effective 7/1/2019  15A-4-107. Amendments to IBC applicable to Sandy City.  The following amendments are adopted as amendments to the IBC for Sandy City:  (1) A new IBC, Section (F)903.2.13, is added as follows: "(F)903.2.13 An automatic sprinkler system shall be installed in accordance with NFPA 13 throughout buildings containing all occupancies where fire flow exceeds 2,000 gallons per minute, based on Table B105.1 (2) of the 2018 International Fire Code. A one- or two-family dwelling or a town home is not required to have a fire sprinkler system except in accordance with Section 15A-5-203."     (2) A new IBC, Appendix N, is added and adopted as follows: "Appendix N BUILDINGS AND STRUCTURES CONSTRUCTED IN AREAS DESIGNATED AS WILDLAND-URBAN INTERFACE AREASAL 101.1 General. Buildings and structures constructed in areas designated as Wildland-Urban Interface Areas by Sandy City shall be constructed using ignition resistant construction as determined by the Fire Marshal. Section 502 of the 2006 International Wildland-Urban Interface Code (IWUIC), as promulgated by the International Code Council, shall be used to determine Fire Hazard Severity. The provisions listed in Chapter 5 of the 2006 International Wildland-Urban Interface Code, as modified herein, shall be used to determine the requirements for Ignition Resistant Construction."     (3) In Section 504 of the IWUIC Class I IGNITION-RESISTANT CONSTRUCTION a new Section 504.1.1 is added as follows: "504.1.1 General. Subsections 504.5, 504.6, and 504.7 shall only be required on the exposure side of the structure, as determined by the fire code official, where defensible space is less than 50 feet as defined in Section 603 of the 2006 International Wildland-Urban Interface Code."     (4) In Section 505 of the IWUIC Class 2 IGNITION-RESISTANT CONSTRUCTION Subsections 505.5 and 505.7 are deleted.    Amended by Chapter 20, 2019 General Session
UT Code § 15A-4-201 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 4 - Local Amendments Incorporated as Part of State Construction Code|Part 2 - Local Amendments to International Residential Code|Section 201 - General provision.

 Effective 5/9/2017  15A-4-201. General provision.  The amendments in this part are adopted as amendments to the IRC to be applicable to specified jurisdiction. Amended by Chapter 341, 2017 General Session