TX Health & Safety Code § 341.0359 (2021)
2021 Texas Statutes|Health and Safety Code|Title 5 - Sanitation and Environmental Quality|Subtitle A - Sanitation|Chapter 341 - Minimum Standards of Sanitation and Health Protection Measures|Subchapter C. Sanitary Standards of Drinking Water; Protection of Public Water Supplies and Bodies of Water|Section 341.0359. Fire Hydrant Flow Standards

Sec. 341.0359.  FIRE HYDRANT FLOW STANDARDS.  (a)  In this section:(1)  "Municipal utility" means a retail public utility, as defined by Section 13.002, Water Code, that is owned by a municipality.(2)  "Residential area" means an area used principally for private residences that is improved with at least 100 single-family homes and has an average density of one home per half acre.(3)  "Utility" includes a "public utility" and "water supply or sewer service corporation" as defined by Section 13.002, Water Code.(b)  The governing body of a municipality by ordinance may adopt standards set by the commission under Subsection (c) requiring a utility to maintain a minimum sufficient water flow and pressure to fire hydrants in a residential area located in the municipality or the municipality's extraterritorial jurisdiction.(c)  The commission by rule shall establish standards for adoption by a municipality under Subsection (b).  The standards:(1)  in addition to a utility's maximum daily demand, must provide, for purposes of emergency fire suppression, for:(A)  a minimum sufficient water flow of at least 250 gallons per minute for at least two hours; and(B)  a minimum sufficient water pressure of at least 20 pounds per square inch;(2)  must require a utility to maintain at least the minimum sufficient water flow and pressure described by Subdivision (1) in fire hydrants in a residential area located within the municipality or the municipality's extraterritorial jurisdiction;(3)  must be based on the density of connections, service demands, and other relevant factors;(4)  notwithstanding Subdivisions (1) and (2), if the municipality owns a municipal utility, may not require another utility located in the municipality or the municipality's extraterritorial jurisdiction to provide water flow and pressure in a fire hydrant greater than that provided by the municipal utility as determined by the commission; and(5)  if the municipality does not own a municipal utility, may not require a utility located in the municipality or the municipality's extraterritorial jurisdiction to provide a minimum sufficient water flow and pressure greater than the standard established under Subdivision (1).(d)  An ordinance under Subsection (b) may not require a utility to build, retrofit, or improve infrastructure in existence at the time the ordinance is adopted.(e)  A municipality with a population of less than 1.9 million that adopts standards under Subsection (b) or that seeks to use a utility's water for fire suppression shall enter into a written memorandum of understanding with the utility to provide for:(1)  the necessary testing of fire hydrants; and(2)  other relevant issues pertaining to the use of the water and maintenance of the fire hydrants to ensure compliance with this section.(f)  A municipality may notify the commission of a utility's failure to comply with a standard adopted under Subsection (b).(g)  On receiving the notice described by Subsection (f), the commission shall require a utility in violation of a standard adopted under this section to comply within a reasonable time established by the commission.  The commission may approve infrastructure improvements and make corresponding changes to the tariff or rate schedule of a utility that is a public utility as needed to permit compliance with this section.(h)  Notwithstanding any provision of Chapter 101, Civil Practice and Remedies Code, to the contrary, a utility is not liable for a hydrant's or metal flush valve's inability to provide adequate water supply in a fire emergency.  This subsection does not waive a municipality's immunity under Subchapter I, Chapter 271, Local Government Code, or any other law and does not create any liability on the part of a municipality under a joint enterprise theory of liability.|Added by Acts 2013, 83rd Leg., R.S., Ch. 332 (H.B. 1973), Sec. 1, eff. September 1, 2013.|