reglab/housing_qa huggingface dataset:
SD Codified L § 34-37-16.1 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 37 - Fireworks|Section 34-37-16.1 - Periods during which use of consumer fireworks permitted--Violation as misdemeanor.

34-37-16.1. Periods during which use of consumer fireworks permitted--Violation as misdemeanor.Except as otherwise provided in this chapter, a person is guilty of a Class 2 misdemeanor if the person uses consumer fireworks except during the period from June twenty-seventh to the first Sunday after July fourth, and during the period beginning December twenty-eighth to January first. Source: SL 1983, ch 259, §7; SL 2011, ch 162, §3; SL 2013, ch 162, §1; SL 2019, ch 154, §21, eff. Mar. 20, 2019.
SD Codified L § 34-37-16.2 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 37 - Fireworks|Section 34-37-16.2 - Certain fireworks permitted all year.

34-37-16.2. Certain fireworks permitted all year.The provisions of §§34-37-2 and 34-37-16.1 do not apply to:(1)Smoke effects if the smoke effects do not fly, travel, or explode;(2)Single-shot parachute pieces without a flare; or(3)Any fireworks classified as a novelty under section 3.2 of the American Pyrotechnics Association Standard 87-1, 2001 edition. Source: SL 2015, ch 186, §1; SL 2019, ch 154, §22, eff. Mar. 20, 2019.
SD Codified L § 34-37-17 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 37 - Fireworks|Section 34-37-17 - Enforcement of chapter.

34-37-17. Enforcement of chapter.The Department of Public Safety, together with any law enforcement agency of the state or any political subdivision of the state, shall enforce this chapter. Source: SL 1964, ch 31, §9; SL 2003, ch 272 (Ex. Ord. 03-1), §20; SL 2019, ch 154, §23, eff. Mar. 20, 2019.
SD Codified L § 34-37-18 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 37 - Fireworks|Section 34-37-18 - Record forms prescribed by secretary.

34-37-18. Record forms prescribed by secretary.Records required under provisions of this chapter shall be kept on forms prescribed by the secretary of public safety. Source: SL 1983, ch 259, §7; SL 2003, ch 272, §§20, 121.
SD Codified L § 34-37-19 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 37 - Fireworks|Section 34-37-19 - County regulation of fireworks--Use of South Dakota grassland fire danger index.

34-37-19. County regulation of fireworks--Use of South Dakota grassland fire danger index--Violation as misdemeanor. Any county may, by resolution, regulate or prohibit the use of fireworks outside the boundaries of any municipality in those areas where the fire danger, as determined by use of the South Dakota grassland fire danger index published by the National Weather Service, has reached the extreme category in that county during the period from June twentieth to July second, inclusive, and during the period from December twenty-eighth to January first, inclusive. During any such period, the county's action is suspended if the grassland fire danger index falls below the very high category and again becomes effective if the grassland fire danger index reaches the extreme category. Any violation of a resolution adopted pursuant to this section is a Class 2 misdemeanor. Source: SL 1989, ch 302; SL 2002, ch 252 (Ex. Ord. 02-1), §17; SL 2003, ch 187, §1; SL 2004, ch 239, §1; SL 2011, ch 162, §4; SL 2021, ch 156, § 1, eff. Mar. 25, 2021.
SD Codified L § 34-38-2.1 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-2.1 - Self-service pumps--Latch-open device permitted.

34-38-2.1. Self-service pumps--Latch-open device permitted.Notwithstanding any other provisions of this chapter or rules promulgated thereunder, a latch-open device may be used on the hose nozzle valve of a self-service fuel dispensing pump if the valve conforms to applicable requirements of section 19 of Underwriters Laboratories Incorporated pamphlet number 842 entitled "Standards for Valves for Flammable Fluids" published in 1974. Source: SL 1982, ch 268.
SD Codified L § 34-38-23 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-23 - Definition of terms.

34-38-23. Definition of terms.Terms used in this chapter mean:(1)"Aboveground storage tank," a horizontal or vertical tank that is listed and intended for fixed installation at or above grade and is used within the scope of its listing. This includes a tank inside a building;(2)"Authority having jurisdiction," the local or state governing organization, office, or individual responsible for approving equipment, installation, or procedure;(3)"Combustible liquid," a liquid having a flash point at or above 100 degrees Fahrenheit, (37.8 degrees Celsius);(4)"Department," the Department of Public Safety;(5)Repealed by SL 2006, ch 185, §5;(6)"Flammable liquid," a liquid having a flash point below 100 degrees Fahrenheit (37.8 degrees Celsius) and having a vapor pressure not exceeding forty psia (2,068 mm hg) at 100 degrees Fahrenheit (37.8 degrees Celsius) shall be known as a class I liquid;(7)"Listed," equipment or materials included in a list published by an organization acceptable to the authority having jurisdiction and concerned with product evaluation, that maintains periodic inspection of production of listed equipment or materials and whose listing states either that the equipment or material meets appropriate standards or has been tested and found suitable for use in a specified manner; and(8)"Retail sale," the sale of flammable and combustible liquids for any purpose other than for resale. Source: SL 1991, ch 269, §1; SL 2003, ch 272, §§20, 121; SL 2004, ch 17, §225; SL 2006, ch 185, §5.
SD Codified L § 34-38-24 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-24 - Installation of aboveground storage tanks--Approval.

34-38-24. Installation of aboveground storage tanks--Approval.Aboveground storage tanks may be installed at retail locations with the approval of the authority having jurisdiction and as provided for in this chapter. Source: SL 1991, ch 269, §2.
SD Codified L § 34-38-25 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-25 - Letter of approval required before proposed construction begins--Letter and plans to be submitted to division.

34-38-25. Letter of approval required before proposed construction begins--Letter and plans to be submitted to division.Before proposed construction begins the applicant shall obtain a letter of approval from the local governing body within whose jurisdiction the system is to be installed. This letter and two sets of plans, blueprints, or drawings shall be submitted to the division for examination and approval of compliance with this chapter. Source: SL 1991, ch 269, §3.
SD Codified L § 34-38-26 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-26 - Compliance with International Fire Code.

34-38-26. Compliance with International Fire Code.Except as otherwise provided in this chapter, aboveground storage tanks shall comply with the applicable provisions of chapter 57 of the International Fire Code, 2015 edition. Source: SL 1991, ch 269, §4; SL 2006, ch 185, §6; SL 2010, ch 177, §3; SL 2016, ch 181, §3.
SD Codified L § 34-38-27 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-27 - Aboveground storage tank to be listed for such use--Underground tanks not to be installed aboveground--Failure to comply as misdemeanor.

34-38-27. Aboveground storage tank to be listed for such use--Underground tanks not to be installed aboveground--Failure to comply as misdemeanor.Any tank used for aboveground storage shall be listed for aboveground use. No backfill is permitted. No tank designed and built for underground use may be installed for aboveground use. A violation of this section is a Class 2 misdemeanor. Source: SL 1991, ch 269, §5.
SD Codified L § 34-38-28 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-28 - Location requirements for aboveground tanks.

34-38-28. Location requirements for aboveground tanks.Any aboveground storage tank shall be located at least:(1)Fifty feet from the nearest important building on the same property;(2)Fifty feet from any fuel dispenser;(3)Fifty feet from the nearest side of any public way; and(4)Fifty feet from any property line that is or may be built upon.However, distances may be reduced based on site limitations and conditions or quantity of liquid storage at the discretion of the local and division authority having jurisdiction. Source: SL 1991, ch 269, §6.
SD Codified L § 34-38-29 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-29 - Spill control to be in accordance with International Fire Code.

34-38-29. Spill control to be in accordance with International Fire Code.Spill control shall be provided in accordance with chapter 57 of the International Fire Code, 2015 edition. Source: SL 1991, ch 269, §7; SL 2006, ch 185, §7; SL 2010, ch 177, §4; SL 2016, ch 181, §4.
SD Codified L § 34-38-30 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-30 - Impermissible methods for dispensing fuel from aboveground tank--Equipment requirements as to tanks--Failure to comply as misdemeanor.

34-38-30. Impermissible methods for dispensing fuel from aboveground tank--Equipment requirements as to tanks--Failure to comply as misdemeanor.No person may dispense fuel from an aboveground storage tank by either gravity flow or pressurization of the tank. The owner of an aboveground storage tank shall prevent the release of liquid from the tank by syphon flow.If an aboveground storage tank is at an elevation that produces a gravity head on the dispensing device, the tank outlet shall be equipped with a device such as a normally-closed solenoid valve that will prevent gravity flow from the tank to the dispenser. This device shall be located adjacent to and downstream of the outlet valve. The device shall be installed and adjusted so that liquid cannot flow by gravity from the tank to the dispenser if the piping or hose fails.If a submersible pump system is used, a listed rigidly anchored emergency shutoff valve, incorporating a fusible link or other thermally actuated device which is designed to close automatically in the event of severe impact or fire exposure, shall be installed in accordance with the manufacturer's instructions in the supply line at the base of each individual island-type dispenser or at the inlet of each overhead dispensing device. An emergency shutoff valve incorporating a slip joint feature may not be used. The automatic closing feature of this valve shall be checked at the time of initial installation and at least once a year thereafter by manually tripping the hold-open linkage.If a suction pump-type dispensing device is used, a listed, vacuum-actuated shut-off valve, with a shear section, or an equivalent-type valve shall be installed directly beneath each dispensing device.Shut-off and check valve shall be equipped with a pressure-relieving device to relieve the pressure generated by thermal expansion back to the tank and piping shall be routed so that exposure to physical damage is minimized.A violation of this section is a Class 2 misdemeanor. Source: SL 1991, ch 269, §8.
SD Codified L § 34-38-31 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-31 - Protection against vehicular collision.

34-38-31. Protection against vehicular collision.Aboveground tanks shall be protected against vehicular collision by suitable barriers. Source: SL 1991, ch 269, §9.
SD Codified L § 34-38-32 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-32 - Maintenance of area within any dike.

34-38-32. Maintenance of area within any dike.The area within any dike shall be kept free of vegetation, debris, and any other material that is not necessary to the operation of the tank and piping system. Source: SL 1991, ch 269, §10.
SD Codified L § 34-38-33 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-33 - Tank piping system in contact with soil--Protection from corrosion.

34-38-33. Tank piping system in contact with soil--Protection from corrosion.Any portion of a tank piping system that is in contact with the soil shall be protected from corrosion in accordance with chapter 57 of the International Fire Code, 2015 edition. Source: SL 1991, ch 269, §11; SL 2008, ch 175, §1; SL 2010, ch 177, §5; SL 2016, ch 181, §5.
SD Codified L § 34-38-34 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-34 - Delivery and dispensing operations to comply with International Fire Code--Determining liquid level--Equipment requirements.

34-38-34. Delivery and dispensing operations to comply with International Fire Code--Determining liquid level--Equipment requirements.Delivery operations shall comply with applicable requirements of chapter 57 of the International Fire Code, 2015 edition. Dispensing operations shall comply with the provisions of chapter 57 of the International Fire Code, 2015 edition.The delivery vehicle shall be separated from any aboveground tank by at least twenty-five feet.Means shall be provided for determining the liquid level in each tank and this means shall be accessible to the delivery operator. Provisions shall be made either to automatically stop the delivery of fuel to the tank if the liquid level in the tank reaches ninety-five percent capacity or to sound an audible alarm if the liquid level in the tank reaches ninety percent capacity.A check valve, gate valve with quick-connect coupling, or a dry-break valve shall be installed in the piping at the point where connection and disconnection is made for delivery from a vehicle to any aboveground tank. This device shall be protected against tampering and physical damage.If the delivery hose is connected directly to the tank, the fill line at the tank shall be equipped with a tight-fill device for connecting the hose to the tank. Source: SL 1991, ch 269, §12; SL 2006, ch 185, §8; SL 2010, ch 177, §6; SL 2016, ch 181, §6.
SD Codified L § 34-38-35 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-35 - Promulgation of rules.

34-38-35. Promulgation of rules.For the purpose of implementing this chapter, the department may promulgate rules, pursuant to chapter 1-26, to protect the health and safety of persons from fire, explosion and like emergencies based on codes and standards set forth by the International Building Code, the International Fire Code, and the International Mechanical Code, 2015 editions, and referenced standards except such portions as are deleted, modified, or amended. Source: SL 1991, ch 269, §13; SL 2006, ch 185, §9; SL 2010, ch 177, §7; SL 2016, ch 181, §7.
SD Codified L § 34-38-36 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-36 - Power of local governments as to zoning unaffected.

34-38-36. Power of local governments as to zoning unaffected.Nothing in this chapter affects the power of any local government to regulate the use of land by zoning. Any municipality in which there is no comprehensive zoning ordinance in effect may prohibit the installation of flammable or combustible liquids at retail locations within areas which are predominately residential and areas used predominately for retail mercantile purposes. Source: SL 1991, ch 269, §14; SL 1992, ch 60, §2.
SD Codified L § 34-38-37 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-37 - Review of actions by director--Director's decision appealable.

34-38-37. Review of actions by director--Director's decision appealable.Any person aggrieved by any action or decision pursuant to this chapter may seek review of such action or decision by the director of the division pursuant to the contested case provisions of chapter 1-26. The decision of the director may be appealed to circuit court in the manner provided by chapter 1-26. Source: SL 1991, ch 269, §15.
SD Codified L § 34-38-38 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-38 - Application to facilities constructed after July 1, 2016.

34-38-38. Application to facilities constructed after July 1, 2016.The provisions of this chapter apply to facilities constructed after July 1, 2016. Existing installations shall be permitted only if, in the opinion of local and state authorities, the existing installation does not constitute a distinct hazard to life or property. Source: SL 1991, ch 269, §16; SL 2006, ch 185, §10; SL 2010, ch 177, §8; SL 2016, ch 181, §8.
SD Codified L § 34-38-39 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 38 - Flammable And Combustible Liquids|Section 34-38-39 - Limitations as to tank capacity.

34-38-39. Limitations as to tank capacity.Tanks may not exceed an individual capacity of twelve thousand gallons and may not exceed an aggregate capacity of forty-eight thousand gallons. Any variance in excess of these amounts can only be granted by the division pursuant to chapter 1-26. Source: SL 1991, ch 269, §17; SL 2008, ch 175, §2.
SD Codified L § 34-39-1 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 39 - Liquefied Petroleum Gases|Section 34-39-1 - Definitions.

34-39-1. Definitions.Terms used in this chapter mean:(1)"Department," the Department of Public Safety;(2)"Secretary," the secretary of the Department of Public Safety. Source: SL 2016, ch 183, §57.
SD Codified L § 34-39-1.1 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 39 - Liquefied Petroleum Gases|Section 34-39-1.1 - Liquefied petroleum gas defined.

34-39-1.1. Liquefied petroleum gas defined.The term "liquefied petroleum gas," as used in this chapter, shall mean and include any material which is composed predominantly of any of the following hydrocarbons, or mixtures of the same: propane, propylene, butanes (normal butane or isobutane), and butylenes. Source: SL 1941, ch 101, §1; SL 1947, ch 98, §1; SDC Supp 1960, §31.03A01; SDCL §34-39-1.
SD Codified L § 34-39-2 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 39 - Liquefied Petroleum Gases|Section 34-39-2 - Sale of gas by approved weights and measures required--Violation as misdemeanor.

34-39-2. Sale of gas by approved weights and measures required--Violation as misdemeanor.It is a Class 2 misdemeanor to sell or offer for sale, either at wholesale or retail, any liquefied petroleum gas, either in liquid or vapor form, except by weights and measures that are approved by the department. Source: SL 1957, ch 165, §1; SDC Supp 1960, §31.03A06; SL 1977, ch 190, §113; SL 2004, ch 17, §226; SL 2016, ch 183, §2.
SD Codified L § 34-39-3 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 39 - Liquefied Petroleum Gases|Section 34-39-3 - Testing of weighing and measuring devices--Condemnation of devices or rejection for repair--Fee--Safety examination of gas plant.

34-39-3. Testing of weighing and measuring devices--Condemnation of devices or rejection for repair--Fee--Safety examination of gas plant.The department may test all weighing and measuring devices used in the wholesale or retail sale of liquefied petroleum gas, either in liquid or vapor form, and shall condemn or reject for repair, any device which is found either to be inaccurate or does not clearly state the quantity of liquefied petroleum gas, either in liquid or vapor form, in pounds, gallons, cubic feet, or other unit approved by the department.The department shall charge and collect a sixty-eight dollar fee for each test.Any inspector employed by the department may enter and examine any liquefied petroleum gas plant for safety standard purposes no more than every two years, except for any reinspection resulting from a deficiency. The department shall charge and collect a ninety-four dollar fee for each inspection.For the purposes of this section, a liquefied petroleum gas plant is a retail distribution facility with a capacity of at least eight thousand gallons.Revenue from the fees imposed by this section shall be deposited into the general fund. It is the intent of the Legislature that one-half of the inspection program funding may be derived from the general fund and the other half from the fees collected pursuant to this section and §§37-21-9.1, 37-21A-3, 37-21A-7, and 37-22-10, through the General Appropriations Act. Source: SL 1957, ch 165, §2; SDC Supp 1960, §31.03A07; SL 1980, ch 267, §3; SL 1984, ch 29, §3; SL 1996, ch 218; SL 2003, ch 272 (Ex. Ord. 03-1), §20; SL 2006, ch 187, §1; SL 2007, ch 224, §3; SL 2016, ch 183, §3.
SD Codified L § 34-39-3.1 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 39 - Liquefied Petroleum Gases|Section 34-39-3.1 - Department to administer chapter.

34-39-3.1. Department to administer chapter.The department shall perform the functions required by this chapter. Source: SL 1973, ch 2, §54; SL 1979, ch 5, §2; SL 2003, ch 272 (Ex. Ord. 03-1, §23; SL 2004, ch 17, §227; SL 2016, ch 183, §4.
SD Codified L § 34-39-5 (2021)
2021 South Dakota Codified Laws|Title 34 - Public Health and Safety|Chapter 39 - Liquefied Petroleum Gases|Section 34-39-5 - Use of condemned weighing or measuring device as misdemeanor.

34-39-5. Use of condemned weighing or measuring device as misdemeanor.It is a Class 1 misdemeanor to use a weighing or measuring device for determining quantities of liquefied petroleum gas, either in liquid or vapor form, which has been condemned by the department. Source: SL 1957, ch 165, §2; SDC Supp 1960, §31.03A07; SL 1977, ch 190, §115; SL 2004, ch 17, §229; SL 2016, ch 183, §6.