UT Code § 15A-5-205.5 (2021)
2021 Utah Code|Title 15A - State Construction and Fire Codes Act|Chapter 5 - State Fire Code Act|Part 2 - Statewide Amendments and Additions to International Fire Code Incorporated as Part of State Fire Code|Section 205.5 - Amendments to Chapters 11 and 12 of IFC.

 Effective 7/1/2019  15A-5-205.5. Amendments to Chapters 11 and 12 of IFC.    (1) For IFC, Chapter 11, Construction Requirements for Existing Buildings:   (a) In IFC, Chapter 11, Section 1103.2 Emergency Responder Radio Coverage in Existing Buildings, is amended as follows: On line two after the title, the following is added: "When required by the fire code official".     (b) IFC, Chapter 11, Section 1103.5.1 Group A-2, is deleted and replaced with the following: "1103.5.1 Group A-2. An automatic fire sprinkler system shall be provided throughout existing Group A-2 occupancies where indoor pyrotechnics are used."     (c) IFC, Chapter 11, Section 1103.6, Standpipes, is deleted.     (d) In IFC, Chapter 11, 1103.7, Fire Alarm Systems, is deleted and rewritten as follows: "1103.7, Fire Alarm Systems. The following shall have an approved fire alarm system installed in accordance with Utah Administrative Code, R710-4, Buildings Under the Jurisdiction of the State Fire Prevention Board: 1. a building with an occupant load of 300 or more persons that is owned or operated by the state; 2. a building with an occupant load of 300 or more persons that is owned or operated by an institution of higher education; and 3. a building with an occupant load of 50 or more persons that is owned or operated by a school district, private school, or charter school. Exception: the requirements of this section do not apply to a building designated as an Institutional Group I (as defined in IFC 202) occupancy."     (e) IFC, Chapter 11, 1103.7.1 Group E, 1103.7.2 Group I-1, 1103.7.3 Group I-2, 1103.7.4 Group I-3, 1103.7.5 Group R-1, 1103.7.5.1 Group R-1 hotel and motel manual fire alarm system, 1103.7.5.1.1 Group R-1 hotel and motel automatic smoke detection system, 1103.7.5.2 Group R-1 boarding and rooming houses manual fire alarm system, 1103.7.5.2.1 Group R-1 boarding and rooming houses automatic smoke detection system, 1103.7.6 Group R-2 are deleted.     (f) IFC, Chapter 11, Section 1103.9, Carbon monoxide alarms, is deleted and rewritten as follows: "1103.9 Carbon Monoxide Detection. Existing Groups E, I-1, I-2, I-4, and R occupancies shall be equipped with carbon monoxide detection in accordance with Section 915."       (2) For IFC, Chapter 12, Energy Systems:   (a) Delete the section title "1204.2.1 Solar photovoltaic systems for Group R-3 buildings" and replace with the section title "1204.2.1 Solar photovoltaic systems for Group R-3 and buildings constructed in accordance with IRC."     (b) Section 1204.2.1, Solar photovoltaic systems for Group R-3 buildings, Exception 1 is deleted, Exception 2 is renumbered to 1 and a second exception is added as follows: "2. Reduction in pathways and clear access width are permitted where a rational approach has been used and the reduction is warranted and approved by the Fire Code Official."     (c) Section 1204.3.1 Perimeter pathways, and 1204.3.2 Interior pathways, are deleted and rewritten as follows: "1204.3.1 Perimeter pathways. There shall be a minimum three foot wide (914 mm) clear perimeter around the edges of the roof. The solar installation shall be designed to provide designated pathways. The pathways shall meet the following requirements: 1. The pathway shall be over areas capable of supporting the live load of fire fighters accessing the roof. 2. The centerline axis pathways shall be provided in both axes of the roof. Centerline axis pathways shall run where the roof structure is capable of supporting the live load of fire fighters accessing the roof. 3. Smoke and heat vents required by Section 910.2.1 or 910.2.2 shall be provided with a clear pathway width of not less than three feet (914 mm) to the vents. 4. Access to roof area required by Section 504.3 or 1011.12 shall be provided with a clear pathway width of not less than three feet (914 mm) around access opening and at least three feet (914 mm) clear pathway to parapet or roof edge."     (d) Section 1204.3.3 Smoke ventilation, is deleted and rewritten as follows: "1204.3.2 Smoke ventilation. The solar installation shall be designed to meet the following requirements: 1. Arrays shall be no greater than 150 feet (45720 mm) by 150 feet (45720 mm) in distance in either axis in order to create opportunities for fire department smoke ventilation operations. 2. Smoke ventilation options between array sections shall be one of the following: 2.1 A pathway six feet (1829 mm) or greater in width. 2.2 A pathway three feet (914 mm) or greater in width and bordering roof skylights or smoke and heat vents when required by Section 910.2.1 or Section 910.2.2. 2.3 Smoke and heat vents designed for remote operation using devices that can be connected to the vent by mechanical, electrical, or any other suitable means, protected as necessary to remain operable for the design period. Controls for remote operation shall be located in a control panel, clearly identified and located in an approved location."      Amended by Chapter 103, 2019 General Session