reglab/housing_qa huggingface dataset:
MT Code § 50-74-214 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 2. Inspections|50-74-214. Engineer to assist in inspection

  50-74-214. Engineer to assist in inspection. It is the duty of the engineer operating any boiler or boilers to assist the inspectors in their examination of the boilers and point out any defects known to the engineer in the boilers or machinery under the engineer's charge. If an engineer does not comply with this section, the engineer's license must be revoked or suspended.   History: En. Sec. 558, Pol. C. 1895; re-en. Sec. 1647, Rev. C. 1907; amd. Sec. 7, Ch. 30, L. 1913; re-en. Sec. 2718, R.C.M. 1921; re-en. Sec. 2718, R.C.M. 1935; amd. Sec. 6, Ch. 225, L. 1971; amd. Sec. 27, Ch. 182, L. 1975; R.C.M. 1947, 69-1507(part); amd. Sec. 1888, Ch. 56, L. 2009.
MT Code § 50-74-215 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 2. Inspections|50-74-215. Interior and exterior examination of boiler

  50-74-215. Interior and exterior examination of boiler. (1) The inspector must be satisfied by a thorough interior and exterior examination that the:   (a) boilers are well-made and of good and suitable material;   (b) openings for the passage of water and steam, respectively, and all pipes and tubes exposed to heat are of the proper dimensions and free from obstructions;   (c) flues are circular in shape;   (d) fire line of the furnace is at least 2 inches below prescribed minimum waterline of the boilers;   (e) arrangements for delivering the feed water are such that the boilers cannot be injured by the feed water; and   (f) boilers and the steam connections may be safely employed without danger to life.   (2) A boiler or steam pipe or any of the connections to a boiler or steam pipe that are made in whole or in part of bad material or are unsafe from any cause may not be approved. Nothing in this section may be construed to prevent the use of any boiler or steam generator, that is not constructed of riveted iron or steel plates, when the inspector has satisfactory evidence that the boiler or steam generator is equal in strength to and as safe from explosion as boilers of the best quality, constructed of iron or steel plates.   History: (1)En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; Sec. 69-1503, R.C.M. 1947; (2)En. Sec. 556, Pol. C. 1895; re-en. Sec. 1645, Rev. C. 1907; re-en. Sec. 2716, R.C.M. 1921; re-en. Sec. 2716, R.C.M. 1935; amd. Sec. 5, Ch. 225, L. 1971; Sec. 69-1505, R.C.M. 1947; R.C.M. 1947, 69-1503(part), 69-1505; amd. Sec. 1889, Ch. 56, L. 2009.
MT Code § 50-74-216 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 2. Inspections|50-74-216. Hydrostatic pressure test

  50-74-216. Hydrostatic pressure test. When necessary, the boiler inspector shall subject boilers, except those exempted by 50-74-103, to hydrostatic pressure, which hydrostatic pressure shall not exceed 150% of the steam pressure allowed on the boilers, providing there are no such leaks on such boilers which prevent the inspector from applying such hydrostatic pressure.   History: En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; R.C.M. 1947, 69-1503(part).
MT Code § 50-74-217 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 2. Inspections|50-74-217. Other inspection requirements

  50-74-217. Other inspection requirements. The inspector must be satisfied that:   (1) the safety valves are of suitable relieving capacity ratings, sufficient in number and area, and properly arranged and properly adjusted so as not to allow a greater pressure in a boiler than the amount prescribed by the inspection certificate;   (2) there are a sufficient number of gauge cocks properly inserted to indicate the amount of water and suitable gauges that will correctly record the pressure of steam; and   (3) adequate and certain provisions for an ample supply of water to feed the boiler at all times and suitable means for blowing out are provided so as to thoroughly remove mud and sediment from all parts of the boiler when it is under pressure of steam.   History: En. Sec. 555, Pol. C. 1895; re-en. Sec. 1644, Rev. C. 1907; amd. Sec. 6, Ch. 30, L. 1913; re-en. Sec. 2715, R.C.M. 1921; re-en. Sec. 2715, R.C.M. 1935; amd. Sec. 4, Ch. 225, L. 1971; amd. Sec. 9, Ch. 187, L. 1977; R.C.M. 1947, 69-1504(1); amd. Sec. 1890, Ch. 56, L. 2009.
MT Code § 50-74-218 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 2. Inspections|50-74-218. Safe working pressure

  50-74-218. Safe working pressure. (1) If a boiler is constructed with lap horizontal seams on the boiler, dome, or drum, a factor of 4 1/2 must be used in determining the safe working pressure allowed on the boiler.   (2) If a boiler is constructed with butt strap horizontal seams, a factor of four may be used in determining the safe working pressure.   (3) If a boiler is a historical boiler, as defined by the department by rule, on stayed sections, a safety factor of four must be used in determining the safe working pressure.   (4) If a boiler rests on a side wall on lugs, is hung by I-beams, or is in any way set up so that the weight of the boiler is pulling against the horizontal seam of rivets, a factor of five must be used in determining the safe working pressure.   (5) If the horizontal lap seams of a boiler are exposed to the fire, a factor of five must be used in determining the safe working pressure.   (6) On new stay bolts, 7,500 pounds pressure per square inch is allowed. If the stay bolts are corroded or defective, the inspector must determine the pressure to be allowed on the stay bolts.   (7) On braces made of solid material, 8,000 pounds pressure per square inch is allowed. On welded braces or braces with only one crowfoot, 6,000 pounds pressure per square inch is allowed.   (8) Cast iron may not be used in the construction or reinforcements of a boiler if the pressure allowed on the boiler is more than 100 pounds per square inch.   History: En. Sec. 555, Pol. C. 1895; re-en. Sec. 1644, Rev. C. 1907; amd. Sec. 6, Ch. 30, L. 1913; re-en. Sec. 2715, R.C.M. 1921; re-en. Sec. 2715, R.C.M. 1935; amd. Sec. 4, Ch. 225, L. 1971; amd. Sec. 9, Ch. 187, L. 1977; R.C.M. 1947, 69-1504(3); amd. Sec. 1, Ch. 160, L. 2011.
MT Code § 50-74-219 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 2. Inspections|50-74-219. Repealed

  50-74-219. Repealed. Sec. 4, Ch. 440, L. 2021.  History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(1); amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 13, Ch. 514, L. 1995; amd. Sec. 3, Ch. 385, L. 1997; amd. Sec. 2, Ch. 499, L. 2001; amd. Sec. 5, Ch. 68, L. 2005; amd. Sec. 1, Ch. 46, L. 2015; amd. Sec. 3, Ch. 322, L. 2019.
MT Code § 50-74-301 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-301. License required to operate boilers and steam engines

  50-74-301. License required to operate boilers and steam engines. All boilers and steam engines, except as exempted in 50-74-103, come under the provisions of this chapter, and persons operating same are required to hold the proper grade of license.   History: En. Sec. 5, Ch. 32, L. 1905; re-en. Sec. 1655, Rev. C. 1907; amd. Sec. 13, Ch. 30, L. 1913; amd. Sec. 4, Ch. 32, L. 1919; re-en. Sec. 2726, R.C.M. 1921; amd. Sec. 1, Ch. 140, L. 1923; re-en. Sec. 2726, R.C.M. 1935; amd. Sec. 4, Ch. 77, L. 1967; amd. Sec. 14, Ch. 225, L. 1971; amd. Sec. 33, Ch. 182, L. 1975; R.C.M. 1947, 69-1515(part).
MT Code § 50-74-302 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-302. General requirements for licensure

  50-74-302. General requirements for licensure. No person may be granted a license to operate steam or water boilers and steam machinery under the provisions of this chapter who has not met the qualifications for licensing and been found to be competent by examination to perform the duties of an engineer.   History: En. Sec. 559, Pol. C. 1895; re-en. Sec. 1648, Rev. C. 1907; amd. Sec. 8, Ch. 30, L. 1913; re-en. Sec. 2719, R.C.M. 1921; re-en. Sec. 2719, R.C.M. 1935; amd. Sec. 7, Ch. 225, L. 1971; amd. Sec. 10, Ch. 187, L. 1977; R.C.M. 1947, 69-1508(part).
MT Code § 50-74-303 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-303. Engineer's license classifications

  50-74-303. Engineer's license classifications. (1) Engineers entrusted with the operation, care, and management of steam or water boilers and steam machinery, as specified in 50-74-302, are divided into six classes, including first-class engineers, second-class engineers, third-class engineers, agricultural-class engineers, low-pressure engineers, and limited low-pressure engineers.  (2) Licenses for the operation of steam or water boilers and steam machinery are divided into six classifications in accordance with the following schedule:   (a) First-class engineers are licensed to operate all classes, pressures, and temperatures of steam and water boilers and steam-driven machinery with the exception of traction and hoisting engines.   (b) Second-class engineers are licensed to operate steam boilers operating not in excess of 250 pounds per square inch gauge saturated steam pressure, water boilers operating not in excess of 375 pounds per square inch gauge pressure and 450 degrees F temperature, and steam-driven machinery not to exceed 100 horsepower per unit, with the exception of traction and hoisting engines.   (c) Third-class engineers are licensed to operate steam boilers operating not in excess of 150 pounds per square inch gauge saturated steam pressure or not in excess of 150 horsepower per hour and water boilers operating not in excess of 160 pounds per square inch gauge pressure and 350 degrees F temperature.   (d) Agricultural-class engineers are licensed to operate steam boilers that operate not in excess of 150 pounds per square inch saturated steam pressure and that:   (i) are not operated for more than 6 months of the year; and   (ii) are not operated for purposes other than the harvesting or processing of agricultural products.   (e) Low-pressure engineers are licensed to operate steam boilers operating not in excess of 15 pounds per square inch gauge pressure and water boilers operating not in excess of 50 pounds per square inch gauge pressure and 250 degrees F temperature.   (f) Limited low-pressure engineers are licensed to operate hot water heating boilers not in excess of 30 pounds per square inch gauge pressure and 210 degrees F temperature and hot water supply boilers not in excess of 160 pounds per square inch gauge pressure and 210 degrees F temperature.   History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(1), (2); amd. Sec. 14, Ch. 514, L. 1995; amd. Sec. 1, Ch. 392, L. 2003; amd. Sec. 2, Ch. 440, L. 2021.
MT Code § 50-74-305 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-305. Exceptions to requirements for engineer's license

  50-74-305. Exceptions to requirements for engineer's license. Allowable exceptions or variances to the minimum requirements set out in 50-74-304 are as follows:   (1) An applicant for an engineer's license in any classification who holds a valid license in that classification from another state having licensing requirements equal to or exceeding the minimum requirements set out in 50-74-304, who successfully passes a written examination prescribed by the department, and who is found competent to operate a boiler and steam-driven machinery in that classification by the department must be granted a license in that classification.   (2) Operating experience in a classification accumulated in the United States military services or the merchant marine service satisfactory to the department may be accepted in lieu of the operating experience required for licensing of engineers in each of the license classifications.   (3) An applicant who has training in the operation of steam or water boilers and steam machinery and who has been certified as having satisfactorily completed a prescribed training course from a department-approved institution or training program in the classification for which the applicant is applying may, pursuant to department rule, be credited with experience toward a first-, second-, or third-class or low-pressure engineer's license.   History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(4); amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 33, Ch. 308, L. 1995; amd. Sec. 16, Ch. 514, L. 1995.
MT Code § 50-74-306 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-306. Traction licenses -- application without examination from other states

  50-74-306. Traction licenses -- application without examination from other states. (1) The licenses named in 50-74-303 do not entitle the holder to operate a traction engine.   (2) A person who is entrusted with the care and management of traction engines or boilers on wheels is required to pass an examination testing the person's competency to operate that class of machinery and procure a traction license.   (3) A person who is entrusted with the care, management, and operation of steam locomotives not addressed by federal regulations is required to pass an examination testing the person's competency to operate that class of machinery and procure a traction license.   (4) The department may issue a license to an individual holding a valid license from another state upon application without examination if the requirements of 50-74-307(2) are met.   (5) A traction license does not entitle its holder to operate any other class of steam machinery.   History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(part); amd. Sec. 1, Ch. 65, L. 2001; amd. Sec. 4, Ch. 322, L. 2019.
MT Code § 50-74-307 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-307. Requirements for traction licenses

  50-74-307. Requirements for traction licenses. (1) An applicant for a traction engineer's license:   (a) must be 18 years of age or older;   (b) shall attend a steam school approved by the department by rule and may apply steam school hours to the hour requirement established in subsection (3);   (c) must have at least 50 hours total experience in the operation of steam traction engines; and   (d) shall successfully pass a written examination prescribed by the department.   (2) The department may issue a license to an individual holding a valid license from another state under 50-74-306 if the individual is from a state that has standards greater than or equal to the state of Montana.   History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(part); amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 17, Ch. 514, L. 1995; amd. Sec. 2, Ch. 65, L. 2001; amd. Sec. 2, Ch. 160, L. 2011; amd. Sec. 5, Ch. 322, L. 2019.
MT Code § 50-74-308 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-308. Waiver of experience requirement for traction licenses

  50-74-308. Waiver of experience requirement for traction licenses. The department, at its discretion, may waive the experience requirement for operators of traction engines which are maintained and operated as a hobby for the restoration and show purposes of antique equipment.   History: En. Sec. 3, Ch. 32, L. 1905; re-en. Sec. 1649, Rev. C. 1907; amd. Sec. 9, Ch. 30, L. 1913; amd. Sec. 2, Ch. 32, L. 1919; re-en. Sec. 2720, R.C.M. 1921; re-en. Sec. 2720, R.C.M. 1935; amd. Sec. 8, Ch. 225, L. 1971; amd. Sec. 26, Ch. 94, L. 1973; amd. Sec. 28, Ch. 182, L. 1975; amd. Sec. 11, Ch. 187, L. 1977; R.C.M. 1947, 69-1509(part); amd. Sec. 64, Ch. 613, L. 1989.
MT Code § 50-74-309 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-309. Repealed

  50-74-309. Repealed. Sec. 127, Ch. 467, L. 2005.   History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(2); amd. Sec. 18, Ch. 514, L. 1995.
MT Code § 50-74-310 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-310. Repealed

  50-74-310. Repealed. Sec. 28, Ch. 196, L. 2003.   History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(3).
MT Code § 50-74-311 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-311. Waiting period before reexamination permitted

  50-74-311. Waiting period before reexamination permitted. In case of the failure of any applicant to successfully pass an examination, 45 days must elapse before the applicant may again be examined for license.   History: En. Sec. 4, Ch. 32, L. 1905; re-en. Sec. 1652, Rev. C. 1907; amd. Sec. 12, Ch. 30, L. 1913; amd. Sec. 3, Ch. 32, L. 1919; re-en. Sec. 2723, R.C.M. 1921; re-en. Sec. 2723, R.C.M. 1935; amd. Sec. 1, Ch. 54, L. 1959; amd. Sec. 3, Ch. 77, L. 1967; amd. Sec. 1, Ch. 255, L. 1969; amd. Sec. 11, Ch. 225, L. 1971; amd. Sec. 30, Ch. 182, L. 1975; amd. Sec. 1, Ch. 83, L. 1977; R.C.M. 1947, 69-1512(4); amd. Sec. 1891, Ch. 56, L. 2009.
MT Code § 50-74-312 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-312. Review of license rejection -- waiting period

  50-74-312. Review of license rejection -- waiting period. (1) An applicant for a license under the provisions of this chapter whose application has been rejected may, within 45 days after the date of the rejection, set forth in writing any arguments opposing the rejection and request a review by the department. The request must be addressed to the department and must be signed by the applicant.   (2) Within 2 days after receiving the request, the department shall notify the applicant in writing that on a certain day, not less than 5 days or more than 30 days after receipt of the written request, the department shall review and evaluate the application and any arguments opposing the rejection of the license application.   (3) The applicant may appear in person at the review. At least 2 days before the day set for the review, the applicant may designate in writing to the department the name of an engineer holding a valid license of equal or higher grade than the one applied for, and the engineer may testify on behalf of the applicant at the review.   (4) After the review, if the department determines that the applicant is entitled to the license, the department shall issue the license. If the department affirms the decision to not issue the license, the applicant may reapply to take the license examination, as provided in 50-74-311, and may not take the examination within 45 days of the final decision to not issue the license.   History: (1) thru (3)En. Sec. 564, Pol. C. 1895; re-en. Sec. 1653, Rev. C. 1907; re-en. Sec. 2724, R.C.M. 1921; re-en. Sec. 2724, R.C.M. 1935; amd. Sec. 12, Ch. 225, L. 1971; amd. Sec. 31, Ch. 182, L. 1975; Sec. 69-1513, R.C.M. 1947; (4)En. Sec. 565, Pol. C. 1895; re-en. Sec. 1654, Rev. C. 1907; re-en. Sec. 2725, R.C.M. 1921; re-en. Sec. 2725, R.C.M. 1935; amd. Sec. 13, Ch. 225, L. 1971; amd. Sec. 32, Ch. 182, L. 1975; Sec. 69-1514, R.C.M. 1947; R.C.M. 1947, 69-1513, 69-1514; amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 19, Ch. 514, L. 1995; amd. Sec. 186, Ch. 483, L. 2001; amd. Sec. 26, Ch. 196, L. 2003; amd. Sec. 125, Ch. 467, L. 2005.
MT Code § 50-74-313 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-313. Repealed

  50-74-313. Repealed. Sec. 127, Ch. 467, L. 2005.   History: En. Sec. 6, Ch. 32, L. 1905; re-en. Sec. 1656, Rev. C. 1907; amd. Sec. 14, Ch. 30, L. 1913; amd. Sec. 1, Ch. 54, L. 1919; re-en. Sec. 2727, R.C.M. 1921; amd. Sec. 2, Ch. 54, L. 1959; amd. Sec. 167, Ch. 147, L. 1963; amd. Sec. 15, Ch. 225, L. 1971; R.C.M. 1947, 69-1516; amd. Sec. 54, Ch. 492, L. 1997.
MT Code § 50-74-314 (2021)
2021 Montana Code Annotated|Title 50. Health and Safety|Chapter 74. Boilers and Steam Engines|Part 3. Licenses|50-74-314. Repealed

  50-74-314. Repealed. Sec. 46, Ch. 481, L. 1997.   History: En. Sec. 561, Pol. C. 1895; re-en. Sec. 1650, Rev. C. 1907; amd. Sec. 10, Ch. 30, L. 1913; re-en. Sec. 2721, R.C.M. 1921; amd. Sec. 9, Ch. 225, L. 1971; amd. Sec. 29, Ch. 182, L. 1975; R.C.M. 1947, 69-1510; amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 20, Ch. 514, L. 1995.