Potter RMS-2T Die Cast Metal Red Emergency Manual DPST Single Action Fire Alarm Pull Station (1) Description The Potter Pull Station Series offers a complete line of die-cast pull stations for a variety of applications focusing mainly on fire alarm systems. The pull stations are available in single or dual action models. All of the pull stations have a 10-amp snap action switch and a dedicated terminal block for the ease of wire connections. All of the metal is completely coated to inhibit corrosion and provide for a uniform and quality finish. The standard models have a hex key reset, however a key reset is also available. The models are available with shallow and deep surface mount back boxes and as a weatherproof version. Operation The Potter single action series of pull stations operate by pulling the white operating handle straight down and the handle will lock into place. The dual action stations require the lifting of the front cover and then pulling the white operating handle straight down. The stations are reset by opening the front and placing the handle in the normal position. UL and cUL Listed, FM Approved, CSFM Listed, MEA Approved, ADA Compliant 	 Single or Dual Action 	 Terminal connectors 	 10 Amp Snap Action Switch	 	 	 	 Gold plated SPST contacts 	 Optional auxiliary contacts 	 Mounts on standard single gangbox 	 Surface backboxes available 	 High-gloss red enamel finish 	 Glass breakrod 	 Made in the U.S.A Engineering Specifications The contractor shall furnish and install the Potter series of pull stations as indicated. The pull station shall be die cast construction with a "T" type pull handle that is ADA compliant. Single action pull stations shall be a P32-1T. Dual action pull stations shall be the Potter P32-1T-LP. Any manual pull station installed in an outdoor or wet location shall be a RMS-1T-WP weather proof unit. The contact shall be a single pole, single throw switch rated at 1 amp 30V DC/125V AC. The device shall have a terminal block for ease of wiring. Once activated, the pull station shall be reset by opening the front cover. Opening of the cover in a normal state shall initiate an alarm. Specifications Switch Rating: 1 Amp @ 30 VDC 10 Amps @ 125 VAC Pull Station Dimensions: 4-3/4" H x 3-1/4" W x 7/8" D Color: Red with raised white letters, white pull bar with raised red letters For special application manual stations see bulletin #8910014. For explosion proof manual stations see bulletin #8880014.