Aldex Chemical Home About Products Technical Bulletins Technical Guides Safety Data Info Request Contact Us Dr. Preuss: The Ion Exchange Doctor ALDEX C-800 Series Resins C-800 Water Softening Resin Sodium Form NSF/ANSI 44, 61 and 372 Certified. Aldex C-800 is a high capacity, high quality, gel-type cation resin capable of meeting the most exacting requirements of household, farm, commercial, institutional and industrial water softeners. It is supplied in the sodium form as black colored beads in 1 cubic foot bags and larger bulk packages. Aldex C-800 Technical Bulletin: US units (PDF) | Metric units (PDF) | Français (PDF) Aldex C-800 Cut Sheet: English (PDF) Aldex C-800 Safety Data Sheets: English (PDF) | Français (PDF) Physical Chemical Properties Resin Composition: Sulfonated styrene / divinylbenzene copolymer Ionic Form as Shipped: Sodium (Na+) Physical Form: Black colored beads Moisture Content: 45 to 49.9% Total Capacity: 1.9 meq/ml minimum 41 kilograins as CaCO3 per cubic foot Odor and Taste: None Specific Gravity: 1.28 Net Weight (as shipped): 50 lbs per cubic foot Particle Size: 16 to 50 mesh - Less than 0.5% through 50 mesh Recommended Operating Conditions Influent pH: No restrictions Maximum Temperature: 250 °F Bed Depth: Minimum 24” Normal 36” Service Flow Rate: 1 to 5 US GPM per cubic foot Backwash Flow Rate: See Fig. 2 Regenerant: Sodium Chloride (NaCl) or Potassium Chloride (KCl) Regenerant Strength: 5 to 15%, usually 10% Regenerant Flow Rate: 0.3 to 1.0 US GPM per cubic foot of resin Regenerant Contact Time: 15 to 60 minutes Regenerant Dosage Level: 2 to 15 lb per cubic foot Slow Rinse (Displacement) Flow Rate: 0.3 to 1.0 US GPM per cubic foot of resin Slow Rinse Volume: 20 USG per cubic foot resin Fast Rinse Rate: 1.0 to 5.0 US GPM per cubic foot resin Fast Rinse Volume: 30 USG per cubic foot resin C-800 Features No Chlorinated Solvents The absence of chlorinated solvents in the manufacturing of Aldex C-800 results in very low TOC leakage. Very low color, taste or odor Aldex C-800 meets the requirements for paragraph 173.25 of the Food Additive Regulation of the U.S. Food and Drug Administration. High Capacity 30,000 grains of softening capacity when regenerated with 15 lbs of NaCl per cu. ft. and 20,000 grains with 6 lbs of NaCl per cu.ft. ensuring high efficiency and low operating costs. Long Life Strong and durable beads ensure long service life. Reliability Over 34 years of actual field usage by thousands of customers demonstrate the reliability of Aldex C-800. Safety Information A material safety data sheet is available for Aldex C-800. Copies can be obtained from Aldex Chemical Co., LTD. Aldex C-800 is not a hazardous product and is not WHMIS controlled. Caution: Acidic and basic regenerant solutions are corrosive and should be handled in a manner that will prevent eye and skin contact. Before using strong oxidizing agents in contact with ion exchange resin, consult sources knowledgeable in the handling of these materials. C-800 Operating Suggestions Iron Aldex C-800 will remove most of the dissolved iron, can filter much of the suspended iron and may or may not remove organically bound iron from water. When softeners are used to remove iron from the water, periodic cleaning of the bed mechanically or with a chemical iron cleaner may be necessary. Chlorine All cation exchange resins are affected by chlorine and suffer degradation and swelling. It is recommended that the chlorine in the water be maintained below 1.0 ppm when using Aldex C-800. Fig. 1 Exchange capacity vs. regeneration level Sodium form C-800 Cation Resin Backwash Characteristics Aldex C-800 should be backwashed for at least 10 minutes after each service cycle in a conventionally down flow regenerated softener. To reclassify the beads and remove suspended solids from the top of the bed, the resin bed should be expanded at least 50% according to Fig. 2. Fig. 2 Bed expansion vs. backwash flow rate for various water temperatures In the case of non-conventional or upflow regenerated softeners, it may not be necessary to follow the above procedure since the backwash and brine injection are incorporated in the same step. Pressure Drop Figure 3 shows the expected pressure loss per foot of bed depth as a function of flow rate at various temperatures. Fig. 3 Pressure Drop vs. Flow Rate These suggestions and data are based on information we believe to be reliable. They are offered in good faith. However, we do not make any guarantee or warranty. We caution against using these products in an unsafe manner or in violation of any patents. Further, we assume no liability for the consequences of such actions. © 2021 Aldex Chemical Company, Ltd., All rights reserved Home | About | Products | Technical Bulletins | Information | Contact | Dr. Preuss