HomeSolutions for you Products About Us Contact Us Quality Downloads ADE 4F – Ex cable glands for armoured cables ADE4F Data Sheet Documentation Back ADE 4F – Ex cable glands for armoured cables Features Manufactured from nickel plated brass and stainless steel ISO and NPT sizes Suitable for armoured cables Also suitable for industrial and underwater applications ATEX certified: Ex II 2 GD / Ex db/Ex eb IIC / Ex I M2 / Ex db I / Ex eb I / Ex tb IIIC Protection class options: IP66 (dustproof and resistant to powerful water jets) or IP68 (underwater tested to 5 bar) Temperature rating -30ºC to +80ºC with neoprene gasket and -60ºC to +140ºC with silicon gasket Gland accessories including, fibre sealing washers and lock nuts. Dimensions: from M12 x 1.5 to M110 x 2.0 and NPT ¼” to NPT 4” Certification INERIS12ATEX0032X Ex protection type (EN 50018/IEC60079-1 and EN 50019/IEC 60079-7) Ex II 2 GD Ex db Ex eb IIC Ex I M2 Ex db I Ex eb I Ex tb IIIC Ingress protection levels IP66 and 68 (EN 60529/IEC 60529) Ambient temperature -30ºC to +80ºC with neoprene gasket and -60ºC to +140ºC with silicone gasket Description ADE 4F cable glands are available in nickel plated brass and stainless steel are designed to accept armoured cables with overall diameters from 4.5 mm to 104.0 mm with either metric or NPT threads. Thread dimensions range from M12 x 1.5 to M110 x 2.0 and NPT ¼” to NPT 4”. ADE 4F glands are also suitable for industrial and underwater applications and offer ingress protection to IP66 (dustproof and resistant to powerful water jets) or IP68 (underwater tested to 5 bar). ADE 4F glands are ATEX certified to: Ex II 2 GD / Ex db/Ex eb IIC / Ex I M2 / Ex db I / Ex eb I / Ex tb IIIC with two temperature rating options -30ºC to +80ºC with neoprene seal, as standard, and -60ºC to +140ºC with optional silicone seal. Gland accessories including, fibre sealing washers and lock nuts. Article ISO Thread Article NPT Thread Outer Clamping Range Thread length mm NP Brass Stainless Steel NP Brass Stainless Steel > < 00846404 00846409 M12 x 1.5 00848404 00848409 NPT ¼” 6.0 12.0 15.0 00846594 00846595 M16 x 1.5 00848594 00848599 NPT 3/8” 6.0 12.0 15.0 00846504 00846509 M16 x 1.5 00848504 00848509 NPT 3/8” 8.5 16.0 15.0 00846674 00846679 M20 x 1.5 00848674 00848679 NPT ½” 6.0 12.0 15.0 00846694 00846699 M20 x 1.5 00848694 00848699 NPT ½” 8.5 16.0 15.0 00846604 00846609 M20 x 1.5 00848604 00848609 NPT ½” 12.0 21.0 15.0 00846774 00846779 M25 x 1.5 00848774 00848779 NPT ¾” 8.5 16.0 15.0 00846794 00846799 M25 x 1.5 00848794 00848799 NPT ¾” 12.0 21.0 15.0 00846704 00846709 M25 x 1.5 00848704 00848709 NPT ¾” 16.0 27.5 15.0 00846894 00846899 M32 x 1.5 00848894 00848899 NPT 1” 16.0 27.5 15.0 00846804 00846809 M32 x 1.5 00848804 00848809 NPT 1” 21.0 34.0 15.0 00846994 00846999 M40 x 1.5 00848994 00848999 NPT 1¼” 21.0 34.0 15.0 00846904 00846909 M40 x 1.5 00848904 00848909 NPT 1¼” 27.0 41.0 15.0 00847094 00847099 M50 x 1.5 00849094 00849099 NPT 1½” 27.0 41.0 16.0 00847004 00847009 M50 x 1.5 00849004 00849009 NPT 1½” 33.0 48.0 16.0 00847294 00847299 M63 x 1.5 00849294 00849299 NPT 2” 40.0 56.0 17.0 00847204 00847209 M63 x 1.5 00849204 00849209 NPT 2” 47.0 65.0 17.0 00847394 00847399 M75 x 1.5 00849494 00849499 NPT 2½” 47.0 65.0 18.0 00847304 00847309 M75 x 1.5 00849404 00849409 NPT 2½” 54.0 74.0 18.0 00847494 00847499 M80 x 2.0 00849594 00849599 NPT 3” 54.0 74.0 20.0 00847404 00847409 M80 x 2.0 00849504 00849509 NPT 3” 63.0 83.0 20.0 00847594 00847599 M90 x 2.0 – – – 63.0 83.0 22.0 00847504 00847509 M90 x 2.0 00849604 00849609 NPT 3½“ 72.0 93.0 22.0 00847574 00847579 M90 x 2.0 – – – 85.0 107.0 22.0 00847794 00847799 M110 x 2.0 00849704 00849709 NPT 4” 85.0 107.0 22.0 Technical data (Extract) (For detailed information please click here) Protection class IP 66 and 68 (EN 60529/IEC 60529) Dimensions see data sheet Material Nickel Plated Brass or Stainless Steel Weight see data sheet Resistance Impact resistance – see datasheet Documentation ADE4F Data Sheet – for armoured cables Declaration of Conformity Customer requirements – Terminal Boxes Operating Instructions – Empty enclosure CE TEK is proudly powered by WordPress