HOME APPLICATIONS CLOSE COUPLED PUMPS SELF PRIMING PUMPS BOILER FEED & CONDENSATE VACUUM PUMPS CONTACT Russell A612 End Suction. Close Coupled, Bronze Fitted Centrifugal Pump A612 CUT SHEET A612 IOM A612 Capabilities Maximum Working Pressure 175PSI Maximum Gallons Per Minute 110 Maximum Head Produced 148 FT. RPM 3450 Maximum Seal Temp Buna-N 225˚F EPT 300˚F Viton 400˚F Maximum Horsepower 3 Design Features CASING Constructed of ASTM A48 class 30 cast iron. The discharge can be mounted in any 90° position. Drain and air ports are also positioned every 90°, 1/4 npt suction and discharge tappings are standard. Back pull out design allows the pump to be serviced without disturbing the piping. The volute was designed to maximize hydraulic efficiency MECHANICAL SEAL Type 21 buna-n seal is rated to 225°F and pressures to 175PSI. Carbon seal face mates with the ceramic seat providing years of trouble free service. Alternate seals available upon request. IMPELLER The hydraulic design of the impeller maximizes pressure and gpm while minimizing horsepower. The enclosed impeller is made of cast bronze. ADAPTER The precise machining of the adapter allows for easy assembly of the pump. A 1/8 npt hole is provided if a seal flush line is added. Construction consists of ASTM A48 class 30 cast iron. MOTOR The NEMA 56J motor utilizes a 416 stainless steel shaft. The motor’s heavy duty ball bearings withstand axial and radial thrust loads with no problem. Standard enclosure type is drip-proof but alternates are available. Pump Curve Click Here Technical View fullsize View fullsize View fullsize View fullsize View fullsize 102 W. Chicago Street | Albion, IA 50005 | (641) 488-2319 | russpump@heartofiowa.net Site by: BonardiMedia.con Copyright 2018 - Russell Pump & Engineering Inc.

High Quality Centrifugal Pumps & Condensate Systems SIZE YOUR RUSSELL PUMP USING PUMP-FLO PUMP-FLO Since 2001, Russell Pump and Engineering Inc has designed and manufactured high-quality centrifugal pumps and condensate systems for the OEM and Commercial Industries. Russell Pump and Engineering was founded in Marshaltown, IA by two engineers with over 50 years of collective experience who wanted to provide individualized engineering to suite their client’s varying applications. Russell Pump and Engineering has since expanded to a newly constructed state of the art 10,000 sq ft facility in Albion, IA to build and support quality pumps for a variety of applications including: O.E.M Boosters & Circulation Cooling Towers Boiler Feed Process Fluids Irrigation & Lawn Sprinkling Hot and Chilled Water Circulation Chemical Process HVAC Water Transfer Dewatering If you have questions regarding your pump application, take advantage of our 17 years of specialty know-how of pump building and engineering by clicking here. CONTACT US CONTACT ➤ LOCATION 102 W. Chicago Street Albion, IA 50005 ☎ CONTACT Email: russpump@heartofiowa.net Phone: (641) 488-2319 102 W. Chicago Street | Albion, IA 50005 | (641) 488-2319 | russpump@heartofiowa.net Site by: BonardiMedia.con Copyright 2018 - Russell Pump & Engineering Inc.