Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT AAAC - ALLOY BARE ALUMINUM CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION: Used as bare overhead conductor for primary and secondary distribution. Designed utilizing a high-strength aluminum alloy to achieve a high strength-to-weight ratio; affords better sag characteristics. Aluminum alloy gives AAAC higher resistance to corrosion than ACSR. PRODUCT FEATURES: Standard 6201-T81 high strength aluminum conductors, conforming to ASTM Specification B-399, are concentric-lay-stranded, similar in construction and appearance to 1350 grade aluminum conductors. Standard 6201 alloy conductors are similar to other alloy conductors commercially known as Ardival, Aldrey or Almelec. They were developed to fill the need for an economical conductor for overhead applications requiring higher strength that that obtainable by 1350 grade aluminum conductors, but without a steel core. The DC resistance at 20°C of the 6201-T81 conductors and the standard ACSRs of the same diameter are approximately the same. Conductors of the 6201-T81 allows are harder and, therefore, have greater resistance to abrasion than conductors of 1350-H19 grade aluminum. SPECIFICATIONS: AAAC bare conductor meets or exceeds the following ASTM specifications: B-398 Aluminum Alloy 6201-T81 Wire for Electrical Purposes B-399 Concentric-Lay-Stranded 6201-T81 Aluminum Alloy Conductors KINGWIRE AAAC - Alloy Bare Aluminum Code Word Size (KCM) Strand ACSR Cond with Equivalent Resistance Equivalent AL/ST Stranding Diameter Cross Sectional Area (sq. in.) Weight per 1000 ft (Lbs) Rated Strength (Lbs) Resistance OHMS/ 1000 ft Rating (AMPS) Indiv. Wire Complete Cable OD DC @ 20˚C AC @ 75˚C Akron 30.58 7/w 6 6/1 .0661 .198 .0240 28.7 1,110 .659 .785 107 Alton 48.69 7/w 4 6/1 .0834 .250 .0382 45.7 1,760 .414 .493 143 Ames 77.47 7/w 2 6/1 .1052 .316 .0608 72.7 2,800 .260 .310 191 Azusa 123.3 7/w 1/0 6/1 .1327 .398 .0968 115.7 4,460 .163 .195 256 Anaheim 155.4 7/w 2/0 6/1 .1490 .447 .1221 145.9 5,390 .130 .154 296 Amherst 195.7 7/w 3/0 6/1 .1672 .502 .1537 183.7 6,790 .103 .123 342 Alliance 246.9 7/w 4/0 6/1 .1878 .563 .1939 231.8 8,560 .0816 .0973 395 Butte 312.8 19/w 266.8 26/7 .1283 .642 .2456 293.6 11,000 .0644 .0769 460 Canton 394.5 19/w 336.4 26/7 .1441 .721 .3098 370.3 13,300 .0511 .0610 532 Cairo 465.4 19/w 397.5 26/7 .1565 .783 .3655 436.9 15,600 .0433 .0518 590 Darien 559.5 19/w 477.0 26/7 .1716 .858 .4394 521.7 18,800 .0360 .0420 663 Elgin 652.4 19/w 556.5 26/7 .1853 .927 .5124 612.4 21,900 .0309 .0371 729 Flint 740.8 19/w 636.0 26/7 .1415 .991 .5818 695.5 24,400 .0272 .0327 790 Greeley 927.2 19/w 795.0 26/7 .1583 1.108 .7282 870.4 30,500 .0217 .0263 908 1. Resistance is calculated using ASTM standard increments of stranding, and metal conductivity of 52.5% IACS AC resistance at 60 Hz. 2. Current ratings are based on 75°C conductor temperature, 25°C ambient, 2ft/s wine, 96/watts/sq. foot sun, 0.5 coefficients of emissivity and absorption. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep