CALL FOR A QUOTE! 800-321-7436 432-684-9985 HOME SERVICES OUR PRODUCTS RESOURCES GALLERY CONTACT SPECIFICATIONS Co-Ex Pipe Company PE 4710 High Density Polyethylene Pipe Working Pressure VS Temperature The chart below provides maximum working pressure at the corresponding operating temperature for water, produced water, and dry natural gas using PE 4710 material. Operating Temperature DR 73.4°F 7 335 psi 9 250 psi 11 200 psi 13.5 160 psi 17 125 psi 21 100 psi Design working pressures are calculated in accordance with API 15LE specifications. Local or state codes may supersede these ratings. Click here for more information on Plastic Pipe Design factors and Industry Standard processes. See WWW.Plasticpipe.org Meets specifications of API 15LE, ASTM D2513, ASTM D3035, and PPI TR-4 material designation code PE 4710. Working pressures in excess of 73.4°F are calculated using API 15LE, 5.1.4 Table 3- Temperature Service Factors chart. For multiphase fluids, wet natural gas, and liquid hydrocarbons use a 0.5 de-rating service factor applied to the pressures given on the working pressure chart shown above. Service pressure and de-rating factors for various fluids including crude oil and wet natural gas shall be calculated in accordance with API 15LE Fluid Service Factors (API 15LE, 5.1.3 Table 2-Fluid Service Factors). **PE 4710/PE 3608 High Density Polyethylene material ABSOLUTELY should NOT be used in service temperatures in excess of 140°F Revised: May 22, 2014 Co-Ex Pipe Company PE 3608 High Density Polyethylene Pipe Working Pressure VS Temperature The chart below provides maximum working pressure at the corresponding operating temperature for water, produced water, and dry natural gas using PE 3608 material. Operating Temperature DR 73.4°F 7 267 psi 9 200 psi 11 160 psi 13.5 128 psi 17 100 psi 21 80 psi Design working pressures are calculated in accordance with API 15LE specifications. Local or state codes may supersede these ratings. Click here for more information on Plastic Pipe Design factors and Industry standard processes. See WWW.Plasticpipe.org Meets specifications of API 15LE, ASTM D2513, ASTM D3035, and PPI TR-4 material designation code PE 3608. Working pressures in excess of 73.4°F are calculated using API 15LE, 5.1.4 Table 3 Temperature Service Factors chart. For multiphase fluids, wet natural gas, and liquid hydrocarbons use a 0.5 de-rating service factor applied to the pressures given on the working pressure chart shown above. Service pressure and de-rating factors for various fluids including crude oil and wet natural gas shall be calculated in accordance with API 15LE Fluid Service Factors (API 15LE, 5.1.3 Table 2-Fluid Service Factors). **PE 4710/PE 3608 High Density Polyethylene material ABSOLUTELY should NOT be used in service temperatures in excess of 140°F Revised: May 22, 2014 Print Friendly Home Services About Polyethylene Pipe Specifications Dimensions Resources Gallery Contact CONTACT 1823 South Midkiff Midland, TX 79701 800-321-7436 432-684-9985 Copyright © 2020 - 2021 | Co-ex Pipe Co. | All Rights Reserved.