Product Catalog Solid fuel boilers "Prometheus" 60 kW Return to catalog Fuel type: coal, firewood, electricity Power: 60 kW Boilers "Prometey" (60M-1) with a capacity of 60 kW are a continuation of the "classic" line of boilers "Prometheus" with minor design changes and differences. The boiler is equipped with a self-produced smoke exhauster to create forced draft in the chimney. This made it possible to reduce the diameter of the chimney outlet to 145 mm and to reduce the height of the chimney, guaranteeing high-quality fuel combustion. This boiler is not designed with a draft regulator. The boiler water temperature is controlled by a thermostat, the output signal of which is connected to the smoke exhauster. When the boiler water temperature rises above the setpoint set on the thermostat, the smoke exhauster automatically turns off, the intensity of the combustion process decreases sharply, and the temperature drops. When the temperature drops by 10 ° C, the smoke exhauster turns on again - the combustion process takes place in normal mode. Thus, in this boiler, the smoke exhauster operates in the "on-off" mode with reference to the boiler water temperature and regulating the temperature regime. The primary and tertiary air supply to the boiler is carried out by means of dampers located on the side walls of the boiler. Air supply adjustment is carried out in manual mode. The boiler has two grate shaking levers. This is due to the large volume of the loading chamber and, as a consequence, the larger area of the grate, which must be periodically shaken for a more efficient combustion process. The flame baffle in the boiler is made of 40 mm thick chamotte stone, which makes it possible to increase its wear resistance, durability and completely eliminate deformation of the baffle, which is constantly under the influence of high temperature. The fireclay stone bumper also, when heated, carries out the afterburning of pyrolysis gases. Specifications Heating capacity (min./nom.) kw 10/60 Boiler efficiency % up to 82 Main fuel - hard coal (20-40mm), grade DO Allowable fuel - firewood, coal briquettes, compressed fuel Fuel consumption kg / h 18.6 Loading hatch mm 585x370 Loading chamber capacity l 165 Внешний диаметр патрубка дымохода мм 145 Подключение отопительного контура - G 2" Объем воды л 135 Диапазон температур котловой воды °С 65-95 Диапазон температур котловой воды °С 100-250 Содержание СО2 % 13,2 Суммарная площадь греющих поверхностей отопительного котла м2 4 Нормальное рабочее давление кгс/см2 1,0-1,5 Допустимое избыточное рабочее давление кгс/см2 2,0 Максимальное испытательное давление кгс/см2 3,5 Высота мм 1320 Ширина мм 755 Глубина мм 1080 Вес нетто кг 520 Скачать: Руководство по эксплуатации. Котел Прометей 60М1 (1.93 Mb) Листовка. Твердотопливные котлы Прометей 60 кВт (798.5 Kb) Твердотопливные котлы Прометей 60 кВт. Прайс-лист (34 Kb) Сертификат соответствия. Котлы отопительные Прометей (1.38 Mb) Видеофильм (472 Mb) Вернуться в каталог About the company | Product catalog | Modular Boiler Rooms | Modular Buildings | Where to buy | Metalworking Prices | News | Articles | For dealers | Contacts ABOUT COMPANY PRODUCT CATALOG MODULAR BOILERS MODULAR BUILDINGS METALWORKING PRICES NEWS ARTICLES FOR DEALERS WHERE CAN I BUY CONTACTS Plant "Sibenergoterm" Novosibirsk, st. Berdskoe highway, 61/2 Information line: 8-800-100-3212 (toll-free within Russia) Sales department t. (383) 334-08-00, (383) 334-08-01 f. (383) 334-08-03 e-mail: prometey@nzko.su Metalworking department: t. (383) 334-08-02 e-mail: metall@nzko.su Sales department of modular boiler rooms: e-mail: sergey@nzko.su Representative office in Moscow st. Agricultural , 15, bldg. 1 t./f .: (499) 189-78-02, (499) 189-38-53 Our partners © 2015 Plant "Sibenergoterm" Website promotion Site creation