+7 (34145) 55999 home About the plant Products Career Contacts Dealers home → Products → Modular complete transformer substations KTPM → KTPM 35/6 (10) kV SKP series → Description Device selection Low voltage switchgear LVCD series NGW R LVCD series RNM 2 Switchgear KRU 6 (10) - 35 KV KRU series D-12P (PL) KRU series D-12PT KRU series D-12-2S KRU series D-24P KRU series D-40P Mine switchgear 6 (10) KV KRU series PREM-G1dM Modular complete transformer substations KTPM KTPM 6 (10) /0.4 kV SKP series KTPM 35/6 (10) kV SKP series Description Benefits Design Technical specifications Installation Documentation For design Certificates KTPM SKP 35/6 (10) kV - version with a rated voltage on the HV side - 35 kV, on the LV side - 6 (10) kV and a maximum power of power transformers up to 2x16 MVA. In KTPM SKP series, switchgear equipment is installed in special modules, which are heat-insulated electrical containers equipped with working and emergency lighting, heating and ventilation systems. Structurally, each module is a metal frame fixed on a rigid frame base, walls, floor and gable roof. The frame base is made of a rolled channel with a height of 260 mm, which ensures a high degree of rigidity of the module during its transportation and installation, and also allows it to be installed on various types of foundation bases. The floor, walls and roof of the module have a three-layer structure, consisting of heat-insulating material, enclosed between the outer and inner metal shells with a thickness of 1.6–2.2 mm. For the manufacture of metal elements of the module casing, high-quality steel with anti-corrosion aluminum-zinc coating is used. All external surfaces of structural elements are coated with polymer powder paint, which is distinguished by its durability, high resistance to mechanical and weathering influences, as well as high aesthetic characteristics. The entrance doors of the module, due to its flexible design, can be located in any part of it and can be made as single or double, solid or with lattice windows. When installing the modules on high foundations, for ease of operation, the substations are equipped with ladders with handrails and service platforms. All external surfaces of structural elements are covered with polymer powder paint, which is characterized by durability, high resistance to mechanical and weathering, as well as high aesthetic characteristics. The entrance doors of the module, due to its flexible design, can be located in any part of it and can be made as single or double, solid or with lattice windows. When installing the modules on high foundations, for ease of operation, the substations are equipped with ladders with handrails and service platforms. All external surfaces of structural elements are coated with polymer powder paint, which is distinguished by its durability, high resistance to mechanical and weathering influences, as well as high aesthetic characteristics. The entrance doors of the module, due to its flexible design, can be located in any part of it and can be made as single or double, solid or with lattice windows. When installing the modules on high foundations, for ease of operation, the substations are equipped with ladders with handrails and service platforms. solid or with lattice windows. When installing the modules on high foundations, for ease of operation, the substations are equipped with ladders with handrails and service platforms. solid or with lattice windows. When installing the modules on high foundations, for ease of operation, the substations are equipped with ladders with handrails and service platforms. Site development © 2017 LLC ETZ "Vector" All rights reserved Address: Russia, Udmurt Republic, Votkinsk, st. Victory, 2nd Tel: +7 (34145) 55-999 Fax: +7 (34145) 44-429 Email: info@etz-vektor.ru