CONSONNI About Us Products Quality Video Languages Containerized Substations Fixed and mobile substations. Hot rolled steel structure Exterior walls with “sandwich” panels equipped with thermal insulation and fire resistant . Removable panels for access to the interior equipment. Raised floor for electrical interconnection. Less watertight enclosure for passage of cables. Practicable indoor space for interior equipment maintenance. Subestación en contenedor Instalaciones interiores: Normal and emergency lighting. Power suppliers. Pressurisation and forced ventilation. Air conditioning system. Fire detection and fighting system. Facilities and services Containerized substations reference: Duro Felguera. Venezuela Duro Felguera Return to top of page Copyright © 2021 · Associate Theme on Genesis Framework · WordPress · Log in

CONSONNI About Us Products Quality Video Languages Withdrawable Low Voltage M.C.C. Equipment in spaces of 1/20 till 5/10 of column. Adjustable dimensions to particular requirements. Withdrawable cars to 200 hp. engines Front accessibility. SE type: stándar implementation. SE IAC type: ejecución arco interno que incluye: Adequate protection in all compartments and cubicles Single column sectioning. Total selectivity. Main features: Manufacture Standard: IEC61439.1/2. Rated insulation voltage: 690 V., 50/60 Hz. Rated service voltage: 690 V., 50/60 Hz. Busbars: Rated current: Up to 5.000 A. (on double panel depth) Short-time 1 sec. current Up to 100 KA., RMS. Peak withstand current Up to 250 KA. Distribution bar Rated current Up to 80 A. Esquema CCm Tipo SCF Short-time 1 sec. current Up to 800 KA, RMS Degree of protection standard: IP42 (*) Compartimentation type: 3b o 4b. Short-circuit execution according to IEC 61641. * Other values, on request. MCC WITHDRAWABLE (Type SE): Each unit has a load switch 6-pole and double pole break . This switch is the connecting element between the fixed and the removable portion . INTERLOCKS: The door will be locked while the switch are closed. Once opened the switch and door, the equipment Once opened the door switch and the equipment is energized and only strength fed the control circuit: TEST position. With the door open you can not close the switch. With the extracted frame and the closed door you can not close the switch. Withdrawable L.V. MCC Reference: Saica UK. Manchester (Inglaterra) Ver más Referencias. Return to top of page Copyright © 2021 · Associate Theme on Genesis Framework · WordPress · Log in