HomeSolutions for you Products About Us Contact Us Quality Downloads ADE 1F – Ex cable glands for non-armoured cables ADE1F Data Sheet Documentation Back ADE 1F – Ex nickel plated brass and stainless steel cable glands for non-armoured cables Features Nickel plated brass and stainless steel ISO and NPT sizes Suitable for non-armoured cables Also suitable for industrial and underwater applications ATEX certified: Ex II 2 GD / Ex db/Ex eb IIC / Ex I M2 / Ex db I / Ex eb I / Ex tb IIIC Protection class options: IP66 (dustproof and resistant to powerful water jets) or IP68 (underwater tested to 5 bar) Temperature rating -30ºC to +80ºC with neoprene gasket and -60ºC to +140ºC with silicon gasket Gland accessories including, fibre sealing washers and lock nuts. Dimensions: from M12 x 1.5 to M110 x 2.0 and NPT ¼” to NPT 4” Certification INERIS12ATEX0032X Ex protection type (EN 50018/IEC 60079-1 and EN 50019/IEC 60079-7) Ex II 2 GD / Ex db/Ex eb IIC / Ex I M2 / Ex db I / Ex eb I / Ex tb IIIC Ingress protection levels IP66 and 68 (EN 60529/IEC 60529) Ambient temperature -30ºC to +80°C with neoprene gasket and -60ºC to +140ºC with silicon gasket Description ADE 1F cable glands are available in nickel plated brass and stainless steel are designed to accept non armoured cables with overall diameters from 4.5 mm to 104.0 mm with either metric or NPT threads. Thread dimensions range from M12 x 1.5 to M110 x 2.0 and NPT ¼” to NPT 4”. ADE 1F glands are also suitable for industrial and underwater applications and offer ingress protection to IP66 (dustproof and resistant to powerful water jets) or IP68 (underwater tested to 5 bar). ADE 1F glands are ATEX certified to: Ex II 2 GD / Ex db/Ex eb IIC / Ex I M2 / Ex db I / Ex eb I / Ex tb IIIC with two temperature rating options -30ºC to +80ºC with neoprene gasket, as standard, and -60ºC to +140ºC with optional silicon gasket. Gland accessories including, fibre sealing washers and lock nuts. Article ISO Thread Article NPT Thread Outer Clamping Range Thread length mm NP Brass Stainless Steel NP Brass Stainless Steel > < 00816404 00816409 M12 x 1.5 00818404 00818409 NPT ¼” 4.0 8.0 15.0 00816594 00816595 M16 x 1.5 00818594 00818599 NPT 3/8” 4.0 8.5 15.0 00816504 00816509 M16 x 1.5 00818504 00818509 NPT 3/8” 6.0 12.0 15.0 00816674 00816679 M20 x 1.5 00818674 00818679 NPT ½” 4.0 8.5 15.0 00816694 00816699 M20 x 1.5 00818694 00818699 NPT ½” 6.0 12.0 15.0 00816604 00816609 M20 x 1.5 00818604 00818609 NPT ½” 8.5 16.0 15.0 00816774 00816779 M25 x 1.5 00818774 00818779 NPT ¾” 6.0 12.0 15.0 00816794 00816799 M25 x 1.5 00818794 00818799 NPT ¾” 8.5 16.0 15.0 00816704 00816709 M25 x 1.5 00818704 00818709 NPT ¾” 12.0 20.5 15.0 00816894 00816899 M32 x 1.5 00818894 00818899 NPT 1” 12.0 21.0 15.0 00816804 00816809 M32 x 1.5 00818804 00818809 NPT 1” 16.0 27.5 15.0 00816994 00816999 M40 x 1.5 00818994 00818999 NPT 1¼” 16.0 27.5 15.0 00816904 00816909 M40 x 1.5 00818904 00818909 NPT 1¼” 21.0 34.0 15.0 00817094 00817099 M50 x 1.5 00819094 00819099 NPT 1½” 21.0 34.0 16.0 00817004 00817009 M50 x 1.5 00819004 00819009 NPT 1½” 27.0 41.0 16.0 00817294 00817299 M63 x 1.5 00819294 00819299 NPT 2” 33.0 48.0 17.0 00817204 00817209 M63 x 1.5 00819204 00819209 NPT 2” 40.0 56.0 17.0 00817394 00817399 M75 x 1.5 00819494 00819499 NPT 2½” 40.0 56.0 18.0 00817304 00817309 M75 x 1.5 00819404 00819409 NPT 2½” 47.0 65.0 18.0 00817494 00817499 M80 x 2.0 00819594 00819599 NPT 3” 47.0 65.0 20.0 00817404 00817409 M80 x 2.0 00819504 00819509 NPT 3” 54.0 73.0 20.0 00817594 00817599 M90 x 2.0 00819694 00819699 NPT 3½“ 54.0 73.0 22.0 00817504 00817509 M90 x 2.0 00849604 00849609 NPT 3½“ 63.0 82.0 22.0 00817694 00817699 M100 x 2.0 – – – 63.0 83.0 22.0 00817604 00817609 M100 x 2.0 – – – 72.0 92.0 22.0 00817794 00817799 M110 x 2.0 – – – 72.0 92.0 22.0 Technical data (Extract) (For detailed information please click here) Protection class IP 66 and 68 (EN 60529/IEC 60529) Dimensions see data sheet Material Nickel Plated Brass or Stainless Steel Weight see data sheet Resistance Impact resistance – see data sheet Documentation ADE1F datasheet Declaration of Conformity Customer requirements Operating Instructions CE TEK is proudly powered by WordPress