Innovation. Craftsmanship. Reliability. Products Home / Products / Generator Termination Cabinet / Docking Station Pricing Tables: Generator Termination Cabinet / Generator Docking Station Pricing Generator Termination Cabinet with Manual Transfer Switch & Camlocks AMP's provides a quick and convenient generator docking station to connect external generator power. Whether it is long or short term utility outage, facility maintenance, or whatever the needs are; AMP's GTC will keep you up and running. Our generator termination cabinets (GTC) are designed to safely connect and disconnect a portable generator to a building or portable piece of equipment. Our generator tap box solutions can also be used to support temporary and emergency power needs and other urgent needs. Ratings are 400 - 3000A, 600 volt, 3 phase 4 wire, 3 phase 3 wire and 1 phase 3 wire, NEMA 1/3R dual rated and Isc ratings of 85KA RMS symmetrical with no cable lashing required. (Please contact factory for higher ratings) Cabinets are either wall mount or free standing and suitable for indoor or outdoor applications. ETL listed and labeled to UL Standards 1773 terminations Cabinets. Cabinets meet all NEMA and NEC code standards. Cabinets provided with electrical grade plated Aluminum or optional plated Copper bus bars. Our GTCDT meets the NEC 700.3 (F) requirements. Contact factory for additional details. Standard Cam-Lok connection information: 480/277V 3 phase 4 wire (green (ground), gray (neutral), brown (A), orange (B), yellow (C)) Custom Cam-Lok connection information: 208/120V 3 phase 4 wire (green (ground), white (neutral), black (A), red (B), blue (C)) Contact factory for applications with 1200 amp 480 volt and greater, requiring NEC ground fault Contact factory for pricing on dual purpose generator docking station and company switch options Products Bussed Gutter / Multi-Tap / Termination Cabinets Busway Combo-Metering / Single Main / MMP Combo-Metering / Multiple Main Commercial Multi-Tenant Metering Current Transformer Cabinets Disconnects Enclosures Floor Duct / Wireway Generator Termination Cabinet / Docking Station Generator Termination Cabinet / Generator Docking Station Pricing Generator Termination Cabinet with Manual Transfer Switch & Camlocks Ground Bar / Miscellaneous Components Marina Substations Medium Voltage Equipment Residential Multi-Tenant Metering Service Connection Cabinets Service Entrance Automatic Transfer Switch - Switchboards Switchboards - Panelboards ADDITIONAL INFORMATION O&M Manuals: GTC_O&M GTC/GTCDT Brochure GTC/GTCDT Catalog Insert GTCDTNF Non-fused Brochure You must be registered and approved by AMP to view information displaying this icon. Register AMP's Terms & Conditions Policy User Login Register Contact Us (763) 551.1555 (800) 328.8658 Open Mobile Menu Close Mobile Menu PRODUCT LINES Bussed Gutter / Multi-Tap / Termination Cabinets Busway Combo-Metering / Single Main / MMP Combo-Metering / Multiple Main Commercial Multi-Tenant Metering Current Transformer Cabinets Disconnects Enclosures Floor Duct / Wireway Generator Termination Cabinet / Docking Station Ground Bar / Miscellaneous Components Marina Substations Medium Voltage Equipment Residential Multi-Tenant Metering Service Connection Cabinets Service Entrance Automatic Transfer Switch - Switchboards Switchboards - Panelboards CONTACT US American Midwest Power 3131 Vicksburg Lane Plymouth, MN 55447-0036 Search ©2021 All Rights Reserved | PRIVACY POLICY Visit us on Facebook View our Twitter Feed View us on LinkedIn ...