Services Company Material bank Oikojankatu 13 • 33840 TAMPERE • Center 010 583 2900 • info@teollisuuskylma.fi Company Customer benefits Environmental responsibility References Moilanen's bakery Saarioinen Valkeakoski Valio Tampere dairy Personnel News Rekry Valio Oy Tampereen Meijer has a new special milk line refrigeration plant In 2014, Suomen Teollisuuskylmä Oy was implementing a new refrigeration plant for Valio's Tampere dairy line. Like other Valio Tampere dairy refrigeration plants, the new one is an ammonia plant. The filling of the new plant is 1200 kg and the total ammonia is 8400 kg. The refrigeration system provided for a two-stage expansion of the process. Initially, two compressors are used, the power of which is regulated by frequency converters. Two 502 kW compressors were installed in the dairy's 83-square-meter space. Two 502 kW Sabroe SMC 108 L compressors were installed in a total space of 83 square meters. Valio's Tampere dairy refrigeration plant cools the process water, which is used to cool the heat generated in the milk production process. The process water is cooled in a water / propylene glycol heat exchanger and the propylene glycol in turn in an ammonia plant free-circulation wet evaporator. The ammonia is condensed with two air condensers that were already dimensioned for the upcoming power increase. Condensers on the dairy roof. The installation went smoothly Installation of the plant began in January and was already completed in early June. Valio praises the schedule of the project, which went well in every way. At the best, Suomen Teollisuuskylmaa had 10 employees on a busy construction site. The contract is described in more detail in Kylmäextra magazine issue 2/14. You can read the article here . News Arlan Sipoo's dairy renewed its refrigeration equipment READ MORE! To the news archive front page Material bank Contact information Take contact Company Customer benefits Environmental responsibility References Personnel News Rekry Services Installation services Maintenance services Monitoring plans for pressure equipment