+34 93 586 21 68 +34 93 586 21 69 Languages LOW VOLTAGE CABLES MEDIUM VOLTAGE CABLES ABOUT CONTACT XTREM H07RN-F OVERVIEW SPECIFICATIONS TECHNICAL & SALES SUPPORT Flexible rubber cable, for industrial use. Xtrem® H07RN-F rubber cables are designed to supply power to low voltage appliances including electric motors and submersible pumps in deep water installations as well as many other types of electrical equipment. Thanks to its extraordinary flexibility and mechanical strength, the Xtrem® H07RN-F cable is ideal for power transmission in both fixed installation or mobile service. The nominal voltage up to 1000 V thanks to the high dielectric properties of the insulation material (according to HD 516). Top Cable Xtrem® H07RN-F cables are designed to power all types of electrical equipment including motors and submersible pumps in deep water installations (AD8). XTREM® H07RN-F cable performance Electrical performance LOW VOLTAGE 450/750 V Standard EN 50525-2-21 / IEC 60245 Approvals AENOR / HAR / DNV / GOST-R / AWQC / CE / RoHS Safe drinking water certificate Construction Products Regulation (CPR) Eca Thermal performance Maximum service temperature: 90ºC. Maximum short-circuit temperature: 250ºC (max. 5 s). Minimum service temperature: -40ºC (fixed and protected installations) and -35ºC (mobile use) Fire performance Flame non-propagation based on UNE-EN 60332-1 and IEC 60332-1. Reaction to fire CPR: Eca, according to EN 50575. Mechanical performance Minimum bending radius: 3 x cable diameter (up to 12 mm2). 4 x cable diameter (from 12 mm2 onwards). Impact resistance: AG2 Medium severity. Chemical performance Chemical & Oil resistance: Excellent. Grease & mineral oils resistance: Excellent. Water performance Water resistance: AD8 Submersion. Cable for submersible pumps in drinkable water based on AS/NZS 4020. Deep wells Drinkable water AWQC. Other Meter by meter marking. Installation conditions Open Air. Applications Industrial use. Mobile use. Robotics. Windmills Temporary site installations. Packaging Available in rolls of 100 m. and drums. XTREM H07RN-F cable design Conductor Electrolytic copper, class 5 (flexible), based on EN 60228 and IEC 60228. Insulation Rubber (type EPR). The standard identification of insulated conductors is the following: 1 x Natural 2 x Blue + Brown 3 G Blue + Brown + Yellow/Green 4 G Brown + Black + Grey + Yellow/Green 5 G Brown + Black + Grey + Blue + Yellow/Green 6 or more Black numbered + Yellow/Green Outer sheath Flexible rubber. Black colour. DOWNLOAD CABLE DATASHEET DOWNLOAD DoP LOW VOLTAGE 450/750 V Flame non-propagation based on UNE-EN 60332-1 and IEC 60332-1. Maximum service temperature: 90ºC. UNE-EN 60332-1 Industrial use / Mobile use / Robotics / Temporary site installations / Windmills Eca EN 50525-2-21 / IEC 60245 Minimum bending radius: 3 x cable diameter (up to 12 mm2). 4 x cable diameter (from 12 mm2 onwards). Technology 1. Conductor Electrolytic copper, class 5 (flexible), based on EN 60228 and IEC 60228. 2. Insulation Rubber (type EPR). The standard identification of insulated conductors is the following: 1 x Natural 2 x Blue + Brown 3 G Blue + Brown + Yellow/Green 4 G Brown + Black + Grey + Yellow/Green 5 G Brown + Black + Grey + Blue + Yellow/Green 6 or more Black numbered + Yellow/Green 3. Outer sheath Flexible rubber. Black colour. Other cables with similar properties TOPWELD H01N2-D The special cable for welding. TOXFREE ZH XTREM H07ZZ-F (AS) The extra-flexible LSZH rubber cable for mobile service. TECHNICAL & SALES SUPPORT If you have any questions, please contact us. We’ll do our best to help. Select your country * Afghanistan Albania Algeria Andorra Angola Argentina Armenia Australia Austria Azerbaijan Bahamas Bahrain Bangladesh Barbados Belarus Belgium Belize Benin Bhutan Bolivia Bosnia Botswana Brazil Brunei Bulgaria Burkina Faso Burundi Cambodia Cameroon Canada Central African Republic Chad Chile China Colombia Congo Congo, Dem. Rep. Costa Rica Croatia Cuba Cyprus Denmark Djibouti Dominican Republic Ecuador Egypt El Salvador Equatorial Guinea Eritrea Estonia Ethiopia Finland France French Guiana Gabon Gambia Georgia Germany Ghana Greece Guatemala Guinea Guinea-Bissau Guyana Haiti Honduras Hong-Kong Hungary Iceland India Indonesia Iran Iraq Ireland Israel Italy Ivory Coast Jamaica Japan Jordan Kazakhstan Kenya Kuwait Kyrgyzstan Laos Latvia Lebanon Liberia Libya Liechtenstein Lithuania Luxembourg Macedonia Madagascar Malawi Malaysia Mali Malta Mauritania Mexico Moldova Monaco Mongolia Montenegro Morocco Mozambique Myanmar Namibia Nepal Netherlands New Zealand Nicaragua Niger Nigeria North Korea Norway Oman Pakistan Panama Papua New Guinea Paraguay Peru Philippines Poland Portugal Puerto Rico Qatar Rep. Czech Romania Rusia Rwanda Saudi Arabia Senegal Serbia Sierra Leone Singapore Slovakia Slovenia Somalia South Africa South Korea Spain Sri Lanka Sudan Suriname Sweden Switzerland Syria Tadzhikistan Taiwan Tanzania Thailand Timor-Leste Togo Tunis Turkey Turkmenistan Uganda Ukraine United Arab Emirates United Kingdom United States Uruguay Uzbekistan Venezuela Vietnam Western Sahara Yemen Zambia Zimbabwe Activity* Cable Distributor Cable Installer Contractor Other Student Do you need us to contact you?* Yes No I accept the privacy policy* Notice We and selected third parties use cookies or similar technologies as specified in the cookie policy. In case of sale of your personal information, you may opt out by using the link "Do Not Sell My Personal Information". To find out more about the categories of personal information collected and the purposes for which such information will be used, please refer to our privacy policy. Learn more and customize Reject Accept LOW VOLTAGE CABLES RUBBER CABLES PANEL WIRE CABLES XLPE/PVC POWER CABLES XLPE LSOH SAFETY CABLES CONTROL & SCREENED CABLES SOLAR CABLES LOW VOLTAGE SPECIAL CABLES MARINE CABLES MEDIUM VOLTAGE CABLES RHZ1 HEPRZ1 RHVHMVH TYPES OF CABLES ABOUT CONTACT BLOG RESOURCES LINKEDIN Legacy & Privacy Cookie Policy Top Cable 2021 © All rights reserved