HOMEWHO WE AREWHAT WE OFFER CASE STUDIES EVENTS AND TRAININGCAREERS CONTACT REGIONS TOWER PORTFOLIOREGIONS TOWER REGIONS TOWER IN SERVICE Client Name: Regions Tower Project Started: 2014 Location: Shreveport, LA ABOUT PROJECT Problem: 1973 PCV (sidewinder) Trane chiller motor failed. Upon disassembly, we discovered excessive end-play had allowed the 1st-stage impeller to rub against the diaphragm plate and the back of the impeller was extremely thin. Solution: We removed the motor and sent it off for repair/refurbishment. A replacement impeller was not available since the unit was over 40 years old, so original was repaired and rebuilt with epoxy. The repaired impeller was spin-balanced, tested, and returned to service as the chiller compressor was reassembled. Legacy: The owner was able to repair this chiller through their maintenance and repair budget, rather than replace with capital money. RELATED PROJECTS OUR MISSION: Developing People, Leveraging Technology, and Building Processes that enable our Clients to reach their goals. Get in Touch 504 West 67th St, Shreveport, LA 71106 info@storerservices.com 1-800-844-4822 (318) 865-1466 (318) 861-8481 Controls Issues? Our Client Services Team is here to help! support@storerservices.com 1-877-550-4778 Business Hours Monday - Friday: 8am to 5pm After-Hours Support 1-877-550-4778 Service AR 1052130 LA 66407 TACLA 291573C LMP 5237