COMPANY NEWS PRODUCTION PRODUCTS FOR PROJECT ORGANIZATIONS FOR CUSTOMERS Assembly cable for industrial automation KuPe-IEOEz TU 3581-001-92800518-2012 Cable with conductive cores made of copper wires with insulation and sheath made of polymeric materials corresponding to the required fire hazard indicator, with individually shielded foil-clad material elements, with a common foil-clad screen, without armor, with a round cross-section and an extruded substrate and any non-hygroscopic aggregates. The cable complies with the requirements of clause 9.3.1 of GOST IEC 60079-14-2011 “Explosive atmospheres. Part 14. Design, selection and installation of electrical installations " Technical parameters: Nominal cross-section of conductive conductors of cables, mm 2: 0.20; 0.35; 0.5; 0.75; 1.0; 1.2; 1.5; 2.5; four; 6 Number of cores, pairs, triplets, quadruples 1 - 91 Modifications: KuPe-IEOEz - without designation of a fire hazard indicator - with PVC insulation, with a PVC plastic sheath, flame retardant with a single gasket KuPe-IEOEzng (A) - c insulation made of polyvinyl chloride plasticate, with a sheath made of polymeric material of low flammability, flame retardant for group laying according to category A KuPe-IEOEzng (A) -LS - with insulation and sheath made of polymeric materials of reduced fire hazard, with reduced smoke and gas emission, flame retardant in case of group laying according to category A KuPe-IEOEzng (A) -HF - with insulation and sheath made of polymer compounds that do not contain halogens, does not spread combustion during group laying according to category A and does not emit corrosive gaseous products during combustion and smoldering KuPe-IEOEzng (A) -FRLS - with fire-resistant insulation, with a sheath made of polymeric materials of reduced fire hazard, with a reduced smoke and gas emission, flame -retardant when laid in a group according to category A, fire - resistant KuPe-IEOEzng (A) -FRHF - with fire-resistant insulation, with a sheath made of polymer compounds, not containing halogens, flame retardant when laid in a group according to category A, does not emit corrosive gaseous products during combustion and smoldering, fire-resistant Note: - with single-wire conductors, add the suffix "ok"; - with conductive conductors made of tinned copper wires, the index "l" is added; - with screens made of tinned copper wires, the index "l" is added; - with screens made of copper wires, the index "m" is added; - with combined screens the index "fm", "fl", "fkm" or "fkl" is added; - with special protection against damage by rodents in the form of armor made of galvanized steel wires over the outer sheath "G"; - with water-blocking elements, the index "in" is added; - with a circular cross-section, backing and fillers, the index "z" is added; - with insulation made of a crosslinkable polyolefin composition, the index "Ps" is added; - with belt insulation under the screens, the index "p" is added; - with increased protection against crosstalk, the index "PZ" is added; - in the cold-resistant version, the "ХЛ" index is added; - in the heat-resistant version, the index "ts" is added; Electrical resistance of current-carrying conductors to direct current - in accordance with GOST 22483-2012. Electrical resistance of insulation, recalculated per 1 km of length, MOhm, not less: - cables insulated from a crosslinkable polyolefin composition: 500 - cables insulated from organosilicon rubber and from halogen-free polymer compounds: 100 - other cables: 10 Test alternating voltage : - between conductors - 2500 V; - between conductors and screens - 2000 V; Increased operating temperature: - cables with the indexes "ng (A) -HF", "ng (A) -FRLS", "ng (A) -FRHF" - up to 110 ° C - cables in heat-resistant design ("ts") - up to 125 ° С - other cables: + 80 ° С Reduced operating temperature: - cables in the HL version - up to minus 60 ° С - other cables: up to minus 50 ° С Increased air humidity up to 98% at temperatures up to 35 ° С. Resistance to water Resistance to longitudinal water propagation (version "c") Resistance to solar radiation Resistance to oil and petrol Resistance to mounting bending resistance to vibration loads Resistance to impact Resistance to linear load resistance to stretching Resistance to frost Resistant to salt spray resistance to the action of fungi resistance to dynamic effects of dust lifetime of 35 years, Identification number: coupe-IEOEzng ( A) -LS 3x2x0.75 TU 3581-001-92800518-2012: Cable with stranded conductors made of copper wires, with insulation and sheath made of polymeric materials of reduced fire hazard, with reduced smoke and gas emission, flame retardant when laid in a group according to category A, with three pairs individually screened with foil material, with a common screen made of foil material , without armor, with circular cross-section and extruded backing and any non-hygroscopic aggregates. KuPe-IEOEzng (A) -HF 7x2x1.0 l TU 3581-001-92800518-2012: Cable with stranded conductors made of tinned copper wires, insulated and sheathed from halogen-free polymer compounds, flame retardant when laid in a group according to category A and does not emit corrosive gases during combustion and smoldering, with seven individually shielded foil material in pairs, with a common screen of foil-clad material, without armor, with a circular cross-section and an extruded substrate, and any non-hygroscopic aggregates. OUR PRODUCTION KuPe-OEK KuPe-OEz KuPe-OEB KuPe-OE KuPe-K ABOUT COMPANY History Licenses and certificates our clients Personalities PRODUCTS KuPe cables Other products Installation cables MKPS NEWS PRODUCTION COOPERATION CONTACTS Commodity Markets BID ASK Aluminum 0.00 0.00 Nickel 0.00 0.00 Copper 0.00 0.00 15 September 2014 Currency rates of the Central Bank of the Russian Federation Date: Dollar rate Euro exchange rate