+7 (347) 228-57-53, 228-57-70 BACK CALL ABOUT COMPANY CATALOG OUR CUSTOMERS CERTIFICATES CONTACTS PRESSURE MANIFOLD BLOCK HOME > CATALOG > BLOCK OF PRESSURE MANIFOLDS APPOINTMENT BNG pressure manifold blocks are designed to be installed on water distribution pipelines of reservoir pressure maintenance systems and serve to distribute and measure the pressure flow rate and measure the flow rate, pressure of process water pumped into injection wells. COMPLETENESS The technological block contains: pressure head (common) collector; pressure water conduits; drainage collector; shut-off and control valves; automatic signaling devices and sensors; ventilation and lighting system. DESCRIPTION OF CONSTRUCTION The block-box enclosing structures are walls made of ready-made pressed "sandwich" panels in the form of a three-layer structure. Insulation material - basalt slab. The thickness of the profiled sheets is 0.7mm. The load-bearing metal structures include volumetric frames made of rolled profiles. All steel structures are painted with two layers of enamel over a layer of primer. A visor and external lighting are installed above the door. The foundations for the equipment are the steel frame of the floor of the block - shelter. The floor in the room is a corrugated steel sheet, which is made of corrugated steel sheet 4 mm thick with a slope from the side walls towards the center of 0.5%. Under the floor, in the center along the block, channel No. 10 is laid with shelves upward, in the rear wall an outlet to the drain is welded to it. Above the longitudinal channel No. 10, a slot with a width of 40 ... 50 mm is left over the entire length of the block. The base of the block - shelter is designed for technological load up to 20.0 kN / m2 (2000 kgf / m2). The building of the complex is designed for operation with indoor relative humidity up to 80%. All openings in the walls for the passage of technological pipelines are made with the requirements of tightness. The roof shape is flat, removable (depending on customer requirements). External doors are equipped with self-closing door closers. The dimensions of the doors are designed in accordance with the instructions and requirements of SP 1.13130.2009. All door blocks have locks for locking with the ability to open from the inside without a key. SPECIFICATIONS: Parameter name Value Working environment temperature, ° С +5 ... 65 Workspace Industrial water for reservoir pressure maintenance systems (fresh, stratal) Nominal diameter of the pressure header pipeline, mm 100 ... 300 Nominal diameter of the discharge pipeline, mm 65, 80, 100, 150 Number of high-pressure water lines from 2 to 8 Nominal pressure, MPa 10, 16, 21, 25 Ambient temperature, ° С Ambient temperature, ° С Climatic modification according to GOST 15150-69 * U, UHL, HL Unit explosive zone class according to PUE B-1a or B-1b Overall dimensions, mm * Length Width Height 4000 ... 8000 3000 ... 3250 to 3400 Weight, kg, no more * 10000 LAYOUT EXAMPLE: INDUSTRIAL WASTEWATER TREATMENT PLANT SERVICES PRESSURE MANIFOLD BLOCK BLOCK-MODULAR BUILDINGS CAPACITIVE EQUIPMENT STEEL STRUCTURES PUMPING STATIONS DRINKING FOUNTAINS CABINET EQUIPMENT ABOUT COMPANY CATALOG OUR CUSTOMERS CERTIFICATES CONTACTS SCIENTIFIC AND PRODUCTION FIRM "VISMA" © 2015 WEBSITE DEVELOPMENT ARTMAX