CE-LS Generator Neutral and Line Cubicles Generator and Line Cubicles ≤ 15.000A CE-LS cubicles series are designed for use in Power Plants mainly as Generator line exit and Generator neutral earthing. GENERAL CHARACTERISTICS Typically the CE-LS cubicles are uses as interface between Generators, Step-Up transformers and auxiliary tranasformers The specific desing and construction system allow to customise the cubicles for all clients configurations. Conductors can be sized and tested for rated current up to 15.000 A For outdoor application are available version with protection degree up to IP56 or Type 4x VERSIONS The cubicles can be placed: One one side of the generator (combined neutral and line cubicles) On the two side of the generator (separated neutral and line cubicles) On top of the Generator Under the the Generator Interface connection to Generator and Step Up transformer Copper or aluminium bars Bus duct Cabels Insulated compact busbars Isolated Phase Bus Ducts – IPB DOWNLAOD TECHNICAL SHEET (PDF) Other info ELECTRICAL DATA Rated voltage up to 36 kV Rated power frequency withstand voltage (1min.) up to 50/60 Hz Rated lighting impulse withstand voltage up to 170 kV Rated current up to 15.000 A Maximum short-term rated current 1 sec up to 150 KA Maximum peak current up to 375 kA Protection degree up to IP55 - Type 4x Ambient temperature -10°C to + 55°C IAC Classification A-FLR (1 sec) ** 50 kA Seismic acceleration (type tested) 1g ** Internal arc withstanding in option STANDARDS AND TESTS The CE-LS cubicles comply with the main Italian and International standards, these have performed all relevant type tests carried out by qualified Laboratories. Thermal type test can be performed in our internal laboratory with currents up to 15.000A at 50Hz or 60Hz 123456789101112131415 Headquarters and Factory: via G. Rossini, 24 37060 Castel d’Azzano (Verona) Italy Tel. +39 045 8546511 Fax +39 045 8520214 E-mail: info@casagrande.vr.it Production Branch: Via Bortolazzi, 57 37060 Castel d’Azzano (Verona) Italy Production Branch: Contrada Piana Z.I. 86019 Vinchiaturo (Campobasso) Italy Tel. +39 0874 340225 Fax +39 0874 340227 APERTURA NUOVO SITO PRODUTTIVO E RIORGANIZZAZIONE INTERNA AL FINE DI SVILUPPARE NUOVE TIPOLOGIE DI PRODOTTO – ACQUISTO DI N.3 CARRIPONTE DA 15 TON. Il progetto di investimento prevede l’acquisto di n. 3 carriponte da 15 t, installati in un nuovo sito produttivo, che saranno utilizzati nel processo di costruzione di quadri elettrici per generazione di grossa potenza e shelter. Intervento realizzato avvalendosi del finanziamento POR – Obiettivo “Investimenti a favore della crescita e dell’occupazione” Parte FESR fondo europeo di sviluppo regionale 2014-2020. Asse 3 – Azione 3.1.1 ©2021 CASAGRANDE ELETTROCOSTRUZIONI S.P.A. - P.IVA IT00663680239 - PRIVACY POLICY - COOKIE POLICY - LEGAL NOTES SITE BY VERTER.IT MENU HOME ABOUT US COMPANY DEPARTMENTS RESEARCH & DEVELOPMENT AND TESTS MARKET SECTOR AND DISTRIBUTION AREA QUALITY, SAFETY AND ENVIRONMENT NEWS WORK WITH US HOW TO REACH US CONTACT US ALL PRODUCTS LOW VOLTAGE MEDIUM VOLTAGE OTHER PRODUCTS PLANTS & SITE SERVICES