ABOUT AEGIS PIPE FITTING PRODUCTS CONTACT US DISTRIBUTORS READY TO ORDER? FIND A LOCAL DISTRIBUTOR! Aegis Technologies' products are available through our authorized distributor network. Use our online search to find a distributor near you! Overview & Features • Specifications • Downloads Aegis ADJUSTER™ Adjustable Drop Nipple The Aegis Adjuster™ Adjustable Drop Nipple consists of high strength carbon steel casings and ethylene propylene diene monomer (EPDM) O-ring seals. The outer case, with a one inch (1”) male or female NPT inlet, and the inner case, with a half inch (½”) or three quarter inch (¾”) NPT sprinkler outlet, adjusts in or out over a specified range with the use of two (2) O-ring seals and screw type threads to permit, without re-cutting, the adjustment of the distance of the sprinkler from the sprinkler system branch line. Once in its final adjusted position, the Adjuster™ ADN will not extend as a result of system vibrations or pressure surges. Designed for use in wet or dry systems in accordance with NFPA Standards 13, 13R, & 13D, and is rated for use at a maximum pressure and temperature of 300 PSI and 300°F, respectively. UL Listed in accordance to UL 1474 and FM Approved in accordance to FM Class 1631. The inlet and outlet threads conform to ANSI B1.20.1. Each unit has been pressure tested for O-ring integrity prior to shipment. FEATURES: LABOR SAVING Eliminates expensive cutting and re-fitting of the drop nipple in flush to ceiling and wall installations. FOR WET OR DRY AUTOMATIC SPRINKLER SYSTEMS In accordance to NFPA 13, 13R, & 13D. ALLOWS DIRECT ATTACHMENT TO BRANCH CONNECTION with available male inlet. UL LISTED Listed in accordance to UL 1474 5th edition with qualifying tests up to 1500 psi. FM APPROVED Approved in accordance to FM Class 1631 with qualifying tests up to 1200 psi. HIGH STRENGTH Constructed of carbon steel & high performance EPDM rubber. THREADS CONFORMS TO ANSI B1.20.1 NPT Threads machined to very close tolerances. INCREASED CORROSION RESISTANCE Zinc chromate plated. FULLY TRACEABLE Lot number marked on each unit. PRESSURE TESTED All pieces fully tested prior to shipment. QUALITY MATERIALS All material batches are checked by independent laboratories to insure all material standards are met. SPECIFICATIONS STANDARDMetric MODEL # PART # ADJUSTMENT INLET SIZE (A) OUTLET SIZE (B) MIN. LENGTH (C) MAX. LENGTH (D) WEIGHT MAX SPRINKLER K-FACTOR EQUIVALENT LENGTH** RATED PRESSURE MAX. AMBIENT TEMP. BOX QTY. 201 902011005 1" 1" Female ½" Female 3.675" 4.675" 0.7 lbs 11.2 gpm/psi 1/2 1.5' 300 psi 300° F 70 202 902021005 2" 1" Female ½" Female 4.675" 6.675" 0.9 lbs 11.2 gpm/psi 1/2 1.6' 300 psi 300º F 52 203 902031005 3" 1" Female ½" Female 5.675" 8.675" 1.1 lbs 11.2 gpm/psi 1/2 3.2' 300 psi 300° F 42 201M 90201M1005 1" 1" Male ½" Female 4.675" 5.675" 0.9 lbs 11.2 gpm/psi 1/2 1.6' 300 psi 300° F 54 202M 90202M1005 2" 1" Male ½" Female 5.675" 7.675" 1.1 lbs 11.2 gpm/psi 1/2 1.7' 300 psi 300° F 42 203M 90203M1005 3" 1" Male ½" Female 6.675" 9.675" 1.3 lbs 11.2 gpm/psi 1/2 3.3' 300 psi 300° F 30 201E 90201E1007 1" 1" Female ¾" Female 5.25" 6.25" 1.1 lbs 11.2 gpm/psi 1/2 4.8' 300 psi 300° F 36 202E 90202E1007 2" 1" Female ¾" Female 6.25" 8.25" 1.3 lbs 11.2 gpm/psi 1/2 4.8' 300 psi 300° F 30 203E 90203E1007 3" 1" Female ¾" Female 7.25" 10.25" 1.5 lbs 11.2 gpm/psi 1/2 5.9' 300 psi 300° F 25 201EM 90201EM1007 1" 1" Male ¾" Female 6.25" 7.25" 1.3 lbs 11.2 gpm/psi 1/2 4.9' 300 psi 300° F 30 202EM 90202EM1007 2" 1" Male ¾" Female 7.25" 9.25" 1.5 lbs 11.2 gpm/psi 1/2 4.9' 300 psi 300° F 27 203EM 90203EM1007 3" 1" Male ¾" Female 8.25" 11.25" 1.7 lbs 11.2 gpm/psi 1/2 6.0' 300 psi 300° F 25 * length tolerance is +/- .275" ** approximate friction loss expressed in equivalent lengths of straight 1" Sch 40 pipe in feet, where C=120. DISTRIBUTORS READY TO ORDER? FIND A LOCAL DISTRIBUTOR! Aegis Technologies' products are available through our authorized distributor network. Use our online search to find a distributor near you! DATA SHEETS • Adjuster™ Data Sheet • Adjuster™ Material Safety Data Sheet • Adjuster™ UL Listing VGSQ.EX15352 • Adjuster™ FM Approval Guide INSTALLATION • Adjuster™ Easy Installation Instructions • Adjuster™ Female Inlet Installation Instructions • Adjuster™ Male Inlet Installation Instructions • ANPT Inspection Gaging & Recommended Thread Make-Up Procedures SALES & SUBMITTAL • Adjuster™ Submittal Sheet “The Dropster helps free up our cut/thread line from drops allowing us to fab more branch lines.” Nate S. Deacon Industrial & Supply, Harleysville, PA Our Company • Corporate History • Our Facility & Staff • Find an Authorized Distributor • Contact Us • Sales Terms & Conditions Products & Documentation • Adjuster™ Adjustable Drop Nipple • Branchlet™ Welding Outlet • Dropster™ Reducing Nipple • Document Library Aegis Technologies, Inc. 319 Circle of Progress Pottstown PA 19464-3811 610.676.0300 610.676.0383 Newsletter Sign-up Email Address: ©2017, Aegis Technologies, Inc. All Rights Reserved.