Call us Request a Free Quote! 916-722-8300 Home About Services Equipment Tune-Up Specials Contact HVAC Unit Tune-Up Heating and Cooling Equipment Maintenance Regular HVAC maintenance helps prevent system failure, ensuring that you can stay comfortable even during intensely hot or cold weather. Turn to Pro Air Inc. in Citrus Heights, CA for a tune-up service! We will make sure your equipment is running at optimal levels throughout the entire year. What You Can Expect The service technician will arrive at the scheduled time to perform your service. They will ask you several questions in regards to the performance of your Heating and Air Conditioning system, where your equipment is located and whether or not you are having any trouble with the way your systems performing. They will then begin the Check, Test and Record Tune Up as described in the What We Do Check List below. This can take up to an hour and a half to complete depending on your system and its condition. You will be provided a full report upon completion of the Tune Up, with any recommended repairs and the associated costs with warranties, this should be normal for any Tune up. What they won't tell you is that it is very important to maintain a log of the operation of a Heating and Air system to predict when problems may arise. Without that log it is just a crap shoot and guess who gets the crap, YOU! In the form a report that is based on selling you a new system instead of taking care of the one you has. With our one of a kind 64 point CT&R maintenance program, we record & store all the test data, keep a copy forever in YOUR customer file that will be supplied to the technician at future maintenance or service calls made to your home, or to you at anytime. Also, we can email a copy to your real estate agent or tax accountant at your request. Then, YOU can make the choices based on facts for the necessary or optional repairs your system requires, not the desire of some overzealous Sales Tech looking to bag a great commission while trying to sell you a new system for 30-40 percent more than market value, that you very often don't need. Then we would ask you to review us on Yelp and Facebook and here. link to review page Request a Tune-Up * Name: * Phone: * Email: Message: Maintenance Packages We Offer CT&R 64 Point System Maintenance - $178.00 Click here to view the checklist: CHECK AMBIENT AIR TEMP The air temperature around the air conditioner or heat pump CHECK RETURN AIR TEMP The air temperature inside the home CHECK SUPPLY AIR TEMP The temperature of the air coming out of the vents CHECK AIR BALANCE Confirm proper air balance; make necessary adjustment to existing duct system to achieve even temperatures throughout home CLEAN AIR FILTER Confirm proper sizing of filter. Clean or replace owner supplied air filter CHECK FILTER AND GRILL Confirm operation and seal of filter grill CHECK REGISTERS Confirm proper application and seal of register (vents where air comes out) and adjust as need for proper air flow CHECK LOW PRESSURE A/C & heat pump only is used to check the Freon and operations of the refrigeration system CHECK HIGH PRESSURE A/C & heat pump only is used to check the Freon and operations of the refrigeration system. CHECK SUPERHEAT A/C & heat pump only is used to confirm the Freon charge and correct operations of the refrigeration system CHECK SUCTION LINE TEMP A/C & heat pump only used to measure superheat for Freon charge, test metering device and proper operation of refrigeration system CHECK SUBCOOLING A/C & heat pump only is used to check the Freon charge and operation of the refrigeration system CHECK LIQUID LINE TEMP A/C & heat pump only used to measure sub cooling for Freon charge, test metering device and proper operation of refrigeration system CHECK LOW PRESSURE SWITCH A/C & heat pump only confirm operation and trip point of low pressure switch CHECK HIGH PRESSURE SWITCH A/C & heat pump only confirm operation and trip point of high pressure switch TEST FREON LEVEL A/C & heat pump only confirm proper Freon charge per manufacture specification CHECK FOR FREON LEAKS A/C & HEAT PUMP ONLY Inspect accessible areas for Freon leaks CHECK CONTACTOR A/C & HEAT PUMP ONLY Confirm condition and proper operation of contactor and tighten electrical connections CHECK CAPACITOR A/C & HEAT PUMP ONLY Confirm proper operation and test microfarads to confirm proper capacitance CHECK CIRCUIT BREAKER A/C & HEAT PUMP ONLY Confirm tightness of wires and general operation CHECK DISCONNECT A/C & HEAT PUMP ONLY Confirm fuse size and tighten line wires as needed CHECK DUCT WORK Confirm overall cognition, proper strapping and proper sizing of duct system; confirm proper seal of all ducts CHECK SUPPLY AND RETURN AIR PLENUM Confirm proper installation and air seal of supply and return air plenums CHECK COMPRESSOR FULL LOAD AMPS (FLA) A/C & HEAT PUMP ONLY A/C & heat pump only record maximum compressor electric draw as it is the largest consumer of electricity in your air conditioner. TEST COMPRESSOR AMPS A/C & heat pump only actually confirms the amp draw is within specifications, test for proper electrical operation CHECK OUTDOOR COIL A/C & HEAT PUMP ONLY Inspect for cleanliness and overall condition CLEAN OUTDOOR COIL Clean condenser with medium pressure water as needed CHECK OUTDOOR FAN MOTOR FLA A/C & HEAT PUMP ONLY A/C & heat pump only. Record maximum outdoor fan motor amp draw CHECK OUTDOOR FAN MOTOR AMPS A/C & heat pump only. Test motor amps, actually confirms amp draw is within specifications CHECK OUTDOOR MOTOR A/C & HEAT PUMP ONLY Inspect condenser motor shaft seal and bearing wear CHECK OUTDOOR FAN BLADE A/C & HEAT PUMP ONLY Inspect condenser fan blade to confirm true and balanced operation TEST AIR FLOW Confirm proper air flow is in accordance to manufacturer's specification CHECK BLOWER SPEED Set blower speed based on manufactures specification CHECK EVAPORATOR COIL A/C & HEAT PUMP ONLY Inspect for cleanliness and overall condition CHECK CONDENSATE DRAIN A/C & HEAT PUMP ONLY Inspect drain to confirm proper grade and drainage CLEAN CONDENSATE DRAIN AS NEEDED Clean condensate drain line as needed CHECK SECONDARY DRAIN Inspect secondary drain pan for proper operation and cleanliness and clean as needed CHECK BLOWER MOTOR Inspect blower motor shaft and bearing wear CHECK BLOWER WHEEL Inspect for cleanliness and overall condition RECORD INDOOR BLOWER MOTOR FLA Record maximum blower motor amp draw TEST INDOOR BLOWER MOTOR AMPS Actually confirms indoor blower motor amp draw is within specifications CHECK INDOOR BLOWER START TIME Measures indoor blower start time delay relative to system start time, a of 60-180 seconds delay is preferred for the most efficient operation, also prevents hot air on cooling start up and insures warm air on heating start up. CHECK INDOOR BLOWER OFF TIME Measures blower off time delay. Indoor blower motor off time delay of 60-135 seconds is preferred to allow all the cool or hot air to be removed from the air conditioner or heater and put it in your home on shut down. RECORD INDUCER FLA Record maximum inducer motor amp CHECK INDUCER AMP. Test inducer amps, actually confirms amp draw is within specifications CHECK INDUCER ASSEMBLY Confirm proper operation and overall condition TEST DRAFT PRESSURE SWITCHES Confirm proper trip pressure, insures safe operation CHECK THERMOSTAT Confirm operation and calibration of thermostat ADJUST THERMOSTAT Adjust thermostat for proper operation CHECK GAS PRESSURE Used to confirm proper firing rate of furnace. Increases life span of furnace. CHECK GAS LINE Confirm proper installation and confirm there are no leaks ADJUST GAS AIR MIXTURE Adjust gas air mixture for proper operation, allows you to get all the heat out of the gas you buy and increases life of furnace CHECK FURNACE FLUE Confirm proper sizing, condition and overall operation of flue CHECK TEMPERATURE RISE Confirms proper air flow. Prevents overheating of heat exchanger which increases life of heat exchanger CHECK GAS VALVE Confirm proper operation and check for gas leakage CHECK LIMIT SWITCHES Confirm proper operation and proper trip temperatures CHECK CONTROL BOARD Confirm proper configuration of board as they are rarely correct from factory for our area. CHECK IGNITER Confirm igniter residence and adjust as needed for proper ignition, increases igniter life expectancy CHECK & CLEAN FLAME SENSOR Confirm micro amp signal to control board and clean to insure strongest signal. Increases igniter life expectancy CHECK HEAT EXCHANGER Confirm heat exchanger has no leaks or cracks. Safety inspection very important as it will expel carbon monoxide into home if cracked. CHECK BURNERS Confirm proper lighting and adjust as needed CLEAN BURNERS Clean and adjust burners for clean and efficient operation CHECK PILOT Confirm and adjust pilot for proper operation CLEAN PILOT Clean pilot and adjust for proper operation CT&R 43 Point Air Conditioner Maintenance - $89.00 Click here to view the checklist: CHECK AMBIENT AIR TEMP The air temperature around the air conditioner or heat pump CHECK RETURN AIR TEMP The air temperature inside the home CHECK SUPPLY AIR TEMP The temperature of the air coming out of the vents CHECK AIR BALANCE Confirm proper air balance; make necessary adjustment to existing duct system to achieve even temperatures throughout home CLEAN AIR FILTER Confirm proper sizing of filter. Clean or replace owner supplied air filter CHECK FILTER GRILL Confirm operation and seal of filter grill CHECK REGISTERS Confirm proper application and seal of register (vents where air comes out) and adjust as need for proper air flow CHECK LOW PRESSURE A/C & heat pump only is used to check the Freon and operations of the refrigeration system CHECK HIGH PRESSURE A/C & heat pump only is used to check the Freon and operations of the refrigeration system. CHECK SUPERHEAT: A/C & heat pump only is used to confirm the Freon charge and correct operations of the refrigeration system CHECK SUCTION LINE TEMP A/C & heat pump only used to measure superheat for Freon charge, test metering device and proper operation of refrigeration system CHECK SUBCOOLING A/C & heat pump only is used to check the Freon charge and operation of the refrigeration system CHECK LIQUID LINE TEMP A/C & heat pump only used to measure sub cooling for Freon charge, test metering device and proper operation of refrigeration system CHECK LOW PRESSURE SWITCH A/C & heat pump only confirm operation and trip point of low pressure switch CHECK HIGH PRESSURE SWITCH A/C & heat pump only confirm operation and trip point of high pressure switch TEST FREON LEVEL A/C & heat pump only confirm proper Freon charge per manufacture specification CHECK FOR FREON LEAKS Inspect accessible areas for Freon leaks CHECK CONTACTOR Confirm condition and proper operation of contactor and tighten electrical connections CHECK CAPACITOR Confirm proper operation and test microfarads to confirm proper capacitance CHECK CIRCUIT BREAKER Confirm tightness of wires and general operation CHECK DISCONNECT Confirm fuse size and tighten line wires as needed CHECK DUCT WORK Confirm overall cognition, proper strapping and proper sizing of duct system; confirm proper seal of all ducts CHECK SUPPLY AND RETURN AIR PLENUM Confirm proper installation and air seal of supply and return air plenums CHECK COMPRESSOR FULL LOAD AMPS (FLA) A/C & heat pump only record maximum compressor electric draw as it is the largest consumer of electricity in your air conditioner. TEST COMPRESSOR AMPS A/C & heat pump only actually confirms the amp draw is within specifications, test for proper electrical operation CHECK OUTDOOR COIL Inspect for cleanliness and overall condition CLEAN OUTDOOR COIL Clean condenser with medium pressure water as needed CHECK OUTDOOR FAN MOTOR FLA A/C & heat pump only. Record maximum outdoor fan motor amp draw CHECK OUTDOOR FAN MOTOR AMPS A/C & heat pump only. Test motor amps, actually confirms amp draw is within specifications CHECK OUTDOOR MOTOR Inspect condenser motor shaft seal and bearing wear CHECK OUTDOOR FAN BLADE Inspect condenser fan blade to confirm true and balanced operation TEST AIR FLOW Confirm proper air flow is in accordance to manufactures specification CHECK BLOWER SPEED Set blower speed based on manufacturer's specification CHECK EVAPORATOR COIL A/C & HEAT PUMP ONLY Inspect for cleanliness and overall condition CHECK CONDENSATE DRAIN A/C & HEAT PUMP ONLY Inspect drain to confirm proper grade and drainage CLEAN CONDENSATE DRAIN AS NEEDED Clean condensate drain line as needed CHECK SECONDARY DRAIN Inspect secondary drain pan for proper operation and cleanliness and clean as needed CHECK BLOWER MOTOR Inspect blower motor shaft and bearing wear CHECK BLOWER WHEEL Inspect for cleanliness and overall condition RECORD INDOOR BLOWER MOTOR FLA Record maximum blower motor amp draw TEST INDOOR BLOWER MOTOR AMPS Actually confirms indoor blower motor amp draw is within specifications CHECK INDOOR BLOWER START TIME Measures indoor blower start time delay relative to system start time, a 60-180 seconds delay is preferred for the most efficient operation, also prevents hot air on cooling start up and insures warm air on heating start up. CHECK INDOOR BLOWER OFF TIME Measures blower off time delay. Indoor blower motor off time delay of 60-135 seconds is preferred to allow all the cool or hot air to be removed from the air conditioner or heater and put it in your home on shut down. CT&R 38 Point Heating Maintenance - $89.00 Click here to view the checklist: CHECK AMBIENT AIR TEMP The air temperature around the air conditioner or heat pump CHECK RETURN AIR TEMP The air temperature inside the home CHECK SUPPLY AIR TEMP The temperature of the air coming out of the vents CHECK AIR BALANCE Confirm proper air balance; make necessary adjustment to existing duct system to achieve even temperatures throughout home CLEAN AIR FILTER Confirm proper sizing of filter. Clean or replace owner supplied air filter CHECK FILTER AND GRILL Confirm operation and seal of filter grill CHECK REGISTERS Confirm proper application and seal of register (vents where air comes out) and adjust as need for proper air flow TEST AIR FLOW Confirm proper air flow is in accordance to manufactures specification CHECK BLOWER SPEED Set blower speed based on manufacturer's specification CHECK BLOWER MOTOR Inspect blower motor shaft and bearing wear CHECK BLOWER WHEEL Inspect for cleanliness and overall condition RECORD INDOOR BLOWER MOTOR FLA Record maximum blower motor amp draw TEST INDOOR BLOWER MOTOR AMPS Actually confirms indoor blower motor amp draw is within specifications CHECK INDOOR BLOWER START TIME Measures indoor blower start time delay relative to system start time, a of 60-180 seconds delay is preferred for the most efficient operation, also prevents hot air on cooling start up and insures warm air on heating start up. CHECK INDOOR BLOWER OFF TIME Measures blower off time delay. Indoor blower motor off time delay of 60-135 seconds is preferred to allow all the cool or hot air to be removed from the air conditioner or heater and put it in your home on shut down. RECORD INDUCER FLA Record maximum inducer motor amp CHECK INDUCER AMP. Test inducer amps, actually confirms amp draw is within specifications CHECK INDUCER ASSEMBLY Confirm proper operation and overall condition TEST DRAFT PRESSURE SWITCHES Confirm proper trip pressure, insures safe operation CHECK THERMOSTAT Confirm operation and calibration of thermostat ADJUST THERMOSTAT Adjust thermostat for proper operation CHECK GAS PRESSURE Used to confirm proper firing rate of furnace. Increases life span of furnace. CHECK GAS LINE Confirm proper installation and confirm there are no leaks ADJUST GAS AIR MIXTURE Adjust gas air mixture for proper operation, allows you to get all the heat out of the gas you buy and increases life of furnace CHECK FURNACE FLUE Confirm proper sizing, condition and overall operation of flue CHECK TEMPERATURE RISE Confirms proper air flow. Prevents overheating of heat exchanger which increases life of heat exchanger CHECK GAS VALVE Confirm proper operation and check for gas leakage CHECK LIMIT SWITCHES Confirm proper operation and proper trip temperatures CHECK CONTROL BOARD CHECK DUCT WORK Confirm overall cognition, proper strapping and proper sizing of duct system; confirm proper seal of all ducts CHECK SUPPLY AND RETURN AIR PLENUM Confirm proper installation and air seal of supply and return air plenums CHECK COMPRESSOR FLA HEAT PUMP ONLY A/C & heat pump only record maximum compressor electric draw as it is the largest consumer of electricity in your air conditioner. TEST COMPRESSOR AMPS HEAT PUMP ONLY A/C & heat pump only actually confirms the amp draw is within specifications, test for proper electrical operation CHECK OUTDOOR COIL HEAT PUMP ONLY Inspect for cleanliness and overall condition RECORD OUTDOOR FAN MOTOR FLA HEAT PUMP ONLY A/C & heat pump only. Record maximum outdoor fan motor amp draw CHECK OUTDOOR FAN MOTOR AMPS HEAT PUMP ONLY A/C & heat pump only. Test motor amps, actually confirms amp draw is within specifications CHECK OUTDOOR MOTOR HEAT PUMP ONLY Inspect condenser motor shaft seal and bearing wear CHECK OUTDOOR FAN BLADE HEAT PUMP ONLY Inspect condenser fan blade to confirm true and balanced operation If you have any questions or concerns about our tune-up service, call us at 916-722-8300. We will gladly provide the additional information you require. © 2021 Pro-Air Inc. P O Box 2106 Citrus Heights, CA 95611 Tel: 916-722-8300 | Fax: 916-722-7647 E-Mail: shermproair@surewest.net