(812) 612-15-09, (812) 612-25-29 Saint-Petersburg st. Communy, 67 About company Write to us Our address Photo gallery news Articles Industrial fans Radial fans Smoke extraction fans Roof fans Axial fans Axial fan VO 06-300 Fan VO 06-300 Fan ВС 10-400 Fan VO 30-160 Fan VO 13-284 Fan VKOPv 25-188 Fan VKOPv 30-160 Fan VO 25-188 Duct fans VKK Household fans VK8 UHL4.2 "SAMAL" Steel air ducts Industrial pumps Electric motors Heating equipment Transformers Smoke exhauster Heat exchange equipment Metalworking Cooling towers A frequency converter Thermal curtains Our advantages Discounted goods Photo gallery go to photo gallery All news news 02.10.2015 Industrial equipment available 01.09.2015 Dear Customers! We inform you about the collective leave of employees of LLC "Gidroelektromontazh" from 09/11/15 to 09/23/15. 07/17/2015 All duct fans are available Models of duct fans in the warehouse VKK100 according to VKK315 Home / Industrial fans / Axial fans / Axial fan VO 06-300 Axial fan VO 06-300 VO 06-300 No. 3.15; VO 06-300 No. 4; VO 06-300 No. 5 VO 06-300 No. 6.3; VO 06-300 No. 8; VO 06-300 No. 10 VO 06-300 No. 12.5 Purpose of the product Axial fan VO 06-300 is used where it is necessary to supply a large amount of air with low and medium aerodynamic resistance. Exhaust ventilation with axial fans, including VO 06-300, is widely used in industrial, agricultural and other buildings - when it is necessary to make exhaust ventilation in rooms in the most common way. Axial fans are designed to move non-explosive gas environments with a temperature not exceeding 60 C °, containing solid impurities not exceeding 100 mg / m3. Axial fan VO 06-300 (VO 14-320) is made of carbon steel, from dissimilar materials - explosion-proof and from aluminum alloys. Axial fans are the main component of heating units - AO-2 (information can be obtained in the section heaters and heating units). Principle of operation: air from the room is taken by an axial fan, then it is supplied to the heater, where it is heated and exits the unit. The desired air flow direction is achieved with a multi-leaf valve. The units can be installed on the floor of a building, suspended on a column, or placed behind the ceiling. The initial temperature of the air at the outlet depends on the air speed and the temperature of the coolant and ranges from 40-60 degrees Celsius. Промышленные вентиляторы типа АО2 имеют хорошую теплопроизводительность и демонстрируют высокую эффективность. Все эти промышленные вентиляторы качества показывают за счет оптимального расстояния между калорифером и вентилятором. Это исключает зоны застоя в процессе движения воздуха в агрегате. Технические характеристики Табл. Технические характеристики вентиляторов ВО 06-300. № вент. Электродвигатель Параметры в раб. зоне Масса, кг Типоразмер Мощность, кВт Частота вращения, мин-1 Производи-тельность, 103 м3/ч Полное давление, Па 4 АИР56А4 0,12 1500 2,0-3,2 90-25 13,3 АИР63А4 0,25 1500 2,0-3,2 90-25 16,1 5 АИР63В4 0,37 1500 4,8-7,1 128-62 22,0 АИР71А4 0,55 1500 4,8-7,1 128-62 24,4 6,3 АИР80А4 1,1 1500 9,6-15,0 213-110 34 АИР80А6 0,75 1000 6,4-10,05 96-50 34 8 4АМ80А6 0,75 920 13,9-18,3 121-81 67,5 4АМ100S4 3,0 1420 21,4-28,2 296-1293 86 10 4АМ112МА6 3,0 950 28,0-36,9 207-136 146 12,5 4АМ132S8 4,0 720 41,4-54,5 186-122 207 Габаритные и присоединительные размеры Таб. Габаритные и присоединительные размеры ВО 06-300. вент. Размеры, мм D D1 D2 D3 A C B E Fmax H d d1 n 3,15 315 318 350 375 270 300 100 125 275 200 7 12 8 4 400 405 435 460 350 380 110 160 323 260 7 12 8 5 500 510 535 560 450 480 150 200 333 310 7 12 16 6,3 630 640 665 690 550 580 200 250 390 375 7 12 16 8 800 820 850 880 750 800 250 320 437 495 10 16 16 10 1000 1006 1040 1080 900 950 330 400 570 595 12 16 16 12,5 1250 1270 1310 1345 1100 1150 400 500 609 725 12 16 24 Табл. Акустические характеристики вентиляторов ВО-06-300. № вен. n, мин-1 Значение Lpl, дБ в октавных полосах f, Гц Lpa, дБА 63 125 250 500 1000 2000 4000 8000 4 1500 73 80 78 78 74 68 61 55 84 5 1500 84 85 85 84 81 75 67 60 90 6,3 1000 82,5 83 85 85 81 75 68 61 90 1500 91,5 92 94 94 90 84 77 70 99 8 920 91 93 94 95 91 86 76 71 100 1420 100 102 103 104 100 95 85 80 109 10 950 99 101 102 103 99 94 84 79 108 12,5 720 100 102 103 104 100 95 85 80 109 Acoustic performance measured on the discharge side at nominal fan operation. On the suction side, the sound power levels are 3 dB lower than those given in the table. At the boundaries of the working area, the aerodynamic sound power levels are 3 dB higher than the sound power level corresponding to the nominal fan operating mode. © 2009 - 2015 LLC Gidroelektromontazh . All rights reserved. Phone: (812) 612-15-09, (812) 612-25-29; E-mail: gidro2000@yandex.ru Creation of a corporate website - HEIKA