Main Page Catalogue Hydronic radiant heating solutions Heating manifolds HKV PnG with quick connector Heating circuit manifold HKV PnG Pro with push-fit connector end pieces Heating circuit manifold HKV PnG Pro with push-fit connector end pieces Description Technical Features Part no. Downloads Related products Ask a question Description Stainless steel round pipe manifold according to DIN EN 1264-4. Flat-sealing 1" male connection on both sides for manifold accessories and manifold control station. Pre-assembled Push'n'Go connectors on outlets for connection of Ø 16 mm PEX pipe according to DIN EN ISO 15875-2 or PERT pipe (Important: not suitable for connecting to aluminium composite pipes). Centre distance of the outlets 50 mm. Ready-mounted on wall bracket, pipe clamps sound-insulated according to DIN 4109. Supply (top): Shut-off flow meter with very low pressure loss. Flow rate display 0-4 l/min. Return (bottom): regulating and shut-off valves with adaptation M30 x 1.5. Closing dimension 11.8 mm. Scope of delivery: Manifold complete with ball valves KH-SET WMZ and end pieces ES-SET Quattro 1". Technical Features Max. operating pressure: 6 bar Medium temperature: 5 to 55° C Media: Water or water with glycol as per VDI 2035 Connection to the primary circuit and end set: G 1" male thread Heating circuit connection: Ø 16 PE-X pipe in accordance with DIN EN ISO 15875-2 or PER-T pipe (not suitable for connecting to aluminium composite pipes) Connection for actuator: M30 x 1.5 / closing point 11.8 mm / stroke 2.5 mm Manifold: Stainless steel 1.4301 Part no. Typ Part no. HKV 0-4 1" VA PnG Pro 02 10084890 for 2 heating circuits HKV 0-4 1" VA PnG Pro 03 10084891 for 3 heating circuits HKV 0-4 1" VA PnG Pro 04 10084892 for 4 heating circuits HKV 0-4 1" VA PnG Pro 05 10084893 for 5 heating circuits HKV 0-4 1" VA PnG Pro 06 10084894 for 6 heating circuits HKV 0-4 1" VA PnG Pro 07 10084895 for 7 heating circuits HKV 0-4 1" VA PnG Pro 08 10084896 for 8 heating circuits HKV 0-4 1" VA PnG Pro 09 10084897 for 9 heating circuits HKV 0-4 1" VA PnG Pro 10 10084898 for 10 heating circuits HKV 0-4 1" VA PnG Pro 11 10084899 for 11 heating circuits HKV 0-4 1" VA PnG Pro 12 10084900 for 12 heating circuits Downloads LEAFLETS & DATA SHEET USER MANUAL Related products used in conjunction with ISOMIX - F ready-to-mount control unit Electrothermic actuator 22CX Manifold insulation for HKV ‹ › similar or alternative products Stainless Steel Manifold HKV2013AF+ with Flow Meters for Underfloor Heating equipped with end set and ball valve set Watts Water Technologies EMEA B.V. is the European Holding of Watts Water Technologies Inc. SITEMAP Products Solutions Case Studies Downloads Company LEGAL Legal Notices Terms of USE Data Privacy Policy Disclaimer General Terms and Conditions FOLLOW US YouTube Facebook LinkedIn ©2021 Watts Water Technologies EMEA Region: Europe Developed by Media Army Cookie Control Your choice regarding cookies on this site We use cookies to optimise site functionality and give you the best possible experience. By clicking on “I Accept”, you accept the use of cookies. You can refuse the use of cookies or adjust them in the “Settings”. For more information please read our Privacy Statement. I AcceptSettings