PUMP PORTAL® LOGIN Contact us: 888.733.9283 PRODUCTS CUSTOM SOLUTIONS PUMP PORTAL® SERVICE COMPANY RESOURCES MEDIA CONTACT US THREE PHASE DUPLEX DEMAND WD3P-4 PUMP CONTROL PANEL PRODUCTS PUMP PANELS LITERATURE Engineering Specifications Catalog Installation WD3P-4-(3021-3030) WD3P-4-(3031-3033) WD3P-4-3034 The WS Series® duplex control panels will control two 208/240/480V three phase pumps designed for dewatering, wastewater, and sewage applications. See Water duplex control panels come standard with a clear front NEMA 4X rated enclosure, IEC rated contactors, and motor protective switches. All panels are UL listed for the United States and Canada and come standard with a five-year warranty. REQUEST A QUOTE Model Voltage Full Load Amps WD3P-4-3021 208/240/480 1.0-1.6 WD3P-4-3022 208/240/480 1.6-2.5 WD3P-4-3023 208/240/480 2.5-4.0 WD3P-4-3024 208/240/480 4.0-6.3 WD3P-4-3025 208/240/480 6.0-10.0 WD3P-4-3026 208/240/480 9.0-14.0 WD3P-4-3027 208/240/480 13.0-18.0 WD3P-4-3028 208/240/480 17.0-23.0 WD3P-4-3029 208/240/480 20.0-25.0 WD3P-4-3030 208/240/480 24.0-32.0 WD3P-4-3031 208/240/480 30.0-40.0 WD3P-4-3032 208/240/480 37.0-50.0 WD3P-4-3033 208/240/480 48.0-65.0 WD3P-4-3034 208/240/480 65.0-115.0 Add Pump Portal® remote pump monitoring to this control panel! LEARN MORE Features UL listed for the United States and Canada (panel and controls) Indoor/Outdoor NEMA 4X rated enclosure: Heavy duty polycarbonate with stainless steel lockable latches Duplex provides: Two-pump alternation and high demand two-pump operation Pump control visible indicators: Pump #1 and #2 hand-off-auto (H.O.A.) switch, green Pump Run lights, red Pump Fault lights with reset button, and Power On light Alarm visible indicators: Red beacon alarm light, alarm test and silence buttons Alarm horn sounds at 85 decibels at 10 feet Remote monitoring dry contacts: High Liquid, Pump Run(s), Pump #1 Fault, and Pump #2 Fault Upgraded pump protection: Motor protective switches included for both pumps (branch circuit protection, adjustable overload and disconnect) and thermal cutout with indicators Applications Sewage pump chambers Grinder pumps Sump pump basins Lift stations Custom Options 24 = Pump Exerciser 28 = Power On Dry Contact (Normally Open) 3R = Painted Steel Enclosure AF = Alarm Flasher AH = Anti Condensation Heater C = Additional Cord Length Per Foot Per Component* CCD = Cycle Counter w/ LCD Display and Reset CO = Convenience Outlet (User to supply 120 VAC) D1 = 120V Dry Contacts ETD = Elapsed Time Meter w/ LCD Display and Reset GR = Generator Receptacle, Includes Transfer Switch ISD = Intrinsically Safe LAD/LAW = Lightning Secondary Surge Arrestor (LAD Delta / LAW Wye) LL = Low Level Alarm MD = Main Disconnect; Up to 100 FLA MD2 = Main Disconnect; 100 to 230 FLA PM = Phase Monitoring PX = Pump Portal® Wireless Remote Communication SFD = Seal Failure Circuit w/ Indicator Lights S3 = No Floats Option SS4 = Upgraded Enclosure (304 Stainless Steel) SS6 = Upgraded Enclosure (316 Stainless Steel) *Additional cord length greater than 20’: Specify after C. Example: (WD3P-4-3021-C50) Indicates 50’ cord lengths for all floats. 22220 Opportunity Way Suite 101, Riverside CA, 92518 Phone: 951.487.8073 NEWSLETTER SIGN UP ©2021 See Water Inc. - All Rights Reserved.