+34 93 586 21 68 +34 93 586 21 69 Languages LOW VOLTAGE CABLES MEDIUM VOLTAGE CABLES ABOUT CONTACT X-VOLT RHZ1 6,35/11kV AL OVERVIEW SPECIFICATIONS TECHNICAL & SALES SUPPORT Aluminium Medium Voltage cable, XLPE insulation, halogen free, in triplex formation. X-VOLT RHZ1 6,35/11kV Aluminium cables for transmission and distribution of electricity in a medium voltage network in triplex formation. Halogen free. X-VOLT RHZ1 6,35/11kV AL cable performance Electrical performance MEDIUM VOLTAGE: 6,35/11 kV. Standard BS 7870-4.10 / IEC 60502-2. Thermal performance Maximum service temperature: 90ºC. Maximum short-circuit temperature: 250ºC (max. 5 s). Minimum service temperature: -15ºC Fire performance Halogen free: based on UNE-EN 50267. Mechanical performance Minimum bending radius: x15 cable diameter. Installation conditions Open Air. Buried. In conduit. Applications Distribution networks. Other Meter by meter marking. X-VOLT RHZ1 6,35/11kV AL cable design Conductor Aluminium conductor, class 2, based on EN 60228 and IEC 60228. Internal semiconductor Screen over the conductor, made of thermosetting semiconductor material. Insulation Cross-linked polyethylene (XLPE), in dry atmosphere catenary tube, through a triple layer extrusion process. External semiconductor Screen over the insulation, made of thermosetting non-strippable semiconductor material. Metallic screen Screen of copper wires and copper tape, applied over the outer semiconductirng layer, with a minimum cross-section of 32mm2. Longitudinal sealing Hygroscopic tape applied over the metallic screen. Outer sheath External sheath of halogen-free polyolefin, red colour. Assembly of single-core cables Three stranded single-core cables in triplex formation. DOWNLOAD CABLE DATASHEET MEDIUM VOLTAGE 6,35/11 kV. Halogen free: based on UNE-EN 50267. Maximum service temperature: 90ºC. Distribution networks. BS 7870-4.10 / IEC 60502-2. Technology 1. Conductor Aluminium conductor, class 2, based on EN 60228 and IEC 60228. 2. Internal semiconductor Screen over the conductor, made of thermosetting semiconductor material. 3. Insulation Cross-linked polyethylene (XLPE), in dry atmosphere catenary tube, through a triple layer extrusion process. 4. External semiconductor Screen over the insulation, made of thermosetting non-strippable semiconductor material. 5. Metallic screen Screen of copper wires and copper tape, applied over the outer semiconductirng layer, with a minimum cross-section of 32mm2. 6. Longitudinal sealing Hygroscopic tape applied over the metallic screen. 7. Outer sheath External sheath of halogen-free polyolefin, red colour. 8. Assembly of single-core cables Three stranded single-core cables in triplex formation. Other cables with similar properties X-VOLT RHZ1 Aluminium or Copper Medium Voltage cable, XLPE insulation, halogen free. TECHNICAL & SALES SUPPORT If you have any questions, please contact us. We’ll do our best to help. Select your country * Afghanistan Albania Algeria Andorra Angola Argentina Armenia Australia Austria Azerbaijan Bahamas Bahrain Bangladesh Barbados Belarus Belgium Belize Benin Bhutan Bolivia Bosnia Botswana Brazil Brunei Bulgaria Burkina Faso Burundi Cambodia Cameroon Canada Central African Republic Chad Chile China Colombia Congo Congo, Dem. Rep. Costa Rica Croatia Cuba Cyprus Denmark Djibouti Dominican Republic Ecuador Egypt El Salvador Equatorial Guinea Eritrea Estonia Ethiopia Finland France French Guiana Gabon Gambia Georgia Germany Ghana Greece Guatemala Guinea Guinea-Bissau Guyana Haiti Honduras Hong-Kong Hungary Iceland India Indonesia Iran Iraq Ireland Israel Italy Ivory Coast Jamaica Japan Jordan Kazakhstan Kenya Kuwait Kyrgyzstan Laos Latvia Lebanon Liberia Libya Liechtenstein Lithuania Luxembourg Macedonia Madagascar Malawi Malaysia Mali Malta Mauritania Mexico Moldova Monaco Mongolia Montenegro Morocco Mozambique Myanmar Namibia Nepal Netherlands New Zealand Nicaragua Niger Nigeria North Korea Norway Oman Pakistan Panama Papua New Guinea Paraguay Peru Philippines Poland Portugal Puerto Rico Qatar Rep. Czech Romania Rusia Rwanda Saudi Arabia Senegal Serbia Sierra Leone Singapore Slovakia Slovenia Somalia South Africa South Korea Spain Sri Lanka Sudan Suriname Sweden Switzerland Syria Tadzhikistan Taiwan Tanzania Thailand Timor-Leste Togo Tunis Turkey Turkmenistan Uganda Ukraine United Arab Emirates United Kingdom United States Uruguay Uzbekistan Venezuela Vietnam Western Sahara Yemen Zambia Zimbabwe Activity* Cable Distributor Cable Installer Contractor Other Student Do you need us to contact you?* Yes No I accept the privacy policy* LOW VOLTAGE CABLES RUBBER CABLES PANEL WIRE CABLES XLPE/PVC POWER CABLES XLPE LSOH SAFETY CABLES CONTROL & SCREENED CABLES SOLAR CABLES LOW VOLTAGE SPECIAL CABLES MARINE CABLES MEDIUM VOLTAGE CABLES RHZ1 HEPRZ1 RHVHMVH TYPES OF CABLES ABOUT CONTACT BLOG RESOURCES LINKEDIN Legacy & Privacy Cookie Policy Top Cable 2021 © All rights reserved Notice We and selected third parties use cookies or similar technologies as specified in the cookie policy. In case of sale of your personal information, you may opt out by using the link "Do Not Sell My Personal Information". To find out more about the categories of personal information collected and the purposes for which such information will be used, please refer to our privacy policy. Learn more and customize Reject Accept