"Since 1952, the best products and tools for non-destructive testing" HOME WHO WE ARE PRODUCTS DOCUMENTS CONTACTS English LEAK DETECTION DESIGNATION ASTM E 515-95 BUBBLE TEST GAS PROOF CERCAFUG Gas leak detection system. Gas leaks both for civil use (eg Methane) and for technical-industrial use (eg Oxygen, Butan-propane, Nitrogen, Hydrogen, Argon, etc.) constitute a serious danger and a considerable cost for dispersions in the atmosphere, as well as a cause of pollution such as ozone-depleting gases contained in refrigeration systems. The most effective, simple and economical way to detect and eliminate GAS leaks is to apply the GAS PROOF foaming solution on the suspicious parts. A mushroom of very small foam bubbles will indicate the area of the leak. GAS PROOF does notit is a soap, but a safe technical product (it can also be used on oxygen) and very sensitive (it detects leaks up to 4.5 x 10 -10 mol / s = 1 x 10 -5 Std cm³ / s). Dilute the GAS PROOF paste (Code 14.100 GP1KG) at 0.3 / 0.5% in water and apply with a brush to the parts to be inspected with pressure from 0.01 to 0.1 MPa. Use the spray pack (Code 14.111 GPKSP) for greater ease of use. Approved according to DIN 2470 in the construction of gas pipes. It can be used on all junction parts, taps, valves, pressure gauges, cylinders, coils, to check the quality of the welds even on plastic pipes. 14.100 GP1KG - 1 KG CONCENTRATED PROOF GAS for 200/400 L of water 14.111 GPKSP - 400 ml GAS PROOF SPRAY VACUUM BOX SET WITH PUMP Code 14.120 SVPB. The VACUUM BOX equipment becomes indispensable when it is not possible to create a differential pressure on the side opposite to where the GAS PROOF leak detector is applied. The transparent VACUUM BOX boxes adhere by vacuum to the part to be examined previously wetted with GAS PROOF, revealing any leaks. The set consists of PUMP - Code 14.190 PVB For dry vacuum - Weight kg. 9 - 230V power supply with ON / OF switch, for continuous service. Flow rate 60 L / min. CASSETTA PER SALDATURE PIANE - Codice 14.140 VB1 In metacrilato trasparente rinforzato. Completa di guarnizione, portagomma e vuotometro tarato. Dimensioni cm. 50x10x7 interno. CASSETTA PER SALDATURE D'ANGOLO A 90° - Codice 14.150 VB2 In metacrilato trasparente rinforzato. Completa di guarnizione, portagomma e vuotometro tarato. Dimensioni cm. 35x10x7 interno. Guarnizione per vacuum box - Codice 14.160 GVB Guarnizione perimetrale di tenuta della cassetta con la superficie; mt. 2 (lunghezze maggiori a richiesta). TUBO PER VUOTO PER VACUUM BOX - Codice 14.170 TVVB Per collegamento con la pompa; mt. 10 (lunghezze maggiori a richiesta). N. 1 SPECIFICA TECNICA DI PROCEDIMENTO CON VACUUM BOX Oppure in alternativa: VACUUM BOX SET CON EIETTORE PER VUOTO Codice 14.130 SVBE Da utilizzare quando non è possibile usare pompe per vuoto elettriche. Entrambe le cassette per saldature piane e d'angolo sono dotate di EIETTORE (generatore di vuoto a tubo Venturi) da collegare ad una linea di aria compressa o ad un compressore (non fornito). 14.230 LAB416 ADDITIVI Il LAB A416 è un additivo per prove di tenuta idraulica. Segnala i difetti passanti con tracce brillanti fluorescenti giallo-blu sotto luce ultravioletta. In più il LAB 416 abbassa la tensione superficiale ed aumenta la capacità di penetrazione dell'acqua. MAGGIORI INFORMAZIONI NDT ITALIANA srl Via del Lavoro, 28 - 20863 Concorezzo - (MB) ITALY Tel (+39) 039.647590 - Fax (+39) 039.647799 - info@ndt.it p.iva IT01013410152 | privacy REV.2 NDT ITALIANA is UNI EN ISO 9001 certified