Clean Water Man, Inc. 203-313-8291 Water Treatment Experts Serving Connecticut Home Service Water Treatment Systems Blog Contact Us Blue Frog E1 Water Softeners E1 Water Softener E1 Controller Blue Frog E1 Softeners (No Longer Sold, But Kept Here So You Can Find The Online Manual) Soft water makes your skin and hair feel better and soft water will make water using appliances work efficient and last longer. Soft water can also improve the efficiency of your water heater by 20% which will save you energy and money. With our exclusive E1 controller, the E1 Water Softeners are rugged and efficient. Easy to program with an intuitive menu. Control surfaces are made of sapphire ceramic to resist wear, scratching, and corrosion. Available in 24,000 grain, 32,000 grain and 48,000 grain sizes and custom sizes for special installation considerations. Our online manual for this controller is here, (individual installations may vary): F79-B & F82-B Manual 9-29-11 Recent Posts Award winning service and installations! Recent Comments admin on Blog Archives January 2014 Categories Uncategorized Meta Log in Entries feed Comments feed WordPress.org Wordpress theme built with Lubith

Clean Water Man, Inc. 203-313-8291 Water Treatment Experts Serving Connecticut Home Service Water Treatment Systems Blog Contact Us Low Pressure After Power Outage Low Pressure After Power Outage Dear Clean Water Man:The other day, our power went out for several hours and ever since we have had very low water pressure. What is going on?Sincerely,Trickles, Greenwich, Connecticut Dear Trickles:After I met with you and inspected your water system, I repaired the problem. I wanted to post here so that my readers could know what happened. Your water system consisted of a submersible pump, a Well-X-Trol bladder tank, a backwashing aggregate filter, and a water softener. Here is what happened: The power went out but your family continued to use water. The Well-X-Trol tank has several gallons of water stored within the air pressurized bladder and is generally enough for a few toilet flushes or turning on other fixtures. As the water emptied out of the bladder tank, a great amount of iron sludge came off of the inside of the bladder and entered the aggregate filter. While this filter is designed to remove this precipitated iron, the huge amount of sludgy iron clogged the filter and all it needed was a few extra backwashes, which I took care of while I was at your home. The pressure improved after the manual backwashes. The best approach is to stop using water when the power goes off so to prevent this fouling of the filtration system. Water problems in Connecticut? Call Ted Mullen, of Clean Water Man, Inc. at 203-417-9601. Recent Posts Award winning service and installations! Recent Comments admin on Blog Archives January 2014 Categories Uncategorized Meta Log in Entries feed Comments feed WordPress.org Wordpress theme built with Lubith