Follow @Gomax HOME PRODUCTS DOWNLOAD DISTRIBUTORS ABOUT US NEWS INFINITY Gomax® > Products > INFINITY INFINITY is the range of assembled hoses for air conditioning and refrigeration. It is the flexible thermoplastic system that fits any circuit. It is assembled with two types of combinable fittings: brazing fitting with heat dissipator and Rotalock fitting. The INFINITY system offers an absolutely innovative solution for air conditioning and refrigeration systems. With just one flexible piece you can now connect the compressor directly to the condenser or the evaporator without any intermediate solderings. Performance and condition of use Working pressure Burst pressure Working temperature WP BP WT – °C WT – °F maximum working pressure minimum bursting pressure allowable temperature bar MPa psi bar MPa psi min max min max 50 5,0 724 250 25 3620 -45 +110 -49 +230 Permitted Fluids ^ to top Type of Gas Type of Oil HFC (R134a, R404A, R407A, R407B, R407C, R410A, R507) polyol ester based HCFC (R22) mineral oils CO2 polyol ester based Classification according to Directive 97/23/CE ^ to top DN Classification 15 – 21 – 28 paragraph 3 article 3 38 – 54 category I (marking ) Pressure drop and permeability ^ to top DN Pressure Drop (bar/m) Permeability at 100°C (g/year) 10 m3/h 20 m3/h 50 m3/h 100 m3/h R134a R407C 15 0,0318 0,1275 52 73 21 0,0059 0,0237 70 97 28 0,0056 0,0348 89 123 38 0,0076 0,0304 78 110 54 0,0053 0,0014 112 156 The permeability value provides an indication of the maximum Ieakage tested at constant conditions of use of the hose at 100°C / 212°F for an entire year. The real permeability value must therefore be measured considering the actual working time and temperatures to which the hose is subjected, keeping in mind that significant and detectable values are obtained with temperatures of more than 50°C /122 °F and that the permeability increases proportionally to the temperature. The permeability values obtained at 100°C / 212°F for the GOMAX hose range, of approximately 1 kg/m2/year, are much lower than those set in the standard UNI EN 1736, which foresees a maximum permeability value of 5 kg/m2/year. Infinity hose fittings ^ to top brazing fittings with heat dissipator radiator Material Used Surface Coupling process Filter material drawn steel zinc plating hard brazing silver alloy with low melting point Rotalock ^ to top Material Used Surface Coupling process Filter material drawn steel zinc plating screw-on none Inner tube Thermoplastic polymer Reinforcement Polyester braid of high tensile strength with high modulus. Cover Black polyester braid of high textile strength, abrasion resistant Features Lightweight – Compact design – High flexibility – Vibration absorber Temperature range -45 °C to +110 °C (-49 °F to +230 °F) QUADRA ZERO INFINITY Brazing Fittings Rotalock Fittings Brazing/Rotalock Fittings Attachment GOMAX® - Hose installation factors GOMAX® - Avvertenza installazione tubi INFINITY™ - General information INFINITY™ - Conformity declaration Pages Home Location Contacts Download Distributors News QUADRA DN2 QUADRA DN4 QUADRA DN6 ZERO INFINITY Latest news Chillventa 2018 open its gates GOMAX @ Chillventa 2018 – Hall 6 – Stand 139 QUADRA – UL/CSA certification Thank you for Visiting GOMAX @ CHILLVENTA Chillventa 2016 open its gates Follow GOMAX® RSS Linkedin Youtube GOMAX® a brand of Transfer Oil S.p.A. Via Sacca, 64 43052 - Colorno (Parma) - Italy ph. +39 0521 3139 fax +39 0521 814160 info@transferoil.com VAT and business register of parma: IT02306450343 - share capital: EUR 2.500.000 fully paid-up General Sales Conditions GOMAX® - Hose installation factors GOMAX® - Avvertenza installazione tubi © Copyright Privacy This website makes use of cookies. Cookies are necessary for a correct navigation. By clicking Accept button You agree to our use of cookies. Accept Read More