English EN 50588 Um=36kV Insulation Class 36kV EU Regulation 548/2014 European Standard EN 50588-1 Ucc 6,5% Loss Tolerance +0% Rated Performance Class Losses Power EU548 EN50588-1 Po Pk lo LwA a1 b1 h1 e Ø t Mass Term Encl kVA W W % dB(A) mm mm mm mm mm mm Kg Type Type 50 Tier 1 Ao Bk 230 1870 2,5 49 1500 600 1600 520 125 40 1100 A 7 – Ao Ak 230 1650 2,5 49 1500 600 1600 520 125 40 1100 A 7 Tier 2 AAo Ak 200 1650 2,3 48 1500 600 1600 520 125 40 1100 A 7 100 Tier 1 Ao Bk 320 2250 2,3 51 1550 600 1600 520 125 40 1300 A 7 – Ao Ak 320 1980 2,3 51 1550 600 1600 520 125 40 1300 A 7 Tier 2 AAo Ak 280 1980 2,1 50 1500 600 1600 520 125 40 1300 A 7 150 Tier 1 Ao Bk 430 3020 2,0 54 1700 600 1600 520 125 40 1500 A 7 – Ao Ak 430 2700 2,0 54 1700 600 1600 520 125 40 1500 A 7 Tier 2 AAo Ak 390 2700 1,9 53 1700 600 1600 520 125 40 1500 A 7 160 Tier 1 Ao Bk 460 3190 2,0 54 1700 600 1600 520 125 40 1600 A 7 – Ao Ak 460 2860 2,0 54 1700 600 1600 520 125 40 1600 A 7 Tier 2 AAo Ak 410 2860 1,9 53 1700 600 1600 520 125 40 1600 A 7 200 Tier 1 Ao Bk 510 3630 1,8 55 1750 600 1700 520 125 40 1800 B 7 – Ao Ak 510 3240 1,8 55 1750 600 1700 520 125 40 1800 B 7 Tier 2 AAo Ak 460 3240 1,7 54 1750 600 1700 520 125 40 1800 B 7 250 Tier 1 Ao Bk 590 4180 1,6 57 1750 600 1800 520 125 40 2000 B 7 – Ao Ak 590 3740 1,6 57 1750 600 1800 520 125 40 2000 B 7 Tier 2 AAo Ak 530 3740 1,5 56 1750 600 1800 520 125 40 2000 B 7 315 Tier 1 Ao Bk 700 4980 1,5 58 1800 750 1900 670 125 40 2400 B 8 – Ao Ak 700 4250 1,5 58 1800 750 1900 670 125 40 2400 B 8 Tier 2 AAo Ak 630 4250 1,4 57 1800 750 1900 670 125 40 2400 B 8 400 Tier 1 Ao Bk 860 6050 1,4 60 1800 750 2000 670 125 40 2600 B 8 – Ao Ak 860 4950 1,4 60 1800 750 2000 670 125 40 2600 B 8 Tier 2 AAo Ak 770 4950 1,3 59 1800 750 2000 670 125 40 2600 B 8 500 Tier 1 Ao Bk 1030 7050 1,3 61 1850 750 2050 670 125 40 2900 C 8 – Ao Ak 1030 6190 1,3 61 1850 750 2050 670 125 40 2900 C 8 Tier 2 AAo Ak 930 6190 1,2 60 1850 750 2050 670 125 40 2900 C 8 630 Tier 1 Ao Bk 1260 8360 1,3 62 1900 850 2100 670 125 40 3200 D 8 – Ao Ak 1260 7810 1,3 62 1900 850 2100 670 125 40 3200 D 8 Tier 2 AAo Ak 1130 7810 1,2 61 1900 850 2100 670 125 40 3200 D 8 750 Tier 1 Ao Ak 1420 8500 1,2 63 1900 850 2200 670 125 40 3600 E 8 Tier 2 AAo Ak 1270 8500 1,1 62 1900 850 2200 670 125 40 3600 E 8 800 Tier 1 Ao Ak 1490 8800 1,2 64 1900 850 2250 670 125 40 3800 E 8 Tier 2 AAo Ak 1340 8800 1,1 63 1900 850 2250 670 125 40 3800 E 8 1000 Tier 1 Ao Ak 1780 9900 1,1 65 2000 1000 2300 820 125 40 4300 F 9 Tier 2 AAo Ak 1600 9900 1,0 64 2000 1000 2300 820 125 40 4300 F 9 1250 Tier 1 Ao Ak 2070 12100 1,1 67 2100 1000 2450 820 160 50 5000 G 9 Tier 2 AAo Ak 1860 12100 1,0 66 2100 1000 2450 820 160 50 5000 G 9 1500 Tier 1 Ao Ak 2390 13660 1,0 68 2250 1000 2500 820 160 50 6100 H 10 Tier 2 AAo Ak 2150 13660 0,9 67 2250 1000 2500 820 160 50 6100 H 10 1600 Tier 1 Ao Ak 2530 14300 1,0 68 2250 1000 2500 820 160 50 6400 H 10 Tier 2 AAo Ak 2270 14300 0,9 67 2250 1000 2500 820 160 50 6400 H 10 2000 Tier 1 Ao Ak 2990 17600 1,0 70 2300 1310 2700 1070 200 70 7700 I 10 Tier 2 AAo Ak 2690 17600 0,9 69 2300 1310 2700 1070 200 70 7700 I 10 2500 Tier 1 Ao Ak 3560 20900 0,9 71 2400 1310 2750 1070 200 70 8600 J 10 Tier 2 AAo Ak 3200 20900 0,8 70 2400 1310 2750 1070 200 70 8600 J 10 3000 Tier 1 Ao Ak 4170 23430 0,8 73 2500 1310 2800 1070 200 70 9200 J 11 Tier 2 AAo Ak 3760 23430 0,7 72 2500 1310 2800 1070 200 70 9200 J 11 3150 Tier 1 Ao Ak 4370 24200 0,8 74 2600 1310 2800 1070 200 70 9400 J 11 Tier 2 AAo Ak 3930 24200 0,7 73 2600 1310 2800 1070 200 70 9400 J 11 Disclaimer: Dual voltage in one winding: The maximum level of losses can be increased by 15% for no load loss and by 10 % for load loss. Dual voltage in both windings: The maximum level of losses can be increased by 20% for no load loss and by 10 % for load loss. A B H e Mass Enclosure mm mm mm mm Kg Type Insulation Class 12 – 17,5 – 24 kV 1 1850 1100 1560 See transformer tables 150 2 1900 1100 1760 160 3 2050 1150 1960 180 4 2300 1250 2500 230 5 2500 1310 2650 250 6 2750 1400 2850 320 Insulation Class 36 kV 7 2400 1400 1960 See transformer tables 260 8 2600 1500 2500 300 9 2800 1500 2650 340 10 3000 1600 3000 400 11 3300 1700 3300 460 Standard Cast Resin Transformers General Information EN 50588 Um≤24kV EN 50588 Um=36kV EN 50541 Um≤12/28/75 kV EN 50541 Um=17,5/38/95 kV EN 50541 Um=24/50/125 kV EN 50541 25kV Um=36/70/145 kV EN 50541 Um=36/70/170 kV Standard Transformers Gallery Special Transformers Special Cast Resin Transformers Dry Type Transformers Oil Cooled Transformers Transformer Gallery Reactors Shunt Reactors Current Limiting Reactor Damping Reactors Reactors for Tuning Smoothing Reactors Neutral Earthing Reactors Reactor Gallery Transformers Manufacturing Company España S.A.U. Poligono Bildosola, Parcela B1 48142 Artea (Bizkaia) España Email: ventas@tmc.com.au Tel: +34 94 631 22 80 Fax: +34 94 631 45 24 Transformers Manufacturing Company Pty Ltd 19 Ewing Street Brunswick Melbourne Victoria 3056 Australia. Email: sales@tmc.com.au Tel: +61 3 9356 8700 Fax: +61 3 9356 8701 TMC TRANSFORMERS MANUFACTURING COMPANY © 2014 BY SIROPE