Home Solutions Products Experts Service DEHN Choose your country HOME _ CURRENT: DEHNVAP DEHNvap Prewired type 1 + type 2 spark-gap-based combined arrester, optimised for protecting mobile radio systems Maximum system availability thanks to Rapid Arc Control / RADAX Flow follow current limitation Discharge capacity up to 100 kA (10/350 µs) No tripping of 32 A gG fuses up to short-circuit currents of 25 kArms Protection of terminal devices within 10m Visual status indication integrated in the module (green = ok, red = faulty); status is signalled via remote signalling contact Different products tailored to the specific requirements of mobile radio systems DVA M NG 3P 100 FM 1 Product Part No. 900352 DVA M NG 3P 100 FM GTIN 4013364455931, Customs tariff No.: 85363090, Gross weight: 598.33 g, PU: 1.00 pc(s) Images Previous Slide Next Slide Additional information Specification sheets CAD files Tender specifications Instruction Certificates Technical data SPD according to EN 61643-11 / ... IEC 61643-11 type 1 + type 2 / class I + class II Max. continuous operating voltage (a.c.) [L-N]/[N-PE] (UC ) 255 V (50 / 60 Hz) Lightning impulse current (10/350 µs) [L1+L2+L3+N-PE] (Itotal ) 100 kA Specific energy [L1+L2+L3+N-PE] (W/R ) 2.50 MJ/ohms Lightning impulse current (10/350 µs) [L-N]/[N-PE] (Iimp ) 25 / 100 kA Specific energy [L-N]/[N-PE] (W/R ) 156.25 kJ/ohms / 2.50 MJ/ohms Nominal discharge current (8/20 µs) [L-N]/[N-PE] (In ) 25 / 100 kA Voltage protection level [L-N]/[N-PE] (UP ) ≤ 1.5 / ≤ 1.5 kV Approvals KEMA Accessory Add to Notepad DVA M NG 1P 50 FM 1 Product Part No. 900351 DVA M NG 1P 50 FM GTIN 4013364455948, Customs tariff No.: 85363090, Gross weight: 320.37 g, PU: 1.00 pc(s) Images Previous Slide Next Slide Certificates Technical data SPD according to EN 61643-11 / ... IEC 61643-11 type 1 + type 2 / class I + class II Max. continuous operating voltage (a.c.) [L-N]/[N-PE] (UC ) 255 V (50 / 60 Hz) Lightning impulse current (10/350 µs) [L+N-PE] (Itotal ) 50 kA Specific energy [L+N-PE] (W/R ) 625.00 kJ/ohms Lightning impulse current (10/350 µs) [L-N]/[N-PE] (Iimp ) 25 / 50 kA Specific energy [L-N]/[N-PE] (W/R ) 156.25 / 625.00 kJ/ohms Nominal discharge current (8/20 µs) [L-N]/[N-PE] (In ) 25 / 50 kA Voltage protection level [L-N]/[N-PE] (UP ) ≤ 1.5 / ≤ 1.5 kV Approvals KEMA Accessory Add to Notepad DVA CSP 3P 100 FM 1 Product Part No. 900360 DVA CSP 3P 100 FM GTIN 4013364111332, Customs tariff No.: 85363090, Gross weight: 1.34 kg, PU: 1.00 pc(s) Images Previous Slide Next Slide Certificates Technical data SPD according to EN 61643-11 / ... IEC 61643-11 type 1 + type 2 / class I + class II Max. continuous operating voltage (a.c.) [L-N]/[N-PE] (UC ) 264 V (50 / 60 Hz) Max. continuous operating voltage (a.c.) [N-PE] (UC (N-PE) ) 255 V (50 / 60 Hz) Lightning impulse current (10/350 µs) [L1+L2+L3+N-PE] (Itotal ) 100 kA Specific energy [L1+L2+L3+N-PE] (W/R ) 2.50 MJ/ohms Lightning impulse current (10/350 µs) [L-N]/[N-PE] (Iimp ) 25 / 100 kA Specific energy [L-N]/[N-PE] (W/R ) 156.25 kJ/ohms / 2.50 MJ/ohms Nominal discharge current (8/20 µs) (In ) 25 / 100 kA Voltage protection level [L-N]/[N-PE] (UP ) ≤ 1.5 kV / ≤ 1.5 kV Approvals KEMA Add to Notepad DVA CSP 3P 100 S FM 1 Product Part No. 900367 DVA CSP 3P 100 S FM GTIN 4013364322288, Customs tariff No.: 85363090, Gross weight: 529.00 g, PU: 1.00 pc(s) Images Previous Slide Next Slide Certificates Technical data SPD according to EN 61643-11 / ... IEC 61643-11 type 1 + type 2 / class I + class II Max. continuous operating voltage (a.c.) [L-N]/[N-PE] (UC ) 255 V (50 / 60 Hz) Lightning impulse current (10/350 µs) [L-N]/[N-PE] (Iimp ) 25 / 100 kA Specific energy [L-N]/[N-PE] (W/R ) 156.25 kJ/ohms / 2.50 MJ/ohms Nominal discharge current (8/20 µs) (In ) 25 / 100 kA Voltage protection level [L-N]/[N-PE] (UP ) ≤ 1.5 kV / ≤ 1.5 kV Approvals KEMA Accessory Add to Notepad DVA CSP 1P 50 S FM 1 Product Part No. 900366 DVA CSP 1P 50 S FM GTIN 4013364374669, Customs tariff No.: 85363090, Gross weight: 265.52 g, PU: 1.00 pc(s) Images Previous Slide Next Slide Certificates Technical data SPD according to EN 61643-11 / ... IEC 61643-11 type 1 + type 2 / class I + class II Max. continuous operating voltage (a.c.) [L-N]/[N-PE] (UC ) 255 V (50 / 60 Hz) Lightning impulse current (10/350 µs) [L-N]/[N-PE] (Iimp ) 25 / 50 kA Specific energy [L-N]/[N-PE] (W/R ) 156.25 kJ/ohms / 625.00 kJ/ohms Nominal discharge current (8/20 µs) (In ) 25 / 50 kA Voltage protection level [L-N]/[N-PE] (UP ) ≤ 1.5 kV / ≤ 1.5 kV Approvals KEMA Accessory Add to Notepad Contact Legal Notice Data Privacy Statement © DEHN SE + Co KG Follow us