IT EN DE FR HOME COMPANY PRODUCTS DOWNLOAD WHERE WE ARE CONTACTS GENERATING SETS FUELED BY METHANE GAS AND LPG Natural gas or LPG at 1500 rpm - Water cooling The range, fitted with natural gas and / or LPG engines, was created to respond to the increasingly demanding requests for respect for the environment. Choosing a generator of this range means decreasing emissions of harmful gases into the atmosphere compared to a diesel model, it means having a very low noise level and above all it means being able to connect to the public network, or to the cylinders and not having to always fill the generator set tank with fuel. Powers from 25 to 90 Kva; Water-cooled 1500 rpm General Motors engines; Applicable options such as soundproof booths, automatic intervention panels, slow towing trolleys or homologated for road circulation and engine pre-heating heaters. Template Continuous power Pot. In Emergency Engine type N. Cylinders Power [HP / KW] Displacement [cm 3 ] Consumption ¾ load [m3 / h] [KVA] [KW] [KVA] [KW] EY 25 NG 25 20 27.5 22 RMG3000 4 37.4 / 27.5 3000 8.5 EY 40 NG 40 32 44 35.2 RMG4300 6 58.4 / 42.9 4300 10.4 EY 50 NG 50 40 55 44 RMG5700 8 77.3 / 56.8 5700 15.6 EY 80 NG 80 64 88 70.4 RMG8000 8 112.9 / 83 7900 22.2 EY 90 NG 90 72 99 79 RMG9000 8 128.3 / 94.4 8850 23.2 Template Open Silenced Download PDF Weight [Kg] Dimensions L x LW x H [mm] Weight [Kg] Dimensions L x LW x H [mm] EY 25 NG 700 1500x900x1500 920 2200x1000x1500 EY 40 NG 880 1800x900x1500 1150 2200x1000x1500 EY 50 NG 1050 2000x1000x2250 1300 2200x1000x1800 EY 80 NG 1200 2200x1000x2250 1550 2600x1100x2000 EY 90 NG 1300 2200x1000x2250 1650 2600x1100x2000 Template Continuous power Pot. In Emergency Engine type N. Cylinders Power [HP / KW] Displacement [cm 3 ] Consumption ¾ load [L / h] [KVA] [KW] [KVA] [KW] EY 30 LPG 30 24 33 26.4 RMG3000 4 44.2 / 32.5 3000 11.9 EY 40 LPG 40 32 44 35.2 RMG4300 6 61.6 / 45.3 4300 16.4 EY 55 LPG 55 44 60.5 48.4 RMG5700 8 84 / 63.2 5700 21.2 EY 90 LPG 90 72 99 79.2 RMG8000 8 122 / 89.7 7900 30.1 EY 100 LPG 100 80 110 88 RMG9000 8 146.4 / 107.7 8850 31.5 Template Open Silenced Download PDF Weight [Kg] Dimensions L x LW x H [mm] Weight [Kg] Dimensions L x LW x H [mm] EY 30 LPG 700 1500x900x1500 920 2200x1000x1500 EY 40 LPG 880 1800x900x1500 1150 2200x1000x1500 EY 55 LPG 1050 2000x1000x2250 1300 2200x1000x1800 EY 90 LPG 1200 2200x1000x2250 1550 2600x1100x2000 EY 100 LPG 1300 2200x1000x2250 1650 2600x1100x2000 REQUEST A QUOTE Company Data | Privacy by Auxonet RESERVED AREA username password info@energy-gruppi.it +39 0444450422