TMA-EU OPEN CIRCUIT COOLING TOWER EVAPORATIVE COOLING TOWERS WITH AXIAL FANS TMA-EU series open circuit cooling towers are designed and manufactured by Decsa to best suit all plant applications where high efficiency and low operating cost are required cooling towers . Designed to optimise the L/G ratio within the unit, thus optimising the power input and reducing operating costs - the TMA-EU cooling water tower is now a benchmark in the global HVAC markets thanks to its best-in-class noise levels, together with low power consumption and low operating costs. The important thermodynamic performance certifications issued by both Eurovent and by Cooling Technology InstituteThe important certifications on thermodynamic performance issued by both the company and Decsa, together with the experience and professionalism gained by Decsa in over 45 years of history, confirm the reliability and quality of the TMA-EU cooling tower. Moreover, like the other Decsa products, also the TMA-EU series is built according to the quality standards of the ISO 9001 and ISO 14001 Quality System. TMA-EU OPEN CIRCUIT COOLING TOWER: TECHNICAL FEATURES Structure and panels Decsa made all open circuit cooling tower structures in Z-725 hot-dip galvanized steel sheet (725 g/sqm zinc coating). Panels are bolted and sealed for perfect water tightness, complete with one or more manholes for internal inspection. Cold water basin The TMA-EU series has a water basin (when supplied) in a hot-dip galvanized Z-725 steel sheet, complete with an anti-legionella sloped bottom to avoid water stagnation. The water basin of this open circuit cooling tower comprises a water outlet connection with an anti-vortex filter, a bleed-off and overflow connection, a make-up water connection complete with a float valve, reinforced PVC air inlet grilles, a bleed-off pipe. Heat Exchanger The TMA-EU cooling tower is equipped with the exclusive DecsaPACK (Onda 12) fill pack, made up of PVC sheets welded together and suitably shaped to optimise the turbulence of the fluids in counterflow and increase the efficiency of heat exchange. Onda 19, Splash or Tridimensional fill packs can be supplied depending on system requirements (more information on the most suitable fill pack read: Cooling towers fill packs) Fan section The TMA-EU series is equipped with the latest generation of axial fans with a balanced impeller, featuring stationary adjustable blades with a high efficiency aluminium or FRP airfoil. All types of axial fans can be directly connected to electric motors. Alternatively they can be connected to the electric motors by means of belts and pulleys or with angle drives. Low noise fans are available on request. Finishing The TMA-EU cooling tower can be protected with the special interior and exterior epoxy powder coating DecsaCOATING PLUS, available in all RAL colours. Highlight Materials Hot-dip galvanised steel sheet Z-725 Number of models 128 Capacity from 190 to 5700 kW OPEN CIRCUIT COOLING TOWER TMA-EU For all technical details, download the catalogue IDEAL FOR... HVAC E PROCESS COOLING Conceived for all types of air conditioning(HVAC) applications aiming at concrete savings in operating costs and guaranteeing high efficiency thermodynamic performance, the TMA-EU series open circuit cooling tower is made of Z-725 galvanised steel and designed for water cooling in civil and industrial applications. These cooling towers are therefore ideal for air conditioning applications in the hospital, commercial, industrial and service sectors. Low operating costs TMA-EU open cooling tower has low operating costs, partly because of the reduced energy consumption of the motors powering the axial fans. High resistance structure The evaporative tower has a structure equipped with Z-725 galvanised steel panels; the panels are bolted and sealed for perfect water tightness and complete with one or more watertight doors for internal inspection. Quick and easy maintenance The TMA-EU series guarantees very simple and fast maintenance of the moving parts; even the panels can be removed without the need for dedicated tools. ‍ Reduced transport costs All the TMA-EU open cooling towers allow for minimizing transport costs. Indeed, you can transport the sections on trucks or through standard containers (in case of transport by sea). Spare parts, maintenance and service for TMA-EU? Visit the Service page WEBINAR TMA-EU Cooling tower maintenance What ordinary maintenance activities should you carry out on the TMA-EU open circuit cooling tower? Here are the highlights of the webinar: Maintenance of an open circuit cooling tower Ordinary maintenance activities: 3 assembled sections Maintenance of the upper fan section Maintenance of the heat exchanger section Maintenance of the lower water basin section Read more: Cooling tower maintenance: guideline Decsa Srl Via Cappelletta 1 Voghera (PV) - Italy +39 0383 69411 P.I. IT08325980152 ABOUT US History R&D Design Construction details Operations Test area Sales Manufacturing Engineering Marketing Service Safety & Environment PRODUCTS Cooling towers open circuit Cooling towers closed circuit Evaporative condensers SOLUTIONS HVAC Process cooling Industrial refrigeration SERVICE CERTIFICATIONS ARCHIVE Catalogues Video News Spare parts FAQ Glossary CONTACT Privacy Policy Integrated Quality & Environment Policy General terms and conditions of sale General Terms and Conditions of Purchase European Regional Development Fund × Questo sito web utilizza cookie Questo sito web utilizza i cookie per migliorare la tua esperienza di navigazione. Utilizzando il nostro sito web acconsenti a tutti i cookie in conformità con la nostra policy per i cookie. Leggi di più STRETTAMENTE NECESSARI PERFORMANCE TARGETING FUNZIONALITÀ ACCETTA TUTTO RIFIUTA TUTTO MOSTRA DETTAGLI