Italian Log in or open an account Tecnoware Website Menu HOME CATALOG Professional line UPS UPS LINE INTERACTIVE UPS LINE INTERACTIVE RM UPS LINE INTERACTIVE SINUSOIDAL SINGLE-PHASE ONLINE UPS HE - HIGH EFFICIENCY ONLINE SINGLE-PHASE RM / RT HE UPS - HIGH EFFICIENCY THREE-PHASE ONLINE UPS HE - HIGH EFFICIENCY THREE-PHASE ONLINE UPS CSS (RESCUER IN COMPLIANCE WITH EN 50171) UPS FOR CABIN (CEI 0-16 COMPLIANT) ACCESSORIES FOR UPS LEAD SEALED BATTERIES INVERTER IT INFRASTRUCTURE RACK PANELS RACK CABINETS RACK CABINETS FOR SERVER PATCH PANEL FOR 19 "RACK PDU FOR 19 "RACK ACCESSORIES FOR RACK LAN CABLES EASY SERVICE LUBRICANTS CLEANERS Consumer Line UPS UPS LINE INTERACTIVE UPS LINE INTERACTIVE SINUSOIDAL ACCESSORIES FOR UPS SUPPLY SYSTEMS MOBILE POWER ADAPTER HD SERIES MOBILE POWER ADAPTER UNIVERSAL POWER ADAPTER HD SERIES UNIVERSAL POWER ADAPTER ALIMENTATORI PER PC MULTIPRESE CAVI USB LED LAMP EVOLUTION LAMPADA LED FILAMENTO LAMPADA LED ALADINO - LAMPADA GENIALE SERVIZI Cataloghi Configuratore rack Configuratore UPS SOFTWARE Registra UPS Richiedi connettori ASSISTENZA Richiesta RMA Verifica stato RMA NEWS CONTATTI Home Catalogo UPS UPS ONLINE MONOFASE HE - HIGH EFFICIENCY FGCEVDP6803MM UPS EVO DSP PLUS 6.8 MM HE - HIGH EFFICIENCY Codice prodotto:FGCEVDP6803MM Chiedi informazioni Caratteristiche: • Tecnologia On-Line Doppia Conversione senza trasformatore (VFI-SS-111) • Rectifier ad IGBT • Circuito PFC Attivo (0.99) • Compatibilità con gruppo elettrogeno • Tensione e frequenza di uscita impostabili dal pannello frontale • Bypass statico • Porte USB ed RS232 • Software UPS Management TecnoManager (WINDOWS, UNIX, LINUX, ecc.) Descrizione Documenti Garanzia UPS HE ALTA EFFICIENZA (94%) CALCOLATA IN MODALITÀ DOPPIA CONVERSIONE AL 100% DEL CARICO, SECONDO LA NORMATIVA 62040-3:2011. INGRESSO/USCITA MONOFASE 230/230 50/60HZ, POTENZA 6,8 KVA, COS 0,7, TECNOLOGIA ONLINE DOPPIA CONVERSIONE SENZA TRASFORMATORE, SISTEMA DSP (DIGITAL SIGNAL PROCESSOR), DISPLAY LCD GRAFICO MULTIFUNZIONE, AMPIA TOLLERANZA TENSIONE D'INGRESSO, SISTEMA DI RICARICA BATTERIE GESTITO A MICROPROCESSORE, BYPASS STATICO, PORTE DI COMUNICAZIONE USB ED RS232 PER IL CONTROLLO E LA PROGRAMMAZIONE DI ACCENSIONE/SPEGNIMENTO TRAMITE IL SOFTWARE TECNOMANAGER (SCARICABILE GRATUITAMENTE DAL SITO WWW.TECNOWARE.COM), SCHEDA SNMP O DRY CONTACT (OPZIONALI IN SOSTITUZIONE DI USB ED RS232), PESO 46 KG, DIMENSIONI 19X57,3X36,9 CM, CONTIENE 12 BATTERIE DA 12VDC 9AH, AUTONOMIA 10 MIN GARANZIA ON-SITE: 12 MESI SULLE PARTI ELETTRONICHE E 12 MESI SULLE BATTERIE ** PREVIA REGISTRAZIONE SU WWW.TECNOWARE.COM ** Similar UPS EVO DSP PLUS 1.2 MM HE - HIGH EFFICIENCY UPS EVO DSP PLUS 6.8 MM HE - HIGH EFFICIENCY UPS EVO DSP PLUS 3.6 MM HE - HIGH EFFICIENCY UPS EVO DSP PLUS 2.4 MM HE - HIGH EFFICIENCY Quick links Company Contacts Software Privacy Assistance Products UPS Inverter Structured cabling Power Systems Led lamps Information Tecnoware srl Via Montetrini, 2 / E 50065 Molino del Piano Florence - Italy Tel +39 055 88404 Fax +39 055 8367457 Mail: info@tecnoware.com. Look where we are Tecnoware srl - VAT number: 03831070481 Website by FormatStudio