Website about UPS INELT PARTNER LOGIN +7 (495) 787-68-54 ABOUT US CATALOG WHERE CAN I BUY SUPPORT FORUM CONTACTS Home / UPS catalog Inelt / 3-phase UPS / UPS INELT Monolith XM 20 - 520 kVA PRINTING Click to enlarge Back to comparison UPS INELT Monolith XM 20 - 520 kVA INELT Monolith XM 20-520 kVA is a modular, redundant scalable uninterruptible power supply system (UPS for DC) on-line with double conversion voltage, which allows to provide the highest level of availability at a relatively low cost. This UPS is designed to protect data centers, telecommunications systems, computer networks. The UPS consists of one, two or three cabinets of standard size 600 x 800 mm, in which a static switch module, a control and monitoring module, as well as the required number (up to 26 in total) of power modules with a capacity of 20 kVA / 16 kW are installed. In particular, a system with 10 power modules (200 kW of total power) is located in a cabinet that occupies an area of only 0.48 m 2 , which is extremely important in conditions of a shortage of space in modern data centers. The number of power modules is selected based on the total power of the load, plus one or more redundant ones ( N + 1 or N + m redundancy ) . As a result, failure of any power module does not interrupt the load protection. All modules, including the control module and the static switch, are hot-swappable, so there is no need to turn off the protected equipment to recover the system. The Power Modules operate normally even after physically removing the Control Module from the UPS. In fact, the functions of the control module are reduced to setting up and monitoring the system. The highest efficiency and low (less than 3%) input current THD reduce energy costs and reduce the required headroom of the standby generator set. Output power factor, maximizes cost efficiency while protecting modern equipment with input power factor corrected. Compactness, low weight and dimensions, as well as ease of replacement of modules make it easier and cheaper to maintain the UPS. This is especially important in remote regions, because in the event of a malfunction, the site personnel simply change the defective module to a serviceable one, removing one from the cabinet and inserting the other. The module is repaired in a service center, while the cost of shipping the module is much less than the costs of an engineer visit to repair a powerful UPS. At this time, we emphasize again, the UPS is not taken out of service, but continues to protect the connected equipment. The Monolith XM is equipped with a 7-inch color touch screen, RS-232 and RS-485 ports , SNMP card and MODBUS interface as standard . ASK A QUESTION CHOOSE UPS DOWNLOAD PDF DIRECTORY BY MAIL Model XM 120 ХM 200 ХM 260 ХM 520 Максимальная мощность, кВА 120 200 260 520 Мощность силового модуля, кВА/кВт 20кВА/16кВт Макс. количество модулей 6 10 13 26 Конфигурация 3 фазы 4 провода + заземление Номинальное напряжение, В 380/400/415 Диапазон входного напряжения, В 285 ~ 475 Диапазон входной частоты 50/60 Гц ±10% Входной коэффициент мощности >0,99 THDi <3% Напряжение цепи постоянного тока, В ±360 Ток заряда батарей, А 2 х число модулей Выходной коэффициент мощности 0,8 Диапазон частоты, Гц 50/60 ± 0,1 Гц в батарейном режиме Стабильность напряжения ±1% (статический режим); ±2% (динамический режим 0 - 100%) Перегрузочная способность до 125% - 10 мин, 150% - 1 мин Время переключения 0 мс КПД до 95% от сети, 97% от батарей Коммуникационный интерфейс «сухие» контакты, RS-232/RS-485, WEB/SNMP-адаптер Дисплей Сенсорный, 7 дюймов Рабочая температура -5°С - 40°С Относительная влажность < 95% без конденсата Степень защиты IP20 Шум < 60 дБ < 65 дБ Силоовой модуль Габариты (Ш х В х Г) мм 497 х 133 х 590 Силовой модуль, Вес (кг) 25,5 Габариты ИБП, (Ш х В х Г), мм 600 х 1400 х 800 600 х 2000 х 800 1200 х 2000 х 800 1800 х 2000 х 800 Вес шкафа без силовых модулей, кг 200 278 330 + 170 340 + 2 х 170 *Технические характеристики могут быть изменены без предварительного уведомления Расчет примерного времени автономной работы UPS INELT Monolith XM 20 - 520 кВА Нагрузка/ Емкость* 40 кВт 60 кВт 80 кВт 100 кВт 120 кВт 140 кВт 160 кВт 180 кВт 200 кВт 240 кВт 300 кВт 360 кВт 400 кВт 500 кВт 28 Ач 14 мин 8 мин 33 Ач 20 мин 10 мин 6 мин 45 Ач 27 мин 14 мин 8 мин 55 Ач 33 мин 20 мин 12 мин 7 мин 75 Ач 55 мин 33 мин 20 мин 13 мин 9 мин 6 мин 100 Ач 1,3 ч 45 мин 33 мин 20 мин 15 мин 10 мин 8 мин 120 Ач 1.7 ч 55 мин 40 мин 27 мин 19 мин 14 мин 11 мин 9 мин 6 мин 150 Ач 2,3 ч 1,8 ч 55 мин 39 мин 32 мин 28 minutes 22 minutes 17 minutes 14 minutes 9 minutes 5 minutes 200 Ah 3 h 2 h 1.8 h 55 minutes 43 minutes 40 minutes 32 minutes 29 minutes 20 minutes 14 minutes 9 minutes 7 minutes 300 Ah 4.8 h 3.2 h 2.3 h 1.7 h 58 minutes 55 minutes 50 minutes 43 minutes 32 minutes 26 minutes 20 minutes 14 minutes 12 minutes 8 minutes 400 Ah 1 h 55 minutes 45 mins 30 min 23 minutes 20 minutes 13 minutes 500 Ah 1.3 h 1.2 h 1 h 45 mins 33 minutes 29 minutes 22 minutes 600 Ah 1.4 h 1.3 h 1 h 48 minutes 38 minutes 29 minutes 700 Ah 1.6 h 1.2 h 1 h 50 minutes 33 minutes * Connection of 2 groups of 30 batteries of specified capacity. Maximum connected battery capacity 60 Ah x number of power modules installed in the UPS Flyer (131.3 KB) Operation manual (3.5 MB) Certificate of conformity to the requirements of the Customs Union (1.6 MB) Discuss on the forum Add to favorites You previously viewed Monolith K1000LT Monolith K3000ULT Monolith K1000ULT DC Guard 10 / 30W <one2> E-mail: info@ineltups.ru 2016 © INELTUPS Easy IT - Website improvement