C802.2 Certification Advantages Higher efficiency than with the conventional transformer Core entirely bolted to reduce the vibrations Fast investment recovery Core and enclosure heating reduction Noise level reduced Characteristics Copper and Aluminum windings Epoxy dipped 2@2.5% FCAN and 2@2.5% FCBN adjustments plugs Options Temperature Rise of 115oC & 80oC Electrostatic shield(s) K factors Enclosure types: NEMA 3R, NEMA 4 or NEMA 12 Epoxy Vacuum Impregnation (V.P.I.) Tech Sections Certifications Options Contact Us C802.2 Compliant Transformers, Full Load Current kVA 208 240 347 380 480 600 6 16.7 14.4 10 9.1 7.2 5.8 10 27.8 24.1 16.6 15.2 12 9.6 15 41.6 36.1 25 22.8 18 14.4 22 61.1 52.9 36.6 33.4 26.5 21.2 30 83.3 72.2 49.9 45.6 36.1 28.9 45 124.9 108.3 74.9 68.4 54.1 43.3 50 138.8 120.3 83.2 76 60.1 48.1 75 208.2 180.4 124.8 114 90.2 72.2 112.5 312.3 270.6 187.2 170.9 135.3 108.3 150 416.4 360.9 249.6 227.9 180.4 144.3 225 624.6 541.3 374.4 341.9 270.6 216.5 300 832.7 721.7 422.2 455.8 360.9 288.7 Contact Us Tel: 800-892-3755 Email Customer Service Request a quote Find a representative Parent Company Pioneer Dry Type Transformer Group Jefferson Electric Navigation Home About Us News Literature Request a quote Products Ventilated Transformers Encapsulated Transformers Industrial Control Transformers Medium Voltage Transformers Product Specifier (Jefferson Electric link) ©2020 Pioneer Dry Type Transformers Group Optimizer WordPress Theme ENFR