INDUSTRIAL REFRIGERATION VALVES & CONTROLS PRODUCTS RESOURCES CONTACT & SUPPORT LOGIN MVP65 - MVP100 Multi-Valve Platform Introduction Hansen Technologies introduces the MVP65 - MVP100 valve station sizes to the MVP Multi-Valve Platform product line. These offer the enhanced control functionality of a gas-powered two-step suction stop valve, a brand new feature for MVP valves. Ships pretested and assembled for quick and easy installation, requiring only two welds to complete most valve station applications. No disassembly is required. These new additions to the MVP family now offer 3"(80mm) and 4"(100mm) port sizes and are configured using standard Hansen parts and parts kits—saving you time and money on installation and training. Features Reduced installation time and cost Manual opening function standard No stop valve stems in the bottom of valve Pressure regulator or solenoid control function Motorized control functions Gas-powered two-step suction stop function Four to six control functions in one unit All stop valve stems are in vertical up position Simple, identifiable configuration Eliminates ﬂange gasket leak potential ACT standard Applications The functions available on MVP65 - MVP100 are: stop valve, control valve (solenoid/pressure regulator/motorized), or gas-powered suction stop valve Advantages Installed cost savings is a huge advantage of the entire MVP family; faster installation and less pipe cutting, welding, assembly time, insulation and freight equals reduced cost. In addition, the compact valve body saves installation space. MVP65 - MVP100 valves include 3 pressure gauge ports as well as a customizable side port feature for use with defrost condensate piping. Comes standard with ACT coating to provide high corrosion resistance for long life in harsh environments. To Order Specify connection size, control valve configuration (solenoid / regulator / suction stop / motorized), coil voltage and connection (leaded or DIN) and options if required. Unless specified, solenoid will have standard coil with 18" leads and 1⁄2" fitting, 115V. For product bulletins and additional information: CLICK HERE Charts (Click the chart to view enlarged image.) View fullsize Technical Specifications Safe Working Pressure: 400 psig (28 bar g) Operating Temperature: -60° to 240°F (-51º to 115ºC) Materials: Body: ACT coated cast steel, ASTM A352 Grade LCB Bonnet: Ductile iron, ASTM A536 Other: ACT coated or stainless steel Port Size 2-1/2” (65mm) 3" (80mm) 4" (100mm) Connection Styles Butt Weld: 2-1⁄2" to 4" (65mm to 100mm) CONTACT US Copyright © 2016-2020 Hansen Technologies Site Design: i6.graphics Terms & Conditions Careers Certifications Privacy Policy Safety Precautions 800.426.7368 By proceeding on this page, you agree to the use of the cookies according to the terms of our Privacy Policy. OK