HOME PRODUCTS & SOLUTIONS COMMERCIAL NETWORK TECHNICAL AREA DOWNLOAD COMPANY contacts site map login home collector brescia BRESCIA MANIFOLDS WITH FLOW METERS View Enlargement BRESCIA manifolds are distribution systems complete with delivery and return manifolds, fill and drain valves, manual air vents and fixing brackets for easy hydraulic connection in boxes. The return manifold is complete with a micrometric and thermostatic balancing valve as well as flow meters from 60 to 180 l / h (1 to 3 l / min) with which it is possible to balance the heating circuits. The delivery manifold is equipped with a shut-off valve for manual interception of the flow. All BRESCIA manifolds are made from drawn brass bar with a special profile and each single BRESCIA manifold is pressure tested with all the fittings and accessories mounted to ensure the safety of the seal. The heating circuits can be connected by means of a union with 3/4 EUROKONUS male thread; mounted on the manifold with o-ring seal and glued to avoid unscrewing in case of disassembly of the fitting. Field of use BRESCIA is used as a distribution manifold for underfloor heating applications. It is designed in a simple and functional way to meet the needs of medium-large construction sites. The standard equipment of the flow meters allows a quick adjustment of the flow rates according to the thermotechnical project and allows to have the circuits always under control with a simple glance. BRESCIA manifolds are designed for operating temperatures of 120 ° C and for operating pressures of 10 bar. Technical data UM BRESCIA manifolds Code SGLB03 -> Code SGLB13 Operating temperature ° C 120 Operating pressure Cafe 10 Flowmeter measurement range l / min 0-3 No. of outputs 3-13 Technical design Template N ° ways Quote "A" BRESCIA-03 3 215 BRESCIA-04 4 265 BRESCIA-05 5 315 BRESCIA-06 6 365 BRESCIA-07 7 415 BRESCIA-08 8 465 BRESCIA-09 9 515 BRESCIA-10 10 565 BRESCIA-11 11 615 BRESCIA-12 12 665 BRESCIA-13 13 715 Voce di capitolato Collettore di distribuzione in ottone nichelato da 1" con flussimetri integrati e regolazione micrometrica di serie, composto da collettore di mandata e collettore di ritorno, zanche di fissaggio, raccordi 3/4" eurokonus, dotato di accessori per carico e scarico impianto e sfiati aria manuali. N Uscite. Schemi / Grafici I dispositivi di regolazione e lettura consentono il bilanciamento idraulico delle derivazioni e la lettura immediata della portata attraverso ciascun circuito. Download Documenti da scaricare Scheda tecnica collettore brescia 93.82 KB Registrati o effettua il login per scaricare i file di questa categoria. Catalogo generale radiante systech 2.71 MB Technical manual systech radiant floor 5.74 MB Register or login to download files from this category. code product packaging SGLB03 Brescia manifold with 03 outputs box of 1 pc SGLB04 Brescia manifold with 04 outputs box of 1 pc SGLB05 Brescia manifold with 05 outputs box of 1 pc SGLB06 Brescia manifold with 06 outlets box of 1 pc SGLB07 Brescia manifold with 07 outputs box of 1 pc SGLB08 Brescia manifold with 08 outputs box of 1 pc SGLB09 Brescia manifold with 09 outputs box of 1 pc SGLB10 Brescia manifold with 10 outlets box of 1 pc. SGLB11 Brescia collector with 11 outlets box of 1 pc. SGLB12 Brescia manifold with 12 outlets box of 1 pc. SGLB13 Brescia manifold with 13 outlets box of 1 pc. LOKITHERM 17X2 TUBE - 5-LAYERS Recently Viewed Products Neoclassic (Category: Cast iron radiators ) RADIATORS RADIANT HEATING AND COOLING CONTROLLED MECHANICAL VENTILATION THE RADIANTORI LOGIN Username Password remember me Forgot password? Forgot Username? Sign in TECHNICAL AREA - LATEST ARTICLES Calculation of thermal emissions from radiators General features Underfloor heating system Fundamentals of acoustics in radiant heating systems Water treatment in thermal plants Calculation of emissions home collector brescia HOME PRODUCTS & SOLUTIONS COMMERCIAL NETWORK TECHNICAL AREA DOWNLOAD COMPANY THEME NEOCLASSIC ACOUSTIC EVO SYSTEM LOKI SYSTEM BRESCIA COLLECTOR CALCULATION OF RADIATOR POWER Ideal Clima srl Via della Volta, 183 - 25124 Brescia (BS) e-mail: info@idealclima.eu Tel. +39 030 35 45 319 Fax: +39 030 51 09 329 CF and VAT number 03111240986 CS 100'000 Euro iv Budgeting area Agents area Terms of sale Where we are Privacy Copyright © 2012 Ideal Clima. All rights reserved.