ABOUT PRODUCTS PRICE LIST CHARTS FAQ RESOURCES WARRANTY CONTACT Potable Water SDR’s White Gasketed Specification Pacific Plastics IPS SDR series of PVC pipe is produced for use in the pressure applications in which the maximum operating temperature is 140°F. The compound is PVC 1120 Type 1 Grade 1, with a cell class of 12454B, per ASTM D1784. Each one of the categories of our SDR series listed below is produced in strict compliance to ASTM D2241. It is listed with NSF and complies with NSF/ANSI Standard 14 and Standard 61. The IPS Gasketed SDR Series of PVC pipe are produced with an integral bell that includes a factory installed Reiber gasket in the bell. The gaskets will conform to ASTM F477, and the assembled gasketed joints conform to ASTM D3139. Our IPS Gasketed SDR Series of PVC pipe is produced in the following categories: White SDR21, SDR26, SDR32.5, SDR41, SDR64 for use in potable water applications. Sizes 2″ – 12″ are produced in White color, 20 foot lengths and Gasketed. The outside diameter and wall thickness of the SDR series of PVC pipe are measured in accordance to ASTM D2122 and are shown in the following table: Dimensions Size OD B C D T – SDR 21 T – SDR 26 T – SDR 32.5 T – SDR 41 T – SDR 64 2 2.375 3.00 3.75 2.65 0.113 0.091 0.073 2 ½ 2.875 3.50 4.50 3.40 0.137 0.110 0.088 3 3.500 4.50 4.80 3.65 0.167 0.135 0.108 0.085 4 4.500 6.00 5.35 4.20 0.214 0.173 0.138 0.110 6 6.625 8.25 7.30 5.65 0.316 0.255 0.204 0.162 0.104 8 8.625 10.75 8.65 6.40 0.410 0.332 0.265 0.210 0.135 10 10.750 13.50 9.25 7.00 0.511 0.413 0.331 0.262 0.168 12 12.750 15.75 10.25 8.00 0.606 0.490 0.392 0.311 0.199 OD – Outside Diameter B – Approximate Bell Diameter C – Approximate Bell Depth D – Insert Mark T – Wall Thickness PSI – Pressure Rating Certification This is to certify that, in this category of PVC pipe, all the products manufactured by Pacific Plastics have been inspected, sampled and tested in accordance with the following specifications and have been found to meet or exceed the requirements of those specifications. Raw Materials PVC1120 Type1 Grade1 Cell Class 12454 ASTM D1784 Specification for Rigid PVC Compounds NSF Listed PVC Pipe SDR21(Cl200), SDR26(Cl160), SDR32.5(Cl125), SDR41(Cl100), SDR64(Cl63) White Gasketed (using Rieber Elastomeric Seals to join) 2″ – 12″ IPS ASTM D2241 Specification for PVC Pressure Rated Pipe ASTM D3139 Specification for Joints for Gasketed PVC Pressure Pipe ASTM F477 Specification for Flexible Elastomeric Seals (Gaskets) Complies with NSF / ANSI Standard 14 Complies with NSF / ANSI Standard 61 Part Numbers Click here for Part Numbers Price List Click here for Price List Loading Chart Click here for Loading Chart Weights Click here for Weights Products Potable Water Sch40 White Solvent Weld Potable Water SDR’s White Solvent Weld Potable Water SDR’s White Gasketed Potable Water Sch80 Grey Solvent Weld Plain End Potable Water Sch80 Grey Solvent Weld Belled End Reclaimed Water SDR’s Purple Solvent Weld Reclaimed Water SDR’s Purple Gasketed Reclaimed Water Sch40 Purple Solvent Weld PIP SDR’s White Gasketed UVR Sch40 Brown Solvent Weld Sewer SDR35 Green Gasketed Sewer SDR35 White Solvent Weld Drain D2729 White Solvent Weld Drain Sch40 Perforated White Solvent Weld Electrical Conduit Sch40 Grey Solvent Weld Copyright © 2017 Pacific Plastics Inc. All rights reserved. Orange County Web Design by MH Design v2