Address: 2395 Washington Avenue, Bronx, NY 10458 Customer Support Leave Us A Review Home Product About Us Contact Us Industrial Combustion Burners Wymbs Inc is the largest distributor of Industrial Combustion Burners and is the exclusive distributor for New York City (5 Boroughs), Westchester, Putnam, Dutchess, Nassau and Suffolk Counties and Southern Connecticut. We carry an inventory of over 200 burners ready for immediate delivery to the job site. D/LND Burner D series burners are performance proven in boiler, heater, furnace, kiln and dryer applications worldwide. The standard D series offers natural gas, propane gas, air atomized #2-#6 oil and combination gas/oil fuel options at capacities from 4,200,000 to 42,000,000 MBTU/Hour. The low NOx D series offers natural gas, propane gas, air atomized #2-#6 oil, and combination gas/oil fuel options at capacities from 3.4 to 42.0 MMBTU/Hour. A true forced draft design provides the ability to deliver rated capacities against furnace pressures up to 4" W.C. Stock Burners Include: DLG - Combination natural gas and air atomized #2 Oil Low-pressure air atomizing system on oil with rotary vane compressor Full Modulation Auto Fuel Changeover Piston-type positive displacement oil metering system Hinged combustion head for easy access and maintenance Backward-curved impeller provides adequate combustion air for various furnace pressures UL & cUL listed Burners ranging in size from DLG 42 - 145 are stocked in Wymbs warehouse ready for immediate delivery (larger burners up to DLG 420 - 1000 HP Boiler must be special ordered) Optional Features Include: (Burner must be Special Ordered) DG - Natural Gas only, DL - air atomized #2 Oil only, LNDL / LNDLG - Lo Nox D Burners, DMG - air atomized #4 oil and natural gas, DM - air atomized #4 oil, DEG - air atomized #6 oil and natural gas, DE - air atomized #6 oil Siemens ventless gas trains (Fully assembled) in stock and available for delivery with your burner Parallel positioning available for optimal control throughout the firing range (Siemens LMV, Fireye Nexus & PPC, Honeywell Control Links) High Efficiency (TEFC) Motors VFD Drives for high efficiency motors (Requires Parallel Positioning) Cam trim available with 14-point adjustment range for consistent air/fuel ratios Low NOx with FGR capabilities FGR modulating valve Nozzle line electric heater standard on medium to heavy oil burners Many other accessory items including Sequence Draft Control System, Lead Lag System, and Smoke Opacity Monitors Burners can be built to job specifications Capacities and Specifications (For stock DLG Burners) Burner Size 42 54 63 84 105 145 175 210 252 300 Gas Input (Mbtu/hr) 4,200 5,400 6,550 8,400 10,500 15,000 17,500 21,000 25,200 30,000 #2 Oil Input (US gph) 30 39 47 60 75 107 125 150 180 215 Burner Voltage *1 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 440/3/60 Boiler Horsepower 100 129 156 200 250 357 417 500 600 714 Blower Motor Horsepower "S" 3 3 5 5 7-1/2 15 20 20 25 40 Blower Motor Horsepower "P" 3 5 5 7-1/2 10 15 20 25 30 40 Furnace Pressure "S" (w.c.) 1.5 1.5 1.5 1.5 1.5 1.5 1.5 1.5 1.5 1.5 Furnace Pressure "P" (w.c.) 4.0 4.0 4.0 4.0 4.0 4.0 4.0 4.0 4.0 4.0 Gas Pressure Required 4" Train ("w.c.) *2 3.4" 5.2" 7.4" 5.1" 5.6" 7.5" 7.8" 11" *3 *3 Shipping Weight 1,000 1,100 1,200 1,300 1,400 1,850 2,250 2,750 3,100 3,500 *1 Burner voltage is for our in stock burners, please call to order burners with different voltages *2 Minimum gas pressure required at train inlet with a 4" Siemens Gas Train, please call us for pressure requirements on smaller Siemens Gas Trains. A gas booster is required for lower pressures than listed above, we can supply you with an Eclipse Gas Booster. *3 Please call us for gas pressure requirements on DLG 252 and larger M Burner M series burners are designed for a wide range of applications such as boilers, heaters, furnaces, kilns and dryers. The M series offers natural gas, propane gas, air atomized #2-#6 oil and combination gas/oil fuel options at capacities from 1,400,000 to 10,500,000 MBTU/Hour. Full modulation and cam trim adjustment provides optimum performance to meet load demand. Stock Burners Include: MMG #2 Oil - Combination natural gas and air atomized #2 Oil Low-pressure air atomizing system on oil with rotary vane compressor Full Modulation Auto Fuel Changeover Piston-type positive displacement oil metering system Hinged combustion head for easy access and maintenance Backward-curved impeller provides adequate combustion air for various furnace pressures UL & cUL listed Burners ranging in size from MMG 22 - 84 are stocked in Wymbs warehouse ready for immediate delivery (MMG 14 & 105 must be special ordered) Optional Features Include: (Burner must be Special Ordered) MG - Natural Gas only, MM - air atomized #2 Oil only, MM - air atomized #4 Oil, MMG - air atomized #4 oil and natural gas, ME - air atomized #6 oil. MEG - air atomized #6 oil and natural gas Siemens ventless gas trains (Fully assembled) in stock and available for delivery with your burner Parallel positioning available for optimal control throughout the firing range (Siemens LMV, Fireye Nexus, Honeywell Links) Cam trim available with 14-point adjustment range for consistent air/fuel ratios Low NOx with FGR capabilities FGR modulating valve Nozzle line electric heater standard on medium to heavy oil burners Many other accessory items including Sequence Draft Control System, Lead Lag System, and Smoke Opacity Monitors Burners can be built to job specifications Capacities and Specifications (For stock MMG Burners) Burner Size 14 22 28 30 34 42 54 63 84 105 Gas Input (Mbtu/hr) 1,400 2,200 2,800 3,150 3,500 4,200 5,600 6,300 8,400 10,500 #2 Oil Input (US gph) 10 15.7 20 22.5 25 30 40 45 60 75 Burner Voltage *1 115/1/60 115/1/60 230/1/60 230/1/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 Boiler Horsepower 33 52 67 75 83 104 133 150 200 250 Blower Motor Horsepower "S" *2 1/2 1/2 2 2 2 2 2 3 5 7-1/2 Blower Motor Horsepower "P" 2 2 3 3 7-1/2 7-1/2 Furnace Pressure "S" (w.c.) *2 0.75 0.75 0.75 0.75 0.75 0.75 0.75 0.75 0.75 0.75 Furnace Pressure "P" (w.c.) 2.0 2.0 2.0 2.0 2.0 2.0 Gas Pressure Required 4" Train ("w.c.) *3 2.0" 2.2" 1.5" 1.7" 2.2" 2" 5.5" 6.9" 5.1" 5.6" Shipping Weight 450 450 500 500 650 650 750 750 1,200 1,250 *1 Burner voltage is for our in stock burners, please call to order burners with different voltages *2 MMG 14-30 do not have an "S" or "P" designation *3 Minimum gas pressure required at train inlet with a 4" Siemens Gas Train, please call us for pressure requirements on smaller Siemens Gas Trains. A gas booster is required for lower pressures than listed above, we can supply you with an Eclipse Gas Booster. V/LNV Burner V Series burners are suitable for firetube, watertube and cast iron boilers. The V series features a unique aerodynamic air damper design which permits accurate air-to-fuel settings for maximum combustion efficiency. The standard V series offers natural gas, propane gas, pressure atomized #2 oil and combination gas/oil fuel options at capacities from 1,300,000 to 16,800,000 Btu/hour. The low NOx V series offers natural gas, propane gas, pressure atomized #2 oil, and combination gas/oil fuel options at capacities from 1,300,000 to 14,700,000 Btu/hour. Through the use of advanced technology, the V series offers high turndown up to 10:1 on natural gas (requires parallel positioning to obtain 10:1 turndown), and low emission capabilities with turndown up to 5:1. Wymbs has a full inventory of stock VLG burners ready for immediate delivery ranging in size from VLG-13 to VLG 84. V Burners with optional features can be special ordered from our factory with a normal lead time of 4-6 weeks, please call us for additional information. Stock Burners Include: VLG - Combination natural gas and pressure atomized #2 Oil For Firetube Boilers (Special Order for Cast Iron & Watertube Boilers) Fireye Flame Safeguard (Less Display Module) Full Modulation Auto Fuel Changeover Remote Oil Pump Unique aerodynamic air damper design for optimal flow control Forced draft for clean and efficient combustion UL & cUL listed Siemens Ventless Gas Train (Loose Components - Must be assembled by Contractor - Fully assembled trains can be supplied for an additional charge) Burners are stocked in Wymbs warehouse ready for immediate delivery Optional Features Include: (Burner must be Special Ordered) VG -Natural gas only, VL -pressure atomized #2 oil only, and LNV - Lo Nox V burners Display Module for Flame Safeguard Honeywell Flame Safeguard Cam trim with 14-point adjustment range for consistent air/fuel ratios Parallel positioning available for optimal control throughout the firing range (Siemens LMV, Fireye Nexus, Honeywell Links) Up to 10:1 turndown on natural gas (requires parallel positioning to achieve 10:1 turndown) and optional low NOx with up to 5:1 turndown Top or rear mount panel options Induced FGR FGR modulating valve FGR shutoff valve Cam trim available with 14-point adjustment range on FGR Many other accessory items including Sequence Draft Control System, Lead Lag System, and Smoke Opacity Monitors Capacities and Specifications (For Stock VLG Burners) Burner Size 13 17 21 25 30 34 40 42 54 63 80 84 Frame Size 1 1 1 1 2 2 2 2 3 3 3 3 Burner Voltage *1 115/1/60 115/1/60 115/1/60 115/1/60 208/1/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 208/3/60 Gas Input (MBTu/hr) 1,300 1,700 2,100 2,500 3'000 3,400 4,000 4,200 5,400 6,300 8,000 8,400 Oil Input (US gph) 9.3 12.1 15.0 17.9 21.4 24.3 28.6 30.0 38.6 45.0 57.1 60.0 Boiler HP @80% Eff. 31 40 50 60 71 81 95 100 129 150 190 200 Blower Motor *2 1/2 1/2 3/4 3/4 1 1 1 2 5 5 7-1/2 7-1/2 Remote Oil Pump Motor HP *3 1/2 1/2 1/2 1/2 1/2 1/2 1/2 1/2 3/4 3/4 3/4" 3/4 Standard Siemens Train *4 2" 2" 2" 2" 2-1/2" 2-1/2" 2-1/2" 2-1/2" 2-1/2" 2-1/2" 3" 3" Min Pressure Standard Train ("w.c) *5 1.6" 2.7" 2.4" 3.3" 2.7" 3.4" 5.1" 5.2" 6.7" 8.9" Min Pressure 4" Siemens Train ("w.c) *6 1.4" 2.1" 1.6" 2.1" 2.1" 2.6" 4.1" 4.2" 4.9" 6.5" Shipping Weight 450 450 450 450 450 450 600 600 700 700 700 700 *1 Burner voltage is for our in stock burners, please call to order burners with different voltages *2 Motor ratings for gas only or gas/oil burners using a remote oil pump *3 Remote oil pump standard on our stock burners *4 Standard Gas Train size on our stock burners - train can be upgraded to larger gas train *5 Minimum pressure required at train inlet for standard gas train - please call for minimum pressure for other gas train sizes *6 Minimum gas pressure required at train inlet with a 4" Siemens Gas Train. A gas booster is required for lower pressures than listed above, we can supply you with an Eclipse Gas Booster. Q Burner Q Series burners are designed around efficiency and operational simplicity, the Q series is perfect for cast iron sectional boilers, firebox, commercial watertube, firetube, furnace and oven applications. The standard Q series features linkageless operation with DC pulse width modulation and parallel positioning gas actuator control for increased efficiencies and ease of use. The standard Q series includes on/off or full modulation linkageless operation and offers natural gas from 0.375 to 2.5 MM BTU per hour. Its totally enclosed, compact design allows provisions for sealed combustion or fresh air intake. Outside air can easily be connected to the blower inlet without any modifications to the burner. Features Include: Linkageless System standard for optimal control throughout the firing range DC Pulse Width Modulation allows full blower speed control without the use of air dampers Fully enclosed air housing features a hinged cover for easy access to internal components and quiet operation Combustion air fan efficient airfoil blade design smoothly lifts airflow over the entire blade, resulting in less motor horsepower requirements and significant noise reduction when compared to standard force draft fans Sealed combustion eliminates the need for outside air dampers and make-up air units typically required in every boiler room. UL & cUL listed CSA package listed Home Products About Us Contact Us Address 2395 Washington Avenue, Bronx, NY 10458 Business Hours Mon - Fri 7:30 am - 4:00 pm Sat - Sun Closed E-mail joe@wymbs.com Content, including images, displayed on this website is protected by copyright laws. Downloading, republication, retransmission or reproduction of content on this website is strictly prohibited. Terms of Use | Privacy Policy Contact