Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT SERVICE DROP CABLE - QUADRUPLEX CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION: Used to supply 3 phase power, usually from a pole mounted transformer to the user’s service head where connection to the service entrance cable is made. To be used at voltages of 600 volts or less phase to phase and at conductor temperatures not to exceed 75°C for polyethylene insulated conductors or 90°C for crosslinked polyethylene (XLP) insulated conductors. PRODUCT FEATURES: Conductors are concentrically stranded, compressed 1350-H19 aluminum. Insulated with either polyethylene or XLP crosslinked polyethylene. Neutral messengers are concentrically stranded 6201, AAC or ACSR. STANDARDS: Service drop cable meets or exceeds the following ASTM specifications: • B-230 Aluminum Wire, 1350-H19 for Electrical Purposes • B-231 Aluminum Conductors, Concentric-Lay-Stranded • B-232 Aluminum Conductors, Concentric-Lay-Stranded, Coated Steel Reinforced (ACSR) • B-399 Concentric-Lay-Stranded, 6201-T81 Aluminum Alloy Conductors • B-901 Compressed Round Stranded Aluminum Conductors Using Single Input Wire • ANSI/ICEA S-76-474 KINGWIRE Quadruplex Service Drop - Aluminum Conductor AAC - Neutral Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Clydesdale 4 Solid 45 4 7 881 208 201 100 80 Pinto 4 7/w 45 4 7 881 223 207 100 80 Mustang 2 7/w 45 2 7 1,350 333 312 135 105 Criollo 1/0 19/w 60 1/0 7 1,990 529 504 180 135 Percheron 2/0 19/w 60 2/0 7 2,510 649 620 205 155 Hanovarian 3/0 19/w 60 3/0 19 3,310 799 765 235 180 Oldenburg 4/0 19/w 60 4/0 19 4,020 986 946 270 205 Lippizaner 336.4 19/w 60 336.4 19 6,146 1,546 1,519 330 240 KINGWIRE Quadruplex Service Drop - Aluminum Conductor ACSR- Neutral Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Morochuca 6 Solid 45 6 6/1 1,190 152 147 75 60 Chola 6 7/w 45 6 6/1 1,190 162 151 75 60 Morgan 4 Solid 45 4 6/1 1,860 226 220 100 80 Hackney 4 7/w 45 4 6/1 1,860 241 226 100 80 Palomino 2 7/w 45 2 6/1 2,850 362 342 135 105 Costena 1/0 19/w 60 1/0 6/1 4,380 575 550 180 135 Grullo 2/0 19/w 60 2/0 6/1 5,310 707 678 205 155 Suffolk 3/0 19/w 60 3/0 6/1 6,620 872 838 235 180 Appaloosa 4/0 19/w 60 4/0 6/1 8,350 1,079 1,039 270 205 Bronco 336.4 19/w 60 336.4 18/1 8,580 1,613 1,568 330 240 Gelding 336.4 19/w 60 4/0 6/1 8,350 1,548 1,494 330 240 KINGWIRE Quadruplex Service Drop - Aluminum Conductor AAAC-Alloy - Neutral Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Bay 6 Solid 45 6 7 1,110 145 140 75 60 French Coach 6 7/w 45 6 7 1,110 155 144 75 60 German Coach 4 Solid 45 4 7 1,760 214 208 100 80 Arabian 4 7/w 45 4 7 1,760 229 214 100 80 Belgian 2 7/w 45 2 7 2,800 344 323 135 105 Shetland 1/0 19/w 60 1/0 7 4,460 546 521 180 135 Thouroughbred 2/0 19/w 60 2/0 7 5,390 670 641 205 155 Trotter 3/0 19/w 60 3/0 7 6,790 825 791 235 180 Walking 4/0 19/w 60 4/0 7 8,560 1,019 979 270 205 * Note: Designated sizes are ACSR 6/1 diameter equivalent resistivity per ASTM-B-399 for 6201. Conductor temperature of 90°C for XLP, 75°C for Poly; ambient temperatures of 40°C; emissivity 0.9; 2ft/sec. wind in sun. ** To determine current ampacity by conductor size, please consult The National Electric Code, latest edition. The data is approximate and subject to normal manufacturing tolerances. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep