CFR-A EVAPORATIVE CONDENSERS EVAPORATIVE CONDENSERS WITH AXIAL FANS Decsa's CFR-A series evaporative condensers, made of hot-dip galvanised Z-725 steel sheet, are equipped with state-of-the-art axial fans that optimise the L/G ratio within the units, thus reducing the power input and operating costs. Like Decsa's other products, the CFR-A evaporative condensers stand out on the market for the important certifications obtained. In fact, the CFR-A model is designed and manufactured in accordance with the Quality System certified according to ISO 9001:2015 and according to the Directive 2014/68/EU (PED) which allows the pressure sealing of the coils used up to 40 bar and the use with pressures up to 28 bar. The special DecsaCOATING PLUS protection also ensures a reduction in the use of chemicals products for water quality control, thus guaranteeing significant economic savings and greater environmental sustainability. The wide range of variants available completes the offer, making the CFR-A series an extremely flexible and suitable evaporative condenser for any type of application in refrigeration systems and cold chain applications. EVAPORATIVE CONDENSERS CFR-A: TECHNICAL FEATURES Structure and panels The CFR-A series is designed with structures and panels made of hot-dip galvanised Z-725 steel. To simplify routine maintenance, the panels are easily removable without the need for dedicated tools. Cold water basin The cooled water collection basin is made of hot-dip galvanised Z-725 steel sheet, complete with a sloping bottom to prevent water stagnation, a cooled water outlet fitting with an easy-to-inspect anti-vortex filter, a drain and overflow fitting, a make-up water fitting with float, reinforced PVC air inlet grilles and a bleed pipe. Heat Exchanger The coil of the heat exchange section of the evaporative condensers series CFR-A is made up of coils in top quality steel tube, bent and then tested in a water tank at a pressure of 25 bar. The coil is then tested with compressed air at 40 bar, and subsequently galvanised by immersion in a molten zinc bath. Fan section The CFR-A evaporative condensers are manufactured with axial fans with a balanced impeller equipped with stationary adjustable blades with a high efficiency profile. The peripheral speed of the impeller is deliberately limited in order to ensure low noise levels. As with the REF-A and TMA-EU cooling towers, the CFR-A is also available with low-noise fans on request. Finishing It is possible to add the special protective epoxy powder coating DecsaCOATING PLUS to equipment , an additional protection available in all RAL colours. Highlight Materials Hot-dip galvanised steel sheet Z-725 Number of models 36 Capacity from 148 to 7281 kW EVAPORATIVE CONDENSERS CFR-A For all technical details, download the catalogue IDEAL FOR... INDUSTRIAL REFRIGERATION The CFR-A series is designed and manufactured to meet the reliability and low noise requirements of our customers. Designed to cool ammonia or refrigerant gases, these evaporative condensers are equipped with airfoil axial fans available in aluminium or FRP, depending on the model. Equipment certification to Directive 2014/68/EU (PED) ensures use with operating pressures up to 28 bar. Particularly suitable where high efficiency evaporative condensers with low operating costs are required, the CFR-A series is ideal for all applications in industrial refrigeration. Low operating costs The CFR-A series is designed to ensure low running costs, also thanks to the limited energy consumption of the motors that power the axial fans. High resistance structure The structure and panels are made of high-strength Z-725 hot-dip galvanised steel (725 g/sqm); the panels are complete with one or more watertight doors for internal inspection. Certified coils CFR-A evaporative condensers are manufactured in accordance with Directive 97/23/EC (PED) which guarantees the pressure tightness of coils installed up to 40 bar and authorises their use with operating pressures up to 28 bar. Axial fans The CFR-A series is equipped with the latest generation of axial fans, which optimise the L/G ratio within the unit, resulting in lower power consumption and reduced running costs. Spare parts, maintenance and service for CFR-A? Visit the Service page AVAILABLE OPTIONS ‍ Silenced fans (Axilent) Motor - fan coupling with belt and pulley transmission or with angle drive with oil bath gears Internal and external protection with DecsaCOATING PLUScoating WEBINAR CFR-A Cooling tower maintenance How to preserve the performance of closed-circuit cooling towers and evaporative condensers equipped with axial fans? Below are the highlights of the webinar: Evaporative Condenser CFR-A series Closed Circuit Cooling Tower REF-A series Maintenance of the upper fan section Maintenance of the heat exchanger section Maintenance of the water basin Read more: Cooling tower maintenance: guideline Decsa Srl Via Cappelletta 1 Voghera (PV) - Italy +39 0383 69411 P.I. IT08325980152 ABOUT US History R&D Design Construction details Operations Test area Sales Manufacturing Engineering Marketing Service Safety & Environment PRODUCTS Cooling towers open circuit Cooling towers closed circuit Evaporative condensers SOLUTIONS HVAC Process cooling Industrial refrigeration SERVICE CERTIFICATIONS ARCHIVE Catalogues Video News Spare parts FAQ Glossary CONTACT Privacy Policy Integrated Quality & Environment Policy General terms and conditions of sale General Terms and Conditions of Purchase European Regional Development Fund × Questo sito web utilizza cookie Questo sito web utilizza i cookie per migliorare la tua esperienza di navigazione. Utilizzando il nostro sito web acconsenti a tutti i cookie in conformità con la nostra policy per i cookie. Leggi di più STRETTAMENTE NECESSARI PERFORMANCE TARGETING FUNZIONALITÀ ACCETTA TUTTO RIFIUTA TUTTO MOSTRA DETTAGLI