REP LOCATOR SERIES QUICKSHIP ALL PRODUCTS INSPIRATION CONTACT FRACTALZ BFZ100-R 2-1/4” wide recessed flush mount LED luminaire CutsheetExplore Fractalz       DOWNLOADS FEATURES PERFORMANCE SPECS DATA SECTION Product Guide Related Products Get Help Find a Rep DOWNLOADS Documentation Cutsheet Application Photo BIM Files 45° | 45° 45° | Dead End Dead End | Dead End Photometry PDF IES FRACTALZ INSPIRATION FEATURES The BFZ100-R is part of the dynamic Fractalz series linear LED luminaires. This flush mount design not only creates clean, linear runs of light but also serves as a mounting point for Fractalz Through-Space luminaires to project luminous lines into interior volumes. PERFORMANCE Nominal Length: 4' Output: R: regular | H: high Lumens/ft.: R: 665 | H: 1000 Watts/ft.: R: 7.4 | 11.1 Luminaire Lumens: R: 2653 | H: 3990 Efficacy (LPW): R: 90 | H: 90 Note: All data reflects fixtures with 3500K LEDs SPECIFICATIONS Fixture constructed of an extruded aluminum housing, sheet formed plaster flanges and frosted acrylic lens Fixture flush mounts in walls or hard ceilings and integrates with the Fractalz series Through-Space luminaires Available in nominal lengths of 24”-96” at 6” intervals Removable end plaster flanges convert single fixtures for use in continuous runs Fixtures provided with 18 ga. wiring harness for 6 Amp maximum load Standard integral 120-277V constant voltage driver offered with 0-10V dimming or non-dim Standard outputs are 665 or 1000 lumens per foot LEDs available in 2700K, 3000K, 3500K, and 4000K, within a 3 step MacAdam ellipse, all with 90+ CRI typical Life: 50,000 hours L70 Limited five year warranty UL and C-UL listed for dry and damp locations IBEW manufactured and assembled Made in U.S.A. PRODUCT DATA Nominal Fixture Length 24: 24"30: 30"36: 36" 42: 42"48: 48"54: 54"60: 60"66: 66"72: 72"78: 78"84: 84"90: 90"96: 96" Actual length dependent on interface A and B configuration Correlated Color Temperature 27: 2700K - 90+ CRI 30: 3000K - 90+ CRI35: 3500K - 90+ CRI 40: 4000K - 90+ CRI Driver N: non-dimmingD: dimming, 0-10V, 10% Light Output (lumens per foot) R: regular - 665H: high - 1000 Interface Configuration A DE: dead end45: 45° interface Interface Configuration B DE: dead end45: 45° interface SECTION RELATED PRODUCTS BFZ100-S BFZ100-T READY TO ILLUMINATE YOUR NEXT PROJECT? Find your nearest Bartco rep now GO  BARTCO LIGHTING DIGITAL PRODUCT GUIDE SEE THE GUIDE ©2021 Bartco Lighting 5761 Research Drive Huntington Beach, CA 92649 SIGN UP FOR THE LATEST NEWS Get our latest insights, exclusive industry news, & lighting design trends. Email Address SIGNUP This field should be left blank About Bartco Privacy Notice Terms & Conditions Events Downloads Resources Spec Registration Visit Huntington Beach, CA WEBSITE BY ISIMPLIFYME