Russell PA515 Self Priming, Close Coupled, Bronze Fitted, Centrifigal Pump PA515 CUT SHEET PA515 IOM PA515 Capabilities Maximum Working Pressure 175PSI Maximum Gallons Per Minute 90 Maximum Head Produced 103 FT. RPM 3450 Maximum Seal Cavity Temp Buna-N 225˚F EPT 300˚F Viton 400˚F Maximum Horsepower 2 View fullsize Design Features CASING Constructed as ASTM A48 class 30 cast iron. Back pull-out design allows the pump to be serviced without disturbing the piping. 1/4 npt suction gauge and 1/8 npt drain tappings are standard. Self-venting design prevents air binding within the pump. After initial priming the pump never needs to be primed again. MECHANICAL SEAL Type 21 buna-n seal is rated to 225°F and pressures to 175PSI. Carbon seal face mates with the ceramic seat providing years of trouble free service. Alternate seals available upon request. IMPELLER The hydraulic design of the impeller maximizes pressure and gpm while minimizing horsepower. The enclosed vacuum cast impeller is made of cast bronze. ADAPTER The precision machining of the adapter allows for easy assembly of the pump. Construction consists of ASTM A48 class 30 cast iron. MOTOR The NEMA 56J motor utilizes a 416 stainless steel shaft. The motor’s heavy duty ball bearings withstand axial and radial thrust loads with no problem. Standard enclosure type is drip-proof but alternates are available. Pump Curve Click Here Technical View fullsize View fullsize View fullsize View fullsize View fullsize 102 W. Chicago Street | Albion, IA 50005 | (641) 488-2319 | russpump@heartofiowa.net Site by: BonardiMedia.con Copyright 2018 - Russell Pump & Engineering Inc.