CONTACT US BILL PAY 1.855.622.6583 ABOUT US PRODUCTS + SERVICES INDUSTRIES LOCATIONS NEWS CAREERS BACKFLOW PREVENTERS – A CRITICAL COMPONENT IN FIRE PROTECTION SYSTEMS Posted October 19, 2021 by Koorsen Fire & Security Backflow preventers provide a critical interface between a building's fire protection system and the water supply that feeds it. A backflow preventer is a device designed to ensure that water inside a building's fire sprinkler system flows in one direction only -- from the water main to the system's pipes. This is necessary to prevent any potential cross-contamination that can occur when water from the fire sprinkler system flows backward into the water main, carrying with it potentially hazardous contamination into the public's drinking water supply. For example, the U.S. Environmental Protection Agency reported a 1997 incident in which an estimated 40,000 neighborhood taps in Charlotte-Mecklenburg, North Carolina, were contaminated when a fire truck pump created backpressure on a fire hydrant before the valve was closed. This caused a pressurized backflow into the public water supply of more than 60 gallons of liquid fire-fighting foam. In Pittsburgh, Pennsylvania, in 2008, a similar incident happened when water pressure from the city's fire trucks connected to two fire hydrants and overwhelmed the city's drinking water supply lines. As in the 1997 incident, this created a backflow that introduced fire suppression foam into the water supply. While the foam did not pose a significant health threat, water users in the downtown area were told not to use the water until the foam could be flushed from the system because it could irritate the skin and eyes. According to the American Backflow Prevention Association, 6.2% of the pressure losses reported are due to fire-fighting activities. It is difficult to say how often incidents like these now occur because the data is lacking. But, the actual number is likely higher because many backflow incidents go unreported. Questions? Contact Us Now! How Do They Work? Backflow preventers are typically installed in wet sprinkler systems and standpipe systems in which water is held at pressure inside the pipes and only released when the system is activated. Over time, this water can become stagnant and contaminated with bacteria and chemicals such as corrosion inhibitors, antifreeze, and other chemicals added to the system. When sprinkler systems and standpipes are connected to a public water supply, this contaminated water could potentially contaminate drinking water or "potable" water supplies without backflow preventers. Even if a sprinkler system is connected to a non-potable water source, the potential for contamination still exists if there are any cross-connections between that system and a community's drinking water supply. Backflow preventers are equipped with two one-way valves, called check valves, which allow the water to flow only in one direction. This redundancy ensures that if one check valve fails, the other will continue to protect the water supply and create a more reliable seal, which guards against minor backflow leakages. The check valves in a backflow preventer operate independently with a differential pressure-relief valve between them, enabling the closure of one valve to reduce the pressure differential across the other. Check valves are installed in various places in a fire protection system to prevent water from backing up into the supply line. However, it is important to note that check valves alone are not adequate to protect water supply lines from contamination. Other key parts of a backflow preventer include a shutoff valve and two test cocks (small ball valves) to allow for required testing of each valve and the assembly. The two main types of backflow preventers designed for fire protection systems are: Double Check Valves (DCVs) The most common type of backflow prevention device. Suitable for low-hazard settings, defined by the American Water Works Association (AWWA) as a situation in which a cross-connection might create a nuisance or be aesthetically unpleasant but would not create a health hazard. DCVs consist of an inlet shutoff valve, two independently operating spring-loaded check valves (usually inside a single valve body), four test cocks, and an outlet shutoff valve. Reduced Pressure Zones (RPZ) More complex but also more reliable than DCVs. Generally required for high-hazard settings, defined by the AWWA as those in which an unprotected cross-connection could introduce substances capable of causing illness, death, or disease spread if introduced into the public water supply. Equipped with a hydraulically operated relief valve in addition to two spring-loaded check valves. If you want to learn more about how a backflow preventer works, the American Water College provides an excellent illustration in this video entitled, Backflow Prevention: Fire Hydrants and Valves. What are the Requirements for Backflow Preventers? While the requirement to have backflow preventers in fire protection systems is usually found in local plumbing codes, their installation, inspection, testing, and maintenance generally follow the National Fire Protection Association (NFPA) standards: NFPA 13: Standard for the Installation of Sprinkler Systems NFPA 25: Standard for the Inspection, Testing, and Maintenance of Water-Based Fire Protection Systems Since local plumbing codes also govern backflow preventers, it is important to check with your local water authority to determine if there are any additional requirements for backflow preventers. Some jurisdictions may allow alternatives to backflow preventers depending on the specific situation. However, most water suppliers require backflow preventers on all fire department connections (FDCs) to guard against potential contamination from the non-potable water that firefighters might bring in their vehicles to help fight a fire. This water is often treated with antifreeze, corrosion inhibitors, or extinguishing agents, all of which could pose public health concerns if they were to backflow into the water supply. This is why fire protection systems with FDCs are high-hazard situations with regard to backflow. Testing and Maintenance Requirements One might reasonably assume that NFPA 25 requires testing of any backflow preventers installed on fire protection systems. This used to be the case. However, the 2011 edition of the code removed this requirement -- that and all the editions published since contain requirements for forward flow only. The NFPA explained its decision to remove testing requirements for backflow preventers in the following way: "While backflow remains a legitimate health concern, preventing it is now considered outside the scope of NFPA 25. The standard presumes that local or state requirements will continue to ensure that the devices are properly tested by qualified personnel." This makes sense when one considers that the NFPA's primary focus is on fire safety, not the protection of public water supplies. Firefighters (and the NFPA) are interested in making sure water will flow when needed, which is why forward flow testing is still required. Backflow testing is now regulated by local plumbing code and typically required annually, although it may be required more frequently in some jurisdictions. Backflow tests usually take about 15 minutes to perform and involve trying to force a backflow under protected conditions to see if the assembly functions properly. If any water escapes a device, that device must be immediately repaired or replaced. Repairs can vary from relatively simple things like replacing o-rings and rubber gaskets to replacing one or both valves or replacing the entire assembly. It is important to always work with qualified fire safety professionals when installing and testing backflow preventers in your fire protection system. Improper installation of backflow preventers can lead to premature failure, and improper testing can damage the assemblies. Koorsen can work with you to ensure your fire protection system meets all backflow testing requirements and can help you determine the best and most cost-effective course of action should one or more of your backflow preventers fail. Our certified technicians and engineers can design, install, inspect and maintain all aspects of your fire protection systems and products, including backflow preventers. Contact us today to learn more about our services! Questions? Contact Us Now! Share Topics: Fire Sprinkler Systems, Backflow Preventer Contact Us Now! FIRST NAME* LAST NAME EMAIL* PHONE NUMBER WORK SITE ZIP CODE* WORK SITE CITY WORK SITE STATE HOW CAN WE HELP YOU TODAY? Disclaimer: The information in this article is for informational purposes only. It is believed to be reliable, but Koorsen Fire & Security assumes no responsibility or liability for any errors or omissions in the content of this article. It does not constitute professional advice. The user of this article or the product(s) is responsible for verifying the information's accuracy from all available sources, including the product manufacturer. The authority having jurisdiction should be contacted for code interpretations. RELATED POSTS Taking a Closer Look at Dry Systems What is a Post Indicator Valve (PIV) and Are They Required? How Do Fire Sprinklers Work? What is a Victaulic Coupling? Questions? Contact Us Now! SEARCH OUR BLOG SUBSCRIBE TO OUR BLOG EMAIL* NOTIFICATION FREQUENCY* DAILY WEEKLY RECENT POSTS What Are the Most Popular Kinds of Restaurant Fire Suppression Systems? What Sets Off Kitchen Hood Suppression Systems? Taking a Closer Look at Dry Systems Backflow Preventers – A Critical Component in Fire Protection Systems Types of Access Control Key Cards CATEGORIES Commercial Security (76) Fire Protection (76) Koorsen News (71) Fire Safety & Security (65) Fire Extinguisher (42) see all Koorsen Fire & Security Based on 414 Trustindex reviews. See all reviews Write a review James Jarrell November 24, 2021. They were masked up and ready to do the Job. Was impressed with the knowledge I received from them on my system.. thanks again. Matthew Bazemore November 22, 2021. I am a pastor of a church in Medina and we have worked with Koorsen for several years now. Most recently, after playing phone tag a couple of times, Bob fit me into his schedule right away because of my holiday schedule. I really appreciated him going the extra mile and responding very quickly. He was professional, friendly and prompt with his service. Thank you, Bob and Koorsen! bia November 2, 2021. It’s really cool to find out there is so much that goes on behind fire fighting than simply spraying water at a fire and calling it a day. From the fire extinguishers made of agents that specialize in depriving small fires of oxygen to the fire fighting nozzles and hoses that let firemen battle against the biggest of infernos. My friend is planning on becoming one day and I thought it’d be good if he did some reading on them before applying. This article will be a nice primer for him on the equipment they use, I’ll be sure to send it to him for his reading. https://firesafetyitems.com/ Kerry Mattox October 19, 2021. Courteous, prompt and knowledgeable. Ira Sivley October 6, 2021. Great Teresa Doss October 5, 2021. Always great service no matter the need. Great, professional people everytime. Emma Church September 29, 2021. Very friendly gentlemen arrived to inspect our fire extinguishers. He took care of whatever issue he found during inspections, and left. Very efficient and stress-free for us. :) Rob Webber September 29, 2021. Bob does an awesome and efficient job during his inspections! Kaitlin Bales September 29, 2021. Fast and friendly service Sima Patel (Hampton Inn) September 21, 2021. We had two really nice guys that came out on September 15 , 2021 to check our Fire Alarm System. They answered all of our questions and were very kind. Sima Patel General Manager ALL PRODUCTS AND SERVICES FIRE EXTINGUISHERS GENERAL FIRE PRODUCTS EMERGENCY/EXIT LIGHTING FIRE ALARM SYSTEMS FIRE SPRINKLER SYSTEMS KITCHEN FIRE SUPPRESSION FIRE SUPPRESSION SYSTEMS COMMERCIAL SECURITY EMERGENCY NOTIFICATION COMMUNICATIONS HOME SECURITY NURSE CALL SYSTEMS OTHER COMPANIES KOORSEN ENVIRONMENTAL KOORSEN FACILITIES MANAGEMENT CONTACT KOORSEN 855-622-6583 info@koorsen.com FAQS KOORSEN CAREERS MEDIA RELATIONS © 2021 KOORSEN FIRE & SECURITY | PRIVACY POLICY