Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT SERVICE DROP CABLE - TRIPLEX CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION: To supply power from the utility’s lines to the consumer’s weatherhead. For service at 600 volts or less (phase to phase) at a conductor temperature of 75°C maximum for polyethylene insulation or 90°C maximum for crosslinked polyethylene (XLP) insulated conductors. PRODUCT FEATURES: Conductors are concentrically stranded, compressed 1350-H19 aluminum. Insulated with either polyethylene or XLP crosslinked polyethylene. Neutral messengers are concentrically stranded 6201, AAC or ACSR. STANDARDS: Service drop cable meets or exceeds the following ASTM specifications: • B-230 Aluminum Wire, 1350-H19 for Electrical Purposes • B-231 Aluminum Conductors, Concentric-Lay-Stranded • B-232 Aluminum Conductors, Concentric-Lay-Stranded, Coated Steel Reinforced (ACSR) • B-399 Concentric-Lay-Stranded, 6201-T81 Aluminum Alloy Conductors • B-901 Compressed Round Stranded Aluminum Conductors Using Single Input Wire • ANSI/ICEA S-76-474 KINGWIRE Triplex Service Drop - AAAC-Alloy Neutral Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Minex 6 Solid 45 6 7 1,110 106.6 102.9 85 70 Hippa 6 7/w 45 6 7 1,110 107.0 105.7 85 70 Prawn 4 Solid 45 4 7 1,760 158.4 154.1 110 90 Barnacles 4 7/w 45 4 7 1,760 160.0 157.0 110 90 Shrimp 2 7/w 45 2 7 2,800 243.0 238.0 150 115 Gammarus 1/0 7/w 60 1/0 7 4,460 390.0 384.0 200 155 Leda 1/0 19/w 60 1/0 7 4,460 384.0 378.0 200 155 Dungenese 2/0 7/w 60 2/0 7 5,390 481.0 474.0 230 180 Cyclops 2/0 19/w 60 2/0 7 5,390 473.0 467.0 230 180 Flustra 3/0 19/w 60 3/0 7 6,790 596.0 589.1 260 205 Lepas 4/0 19/w 60 4/0 7 8,560 725.0 716.0 300 235 KINGWIRE Triplex Service Drop - Aluminum Conductor - AAAC - Alloy Reduced Neutral Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Artemia 4 Solid 45 6 7 1,110 134.0 132.0 110 90 Crab 4 7/w 45 6 7 1,110 144.0 141.2 110 90 Solaster 2 7/w 45 4 7 1,760 216.0 212.6 150 115 Sandcrab 1/0 7/w 60 2 7 2,800 348.0 341.0 200 155 Echinus 1/0 19/w 60 2 7 2,800 342.0 336.0 200 155 Crayfish 2/0 7/w 60 1 7 3,530 452.6 422.5 230 180 Sipho 2/0 19/w 60 1 7 3,530 441.0 422.5 230 180 Fulgar 3/0 19/w 60 1/0 7 4,460 525.0 518.0 260 205 Arca 4/0 19/w 60 2/0 7 5,360 640.0 632.0 300 235 KINGWIRE Triplex Service Drop - Aluminum Conductor - AAC - Neutral Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Haiotis 6 Solid 45 6 7 563 102.5 98.8 85 70 Patella 6 7/w 45 6 7 563 104.0 101.6 85 70 Fusus 4 Solid 45 4 7 881 151.9 147.6 110 90 Oyster 4 7/w 45 4 7 881 154.0 151.7 110 90 Clam 2 7/w 45 2 7 1,350 232.0 228.0 150 115 Murex 1/0 7/w 1/0 1/0 7 1,990 374.0 367.0 200 155 Purpura 1/0 19/w 1/0 1/0 7 1,990 368.0 362.0 200 155 Nassa 2/0 7/w 2/0 2/0 7 2,510 461.0 453.0 230 180 Melita 3/0 19/w 3/0 3/0 19 3,310 585.2 562.9 260 205 Portunus 4/0 19/w 4/0 4/0 19 4,020 693.0 684.0 300 235 Nannynose 336.4 19/w 336.4 336.4 19 6,146 1,111.0 1,096.0 380 290 KINGWIRE Triplex Service Drop - Aluminum Conductor - Full Size ACSR Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Paludina 6 Solid 45 6 6/1 1,190 114 113 85 70 Voluta 6 7/w 45 6 6/1 1,190 115 112 85 70 Whelk 4 Solid 45 4 6/1 1,860 163 161 110 90 Periwinkle 4 7/w 45 4 6/1 1,860 172 169 110 90 Conch 2 7/w 45 2 6/1 2,850 262 257 150 115 Neritina 1/0 7/w 60 1/0 6/1 4,380 420 414 200 115 Cenia 1/0 19/w 60 1/0 6/1 4,380 414 408 200 115 Runcina 2/0 7/w 60 2/0 6/1 5,310 519 512 230 180 Triton 2/0 19/w 60 2/0 6/1 5,310 511 505 230 180 Cherrystone 3/0 7/w 60 3/0 6/1 6,620 656 643 260 205 Mursia 3/0 19/w 60 3/0 6/1 6,620 633 626 260 205 Razor 4/0 7/w 60 4/0 6/1 8,350 814 799 300 235 Zuzara 4/0 19/w 60 4/0 6/1 8,350 785 777 300 235 Limpet 336.4 19/w 80 336.4 18/1 8,680 1,160 1,147 300 290 KINGWIRE Triplex Service Drop - Aluminum Conductor - ACSR Reduced Size Messenger Code Word Phase Conductors Bare Neutral Weight per 1000 (lbs) Rating (AMPS) Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Breaking Strength (lbs) XLP Poly XLP Poly Scallop 4 Solid 45 6 6/1 1,190 142 139 110 90 Strombus 4 7/w 45 6 6/1 1,190 151 148 110 90 Cockle 2 7/w 45 4 6/1 1,860 228 224 150 115 Janthina 1/0 7/w 60 2 6/1 2,850 367 360 200 155 Ranella 1/0 19/w 60 2 6/1 2,850 361 356 200 155 Cavolinia 2/0 7/w 60 1 6/1 3,550 452 444 230 180 Clio 2/0 19/w 60 1 6/1 3,550 444 437 230 180 Sanddollar 3/0 7/w 60 1/0 6/1 4,380 570 557 260 205 Aega 3/0 19/w 60 1/0 6/1 4,380 565 552 260 205 Cutlefish 4/0 7/w 60 2/0 6/1 5,310 706 691 300 235 Cerapus 4/0 19/w 60 2/0 6/1 5,310 678 670 300 235 Cowry 336.4 19/w 80 4/0 6/1 8,350 1,135 1,093 380 290 * Note: Designated sizes are ACSR 6/1 diameter equivalent resistivity per ASTM-B-399 for 6201. Conductor temperature of 90°C for XLP, 75°C for Poly; ambient temperatures of 40°C; emissivity 0.9; 2ft/sec. wind in sun. ** To determine current ampacity by conductor size, please consult The National Electric Code, latest edition. The data is approximate and subject to normal manufacturing tolerances. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep