Camfil Clean air solutions Country Please select Search Search Teléfono Archivo / CamTab Acerca de Camfil Industrias Productos Casos Prácticos Tecnología de la filtración Contacto Startpage / Tecnología de la filtración / Especificaciones industriales / EN779:2012 TECNOLOGÍA DE LA FILTRACIÓN LCC - Un aire puro con ventajas económicas Principios de filtración Test y banco de ensayos Especificaciones industriales Normativas ATEX EN779:2012 EN 1822 EN 13779 UL 900 y 586 Camfil da la bienvenida a la nueva ISO 16890 estándar PM1 Norma ISO 14644-1 ASHRAE 52 Gestión de residuos Camfil Software Movies and Media Enlaces importantes Calidad de aire interior Clasificación de ozono R&D network – Tech centre Diccionario EN779:2012 The new standard forces air filters to perform better At Camfil, we have always put every effort into improving indoor environments. Thus, no one is more pleased than us that, from 2012, a new air filter standard imposes tougher requirements. Unfortunately, the requirements are not as tough as we would have liked. For example, our Hi-Flo XLT7 (a class F7 filter) has a minimum filtration efficiency of 54 percent. For an F7 filter, the new standard requires no more than 35 percent. However, that does not meet the quality levels we have set for ourselves. Indeed, our development of the market's most efficient, energyoptimised filters will continue. What does EN779:2012 do? The new European standard for air filters (EN779:2012) comes into force in 2012. Its purpose is to classify air filters based on their lowest filtration efficiency. This latter is also referred to as minimum efficiency (ME). The standard is an initiative that we welcome and a step towards better indoor environments. The new standard will help to eradicate a number of problems. One of these is presented by electrostatic charged synthetic filters. While such filters can demonstrate good initial filtration efficiency, they discharge extremely rapidly. This entails a considerable deterioration in their air cleaning ability. Unfortunately, one result of the foregoing is that far too many European properties are now using F7 class filters that have ME values of between 5 and 10 percent. This means that as much as 90 to 95 percent of the contaminants in the outdoor air find their way into buildings and pollute the indoor environment. By basing classification on ME value, the new standard will force these filters out of the market. At the same time, it will contribute to the development of synthetic filter materials offering considerably higher particle separation. Regrettably, the price for this will include higher pressure drops and increased energy consumption. Not all filters are the same – even when they are in the same class! The problem with the new classification is that, although the worst filters will vanish from the market, there is room for good filters to be made worse. Although energy savings can be achieved by having the lowest possible pressure drop, such development could be retrograde. For example, with 0.4 μm particles, our Hi-Flo XLT7 (class F7) filter has an ME value of a full 54 percent. However, for classification as an F7 filter, the standard requires no more than 35 percent. As we have already made clear, we will not be lowering the efficiency of our Hi-Flo filters. That would result in an approximately 40 percent worsening of air quality. However, there is a risk that other manufacturers will not think the same way. Instead, they may see the standard as an opportunity to reduce pressure drop and, thereby, energy consumption. This will result in poorer air quality. Classification of air filters1) Group Class Final pressure drop (test) Pa Average arrestance (Am) of synthetic dust % Average efficiency (Em) for 0.4 μm particles % Minimum efficiency2) for 0.4 μm particles % Coarse G1 250 50≤Am<65 - - G2 250 65≤Am<80 - - G3 250 80≤Am<90 - - G4 250 90≤Am - - Medium M5 450 - 40≤Em<60 - M6 450 - 60≤Em<80 - Fine F7 450 - 80≤Em<90 35 F8 450 - 90≤Em<95 55 F9 450 - 95≤Em 70 NOTE 1) The characteristics of atmospheric dust vary widely in comparison with those of the synthetic loading dust used in the tests. Because of this, the test results do not provide a basis for predicting either operational performance or service life. Loss of media charge or shedding of particles or fibres can also adversely affect efficiency. 2) Minimum efficiency is the lowest of any of the following three values: initial efficiency, discharged efficiency or efficiency throughout the test’s loading procedure. CONTACT Getting in touch with us is easy Contact details EN779:2012 Download broschure KEEP UPDATED! Subscribe to Camfil newsletter SIGN UP CAMFIL CORPORATE Camfil Contact information Contact us Login web admin Sign in YOU MIGHT BE INTERESTED IN Industrias Industria farmacéutica Agroalimentación Colectores de polvo Hospitales & Salud Microelectrónica Tratamiento de superficie Productos Hi-Flo XLT Opakfil ST Megalam MD14, MX14, MG14-GEL City-Flo XL CamCarb CG Acerca de Camfil Concepto empresarial Áreas de negocio Camfil en todo el mundo Valores esenciales Síguenos en Subscribirse a RSS Política de privacidad y Cookies VIEW FULL SITE MAP