+34 93 586 21 68 +34 93 586 21 69 Languages LOW VOLTAGE CABLES MEDIUM VOLTAGE CABLES ABOUT CONTACT TOPSOLAR H1Z2Z2-K OVERVIEW SPECIFICATIONS TECHNICAL & SALES SUPPORT TÜV solar PV cable. The Topsolar PV H1Z2Z2-K cable, which is TÜV certified according to IEC 62930 and EN 50618, is suitable for both fixed and mobile solar installations (solar farms, rooftop solar installations and floating plants). It is a highly flexible cable compatible with all major connectors and specially designed for the connection of photovoltaic panels. This versatile single-conductor cable is designed to meet the varying needs of the solar industry. Suitable for wet, damp and humid locations. TOPSOLAR PV H1Z2Z2-K cable performance Electrical performance LOW VOLTAGE 1,5/1,5 1kV · (1,8) kV DC. 1,0/1,0 kV · (U0/U). Standard EN 50618/ IEC 62930 / UTE C 32-502 Approvals TÜV / RETIE / CE / RoHS CPR Construction Product Regulation Cca -s1b, d2, a1 Thermal performance Maximum service temperature: 120ºC. Maximum short-circuit temperature: 250ºC (max. 5 s). Minimum service temperature: -40ºC. (fixed and protected installations) Fire performance Flame non-propagation based on UNE-EN 60332-1 and IEC 60332-1. LSHF (Low Smoke Halogen Free) based on UNE-EN 60754-1 and IEC 60754-1. Low smoke emission based on UNE-EN 61034 and IEC 61034: Light transmittance > 60% Low corrosive gases emission based on UNE-EN 60754-2 and IEC 60754-2. Reaction to fire CPR: Cca -s1b, d2, a1, according to EN 50575. Mechanical performance Minimum bending radius: x5 cable diameter. Impact resistance: AG2 Medium severity. Chemical performance Chemical & Oil resistance: Excellent. Grease & mineral oils resistance: Excellent. Ozone resistant based on EN 50618. UV Resistant based on EN 50618. Water performance Water presence: AD8 submerged. Estimated Lifetime Estimated lifetime 30 years based on EN 50618. Other Meter by meter marking. Optional: rodent-proof and termite-proof. Installation conditions Open Air. Buried. In conduit. Applications Solar PV installations. Packaging Available in rolls (lengths of 100 m) and reels. TOPSOLAR PV H1Z2Z2-K cable design Conductor Class 5 (flexible) tinned copper, based on EN 60228 and IEC 60228. Insulation Low smoke halogen Free (LSHF) rubber. Outer sheath Low smoke halogen Free (LSHF) rubber, red or black colour. DOWNLOAD CABLE DATASHEET DOWNLOAD DoP LOW VOLTAGE CA: 0,6/1kV · CC: 1,8 kV Flame non-propagation based on UNE-EN 60332-1 and IEC 60332-1. Maximum service temperature: 120ºC. EN 50618/ IEC 62930 / UTE C 32-502 Solar PV installations. TUV, RETIE, CE, ROHS Cca-s1b,d2,a1 EN 50618/ IEC 62930 / UTE C 32-502 Available in rolls (lenghts of 100m) and reels. Estimated lifetime 30 years based on EN 50618. Technology 1. Conductor Class 5 (flexible) tinned copper, based on EN 60228 and IEC 60228. 2. Insulation Low smoke halogen Free (LSHF) rubber. 3. Outer sheath Low smoke halogen Free (LSHF) rubber, red or black colour. Other cables with similar properties TOXFREE ZH OUTDOOR H07Z1-K (AS) Cu/Sn Flexible and halogen free earthing connections. TOPSOLAR PV DUAL H1Z2Z2-K TÜV and UL solar PV cable. TOPSOLAR PV AL 1500V Aluminium PV cable. TECHNICAL & SALES SUPPORT If you have any questions, please contact us. We’ll do our best to help. Select your country * Afghanistan Albania Algeria Andorra Angola Argentina Armenia Australia Austria Azerbaijan Bahamas Bahrain Bangladesh Barbados Belarus Belgium Belize Benin Bhutan Bolivia Bosnia Botswana Brazil Brunei Bulgaria Burkina Faso Burundi Cambodia Cameroon Canada Central African Republic Chad Chile China Colombia Congo Congo, Dem. Rep. Costa Rica Croatia Cuba Cyprus Denmark Djibouti Dominican Republic Ecuador Egypt El Salvador Equatorial Guinea Eritrea Estonia Ethiopia Finland France French Guiana Gabon Gambia Georgia Germany Ghana Greece Guatemala Guinea Guinea-Bissau Guyana Haiti Honduras Hong-Kong Hungary Iceland India Indonesia Iran Iraq Ireland Israel Italy Ivory Coast Jamaica Japan Jordan Kazakhstan Kenya Kuwait Kyrgyzstan Laos Latvia Lebanon Liberia Libya Liechtenstein Lithuania Luxembourg Macedonia Madagascar Malawi Malaysia Mali Malta Mauritania Mexico Moldova Monaco Mongolia Montenegro Morocco Mozambique Myanmar Namibia Nepal Netherlands New Zealand Nicaragua Niger Nigeria North Korea Norway Oman Pakistan Panama Papua New Guinea Paraguay Peru Philippines Poland Portugal Puerto Rico Qatar Rep. Czech Romania Rusia Rwanda Saudi Arabia Senegal Serbia Sierra Leone Singapore Slovakia Slovenia Somalia South Africa South Korea Spain Sri Lanka Sudan Suriname Sweden Switzerland Syria Tadzhikistan Taiwan Tanzania Thailand Timor-Leste Togo Tunis Turkey Turkmenistan Uganda Ukraine United Arab Emirates United Kingdom United States Uruguay Uzbekistan Venezuela Vietnam Western Sahara Yemen Zambia Zimbabwe Activity* Cable Distributor Cable Installer Contractor Other Student Do you need us to contact you?* Yes No I accept the privacy policy* Notice We and selected third parties use cookies or similar technologies as specified in the cookie policy. In case of sale of your personal information, you may opt out by using the link "Do Not Sell My Personal Information". To find out more about the categories of personal information collected and the purposes for which such information will be used, please refer to our privacy policy. Learn more and customize Reject Accept LOW VOLTAGE CABLES RUBBER CABLES PANEL WIRE CABLES XLPE/PVC POWER CABLES XLPE LSOH SAFETY CABLES CONTROL & SCREENED CABLES SOLAR CABLES LOW VOLTAGE SPECIAL CABLES MARINE CABLES MEDIUM VOLTAGE CABLES RHZ1 HEPRZ1 RHVHMVH TYPES OF CABLES ABOUT CONTACT BLOG RESOURCES LINKEDIN Legacy & Privacy Cookie Policy Top Cable 2021 © All rights reserved