EnerLINE Medium Voltage Switchboards SUBCOE ESP Switchboards EnerLINE DOL Switchboard Front At SUBCOE we understand that the control exerted over the quality of the electric power feeding the motor system may have a big impact on your business. Our SUBCOE EnerLINE direct-on-line and soft starting switchboards are built to meet CSA standards so you will receive years of uninterrupted reliable service. Our CUBE motor controller is integrated to give digital control over the vacuum contactor starter to provide full monitoring and alarming based upon the real time three phase voltage, current, frequency and power factor values. The CUBE directly monitors the medium voltage output to provide near instantaneous short circuit protection for your valuable submersible pump motor. The SUBCOE EnerLINE switchboard may be used with any motor regardless of manufacturer or type. As a standard the board comes complete with fused disconnect switch, vacuum contactor, current limiting fuses, optional amp chart recorder, instrument and control transformers, Rogowski coils (current), lightning arrestors, control switches, push buttons, pilot lights. SUBCOE Switchboard Specifications Enclosure Type IP55, dust/rain proof Application Outdoor Material 2mm thick sheet steel Finish Powder coated smooth Gasket Neoprene Cable terminations separate lockable enclosure Low voltage compartment Separate lockable enclosure High voltage compartment Separate lockable enclosure, door interlocked Base frame 90mm U channel Lifting eye four top mounted Rating Maximum voltage 3600/4800 V Maximum current 160/200 Interrupting current 4400 A Frequency 50/60 Hz Temperature -40 °C to +60 °C Fusing Power Fuse Type Bussman JCL or equivalent Rating 5500 V Interrupting 50 kA Control Fuse Type E rated, current limiting, 5000 V Vacuum Contactor Manufacturer Joslyn Clark/Danaher Voltage Rating 600/1500/2500/3300/5000 V Current Rating 160/200 A Control Voltage 120/240 V, 50/60 Hz Interrupting current 4400 A Expected life 1,000,000 operations Auxiliary Contacts 2 NO & 2 NC Amp Chart Recorder (Optional) Manufacturer Bristol Babcock Enclosure Rating NEMA 4, die cast aluminum Finish Grey epoxy Chart Drive Spring wound Cartridge Fiber tip pen Meter Movement Moving iron Input range 0-5 A Frequency 50/60 Hz Chart 8” circular, 1 or 7 day Obsolete end 2014, SUBCOE ACR replaces Q4-2014 Instrument Transformer Rating 25 VA Primary Voltage 0-3600 V 0-5400 Volt (5 kV board) Secondary Voltage 120 Volt EnerLINE-CUBE EnerLINE CUBE Intelligent Motor Controller Frequency 50/60 Hz BIL 10 kV Control Transformer Rating 1 kVA Primary Voltage 730/860/1020/1205/1420/ 1685/1990/2180/2560/ 3030/3600 V 1900/2100/2300/2800/ 3080/3400/3750/4200/ 4400/4700/5000 V (5 kV board) Secondary Voltage 120 V Phase Single Frequency 50/60 Hz BIL 10 kV Current Transformer Type Current Transformer Ratio 75/100/150/200:5A Rating 600 Volt Frequency 50-400 Hz Power Cable Rating 7500 Volts Size #1/0 AWG tinned stranded copper PT Wire Rating 15000 Volts Size #14 AWG TEW Lugs Type Aluminum Alloy Size #6-350 MCM Paint Description Epoxy powder coat smooth, white or RAL9003 Thickness 5 mil HOME POWER SYSTEMS CONTROL DEVICES OEM MANUFACTURING SERVICES GALLERY CONTACT US NEWS ©Copyright SUBCOE 2015