About company Products and Services | News | Vacancies | Contacts | ABS Electro » Small- channel controller Remikont R-130 » CROSS-500 » Controller MK2 Programmable logic controller MK2 Home Industrial controllers Programmable logic controller MK2 The company "ABS ZEiM Automation" presents a new development - a productive programmable logic controller MK2, included in the line of the industrial controller "KROSS-500" used in heat power engineering, industry and housing and communal services. The new controller is designed to work both as a main processor for systems of small and medium complexity (up to 512 channels when connecting external I / O modules), and as a component in systems with distributed intelligence (while the number of processed signals is practically unlimited) ... The MK2 controller is built on the basis of a 32-bit processor with ARM9 architecture and a clock frequency of 96 MHz (execution time for a thousand instructions - 1 ms), has a full functional set of interfaces (RS-232, RS-485, Ethernet 100 Mb / s, wireless ZigBee interface optional), supports popular Modbus RTU and Modbus TCP protocols, as well as protocols of various meters. The controller is programmed in the ISaGRAF environment, in all languages of the IEC-61131-3 standard, has a wide library of additional algorithms (algorithms from the P-130 controller are implemented, autotuning of regulators, regulators based on fuzzy logic, arrays in the controller's memory, etc.) ). MK2 has the ability to provide hardware redundancy (via Ethernet), connect up to 64 plug-in I / O modules from the KROSS-500 controller or other intelligent devices, hot restart (there is non-volatile RAM), store archives (there is flash memory 512 KB , on request - up to 32 MB), work in an extended temperature range (-40 ... + 85 ° С). A distinctive feature of the MK2 controller is a unique, flexible input-output system that allows you to independently form in the controller any set of input-output channels (up to 32 channels), as well as change the number and types of input-output channels during operation, since channel cells are mounted on connectors. Optionally, the MK2 controller can have a built-in operator panel with a keyboard or additional ports for connecting an external operator panel. For all its functionality, this product has a low cost. Leaflet "Programmable logic controller MK2" 0.7 Mb © 1998 - 2015 ABS ZEiM Automation Russia, 428020, Cheboksary, I. Yakovlev Ave., 1. tel .: (8352) 305-148, (8352) 305-221, fax: (8352) 305-111 e-mail: adm@zeim.ru , sales@zeim.ru