HomeSolutions for you Products About Us Contact Us Quality Downloads Alpha X – Ex cable gland for non-armoured cables Data Sheet Documentation Back Alpha X – Ex cable gland for non-armoured cables Features Nickel plated brass, 304 and 316 stainless steel ISO and NPT sizes Suitable for non-armoured cables Ex II 2GD Increased safety Ex e IIC Gb and Ex tb IIIC Db Explosion proof Ex d IIC Gb Also suitable for industrial and underwater applications Protection class options: IP66 (dust tight and water jet proof) or IP68 (underwater tested) Temperature rating -40ºC to +100ºC (Neoprene seal) and -60ºC to + 180ºC (Silicone seal) Gland accessories including, earth tags, fibre and sealing washers, cable shrouds and lock nuts. Dimensions: from M16 x 1.5 to M110 x 2.0 and NPT 3/8” to 4” Certification IMQ08ATEX021X Ex protection type (EN 50018/IEC 60079-1 and EN 50019/IEC 60079-7) Ex II 2GD Ex e IIC Gb Ex tb IIIC Db Ex d IIC Gb Ingress protection levels IP66 and 68 (EN 60529/IEC 60529) Ambient temperature -40ºC to +100ºC (Neoprene seal) and -60ºC to + 180ºC (Silicone seal) Description CE-TEK’s metallic glands are available as Nickel plated brass and stainless steel variations. CE-TEK’s next generation cable glands meet the latest EN 60079-0:2009 standards for hazardous area application. This group comprises of three ranges – Alpha X, Gamma X and Delta X in nickel plated brass and stainless steel, rated to IP66 as standard and IP68 as an option. Temperature ranges are -40ºC to +100ºC with neoprene seals and -60ºC to +180ºC with silicone seals. Alpha X (Ex d IIC, Ex e IIC Gb, Ex tb IIIC Db, and Ex II 2GD) sizes from M16 to M110 and NPT 3/8” to 4” for non-armoured cables. Article ISO Thread Article NPT Thread Clamping Range Thread length mm > < KU01BPM16 M16 x 1.5 KU01BPN38 NPT 3/8” 3.0 12.0 16.0 KU1BPM20 M20 x 1.5 KU1BPN12 NPT ½” 3.0 12.0 16.0 KU12BPM20 M20 x 1.5 KU12BPN12 NPT ½” 10.0 16.0 16.0 KU2BPM25 M25 x 1.5 KU2BPN34 NPT ¾” 10.0 18.0 16.0 KU23BPM25 M25 x 1.5 KU23BPN34 NPT ¾” 14.0 20.0 16.0 KU3BPM32 M32 x 1.5 KU3BPN100 NPT 1” 14.0 24.0 16.0 KU34BPM32 M32 x 1.5 KU34BPN100 NPT 1” 22.0 28.0 16.0 KU4BPM40 M40 x 1.5 KU4BPN114 NPT 1 ¼” 22.0 32.0 18.0 KU45BPM40 M40 x 1.5 KU45BPN114 NPT 1 ¼” 26.0 34.0 18.0 KU5BPM50 M50 x 1.5 KU5BPN112 NPT 1 ½” 26.0 35.0 18.0 KU56BPM50 M50 x 1.5 KU56BPN112 NPT 1 ½” 35.0 44.0 18.0 KU6BPM63 M63 x 1.5 KU6BPN200 NPT 2” 35.0 45.0 18.0 KU67BPM63 M63 x 1.5 KU67BPN200 NPT 2” 46.0 56.0 18.0 KU7BPM75 M75 x 1.5 KU7BPN212 NPT 2 ½” 46.0 62.0 20.0 KU78BPM75 M75 x 1.5 KU78BPN212 NPT 2 ½” 60.0 70.0 20.0 KU9BPM90 M90 x 2.0 KU8BPN300 NPT 3” 60.0 75.0 20.0 KU910BPM90 M90 x 2.0 KU810BPN300 NPT 3” 75.0 85.0 20.0 KU10BPM100 M100 x 2.0 KU10BPN400 NPT 4” 75.0 85.0 20.0 KU11BPM110 M110 x 2.0 KU11BPN400 NPT 4” 85.0 95.0 20.0 Technical data (Extract) (For detailed information please click here) Protection class IP 66 and 68 (EN 60529/IEC 60529) Dimensions see data sheet Material Nickel Plated Brass, 304 or 316 Stainless Steel Weight see data sheet Resistance Impact resistance – see data sheet Documentation Alpha X Data Sheet – Ex non armoured cable glands Declaration of Conformity Customer requirements Operating Instructions CE TEK is proudly powered by WordPress