BEGINNING ALQUIANSA PRODUCTS SECTORS SOLUTIONS 360º CATALOGS PRESENT CONTACT 954 645 526 CONTACT US CATEGORY: PROJECTS Assembly of scaffolding for the placement of SATE in a wooden house Posting in November 8, 2021by admin Table of Contents Drawing of the scaffolding assembly for the placement of Sate in a wooden house. Photos of the assembly of the scaffolding for the placement of Sate in a wooden house. Anchor testing We are going to mount a scaffold around the perimeter of a wooden house that is built with cross-laminated panels (CLT), in this case they are made up of three layers of spruce sawn and glued, the orientation of their fibers must be transverse between the adjacent layers . It is a versatile system that has surpassed those that have previously been used using wood as a base; it is easy and quick to assemble and allows it to reach heights of similar buildings built with concrete or steel. Panels with at least three layers are used for their manufacture, these must be dry and with a resistance ranging from classes C16 to C24. This type of construction responds to the climatic requirements and the demands of the building, complying with the requirements of the Technical Building Code. In addition to its hydrothermal and acoustic behavior, it is joined by its long useful life and energy savings due to its insulating capacity. En esta ocasión a las cualidades y características del material utilizado para el cerramiento, se le une el recubrimiento de los paramentos de madera con SATE (Sistema de Aislamiento Térmico Exterior), utilizado como aislante tanto para el frio como para el calor, llega a garantizar un ahorro energético de hasta el 60%, evitando la condensación y creando en este caso un doble aislante tanto térmico como acústico. Para la colocación del SATE, Alquiansa utilizará un andamio multidireccional que cubra el perímetro del edificio dando un paso diáfano y corrido a todas sus caras. La complicación la encontramos a la hora de amarrar el andamio a los paramentos pues la madera no es un elemento sobre el que se suela fijar un andamio. Nos remitimos al manual de nuestro fabricante, en el que nos indica la necesidad de realizar el testeo de los anclajes cuando no sabemos la calidad del material sobre el que se van a fijar. Previamente hemos realizado el cálculo de la estructura y la carga que reciben dichos anclajes en sus diferentes puntos. Aplicando el coeficiente de seguridad, mayoramos la carga máxima obtenida y hacemos la comprobación en obra y sobre el panel de madera CLT donde se fijan. Si el valor máximo aportado en el cálculo ha sido 3,2kN, verificamos que los anclajes utilizados llegan a soportar una carga de hasta 14kN, en este punto se produce el desgarro de la madera en el perímetro de dicho anclaje. On many occasions, and especially in old buildings where the façades are being rehabilitated, we find that we are fixing the scaffolding on walls whose base material is disintegrated due to the poor quality of the mortars. In these cases it will be necessary to test the anchors and if they do not comply with the loads they may receive, we will have to provide alternative solutions that guarantee the stability of the installed structure. Drawing of the scaffolding assembly for the placement of Sate in a wooden house. Photos of the assembly of the scaffolding for the placement of Sate in a wooden house. Anchor testing Link to product Transfer of a cannon to the upper galleries of the Archivo de Indias-Sevilla Restoration tower Church of the Holy Spirit La Rambla - Córdoba LOOK FOR CATEGORIES: Our heritage Projects RECENT LOGINS Historical Archive of the Navy in the Campamento neighborhood - Madrid Restoration tower Church of the Holy Spirit La Rambla - Córdoba Assembly of scaffolding for the placement of SATE in a wooden house Transfer of a cannon to the upper galleries of the Archivo de Indias-Sevilla Restoration of walls and vault of the Puerta de la Macarena in Seville FOLLOW US ON FACEBOOK ALQUIANSA SCAFFOLD RENTAL SEVILLA SEVILLA Calle Río Viejo, 22. 41700. Dos Hermanas. Seville. 954,645,526 / 680,401,100 CÁDIZ Calle de Poniente, 9. 11130. Chiclana de la Fra. Cadiz. 956535808 / 606463805 MADRID Calle Lagasca, 95 28006. Madrid. 680 401 102 SOCIAL NETWORKS All rights reserved. Legal notice and privacy and data protection policy . Development by: This website uses cookies, both its own and those of third parties, to collect statistical information about your browsing and show you advertising related to your preferences, generated from your browsing patterns. If you go on surfing, we will consider you accepting its use. More information here . I agree