Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT TYPE SE STYLE (R) CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION KINGWIRE Service Entrance Cable Style R (SER) is used to convey power from the service drop to the meter base and from the meter base to the distribution panel board. It can be used for both above ground service entrance and interior wiring applications at temperatures not to exceed 90°C. PRODUCT FEATURES KINGWIRE Type SE cable is constructed with AA-8000 series aluminum alloy, compact stranded conductors. Cross-linked polyethylene insulation rated for a maximum operation temperature of 90°C in wet and dry locations. Eco friendly sunlight resistant, flame retardant and heavy metal free Polyvinyl Chloride (PVC) Jacket. Insulation and Jacket materials are in compliance with RoHS, Directive 2002/95/EC. Sequential foot markings for easier inventory control management. STANDARDS UL Standard 44 for type XHHW-2 conductors, (UL) Standard 854, Federal Specification JC-30B NEC KINGWIRE Service Entrance Cable Style R (SER) - 2 Conductor with Ground SER Size AWG & Construction Stranding Nominal Diameter (in) Weight per 1000 ft. (lbs) Ampacity (AMPS) * Phase Conductors Equipment Ground Conductor 90˚ C Dwelling 6-6-6 7 - .650 150 60 - 4-4-6 7 - .681 196 75 - 4-4-4 7 - .682 196 75 - Notes: Data are approximate and subject to normal manufacturing tolerances. * To determine correct ampacity by conductor size, please consult the National Electric Code, latest edition. KINGWIRE Service Entrance Cable Style R (SER) - 3 Conductor with Ground SER Size AWG & Construction Stranding Nominal Diameter (in) Weight per 1000 ft. (lbs) Ampacity (AMPS) * Phase Conductors Equipment Ground Conductor 90˚ C Dwelling 8-8-8-8 Solid Solid .588 128 45 - 6-6-6-6 7 7 .684 180 60 - 4-4-4-6 7 7 .754 240 75 - 2-2-2-4 7 7 .893 344 100 100 1-1-1-3 19 7 1.003 432 115 110 1/0-1/0-1/0-2 19 7 1.097 521 135 125 2/0-2/0-2/0-1 19 19 1.197 633 150 150 3/0-3/0-3/0-1/0 19 19 1.314 771 175 175 4/0-4/0-4/0-2/0 19 19 1.443 942 205 200 250-250-250-3/0 37 19 1.601 1106 230 225 300-300-300-4/0 37 19 1.719 1360 255 230 KINGWIRE Service Entrance Cable Style R (SER) - 4 Conductor with Ground SER Size AWG & Construction Stranding Nominal Diameter (in) Weight per 1000 ft. (lbs) Ampacity (AMPS) * Phase Conductors Equipment Ground Conductor 90˚ C Dwelling 2-2-2-2-4 7 7 1.004 450 100 100 2/0-2/0-2/0-2/0-1 19 19 1.346 824 150 150 4/0-4/0-4/0-4/0-2/0 19 19 1.621 1226 205 200 250-250-250-250-3/0 37 19 1.950 1454 230 225 Notes: Data are approximate and subject to normal manufacturing tolerances. * To determine correct ampacity by conductor size, please consult the National Electric Code, latest edition. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep