(903) 534-7052 office@tylerfire.com Products Services FAQ About Contact (903) 534-7052 STORED PRESSURE FIRE EXTINGUISHERS SENTRY Dry Chemical Fire Extinguishers Versatile fire protection: Compact and Portable Simple Operation and Maintenance Rechargeable Built for Commercial Environments Economically Priced Various Agent Options Six-Year Limited Warranty Corrosion-Resistant Finish and High-Flow Models Fire Protection Anywhere You Need It Compact and portable, SENTRY dry chemical extinguishers are designed for the protection of light and ordinary hazards and are suited for commercial fire protection needs. Found virtually anywhere a general-purpose fire extinguisher is needed, they are economically priced without sacrificing performance. Powerful and engineered to last, these extinguishers are UL/ULC listed, USCG approved and comply with NFPA 10. Specific Agents Are Available to Fight Class A, B or C Fires ■ FORAY Dry Chemical—A monoammonium phosphate-based agent for use on Class A (wood, paper, cloth), Class B (flammable liquids and gases), and Class C (electrical) fires. ■ Purple-K Dry Chemical—A potassium bicarbonate-based agent that is the most effective dry chemical for knock-down and suppression of Class B (flammable liquids and gases) and Class C (electrical) fires. ■ PLUS-FIFTY C Dry Chemical—A sodium bicarbonate-based agent for use on Class B (flammable liquids and gases) and Class C (electrical) fires. Top Quality Construction for Top-of-the-Line Performance Standout features include a seamless steel cylinder with high tensile strength and 100% factory air tested in excess of 600 psi (41.4 bar). These compact and lightweight extinguishers consist of aluminum alloys and plated steel components with tough exterior shell coatings. In addition, valve bodies are made from a durable extruded aluminum alloy. Valve assemblies feature plated steel valve stems that contain o-ring and seat material compatible with the agent to provide reliable performance and long life. Rugged all-steel pick-up tubes provide proper and dependable agent flow through the valve body. Extinguisher sizes are 2.5 lb (1.13 kg), 5 lb (2.27 kg), 10 lb (4.54 kg) and 20 lb (9.07 kg) agent capacity. High-Flow Models Meet NPFA 10, Section 5.5 SENTRY High-Flow Extinguishers are available with 10 lb and 20 lb (4.54 kg and 9.07 kg) dry chemical agent capacities and flow rates of 1 lb (0.45 kg) per second or greater in accordance with NFPA 10 Standard, Section 5.5. Typical hazards for high-flow, stored pressure units include pressure fires commonly found in gas stations, propane filling/storage facilities, maintenance shops and small paint spray booths. Serving East Texas Since 1949 Get In Touch Charging Inspection Training Kitchens Food Trucks CO2 Water Stored Pressure Signs & Lighting Restaurant FAQ © 2021 Tyler Fire Extinguisher Company | Designed and Powered by Lightray Photoimagery