Search 0 items(s) in your Cart Check Valves & Backflow Preventer Acces. Send this Page MONITEUR 41N-E1N-SF AM41NE1NSF Moniteur 41N-E1N-SF 41 Series Electro-Pneumatic Valve Positioner, 1/4 in NPT, -4 to 158 deg F, Metal Brand Name: Moniteur Manufacturers: Moniteur Devices MKSPN: AM41NE1NSF MPN: 41N-E1N-SF Min. Order Qty: 1 Qty. Interval: 1 Availability: Call for Availability LOGIN OR REGISTER FOR PRICING Qty ADD TO CART Add To Product Group DESCRIPTION Improving control through advanced technology. Moniteur's Series 40N /41N pneumatic (3-15psi) and electro-pneumatic (4-20mA) valve positioners are advanced control devices which provide unparalleled stability in difficult environments. In virtually any application, this positioner's performance is improved compared with typical spool valve type designs. Moniteur Valve Positioner, Electro-Pneumatic, Series: 41 Series, 1/4 in NPT, -4 to 158 deg F, 20 to 100 psig Supply, 4 to 20 mA at 24 VDC, Metal SPECIFICATIONS Connection Size : 1/4 in NPT Material : Metal Series : 41 Series Specifications : 20 to 100 psig Supply, 4 to 20 mA at 24 VDC Temperature Rating : -4 to 158 deg F Type : Electro-Pneumatic FEATURES Unique magnetic torque motor 4 to 20 mA input automatically compensates for supply pressure, atmospheric pressure and ambient temperature changes, and is unaffected by EMF The vibration resistant design has no resonance effects from 5 to 200 Hz, in real life, the performance and sensitivity are clearly superior to standard valve positioner designs Reduced bleed pilot valve reduces air consumption by more than 50% - No Spool Valves are used for air delivery, improving resistance to dirty plant air Rugged aluminum housing with a triple corrosion-resistant interior and exterior coating stands up to harsh environments Precise calibration with simple span and zero adjustments Precision zero hysteresis coupling system for NAMUR actuators provides superior accuracy and repeatability by eliminating slop Stainless steel gauges standard Optional limit switches and 4 to 20 mA feedback Each valve positioner performance tested, test results included in the box with each positioner guarantee consistent performance 250 +/- 15 Ohm impedance 0 to 90 deg stroke range 7 scfm air delivery 0.15 scfm air consumption 1/8 NPT gauge ports and 1/4 in NPT supply or outlet +/- 1 % linearity, hysteresis and +/- 0.5 % sensitivity, repeatability Electrical rating: Ex md IIT6 Pilot valve: Standard orifice S: Standard gauges Indication: Flat dial DOCUMENTS Catalog Specification Sheet Recently Viewed Items Moniteur AMYB-5120 COMPANY INFORMATION About Us Our Manufacturer Blog Events CUSTOMER SUPPORT Contact Us Line Cards PRODUCT SUPPORT Your Orders Return & Cancellation Location EMAIL SUBSCRIPTION Sign me up B2B eCommerce platform powered by Unilog Copyright © 2021 MKS Pipe and Valve.