+7 (812) 200-47-00 RU EN CONTACT INFO COMPANY SERVICE FIRE PROTECTION As part of the R & D developed a unique innovative products INFLEX® are produced and used. Fire-retardant mesh INFLEX®-FK-31 allows efficient and guaranteed to provide fire protection for cable lines. Compositions INFLEX®FO-11 (FV-11) and INFLEX®FA-21 - high-tech solutions improve the fire resistance of bearing metal constructions, including in terms of hydrocarbon fire. REASONABLE CHOICE Company Experts have developed, certified and now produce INFLEX®-FK-31, a unique cable fire-protection system, which is a special mesh impregnated with a fire-retardant compound that intumesce under high temperatures and protects cables against fire spread. Fire-retardant mesh is designed for protection of cables with decreased parameters of fire-protection, including the conditions of increased humidity; for cable protection at reconstruction facilities; for protection of cables with «old» fire-retardant coatings, without their disassembly. Unlike intumescent fire-retardant paints, special equipment and skills are not required during the installation, it is easily controlled during operation and installation. INFLEX®-FK-31 INFLEX®-FK-31 performs several functions: • Prevents flame spread along electric cable sheaths in case of fire in accordance with GOST R 53311-2009. • Localizes fire emerging in the cable line (cable tray) – high-tensile foam is formed in the ignition point, forms a protective closure which prevents the outside oxygen from penetrating and development of heat source. • Decreases effects of ignition – toxicity, smoke formation, corrosion activity of smoke- and gas emission products during burning and smoldering of materials of integrated cable system. ADVANTAGES Operation time is over 25 years. No repair, restoration, maintenance costs during the whole service life. Restoration of cable line fire-protection during cable repair, replacement, disassembly/assembly hardly requires additional costs. In the places of heated cable the materials change colour, which allows for defining the place of potential breakdown visually. INFLEX®-FK-31 perforation ensures normal natural ventilation of cables. High technological properties of assembly guarantees the possibility of works performance under any ambient conditions – temperature, humidity, lack of space, without the necessity of cable surface preparation. TESTS The fire retardant mesh INFLEX®-FK-31 has been successfully tested in accordance with GOST 53311-2009 "Fireproof cable coatings. Methods for determining the flame retardant efficiency ", on the basis of which the certificate of conformity No.C-RU.PB25.V.03554 of February 24, 2016 was obtained CONCLUSION Based on the results of the tests carried out, the fire retardant (fire retardant mesh) for cables has a fire retardant efficiency according to GOST R 53311-2009. APTEKARSKAYA NAB., 8A, “LUKOIL”, SAINT-PETERSBURG, RUSSIA, 197022 Subscribe for newsletters and receive news about the state-of-the-art process solutions from «UIC». Сalculate an individual design Send a request