HOME APPLICATIONS CLOSE COUPLED PUMPS SELF PRIMING PUMPS BOILER FEED & CONDENSATE VACUUM PUMPS CONTACT Russell VA612SS Tank Mounted, Close Coupled, All Stainless Centrifugal Pump VA612SS CUT SHEET VA612SS IOM VA612SS Capabilities Maximum Working Pressure 175PSI Maximum Gallons Per Minute 120 Maximum Head Produced 147 FT. RPM 3450 Maximum Seal Cavity Temp Buna-N 225˚F EPT 300˚F Viton 400˚F Maximum Horsepower 3 View fullsize Design Features CASING Constructed of cast 304 stainless steel, 1/8 npt drain port and 1/4 npt discharge tappings are standard. Back pull out design allows the pump to be serviced without disturbing the piping. The volute was designed to maximize hydraulic efficiency. MECHANICAL SEAL Type 21 buna-n seal is rated to 225°F and pressure to 175PSI. Carbon seal face mates with the ceramic seat providing years of trouble free service. Alternate seals available upon request. IMPELLER The hydraulic design of the impeller maximizes pressure and gpm while minimizing horsepower. The enclosed impeller is made of cast 304 stainless steel. ADAPTER The precise machining of the adapter allows for easy assembly of the pump. A 1/8 npt hole is provided if a seal flush line is added. Construction consists of cast 304 stainless steel. MOTOR The NEMA 56J motor utilizes a 416 stainless steel shaft. The motor’s heavy duty ball bearings withstand axial and radial thrust loads with no problem. Standard Enclosure type is drip proof but alternates are available. Pump Curve Click Here Technical View fullsize View fullsize View fullsize View fullsize View fullsize 102 W. Chicago Street | Albion, IA 50005 | (641) 488-2319 | russpump@heartofiowa.net Site by: BonardiMedia.con Copyright 2018 - Russell Pump & Engineering Inc.