COMPANY (CURRENT) PRODUCTS MARKETS DISTRIBUTORS AND AFFILIATES ONEWS CONTACT IT IS CPR The CPR Regulation defines as Construction Product all those destined to be permanently incorporated into construction works. The Construction Products Regulation (CPR) is the new European legislation that establishes the basic requirements and harmonized essential characteristics that all products intended for construction must comply with the scope of application in the EU. . The CPR specifies seven basic safety requirements to be met by construction sites and one of them is safety in case of fire. The CPR Regulation defines a construction product as all those destined to be permanently incorporated into construction works, in a broad sense, not only buildings but also civil engineering works. Therefore, power, communications, data and control cables are included. The essential characteristics currently applicable for cables in the field of CPR are the reaction to fire and the emission of dangerous substances in normal operation. The European Union has created a single and uniform classification criterion throughout Europe, a common language to define the reaction to fire performance of cables; For this, classes have been defined that indicate the contribution to the development of the fire of the cables based on a series of parameters obtained in the corresponding tests. The figure summarizes the different classes, each with its classification criteria and the additional classification, if any. OPTRAL has a range of products that comply with this regulation. To see the catalog of available products click here . Smoke opacity: s1: low production and slow smoke spread. s1a: s1 and smoke transparency higher than 80% (UNE-EN 61034-2). s1b: s1 and smoke transparency greater than 60% and less than 80% (UNE-EN 61034-2) s2: intermediate values of smoke production and spread. s3: neither s1 nor s2. Droplet detachment during combustion: d0: without falling drops and flaming particles for 1200 s (UNE-EN 50399). d1: no falling drops and flaming particles for more than 10 s (UNE-EN 50399). d2: neither d0 nor d1. Acidity of the fumes: a1: low acidity (UNE-EN 60754-2 -> conductivity <2.5 μS / mm and pH> 4.3). a2: valor intermedio de acidez (UNE-EN 60754-2conductividad<10 μS/mm y pH> 4,3). a3: ni a1 ni a2. [Fuente extraída de la Asociación Española de Fabricantes de Cables y Conductores Eléctricos y de Fibra Óptica]. * Si esta interesado en obtener la Declaración de Prestaciones de OPTRAL, puede solicitarlo a través del formulario de contacto. COMPAÑÍA (CURRENT) PRODUCTOS MERCADOS DISTRIBUIDORES Y FILIALES ONEWS CONTACTAR SUSCRIPCIÓN A NUESTRA NEWSLETTER Suscribirse CENTRO TECNOLÓGICO Y PRODUCTIVO: Pol. Industrial - Ctra. BV-5128 Km-22 08359 Sant Iscle de Vallalta (Barcelona) T. +34937418686 - Fax. +34937418699 optral@optral.com MADRID OFFICE: Av. De la Industria 32 - PAYMA Building - 2ª Pl - Office 2P 5-1 28108 Alcobendas (Madrid) Sales Office: +34 902 401 213 / Fax. +34 913 590 849 T. Administration: +34 937 418 686 / Fax. +34 913594509 info@optral.com PRODUCTION AND LOGISTICS CENTER: Calle Comunidad de Castilla y León, parcela 12 22520 Fraga (Huesca) T. +34 937 418 686 Optral © 2021 | Legal Notice | Terms of use | Cookies policy | JCS cookies We inform you that we use cookies to improve the browsing experience. By accepting this notice, you are accepting its full use. If you want to know what cookies we use and select the ones you want to accept, please go to "settings". To accept Settings