HIGH MODULATION MIXER High modulation at a minimum cost! The Polidoro HM MIXER fits perfectly into the current pneumatic control systems without modifying any components even electronic, doubling the existing modulation range. Minimum impact therefore means minimum cost. Why high modulation? High modulation, for example 1:10 allows for an increase in the efficiency of the system, reducing the number of on/off cycles. On the future ERP labeling, this means moving towards higher classes (A; A+; A++; A+++) makes the boiler compatible for connection to solar panels broadens the scope of applications allowing for a reduction in the number of sizes of devices lowers the “weighted” emissions values from the device, thanks to a broader modulation range on the lower end Operation: The Polidoro HM MIXER mounts a venturi with a neck with modular sections. A non-return valve (clapet) within partializes the section by the movement induced by the force of gravity. Applicability: Polidoro produces the following types of HM MIXERS: MINI L=60mm Ø 64 – from 2 to 55kW, according to the components of the system BIG L=105mm Ø 82 – up to 120kW, according to the components of the system The Polidoro HM MIXER is made up of: flange for connection to the fan plastic venturi of different diameters according to the power required heavier clapet: this is the key component since with its weight it closes or opens one of the two channels, rendering it a device with modular sections and therefore allowing the extension of the modulation range from 1:5 to 1:10 lighter flap: closes the gas inlet when a channel is closed, eliminating any recirculation List of applications associated to this product WALL-HUNG CONDENSING BOILERS FLOOR-STANDING BOILERS STORAGE WATER HEATERS CATERING EQUIPMENT HIGH OUTPUT GAS HEATING UNITS Technical Drawings High Modulation Mixer Download REQUEST INFORMATION Fill in the form below to ask questions about the company or the products. REQUEST FROM:* Company Private I agree to the processing of my personal data THE POLIDORO STORY The business was established in 1945. It has been a great adventure in technological development, production and continual innovation lasting over half a century. COMBUSTION RESEARCH CENTRE There are 7 labs available to our customers for running combustion, adaptability and operating tests. SALES NETWORK Our products are exported all over the world. Please, look up the dealer nearest you. POLIDORO Via Lago di Misurina 76, 36015 - SCHIO (italy) - tel.+39 0445/678678 fax+39 0445/678679 - P.IVA 02907940247 R.E.A n.283561/Vicenza | Capitale sociale: €24.000.000,00 i.v. handmade by studio375.it We use cookies to ensure that we give you the best experience on our website. If you continue to use this site we will assume that you are happy with it.Ok