Since 1973 CALL TOLL-FREE +1 (888) 347-8265 44313 PROGRESS WAY CHILLIWACK, B.C., CANADA HOME ABOUT SERVICES PRODUCTS CERTIFICATIONS GALLERY CONTACT PRODUCTS ULC LISTED PRODUCTS AVAILABLE ULC S601 Horizontal Single Wall for Flammable Liquids ULC S601 Horizontal Double Wall Vacuum Monitored for Flammable Liquids ULC S601(S653) Horizontal Contained Tank Assembly for Flammable Liquids ULC S601(S603) Vertical Single Wall for Flammable Liquids ULC S601(S603) Vertical Double Wall Vacuum Monitored for Flammable Liquids ULC S601(S603) Vertical Contained Tank Assembly for Flammable Liquids ULC S655 Horizontal Fireguard Storage Tank ULC S655 Vertical Fireguard Storage Tank ULC S655 Cylindrical Fireguard Storage Tank ULC S652 Horizontal Double Wall Vacuum Monitored for USED OIL ULC S652 Horizontal Contained Tank for USED OIL ULC S652 Vertical Double Wall Vacuum Monitored for USED OIL ULC S652 Vertical Contained Tank for USED OIL ULC S602 Horizontal Single Wall for Fuel Oil & Lubricating Oil ULC S602 Horizontal Double Wall for Fuel Oil & Lubricating Oil ULC S602 Horizontal 1/2 Obround contained for Fuel & Lubricating Oil ULC S602 Horizontal Contained Tank for Fuel Oil & Lubricating Oil ULC S602 Vertical Single Wall for Fuel Oil & Lubricating Oil ULC S602 Vertical Double Wall for Fuel Oil & Lubricating Oil ULC S602 Vertical Contained Tank for Fuel Oil & Lubricating Oil UN to CAN/CGSB-43.146-2002 Intermediate Bulk Container (IBC) for the Transportation of Dangerous Goods UNDERGROUND TANKS ULC S603 Unprotected Single Wall ULC S603 Unprotected Double Wall Vacuum Monitored ULC S603.1 Protected Single Wall ULC S603.1 Protected Double Wall Vacuum Monitored ULC S603.1 Protected Single Wall Oil/Water Separator ULC S603.1 Protected Double Wall Vacuum Monitored Oil/Water Separator PRODUCTS HORIZONTAL DOUBLE WALL VACUUM MONITORED FOR FLAMMABLE AND COMBUSTIBLE LIQUIDS The DWVM includes cathodic protection (ULC spec. CAN/ILC S603.1-92), screwed openings c/w nylon isolating bushing, exterior coal tar epoxy coated c/w sacrificial magnesium anodes and remote audio/visual vacuum monitoring (leak detection) system. Also comes with containment chamber for grade for housing vacuum monitoring. Optional Features: Containment chamber for monitoring double wall piping, interior lining, hold down straps, piping, fittings and complete pumping/dispensing system. INTERMEDIATE BULK CONTAINER FOR TRANSPORTATION OF DANGEROUS GOODS Intermediate Bulk Container for Transportation of Dangerous Goods Available in Single OR double wall contained The tank is manufactured and labeled to CAN/CGSB-43.146-2002 c/w certification label. Single Wall: 12 gallon plate construction with a fill cap, pressure relief valve, gate valve and suction pipe. Also included are hold down straps c/w nuts and washers and one coat of red industrial enamel. Available in 50, 70, 100 and 135 gallon. Options for Single Wall are lifting lugs and locking fill cap. Double Wall: 12 gallon plate construction with a locking fill cap, pressure relief valve, gate valve, suction pipe and baffle. Also included are hold down straps c/w nuts and washers, lifting lugs for handling tank full of product and one coat of industrial enamel. Available in 85 and 110 gallon. For weights and measurements call us at 604-793-9734 HORIZONTAL DOUBLE WALL VACUUM MONITORED WITH POSITIVE LEAK DETECTION FOR FLAMMABLE LIQUIDS Horizontal Double Wall construction with factory installed “Positive, Continuous Leak Detection System” c/w Visual Monitor (Remote Audible System also available). The DWVM includes a 95% overfill prevention system, lockable fill/spill box c/w drain back tank and locking cap and collar. Additional features include: Ladder and platform, bottom or top discharge, sounding port and wear late, atmospheric and emergency venting, support saddles, sandblasted and one coat of Self-Priming Industrial Enamel. Standard and custom sizes up to 200,000 litres Optional Features: Paint systems and linings DOWNLOAD FILE HORIZONTAL DOUBLE WALL VACUUM MONITORED FOR FUEL OIL AND LUBRICATING OIL Manufactured and labeled to ULC S602-DBL Wall with factory installed “Positive, Continuous Leak Detection System” c/w Visual Monitor (Remote Audible System also available). The DWVM includes screwed openings to suit top centerline of tank, 1 set of saddles and bands, sandblasted and one coat of Self-Priming Industrial Enamel and grounding lugs. Available up to 2500 litres DOWNLOAD FILE HORIZONTAL CONTAINED TANK ASSEMBLY FOR FLAMMABLE LIQUIDS “The Regal “Enviro-Safe” Contained Tank Assembly is a combination of a “ULC Listed Aboveground Horizontal Tank” housed in it’s own “Steel Dyking System”. The need for any further dyking or burning has virtually been eliminated, however it is advised to consult with the authority having jurisdiction if any further environmental or safety precautions as required. The tank is portable and easy to install as well as has adaptability for custom configurations for pump, hose reel and cabinet mounting, It has a sealed dyking system designed to withstand air pressure testing, full flooding and gasoline explosions. The steel sub frame comes with stair, platform and handrails, as well as a 95% capacity overfill protection. Optional Features: Lockable fill/spill box w/c drain back to tank and lockable cap and collar, bottom discharge with inline anti siphon valve and exterior operated enclosed fire safe shut off valve, discharge dip collector with drain port, dyke sump and suction assembly, atmospheric and emergency venting, sandblasted and coated with Self-Priming Industrial Enamel. Standard and custom sizes up to 95,000 litres HORIZONTAL CYLINDRICAL CONTAINED TANK ASSEMBLY FOR FLAMMABLE LIQUIDS The tank includes top or bottom discharge with sealed diking system (air pressure tested) as well as striker (wear) plate under sounding (dipping) opening in primary tank. Additional Features: Saddles and bands, heavy duty sub frame or skid options, access stair c/w handrail, galvanized sure grip treads and grating OR step access, condensation removal suction tube assembly installed in dike, lockable fill/spill containment box c/w 4″ locking cap and collar, sounding port with caps, pump with drain back to tank valve. Also 95% overfill protection assembly c/w aluminum drop tube, normal and emergency venting, sandblasted and one coat of Self-Priming Industrial Enamel. Standard and custom sizes up to 95,000 litres Optional Features: Linings and compete pumping systems DOWNLOAD FILE 1/2 OBROUND CONTAINED TANKS FOR FUEL OIL AND LUBRICATING OIL The tank includes 110% secondary containment as well as 6 – 2″ NPT top openings. Also includes secondary containment pump out access opening, vent pipe and cap. Optional Features: Top discharge, lifting lug, hold down system, sandblasted and white enamel finish. Standard and custom sizes up to 500 litres (110 gallon) DOWNLOAD FILE HORIZONTAL CONTAINED TANKS FOR FUEL OIL AND LUBRICATING OIL The tank includes 110% secondary containment as well as 6 – 2″ NPT top openings. Also includes secondary containment pump out access opening, vent pipe and cap. Optional Features: Top discharge, lifting lug, hold down system, sandblasted and white enamel finish Standard and custom sizes up to 2500 litres DOWNLOAD FILE HORIZONTAL CONTAINED TANKS FOR USED OIL The tank includes 110% secondary containment as well as lockable used oil hopper c/w straining screen, 2″ diameter, suction pipe, male camlock and cap. Optional Features: Step-up platform for smaller sizes, stairs (if required) for larger sized tanks, support saddles (4-leg brackets for smaller sizes), vent pipe and cap, atmospheric and emergency venting, sandblasted and one coat of Self-Priming Industrial Enamel Standard and custom sizes Optional Equipment: Painting systems and linings FIREGUARD ABOVEGROUND STORAGE TANKS Fireguard tanks include 2 hour fire rated protected tanks that are available in both ULC and UL listings. They have built in secondary containment, light weight thermal insulation and are manufactured to STI, ULC and UL stringent specifications. Every Fireguard Tank comes with a 30 year warranty. Standard and custom sizes Optional Features: Heavy duty skids, dispensing systems, special paints and linings, ladder and platforms DOWNLOAD FILE VERTICAL DOUBLE WALL VACUUM MONITORED WITH POSITIVE LEAK DETECTION FOR FLAMMABLE LIQUIDS DWVM includes a vertical double wall construction with a factory installed “Positive, Continuous Precision Leak Detection System” c/w Visual Monitor (Remote Audible System also available). Also included is a 95% overfill prevention system, lockable fill/spill box c/w drain back to tank and locking cap and collar, atmospheric and emergency venting, sandblasted and one coat Self-Priming Industrial Enamel. Standard and custom sizes Optional Equipment: Paint systems and linings DOWNLOAD FILE VERTICAL DOUBLE WALL VACUUM MONITORED WITH POSITIVE LEAK DETECTION MODEL LPV-2500 DW FOR USED OIL Additional Features: Large galvanized non-slip pouring platform c/w kick plate and direct one step access, heavy duty sub frame mounted underside, atmospheric and emergency venting, sandblasted and coated with Self-Priming Industrial Enamel Standard and custom sizes Optional Features: Painting systems and linings, optional two (2) hour fire ratings, also available for gas and fuel dispensing DOWNLOAD FILE VERTICAL CONTAINED TANK ASSEMBLY FOR FLAMMABLE LIQUIDS ULC listed, low profile vertical tank built heavy duty with 3/16″ minimum thickness. Has 110% secondary containment with a sealed diking system (air pressure tested). Additional Features: 95% overfill prevention system, lockable fill/spill box c/w drain back to the tank and locking cap and collar, atmospheric and emergency venting, sandblasted and one coat of White Self-Priming Industrial Enamel Standard and custom sizes Optional Equipment: Painting systems, linings and equipment DOWNLOAD FILE VERTICAL CONTAINED TANK FOR USED OIL ULC listed, low profile vertical tank built heavy duty with 3/16″ minimum thickness. Has 110% secondary containment with a sealed diking system (air pressure tested). Additional Features: 2 sleepers, dip tube monitored leak detection, atmospheric venting, emergency venting lockable used oil hopper c/w straining screen, fixed suction pipe c/w camlock, 1-step for 500 gallon (none required for smaller sizes), sandblasted and one coat of White Self-Priming Industrial Enamel Standard and custom sizes Optional Features: Painting systems, linings and equipment DOWNLOAD FILE INTERMEDIATE BULK CONTAINERS INTERMEDIATE BULK CONTAINERS FOR THE TRANSPORTATION OF DANGEROUS GOODS Manufactured to CAN/CGSB-43.146-2002 Available in Single Wall and Double Wall Contained Manufactured & labeled to CAN/CGSB-43.146-2002 c/w Certification label REGAL “ENVIRO-SAFE”® ABOVEGROUND SINGLE WALL: – 12 gallon plate construction – Fill cap – Pressure relief valve – Gate valve – Suction pipe – Hold down straps c/w nuts & washers – One coat of Red Industrial Enamel -* Baffle Sizes Available in Single Wall: 50 gallon 70 gallon 100 gallon 135 gallon Options for SW: – Locking lugs – Locking fill cap REGAL “ENVIRO-SAFE” ABOVEGROUND DOUBLE WALL: – 12 gallon plate construction – Locking fill cap – Pressure relief valve – Gate valve – Suction pipe – Baffle – Hold down straps c/w nuts & washers -Lifting lugs for handling tank full of product – One coat of Red Industrial Enamel Sizes Available for Double Wall: 85 gallon 110 gallon WEIGHTS AND MEASURES – 12 GAUGE CONSTRUCTION DOWNLOAD FILE ABOUT US Regal Tanks Ltd. under the brand name of Tidy Steel-Fab Ltd. has been fabricating Tanks for liquid storage including Diesel, Gasoline and Jet Fuel and other various chemicals. Regal Tanks are sold and distributed throughout the world. QUICK LINKS Home About Services Products Certifications Gallery Contact CONTACT US 44313 Progress Way, Chilliwack, B.C., V2R 0L1, Canada Toll Free: +1 (888) 347-8265 Fax: +1 (604) 792-1880 Email: sales@regaltanks.com Hours of Operation: Monday – Friday: 7:00AM to 3:30PM © 2021 Regal Tanks Ltd. | Website by Agency Media