home Site sections ↓ Engines Spare parts Synchronous generators Leroy-Somer Generators LSA 40 VS1 LSA 40 VS2 LSA 40 S3 LSA 40 S4 LSA 40 M5 LSA 40 L7 LSA 42.3 VS1 LSA 42.3 VS2 LSA 42.3 VS3 LSA 42.3 S4 LSA 42.3 S5 LSA 42.3 M7 LSA 42.3 M8 LSA 42.3 L9 LSA 43.2 L65 LSA 43.2 L8 LSA 44.2 VS3 LSA 44.2 VS45 LSA 44.2 S7 LSA 44.2 S75 LSA 44.2 M95 LSA 44.2 L12 LSA 46.2 M3 LSA 46.2 M5 LSA 46.2 L6 LSA 46.2 L9 LSA 46.2 VL12 LSA 47.2 VS2 LSA 47.2 S4 LSA 47.2 S5 LSA 47.2 M7 LSA 47.2 M8 LSA 47.2 L9 LSA 49.1 S4 LSA 49.1 M6 LSA 49.1 M75 LSA 49.1 L9 LSA 49.1 L10 LSA 49.1 L11 LSA 50.2 M6 LSA 50.2 L7 LSA 50.2 L8 LSA 50.2 VL10 Generators Linz Electric Baranchinskie generators Kursk generators Delivery Company Special offers Site Map Synchronous generator Leroy-Somer LSA 40 S4 (Leroy-Somer, France) ↓ Characteristics of the Leroy-Somer LSA 40 S4 synchronous generator: Power: 14 kW / 17.5 kVA Voltage: 400/230 V Current: 25.2 A AC current, three-phase / single-phase, frequency 50 Hz Rotation speed: 1500 rpm Efficiency : 86% Body length: 435 mm Weight: 92 kg Leroy-Somer LSA 40 S4 synchronous generators (Leroy-Somer, France) have a built-in brushless self-excitation system and automatic voltage regulation (AVR). • Accuracy of voltage maintenance in steady state not more than 0.5%. • Allowed to load 110% of rated power for 1 hour every 6 hours of operation, 120% of rated power for 2 minutes. • Short overloads (up to 10 seconds) can be up to 300% of the generator rated current (with AREP and PMG excitation systems) or 200% of the generator rated current (with SHUNT excitation system). • The coefficient of nonlinear distortion of the output voltage (the content of higher harmonics) - less than 4%. • The generator winding is in a "star" scheme with a step of 2/3 and has 12 outputs. • Reduced reactance of the stator winding due to the increased air gap between stator and rotor. • Anti-condensation heaters with sensors for winding temperature, temperature and bearing vibration. • Insulation with material class H. • Minimum standard of protection - IP23, upgradeable to IP44, IP54, IP55 is possible. • Service life of 1,000,000 hours. • Leroy-Somer LSA 40 VS1 generators are manufactured in full compliance with European standards IEC 60034, NEMA MG 1.22, ISO 8528-3, CSA / UL. They can be installed on diesel power plants with CE (European conformity) marking. • Leroy Somer are the only foreign electric generators in Russia that have successfully passed certification in accordance with strict Russian GOST standards: GOST R 52776-2007 “Rotating electrical machines. Nominal data and technical characteristics "; GOST 22407-85 “Rotating electrical machines from 63 to 335 inclusive. General purpose synchronous salient-pole generators. General technical conditions ", GOST R 50783-95" Electric units and mobile power plants with internal combustion engines. General technical requirements "; GOST 14965-80 “Three-phase synchronous generators with a power over 100 kW. General technical conditions ". © 2005-2015 Diesel Export LLC E-mail: sales@ecomd.ru Yaroslavl +7 (4852) 37-01-02 Samara +7 (846) 230-03-03 Krasnodar +7 (861) 227-82-24 Moscow +7 (495) 505-63-72 Call toll free 8 800 3333-702 SALE! Sale of engines from the warehouse Engines Synchronous generators Spare parts Delivery Company