Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT XHHW-2 ALUMINUM CONDUCTOR CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION: KINGWIRE 1000/600 Volt Type XHHW-2 is intended for use as general purpose wiring for up to 1000 volt rated services in air conduit or other recognized raceways for services, feeders and branch circuit wiring as specified in the National Electrical Code at a maximum conductor temperature of 90 °C in wet or dry locations. PRODUCT FEATURES: Compact stranded 8000 Series aluminum alloy conductor. Insulation is an abrasion, moisture, heat and sunlight resistant black cross-linked polyethylene. Cable can be installed without pulling lubricant. Sizes 1/0 AWG and larger are CT Rated. STANDARDS: UL Standard 44 and Federal Specification JC-30B NEC, ASTM B-800, B-801 Compliant to RoHS, Directive 2002/95/EC, ICEA S-95-658, NEMA WC 70 COLORS: Sizes 6 to 1 gauge are stocked in Black, White, Red, Blue and Green. Sizes 1/0 to 750MCM stocked in all the above colors plus Brown, Yellow, Orange, Gray, Green and Purple. KINGWIRE XHHW-2 Conductor (AWG or MCM) Stranding Insulation Thickness (mls) Outside Diameter (in) Weight per 1000 ft. (lbs) Ampacity (AMPS) * 90° C 6 7/w 45 .260 39 60 4 7/w 45 .305 57 75 2 7/w 45 .360 84 100 1 19/w 55 .415 108 115 1/0 19/w 55 .450 132 135 2/0 19/w 55 .490 161 150 3/0 19/w 55 .540 198 175 4/0 19/w 55 .590 244 205 250 37/w 65 .655 292 230 300 37/w 65 .705 344 255 350 37/w 65 .750 396 280 400 37/w 65 .795 448 305 500 37/w 65 .870 550 350 600 61/w 80 .980 671 385 700 61/w 80 1.040 774 420 750 61/w 80 1.075 824 435 900 61/w 80 1.161 .979 480 1000 61/w 80 1.230 1079 500 1. Data are approximate and subject to normal manufacturing tolerances. 2. Standard lengths are subject to normal manufacturing tolerance of +/- 10% 3. Two, Three or four conductors can be paralleled on a reel. 4. 90°C- XHHW-2 wet or dry locations. * To determine correct ampacity by conductor size, please consult the National Electric Code, latest edition. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep