Support input Infrastructure The computing power and network infrastructure required for the operation of the system are located in two geographically distributed cloud data centers in Russia and Europe. Data Center DataLine Located in Moscow, PCI DSS Level 1 and ISO / IEC 27001: 2005 certified The multi-level infrastructure of the physical protection of the data center includes a gas fire extinguishing system, CCTV and burglar alarm systems, an access control and management system. There is round-the-clock surveillance and video recording of the situation in the premises and adjacent territories. At the entrances, airlock rooms are organized, controlled by the security service. The power supply of the data center is organized with redundancy according to the 2N scheme - power is supplied to each rack in the halls through 2 beams. Uninterruptible power supplies inside data center modules with a capacity of 500 kW provide autonomous power supply for 5-6 minutes - time with a good margin for starting a diesel generator set. Diesel generator sets (DGS) as backup power sources are automatically started in the event of a power failure of MosEnergo. The oil and antifreeze of diesel engines are constantly warmed up, due to which the diesel generator set is always ready to start (the time of starting and reaching the mode is less than 1 minute). Fuel tanks of diesel generators are designed for 6 hours of operation, while contracts have been concluded for the prompt delivery of diesel fuel, which will ensure the operation of the data center even in the event of a long-term failure of the city supply network. Uninterrupted access to equipment located in the data center is carried out through redundant high-speed data transmission channels with a bandwidth of up to 10 GB. The data centers are united into a fiber-optic ring (with a bandwidth of up to 40 Gb / s), including the DataLine points of presence on MMTC9 and MMTS10. There is a 10 Gbps channel up to MSK-IX. Data center Armor Based in Amsterdam, PCI DSS Level 1, ISO / IEC 27001: 2005, SSAE 16 and HIPAA certified Armor is one of the largest international cloud data centers. In numbers: 5000 secure cloud server capacity Multiple N + 1 config, 7 minutes of autonomy on load N + 1 conform distributed redundancy model 4 x 2,000 kw diesel generators 55 hours fuel supply onsite with priority refueling Cooling circuits in 2N. CRAC-units in N + 2 VESDA throughout Zoned, nitrogen cold steam fire suppression Analogue optical fire detectors operating a double knock protocol ABOUT THE SYSTEM Acceptance of payments Recurring payments Personal Area Security Infrastructure SLA CONNECTION Connection procedure Offer Site requirements Example of information placement INTEGRATION general information Terms and Definitions Types of operations Payment schemes Payment Methods 3-D Secure Modules and SDK Payment Widget Installation Options Localization Create a subscription Checkout script Requirements Installation Notifications Check Pay Fail Refund Recurrent Check SDK for mobile apps IOS SDK Android SDK API Authentication Payment by cryptogram Payment by token Proof of payment Cancellation of payment Refund Checking payment status Uploading a list of operations Create a subscription Subscription status request Search subscriptions Change subscription Subscription cancellation Sending an invoice by mail Localization Long entry Testing Directories Error codes Operation statuses Subscription statuses Currencies Time zones PCI DSS Integration scenarios Payment form Registration of payments Verification and registration of payments Auto Payments for ISPs Auto payments for charitable foundations Payment by installments One click payments Recurring payments Business solutions Security Contacts Cloud Payments © 2016