CE-B Metal Clad Switchboards ≤ 40,5kV ≤ 63kA ≤ 3.150A - 4.000A - 7.000A CE-B Metal Clad Switchboards are designed for use in public and industrial distribution system up to 40.5kV for the operation and protection of lines, generators, transformer, motors, capacitor banks GENERAL CHARACTERISTICS The switchboards are composed combining the various standards cubicles. According to the international standards IEC 62271-200 the CE-B switchboards are classified for “loss of service continuity category” as LSC2B with partition class PM (Metallic Partition) or PI (Partitions non-metallic) Optional version A is also foreseen fully withstanding to internal arc fault IAC (AFLR) For outdoor application the versione CE-BO is available with protection degree up to IP55 or Type 4x VERSIONS Switchboards can be supplied in the following versions: CE-B12 METAL CLAD SWITCHGEARS UP TO 12kV – 50kA CE-B17 METAL CLAD SWITCHGEARS UP TO 17.5kV – 63kA CE-BP METAL CLAD SWITCHGEARS UP TO 24kV – 25kA CE-B24 METAL CLAD SWITCHGEARS UP TO 24kV – 50kA CE-B36 METAL CLAD SWITCHGEARS UP TO 36kV – 31,5kA CE-B40 METAL CLAD SWITCHGEARS UP TO 40,5kV – 31,5kA Other info ELECTRICAL DATA Rated Voltage 12 - 17.5 - 24 - 36 - 40,5 kV Rated frequency 50/60 Hz Test Voltage 1min up to 28 - 38 - 50 - 70 -90 kV Impulse withstand voltage up to 75 -80 - 125 - 170 - 185 kV Rated Current with natural cooling up to 3150 A Rated current with forced cooling 4000 A Rated current with two breakers in parallel and cooling system 7000 A Maximum short-term rated current 3 sec. up to 63 kA (depending on voltage) Maximum peak short circuit current up to 170kA (depending on voltage) IAC classification A-FLR (1 sec.) Optional up to 63 kA (depending on voltage) Protection degree IP31 - IP55 Ambient temperature -5 +55 °C STANDARDS AND TESTS The CE-B series complies with the main Italian and International standards, these have performed all relevant tests carried out by qualified laboratories. 12345 Headquarters and Factory: via G. Rossini, 24 37060 Castel d’Azzano (Verona) Italy Tel. +39 045 8546511 Fax +39 045 8520214 E-mail: info@casagrande.vr.it Production Branch: Via Bortolazzi, 57 37060 Castel d’Azzano (Verona) Italy Production Branch: Contrada Piana Z.I. 86019 Vinchiaturo (Campobasso) Italy Tel. +39 0874 340225 Fax +39 0874 340227 APERTURA NUOVO SITO PRODUTTIVO E RIORGANIZZAZIONE INTERNA AL FINE DI SVILUPPARE NUOVE TIPOLOGIE DI PRODOTTO – ACQUISTO DI N.3 CARRIPONTE DA 15 TON. Il progetto di investimento prevede l’acquisto di n. 3 carriponte da 15 t, installati in un nuovo sito produttivo, che saranno utilizzati nel processo di costruzione di quadri elettrici per generazione di grossa potenza e shelter. Intervento realizzato avvalendosi del finanziamento POR – Obiettivo “Investimenti a favore della crescita e dell’occupazione” Parte FESR fondo europeo di sviluppo regionale 2014-2020. Asse 3 – Azione 3.1.1 ©2021 CASAGRANDE ELETTROCOSTRUZIONI S.P.A. - P.IVA IT00663680239 - PRIVACY POLICY - COOKIE POLICY - LEGAL NOTES SITE BY VERTER.IT MENU HOME ABOUT US COMPANY DEPARTMENTS RESEARCH & DEVELOPMENT AND TESTS MARKET SECTOR AND DISTRIBUTION AREA QUALITY, SAFETY AND ENVIRONMENT NEWS WORK WITH US HOW TO REACH US CONTACT US ALL PRODUCTS LOW VOLTAGE MEDIUM VOLTAGE OTHER PRODUCTS PLANTS & SITE SERVICES