HOME PRODUCTS AND SERVICES ABOUT NEWS ABOUT POWER QUALITY CONTACT SVENSKA Home About power quality Evaluating direction of harmonics – Power Harmonics EVALUATING DIRECTION OF HARMONICS – POWER HARMONICS One imoprtant issue is how to trace the source of harmonics. The example below shows harmonic filters connected until 11.00 and there is no voltage distortion as expected. After 11.00 the filters were disconnected due to a fault and voltage harmonics can be seen. THERE ARE AT LEAST 2 WAYS TO DETERMINE THE DIRECTION OF HARMONICS: First is to simply look at current with current harmonics and compare with voltage. If there is obvious correlation between current and voltage harmonics, then the source is downstream i.e. the load current is causing the voltage distortion. The second, and easier, way to study harmonics direction is to study the power harmonics. For each frequency voltage and current creates active power, P. With normal references the sign of P tells the direction of power flow, + means from grid to load (source upstream) and – means from load to grid (source downstream). Below are the power harmonics from the above example. You clearly see that 5th (green) and 7th (red) harmonics have negative sign meaning a downstream direction, i.e. going from load into the grid. QUESTIONS? CONTACT US CATEGORIES News NEWS ARCHIVE ⇱2021 ⇲2020 ⇲2019 ⇲2018 ⇲2017 ⇲2016 ⇲2015 ⇲2014 ⇲2013 ⇲2012 SEARCH OUR SITE SEARCH Search for: CONTACT US Phone: +46 322 638020 Email: info@unipower.se • Official postal address: Box 411, 44128 Alingsås, Sweden • Visiting and courier address: Metallgatan 4C, 44132 Alingsås, Sweden © Copyright 1998 - 2020 - Unipower AB, Sweden Privacy Policy (English) - Integritetspolicy (svenska) - Kvalitets- och Miljöpolicy (svenska) By continuing to use the site, you agree to the use of cookies. more information ACCEPT