Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT USE-RHH-RHW-2 CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION: Type USE-RHH-RHW-2 building wire and service cable is recognized for use as general purpose wiring at a maximum conductor temperature of 90°C in wet or dry locations for installation in air, conduit or other recognized raceways and for direct burial in circuits not exceeding 600 volts. PRODUCT FEATURES: Compact stranded 8000 Series aluminum alloy conductor. Insulation is an abrasion, moisture, heat and sunlight resistant black cross-linked polyethylene (XLPE). STANDARDS: UL Standard 44 (RHW or RHH), UL Standard 854 (USE) and Federal Specification JC-30B NEC. KINGWIRE USE-RHH-RHW-2 Conductor AWG or MCM Stranding Insulation Thickness (mils) Outside Diameter (in) Weight per 1000 ft. (lbs) Ampacity (AMPS) 90°C 6 7/w 60 .290 49 60 4 7/w 60 .334 65 75 2 7/w 60 .390 94 100 1 19/w 80 .460 125 115 1/0 19/w 80 .500 150 135 2/0 19/w 80 .540 181 150 3/0 19/w 80 .590 220 175 4/0 19/w 80 .635 268 205 250 37/w 95 .710 320 230 350 37/w 95 .810 428 280 500 37/w 95 .930 591 350 600 61/w 110 1.035 715 385 750 61/w 110 1.130 873 435 1000 61/w 110 1.280 1132 500 1. Data are approximate and subject to normal manufacturing tolerances. 2. Standard lengths are subject to normal manufacturing tolerance of +/- 10% 3. Two, Three or four conductors can be paralleled on a reel. 4. 90°C-RHH dry locations, RHW-2 wet or dry locations. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep