HomeSolutions for you Products About Us Contact Us Quality Downloads Delta X – Ex cable glands for armoured cables Data Sheet Documentation Back Delta X – Ex cable glands for armoured cables Features Nickel plated brass, 304 and 316 stainless steel ISO and NPT sizes Suitable for armoured cables Ex I M2, Ex II 2GD Increased safety Ex e I Mb, Ex e IIC Gb and Ex tb IIIC Db Explosion proof Ex d I Mb, Ex d IIC Gb Also suitable for industrial and underwater applications Protection class options: IP66 (dust tight and water jet proof) or IP68 (underwater tested) Temperature rating -40ºC to +100ºC (Neoprene seal) and -60ºC to + 180ºC (Silicone seal) Gland accessories including, earth tags, fibre and sealing washers, cable shrouds and lock nuts. Dimensions: from M16 x 1.5 to M110 x 2.0 and NPT 3/8” to 4” Certification IMQ08ATEX25 Ex protection type (EN 50018/IEC 60079-1 and EN 50019/IEC 60079-7) Ex I M2, Ex II 2GD Ex e I Mb, Ex e IIC Gb and Ex tb IIIC Db Ex d I Mb, Ex d IIC Gb Ingress protection levels IP66 and 68 (EN 60529/IEC 60529) Ambient temperature -40ºC to +100ºC (Neoprene seal) and -60ºC to + 180ºC (Silicone seal) Description CE-TEK’s metallic glands are available as Nickel plated brass and stainless steel variations. CE-TEK’s next generation cable glands meet the latest EN 60079-0:2009 standards for hazardous area application. This group comprises of three ranges – Alpha X, Gamma X and Delta X in nickel plated brass and stainless steel, rated to IP66 as standard and IP68 as an option. Temperature ranges are -40ºC to +100ºC with neoprene seals and -60ºC to +180ºC with silicone seals. Delta X double seal cable gland (Ex d I Mb, Ex e I Mb, Ex d IIC Gb, Ex e IIC Gb, Ex tb IIIC Db, Ex I M2, Ex II 2 GD) sizes from M16 to M110 and NPT 3/8” to 4” for armoured cables. Article ISO Thread Article NPT Thread Outer Clamping Range Thread length mm > < KA01SBPM16 M16 x 1.5 KA01SBPN38 NPT 3/8” 6.0 12.0 14.0 KA01BPM16 M16 x 1.5 KA01BPN38 NPT 3/8” 9.0 18.0 16.0 KA1BPM20 M20 x 1.5 KA1BPN12 NPT ½” 9.0 18.0 16.0 KA2BPM25 M25 x 1.5 KA2BPN34 NPT ¾” 14.0 26.0 18.0 KA3BPM32 M32 x 1.5 KA3BPN100 NPT 1” 20.0 33.0 18.0 KA4BPM40 M40 x 1.5 KA4BPN114 NPT 1¼” 29.0 41.0 18.0 KA5BPM50 M50 x 1.5 KA5BPN112 NPT 1½” 36.0 52.0 20.0 KA6BPM63 M63 x 1.5 KA6BPN200 NPT 2” 42.0 62.0 20.0 KA7BPM75 M75 x 1.5 KA7BPN212 NPT 2½” 54.0 78.0 20.0 KA8BPM90 M90 x 2.0 KA8BPN300 NPT 3” 63.0 88.0 20.0 KA10BPM110 M110 x 2.0 KA10BPN400 NPT 4” 88.0 105.0 20.0 Technical data (Extract) (For detailed information please click here) Protection class IP 66 and 68 (EN 60529/IEC 60529) Dimensions see data sheet Material Nickel Plated Brass, 304 or 316 stainless steel Weight see data sheet Resistance Impact resistance – see data sheet Documentation Delta X Cable Glands Data Sheet – for armoured Ex cables Declaration of Conformity Customer requirements – Terminal Boxes Operating Instructions – Empty enclosure CE TEK is proudly powered by WordPress