LF POWER CENTER MCC AUTOMATION SPECIAL CONSTRUCTIONS SERVICES CONTACTS REFERENCES GENERAL CHARACTERISTICS LV2002 Electrical characteristics LV2001 LV2002 Rated insulation voltage (Ui) 1000V 1000V Rated operating voltage (Ue) 690V 690V Nominal frequency 50/60 Hz 50/60 Hz Rated current main bars ≤ 2700A ≤ 6300A derived bars ≤ 2200A ≤ 3200A Rated short-time current for 1 sec. (Icw) ≤ 70 kA ≤ 100 kA Rated peak current (Ipk) ≤ 154 kA ≤ 220 kA Degree of protection (according to EN 60529) outer casing IP31 standard IP31 standard with the door open IP2X IP2X Maximum number of modules per compartment 48 48 Internal subdivisions shapes 2,3,4 shapes 2,3,4 Surface protection outer casing sheet painted RAL9002 sheet painted RAL9002 internal structure (Az-150) - Aluzinc (Az-150) - Aluzinc Accessibility from the front from the back Installation counter-wall or double front with space on the back Cable entry and exit from above or below from above or below Compartment dimensions width [mm] 900,1050,1150,1550 600,800,900,1200,1400 height [mm] 2365 2365 depth [mm] 600 1035,1385,1510 Internal arc protection (IEC 61641) on request on request Power center | SYSTEM LV2002 < click to enlarge > © Copyright - LF Srl - Registration in the Register of Companies of Ancona 01499640421 - REA 146706 - VAT: 01499640421 - Paid up share capital € 119.000,00 privacy | credits