COMPANY COMPRESSED AIR TREATMENT WATER TREATMENT QUALITY CONTACTS NEWS ITA | ENG | CYR Reserved area Search form Search for WATER TREATMENT The range of CWT water chillers was the first produced by Friulair, the one that allowed us to introduce ourselves to the world of air conditioning and industrial cooling processes and that offered us the opportunity to confirm the quality of the products we sell. , also in the face of decades of experience in the refrigeration sector, albeit in different fields of application. The series is designed for outdoor installation and is specifically designed to meet the application requirements in the industrial sector and provide accurate control of the chilled water temperature, with absolute reliability of continuous operation. It was developed with air-cooled condensates and axial fans and consists of 16 basic models, which cover cooling capacities from 7 to 128 kW. Refrigerant circuit and expansion valve. Made with top quality materials by specialized personnel according to rigorous brazing procedures, compliant with directive 97/23. It is made up of: · Rotary (models CWT007 and CWT010) and scroll compressors designed for R410A; · AISI 316 stainless steel brazed plate evaporators; · Microchannel aluminum condensers; · Filter drier; · Flow indicator with humidity indicator; · Thermostatic expansion valve with external equalization; the thermostatic expansion valves regulate the liquid injection of refrigerant into the evaporator. The injection is controlled by the superheat of the refrigerant. The range of thermostatic valves we use is designed for specific applications and are connected to the circuit by bi-metal brazing; · One-way valves (only for multi-compressor units); · High pressure switch with manual reset and low pressure switch with automatic reset; · High and low pressure gauges; · Pressure points for checks and maintenance. Hydraulic circuit and circulation pumps . Costituito da evaporatore e tubazioni interne alla macchina, esso comprende anche: · serbatoio di accumulo realizzato in acciaio al carbonio e isolato termicamente; · elettropompa in acciaio inox, isolata termicamente; · bypass acqua (previene gli inconvenienti legati ad una erronea chiusura delle valvole di intercettazione); · vaso di espansione; · valvola di sicurezza; · valvola di sfiato automatica; · sensore di livello acqua; · pressostato differenziale acqua; · rubinetti a sfera di intercettazione; · filtro acqua in ingresso all’unità; · manometro; · rubinetto di svuotamento. INFO & DOWNLOAD Depliant CWT (PDF) I nostri prodotti sono tutti MADE IN ITALY, rispettano l'ambiente e sono certificati in base alle attuali norme in materia di qualità. AZIENDA Chi siamo Struttura TRATTAMENTO ARIA... AMD - Standard ACT - Premium HDT - Adsorbimento PLH - Alta Pressione AMH - Alta Temperatura Standard AHT - Alta Temperatura Premium PCD - Bassa Temperatura FT - Alluminio LF - Spin On FW - Flangiati FH - Alta pressione AFR Temporizzati Galleggianti Capacitivi WOSS CCS FTC TRATTAMENTO ACQUA QBE - Potenze Frigorifere 2-25 kW CWT - Potenze Frigorifere 7-128 kW CWE/HWE - Potenze Frigorifere 13-141 kW CWB - Potenze Frigorifere 140-570 kW QUALITÀ Certificazioni e ambiente Ricerca e sviluppo CONTATTI Richiesta Informazioni Richiesta Assistenza Richiesta Dichiarazione CE Invia Curriculum NEWS FRIULAIR Srl Legal and operational headquarters Via Cisis, 36 - Fraz. STRASSOLDO - 33052 Cervignano del Friuli (UD) - Tel. +39 0431 939416 - Fax +39 0431 939419 e-mail: friulair@friulair.com - PEC: amm @ cert .friulair.com Cap.Soc. € 12,480 fully paid-up - VAT, Tax Code 00430110312 - COD.CEE IT 00430110312 - REA UD n. 23858 Privacy and Cookies - © MULTIWAYS