Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT 600 VOLT SECONDARY UD - QUADRUPLEX CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION Directly buried or installed in ducts for 600 volt secondary distribution. PRODUCT FEATURES Concentric stranded or compressed 1350-H19 aluminum conductor, crosslinked polyethylene insulation. Insulated conductors surface printed, neutral, triple yellow striped or solid yellow. Black neutrals may be specified if desired. STANDARDS UL Standard 854 for Type USE-2 ASTM B-230, B-231 and ICEA S-105-692 Federal Specification JC-30B NEC KINGWIRE Quadruplex Conductor 600 Volt Secondary Type URD Cable - Aluminum Conductor Code Word Phase Conductors Neutral Conductor Single Phase Conductor (in) Outside Diameter (in) Weight per 1000 ft (lbs) Ampacity Size AWG Strand Insulation Thickness (MLS) Size AWG Strand Insulation Thickness (MLS) Direct Burial In Duct Tulsa 4 7/w 60 4 7/w 60 .345 .833 258 119 85 Dyke 2 7/w 60 4 7/w 60 .403 .938 346 153 115 Wittenberg 2 7/w 60 2 7/w 60 .403 .973 375 153 115 Notre Dame 1/0 19/w 80 2 7/w 60 .522 1.188 541 198 150 Purdue 1/0 19/w 80 1/0 19/w 80 .522 1.260 596 198 150 Syracuse 2/0 19/w 80 1 19/w 80 .566 1.316 664 225 170 Wake Forest 4/0 19/w 80 2/0 19/w 80 .672 1.560 979 290 225 Rust 250 37/w 95 3/0 19/w 80 .748 1.725 1,176 319 240 Slippery Rock 350 37/w 95 4/0 19/w 80 .851 1.945 1,544 385 305 Wofford 500 37/w 95 350 37/w 95 .851 2.348 2,174 467 420 Westminster 750 61/w 110 350 37/w 95 .979 2.722 2,816 615 492 Ampacity: 90°C conductor temperature, 20°C ambient, RHO 90, 100% load factor for three conductor triplex with neutral carrying only unbalanced load. All Yellow Extruded Stripe, cable is XLP insulation. * To determine correct ampacity by conductor size, please consult the National Electric Code, latest edition. The above data are approximate and subject to normal manufacturing tolerances. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep

Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT CLICK HERE TO DOWNLOAD SPEC SHEET POWER SUPPLY CORDS KINGWIRE offers power supply cords ranging from 14-3 to 16-3 in 3, 6, and 9 foot lengths. The power supply cords range from 13 Amps to 15 Amps and have a thick vinyl insulation for safety and longevity. KINGWIRE PVC Power Supply Cords Gauge/Cond Type Color Length (ft.) Rating (Amp) Plug Config Master Pck 16-3 SJTW Black 3 13A Nema 5-15 Straight 25 16-3 SJTW Black 6 13A Nema 5-15 Straight 25 14-3 SJTW Black 6 15A Nema 5-15 Straight 25 14-3 SJTW Black 9 15A Nema 5-15 Straight 25 16-3 SPT-3 Grey 3 13A Nema 5-15 Straight 25 16-3 SPT-3 Grey 6 13A Nema 5-15 Right Angle 25 16-3 SPT-3 Grey 6 13A Nema 5-15 Straight 25 16-3 SPT-3 Grey 9 13A Nema 5-15 Straight 25 14-3 SPT-3 Beige 6 15A Nema 5-15 Straight 25 14-3 SPT-3 Beige 9 15A Nema 5-15 Straight 25 Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep