DOWNLOADS CONTACT (800) 442-5279 Products Why Clary Company Support HomeContact Contact Company* Name* Phone* Email* Subject* Your Messag* Mail Clary Corporation 150 East Huntington Drive Monrovia, CA 91016 Sales Email: sales@clary.com Phone: (626) 359-4486 Fax: (626) 305-0254 Service Email: service@clary.com Phone: (626) 775-3259 Fax: (626) 301-0049 Accounts Payable Phone: (626) 775-3264 Fax: (626) 301-0659 Accounts Receivable Phone: (626) 775-3264 Fax: (626) 301-0659 Contact us to learn more about our innovative products! CONTACT US © 2021 Clary Corporation. All Rights Reserved. Contact Terms of Use Privacy Policy

DOWNLOADS CONTACT (800) 442-5279 Products Why Clary Company Support HomeCritical Applications We keep electronics working when failure is not an option Clary Advantage Operational temperature Engineered to operate in extreme conditions Our systems are proven to perform in some of the world's harshest environments, including temperatures from -40°C to +74°C. You can count on Clary for outdoor applications in locations from the hottest desert to the coldest tundra. Continuous digital power Power factor correction Bidirectional communications NEMA environmental certification Customer Success Stories Critical Applications Products (5) Contact us to learn more about our innovative products! CONTACT US © 2021 Clary Corporation. All Rights Reserved. Contact Terms of Use Privacy Policy

DOWNLOADS CONTACT (800) 442-5279 Products Why Clary Company Support HomeSP 1250DLE SP 1250DLE Clean power for the next generation SP 1250DLE Overview Our newest digital UPS is designed for ITS and traffic applications, including the new low-voltage ATC cabinets. It’s the only double conversion, true on-line UPS with both AC and DC power inputs and outputs, and it comes in a compact 1U rack-mounted package. The SP 1250DLE is designed for temperature extremes of ‑40°C to +74°C (-40°F to +165°F) and supports 85-155 VAC or 48 VDC input voltages, as well as generator input. The unit provides a 120 VAC output and 48 VDC, 24 VDC, and 12 VDC outputs, up to an 875 watt maximum for all outputs combined. For customers who do not yet require DC support but anticipate a future need, the SP 1250DLE can be ordered without DC output and later upgraded in the field. Downloads SP 1250DLE Data Sheet SP 1250DLE Manual SP Series Warranty Related Links RMA Request Downloads CONTACT US SP 1250DLE 360° View SP 1250DLE Specifications Electrical Input Input #1 Voltage 85 - 155 VAC Frequency 60 Hz ±5 Hz Power Factor Power factor corrected Input #2 Voltage 48 VCD nominal battery pack Isolation Thru-neutral design Electrical Output Environmental Mechanical Design Control and Indicators Options Related Products Contact us to learn more about our innovative products! CONTACT US © 2021 Clary Corporation. All Rights Reserved. Contact Terms of Use Privacy Policy