Conversion Chart PRODUCT CATALOG ABOUT KINGWIRE RESOURCES CONTACT SOOW UL CLICK HERE TO DOWNLOAD SPEC SHEET APPLICATION: Type SOOW UL/CSA is designed for extra hard usage on industrial equipment, heavy tools, battery chargers, power extensions and mining applications, it is permitted for use as specified by Article 400 and related articles of the 2011 NEC. CONSTRUCTION: CONDUCTOR: 18 AWG-2AWG Class K stranded bare copper per ASTM B-174 INSULATION: EPDM COLOR CODE: See Color Chart Below JACKET: CPE COLOR: Black TEMPERATURE RANGE: -40°C to 90°C PHYSICAL PROPERTIES: Oil and Water Resistant Non-Marking Jacket, Lightweight & Very Flexible at Low Temp. STANDARDS: UL Standard 62, CSA Standard C22.2 No. 49, Passes CSA FT2 Flame Test, MSHA listed, passes MSHA flame test (P-136-MSHA), RoHS KINGWIRE SOOW UL/CSA Number of Conductors Color 2 Black, White 3 Black, White, Green 4 Black, White, Red, Green 5 Black, White, Red, Orange, Green KINGWIRE SOOW UL/CSA Conductor Size AWG Conductor Stranding Nominal Insulation Thickness (in) Nominal Jacket Thickness (in) Nominal Overall Diameter (in) Weight per 1000 ft. (lbs) Ampacity 18/2 16 X 30 0.030 0.060 0.347 54 10 18/3 16 X 30 0.030 0.060 0.366 64 10 18/4 16 X 30 0.030 0.060 0.390 79 7 18/5 16 X 30 0.030 0.060 0.465 108 6 16/2 26 X 30 0.030 0.060 0.369 62 13 16/3 26 X 30 0.030 0.060 0.390 77 13 16/4 26 X 30 0.030 0.080 0.415 90 10 16/5 26 X 30 0.030 0.080 0.492 125 8 14/2 41 X 30 0.045 0.080 0.500 115 18 14/3 41 X 30 0.045 0.080 0.522 141 18 14/4 41 X 30 0.045 0.080 0.567 167 15 14/5 41 X 30 0.045 0.095 0.642 213 12 12/2 65 X 30 0.045 0.095 0.570 154 25 12/3 65 X 30 0.045 0.095 0.592 184 25 12/4 65 X 30 0.045 0.095 0.643 226 20 12/5 65 X 30 0.045 0.095 0.707 282 16 10/2 104 X 30 0.045 0.095 0.617 195 30 10/3 104 X 30 0.045 0.095 0.652 246 30 10/4 104 X 30 0.045 0.095 0.703 300 25 10/5 104 X 30 0.045 0.095 0.765 360 20 8/3 133 X 29 0.060 0.110 0.855 420 40 8/4 133 X 29 0.060 0.125 0.941 532 35 8/5 133 X 29 0.060 0.125 1.039 667 28 6/3 133 X .0142 0.060 0.125 0.975 580 55 6/4 133 X .0142 1.060 1.140 1.075 743 45 6/5 133 X .0142 0.060 0.140 1.185 874 36 4/3 133 X .0171 0.060 0.140 1.132 835 70 4/4 133 X .0171 0.060 0.155 1.265 1075 60 4/5 133 X .0171 0.060 0.155 1.386 1300 48 2/3 133 X .0220 0.060 0.155 1.305 1160 95 2/4 133 X .0220 0.060 0.170 1.457 1520 80 2/5 133 X .0220 0.060 0.170 1.558 1735 64 Note: Specifications contained herein reflect current data and are subject to change. Values are nominal and/or approximate. Conversion Chart Corporate Headquarters KWI LLC. Number One Cable Place North Chicago, Illinois 60064 Phone No: (847) 688-1100 Fax: (847) 688-0244 Copyright © 2021 All Rights Reserved, KWI LLC. Find a Rep