English EN 50541 Um=17,5/38/95 kV CoBk KVA 160 250 315 400 500 630 800 1000 1250 1600 2000 2500 3150 W0 W 650 880 1000 1200 1300 1650 2000 2300 2800 3100 4000 5000 6000 Wcc (120°C) W 2900 3800 4500 5500 6800 7600 9400 11000 13000 16000 18000 23000 28000 Vcc % 6 6 6 6 6 6 6 6 6 6 6 6 6 I0 % 1,9 1,5 1,4 1,3 1,2 1,2 1,1 1 1 0,9 0,9 0,8 0,7 Lwa dB(A) 62 65 67 68 68 70 72 73 75 76 78 81 83 a1 mm 1150 1200 1200 1300 1300 1400 1400 1450 1550 1700 1800 2000 2100 b1 mm 600 600 750 750 750 850 850 1000 1000 1000 1310 1310 1310 h1 mm 1110 1350 1400 1400 1500 1600 1750 1800 1950 2050 2150 2400 2400 e mm 520 520 670 670 670 670 670 820 820 820 1070 1070 1070 ø mm 125 125 125 125 125 125 125 125 160 160 200 200 200 t mm 40 40 40 40 40 40 40 40 50 50 70 70 70 W kg 730 950 1050 1200 1370 1630 1900 2230 2700 3450 4070 5350 6300 BoBk KVA 160 250 315 400 500 630 800 1000 1250 1600 2000 2500 3150 W0 W 480 650 750 940 1050 1250 1500 1800 2100 2400 3000 3600 4300 Wcc (120°C) W 2900 3800 4500 5500 6800 7600 9400 11000 13000 16000 18000 23000 28000 Vcc % 6 6 6 6 6 6 6 6 6 6 6 6 6 I0 % 1,9 1,5 1,4 1,3 1,2 1,2 1,1 1 1 0,9 0,9 0,8 0,7 Lwa dB(A) 54 57 59 60 61 62 64 65 67 68 70 71 74 a1 mm 1250 1250 1300 1350 1400 1450 1500 1550 1650 1700 1850 2050 2150 b1 mm 600 600 750 750 750 850 850 1000 1000 1000 1310 1310 1310 h1 mm 1200 1400 1400 1450 1500 1600 1750 1800 1950 2100 2150 2450 2450 e mm 520 520 670 670 670 670 670 820 820 820 1070 1070 1070 ø mm 125 125 125 125 125 125 125 125 160 160 200 200 200 t mm 40 40 40 40 40 40 40 40 50 50 70 70 70 W kg 900 980 1150 1300 1500 1750 2150 2400 3000 3500 4200 5650 6800 AoAk KVA 160 250 315 400 500 630 800 1000 1250 1600 2000 2500 3150 W0 W 400 520 650 750 950 1100 1300 1550 1800 2200 2600 3100 3800 Wcc (120°C) W 2600 3400 4100 4500 5900 7100 8000 9000 11000 13000 16000 19000 22000 Vcc % 6 6 6 6 6 6 6 6 6 6 6 6 6 I0 % 1,9 1,5 1,4 1,3 1,2 1,2 1,1 1 1 0,9 0,9 0,8 0,7 Lwa dB(A) 54 57 59 60 61 62 64 65 67 68 70 71 74 a1 mm 1300 1350 1400 1500 1500 1500 1600 1700 1800 1850 1900 2050 2150 b1 mm 600 600 750 750 750 850 850 1000 1000 1000 1310 1310 1310 h1 mm 1400 1450 1500 1600 1650 1800 1900 2050 2100 2200 2500 2550 2600 e mm 520 520 670 670 670 670 670 820 820 820 1070 1070 1070 ø mm 125 125 125 125 125 125 125 125 160 160 200 200 200 t mm 40 40 40 40 40 40 40 40 50 50 70 70 70 W kg 920 1150 1350 1700 1900 2000 2450 2900 3500 4150 4950 6150 7000 The dimensions may change slightly depending on the voltages of transformer. ENCLOUSURE DIMENSIONS KVA 160 250 315 400 500 630 800 1000 1250 1600 2000 2500 3150 A mm 1850 1850 1850 1900 1900 2050 2050 2300 2300 2300 2500 2500 2500 B mm 1100 1100 1100 1100 1100 1150 1150 1250 1250 1250 1310 1310 1310 C mm 1560 1560 1560 1760 1760 1960 1960 2460 2460 2460 2650 2650 2650 EW kg 145 145 145 155 155 175 175 225 225 225 250 250 250 LV TERMINALS KVA 160 250 315 400 500 630 800 1000 1250 1600 2000 2500 3150 Type A-B B B B C D E F G H I J J Standard Cast Resin Transformers General Information EN 50588 Um≤24kV EN 50588 Um=36kV EN 50541 Um≤12/28/75 kV EN 50541 Um=17,5/38/95 kV EN 50541 Um=24/50/125 kV EN 50541 25kV Um=36/70/145 kV EN 50541 Um=36/70/170 kV Standard Transformers Gallery Special Transformers Special Cast Resin Transformers Dry Type Transformers Oil Cooled Transformers Transformer Gallery Reactors Shunt Reactors Current Limiting Reactor Damping Reactors Reactors for Tuning Smoothing Reactors Neutral Earthing Reactors Reactor Gallery Transformers Manufacturing Company España S.A.U. Poligono Bildosola, Parcela B1 48142 Artea (Bizkaia) España Email: ventas@tmc.com.au Tel: +34 94 631 22 80 Fax: +34 94 631 45 24 Transformers Manufacturing Company Pty Ltd 19 Ewing Street Brunswick Melbourne Victoria 3056 Australia. Email: sales@tmc.com.au Tel: +61 3 9356 8700 Fax: +61 3 9356 8701 TMC TRANSFORMERS MANUFACTURING COMPANY © 2014 BY SIROPE