Water And Sewerage Citation and commencement 1 These Regulations may be cited as the Control of Pollution (Oil Storage) Regulations (Northern Ireland) 2010 and shall come into operation on 20 March 2011. Interpretation 2 In these Regulations— “container” means a fixed tank, a drum, a mobile bowser or (even if not connected to fixed pipework) an intermediate bulk container; “draw off pipe” means a pipe used to withdraw oil from the container; “drum” means an oil drum or similar container used for storing oil; “fill pipe” means a pipe used to deliver oil into the container; “fixed tank” includes an intermediate bulk container, which is connected to fixed pipework; “oil” means any kind of oil and includes petrol, diesel, waste, vegetable and plant oil, but does not include uncut bitumen; “secondary containment system” means a drip tray, an area surrounded by a bund or any other system for preventing oil which is no longer in its container from escaping from the place where it is stored. Application of Regulations 3 1 Subject to paragraph (2), these Regulations apply to the storage of oil on any premises. 2 These Regulations do not apply to the storage of oil— a in any container with a storage capacity of 200 litres or less; b on any premises used wholly or mainly as a private dwelling if the storage capacity of the container in which it is stored is 3500 litres or less; c on any farm if the oil is used in connection with agriculture within the meaning of the Agriculture Act (Northern Ireland) 1949 ; d on any premises regulated under the Control of Major Accident Hazards Regulations (Northern Ireland) 2015 if the storage capacity of the container in which it is stored is 2,500 tonnes or more ; and e in any container which is wholly underground. Requirements for oil storage – general 4 1 Oil shall be stored in a container which is of sufficient strength and structural integrity to ensure that it is unlikely to burst or leak in its ordinary use. 2 The container shall be situated within a secondary containment system which satisfies the following requirements— a subject to paragraph (6) it shall have a capacity of not less than 110% of the container’s storage capacity or, if there is more than one container within the system, of not less than 110% of the largest container’s storage capacity or 25% of their aggregate storage capacity, whichever is the greater; b it shall be positioned, or other steps shall be taken, so as to minimise any risk of damage by impact so far as is reasonably practicable; c its base and walls shall be impermeable to liquid and oil; d its base and walls shall not be penetrated by any valve, pipe or other opening which is used for draining the system; and e if any fill pipe, or draw off pipe, penetrates its base or any of its walls, the junction of the pipe with the base or walls shall be adequately sealed to prevent oil escaping from the system. 3 Where a fill pipe is not within the secondary containment system, a drip tray shall be used to catch any oil spilled when the container is being filled. 4 Any valve, filter, sight gauge, vent pipe or other equipment ancillary to the container (other than a fill pipe or draw off pipe or a pump) shall be situated within the secondary containment system. 5 Where any drum is used for the storage of oil in conjunction with a drip tray as the secondary containment system, it is sufficient if the tray has a capacity of not less than 25% of — a the drum’s storage capacity; or b if there is more than one drum used at the same time with the tray, the aggregate storage capacity of the drums. Fixed tanks 5 1 Any fixed tank used to store oil shall satisfy the following requirements — a any sight gauge shall be properly supported and fitted with a valve which closes automatically when not in use; b any fill pipe, draw off pipe or overflow pipe shall be positioned, or other steps shall be taken, so as to minimise any risk of damage by impact so far as is reasonably practicable; and i if above ground, shall be properly supported; ii if underground— aa shall have no mechanical joints, except at a place which is accessible for inspection by removing a hatch or cover; bb shall be adequately protected from physical damage; cc shall have adequate facilities for detecting any leaks; dd if fitted with a leakage detection device which is continuously to monitor for leaks, the detection device shall be maintained in working order and tested at appropriate intervals to ensure that it works properly; and ee if not fitted with such a device, shall be tested for leaks before it is first used and further tests for leaks shall be performed, in the case of pipes which have mechanical joints, at least once in every five years and, in other cases, at least once in every ten years. iii if made of materials which are liable to corrosion, shall be adequately protected against corrosion. 2 The tank shall be fitted with an automatic overflow prevention device (which may include an alarm sounding device) if the filling operation is controlled from a place where it is not reasonably practicable to observe the tank and any vent pipe. 3 Where a screw fitting or other fixed coupling is fitted it shall be maintained in good condition and used whenever the tank is being filled with oil. 4 Where oil from the tank is delivered through a flexible pipe which is permanently attached to it— a the pipe shall be fitted with a tap or valve at the delivery end which closes automatically when not in use; b the tap or valve shall not be capable of being fixed in the open position unless the pipe is fitted with an automatic shut off device; c the pipe shall be enclosed in a secure cabinet which is locked shut when not in use and is equipped with a drip tray, or the pipe shall— i have a lockable valve where it leaves the tank which is locked shut when not in use; and ii be kept within the secondary containment system when not in use. 5 Any pump shall be— a fitted with a non return valve in its feed line or an isolating device; b positioned, or other steps shall be taken so as to minimise any risk of damage by impact so far as is reasonably practicable; and c protected from unauthorised use. 6 Any permanent vent pipe, tap or valve through which oil can be discharged from the tank to the open shall satisfy the following requirements— a it shall be situated within the secondary containment system; b it shall be arranged so that any oil discharged is contained within the system; and c in the case of a tap or valve, it shall be fitted with a lock and locked shut when not in use. Mobile bowsers 6 1 Any mobile bowser used for storing oil shall satisfy the following requirements — a any tap, or valve permanently fixed to the mobile bowser through which oil can be discharged to the open shall be fitted with a lock and locked shut when not in use; b any sight gauge shall be secured to the mobile bowser and be fitted with a valve or tap which shall be locked in the shut position when not in use. 2 Where oil is delivered through a flexible pipe which is permanently attached to the mobile bowser— a the pipe shall be fitted with a manually operated pump or with a valve at the delivery end which closes automatically when not in use; b the pump or valve shall be provided with a lock and locked shut when not in use; and c the pipe shall be fitted with a lockable valve at the end where it leaves the mobile bowser and shall be locked shut when not in use. Transitional provisions 7 1 Subject to paragraph (2), where oil is stored in any container and that storage— a commenced before 20 March 2011, these Regulations shall not apply to that storage until 31 December 2015 unless it is being carried on less than, i 10 metres from any waterway; or ii 50 metres from any well, spring or borehole; in which case these Regulations shall apply to it from 20 March 2013; b commenced on or after 20 March 2011 but before 20 September 2011, these Regulations shall not apply to it until 20 September 2011. 2 If a notice served under regulation 8 is not complied with in relation to any container by the date specified in the notice, these Regulations shall apply from whichever is the latest of the following— a the date specified in the notice; b if the period for compliance is extended under regulation 8(4), the expiry of that extension; or c if there is an appeal against the notice, the date on which that appeal is determined or withdrawn. Notices to minimise pollution risks in transitional cases 8 1 In any case— a to which regulation 7(1) ... applies; and b where it appears to the Department that there is significant risk of pollution from the entry of the oil in question into any waterway or water contained in any underground strata if steps are not immediately taken to minimise that risk; the Department may serve a notice on the person having custody or control of that oil requiring him to carry out such works, take such precautions or such steps as, in the opinion of the Department, are appropriate for minimising that risk having regard to the requirements of regulations 4, 5 and 6. 2 The notice shall— a specify or describe the works, precautions or other steps which the person is required to carry out or take; b state the period within which any such requirement is to be complied with; and c inform the person of their rights under regulation 9. 3 The period for compliance shall be such as is reasonable in the circumstances and shall not in any case be less than 28 days. 4 The Department may at any time— a withdraw the notice; b extend the period for compliance with any requirement of the notice; c with the consent of the person on whom it is served, modify the requirements of the notice. Right of appeal in transitional cases 9 A person on whom a notice is served under regulation 8 may, within 28 days beginning with the date on which the notice is served, appeal in writing against the notice to the Water Appeals Commission. Offences 10 1 A person who has custody or control of any oil in circumstances in which there is a contravention of any provision of regulations 4, 5 and 6 or the requirements of a notice under regulation 8 shall be guilty of an offence and shall be liable— a on conviction on indictment, to imprisonment for a term not exceeding 2 years or to a fine or to both; b on summary conviction, to imprisonment for a term not exceeding 3 months or to a fine not exceeding £20,000 or to both. Sealed with the Official Seal of the Department of the Environment on 9 December 2010 Denis McMahon A senior officer of the Department of the Environment