Leakage inductance. Leakage inductance derives from the electrical property of an imperfectly coupled transformer whereby each winding behaves as a self-inductance in series with the winding's respective ohmic resistance constant. These four winding constants also interact with the transformer's mutual inductance. The winding leakage inductance is due to leakage flux not linking with all turns of each imperfectly coupled winding.

Leakage reactance is usually the most important element of a power system transformer due to power factor, voltage drop, reactive power consumption and fault current considerations.

Leakage inductance depends on the geometry of the core and the windings. Voltage drop across the leakage reactance results in often undesirable supply regulation with varying transformer load. But it can also be useful for harmonic isolation (attenuating higher frequencies) of some loads.

Leakage inductance applies to any imperfectly coupled magnetic circuit device including motors.

Leakage inductance and inductive coupling factor

The magnetic circuit's flux that does not interlink both windings is the leakage flux corresponding to primary leakage inductance LPσ and secondary leakage inductance LSσ. Referring to Fig. 1, these leakage inductances are defined in terms of transformer winding open-circuit inductances and associated coupling coefficient or coupling factor .

The primary open-circuit self-inductance is given by

 ------ (Eq. 1.1a)

where

 ------ (Eq. 1.1b)
 ------ (Eq. 1.1c)

and

 is primary self-inductance
 is primary leakage inductance
 is magnetizing inductance
 is inductive coupling coefficient
Measuring basic transformer inductances & coupling factor

Transformer self-inductances  &  and mutual inductance  are, in additive and subtractive series connection of the two windings, given by,

in additive connection, 
, and,

in subtractive connection, 

such that these transformer inductances can be determined from the following three equations:Harris 1952, p. 723, fig. 43

 
.

The coupling factor is derived from the inductance value measured across one winding with the other winding short-circuited according to the following:

Per Eq. 2.7,
 and  
Such that

The Campbell bridge circuit can also be used to determine transformer self-inductances and mutual inductance using a variable standard mutual inductor pair for one of the bridge sides.Khurana 2015, p. 254, fig. 7.33
It therefore follows that the open-circuit self-inductance and inductive coupling factor  are given by
 ------ (Eq. 1.2), and,
, with 0 <  < 1 ------ (Eq. 1.3)

where

and

 is mutual inductance
 is secondary self-inductance
 is secondary leakage inductance
 is magnetizing inductance referred to the secondary
 is inductive coupling coefficient
 is the approximate turns ratio

The electric validity of the transformer diagram in Fig. 1 depends strictly on open-circuit conditions for the respective winding inductances considered. More generalized circuit conditions are as developed in the next two sections.

Inductive leakage factor and inductance

A nonideal linear two-winding transformer can be represented by two mutual inductance-coupled circuit loops linking the transformer's five impedance constants as shown in Fig. 2. 

where

M is mutual inductance
 &  are primary and secondary winding resistances
Constants , , ,  &  are measurable at the transformer's terminals
Coupling factor  is defined as
, where 0 <  < 1 ------ (Eq. 2.1)
 
The winding turns ratio  is in practice given as
 ------ (Eq. 2.2).

where

NP & NS are primary and secondary winding turns
vP & vS and iP & iS are primary & secondary winding voltages & currents.

The nonideal transformer's mesh equations can be expressed by the following voltage and flux linkage equations,

 ------ (Eq. 2.3)
 ------ (Eq. 2.4)
 ------ (Eq. 2.5)
 ------ (Eq. 2.6),

where

 is flux linkage	
 is derivative of flux linkage with respect to time.

These equations can be developed to show that, neglecting associated winding resistances, the ratio of a winding circuit's inductances and currents with the other winding short-circuited and at open-circuit test is as follows,

 ------ (Eq. 2.7),

where,

ioc & isc are open-circuit and short-circuit currents	
Loc & Lsc are open-circuit and short-circuit inductances.
 is the inductive leakage factor or Heyland factor
 &  are primary and secondary short-circuited leakage inductances.

The transformer inductance can be characterized in terms of the three inductance constants as follows,
 ------ (Eq. 2.8) 
 ------ (Eq. 2.9) 
 ------ (Eq. 2.10) ,

where,

LM is magnetizing inductance, corresponding to magnetizing reactance XM
LPσ & LSσ are primary & secondary leakage inductances, corresponding to primary & secondary leakage reactances XPσ & XSσ.

The transformer can be expressed more conveniently as the equivalent circuit in Fig. 3 with secondary constants referred (i.e., with prime superscript notation) to the primary,

.

Since 
 ------ (Eq. 2.11)

and

 ------ (Eq. 2.12),

we have
 ------ (Eq. 2.13),

	
which allows expression of the equivalent circuit in Fig. 4 in terms of winding leakage and magnetizing inductance constants as follows,

 ------ (Eq. 2.14  Eq. 1.1b)
 ------ (Eq. 2.15  Eq. 1.1c).
The nonideal transformer in Fig. 4 can be shown as the simplified equivalent circuit in Fig. 5, with secondary constants referred to the primary and without ideal transformer isolation, where,
 ------ (Eq. 2.16)
 is magnetizing current excited by flux ΦM that links both primary and secondary windings
 is the primary current
 is the secondary current referred to the primary side of the transformer.

Refined inductive leakage factor
Refined inductive leakage factor derivation

a. Per Eq. 2.1 & IEC IEV 131-12-41 inductive coupling factor  is given by
 --------------------- (Eq. 2.1):
b. Per Eq. 2.7 & IEC IEV 131-12-42 Inductive leakage factor  is given by
 ------ (Eq. 2.7) & (Eq. 3.7a)
c.  multiplied by  gives
 ----------------- (Eq. 3.7b)
d. Per Eq. 2-8 & knowing that 
 ---------------------- (Eq. 3.7c)
e.  multiplied by  gives
 ------------------ (Eq. 3.7d)
f. Per Eq. 3.5  Eq. 1.1b & Eq. 2.14 and Eq. 3.6  Eq. 1.1b & Eq. 2.14:
 --- (Eq.3.7e)

All equations in this article assume steady-state constant-frequency waveform conditions the  &  values of which are dimensionless, fixed, finite & positive but less than 1.

Referring to the flux diagram in Fig. 6, the following equations hold:
	

	
σP = ΦPσ/ΦM = LPσ/LM ------ (Eq. 3.1  Eq. 2.7)
	
In the same way,
	
σS = ΦSσ'/ΦM = LSσ'/LM ------ (Eq. 3.2  Eq. 2.7)
	
And therefore,
	
ΦP = ΦM + ΦPσ = ΦM + σPΦM = (1 + σP)ΦM ------ (Eq. 3.3)
	
ΦS' = ΦM + ΦSσ' = ΦM + σSΦM = (1 + σS)ΦM ------ (Eq. 3.4)

LP = LM + LPσ = LM + σPLM = (1 + σP)LM ------ (Eq. 3.5  Eq. 1.1b & Eq. 2.14)	
	
LS' = LM + LSσ' = LM + σSLM = (1 + σS)LM ------ (Eq. 3.6  Eq. 1.1b & Eq. 2.14),
	
where

σP & σS are, respectively, primary leakage factor & secondary leakage factor
	
ΦM & LM are, respectively, mutual flux & magnetizing inductance
	
ΦPσ & LPσ are, respectively, primary leakage flux & primary leakage inductance
 
ΦSσ' & LSσ' are, respectively, secondary leakage flux & secondary leakage inductance both referred to the primary.
 	
The leakage ratio σ can thus be refined in terms of the interrelationship of above winding-specific inductance and Inductive leakage factor equations as follows:

 ------ (Eq. 3.7a to 3.7e).

Applications
Leakage inductance can be an undesirable property, as it causes the voltage to change with loading.

In many cases it is useful. Leakage inductance has the useful effect of limiting the current flows in a transformer (and load) without itself dissipating power (excepting the usual non-ideal transformer losses). Transformers are generally designed to have a specific value of leakage inductance such that the leakage reactance created by this inductance is a specific value at the desired frequency of operation. In this case, actually working useful parameter is not the leakage inductance value but the short-circuit inductance value.

Commercial and distribution transformers rated up to say 2,500 kVA are usually designed with short-circuit impedances of between about 3% and 6% and with a corresponding  ratio (winding reactance/winding resistance ratio) of between about 3 and 6, which defines the percent secondary voltage variation between no-load and full load. Thus for purely resistive loads, such transformers' full-to-no-load voltage regulation will be between about 1% and 2%.

High leakage reactance transformers are used for some negative resistance applications, such as neon signs, where a voltage amplification (transformer action) is required as well as current limiting. In this case the leakage reactance is usually 100% of full load impedance, so even if the transformer is shorted out it will not be damaged. Without the leakage inductance, the negative resistance characteristic of these gas discharge lamps would cause them to conduct excessive current and be destroyed.

Transformers with variable leakage inductance are used to control the current in arc welding sets. In these cases, the leakage inductance limits the current flow to the desired magnitude. Transformer leakage reactance has a large role in limiting circuit fault current within the maximum allowable value in the power system.

In addition, the leakage inductance of a HF-transformer can replace a series inductor in a resonant converter. In contrast, connecting a conventional transformer and an inductor in series results in the same electric behavior as of a leakage transformer, but this can be advantageous to reduce the eddy current losses in the transformer windings caused by the stray field.

See also

Blocked rotor test
Circle diagram
Mutual inductance
Steinmetz equivalent circuit
Short-circuit inductance
Short-circuit test
Voltage regulation

Notes

References

Bibliography

External links
IEC Electropedia links:

Linked flux
Ideal voltage source
Inductance
Ideal current source 
Coupling
Inductive coupling

Inductive coupling factor
Inductive leakage factor
Ideal transformer
Magnetic leakage factor
Self-inductance
Mutual inductance

Electric transformers

de:Streufluss#Streuinduktivität