Transformer oil testing. Transformer oil, a type of insulating and cooling oil used in transformers and other electrical equipment, needs to be tested periodically to ensure that it is still fit for purpose. This is because it tends to deteriorate over time. Testing sequences and procedures are defined by various international standards, many of them set by ASTM. Transformer oil testing consists of measuring breakdown voltage and other physical and chemical properties of samples of the oil, either in a laboratory or using portable test equipment on-site.

Motivation for testing
The transformer oil (insulation oil) of voltage transformers and current transformers fulfills the purpose of insulating as well as cooling. Thus, the dielectric quality of transformer oil is essential to secure operation of a transformer.

As transformer oil deteriorates through aging and moisture ingress, transformer oil should, depending on economics, transformer duty and other factors, be tested periodically. Electric utility companies have a vested interest in periodic oil testing because transformers represent a large proportion of their total assets. Through such testing, transformers' life can be substantially increased, thus delaying new investment of replacement transformer assets.

On-site testing 

Recently time-consuming testing procedures in test labs have been replaced by on-site oil testing procedures. There are various manufacturers of portable oil testers. With low weight devices in the range of 20 to 40 kg, tests up to 100 kV rms can be performed and reported on-site automatically. Some of them are even battery-powered and come with accessories.

Breakdown voltage testing procedure 

To assess the insulating property of dielectric transformer oil, a sample of the transformer oil is taken and its breakdown voltage is measured. The lower the resulting breakdown voltage, the poorer the quality of the transformer oil.

 The transformer oil is filled in the vessel of the testing device. Two standard-compliant test electrodes with a typical clearance of 2.5 mm are surrounded by the dielectric oil.
 A test voltage is applied to the electrodes and is continuously increased up to the breakdown voltage with a constant, standard-compliant slew rate of e.g. 2 kV/s.
 At a certain voltage level breakdown occurs in an electric arc, leading to a collapse of the test voltage.
 An instant after ignition of the arc, the test voltage is switched off automatically by the testing device. Ultra fast switch off is highly desirable, as the carbonisation due to the electric arc must be limited to keep the additional pollution as low as possible.
 The transformer oil testing device measures and reports the root mean square value of the breakdown voltage.
 After the transformer oil test is completed, the insulation oil is stirred automatically and the test sequence is performed repeatedly: typically 5 repetitions, depending on the standard.
 As a result the breakdown voltage is calculated as mean value of the individual measurements.

Types of test
Color; e.g., ASTM D1500.
Dielectric breakdown voltage; e.g., D 877, ASTM D1816
Dissolved gas analysis; e.g., ASTM D3612
Dissolved metals; e.g., ASTM D7151
Flash point, fire point; e.g., ASTM D92
Interfacial tension; e.g. D 971
Furanic compounds; e.g., ASTM D5837
Karl Fischer moisture; e.g., ASTM D1533
Liquid power factor; e.g., ASTM D924
Neutralization number; e.g., ASTM D974
Oxidation inhibitor content; e.g., ASTM D2668
Polychlorinated biphenyls content; e.g., ASTM D4059
Relative density (specific gravity); e.g., D 1298, ASTM D1524
Resistivity; e.g., ASTM D1169
Visual examination; e.g., D1524

International transformer oil testing standards 

 VDE370-5/96
 OVE EN60156
 IEC 60156/97,
 ASTM1816-04-1
 ASTM1816-04-2
 ASTM877-02
 ASTM877-02B
 AS1767.2.1
 BS EN60156
 NEN 10 156
 NF EN60156
 PA SEV EN60156
 SABS EN60156
 UNE EN60156
 IS:6792 
 IS 335

See also
 Electrical measurements
 Severity factor

References 

Electric transformers
Electrical tests