Turn to Turn Fault Detection for Air Core Reactors

The goal of this project is to create a small scale model of a 3 phase dry type shunt air core reactor in order to simulate and test inter-turn faults. The project will also entail an RTDS model of the system to further test more in depth fault scenarios, as well as correlating data.
==Problem==
===Background===
Avista deployed a system of air core reactors at their Noxon Rapids Dam in Montana in order to drop the bus voltage at the dam to help keep voltage levels even across the grid. Although the reactors have common protection schemes deployed already, there is currently no way for a protective relay to detect an inter-turn fault within a single phase of an air core reactor; a situation which could lead to complete failure and destruction of a reactor.
===Deliverables===
thumb|right|200x400px|Start/Stop Test Circuit
The goal of this project is to develop a protective relaying algorithm which will enable an IED, specifically an SEL 487E, to detect inter-turn faults within a single phase of an air core reactor.
===Specifications===
:* Voltage: 120V Line to Neutral
:* Current: Less than 5A
:* Wire: 15AWG
:* Multiple test points necessary for simulating short circuiting
:* Range of test coil inductance sizes to short across
:* Must be air-core
:* Needs to be solid and mobile with a non-conducting frame
==Project Learning==
===Client Interview===
:* Wrote a list of technical, budget, and miscellaneous questions for client to make sure we approached this project fitting our client's needs
:* From the answers we obtained, we were able to build a better foundation for starting this project
:*
===Lead Instructor and Technical Advisor Meetings===
:* Every week we meet with our lead instructor and our technical advisor to go over the progress of the project
:* Topics such as due dates, technical progress, budgets, and brainstorming are all discussed during these meetings
===Tour of Noxon Rapids Dam and Reactor Substation===
thumb|right|200x400px|Noxon Reactor Bank Tour
:*The VARsity senior design team along with the graduate student mentor were given a tour of Avista's Noxon Rapids Dam and reactor substation in order to ask questions and learn more insight into exactly how the work performed in the senior design project would benefit our customer's SEL and Avista.
===Load Calculations:===
:File:VARsity_Load_Calculations.JPG
===Self Wound Coil Calculations:===
thumb|right|200x400px|Hand Wound Shunt Coil
:File:Coil_Calculations_VARsity.JPG 
===Research===
:
==Design==
===Scaled Test Circuit===
thumb|right|200x400px|Jantzen Audio 10mH Inductor
In order to create an environment for testing, it will be necessary to build a scaled test circuit that can operate at 120V per phase which we can use to manipulate in order to test for inter-turn faults.
For the small scale model air core reactors, we will be using Jantzen Audio 10mH 15AWG air core inductors as seen to the right. The plan is to have about 7 of these per phase hooked in series to create the modeled inductor bank. On one of the phases, a single coil will be removed and replaced with a self wound coil that has been manipulated in order to introduce a shorted winding fault into the circuit.
The phase current is to be limited to run below 5 Amps RMS in order to deviate from having to use potential and current transformers for relay metering purposes.
For the design, we will use PVC pipe to stack the coils on top of each other vertically. two of the "towers" will be 80mH and the third tower will be 66mH with a 14mH special coil connected in series with multiple shorted test points to give three equal phases.
After stacking the coils on top of each other on the mounting frame, it was important to make sure each phase had the same amount of inductance and resistance. In order to compensate for the additional resistance on the test phase, a 1 Ohm power resistor was connected in series with the two steady state phases to bring us back to specifications.
===RTDS Model===
thumb|right|200x400px|RTDS Fault Simulation Circuit
In order to correlate data, it is necessary to have an RTDS model simulation program to see if certain test points give the same data during a fault condition. The model can also be easily scaled up to the rated values of the Noxon Reactor substation in order to see how well the small scale model correlates data during normal operating and fault conditions as opposed to the live system.
The RTDS model makes it easier to show the magnitude of the fault current that would flow through a shorted winding, as well as give the design team a good starting point as for the magnitude of fault to introduce on the small system.
Further down the road, the model may be used to hook up to an SEL relay's low level voltage test interface to be able to simulate the RTDS circuit to the relay to test protection schemes and validate relaying algorithms.
==Results==
After capturing fault and steady state current waveforms from the small-scale model and comparing them with the waveforms simulated by the RTDS model, we were able to prove that the small-scale model we created was an accurate representation of an air core reactor.
In addition to our testing, our graduate mentor Asad was successfully able to use the project to help defend his masters thesis which also helps validate our construction of the small-scale air core reactor.
thumb|right|200x400px|Final Small Scale Model
thumb|center|200x400px|RTDS Fault Waveform
==Team Information==
 	 	
 	Jacquelyn England 	Interests: Power Analysis
Hobbies: Hiking, Running, Fishing, Camping, Watching Movies.
 	Electrical Engineering 	Interests: Power Analysis
Hobbies: Hiking, Running, Fishing, Camping, Watching Movies.
 	Email: lyn.duffau.england@gmail.com	Interests: Power Analysis
Hobbies: Hiking, Running, Fishing, Camping, Watching Movies.
 	 	
 	Andrew Hoth 	Interests: Power and Microelectronics
Hobbies: Traveling
 	Electrical Engineering 	Interests: Power and Microelectronics
Hobbies: Traveling
 	Email: scypherhoth@gmail.com 	Interests: Power and Microelectronics
Hobbies: Traveling
 	Justin Jeter 	Interests: Power and Power Protection
Hobbies: Home brewing, active in Homebrewers of Palouse (HOPS), and placed in several brewing competitions. Hiking, camping, mountain biking, snowboarding, and anything outdoors . Motorcycling around PNW.
 	Electrical Engineering 	Interests: Power and Power Protection
Hobbies: Home brewing, active in Homebrewers of Palouse (HOPS), and placed in several brewing competitions. Hiking, camping, mountain biking, snowboarding, and anything outdoors . Motorcycling around PNW.
 	Email: justin_jeter@selinc.com 	Interests: Power and Power Protection
Hobbies: Home brewing, active in Homebrewers of Palouse (HOPS), and placed in several brewing competitions. Hiking, camping, mountain biking, snowboarding, and anything outdoors . Motorcycling around PNW.
150px|center	Tanner Mort 	Interests: Microcontrollers and Digital Systems, Power and Power Electronics, Automation.
Hobbies: Hunting, Fishing, Playing with my Dogs.
150px|center	Electrical Engineering 	Interests: Microcontrollers and Digital Systems, Power and Power Electronics, Automation.
Hobbies: Hunting, Fishing, Playing with my Dogs.
150px|center	Email: mort7075@vandals.uidaho.edu 	Interests: Microcontrollers and Digital Systems, Power and Power Electronics, Automation.
Hobbies: Hunting, Fishing, Playing with my Dogs.
150px|center	 	
==Document Archive==
===Client Interview===
:
===Design Review===
:
:
:
===Expo Poster===
:
===Final Report===
:
===Meeting Minutes===
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
: