Maksimal isroflar vaqtining “τ” maksimal yuklamalar ishlatilloyihasi “T” vaqtiga bog’liqligi

Maksimal isroflar vaqtining “τ” maksimal yuklamalar ishlatilloyihasi “T” vaqtiga bog’liqligi
T, soat
|
cosφ da τ(soat)ning qiymati
|
0,6
|
0,7
|
0,8
|
0,9
|
1
|
2000
|
|
1200
|
1000
|
900
|
800
|
3000
|
2800
|
2400
|
2000
|
1600
|
1300
|
4000
|
3300
|
3000
|
2700
|
2350
|
2000
|
5000
|
4000
|
3750
|
3500
|
3250
|
3000
|
6000
|
5000
|
4800
|
4600
|
4300
|
4000
|
7000
|
6000
|
5950
|
5900
|
5700
|
5500
|
8000
|
7300
|
7300
|
7300
|
7300
|
7300
|
8760
|
8760
|
8760
|
8760
|
8760
|
8760
|
6.6– jadval
Yuqori kuchlanish transformatorlarning texnik ma’lumotlari
To’la quvvati SN,MVA
|
Rusumi
|
UN, kV
|
∆Psx
kVt
|
∆Qs
|
RT
Om/km
|
XT
Om/km
|
Narxi
mln.
so’m
|
YuK
|
PK
|
35kV uch fazali ikki cho’lg’amli transformator
|
10
|
TDNS-10000/35
|
36,75
|
6,3 10,5
|
14,5
|
80
|
1,14
|
18
|
150
|
16
|
TDN-16000/35
|
36,75
|
10,5
|
21
|
120
|
0,48
|
6/75
|
180
|
25
|
TRDN-25000/35
|
36,75
|
10,5
|
29
|
175
|
0,31
|
5,1
|
205
|
32
|
TRDN-32000/35
|
36,75
|
10,5
|
33
|
224
|
0,23
|
4,85
|
260
|
40
|
TD-40000/35
|
36,75
|
10,5
|
39
|
260
|
0,15
|
2,87
|
245
|
40
|
TRDN-40000/35
|
36,75
|
10,5
|
30
|
260
|
0,2
|
2,9
|
320
|
63
|
TRDN-63000/35
|
36,75
|
10,5
|
55
|
378
|
0,1
|
2,5
|
400
|
80
|
TDS-80000/35
|
38,5
|
10,5
|
65
|
480
|
0,07
|
1,53
|
360
|
110kV uch fazali uch cho’lg’amli transformator
|
16
|
TDN-16000/110
|
115
|
6,6
|
21
|
136
|
4,38
|
86,7
|
280
|
25
|
TRDN-25000/110
|
115
|
11
|
29
|
200
|
2,54
|
55,5
|
400
|
32
|
TRDN-32000/110
|
115
|
11
|
35
|
240
|
1,87
|
43,5
|
440
|
40
|
TRDN-40000/110
|
115
|
11
|
42
|
280
|
1,44
|
34,8
|
500
|
40
|
TD-40000/110
|
121
|
6,3
10,5
|
52
|
280
|
1,44
|
34,8
|
360
|
63
|
TRDTSN-63000/110
|
115
|
10,5
|
59
|
410
|
0,7
|
22
|
600
|
80
|
TRDTSN-80000/110
|
115
|
10,5
|
70
|
480
|
0,5
|
17,2
|
640
|
80
|
TD-80000/110
|
121
|
6,3 10,5
|
70
|
480
|
0,65
|
1723
|
450
|
125
|
TDS-125000/110
|
121
|
10,5
|
120
|
678
|
0,33
|
11,1
|
520
|
200
|
TDS-200000/110
|
121
|
13,8
|
170
|
1000
|
0,23
|
6,95
|
800
|
250
|
TDS-250000/110
|
121
|
15,75
|
200
|
1250
|
0,17
|
5,55
|
920
|
220kV uch fazali uch cho’lg’amli transformator
|
32
|
TRDN-32000/220
|
230
|
6,6
|
53
|
288
|
8,66
|
198,5
|
420
|
63
|
TRDTSN-63000/220
|
230
|
6,6 11
|
82
|
504
|
4
|
100
|
680
|
80
|
TD-80000/220
|
242
|
6,3 10,5
|
105
|
480
|
2,64
|
72,8
|
640
|
100
|
TRDTSN-100000/220
|
230
|
11
|
115
|
700
|
1,9
|
62
|
840
|
125
|
TDS-125000/220
|
242
|
6,3
|
135
|
625
|
1,27
|
46,5
|
720
|
160
|
TRDTSN-160000/220
|
230
|
11
|
167
|
960
|
1,08
|
39,7
|
1000
|
200
|
TDS-200000/220
|
242
|
13,8
|
200
|
900
|
0,77
|
29
|
920
|
250
|
TDS-250000/220
|
242
|
13,8
|
240
|
1125
|
0,55
|
23,2
|
1000
|
6.7(a) jadval
110kV uch fazali uch cho’lg’amli transformator
To’la quvvati
SN, MVA
|
Rusumi
|
UN, kV
|
ΔPSI
kVt
|
ΔQSI
kVAr
|
Yuk
|
O’K
|
PK
|
25
|
TDTN-25000/110
|
115
|
38,5
|
6,6
1,1
|
36
|
1000
|
40
|
TDTN-40000/110
|
115
|
38,5
|
-
|
50
|
1560
|
63
|
TDTN-63000/110
|
115
|
38,5
|
-
|
70
|
2144
|
80
|
TDSTN-80000/110
|
115
|
38,5
|
-
|
82
|
2560
|
220kV uch fazali uch cho’lg’amli transformator
|
25
|
TDTN-25000/220
|
230
|
38,5
|
6.6
1,1
|
50
|
1200
|
32
|
A TDTN-32000/220/110
|
230
|
121
|
-
|
32
|
800
|
40
|
TDTN-40000/220
|
230
|
38,5
|
-
|
66
|
1760
|
63
|
TDTN-63000/220
|
230
|
38,5
|
-
|
91
|
2520
|
63
|
ATDTN-63000/220/110
|
230
|
121
|
-
|
45
|
1260
|
80
|
ATDTN-80000/220/110
|
230
|
121
|
-
10,5
|
-
|
-
|
100
|
ATDTSN-100000/220/110
|
230
|
121
|
6,6
1,1
|
75
|
2000
|
125
|
ATDTSN-125000/220/110
|
230
|
122
|
6,6
1,1
|
85
|
2500
|
160
|
ATDTSN-160000/220/110
|
230
|
121
|
6,6
1,1
|
100
|
3200
|
200
|
ATDTSN-200000/220/110
|
230
|
121
|
-
|
125
|
4000
|
6.7(b) jadval
110kV uch fazali uch cho’lg’amli transformator (Davomi)
To’la quvvati SN, MVA
|
Rusumi
|
Rt, Om
|
Xt, Om
|
Narxi mln.
so’m
|
Yuk
|
O’K
|
PK
|
YuK
|
O’K
|
PK
|
25
|
TDTH-25000/110
|
1,5
|
1,5
|
1,5
|
54
|
0
|
33
|
408
|
40
|
TDTH-40000/110
|
0,95
|
0,95
|
0,95
|
35,4
|
0
|
20,6
|
420
|
63
|
TDTH-63000/110
|
0,52
|
0,52
|
0,52
|
22,6
|
0
|
13,1
|
600
|
80
|
TDSTH-80000/110
|
0,4
|
0,4
|
0,4
|
27,6
|
0
|
10,3
|
680
|
6.8- jadval
220kV uch fazali uch cho’lg’amli transformator va avtotransformatorlar. (Davomi)
To’la quvvati SN, MVA
|
Rusumi
|
Rt, Om
|
Xt, Om
|
Narxi mln.
so’m
|
Yuk
|
O’K
|
PK
|
YuK
|
O’K
|
PK
|
25
|
TDTH-25000/220
|
5,72
|
5,72
|
5,72
|
276
|
0
|
148
|
532
|
32
|
ATDTH-32000/220/110
|
3,74
|
3,74
|
7,5
|
198
|
0
|
364
|
508
|
40
|
TDTH-40000/220
|
3,97
|
3,97
|
3,97
|
165
|
126
|
0
|
624
|
63
|
TDSTH-63000/220
|
2,13
|
2,13
|
2,13
|
109
|
92,5
|
0
|
704
|
63
|
ATDTH-63000/220110
|
1,43
|
1,43
|
2,9
|
100
|
0
|
193
|
664
|
80
|
ATDTH-80000/220/110
|
-
|
-
|
-
|
-
|
-
|
-
|
732
|
100
|
ATDSTH-100000/220/110
|
0,69
|
0,69
|
1,38
|
60,8
|
0
|
103
|
816
|
125
|
ATDSTH-125000/220/110
|
0,5
|
0,5
|
1
|
48,6
|
0
|
82,5
|
888
|
160
|
ATDSTH-160000/220/110
|
39
|
0,78
|
-
|
38
|
0
|
68
|
992
|
200
|
ATDSTH-200000/220/110
|
0,39
|
0,2
|
1,5
|
30,4
|
0
|
54
|
1104
|
6.9 – jadval
|