nyuuzyou/kompy huggingface dataset:
Namangan Institute of Engineering and Technology

|
Namangan Institute of Engineering and Technology Pdf ko'rish
|
bet | 30/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq ТўпламNamangan Institute of Engineering and Technology
nammti.uz
10.25.2023
Pg.26
∆𝑈
𝑛.𝑘
=
∆𝑈
𝑈
𝑛
=
𝐼
𝑎
𝑅 + 𝐼
𝑟
𝑋
𝑈
𝑛
=
𝑃𝑅 + 𝑄𝑋
𝑈
𝑛
=
𝑃
𝑅
𝑋 + 𝑄
√3𝑈
𝑛
𝑈
𝑛
𝑋
≈
𝑄
𝑆
𝑞𝑡
, (4)
bu yerda:
𝑆
𝑞𝑡
−
qisqa tutashuv (QT) quvvati,
𝑃 −
aktiv quvvat,
𝑄 −
reaktiv quvvat.
(5) formuladan ko‘rinib turibdiki, elektr tarmoqlarida ko‘p hollarda kuchlanish rejimi reaktiv
quvvat rejimi bilan bog‘liq [4], [6].
Viloyatdagi mavjud tekstil korxonalardan biri “National silk cotton” ga tegishli quvvati 1000
kVA bo‘lgan transformatorda tadqiqot ishlari olib borildi. Tadqiqot natijasida elektr energiyasining
sifat ko‘rsatkichlari aniqlash “Malika-01” qurilmasida amalga oshirildi.
𝑺
𝒏𝒐𝒎
= √𝑷
𝟐
+ 𝑸
𝟐
(5)
Bu yerda kuchlanishning minimal qiymati
𝑈
𝑚𝑖𝑛
= 198 𝑉
ni, maksimal qiymati
𝑈
𝑚𝑎𝑥
= 221 𝑉
ni tashkil etgan. Bu GOST 32144-2013 talabi bo‘yicha chegaraviy qiymatgacha o‘zgarishini ko‘rsatib
turibdi. Bundan kelib chiqib transformatorda (kuzatilayotgan korxonada) reaktiv quvvatni
kompensatsiyalash zarurligini ko‘rish mumkin [4].
𝑺
𝒏𝒐𝒎
= √𝑷
𝟐
+ (𝑸 − 𝑸
𝒌
)
𝟐
(6)
𝑄
𝑘
= 𝑃 ⋅ tan 𝜑
(7)
[5] dan foydalanib kompensatsiyalanishi zarur bo‘lgan reaktiv quvvat miqdori aniqlanadi.
Shundan so‘ng quvvati 180 kVAr li, PRF-12 tipli avtomatik reaktiv quvvatni kompensatsiyalash
qurilmasi o‘rnatildi. Bu qurilma istemolchi qancha reaktiv quvvat istemol qilayotganini o‘lchaydi va
kerakli bo‘lgan reaktiv quvvatni avtomatik ravishda tarmoqqa ulaydi va uzadi [6]. Qurilmaning 12 ta
pog‘onasi mavjud bo‘lib har-bir pog‘onasiga kondensator batareyasi ulandi va avtomatik ravishda
pog‘onalar boshqarilib tarmoqqa reaktiv quvvatni silliq ta’minlashga erishiladi.
Bundan tashqari bir-biriga yaqin oraliqlardagi kuchlanishning qiymatlarining takrorlanishi
ham ortgan. Kompensatsia qurilmasi o‘rnatilgandan so‘ng kuchlanishning qiymati nominal holatga
nisbatan 5 % dan kamroqga o‘zgarishini ko‘rishimiz mumkin.
|
| |
Regenerativ takrorlagich (Regenerative Repeater)

|
Regenerativ takrorlagich (Regenerative Repeater)
|
bet | 5/35 | Sana | 22.05.2024 | Hajmi | 9,66 Mb. | | #249839 |
Bog'liq Raqamli YNRegenerativ takrorlagich (Regenerative Repeater)
Qayta tiklanadigan takrorlagich signalning yo'qolishini kompensatsiya qilish va signalni qayta tiklash uchun ishlatiladi. Shuningdek, u signal kuchini oshirishga yordam beradi. Demak, kanalning chiqishi bitta regenerativ takrorlash sxemasi bilan jihozlanadi.
Dekoder (Decoder)
Dekoder impuls kodli to'lqin shaklini dekodlash orqali asl signalni shakllantirishga yordam beradi. Dekoder demodulyator vazifasini bajaradi.
Qayta tiklash filtri (Reconstruction Filter)
Qayta tiklash filtri asl signalni olishga yordam beradi. Impuls kod modulatori sxemasida berilgan analog signal raqamlashtiriladi, kodlanadi va diskretlanadi. Olingan signal analog shaklda uzatiladi. Asl signalni olish uchun butun jarayon teskari tartibda takrorlanadi.
6-savol.Impuls kodli modulyatsiyaning afzalliklari
Yuqori shovqinbardoshlilik (High noise immunity)
Shovqinbardoshik tizimning shovqindan ta'sirlanmaslik qobiliyatini anglatadi. IKM yuqori shovqinbardoshhlilikka ega, chunki axborot impulsning kengligi yoki holatini o'zgartirishdan ko'ra kodlangan shaklda (raqamli shaklda) uzatiladi, bu shovqindan kamroq ta'sirlanadi.
Uzoq masofaga uzatish (Long distance transmission)
Raqamli signallarni uzatish tezligi analog signallarga qaraganda tezroq. Shunday uchun IKM uzoq masofalarga uzatish jarayoni uchun qo‘llanilishi mumkin.
Oson kodlash immkoniyati (Easy encoding)
IKM ni kodlash jarayoni ma'lumotlarning raqamli uzatilishi tufayli oson hisoblanadi.
Xavfsiz uzatish (Secure transmission)
IKM da ma’lumotlarni uzatish jarayoni kodlash va dekodlash mavjudligi sababli xavfsiz hisoblanadi. Shuningdek, turli xil kodlash usullaridan foydalanish mumkin, ular orqali faqat ma’lum bir foydalanuvchi chiqishdagi signalni dekodlashi mumkin.
|
| |
Namangan Institute of Engineering and Technology

|
Namangan Institute of Engineering and Technology Pdf ko'rish
|
bet | 18/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq ТўпламNamangan Institute of Engineering and Technology
nammti.uz
10.25.2023
Pg.15
matching the colors of the dispersion spectrum, is called the dispersion angle: the width of the
spectrum depends on this angle and is calculated using the formula;
(n
1) (1)
The external appearance of the spectra can vary greatly depending on the characteristics of
the light source in a dark environment. There are three main types of spectra: continuous spectra,
line spectra, and band spectra. Continuous spectra encompass all colors (wavelengths), transitioning
smoothly from one color to the next (Figure 4a).
Figure 4a
The line spectrum consists of distinct, narrow, dark intervals separated by wide black regions
(Figure 4b).
Figure 4b
Each line corresponds to a specific wavelength of light. The band spectrum is a distinct group
formed by a large number of closely spaced lines. The lines within each group are so closely packed
that when viewed through a tool with limited resolution, they appear as a single band (Figure 4-d).
Figure 4d
In this way, each path corresponds to a specific interval of light wavelength.
The interaction between line spectra is the result of individual atoms that have absorbed light.
This is due to the transition of the involved electrons to lower energy levels (orbitals).
Band spectra, on the other hand, result from interactions among individual molecules.
In atoms, the emission of light is due to the vibrational motions of atoms in molecules, similar
to the transitions of electrons in atoms.
The combination of molecules and atomic ions that interact with each other produces the
spectra of continuous spectra. In this case, chaotic motion (vibration and rotation) plays a major
role, which occurs due to the higher states of the particles.
Therefore, the emission spectra of condensed and solid bodies and condensed gases differ
from the ones mentioned earlier. Excited gases (atoms and molecules, for example, excited by
heating or electrical discharge) exhibit line and band spectra. Single-atom gases, on the other hand
(inert gases, metal vapors, dissociated multiple-atom gases), exhibit line spectra.
For each chemical element (in a gaseous or condensed state), its characteristic emission
spectrum exists, characterized by the number of spectral lines, their colors, and their arrangement.
The spectral method (spectral analysis) is based on identifying the chemical composition of
substances.
If the source of the emission spectrum is initially a condensed gas (or solid), then in the
spectrum, the emission lines (or bands) of that gas will appear. Such a spectrum is called an
|
| |
Namangan Institute of Engineering and Technology

|
Namangan Institute of Engineering and Technology Pdf ko'rish
|
bet | 19/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq ТўпламNamangan Institute of Engineering and Technology
nammti.uz
10.25.2023
Pg.16
absorption spectrum, and according to Kirchhoff's law, the appearance of these lines in the gas
spectrum corresponds to the same lines that this gas absorbs.
The absorption spectrum of the solar atmosphere (photosphere) serves as an example of such
an absorption spectrum. In the emission spectrum of the solar radiation, dark absorption lines can
be observed (Figure 4-e), and these lines are called Fraunhofer lines.
Figure 4e
Studying spectra is of great importance in understanding the processes that occur in atoms
and molecules, and is crucial in understanding the structure of substances.
References
1.
17.02.2012y “Uzbekiston Today” xaftalik gazetasi
2.
Yunusov B.Yu. YunusovaT.Q Geliokonvektivnaya sushka selg’xozproduktov
3.
Sovremennqe problemq energetiki Mejd. Konfer-ya , Tashkent 2011
4.
B.E. Xayriddinov, N.S. Xolmirzayev,B.N. Sattorov. “Quyosh energiyasidan foydalanishning
fizik asoslari”. О’zbekiston Respublikasi Fanlar akademiyasi «Fan» nashriyoti. Toshkent-2011
YOMG’IR TOMCHISIDAN ELEKTR ENERGIYASI OLISH
N.S.Abduhalilov, O.B.Ergashev
Namangan muhandislik-texnologiya instituti
Annotatsiya: Hozirgi kunda elektr energiyasi muammo bo’layotgan bir paytda aholiga elektr
energiyasini uzluksiz yetkazib berish uchun turli elektr stantsiyalar qurilmoqda shu qatorda yana bi
energiya ishlab chiqarish uchun yomg’irda foydalanib elektr energiya olish mumkindir bunda bir
tomchi yomg‘ir energiyasi 100 dona yorug‘lik diodli lampochkani yoqishga yetadi.
Kalit so’zlar: Yomg’ir energiyasi, tomchi, generator, oksid, elektrod, politetraftoretilen
plenkalari.
Yomg‘ir tomchilari generator plastinasi yuzasiga tushib, alyuminiyli elektrod hamda indiy va
qalay oksidli elektrod orasida suv ko‘prigini hosil qiladi. Ushbu qurilmada tomchilar rezistor,
qoplama esa kondensator vazifasini bajaradi.
Kelajakda har qanday yuzaga – uy tomi, qayiq korpusi yoki soyabonga tushadigan yomg‘ir
tomchilaridan energiya olish mumkin bo‘ladi. Yilning ma'lum davrida kuchli yog‘ingarchiliklar yuz
beradigan hududlarda esa energiya olishning bu usuli katta foyda keltirishi mumkin.
To‘g‘ri, o‘z-o‘zimizni aldamaylik, hozircha bu yo‘nalishda olinayotgan elektrda smartfonni ham
quvvatlantirib bo‘lmaydi. Bungacha hali ancha bor. Biroq, ishlab chiqilgan uslub, umid uyg‘otadi. Gap
shundaki, tadqiqotchilar yomg‘irning bittagina tomchisidan 100 ta svetodiod lampochkalarini
yoritish uchun yetadigan usulni ishlab chiqdi.
Elektr quvvati olishning bunday uslubi ko‘p yillardan beri olimlarni o‘ylantirib kelardi. Yomg‘ir
tomchilari quvvatini elektr quvvatiga aylantirish fizikasi, oqimdan energiya olishga qaraganda bir
muncha murakkab. Muntazam ravishda tomchilar tushayotgan maydondan politetraftoretilen
plenkalari (PTFE) orqali zaryadlarni yig‘ib olish g‘oyasi umumiy maqsadning salgina siljishiga
ko‘maklashdi.
|
| |
XALQARO ENERGETIKA TIZIMIDA ENERGIYA ISHLAB CHIQARISH MUAMMO VA YECHIMLAR

Namangan Institute of Engineering and Technology
nammti.uz
10.25.2023
Pg.20
Biz "energiya mutaxassislari triadasi" haqida gapirishimiz mumkin. muammolar”, har
tomondan eng katta ta'sir ko'rsatadi! inson hayotiga taalluqlidir va sivilizatsiyaning barqaror
rivojlanishining asoslariga ta'sir qiladi.
Ushbu triada quyidagilardan iborat:
• energiya resurslari va elektr energiyasi taqchilligi (jurnalistlar bu muammoni “energiya
ochligi” deb atashgan);
• atrof-muhitning farovonligiga tahdid! energiya inshootlaridan texnogen ta'sirlarning ta'siri!
getiklar ("ekologik infarkt" tahdidi);
• geosiyosiy va ijtimoiy tahdidlar.
Birinchi muammo bugungi va juda uzoq kelajak uchun asosiy energiya manbalarining tugashi
(qayta tiklanmasligi) bilan bog'liq. Resurslari (bugungi kunda elektr energiyasining 80% dan ortig'i
ishlab chiqariladi) ularning sayyora bo'ylab taqsimlanishining o'ta notekisligi bilan og'irlashadi. Hatto
G8 ichida ham energiya taqchilligi bor. Energiya zichligi (mavjud energiya resurslari hajmining
ularning talab qilinadigan hajmiga nisbati) kattalik tartibida o'zgaradi, rasm.
Energiya ta'minotini oshirishning 2 yo'li bor.
1) o'z energiya resurslarini (qayta tiklanmaydigan va qayta tiklanadigan) qidirish va
rivojlantirish;
2) energiya tejash va energiyani oshirish samaradorlik.
Namangan Institute of Engineering and Technology

|
Namangan Institute of Engineering and Technology Pdf ko'rish
|
bet | 20/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq ТўпламNamangan Institute of Engineering and Technology
nammti.uz
10.25.2023
Pg.17
Tomchi yuzaga tushganida yoyilib ketib, xuddi ikki elektrod – alyumniy elektrodi va idniy-qalay
oksidi elektrodini birlashtiruvchi ko‘prik vazifasini bajarishi aniqlandi. “Tomchi ko‘prik” o‘z navbatida
yopiq halqa hosil qiladi, natijada yig‘ilgan energiya ozod bo‘ladi, chiqib ketadi. Tomchilar rezistor,
yuza esa kondensator vazifasini bajaradi.
Bunday uslubni suv qattiq yuzaga tushadigan hamma joyda qo‘llab ko‘rish mumkin. Biroq,
yomg‘ir smartfonimizni quvvatlantirishni boshlashidan oldin anchagina harakatlarni amalga oshirishi
kerak bo‘ladi.
O’zbekiston hududida hozirgi kunda yomg’ir kam yog’ishi hisobga olgan holda bu usuldan
foydalanish uchun suniy yomg’irlardan foydalanishga to’g’ri keladi.
Suvning piezoelektrikligi - bu ma'lum materiallarga ega bo'lgan xususiyat bo'lib, ular mexanik
energiyani elektr energiyasiga aylantirish imkonini beradi. Ushbu holatda, mexanik energiya
pyezoelektrik polimerga tushgan suv tomchilari tomonidan hosil bo'ladi. Tizim Frantsiyadan,
xususan, CEA/Leti-MINATEC kompaniyasidan keladi, u yerda olimlar guruhi yomg'ir ta'sirida
energiya ishlab chiqarish mumkinligini aniqladi.
Biroq, bu barcha materiallar uchun ishlamasligi aniq. Ushbu loyiha uchun ular PVDF folgasidan
foydalanganlar, ular eng yaxshi ishlashiga aminlar. Yuqoridagi barcha tizimlardan, Bu eng kam
miqdorda elektr energiyasi ishlab chiqaradigan, ammo uni yaxshilash bo'yicha tadqiqotlar
allaqachon olib borilmoqda.
Dastlab tadqiqotchilar Fransiyaning yomg‘ir ko‘p yog‘adigan mintaqasida har bir kubometrdan
maksimal 1 vatt-soat elektr energiyasini olish mumkinligini hisoblab chiqdi. Agar bu raqamlar to'g'ri
bo'lsa, ishlab chiqarilgan energiya faqat kichik kam iste'mol qilinadigan qurilmalarni
quvvatlantirishga qodir bo'ladi.
Foydalanilgan adabiyotlar ro’yxati
1.
Ya.D. Muxiddinova, D.N. Mamedova, I.N. Qodirov, S.I. Hamrayev. « Issiqlik yuritkichlar va
bosim bilan haydash mashinalari » II – qism. Bosim bilan haydash mashinalari. Darslik - Toshkent-
2019 y.
2.
Саламахова
Т.С.,
Чебышева
К.В.
«Центробежные
вентиляторы»ю
Учебник - М.: Машиностроение, 2001.
3.
Малющенко В.В., Михайлов А.К. Энергетические насосы и компрессоры. Справочное
пособие. – М.: Энергоиздат, 2000.
4.
А.В. Шегляев. Паровие турбини. Энергия, 1967 й.
5.
NATURE jurnali 2020.05.02.
|
| |
4-Laboratoriya ishi gvrp protokolini sozlash va uning ishlash prinsipini o‘rganish Ishning maqsadi

4-Laboratoriya ishi gvrp protokolini sozlash va uning ishlash prinsipini o‘rganish Ishning maqsadi
Download
0,65 Mb.
Matnni ko'rish
bet
1/5
Sana
21.05.2024
Hajmi
0,65 Mb.
#249290
Download
0,65 Mb.
Matnni ko'rish
Bosh sahifa
Aloqalar
Bosh sahifa
Dərs
Mühazirə
Qaydalar
Referat
Xülasə
Yazı
4-Laboratoriya ishi gvrp protokolini sozlash va uning ishlash prinsipini o‘rganish Ishning maqsadi
Download
0,65 Mb.
Matnni ko'rish
Информационные технологии в образовании

|
Информационные технологии в образовании
|
bet | 1/8 | Sana | 24.11.2023 | Hajmi | 16,48 Mb. | | #104869 |
Bog'liq 1 - ma\'ruza. TAT predmet vazifasipptx “TA’LIMDA AXBOROT TEXNOLOGIYALARI” fani
1 – ma’ruza
Taʼlimda axborot texnologiyalari fanining predmeti, maqsadi va vazifalari
Axborotlarga ishlov berish qurilmalari
va ularning tasnifi
Zamonaviy kompyuterlar va ularning
dasturiy ta’minoti
Taʼlimda axborot texnologiyalari fanining
predmeti, maqsadi va vazifalari
MAVZU REJASI:
Texnik vositalarning rivojlanish
tendentsiyalari
Foydalanilgan adabiyotlar ro‘yxati: - S.Tursunov, I.Nazarov. Ta’limda axborot texnologiyalari. Darslik. Toshkent: “Adabiyot uchqunlari”, 2019. 1-tom, 4-64 b.
- N.X.Shoaxmedova, I.M.Abdullayeva. Iqtisodiyotda axborot-kommunikatsion texnologiyalar va tizimlar: Darslik. – T.: «Iqtisodiyot», 2021. – 33 b.
- https://znanio.ru/media/kompyuterning-zamonaviy-texnik-va-dasturiy-taminoti-2522631
- https://uz.wikipedia.org/wiki/Kompyuter
ASOSIY TUSHUNCHALAR: Axborot tеxnologiyasi – ob’yеktning (axborot mahsulotining) holati, jarayon yoki voqеaning yangi xususiyati to‘g‘risida axborot olish uchun ma’lumotlarni yig‘ish, qayta ishlash va uzatish vositalari va usullari majmuidan foydalaniladigan jarayondir. Axborot texnologiyalari usullari bu ma’lumotlarni qayta ishlash va uzatish usullari hisoblanadi. Axborot texnologiyalari vositalari - texnik, dasturiy ta’minot, axborot va boshqa vositalar, ularning yordamida axborot texnologiyalari iqtisodiy ob’ektda amalga oshiriladi
1. Taʼlimda axborot texnologiyalari fanining predmeti, maqsadi va vazifalari.
talabaning kasbiy faoliyati bo‘yicha qo‘yilgan masalalarni yechishda zarur dasturiy vositalarni tog‘ri tanlash;
olingan bilimlar asosida qo‘yilgan masalalarni yecha olish;
zamonaviy axborot texnologiyalari vositalaridan mustaqil foydalana olish ko‘nikmalariga ega bo‘lishga qaratilgan.
|
| |
Namangan Institute of Engineering and Technology nammti uz - bet 682

|
Namangan Institute of Engineering and Technology nammti uz Pdf ko'rish
|
bet | 682/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq Тўплам
356
А.Асқаров.
Эффективные методы автоматизации пожарной безопасности
на трубопроводах транспортировки хлопка
358
А.Асқаров.
Использование систем детекции горения
359
M.A.Ismanov.
Paxta g’aramidagi haroratni avtomatik o’lchab, nazorat qilib
turuvchi scada-tizimining asosiy afzalliklari
361
M.A.Ismanov.
Jarayonlarni loyhalashda tizimli sxematik diagrammasini ishlab
chiqish
363
М.М.Абдумажидова, Д.М.Набижонов.
Автоматик бошқариш системаси
ёрдамида ростлаш тизимини ишлаб чиқиш
366
М.М.Абдумажтдова.
Управление
запасами
и
снабжением:
автоматизированные системы учета тканей и аксессуаров
369
М.М.Абдумажтдова, Х.Ф.Қодиров.
Автоматизация производственных
линий: роботизированные системы для резки и обработки тканей
370
М.М.Абдумажтдова, Д.А.Ахмадалиева.
Стандарты и нормативы в
автоматизации: ознакомление с применимыми стандартами и требованиями
в автоматизации производства
372
D.M.Nabijonov,
M.M.Abdumajidova.
Ta'lim
muassasalarida
arduino
mikrokontrollerlarini qo'llashning zamonaviy tendentsiyalari
373
Д.М.Набижонов,
М.М.Абдумажтдова.
Недавно
в
спектроскопии
инфракрасной (нси) при определении влаги хлопка
375
D.M.Nabijonov, I.I.Ibroximov.
Texnologik jarayonlarni avtomatlashtirishda
mikrokontrollerlardan foydalanish va ularga dastur yozishda dasturini ahamyati
376
|
| |
nammti.uz 
10.25.2023
Pg.623 
X.B.Madaliyev, J.J.Jumabayev

|
nammti.uz
10.25.2023
Pg.623
X.B.Madaliyev, J.J.Jumabayev Pdf ko'rish
|
bet | 684/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq Тўпламnammti.uz
10.25.2023
Pg.623
X.B.Madaliyev, J.J.Jumabayev.
The application of machine learning algorithms
for predictive maintenance and process optimization in manufacturing and
industrial settings
395
X.B.Madaliyev, H.K.Najmiddinov.
Applications of mechatronics and automation
in education: technologies and the future of education
397
Х.Б.Мадалиев, Х.К.Нажмиддинов.
Современная микропроцессорная
техника и влияние программного обеспечения на мехатронные системы
399
M.O.Xamidxonov.
Issiqlik energetikasi ob’yektlari agregatlarini texnologik
parametrlarini intellektual-adaptiv boshqarish tizimi
400
M.O.Xamidxonov, R.T.Yoqubjonov.
Neyrokontrollerli adaptiv-neyron boshqarish
tizimi
404
D.T.Qodirov,
Sh.Sh.Sharibboyev.
Sanoat
robotlarida
energiya
sarfini
optimallashtirish va qayta dasturlash muammolari
408
Ш.С.Джураев, Р.Н.Шарифбаев.
Разделение коконов с использованием
искусственного интеллекта
412
Sh.S.Djuraev, R.N.Sharifbayev.
Cocoon separation using artificial intelligence
414
A.A.Axmadaliyev.
Sun'iy intellekt neyron tarmoqlar daraxti
416
A.A.Axmadaliyev.
Raqamli o'lchash vositalarini qiyoslash va ulardan foydalana
olish
418
Ш.С.Джураев, А.А.Хошимов.
Алгоритмы диагностики асинхронных машин
по сигналам вибрации
420
Sh.S.Djuraev, A.A.Khoshimov.
Algorithms for diagnosing asynchronous
machines using vibration signals
|
| |
Д.М.Набижонов, С.Ж.Нуриддинов

|
Д.М.Набижонов, С.Ж.Нуриддинов Pdf ko'rish
|
bet | 683/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq ТўпламД.М.Набижонов, С.Ж.Нуриддинов.
Методы обнаружения хлопка
378
Д.М.Набижонов.
Интеграция промышленных сетей: рассмотрение сетевых
технологий и стандартов для связи и управления оборудованием
379
К.Я.Тошпулатов.
Развитие цифровой экономики: вызовы и перспективы
380
К.Я.Тошпулатов.
Интегрированные системы управления: механизмы
автоматической регулировки
381
К.Я.Тошпулатов,
Л.У.Вохиджанов.
Автоматизированные
системы
управления и их роль в промышленности
383
К.Я.Тошпулатов, М.Э.Абдухамидхонов.
Природа и структура организаций,
и роль оргуправленческого мышления
384
К.Я.Тошпулатов, А.К.Жўрабоев.
Мехатроника: обзор учебной, научной и
практической литературы
386
К.Я.Тошпулатов.
Развитие цифровой экономики: вызовы и перспективы
388
К.Я.Тошпулатов.
Интегрированные системы управления: механизмы
автоматической регулировки
390
К.Я.Тошпулатов,
Л.У.Вохиджанов.
Автоматизированные
системы
управления и их роль в промышленности
391
X.B.Madaliyev.
The importance of infrared sensors in preventing fire safety in
production enterprises
393
X.B.Madaliyev, J.J.Jumabayev.
The importance of infrared sensors in preventing
fire safety in production enterprises
394
Namangan Institute of Engineering and Technology
|
| |
Ishni bajarish tartibi - 4-Laboratoriya ishi gvrp protokolini sozlash va uning ishlash prinsipini o‘rganish Ishning maqsadi

bo„lganda qo„llash
va olib tashlash kerak, ammo bu odatda administrator uchun
ko„p vaqt talab qiladigan vazifadir va ko„pincha konfiguratsiya
xatolari inson
xatosi
bilan
bog„liq.
Administrator
VLAN
boshqaruv
jarayonini
soddalashtirmoqchi va barcha kommutatorlarda GVRPni yoqishni va interfeyslarda
ro„yxatga olish rejimini o„rnatishni so„radi. Ushbu laboratoriya ishida GVRP ni
sozlash va ro„yxatga olish rejimini o„rnatishni ko„rib chiqiladi.
Qurilmalarni sozlash quyidagicha amalga oshiriladi.
Birinchi navbatda
qurilmalarga nom berish amalga oshiriladi.
LSW1 kommutatorni sozlash:
system-view
[Huawei]sysname LSW1
LSW2 kommutatorni sozlash:
system-view
[Huawei]sysname LSW2
LSW3 kommutatorni sozlash:
system-view
[Huawei]sysname LSW3
LSW4 kommutatorni sozlash:
system-view
[Huawei]sysname LSW4
Kommutatorlar orasida magistral aloqalar (trunk) sozlanadi:
LSW1 kommutatorni sozlash:
[LSW1]interface ethernet 0/0/13
[LSW1-Ethernet0/0/13]port link-type trunk
[LSW1-Ethernet0/0/13]port trunk allow-pass vlan all
LSW3 kommutatorni sozlash:
[LSW3]interface Ethernet 0/0/13
[LSW3-Ethernet0/0/13]port link-type trunk
[LSW3-Ethernet0/0/13]port trunk allow-pass vlan all
[LSW3]interface ethernet 0/0/1
[LSW3-Ethernet0/0/1]port link-type trunk
[LSW3-Ethernet0/0/1]port trunk allow-pass vlan all
LSW4 kommutatorni sozlash:
[LSW4]interface ethernet 0/0/14
[LSW4-Ethernet0/0/14]port link-type trunk
[LSW4-Ethernet0/0/14]port trunk allow-pass vlan all
[LSW4-Ethernet0/0/14]quit
[LSW4]interface ethernet 0/0/1
[LSW4-Ethernet0/0/1]port link-type trunk
[LSW4-Ethernet0/0/1]port trunk allow-pass vlan all
[LSW2]interface Ethernet 0/0/14
[LSW2-Ethernet0/0/14]port link-type trunk
[LSW2-Ethernet0/0/14]port trunk allow-pass vlan all
GVRP ni global miqyosda va barcha tegishli
interfeyslarda sozlash
quyidagicha amalga oshiriladi:
LSW1 kommutatorni sozlash:
[LSW1]gvrp
[LSW1]interface ethernet 0/0/13
[LSW1-Ethernet0/0/13]gvrp
LSW3 kommutatorni sozlash:
[LSW3]gvrp
[LSW3]interface ethernet 0/0/13
[LSW3-Ethernet0/0/13]gvrp
Forbidden - 4-Laboratoriya ishi gvrp protokolini sozlash va uning ishlash prinsipini o‘rganish Ishning maqsadi

va Vlan7 yarating va GVRP ni sozlang.
7.
5 ta kommutator, 4 ta ShK dan tashkil topgan tarmoqni quring.
Vlan10 va Vlan20 yarating va GVRP ni sozlang.
8.
LSW1 va LSW2 kommutator, 7 ta ShK dan tashkil
topgan tarmoqni
quring. Vlan5 va Vlan10 yarating va GVRP ni sozlang.
9.
4 ta kommutator, 5 ta ShK dan tashkil topgan tarmoqni quring.
Vlan20 va Vlan30 yarating va GVRP ni sozlang.
10.
4 ta kommutator, 7 ta ShK dan tashkil topgan tarmoqni quring.
Vlan13 va Vlan15 yarating va GVRP ni sozlang.
11.
3 ta kommutator, 5 ta ShK dan tashkil topgan tarmoqni quring.
LSW2 va LSW3 da Vlan10 va Vlan20 yarating va GVRP ni sozlang.
12.
5 ta kommutator, 8 ta ShK dan tashkil topgan tarmoqni quring.
Vlan10 va Vlan25 yarating va GVRP ni sozlang.
13.
4 ta kommutator, 4 ta ShK dan tashkil topgan tarmoqni quring.
LSW3 va LSW4 da Vlan15 va Vlan20 yarating va GVRP ni sozlang.
14.
4 ta kommutator, 8 ta ShK dan tashkil topgan tarmoqni quring.
LSW3 va LSW4 da Vlan30 va Vlan50 yarating va GVRP ni sozlang.
15.
3 ta kommutator, 6 ta ShK dan tashkil topgan tarmoqni quring.
LSW1 va LSW3 da Vlan14 va Vlan24 yarating va GVRP ni sozlang.
16.
5 ta kommutator, 5 ta ShK dan tashkil topgan tarmoqni quring.
LSW2 va LSW3 da Vlan7 va Vlan12 yarating va GVRP ni sozlang.
17.
4 ta kommutator, 5 ta ShK dan tashkil topgan tarmoqni quring.
Vlan10 va Vlan20 yarating va GVRP ni sozlang.
18.
5 ta kommutator, 9 ta ShK dan tashkil topgan tarmoqni quring.
LSW2 va LSW3 da Vlan20 va Vlan25 yarating va GVRP ni sozlang.
19.
4 ta kommutator, 6 ta ShK dan tashkil topgan tarmoqni quring.
Vlan5 va Vlan10 yarating va GVRP ni sozlang.
20.
4 ta kommutator, 6 ta ShK dan tashkil topgan tarmoqni quring.
Vlan10 va Vlan20 yarating va GVRP ni sozlang.
21.
4 ta kommutator, 6 ta ShK dan tashkil topgan tarmoqni quring.
Vlan17 va Vlan20 yarating va GVRP ni sozlang.
22.
4 ta kommutator, 4 ta ShK dan tashkil topgan tarmoqni quring.
Vlan15 va Vlan25 yarating va GVRP ni sozlang.
23.
4 ta kommutator, 5 ta ShK dan tashkil topgan tarmoqni quring.
Vlan18 va Vlan28 yarating va GVRP ni sozlang.
24.
4 ta kommutator, 3 ta ShK dan tashkil topgan tarmoqni quring.
Vlan18 va Vlan20 yarating va GVRP ni sozlang.
25. 4 ta kommutator, 6 ta ShK dan tashkil topgan tarmoqni quring.
Ushbu laboratoriya ishida quyidagi vazifalar bajariladi:
- 4.1- rasmda ko„rsatilganidek qurilmalarni
interfeyslarini sozlang;
- GVRP ni sozlang;
- GVRP ro„yxatga olish rejimini o„rnating.
А.Х.Сидиков, Д.Бозоров

323 А.Х.Сидиков, Д.Бозоров. Пахта хомашёси таркибидан оғир аралашмаларни
ажратиб олиш самарадорлигини ошириш
327 А.А.Саримсаков, Ы.Сейитбекова. Оптоэлектронное устройство для
контроля микроконтрентрации газообразных веществ
329 K.M.Karimkulov, J.U.Sevinov, G.R.Xamroyev. Avtomatlashtirilgan maxsus
avtotransport vositalarining tasniflash tizimining iqtisodiy samaradorligi
333 A.A.Daliyev, D.R.Orziqulov . “Arduino asosidagi ixchamlashtirilgan avtomatik
elektron qo’ng’oroq qurilmasi” takomilashtirish
336 Т.Т.Мойдунов. Автоматизация РРС-59 с применением современных
технологических платформ
338 И.Х.Сиддиков, Г.Р.Алимова. Адаптивный
алгоритм
управления
технологическим процессом прядения волокна
343 M.M.Mirzakarimov. Bir kamerali ikki silindirli jin mashinasida tolani unumdorligini
modellashtirish
346 A.Abdurasulov , А.А.Obidov. Chiqindilar tarkibidan paxta ajratuvchi regenerator
qurilmasini takomillashtirish bo’yicha tadqiqot
348 F.G’.Uzoqov. Djin mashinasining kolosnigini frezerlash orqali tayyorlash
350 F.G.Uzoqov, A.A.Komilov. Kolosnikli panjarasi arrali silindrlarni tuzilishini tahlili
354
Namangan Institute of Engineering and Technology nammti.uz 10.25.2023
Pg.622
O.A.Yunusov, R.Sh.Abdusalyamova. Technology of metals processing using
low-power induction heating method
Yer osti gaz quvurlarining chuqurligi, nishabligi

|
Yer osti gaz quvurlarining chuqurligi, nishabligi
|
bet | 4/5 | Sana | 22.01.2024 | Hajmi | 126,73 Kb. | | #143070 |
Bog'liq 5-Мa’ruza5.4. Yer osti gaz quvurlarining chuqurligi, nishabligi
Gaz quvurlarining chuqurligi shunday joylashishi kerakki, u chuqurlikda tuproq qatlami hisobiga mexanik ta’sirdan saqlangan bo‘lsin. Shaharlar uchun quvurning minimal chuqurligi quvur tepasidan yer yuzasigacha kamida 0,8 m bo‘lishi kerak. Shahardan tashqarida, bu chuqurlik qatnov yo‘q joylarda kamida 0,6 m bo‘lishi zarur.
Bundan tashqari, quvurning yotqizish chuqurligi gazning namligiga bog‘liq. Agarda gaz nam bo‘lsa, gaz quvurini yerning muzlash qatlamidan chuqurroq joylashtirish kerak, chunki gazdagi namlik kondensatsiyalanadi va bu suyuqlik muzlab, gaz quvurini berkitib qo‘yishi mumkin.
Quritilgan gaz quvurlarini esa yerning muzlash qatlamida ham joylashtirish mumkin. Gazning namligiga qaramasdan, gaz quvurlari nishab o‘tkazilishi kerak, chunki gazdagi suv bug‘lari kondensatsiya bo‘lganda, ular quvurning nishabligi bo‘yicha oqib borib, quvurning eng past joyida to‘planadi. Bu yerda kondensat yig‘gichlar o‘rnatiladi (5.1 – rasm) va u orqali yig‘ilgan kondensat chiqarib tashlanadi.
5.1-rasm. Kondensat yig‘gich
1-korpus; 2-kondensatni chiqarish quvuri; 3-yerga ulangan elektrod; 4-kover ostidagi beton yostiq; 5-kover; 6-quvur yer ostidagi potensiallar farqini o‘lchash uchun kontakt plastinasi.
Minimal nishablik (i=0,002) katta diametrdagi quvurlar uchun yetarli hisoblanadi. Lekin quvurlar diametri kichikroq bo‘lsa (d<150 mm), nishablikni kattaroq olish kerak. Chunki kichik quvurlarning kesimi kichik bo‘lganligi uchun quvurlar cho‘kkan paytda unda suv to‘planib, gazning yo‘lini berkitib qo‘yishi mumkin.
Yer osti gaz quvurlari qurishda xandaq tagining sifati katta ahamiyatga egadir. Sifatsiz bajarilgan yer ishlari ekspluatatsiya davrida gaz ta’minoti va quvurlarning mustahkamligiga ta’sir ko‘rsatishi mumkin. Loyihaga nisbatan chuqur joylar qum bilan to‘ldirilib, zichlanib, tekislanishi zarur. Agarda xandaq toshloq joylardan qazilsa. Unda xandaq tagining notekisliklari 10 yoki 15 sm qalinlikda qum sepilib tekislanishi kerak. Tekislanmasa, toshlarning o‘tkir qirralari gaz quvurining izolatsiyasini ishdan chiqadi va gaz quvuri korroziyasini tezlashtiradi.
150>
|
| |
Hisobot quyidagilardan tashkil topgan bo‘lishi kerak

Hisobot quyidagilardan tashkil topgan bo‘lishi kerak:
1. Laboratoriya ishi nomi, ishdan maqsad, qisqacha nazariy ma‟lumot;
2. Berilgan variant bo„yicha tarmoqni qurish va kerakli
sozlamalarni amalga
oshirish;
3. Natijalarni
hisobotga kiritish;
4. Xulosalar.
Nazorat savollari
1.
GVRP protokoli qanday maqsadda qo„llaniladi?
2.
GVRP da ro„yhatga olish rejimlari nechtani tashkil etadi?
3.
Normal rejimi qanday funksiyani bajaradi?
4.
Fixed rejimi qanday funksiyani bajaradi?
5.
Forbidden rejimi qanday funksiyani bajaradi?
6.
GARP nima va uning funksiyasi nima?
7.
GARP xabarlari turlarini keltiring.
8.
Fixed va Forbidden rejimlarining bir-biridan farqi?
Yer osti gaz quvurlarining har xil tabiiy va sun’iy to‘siqlar bilan kesishishi

|
Yer osti gaz quvurlarining har xil tabiiy va sun’iy to‘siqlar bilan kesishishi
|
bet | 5/5 | Sana | 22.01.2024 | Hajmi | 126,73 Kb. | | #143070 |
Bog'liq 5-Мa’ruza5.5. Yer osti gaz quvurlarining har xil tabiiy va sun’iy to‘siqlar bilan kesishishi
Gaz quvurlari o‘tkazish paytida har xil to‘siqlar bilan kesishishi mumkin. Bunday to‘siqlarga daryolar, jarliklar, temir yo‘l, avtomobil yo‘llari va har xil yer osti inshootlari kiradi. Magistral gaz quvurlari bilan temir yo‘llari kesishgan joylarda, gaz quvurlari futlyar (g‘ilof) ichida o‘tkaziladi (3.2-rasm).
G‘ilof gaz quvurlari temir yo‘l izlari hamda avtomobil yo‘li tagidan o‘tganda gaz quvuridan gaz hamda yong‘in chiqishining oldini olish uchun qo‘laniladi. Bundan tashqari, gaz quvurining yotqizish davrida transport harakatini to‘xtatmasdan qurilish ishalrini teshib o‘tish usulida olib borishga imkon beradi.
5.2-rasm. Gaz quvurlarining temir yo‘l bilan kesishish sxemasi:
1-sham (vityajnaya svecha); 2-bitum;3-futlyar (g‘ilof); 4-gaz quvuri.
G‘ilof metall quvurdan tayyorlanadi. Bunda gaz quvuri d>200 mm bo‘lsa, g‘ilof diametri mm bo‘lishi kerak. Gaz quvuri d<200 mm bo‘lsa, mm bo‘ladi.
G‘ilof ichidagi gaz quvurlari iloji boricha butun quvurdan tayyorlanishi kerak. G‘ilofning uchlari salnik bilan zichlanadi hamda bir uchiga nazorat quvuri yoki chiqarib tashlash quvuri “sham” (svecha) ulanadi. Agarda g‘ilof ichidagi quvurdan gaz chiqa boshlasa, u nazorat quvuri yoki “sham” orqali xavfsizroq joydan chiqarib yuboriladi.
Agarda yer osti gaz quvurlari kanalizatsiya kollektorlarini yoki shunga o‘xshash kanal yoki kollektorlarni kesib o‘tsa, gaz quvuri g‘ilof ichida o‘tkazilishi kerak va g‘ilof kollektorning tashqi devoridan ikki tomonga kamida 2 metrdan chiqib turishi kerak. Bunda ham g‘ilofning diametri sxemaga o‘xshab qabul qilinadi.
Yer osti gaz quvuri bilan suv tarmog‘i, kanalizatsiya kesishgan vaqtda ular orasidagi masofa 15 sm dan kam bo‘lmasligi kerak. Gaz quvuri bilan issiqlik tarmog‘i kanali orasidagi masofa kamida 20 sm bo‘lishi, kabel orasidagi masofa kamida 0,5 m bo‘lishi kerak. Agarda kabel asbotsosement quvur ichidan o‘tgan bo‘lsa, unda 0,25 m bo‘lishi mumkin.
Nazorat savollari:
1.Gazlashtirish tizimlarining tuzilishi va ularni o‘tkazish usullari.
2.Gaz tarmog‘i qanday o’tkaziladi?
3.Kondensat yig‘gich qanday tuzilishga ega?
4.Yer osti gaz quvurlari qanday har xil tabiiy va sun’iy to‘siqlar bilan kesishadi? 200>
|
| |
-rasm G8 davlatlarining energiya xavfsizligi (mavjud energiya resurslari hajmining ularning talab

|
-rasm G8 davlatlarining energiya xavfsizligi (mavjud energiya resurslari hajmining ularning talab Pdf ko'rish
|
bet | 24/693 | Sana | 13.05.2024 | Hajmi | 15,56 Mb. | | #228860 |
Bog'liq Тўплам1-rasm G8 davlatlarining energiya xavfsizligi (mavjud energiya resurslari hajmining ularning talab
qilinadigan hajmiga nisbati), [5] ga asoslanadi
Energiya tanqis bo'lgan davlatlar yalpi ichki mahsulotining muhim qismini energiya sotib
olishga sarflashga majbur. Resurslari, bu iqtisodiyotga salbiy ta'sir ko'rsatadi va ko! ijtimoiy soha.
Bundan tashqari, ular muammoga aylanadi. Siyosiy va ijtimoiy kataklizmlarga qarshi himoyasiz
mamlakatlarda harakat energiya yetkazib beruvchilar bizda xandaq bozori.
Bu paradoksal ko'rinadi, lekin muammo energiyada. Energiyaga boy mamlakatlar ham
resurslarga ega. Biz ular uchun "neft va gaz ignasiga tushish", ya'ni tabiiy renta evaziga yashash xavfi
haqida gapiramiz. Mamlakatning iqtisodiy rivojlanish traektoriyasi qanday, boshida amalga
oshirishning terapevtik qulayligi, natijada konyunktga xavfli qaramlik yuzaga keladi. Global energiya
bozorida biz innovatsion rivojlanish uchun rag'batlantiramiz. So'nggi o'n yilliklarda Rossiya
haqiqatan ham shunday davlatlar qatoriga kirdi. Iqtisodiyotni rivojlantirishning xomashyo
modelidan voz kechish va innovatsiyalarga o‘tish bejiz emas. Milliy taraqqiyot yo'li mamlakat
rahbariyati tomonidan e'lon qilinadi va jamiyat tomonidan eng muhim vazifa sifatida qabul qilinadi.
Ikkinchi muammo - ekologik energiya ishlab chiqarish ko'lami o'sib borishi bilan o'sib
bormoqda. Bugungi kunda energetika sanoati tomonidan qo'llaniladigan shtab-kvartira va
texnologiyalar shundayki, 50% dan ko'prog'i inson tomonidan yaratilgan atmosferaga issiqxona
gazlari chiqindilari energiya ob'ektlaridan keladi. Energetika litosfera va gidrosferani ham intensiv
ravishda ifloslantiradi. Energiya tizimlarida energiya oqimlari solishtirish mumkin bo'ladimi yoki
hatto katta hajmdagi tabiiy tizimlardagi energiya oqimlaridan va taxminan.
Energetika muammolarini hal qilishda insoniyat sanoat miqyosida ma'lum, ammo
o'zlashtirilmagan ta'sirlarga asoslangan muqobil energiyani rivojlantirishga katta umid bog'laydi.
Birinchi navbatda, tezkor neytronlardan foydalangan holda yadroviy reaktorlardan foydalanish
|
| |
Past chastotali to‘g‘rilovchi diodlar (PCh diodlar)

|
Past chastotali to‘g‘rilovchi diodlar (PCh diodlar)
|
bet | 12/16 | Sana | 19.01.2024 | Hajmi | 5,39 Mb. | | #140805 |
Bog'liq 11 bletPast chastotali to‘g‘rilovchi diodlar (PCh diodlar) sanoat chastotasidagi (50 Gs) o‘zgaruvchan tokni o‘zgarmasga o‘girishda qo‘llaniladi. PCh diodlariga qo‘yiladigan asosiy talab – bu katta qiymatga ega bo‘lgan to‘g‘rilangan toklar olish. To‘g‘rilovchi diodlar odatda 0,3 A gacha, 0,3 A dan 10 A gacha va 10 A dan yuqori bo‘lgan to‘g‘rilangan toklarga mo‘ljallangan kichik, o‘rta va katta quvvatli diodlarga bo‘linadi. PCh diodlari katta r-n o‘tish bilan xarakterlanadilar.
Yuqori chastotali to‘g‘rilovchi diodlar (YuCh diodlar) o‘n va yuz megagers chastotagacha bo‘lgan signallarni nochiziqli elektr o‘zgartirishga mo‘ljallangan. YuCh diodlari yuqori chastota signallari detektorlari, aralashtirgichlar, chastota o‘zgartirgich sxemalar va boshqalarda qo‘llaniladi. Yuqori chastota diodlari kichik inersiyaga ega, chunki kichik yuzaga ega bo‘lgan nuqtaviy r-n o‘tishga ega va shu sababli ularning to‘siq sig‘imi pikofaradning bir qismini tashkil etadi.
Shottki to‘sig‘ili (barerili) diodlar kuchlanish manbai qayta ulagichlarida keng tarqalgan, chunki ular qayta ulanish ishchi chastotasini 100 kGs va undan yuqoriga orttirishga, radioelektron apparatura og‘irligi, o‘lchamlarini kichraytirishga va kuchlanish manbai FIK oshirishga imkon yaratadilar. Shottki to‘sig‘i metallni yarim o‘tkazgich bilan kontakti natijasida hosil qilinadi. Yarim o‘tkazgich material sifatida ko‘p hollarda n – turdagi kremniy, metall sifatida esa Al, Au, Mo va boshqalar qo‘llaniladi. Bu vaqtda metall chiqish ishi kremniy chiqish ishidan katta bo‘lishi talab qilinadi. Bunday diodlarda diffuziya sig‘imi nolga teng, to‘siq sig‘imi esa 1 pF dan oshmaydi.
3. BTning turli ulanish sxemalarida statik VAXlarida aktiv va to‘yinish rejimlarini aniqlang
Dinamik rejimda p-n o„tishning xususiyatlarini ifodalash uchun ham qator moddelardan, xususan, dinamik VAX lardan foydalaniladi. Sig„imlar ta‟sirini e‟tiborga olgan holda ushbu model chegarasida p-n o„tish tokini quyidagi ifodadan topish mumkin: dt dU I I U CD ( ) , (2.17) bu yerda, I(U) – statik VAXdan aniqlanadigan tok; CD CB СDIF – ko„rinishga ega bo„lib; u p-n o„tish sig„imini ifodalaydi. (2.17)dan foydalanib, CD(U) sig„im qiymatlarini bilgan holda kuchlanishning turli o„zgarish tezliklari dU / dt uchun, ya‟ni turli chastotalar uchun I f (U,dU / dt) xarakteristikalar oilasini qurish mumkin.
|
| |
blet1. Rezistordan oqib o’tayotgan tok qiymatini aniqlash uchun

|
blet1. Rezistordan oqib o’tayotgan tok qiymatini aniqlash uchun
|
bet | 11/16 | Sana | 19.01.2024 | Hajmi | 5,39 Mb. | | #140805 |
Bog'liq 11 blet18.blet1. Rezistordan oqib o’tayotgan tok qiymatini aniqlash uchun,
ampermetr rezistorga qanday ulanadi, va ampermetr qurilmasiga ta’rif bering
Ampermetr (amper va …metr) — oʻzgarmas va oʻzgaruvchan tok kuchini oʻlchaydigan asbob; elektr zanjiriga ketma-ket ulanadi. Shkalasi asbobning oʻlchash chegarasiga muvofiq mikroamperlarda, milliamperlarda, kiloamperlarda darajalarga boʻlinadi. Oʻlchash chegarasini oshirish uchun shuntlab yoki transformator orqali ulanadi. Tok taʼsirida asbob mili buriladi; milning burilish burchagi tok kuchiga mutanosib boʻladi. Ishlash tarziga qarab, ampermetrlar magnitoelektrik, elektro-magnit, elektrodinamik, ferrodinamik, induksion, issiqlik, termoelektrik, toʻgʻrilagichli tizimdagi ampermetrlarga boʻlinadi.
Ampermetr- elektr tokini oʻlchaydigan asbob. Ampermetr — 100 mA dan 2000 A gacha boʻlgan keng diapazondagi oqim oʻlchovlarini amalga oshirish uchun ishlatiladigan maxsus oʻlchash moslamasi.
Ampermetr, toʻgʻridan-toʻgʻri yoki oʻzgaruvchan elektr oqimini amperda oʻlchash uchun asbob. Ampermetr oqim qiymatlarining keng diapazonini oʻlchashi mumkin, chunki yuqori qiymatlarda elektr oqimining faqat kichik bir qismi hisoblagich mexanizmi orqali yoʻnaltiriladi; metr bilan analog shunt uning katta qismini oladi. Ushbu asbobning ishlash printsipi shundaki, u juda past qarshilik va induktiv reaktivlikka ega boʻlishi kerak. U juda past empedansga ega, chunki u juda past kuchlanish pasayishiga ega boʻlishi kerak va u ketma-ket ulanishi kerak, chunki oqim bir xil boʻladi. seriyali sxema.
Bundan tashqari, pasaytirilgan empedans tufayli quvvat sarfi past boʻladi va agar oʻzaro bogʻlangan boʻlsa, u deyarli aloqa yoʻliga aylanadi va asbob tortadigan yuqori oqim natijasida barcha elektr oqimi ampermetr orqali oqib chiqadi. . Shuning uchun u ketma-ket ulanishi kerak.
2. To‘g‘rilovchi diodlarning qanday turlari bor va ular qanday vazifani bajaradi?
To‘g‘rilovchi diodlarning ishlatilish chastota diapazoni juda keng. Shu sababli ular ishchi chastota diapazoni bo‘yicha sinflanadilar.
|
| |
1- ma’ruza kirish. Ishlab chiqarish korxonalarida texnik kimyoviy nazoratni yo’lga qo’yish va uning vazifalari

|
1- ma’ruza kirish. Ishlab chiqarish korxonalarida texnik kimyoviy nazoratni yo’lga qo’yish va uning vazifalari
|
bet | 1/7 | Sana | 06.09.2024 | Hajmi | 37,08 Kb. | | #270453 |
Bog'liq 1- ma’ruza kirish. Ishlab chiqarish korxonalarida texnik kimyovi
1- MA’RUZA
Kirish. Ishlab chiqarish korxonalarida texnik kimyoviy nazoratni yo’lga qo’yish va uning vazifalari
Reja:
Fanning maqsadi va vazifalari.
Mikrobiologik va texnologik nazoratning ishlab chiqarishdagi ro`li.
Xom-ashyoni standartlashtirish sistemasi.
Ishlab chiqarilayotgan mahsulotiga bo`lgan talab
Respublikamizdagi ijtimoiy-iqtisodiy islohotlar natijalari, xududiy
muammolar va ilm-fan, texnika va texnologiya yutuqlari
Fanning maqsadi va vazifalari
Bizning Respublikamiz oziq ovqat sanoati korxonalari mutaxassislari oldiga oziq ovqat mahsulotlari ishlab chiqarishda, ishlab chiqarish unumini oshirish, ishlab chiqarishning uzluksiz va asosiy texnologik jarayonlarini mexanizatsiya va avtomatizatsiya qilishning yuqori samarasini oshirish, mahsulotning sifatini yaxshilash va chiqish unumini oshirish hamda ishlab chiqarishda xom ashyoni yo‘qolishini kamaytirish borasida muhim masalalar qo‘yilgan.
Tayyor mahsulot standarti talablariga rioya qilish, mahsulot unumini oshirish va texnologik jarayonning har bir bosqichida texnologik va fizik-kimyoviy nazoratni sistemali raviщda olib borish, shu bilan birga ayrim mashina va uskunalarni xolatini nazorat qilish bilan uzviy bog‘liqdir. Buni amalga oshirish uchun xom ashyo, yarim tayyor va tayyor mahsulotlardan namunalar olishni va taxlillarni to‘g‘ri olib borilishini hamda nazoratni to‘g‘ri yo‘lga qo‘yilishini tashkil etish lozim.
Ushbu nazoratlarni oziq ovqat sanoati korxonalarida olib borilishi maxsus ishlab chiqilgan va rasmiy ravishda tasdiqlangan standartlar, uslubiy qo‘llanmalar, me’yoriy xujjatlar, yo‘riqnomalar hamda texnologik reglamentlar asosida olib boriladi. Yillar o‘tishi bilan bu qo‘llanma va yo‘riqnomalar qayta ko‘rib chiqilib, ishlab chiqrishga joriy etiladi.
Ushbu fanni o‘rganishdan maqsad oziq ovqat mahsulotlari ishlab chiqarish korxonalarida xom ashyoni qabul qilishdan tortib saqlash, ishlab chiqarishga berish, qayta ishlab tayyor mahsulot xoliga keltirib, iste’molchilarga jo‘natishgacha bo‘lgan barcha texnologik jarayonlarni to‘g‘ri nazorat qilish va xom ashyo, yarim tayyor,tayyor hamda chiqindilarni sifat ko‘rsatkichlarini to‘g‘ri taxlil qilishni o‘rgatadi. Ishlab chiqarish samaradorligini oshirib, mahsulotlarni chiqish unumini oshiradi va ularni sifatini yaxshilaydi.
|
| |
Energiya resurslaridan savdo-texnik xususiyatlar to'g'risida

7.2. Energiya resurslaridan savdo-texnik xususiyatlar to'g'risida. Bugungi kunda korxonalar tez-tez elektr energiyasini / boshqa energiya
resurslarini texnik hisobini avtomatlashtirishga harakat qilmoqda va iloji
bo'lsa uni tijorat hisob-kitoblari bilan birlashtiradi. Enforsga ko'ra, " ENHAT
Enterprises" kompaniyasining
versiyasi
elektr,
issiqlik, suv, gaz,
kanalizatsiya va boshqa resurslar uchun barcha hisob raqamlarini yagona
ma'lumotlar bazasida to'plash imkoniga ega. Qo'llab-quvvatlaydigan o'lchash
asboblari keng doiradagi dastur tez va iqtisodiy jihatdan foydali bo'ladi.
Dasturiy mahsulotlar o'lchov asboblari / USPD / controllers / tarmoqli /
turli modeldagi modemlardan ma'lumotlarni to'playdi. Foydalaniladigan
aloqa kanallari CSD / GPRS, chekilgan tarmoq, radio kanali, plc va shunga
o'xshash bo'lishi mumkin. "Enforce" dasturiy ta'minoti ma'lum buxgalteriya
qurilmalari va ma'lumotlar uzatish vositalariga bog'liq emas, biz bozorda
to'liq texnik echimlarni qo'llab-quvvatlaymiz.
Ma'lumotlar bazasi sifatida EnFors dasturiy ta'minoti Oracle
ma'lumotlar bazasini ishlatadi, bu tizimning tezligini oshirish va ko'plab
parametrlarni so'rash imkonini beradi. Ko'p ishlov berishli so'rovnoma
o'tkazish modeli qo'llab-quvvatlanadi, ya'ni ma'lumotlar yig'ish tizimi bir
vaqtning o'zida 1000 hisoblash moslamasini so'roq qilishlari mumkin, bu esa
saylov vaqtini bir necha bor qisqartiradi.
Dasturning moslashuvchan sozlamalari tizimga login va parol bilan
tasdiqlangan foydalanuvchilar sonini kiritish imkonini beradi. Har bir
foydalanuvchi uchun tizimning funktsional imkoniyatlari va buxgalteriya
ob'ektlariga kirish darajasi uchun alohida sozlamalar amalga oshiriladi.
Shaxsiy kabinetingiz Internet-interfeys orqali amalga oshiriladi va internetga
141
ulangan yoki uyushtirilgan lokal tarmoq doirasida har qanday kompyuter /
tizza / planshetdan foydalanishga ruxsat beradi.
Loyiha doirasida yangi o'lchov turlarini kiritish, muayyan korxonalar
uchun hisobotlarni ishlab chiqish, zarur funktsiyalarni qo'shish.
Oson multiplekslash jarayonidan o‘tkazish (Easy multiplexing)

|
Oson multiplekslash jarayonidan o‘tkazish (Easy multiplexing)
|
bet | 6/35 | Sana | 22.05.2024 | Hajmi | 9,66 Mb. | | #249839 |
Bog'liq Raqamli YNOson multiplekslash jarayonidan o‘tkazish (Easy multiplexing)
Multiplekslash deganda bir xil aloqa kanalida signallarning bir nechta uzatilishi tushuniladi. Raqamli modulyatsiyada diskretlash va kvantlash bir nechta signallarni samarali uzatish imkonini beradi. TDM (Time Division Multiplexing) IKM da qo‘llaniladigan keng tarqalgan multiplekslash turidir.
Yuqori samaradorlik (High efficiency)
Raqamli uzatish rejimi tufayli yuqori samaradorlikka ega.
Repeaterlardan foydalanish (Use of repeaters)
Ma’lumotlarni saqlash (Data storage)
Raqamli ma’lumotlar qulay va oson usulda saqlanishi mumkin.
7-savol.Impuls kodli modulyatsiyaning kamchiliklari
Murakkab jarayon (Complex process)
IKM analog modulyatsiya usuli bilan solishtirganda murakkab jarayon hisoblanadi. Buning sababi, IKM dagi signal aloqa tizimidagi turli jarayon/bosqichlardan o‘tadi.
Keng polosa kengligi (Large bandwidth)
Bu analog aloqa tizimlariga qaraganda keng polosa kengligini talab qiladi. Bu IKM tizimida disktretlash va kvantlash mavjudligi bilan bog‘liq.
Kvantlash shovqini (Quantization noise)
Analog signal raqamli signalga aylantirilganda, kirish va kvantlangan qiymat o‘rtasidagi vaqt oralig‘i kvantlash shovqinini keltirib chiqaradi. Uni IKM da shovqinni kamaytirish tizimi yordamida olib tashlash mumkin.
8-savol.Impuls kodli modulyatsiyaning qo‘llanish sohalari
Kosmik aloqa (Space communication)
Kosmik aloqada signallar koinotdan yoki atmosferadan Yerga yuboriladi, bu aloqa uchun asos sifatida ishlatiladi. Bu uzoq masofalarga uzatish bilan kichik uzatiladigan quvvatni talab qiladi. Shunday qilib, IKM ning yuqori shovqinbardoshliligi va uzoq masofalarga uzatish qobiliyati tufayli kosmik aloqada afzallik beriladi.
|
| |