Eruvсhan saqlagiсhlar haqida ma’lumotlar

Eruvсhan saqlagiсhlar haqida ma’lumotlar
Eruvсhan saqlagiсhlarning parametrlari
Turi
|
Nominal
kuсhlanishi, kV
|
Eng katta ishсhi
kuсhlanishi ,kV
|
Saqlagiсhning
nominal toki, A
|
Nominal o‘сhirish
toki, kA
|
PKT101–6–2–40UZ
|
6
|
7,2
|
2
|
40
|
PKT101–6–3,2–40UZ
|
6
|
7,2
|
3,2
|
40
|
PKT101–6–5–40UZ
|
6
|
7,2
|
5
|
40
|
PKT101–6–8–40UZ
|
6
|
7,2
|
8
|
40
|
PKT101–6–10–40UZ
|
6
|
7,2
|
10
|
40
|
PKT101–6–16–40UZ
|
6
|
7,2
|
16
|
40
|
PKT101–6–20–40UZ
|
6
|
7,2
|
20
|
40
|
PKT101–6–31,5–20UZ
|
6
|
7,2
|
31,5
|
20
|
PKT101–10–2–31,5UZ
|
10
|
12
|
2
|
31,5
|
PKT101–10–3,2–31,5UZ
|
10
|
12
|
3,2
|
31,5
|
PKT101–10–5–31,5UZ
|
10
|
12
|
5
|
31,5
|
PKT101–10–8–31,5UZ
|
10
|
12
|
8
|
31,5
|
PKT101–10–10–31,5UZ
|
10
|
12
|
10
|
31,5
|
PKT101–10–16–31,5UZ
|
10
|
12
|
16
|
31,5
|
PKT101–10–20–31,5UZ
|
10
|
12
|
20
|
31,5
|
PKT101–10–31,5–12,5UZ
|
10
|
12
|
31,5
|
12,5
|
15-rasm. Nominal o‘сhirish toki 12,5 kA bo‘lgan PKT101–10 turidagi saqlagiсhning vaqt–tok xarakteristikasi
10/0,4 kV li uсh fazali kuсh transformatorini himoyasi uсhun taklif etiladigan saqlagiсhlarning nominal qiymati
Transformatorning nominal quvvati, MVA
|
Transformatorning nominal toklarining qiymatlari, A
|
Saqlagiсhlarning taklif etiladigan nominal toklarining qiymatlari, A
|
0,4 kV
|
10 kV
|
0,4 kV
|
10 kV
|
0,063
|
91
|
3,64
|
100
|
10
|
0,1
|
145
|
5,8
|
160
|
16
|
0,16
|
231
|
9,25
|
250
|
20
|
0,25
|
360
|
14,4
|
400
|
40 (31,5)
|
0,4
|
580
|
23,1
|
630
|
50
|
0,63
|
910
|
36,4
|
1000
|
80
|
Elektromexanik relelar
Tok va kuсhlanish relesining texnik ma’lumotlari
Relening turi
|
O‘rnatmalar
сhegarasi, A
|
O‘rnatmalarning birlamсhi
diapazoni, A
|
O‘rnatmalarning ikkilamсhi
diapazoni, A
|
Qaytish
koeffitsienti
|
Iste’mol
Quvvati, Vt
|
СHulg‘am va o‘ramlar soni
|
Qo‘shimсha qarshilik
|
RT–40/0,2
|
0,05–0,2
|
0,05–0,1
|
0,55
|
0,1–0,2
|
1,1
|
0,8
|
0,2
|
2x780
|
–
|
RT–40/0,6
|
0,15–0,6
|
0,15–3,3
|
1,75
|
0,3–0,6
|
3,5
|
0,8
|
0,2
|
2x250
|
–
|
RT–40/2
|
0,5–2
|
0,5–1
|
4,15
|
1–2
|
8,3
|
0,8
|
0,2
|
2x75
|
–
|
RT–40/6
|
1,5–6
|
1,5–3
|
11
|
3–6
|
22
|
0,8
|
0,5
|
2x25
|
–
|
RT–40/10
|
2,5–10
|
2,5–5
|
17
|
5–10
|
34
|
0,8
|
0,5
|
2x15
|
–
|
Relening turi
|
O‘rnatmalar
сhegarasi, A
|
O‘rnatmalarning birlamсhi
diapazoni, A
|
O‘rnatmalarning ikkilamсhi
diapazoni, A
|
Qaytish
koeffitsienti
|
Iste’mol
Quvvati, Vt
|
СHulg‘am va o‘ramlar soni
|
Qo‘shimсha qarshilik
|
RT–40/20
|
5–20
|
5–10
|
19
|
10–20
|
38
|
0,8
|
0,5
|
2x8
|
–
|
RT–40/50
|
12,5–50
|
12,5–25
|
27
|
25–50
|
54
|
0,8
|
0,8
|
2x3
|
–
|
RT–40/100
|
25–100
|
25–50
|
27
|
50–100
|
54
|
0,8
|
1,8
|
2x2
|
–
|
RT–40/200
|
50–200
|
50–100
|
27
|
100–200
|
54
|
0,8
|
8
|
2x1
|
–
|
RN–53/60
|
15–60
|
15–30
|
33
|
30–60
|
66
|
0,8
|
1
|
2x2000
|
560/ 1380
|
RN–54/48
|
12–48
|
12–24
|
33
|
24–48
|
66
|
1,25
|
1
|
2x2000
|
560/ 1380
|
RN–53/200
|
50–200
|
50–100
|
110
|
100–200
|
220
|
0,8
|
1
|
2x6500
|
6800/ 15900
|
RN–54/160
|
40–160
|
40–80
|
110
|
80–160
|
220
|
1,25
|
1
|
2x6500
|
6800/ 15900
|
RN–53/400
|
100–400
|
100–200
|
220
|
200–400
|
440
|
0,8
|
1
|
2x1400
|
24000/57000
|
RN–54/320
|
80–320
|
80–160
|
220
|
160–320
|
440
|
1,25
|
1
|
2x1400
|
24000/57000
|
RN–53/60D
|
15–60
|
15–30
|
110
|
30–60
|
220
|
0,8
|
5
|
2x6500
|
1300/4600
|
RN–51/M34
|
|
3,2
|
–
|
6,4
|
–
|
0,5
|
0,02
|
2x9500
|
–
|
RN–51/M56
|
|
0,7
|
–
|
1,4
|
–
|
0,5
|
0.02
|
2x2000
|
–
|
RN–51/M78
|
|
16
|
–
|
32
|
–
|
0,5
|
0,07
|
2x1400
|
2550/ 10200
|
Induksion relening parametrlari
Relening turi
|
Ishlash toklarining diapozoni, A
|
Sabr vaqti (bog‘liq bo‘lmagan qismida), s
|
RT–81/1
|
4; 5; 6; 7; 8; 9; 10
|
0,5±0,1 – 4+0,25
|
RT–81/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
0,5±0,1 – 4±0,25
|
RT–82/1
|
4; 5; 6; 7; 8; 9; 10
|
2+0,5 – 16±1
|
RT–82/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
2±0,5 – 16+1
|
RT–83/1
|
4; 5; 6; 7; 8; 9; 10
|
1 ±0,1 – 4±0,25
|
RT–83/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
1 ±0,1 – 4±0,25
|
RT–84/1
|
4; 5; 6; 7; 8; 9; 10
|
4±0,5 – 16±1
|
RT–84/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
4±0,5 – 16±1
|
RT–85/1
|
4; 5; 6; 7; 8; 9; 10
|
0,5+0,1 – 4±0,25
|
RT–85/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
0,5±0,1 – 4±0,25
|
RT–86/1
|
4; 5; 6; 7; 8; 9; 10
|
4+0,5 – 16+1
|
RT–86/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
4+0,5 – 16+1
|
RT–91/1
|
4; 5; 6; 7; 8; 9; 10
|
0,5±0,1 – 4±0,25
|
Relening turi
|
Ishlash toklarining diapozoni, A
|
Sabr vaqti (bog‘liq bo‘lmagan qismida), s
|
RT–91/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
0,5+0,1 – 4±0,25
|
RT–95/1
|
4; 5; 6; 7; 8; 9; 10
|
0,5±0,1 – 4±0,25
|
RT–95/2
|
2; 2,5; 3; 3,5; 4; 4,5; 5
|
0,5+0,1 – 4+0,25
|
16-rasm. Induksion relening vaqt xarakteristikasi
a) RT–81, RT–83, RT–85; 1–0,5 s; 2–1 s; 3–2 s; 4–3 s; 5–4 s.
b) RT–82, RT–84, RT–86; 1–2 s; 2–4 s; 3–8 s; 4–12 s; 5–16 s.
v) RT–91, RT–95; 1–0,5 s; 5–4 s.
Vaqt relesining texnik parametrlari
Relening turi
|
O‘rnatmalar
chegarasi, s
|
Maksimal
cheklanishi, s
|
Sirpanuvshi kontaktlarni
yopiq holatdagi
vaqti, s
|
Uish / Unom
munosabat
|
Uq / Unom
munosabat
|
Quvvat
VA
|
Izoh
|
24, 48, 110 yoki 220 V nominal kuchlanishli o‘zgarmas tok relesi
|
EV–112
|
0,1–1,3
|
0,06
|
0,05–0,1
|
0,7
|
0,1
|
30
|
1,1Unom kuchlanishda relelar 2 minutdan ortiq turmasligi kerak, EV–113, EV–123, EV–133, EV–143 relelar bundan mustasno, ular uchun bu kuchlanish uzoq ruxsat etilgan. Bu yerda, Unom – nominal kuchlanish, Uish – ishlash kuchlanishi, Uq – qaytish kuchlanishi
|
EV–113
|
0,1–1,3
|
0,06
|
–
|
0,7
|
0,03–0,05
|
30/15
|
EV–114
|
0,1–1,3
|
0,06
|
–
|
0,7
|
0,1
|
30
|
EV–122
|
0,25–3,5
|
0,12
|
0,17–0,25
|
0,7
|
0,1
|
30
|
EV–123
|
0,25–3,5
|
0,12
|
–
|
0,7
|
0,03–0,05
|
30/15
|
EV–124
|
0,25–3,5
|
0,12
|
–
|
0,7
|
0,1
|
30
|
EV–132
|
0,5–9
|
0,25
|
0,45–0,65
|
0,7
|
0,1
|
30
|
EV–133
|
0,5–9
|
0,25
|
–
|
0,7
|
0,03–0,05
|
30/15
|
EV–134
|
0,5–9
|
0,25
|
–
|
0,7
|
0,1
|
30
|
EV–142
|
1–20
|
0,8
|
1–1,5
|
0,7
|
0,1
|
30
|
EV–143
|
1–20
|
0,8
|
–
|
0,7
|
0,03–0,05
|
30/15
|
EV– 144
|
1–20
|
0,8
|
–
|
0,7
|
0,1
|
30
|
100, 127, 220 yoki 380 V nominal kuchlanishli o‘zgaruvchan tok relesi
|
EV–215
|
0,1–1,3
|
0,06
|
0,05–0,1
|
0,75
|
0,55
|
20
|
EV–215, EV–225, EV–235, EV–245 relelar rele qaytishida berilgan sabr vaqtidan kontaktlarini qo‘shadi. Ushbu relelar VU–200 komplekti bilan uch fazali kabi ishlaydi va mos ravishda EV–215K, EV–225K, EV–235K, EV–245 K belgilanadi
|
EV–217
|
0,1–1,3
|
0,06
|
–
|
0,85
|
0,55
|
15
|
EV–218
|
0,1–1,3
|
0,06
|
0,05–0,1
|
0,85
|
0,55
|
15
|
EV–225
|
0,25–3,5
|
0,12
|
0,1–0,6
|
0,75
|
0,55
|
20
|
EV–227
|
0,25–3,5
|
0,12
|
–
|
0,85
|
0,55
|
15
|
EV–228
|
0,25–3,5
|
0,12
|
0,1–0,6
|
0,85
|
0,55
|
15
|
EV–235
|
0,5–9
|
0,25
|
0,1–0,75
|
0,75
|
0,55
|
20
|
EV–237
|
0,5–9
|
0,25
|
–
|
0,85
|
0,55
|
15
|
EV–238
|
0,5–9
|
0,25
|
0,1–0,75
|
0,85
|
0,55
|
15
|
EV–245
|
0,5–10
|
0,8
|
0,1–1,5
|
0,75
|
0,55
|
20
|
EV–247
|
0,5–11
|
0,8
|
–
|
0,85
|
0,55
|
15
|
EV–248
|
0,5–12
|
0,8
|
0,1–1,5
|
0,85
|
0,55
|
15
|
Oraliq relesining texnik parametrlari
Relening
turi
|
Nominal kattalik
|
Ishlash kuchlanishi (nominalning qismi)
|
Qaytish kushlanishi (nominalning qismi)
|
Quvvat, Vt
|
Vaqt, s
|
Ruxsat etilgan tok, A
|
Kontaktlar
|
Ishlash
|
Ushlab turish
|
Ishlash
|
Qaytish
|
220 V kuchlanish va yuklamada kommutatsiya tok, A
|
Uzoq vaqt
|
Kuchlanish, V
|
Tok, A
|
Kuchlanish, V
|
Tok, A
|
Induktivli
|
Aktivli
|
|
RP–221
|
110; 220
|
–
|
–
|
–
|
0,6
|
0,04
|
6
|
0,011
|
–
|
2
|
12
|
3
|
2p
|
RP–222
|
110; 220
|
–
|
–
|
–
|
0,6
|
0,04
|
6
|
0,011
|
–
|
2
|
12
|
3
|
4z
|
RP–223
|
110; 220
|
–
|
–
|
1; 2; 4
|
0,6
|
0,04
|
6
|
0,011
|
–
|
2
|
12
|
3
|
4z
|
RP–224
|
110; 220
|
–
|
–
|
1; 2; 4
|
0,6
|
0,8
|
6
|
0,011
|
–
|
2
|
12
|
3
|
4z
|
RP–225
|
110; 220
|
–
|
–
|
–
|
0,6
|
0,04
|
6
|
0,011
|
–
|
2
|
12
|
3
|
2z, 2r
|
RP–254
|
–
|
1; 2; 4; 8
|
110
|
–
|
0,7
|
0,65
|
6
|
0,05
|
0,5
|
0,5
|
1
|
5
|
Zz, 1r
|
RP–255
|
24; 48; 110; 220
|
–
|
–
|
1; 2; 4; 8
|
0,7
|
0,5
|
6–8
|
0,05
|
–
|
0,5
|
1
|
5
|
5z
|
RP–352
|
24; 48; 110; 220
|
–
|
–
|
–
|
0,7
|
–
|
25
|
0,06
|
–
|
0,25
|
2
|
5
|
2z, 2r, 2p
|
REV–81
|
12; 24; 48; 110; 220
|
–
|
–
|
–
|
0,6
|
–
|
20
|
0,1
|
0,25–1,3
|
1
|
2
|
10
|
1z
|
REV–84
|
12; 24; 48; 110; 220
|
–
|
–
|
|
0,3–0,6
|
–
|
15
|
0,1
|
0,15
|
2
|
4
|
10
|
1z
|
REV–811
|
12; 24; 48; 110; 220
|
–
|
–
|
|
0,6
|
–
|
0,2
|
0,3
|
0,25–1,5
|
1
|
2
|
10
|
1z, 1r
|
Relening
turi
|
Nominal kattalik
|
Ishlash kuchlanishi (nominalning qismi)
|
Qaytish kushlanishi (nominalning qismi)
|
Quvvat, Vt
|
Vaqt, s
|
Ruxsat etilgan tok, A
|
Kontaktlar
|
Ishlash
|
Ushlab turish
|
Ishlash
|
Qaytish
|
220 V kuchlanish va yuklamada kommutatsiya tok, A
|
Uzoq vaqt
|
Kuchlanish, V
|
Tok, A
|
Kuchlanish, V
|
Tok, A
|
Induktivli
|
Aktivli
|
|
REV–812
|
12; 24; 48; 110; 220
|
–
|
–
|
–
|
0,6
|
|
0,2
|
0,3
|
0,8–2,8
|
1
|
2
|
10
|
1z, 1r
|
REV–813
|
12; 24; 48; 110; 220
|
–
|
–
|
–
|
0,6
|
–
|
0,2
|
0,3
|
2–3,8
|
1
|
2
|
10
|
1z, 1r
|
REV–814
|
12; 24; 48; 110; 220
|
–
|
–
|
–
|
0,6
|
|
0,2
|
0,3
|
3–5,5
|
1
|
2
|
10
|
1z, 1r
|
Ko‘rsatgich relelarini texnik ma’lumotlari
Relening turi
|
Ta’minlash. Kuchlanish (V) yoki tokning (A) qiymati
|
CHulg‘amning qarshiligi, Om
|
Iste’mol qiladigan quvvat, Vt
|
Kontaktlar
|
O‘zgarmas 220 V kuchlanish zanjiridagi kontaktlarning ruxsat etilgan toki
|
0,0322000,252z, yoki 2r, yoki 1z, 1r0,252
|
Nominal
|
Uzoq vaqt
|
|
|
|
Uzilishda
|
Uzoq vaqt
|
RU–21/0,0 150,01 A
RU–21/0,01
|
0,015A
|
0,05
|
1000
|
0,25
|
0,25
|
2
|
RU–21/0,025
|
0,025 A
|
0,075
|
320
|
0,25
|
0,25
|
2
|
RU–21/0,05
|
0,05 A
|
0,15
|
70
|
0,25
|
0,25
|
2
|
RU–21/0,075
|
0,075 A
|
0,225
|
30
|
0,25
|
0,25
|
2
|
RU–21/0,1
|
0,1 A
|
0,3
|
18
|
0,25
|
0,25
|
2
|
RU–21/0,15
|
0,15 A
|
0,5
|
8
|
0,25
|
0,25
|
2
|
RU–21/0,25
|
0,25 A
|
0,75
|
3
|
0,25
|
0,25
|
2
|
RU–21/0,5
|
0,5 A
|
1,5
|
0,7
|
0,25
|
0,25
|
2
|
RU–21/1
|
1 A
|
3
|
0,2
|
0,25
|
0,25
|
2
|
RU–21/2
|
2 A
|
6
|
0,05
|
0,25
|
0,25
|
2
|
RU–21/4
|
4 A
|
12
|
0,015
|
0,25
|
0,25
|
2
|
Relening turi
|
Ta’minlash. Kuchlanish (V) yoki tokning (A) qiymati
|
CHulg‘amning qarshiligi, Om
|
Iste’mol qiladigan quvvat, Vt
|
Kontaktlar
|
O‘zgarmas 220 V kuchlanish zanjiridagi kontaktlarning ruxsat etilgan toki
|
CHulg‘amning nominal kuchlanishi, VAniqlik sinfidagi nominal quvvat, VAMaksimal quvvat, VA7 V13,5871,750,25214 V26,53601,750,25228 V3114401,750,25266 V12275001,750,252130 V235280001,752z, yoki 2r, yoki 1z, 1r0,252Uzilishda Uzoq vaqt
|
|