tasmali zirh - Andijon mashinasozlik instituti mualliflar: Maxsudov Moxirbek Tolibjonovich Abdurashidov Eldorbek Ergashboy o‘g‘li

tasmali zirh
6/10
50/70
3
10GT-3-50/70-
M
10GT-3-
50/70-AM
1100
145
6/10
70/150
3
10G T-3-
70/150-]
10G T-3-
70/150-A
1100
150
6/10
150/240
3
10GT-3-
159/240-
10GT-3-
159/240-A
1100
160
6/10
240/300
3
10GT-3-
240/300-
10GT-3-
240/300-A
1100
170
1CЛX-B-М ulash muftanig texnikaviy parametrlari
3.2 - jadval
Nominal
ko‗chlanishi, kV
Kabel tolalarinig
soni
Tolalaiarnig
kesimi,mm
2
Belgilanishi
1 gacha
3
16/25
eks-1CnX-3-16/25-B
1 gacha
3
35/50
eks-1CnX-3-35/50-B-M
1 gacha
3
70/120
eks-1CnX-3-70/120-B-M
1 gacha
3
150/240
eks-1CnX-3-150/240-B-M
1 gacha
4
16/25
eks-1CnX-4-16/25-B
1 gacha
4
35/50
eks-1CnX-4-35/50-B-M
1 gacha
4
70/120
eks-1CnX-4-70/120-B-M
1 gacha
4
150/240
eks-1CnX-4-150/240-B-M
Bino ichidagi qurilmalar uchun oxirgi muftalar
3.3 - jadval
Nominal
kuchlanish,
kV
Tolalar
kesimi,mm
2
Kabelni
tolalar soni
Zirxlanmagan
Tasmali
zirxlangan
Ajratish
uzunligi,mm(L)
6/10
35/50
3
rek-10BC-3-
35/50-
M
rek-10BC-3-
35/50-AM
430
6/10
70/95
3
rek-10BC-3-
70/95-
M
rek-10BC-3-
70/95-AM
450
6/10
120/240
3
rek-10BC-3-
120/240-M
rek-10BC-3-
150/240-M
460
6/10
240/300
3
rek-10BC-3-
240/300-M
rek-10BC-3-
240/300-M
525
Tashqaridagi qurilmalar uchun oxirgi muftalar
3.4- jadval
Nominal
kuchlanish, kV
Tolalar
kesimi,mm
2
Kabelni
tolalaf soni
Zirxlanmagan
Tasmali zirxlangan
Ajratish
uzunlig,
mm(L)
6/10
35/50
rek-10B2C-3-
50/70-M
rek-10BC2-3-50/70-
AM
620
6/10
35/50
rek-10BC2-3-
70/120-M
rek-10BC2-3-70/120-
AM
650
6/10
35/50
rek-10BC2-3-
120/150-M
rek-10BC2-3-
120/150-AM
660
Ichki qurilmalar uchun ohirgi muftalar
Nominal
kuchlani
sh,kV
Tolalar
kesimi,
mm
2
Kabllarnig
tolalar soni
Kabellarnig belgilanishi zirhlanmagan tagmali
zirxlangan
Ajratish
ng ing
kichik
uzunligi,
mm,(L)
6/10
35/50
3
rek-10HH-3-35/50-M
rek-10HH-3-35/50-AM
450
6/10
70/95
3
rek-10HH-3-70/95-M
rek-10HH-3-70/95-AM
450
6/10
120/24
0
3
rek-10HH-3-120/240-M rek-10HH-3-120/240-AM
450
6/10
240/30
0
3
rek-10HH-3-300/5-M rek-10HH-3-240/300-AM
450
3.5 - jadval
Tashqi qurilmalar uchun oxirgi muftalar
Nominal
kuchlanish,
kV
Tolalar
kesimi,m
m
2
Kabllar
nig
tolalar
soni
Kabellarnig belgilanishi zirhlanmagan tagmali
zirxlangan
Ajratishn g
in
g kichik
uzunligi,m
m,(L)
6/10
50/70
3
rek-10HH2-3-50/70-M rek-10HH2-3-50/70-AM 800
6/10
70/120
3
rek-10HH2-3-70/120-M rek-10HH2-3-70/120-AM 800
6/10
120/150 3
rek-10HH2-3-120/150-
M
rek-10HH2-3-120150-
AM
800
4 - ILOVA
ENERGIY TEJAMKOR KUCH TRANSFORMATORLARNIG
TEXNIKAVIY
PARAMETRLARI
HOkv kuchlanishli ikki va uch chulg‗amli SFS11 va SZS11 sriyali ku ch
transformatorlari
Asosiy tavsiflari quyidagilar hisoblanadi:
kichik shovqin.
past isrofli.
qisman past razryadli yuqori mexanik va elektirik.
mustahkam.
tula achlangan va bosh.
3.6 - jadval
Kuchlanishni xuklanish osdda rosdagichli samaradcrligini va
energy havsizlik tizimini oshiradi.
Uchchulg'amH
Havo bilan sovutila digam moyii Uchchulg'amli
Modellarnig bdgilanishi
SlF>S(Z)ll-
CV110
Kuchlamshni darajasi(kV)
Nominal quwad(kVA)
Unimdorlik darajasi
272
SZ9-1000-31500/35/10 transformatornig texnikaviy parametrlari
Nom
in
al q
u
vvati, k
VA
Transform
a tsiylash
koeffisyinti
varostlash
oralig‗i
Chu
lg‗
amlar
n
ig u
la
n
ish
gr
u
h
i va s
h
em
asi
|
S
alt ish
las
h
q
u
vvat
isro
fi, kVt
Yuk
lama ost
id
a q
u
vvat
isrof
i, k
Vt
Uk, %
S
alt ish
las
h
t
ok
i, %
Og‗irligi, kg
O‗lchov
hajmi
O‗
lchov as
b
ob
lari
YuK
, k
V
Rost
lash
PK, k
V
Qob
iq
M
oy
B
u
tun
o
g‗
irligi
T
ash
ish
UxKxB
1000
35
1,7
13,0
6,5
1,1
1930
1240
4600
3650
2850x1930x2
4
30
1070x10
7
0
1250
2,0
15,0
1,1
2200
1320
4950
3800
2900x1950x2
4
50
1070x10
7
0
1600
2,4
18,0
7,0
1,0
2550
1400
5300
3980
2950x1980x2
4
90
1070x10
7
0
2000
10,5
2,9
20,0
7,5
1,0
2775
1560
5965
4925
3010x2065x2
5
40
1070x10
7
0
2500
6,3
±3x2,5
3,3
22,0
1,0
3300
1750
6950
5683
3035x2265x2
6
10
1070x10
7
0
3150
4,0
26,0
8,0
0,9
3770
1970
7900
6075
3160x2095x2
6
40
1070x10
7
0
4. 3 - jadval
273
4000
35
38,5
4,9
30,5
0,9
4520
2260
9110
7090
3295x2325x2
8
90
1070x14
7
0
5000
5,8
35,0
0,8
5
5480
2475
10855
8465
3350x2520x3
0
00
1070x14
7
5
6300
7,0
39,0
0,8
5
6810
2620
12300
9870
3475x2645x3
0
50
1070x14
7
5
8000
8,9
44,0
0,7
5
8066
3330
15300
12550
4900x3126x3
2
77
1475x14
7
5
10000
10,5
51,0
0,7
5
9705
3750
17858
14700
5044x3152x3
3
97
1475x14
7
5
12500
Yd11
12,6
60,5
0,7
1096
0
4215
20042
17334
5054x3192x3
4
32
1475x14
7
5
16000
15,2
74
0,6
1395
0
4900
24150
21000
4900x3800x3
6
80
1475x14
7
5
20000
20
87,5
0,5
1670
0
6120
30100
25200
4950x3810x3
6
90
1475x14
7
5
25000
YN
d
11
23,4
104
0,5
1980
0
8500
36500
28700
5050x3900x3
8
50
1475x14
7
5
31500
27,5
123,1
0,4
5
2630
0
9965
0
46800
39800
5130x4050x3
9
20
2040x14
7
5
274
5 - ilova
Kontaktor va avtomatlarni ko‗p martali ulash va uzish sinovlari
5.1 - jadval
Opratsiya
Nominaldan kuchlanishdan
oprativ kuchlanishi, %
Operatsiyalar soni
Ulash
90
5
Ulash va uzishish
100
5
Uzish
80
10
6 -ilova
Elektr motorlarda ruxsat etilgan rolikli podshbniklarda radialli
oraliqlar
6.1- jadval
Podshibniklarni ichki
diametrlari, mm
Oraliq, mm
Yangi podshbniklar uchun
Barchasi uchun (eng
kattalari)
20-30
0,02-0,05
0,1
31-50
0,02-0,06
0,2
51-80
0,03-0,07
0,2
81-100
0,04-0,08
0,3
101-120
0,05-0,09
0,3
Elektr motorlarni markazlashtirishda o‗qnig eng yuqori og‗ishi*
6.2 - jadval
Uqni aylanish
chastotasi,
ay/min
Yarim muftanig og‗ishi, mm, muftalar uchun
qattiq
ko‗ndalang-
uralganlar
qayishqoq
vtulkali-
barmoqli
Qayishqoq
plastinali
rezina- aralash
motali
O‗zgaruvchan
qattiqlikli tasmali
prujinali
V3H yoki M3U
tishlilar
3000
0,04
0,2
0,2
0,25
0,25
1500
0,04
0,3
0,3
0,4
0,4
750
0,04
0,4
0,4
0,5
0,5
500
0,04
0,5
0,5
0,6
0,6
275
TAQSIMLOVCHI QURILMALARNI TEKSHIRISH VA
SINASH
Taqsimlovchi qurilmalarnig ishdan chiqish sabablari
7.1 - jadval
O‗chirgichlarnig ishdan chiqishlari
Ishdan chiqishlar soni,
%
Ishlab chiqarishdagi nuqsonlar (sifatsiz yaratilgan, tuzilishda
yitishmavchiliklar va.bosh.)
18
Qoniqarsiz ishlatish
18
Ta‘mirlashnig sifati past
12
Tashqari dan ta‗sid tishlar
14
Foydalanishga sharoit tug‗ri kelmasligi (tarmoqnig o‗ta kuchlanishi va
bosh.)
3
Tabiiy yimirilish va eskirish
19
Tashishda, saqlashda va montajdagi nuqsonlar
3
Noaniq sabablar
13
|