O‘lshov transformatorlari

O‘lshov transformatorlari
Kuchlanish transformatorlarining texnik ma’lumotlari
Transformator turi
RU–21/12
RU–21/24
RU–21/48
RU–21/110
RU–21/220
|
Nominal
|
Uzoq vaqt
|
|
birlamchi
|
ikkilamchi
|
0,5
|
1
|
3
|
NOS–0,5
|
380
|
100
|
25
|
40
|
100
|
200
|
NOS–0,5
|
500
|
100
|
25
|
40
|
100
|
200
|
NOSK–3
|
3000
|
100
|
30
|
50
|
120
|
240
|
NOSK–6
|
6000
|
100
|
50
|
80
|
200
|
400
|
NOM–6
|
3000
|
100
|
30
|
50
|
120
|
400
|
NOM–6
|
6000
|
100
|
50
|
80
|
200
|
600
|
NOM–10
|
10000
|
100
|
80
|
150
|
320
|
720
|
NTS–0,5
|
380
|
100
|
50
|
80
|
200
|
400
|
NTS–0,5
|
500
|
100
|
50
|
80
|
200
|
400
|
NTMK–6–48
|
3000
|
100
|
50
|
80
|
200
|
400
|
NTMK–6–48
|
6000
|
100
|
80
|
150
|
320
|
640
|
NTMK–10
|
10000
|
100
|
120
|
200
|
480
|
960
|
NTMI–6
|
3000
|
100–100/3
|
50
|
80
|
200
|
400
|
NTMI–6
|
6000
|
100–100/3
|
80
|
150
|
320
|
640
|
NTMI–10
|
10000
|
100–100/3
|
120
|
200
|
480
|
960
|
Izoh. Kuchlanish transformatorlarini belgilanishi: NOS – bir fazali quruq, NTS – uch fazali quruq, NOM – bir fazali moyli, NTMK – kompensatsiyalovchi chulg‘amli uch fazali moyli, NTMI – besh sterjenli moyli uch fazali uch chulg‘amli.
Kuchlanish transformatorlari
Turi
|
Kuchlanish, kV
|
SHulg‘amning nominal kushlanishi, V
|
Aniqlik sinfidagi nominal quvvat, VA
|
Qo‘shimcha ikkilamchi chulg‘amning nominal quvvati, VA
|
CHegaraviy quvvat, VA
|
Ulanish guruhi
|
Og‘irligi, kg
|
birlamchi
|
asosiy ikkilamchi
|
qo‘shimcha
ikkilamchi
|
0,2
|
0,5
|
1
|
3
|
NOS–0,5–U4
|
0,5
|
380
|
100
|
-
|
-
|
25
|
50
|
100
|
-
|
200
|
1/1–0
|
9
|
500
|
NOSK–3–U5
|
3
|
3000
|
30
|
50
|
150
|
240
|
14
|
NOSK–6–66–U5(T5)
|
6
|
6000
|
127–100
|
50
|
75
|
200
|
400
|
13
|
NOM–6–U4(T4)
|
6
|
3000
|
100
|
30
|
50
|
150
|
240
400
|
24
|
6000
|
50
|
75
|
200
|
22
|
NOME–6–U2(T2)
|
6
|
6000
|
|
24
|
NOM–10–66–U2(T2)
|
10
|
10000
|
75
|
150
|
300
|
630
|
–
|
35
|
NOM–15–U4(T4)
|
15
|
13800
|
640
|
1/1–0
|
23
|
15750
|
18000
|
NOM–35–66U1(T1)
|
35
|
35000
|
150
|
250
|
600
|
1200
|
86
|
ZNOM–15–63U2(T2)
|
15
|
6000:√3
|
100:√3/100:3
|
75
|
150
|
300
|
400
|
1/1/1–0–0
|
64
|
10000:√3
|
640
|
63
|
13800:√3
|
15750:√3
|
ZNOM–20–63U2(T2)
|
20
|
18000:√3
|
100:√3/100:3
|
-
|
-
|
75
|
150
|
300
|
–
|
640
|
1/1/1–0–0
|
85
|
20000:√3
|
77,5
|
ZNOM–24–69U1
|
24
|
24000:√3
|
150
|
250
|
600
|
980
|
108
|
ZNOM–35–65U1
|
35
|
27500
|
127–100
|
1200
|
78
|
ZNOM–35–65U1(T1)
|
35000:√3
|
100:√3/100:3
|
Turi
|
Kuchlanish, kV
|
SHulg‘amning nominal kushlanishi, V
|
Aniqlik sinfidagi nominal quvvat, VA
|
Qo‘shimcha ikkilamchi chulg‘amning nominal quvvati, VA
|
CHegaraviy quvvat, VA
|
Ulanish guruhi
|
Og‘irligi, kg
|
birlamchi
|
asosiy ikkilamchi
|
qo‘shimcha
ikkilamchi
|
0,2
|
0,5
|
1
|
3
|
ZNOL.06–6U3(T3)
|
6
|
3000:√3
|
100/√3
|
100/3 yoki 100
|
15
|
30
|
50
|
150
|
|
250
|
–
|
26,5
|
3300:√3
|
100
|
6000:√3
|
100/3 yoki 100
|
30
|
50
|
75
|
200
|
400
|
6300:√3
|
6600:√3
|
6900:√3
|
ZNOL.06–15U3(T3)
|
15
|
13800:√3
|
50
|
75
|
150
|
300
|
300
|
630
|
–
|
29,5
|
15750:√3
|
ZNOL.06–10U3(T3)
|
10
|
10000:√3
|
28,5
|
11000:√3
|
ZNOL.06–20U3(T3)
|
20
|
18000:√3
|
32,5
|
20000:√3
|
ZNOL.06–24U3(T3)
|
24
|
24000:√3
|
100/√3
|
100/3 yoki 100
|
50
|
75
|
150
|
300
|
300
|
630
|
–
|
40,5
|
ZNOL.09–6.02
|
6
|
3000:√3
|
15
|
30
|
50
|
150
|
150
|
250
|
28,5
|
3300:√3
|
6000:√3
|
6300:√3
|
30
|
50
|
75
|
200
|
200
|
400
|
6600:√3
|
6900:√3
|
11000:√3
|
ZNOL.09–10.02
|
10
|
10000:√3
|
50
|
75
|
150
|
300
|
300
|
630
|
31,5
|
Turi
|
Kuchlanish, kV
|
SHulg‘amning nominal kushlanishi, V
|
Aniqlik sinfidagi nominal quvvat, VA
|
Qo‘shimcha ikkilamchi chulg‘amning nominal quvvati, VA
|
CHegaraviy quvvat, VA
|
Ulanish guruhi
|
Og‘irligi, kg
|
birlamchi
|
asosiy ikkilamchi
|
qo‘shimcha
ikkilamchi
|
0,2
|
0,5
|
1
|
3
|
NOL.O8–6UT2
|
6
|
6000
|
100
|
–
|
30
|
50
|
75
|
200
|
–
|
400
|
1/1–0
|
28,5
|
6300
|
100 yoki 110
|
6600
|
6900
|
NOL.08–10UT2
|
10
|
10000
|
100
|
50
|
75
|
150
|
300
|
630
|
31,5
|
11000
|
100 yoki 110
|
NTMI–10–66UZ
|
10
|
10000
|
100
|
100/3
|
–
|
120
|
200
|
500
|
960
|
Yn/Yn/–0
|
81
|
NTMI–18*
|
18
|
13800
|
100/100:3
|
–
|
–
|
120
|
200
|
500
|
–
|
960
|
Yn/Yn/–0
|
94
|
15750
|
18000
|
NKF–110–57U1
|
110
|
110000:
√3
|
100:√3/100
100:√3/100:3
100:√3/100
|
|
|
400
|
600
|
1200
|
|
2000
|
1/1/1–0–0
|
630
|
NKF–110–58U1
|
800
|
NKF–66U1(T1)
|
66
|
66000:√3
132000:√3
220000:√3
|
545
|
NKF–132–73T1
|
132
|
630
|
NKF–220–65T1
|
220
|
1325
|
Iсhki qurilmalar uсhun tok transformatorlari
Turi
|
Nominal kuсhlanish, kV
|
Nominal tok, A
|
Ikkilamсhi сhulg‘amni bajarilish varianti
|
Aniqlik sinfi yoki ikkilamсhi сhulg‘amni belgilanishi
|
Aniqlik sinfidagi nominal yuklama, VA
|
Elektro-dinamik barqarorlik
|
Termik barqarorlik
|
Massa, kg
|
birlamсhi
|
ikkilamсhi
|
0,5
|
1
|
3
|
karralik
|
Idin, kA
|
karralik/
ruxsat etilgan vaqt, birl/s
|
Ruxsat etilgan tok/ ruxsat etilgan vaqt kA/s
|
TVLM–6–1
|
6
|
10; 20; 30; 50; 75; 100; 150; 200; 300; 400
|
5
|
–
|
–
|
1
|
15
|
–
|
–
|
–
|
3,5; 7; 10,6; 17,6; 26,6; 35,2; 52; 52; 52; 52
|
0,64; 1,32; 1,96; 3,6; 4,9; 6,9; 9,7; 13,8; 17,5; 20,5
|
5,3
|
TVLM–10*
|
10
|
20; 30; 50; 100; 150; 200; 300; 400; 600; 800; 1000; 1500
|
5
|
–
|
0,5/R; R/R
|
–
|
15; 10
|
–
|
–
|
–
|
7; 10,6; 17,6; 35,2; 52; 52; 52; 52
|
0,94/4; 1,45/4; 2,45/4; 4,85/4; 6,25/4; 8,75/4; 12,5/4; 15/4
|
20; 20,5
|
TOLK–6,05
|
6
|
20; 30; 40; 50; 80; 100; 150; 200; 300; 400; 500
|
5
|
–
|
–
|
1
|
30
|
–
|
–
|
–
|
7; 10,5; 14; 17,6; 25; 25; 25
|
0,66/4; 0,98/4; 1,4/4; 1,8/4
|
11
|
TLM–6UTZ
|
6
|
300;400
|
5
|
1/R
|
1
|
10/15
|
–
|
–
|
–
|
125
|
–
|
25/4
|
27
|
|
600;800
|
0,5/R
|
0,5
|
10/15
|
|
1000; 1500
|
0,5
|
10/15
|
Turi
|
Nominal kuсhlanish, kV
|
Nominal tok, A
|
Ikkilamсhi сhulg‘amni bajarilish varianti
|
Aniqlik sinfi yoki ikkilamсhi сhulg‘amni belgilanishi
|
Aniqlik sinfidagi nominal yuklama, VA
|
Elektro-dinamik barqarorlik
|
Termik barqarorlik
|
Massa, kg
|
birlamсhi
|
ikkilamсhi
|
0,5
|
1
|
3
|
karralik
|
Idin, kA
|
karralik/
ruxsat etilgan vaqt, birl/s
|
Ruxsat etilgan tok/ ruxsat etilgan vaqt kA/s
|
TPLK–10
|
10
|
10; 15; 30; 50
|
5
|
0,5/10R; 10R/10R
|
|
|
–
|
–
|
–
|
2,47; 3,7; 7,4
|
–
|
0,45/4; 0,675/4; 1,35/4
|
–
|
100–400
|
0,5
|
10
|
74,5
|
|
10R
|
15
|
|
|
600;800
|
|
|
14,8
|
|
1500
|
|
|
74,5
|
|
TLM–10–1
TLM–10–2
|
10
|
50
|
5
|
0,5/10R; 10R/10R
|
|
10R
|
–
|
–
|
–
|
17,6
|
|
2,8(3)
|
–
|
100
|
|
|
35,2
|
6,3(3)
|
150
|
|
|
52,0
|
7,2(3)
|
200
|
0,5
|
10
|
52,0
|
10,1(3)
|
300; 400
|
0,5–10R
|
15
|
100,0
|
18,4(3)
|
600; 800
|
0,5–10R
|
—
|
100,0
|
23,3(3)
|
1000; 1500
|
|
|
100,0
|
26,3(3)
|
TL–10U3;
TL–10T3
|
10
|
50
|
5
|
0,5/R
|
|
|
|
|
|
51
|
|
2,5/4
|
–
|
100
|
|
|
|
|
|
5,0/4
|
150
|
|
|
|
|
|
7,5/4
|
200
|
0,5
|
10
|
–
|
|
|
10,0/4
|
300
|
R
|
–
|
15
|
|
|
15,0/4
|
400
|
|
|
|
|
|
20,0/4
|
600;
800;
1000
|
0,5
|
2,0
|
–
|
–
|
|
80
|
31,5/4
|
1500
|
R
|
–
|
30
|
–
|
–
|
3,5
|
TL–10U3;
TL–10T3
|
10
|
2000
|
5
|
0,5/R
|
R
|
|
30
|
–
|
–
|
81
|
–
|
31,5/4
|
–
|
|
|
–
|
15
|
3000
|
0,5/0,5
|
0,5
|
14
|
–
|
R/R
|
R
|
–
|
15
|
TPK–10
|
10
|
50
|
5
|
–
|
0,5
|
10
|
–
|
–
|
–
|
25
|
–
|
8/1
|
20
|
75; 100
|
10R
|
10
|
52
|
20/1
|
–
|
150;200
|
|
|
|
|
|
52
|
31,5/1
|
16,5
|
300; 400
|
|
|
|
|
|
81
|
31,5/3
|
–
|
600;800
|
|
|
|
|
|
–
|
–
|
–
|
1000;
1500
|
|
|
|
|
|
–
|
–
|
TPOL–10UZ
|
10
|
600; 800
|
5
|
10R
|
0,5
|
10
|
–
|
–
|
81; 81
|
–
|
32(3)
|
–
|
18
|
1000; 1500
|
10R/10R
|
10R
|
0,6
|
69
|
27(3)
|
–
|
|
0,5/R
|
|
15
|
45
|
15(3)
|
TPOL–10T3
|
10
|
600
|
5
|
10R;
10R/10R
0,5/R
|
0,5
|
10
|
|
|
81
|
–
|
32(3)
|
–
|
–
|
800
|
10R
|
|
|
|
|
32(3)
|
1000
|
|
0,6
|
|
|
69
|
27(3)
|
1500
|
|
15
|
|
|
45
|
18(3)
|
TPOLM–10*
|
10
|
400;600
|
5
|
0,5R; R/R
|
0,5
|
15
|
–
|
–
|
160
|
|
65/1
|
–
|
–
|
800
|
R
|
|
–
|
|
1000;
1500
|
|
15
|
155
|
65/1
|
TGYULM–10T*
|
10
|
400; 600; 800
|
5
|
0,5R; R/R
|
0,5
|
15
|
–
|
–
|
160
|
–
|
65/1
|
–
|
–
|
1000; 1500
|
R
|
155
|
TPSHL–10U3
|
10
|
4000
|
5
|
10R; 0,5/10R
|
0,5
|
–
|
–
|
–
|
20
|
–
|
35/3
|
–
|
43
|
5000
|
10R
|
30
|
–
|
–
|
TPSHL–10TZ
|
10
|
4000; 5000
|
5
|
10R; 0,5/10R;
|
0,5
|
–
|
–
|
–
|
20
|
–
|
35/3
|
–
|
43
|
10R
|
30
|
–
|
–
|
TOL–10U3 TOL–10T3
|
10
|
50
|
5
|
R/R
|
|
|
–
|
|
–
|
17,6
|
–
|
2,45/4
|
|
100
|
52
|
4,85/4
|
150
|
52
|
6,25/4
|
200
|
0,5
|
10
|
15
|
52
|
8,75/4
|
300; 400
|
3
|
–
|
–
|
100
|
16/4
|
600;800
|
|
|
|
100
|
20/4
|
1000; 1500
|
100
|
31,5/4
|
TSHLP–10UT3
|
10;
11
|
1000;
200
|
5
|
0,5/R; R/R
|
0,5
|
20
|
|
|
–
|
35/4
|
–
|
–
|
–
|
TSHLPK–10UT3
|
R
|
30
|
|
|
TLSH–10U3(T3)
|
10
|
2000;
3000
|
5
|
N/R; R/R
|
0,5
|
20
|
–
|
–
|
81
|
–
|
31
|
26
|
–
|
–
|
–
|
30
|
–
|
–
|
–
|
TSH–20–UXL3
|
20
|
8000; 10000
|
5
|
–
|
10R
|
30
|
–
|
–
|
|
160(3)
|
|
45
|
|
TSH–20–T3
|
12000
|
0,2
|
–
|
|
–
|
|
49
|
TSH–24
|
24
|
2000
|
5
|
–
|
10R
|
100
|
–
|
–
|
–
|
–
|
–
|
–
|
–
|
|
0,2
|
–
|
105
|
T1SH10–20
|
20
|
400
|
R
|
0,5; R
|
20
|
82
|
7500/4
|
3
|
TPOL–20
|
20
|
400
|
5
|
1/10R;
|
10R
|
–
|
15
|
–
|
–
|
120
|
–
|
16(3)
|
43
|
600
|
0,5/10R 10R/10R
|
0,5; 10R
|
20
|
–
|
24(3)
|
800
|
30
|
32(3)
|
1000; 15000
|
50
|
40(3)
|
TPOL–20T
|
20
|
400;600
|
5
|
10R
|
R
|
20
|
–
|
–
|
75
|
–
|
40/4
|
–
|
–
|
800
|
0,5
|
–
|
–
|
–
|
TSHV–24
|
24
|
24000
|
5
|
0,5
|
10R
|
–
|
–
|
–
|
–
|
–
|
6/3
|
–
|
–
|
3000
|
0,2
|
100
|
106
|
TPOL–27
|
27
|
1500
|
5
|
R/R
|
R
|
20
|
–
|
–
|
70
|
–
|
20/4
|
–
|
105
|
2500
|
–
|
50
|
95
|
TPOL–35
|
35
|
400
|
5
|
10R/10R 1/10R
|
1; 10R
|
15
|
–
|
–
|
–
|
|
–
|
16/3
|
|
600
|
10R/0,5 10R/10R
|
0,5; 10R
|
20
|
100
|
24(3)
|
800
|
10R/0,5 10R/10R
|
30
|
|
32(3)
|
TPOL–35
|
35
|
1000
|
5
|
10R/0,5 10R/10R
|
0,5; 10R
|
50
|
–
|
–
|
–
|
100
|
–
|
40(3)
|
55
|
1500
|
10R/0,5 10R/10R
|
52(3)
|
*Ishlab shiqarishdan olib tashlangan.
Izoh. Transformatorlar turini belgilanishi: T – tok transformatori yoki tropik bajarilgan (agar T sondan keyin turgan bo‘lsa); K – o‘ramli KTQ (KRU) uсhun; P – o‘tiladigan yoki yassi shinadagi qurilmalar uсhun; O – bir o‘ramli (sterjenli) yoki tutib turuvсhi (TOL); L – quyma izolyatsiyali yoki laboratoriyali; V – vtulkali yoki havo izolyatsiyali; U – kuchaytirilgan yoki mo‘tadil iqlimli rayonlar uchun (agar U raqamdan keyin turgan bo‘lsa); M – modernizatsiyalangan yoki kichik o‘lchamli; XL – sovuq iqlimli hududlar uchun; birinchi chiziqdan keyingi raqam – nominal kuchlanish, kV; oxiridagi 1 raqami – birinchi variant yoki ochiq havoda ishlar uchun; 2 raqami – ikkinchi variant yoki tashqi havo erkin ruxsat etiladigan binolarda ishlar uchun; 3 raqami – sun’iy ventilyatsiyali yopiq binolarda ishlar uchun.
Tashqi qurilmalar uchun tok transformatorlari
Turi
|
Nominal kuchlanish, kV
|
Nominal tok, A
|
Ikkilamchi chulg‘amni bajarilish varianti
|
Aniqlik sinfi yoki ikkilamchi chulg‘amni belgilanishi
|
Aniqlik sinfidagi nominal yuklama, VA
|
Elektro-dinamik barqarorlik
|
Termik barqarorlik
|
Massa
|
birlamchi
|
ikkilamchi
|
0,5
|
1
|
3
|
karralik
|
Idin, kA
|
karralik/
ruxsat etilgan vaqt, birl/s
|
Ruxsat etilgan tok/
ruxsat etilgan vaqt kA/s
|
TKLN–10
|
10
|
10–200
|
5
|
0,5/R; R/R
|
0,5
|
–/0,4
|
–
|
–
|
100
|
–
|
50/1
|
–
|
20
|
R
|
–
|
|
0,6
|
–
|
–
|
TFND–33T TFZM–33A–T1
|
33;
35
|
100–400
|
5
|
R/R/0,5
|
0,5
|
30/1,2
|
60/2,4
|
–
|
–
|
14; 21
|
–
|
4/4; 6/4
|
420
|
600; 1200
|
R
|
28; 42; 56; 84; 169
|
8/4; 12/4; 16/4; 24/4 48/4
|
TFN–35M
(TFZM– 35A–U1; TFZM– 35A–XL1)
|
35
|
15–800
|
5
|
0,5/R
|
0,5
|
–/2
|
–/4
|
–
|
150
|
–
|
65/1
|
–
|
–
|
100
|
R
|
–/0,8
|
100
|
TFND–35M (TFZM–35B1U1)
|
35
|
15–600
|
5
|
0,5/R/R
|
0,5
|
–/1,2
|
–/2,4
|
–
|
150
|
–
|
–
|
–
|
–
|
800; 1000
|
R
|
100
|
32; 5/4
|
|
|
TFZM–35A–XL1
|
35
|
15; 20; 30; 40; 50; 75; 100; 150; 200; 300; 400; 600;800; 1000
|
5
|
0,5/10R
|
0,5; 10R
|
50
|
–
|
–
|
–
|
–
|
–
|
–
|
200
|
20
|
–
|
TFZM– 35M–U1
|
35
|
15; 20; 30; 40; 50; 75; 100; 150; 200; 300; 400; 600
|
5
|
–
|
0,5; 10R
|
50
|
100
|
–
|
–
|
3; 4; 6; 8; 10; 15; 21; 31; 42; 63; 84; 127
|
–
|
0,6/3; 1,1/3; 1,5/3; 2,3/3; 5,8/3; 7/3; 15/3; 22/3
|
240
|
20
|
TFZM–35B–IU1
|
35
|
15; 20; 30; 40; 50; 75; 100; 150; 200; 300; 400; 600; 800; 1000; 1500; 2000
|
5
|
–
|
0,5; 10R
|
30
|
60
|
–
|
–
|
3; 4; 6; 8; 10; 15; 21; 31; 42; 63; 3; 4; 6; 8; 10; 15; 21; 31; 42; 63; 84; 127; 107; 134; 106; 141
|
–
|
1/3; 1,5/3; 2,1/3; 2,3/3; 4,7/3; 7/3; 10,5/3; 15/3; 21/3; 31/3; 31/3; 37/3; 41/3
|
500
|
TFZM–35B–IIU1
|
35
|
500
|
5
|
–
|
0,5; 10R
|
30
|
–
|
–
|
–
|
125
|
–
|
55/3
|
500
|
1000
|
50
|
49/3
|
2000
|
145
|
3000
|
57/3
|
1000
|
1
|
30
|
125
|
2000
|
50
|
145
|
49/3
|
3000
|
57/3
|
TFZM–33A–T1
|
33
|
100; 150; 200; 300; 400; 600; 1200
|
5
|
–
|
0,5; 10R
|
30
|
60
|
–
|
–
|
14; 21; 7; 28; 42; 56; 84; 169
|
–
|
4,6/3; 7/3; 9/3; 14/3; 18/3; 28/3; 56/3
|
420
|
20
|
–
|
TFZM–66V–T1
|
66
|
200–400
|
5
|
–
|
0,5
|
30
|
–
|
–
|
–
|
24–48
|
–
|
9/3–18/3
|
380
|
600–1200
|
10R
|
48–96
|
18/3–36/3
|
TFNR–35 (TFZM–35B–IIU1)
|
35
|
500; 1000
|
5
|
0,5/R/R
|
0,5
|
–/1,2
|
–
|
–
|
–
|
125
|
49/4
|
49/4
|
–
|
2000; 3200
|
R
|
–/2
|
145
|
57/4
|
57/4
|
1000
|
1
|
0,5
|
30/–
|
125
|
49/4
|
49/4
|
2000; 3200
|
R
|
50/–
|
145
|
57/4
|
57/4
|
TFN–66ST
|
66
|
200–400
|
5
|
R/R/0,5
|
0,5; R
|
–/1,2
|
–
|
–
|
120
|
–
|
50/3
|
–
|
–
|
TFNU–66ST
|
66
|
200–400
|
5
|
R/R/0,5
|
0,5
|
–/1,2
|
–
|
–
|
–
|
24–48
|
–
|
9,4/4–18,8/4
|
–
|
600–1200
|
R
|
48–96
|
–
|
TFND–110 M (TFZM–110B–1U1)
|
110
|
50–600
|
5
|
0,5/R/R
|
0,5
|
–/1,2
|
–
|
–
|
150
|
–
|
43,3/3
|
–
|
–
|
400–800
|
R
|
110
|
34,6/3
|
TFND–110M–XL
|
110
|
50–600
|
5
|
0,5/R/R
|
0,5
|
–/1,2
|
–
|
–
|
150
|
–
|
43,3/3
|
–
|
–
|
400–800
|
R
|
110
|
34,6/3
|
TFND–110M–II
|
110
|
750–1500
|
5
|
0,5/R/R
|
0,5
|
–/0,8
|
–
|
–
|
75
|
–
|
60/1
|
–
|
–
|
1000–2000
|
R
|
(TFZM–110B–NU1)
|
110
|
750–1500
|
1
|
0,5/R/R
|
0,5
|
20/–
|
–
|
–
|
75
|
–
|
60/1
|
–
|
–
|
1000–2000
|
TFND–110M–II–XL
|
110
|
750–1500
|
5
|
0,5/R/R
|
0,5
|
–/0,8
|
2/–
|
|
75
|
–
|
34,6/3
|
–
|
–
|
1000–2000
|
R
|
–
|
–
|
750–1500
|
1
|
0,5
|
20/–
|
50
|
|
1000–2000
|
|
TFZM–110B–IU1
|
110
|
50–100
|
5
|
–
|
0,5
|
30
|
100
|
–
|
–
|
10–20
|
–
|
2/3–4/3
|
540
|
75–150
|
10R
|
|
15–30
|
3/3–6/3
|
100–200
|
21–42
|
4/3–8/3
|
150–300
|
31–62
|
6/3–12/3
|
200–400
|
|
42–84
|
8/3–16/3
|
300–600
|
63–126
|
13/3–26/3
|
400–800
|
62–124
|
14/3–28/3
|
TFZM– 100B–IIU1
|
110
|
750–1500
|
5
|
–
|
0,5
|
20/–
|
–
|
–
|
–
|
79–158
|
–
|
26/3–52/3
|
11200
|
1000–2000
|
10R
|
10R
|
106–212
|
34/3–68/3
|
–
|
750–1500
|
1
|
–
|
0,5
|
79–158
|
26/3–52/3
|
11200
|
1000–2000
|
10R
|
10R
|
106–212
|
34/3–68/3
|
–
|
TFNU–132ST
|
132
|
200–400
|
5
|
0,5/R/R
|
0,5; R
|
30/–
|
–
|
–
|
–
|
49–90
|
–
|
11–22
|
1645
|
300–600
|
500–1000
|
17–34
|
600–1200
|
750–1500
|
TFNU– 132ST
|
132
|
200–400
|
1
|
0,5/R/R
|
0,5; R
|
30/–
|
–
|
–
|
–
|
49–90
|
–
|
11–22 17–34
|
1645
|
TFND–150–1
|
150
|
600–1200
|
5
|
0,5/R/R/R
|
0,5
|
–/1,6
|
–
|
–
|
–
|
62
|
24,6/3
|
–
|
–
|
(TFZM–150–IU1)
|
150
|
600–1200
|
1
|
0,5/R/R/ R
|
R
|
–/2
|
–
|
–
|
–
|
62
|
24,6/3
|
–
|
–
|
0,5
|
40/–
|
TFND–150–1–XL
|
600–1200
|
5
|
R
|
50/–
|
1
|
0,5
|
1,6/–
|
R
|
2/–
|
0,5
|
40/–
|
R
|
50/–
|
TFZM–150–1U1
|
150
|
600–1200
|
5
|
0,5
|
0,5
|
40/–
|
–
|
–
|
–
|
52–104
|
14–28(3s)
|
–
|
1060
|
10R
|
10R
|
50/–
|
1
|
0,5
|
0,5
|
40/–
|
10R
|
10R
|
50/–
|
*Ishlab shiqarishdan olib tashlangan.
Izoh. 1. Transformatorlar turini belgilanishi: T – tok transformatori yoki tropik bajarilgan (agar T sondan keyin turgan bo‘lsa); K – kabel – kondensatorli (TFKN), kaskadli (TFNKD–500) izolyatsiyali; F – farfor (chinni) izolyatsiyali; U – kuchaytirilgan yoki mo‘tadil iqlimli rayonlar uchun (agar U raqamdan keyin turgan bo‘lsa); N – tashqi qurilmalar uchun; D – differensial himoyalar uchun o‘zakli; XL – sovuq iqlimli hududlar uchun; birinchi chiziqdan keyingi raqam – nominal kuchlanish, kV; oxiridagi 1 raqami – birinchi variant yoki ochiq havoda ishlar uchun; 2 raqami – ikkinchi variant yoki tashqi havo erkin ruxsat etiladigan yopiq binolarda ishlar uchun; 3 raqami –sun’iy ventilyatsiyali yopiq binolarda ishlar uchun; II, III, IV – gabarit; A (B) – tashqi o‘lcham o‘tib ketadigan uzunlik yo‘li bo‘yicha elektr uskunalarning kategoriyasi.
2. Qavs ichida transformatorning zahira turi ko‘rsatilgan.
|