natgillin/translations-raw huggingface dataset:
are classified as range hoods covered by Commission Regulation (EU) No 66/2014 [7] on kitchen appliances.
„prezračevalna enota (PE)“ pomeni napravo na električni pogon z vsaj enim propelerjem, enim motorjem in ohišjem, namenjeno za zamenjavo uporabljenega zraka z zunanjim zrakom v stavbi ali delu stavbe;
Article 2
„stanovanjska prezračevalna enota“ (SPE) pomeni prezračevalno enoto, kjer:
Definitions
največja stopnja pretoka ne preseže 250 m3/h;
For the purposes of this Regulation the following definitions shall apply:
je največja stopnja pretoka med 250 in 1000 m3/h, proizvajalec pa za namen uporabe navede izključno uporabo za stanovanjsko prezračevanje;
‘ventilation unit (VU)’ means an electricity driven appliance equipped with at least one impeller, one motor and a casing and intended to replace utilised air by outdoor air in a building or a part of a building;
„nestanovanjska prezračevalna enota“ (NSPE) pomeni prezračevalno enoto, pri kateri največja stopnja pretoka prezračevalne enote presega 250 m3/h, kjer je največja stopnja pretoka med 250 in 1000 m3/h, proizvajalec pa za namen uporabe ne navede izključne uporabe za stanovanjsko prezračevanje;
‘residential ventilation unit’ (RVU) means a ventilation unit where:
„največja stopnja pretoka“ je navedena največja stopnja pretoka zraka, ki se doseže z vgrajenim ali ločenim priloženim krmiljem pri običajnih pogojih zraka (20 °C) in 101325 Pa, če je enota nameščena v celoti (npr. vključno s čistimi filtri) in v skladu z navodili proizvajalca, pri čemer je za SPE s kanalskim razvodom največji pretok povezan z zračnim pretokom pri 100 Pa zunanje razlike statičnega tlaka in za SPE brez kanalskega razvoda z zračnim pretokom pri najmanjši možni skupni tlačni razliki, ki se izbere iz skupine vrednosti 10 (najmanjša)-20-50-100-150-200-250 Pa, in sicer tista, ki je enaka izmerjeni vrednosti tlačne razlike ali je tik pod njo;
the maximum flow rate does not exceed 250 m3/h;
„enosmerna prezračevalna enota“ (EPE) pomeni prezračevalno enoto, ki proizvaja pretok zraka le v eno smer, in sicer iz notranjega prostora v zunanjega (odvodna) ali iz zunanjega prostora v notranjega (dovodna), kjer je mehansko proizveden pretok zraka uravnotežen z naravnim dovodom zraka ali odvodom;
the maximum flow rate is between 250 and 1000 m3/h, and the manufacturer declares its intended use as being exclusively for a residential ventilation application;
„dvosmerna prezračevalna enota“ (DPE) pomeni prezračevalno enoto, ki proizvaja pretok zraka med notranjim in zunanjim prostorom in je opremljena z ventilatorji za odvajanje in dovajanje;
‘non-residential ventilation unit’ (NRVU) means a ventilation unit where the maximum flow rate of the ventilation unit exceeds 250 m3/h, and, where the maximum flow rate is between 250 and 1000 m3/h, the manufacturer has not declared its intended use as being exclusively for a residential ventilation application;
„enakovredni model prezračevalne enote“ pomeni prezračevalno enoto z enakimi tehničnimi značilnostmi iz veljavnih zahtev za navajanje podatkov o izdelku, vendar ga isti proizvajalec, pooblaščeni zastopnik ali uvoznik da na trg kot drugačen model prezračevalne enote.
‘maximum flow rate’ is the declared maximum air volume flow rate of a ventilation unit that can be achieved with integrated or separately co-supplied controls at standard air conditions (20 °C) and 101325 Pa, where the unit is installed complete (e.g. including clean filters) and according to the manufacturer's instructions, for ducted RVUs the maximum flow is related to the air flow at 100 Pa of external static pressure difference, and for non-ducted RVUs to the air flow at the lowest achievable total pressure difference to be chosen from a set of values of 10 (minimum)-20-50-100-150-200-250 Pa, whichever is equal or just below the measured pressure difference value;
Priloga I vsebuje dodatne opredelitve pojmov za namene prilog II do IX.
‘unidirectional ventilation unit’ (UVU) means a ventilation unit producing an air flow in one direction only, either from indoors to outdoors (exhaust) or from outdoors to indoors (supply), where the mechanically produced air flow is balanced by natural air supply or exhaust;
Člen 3
‘bidirectional ventilation unit’ (BVU) means a ventilation unit which produces an air flow between indoors and outdoors and is equipped with both exhaust and supply fans;
Zahteve za okoljsko primerno zasnovo
‘equivalent ventilation unit model’ means a ventilation unit with the same technical characteristics according to the applicable product information requirements, but placed on the market as a different ventilation unit model by the same manufacturer, authorised representative or importer.
Od 1. januarja 2016 SPE ustrezajo posebnim zahtevam za okoljsko primerno zasnovo iz Priloge II, točka 1.
For the purposes of Annexes II to IX, additional definitions are set out in Annex I.
Od 1. januarja 2016 NSPE ustrezajo posebnim zahtevam za okoljsko primerno zasnovo iz Priloge III, točka 1.
Article 3
Od 1. januarja 2018 SPE ustrezajo posebnim zahtevam za okoljsko primerno zasnovo iz Priloge II, točka 2.
Ecodesign requirements
Od 1. januarja 2018 NSPE ustrezajo posebnim zahtevam za okoljsko primerno zasnovo iz Priloge III, točka 2.
From 1 January 2016 RVUs shall comply with the specific ecodesign requirements set out in Annex II, point 1.
Člen 4
From 1 January 2016 NRVUs shall comply with the specific ecodesign requirements set out in Annex III, point 1.
Zahteve za navajanje podatkov
From 1 January 2018 RVUs shall comply with the specific ecodesign requirements set out in Annex II, point 2.
Od 1. januarja 2016 proizvajalci SPE, njihovi pooblaščeni zastopniki ali uvozniki ravnajo v skladu z zahtevami za navajanje podatkov iz Priloge IV.
From 1 January 2018 NRVUs shall comply with the specific ecodesign requirements set out in Annex III, point 2.
Od 1. januarja 2016 proizvajalci NSPE, njihovi pooblaščeni zastopniki ali uvozniki ravnajo v skladu z zahtevami za navajanje podatkov iz Priloge V.
Information requirements
Ocena skladnosti
From 1 January 2016 manufacturers, their authorised representatives and importers of RVUs shall comply with the information requirements set out in Annex IV.
Proizvajalci prezračevalnih enot izvedejo oceno skladnosti iz člena 8 Direktive 2009/125/ES, in sicer z notranjim nadzorom snovanja iz Priloge IV k navedeni direktivi ali s sistemom upravljanja iz Priloge V k navedeni direktivi.
From 1 January 2016 manufacturers, their authorised representatives and importers of NRVUs shall comply with the information requirements set out in Annex V.
Za namene ocenjevanja skladnosti SPE se izvede izračun specifične porabe energije v skladu s Prilogo VIII k tej uredbi.
Article 5
Za namene ocenjevanja skladnosti NSPE se izvedejo meritve in izračuni za posebne zahteve za okoljsko primerno zasnovo v skladu s Prilogo IX k tej uredbi.
Conformity assessment
Dosje tehnične dokumentacije, pripravljen v skladu s Prilogo IV k Direktivi 2009/125/ES, vsebuje kopijo podatkov o izdelku, navedenih v prilogah IV in V k tej uredbi.
Manufacturers of ventilation units shall carry out the conformity assessment laid down in Article 8 of Directive 2009/125/EC using the internal design control system set out in Annex IV to that Directive or the management system set out in Annex V to that Directive.
Če so bili podatki, vključeni v tehnično dokumentacijo za določen model prezračevalne enote, pridobljeni z izračunom na podlagi načrta in/ali ekstrapolacije iz drugih prezračevalnih enot, tehnična dokumentacija vsebuje naslednje podatke:
For the purposes of the conformity assessment of RVUs, calculation of the specific energy consumption requirement shall be carried out in accordance with Annex VIII to this Regulation.
podrobnosti o takih izračunih in/ali ekstrapolacijah;
For the purposes of the conformity assessment of NRVUs, measurements and calculations for the specific ecodesign requirements shall be carried out in accordance with Annex IX to this Regulation.
podrobnosti o preskusih, ki jih je izvedel proizvajalec za preverjanje točnosti izračunov in ekstrapolacij;
The technical documentation file compiled in accordance with Annex IV to Directive 2009/125/EC shall contain a copy of the product information set out in Annexes IV and V to this Regulation.
seznam vseh drugih modelov prezračevalnih enot, pri katerih so bili podatki, vključeni v tehnično dokumentacijo, pridobljeni na enak način;
Where the information included in the technical documentation for a particular ventilation unit model has been obtained by calculation on the basis of design, or extrapolation from other ventilation units, or both, the technical documentation shall include the following information:
seznam enakovrednih modelov prezračevalnih enot.
details of such calculations or extrapolations, or both;
Člen 6
details of tests undertaken by manufacturers to verify the accuracy of the calculations and extrapolations;
Postopek preverjanja za namene tržnega nadzora
a list of any other ventilation unit models where the information included in the technical documentation was obtained on the same basis;
Pri izvajanju tržnega nadzora iz člena 3(2) Direktive 2009/125/ES za zagotavljanje skladnosti z zahtevami za SPE iz Priloge II k tej uredbi in zahtevami za NSPE iz Priloge III k tej uredbi uporabljajo organi držav članic postopek preverjanja, ki je opisan v Prilogi VI.
a list of equivalent ventilation unit models.
Člen 7
Article 6
Ciljne vrednosti
Verification procedure for market surveillance purposes
Ciljne vrednosti iz točke 2 dela 3 Priloge I k Direktivi 2009/125/ES, ki se uporabijo za prezračevalne enote, so navedene v Prilogi VII k tej uredbi.
The authorities of the Member States shall apply the verification procedure set out in Annex VI when performing the market surveillance referred to in Article 3(2) of Directive 2009/125/EC to ensure compliance with the requirements set out for RVUs in Annex II to this Regulation and for NRVUs in Annex III to this Regulation.
Člen 8
Article 7
Pregled
Benchmarks
Komisija oceni potrebo po določitvi zahtev za stopnje puščanja zraka z vidika tehnološkega napredka in rezultate te ocene predstavi Posvetovalnemu forumu najpozneje do 1. januarja 2017.
The benchmarks referred to in point (2) of Part 3 of Annex I to Directive 2009/125/EC, which are to be applied to ventilation units, are set out in Annex VII to this Regulation.
Komisija to uredbo pregleda z vidika tehnološkega napredka in rezultate tega pregleda predstavi Posvetovalnemu forumu najpozneje do 1. januarja 2020.
Article 8
Pregled vsebuje naslednje ocene:
Review
morebitno razširitev področja uporabe te uredbe na enosmerne enote z električno vhodno močjo, manjšo od 30 W, in dvosmerne enote s skupno električno vhodno močjo za ventilatorje, manjšo od 30 W na tok zraka;
The Commission shall assess the need to set requirements on air leakage rates in the light of technological progress and present the results of this assessment to the Consultation Forum no later than 1 January 2017.
dovoljena odstopanja pri preverjanju iz Priloge VI;
The Commission shall review this Regulation in the light of technological progress and present the results of this review to the Consultation Forum no later than 1 January 2020.
ustreznost upoštevanja učinkov filtrov z nizko porabo energije na energijsko učinkovitost;
The review shall include an assessment of the following:
potrebo za določitev nadaljnjih stopenj s poostrenimi zahtevami za okoljsko primerno zasnovo.
the possible extension of the scope of this Regulation to cover unidirectional units with an electric power input of less than 30 W, and bidirectional units, with a total electric power input for the fans of less than 30 W per air stream;
Člen 9
the verification tolerances set out in Annex VI;
Začetek veljavnosti
the appropriateness of taking into account the effects of low-energy consuming filters on the energy efficiency;
Ta uredba začne veljati dvajseti dan po objavi v Uradnem listu Evropske unije.
the need to set a further tier with tightened ecodesign requirements.
Ta uredba je v celoti zavezujoča in se neposredno uporablja v vseh državah članicah.
Article 9
V Bruslju, 7. julija 2014
This Regulation shall be binding in its entirety and directly applicable in all Member States.
UL L 285, 31.10.2009, str. 10.
Done at Brussels, 7 July 2014.
Uredba Komisije (EU) št. 327/2011 z dne 30. marca 2011 o izvajanju Direktive 2009/125/ES Evropskega parlamenta in Sveta glede zahtev za okoljsko primerno zasnovo ventilatorjev, ki jih poganjajo motorji z električno vhodno močjo med 125 W in 500 kW (UL L 90, 6.4.2011, str. 8).
For the Commission
Delegirana uredba Komisije (EU) št. 1254/2014 z dne 11. julija 2014 o dopolnitvi Direktive 2010/30/EU Evropskega parlamenta in Sveta v zvezi z energijskim označevanjem stanovanjskih prezračevalnih enot (glej stran 27 tega Uradnega lista).
The President
Uredba (EU) št. 1025/2012 Evropskega parlamenta in Sveta z dne 25. oktobra 2012 o evropski standardizaciji (UL L 316, 14.11.2012, str. 12).
OJ L 285, 31.10.2009, p. 10.
Direktiva Evropskega parlamenta in Sveta 94/9/ES z dne 23. marca 1994 o približevanju zakonodaje držav članic v zvezi z opremo in zaščitnimi sistemi, namenjenimi za uporabo v potencialno eksplozivnih atmosferah (UL L 100, 19.4.1994, str. 1).
Commission Regulation (EU) No 327/2011 of 30 March 2011 implementing Directive 2009/125/EC of the European Parliament and of the Council with regard to ecodesign requirements for fans driven by motors with an electric input power between 125 W and 500 kW (OJ L 90, 6.4.2011, p. 8).
Uredba (EU) št. 305/2011 Evropskega parlamenta in Sveta z dne 9. marca 2011 o določitvi usklajenih pogojev za trženje gradbenih proizvodov in razveljavitvi Direktive Sveta 89/106/EGS (UL L 88, 4.4.2011, str. 5).
Commission Delegated Regulation (EU) No 1254/2014 of 11 July 2014 supplementing Directive 2010/30/EU of the European Parliament and of the Council with regard to energy labelling of residential ventilation units (see page 27 of this Official Journal).
Uredba Komisije (EU) št. 66/2014 z dne 14. januarja 2014 o izvajanju Direktive 2009/125/ES Evropskega parlamenta in Sveta glede zahtev za okoljsko primerno zasnovo gospodinjskih pečic, kuhalnih plošč in kuhinjskih nap (UL L 29, 31.1.2014, str.
Directive 94/9/EC of the European Parliament and of the Council of 23 March 1994 on the approximation of the laws of the Member States concerning equipment and protective systems intended for use in potentially explosive atmospheres (OJ L 100, 19.4.1994, p. 1).
PRILOGA I
Regulation (EU) No 305/2011 of the European Parliament and of the Council of 9 March 2011 laying down harmonised conditions for the marketing of construction products and repealing Council Directive 89/106/EEC (OJ L 88, 4.4.2011, p. 5).
Opredelitve pojmov veljajo za namene prilog II do IX k tej uredbi:
Commission Regulation (EU) No 66/2014 of 14 January 2014 implementing Directive 2009/125/EC of the European Parliament and of the Council with regard to ecodesign requirements for domestic ovens, hobs and range hoods (OJ L 29, 31.1.2014, p.
Opredelitve pojmov:
33).
„specifična poraba energije (SEC)“ (izražena v kWh/(m2.a)) pomeni koeficient za izražanje energije, porabljene za prezračevanje na m2 ogrevane talne bivalne ali nebivalne površine, izračunane za SPE v skladu s Prilogo VIII;
ANNEX I
„nivo zvokovne moči (LWA)“ pomeni A-vrednoten nivo zvokovne moči ohišja, izražen v decibelih (dB), glede na zvokovno moč enega pikovata (1 pW), ki ga prenaša zrak z referenčnim zračnim tokom;
Definitions applicable for the purposes of Annexes II to IX to this Regulation:
„večhitrostni pogon“ pomeni motor ventilatorja, ki lahko deluje s tremi določenimi hitrostmi ali več, vključno z ničelno („izključeno“);
Definitions:
„pogon s spremenljivo hitrostjo (VSD)“ pomeni elektronski regulator, ki je integriran ali deluje kot en sistem ali pa je ločeno priložen motorju in ventilatorju ter nenehno prilagaja električno moč, ki napaja motor, z namenom reguliranja stopnje pretoka;
‘specific energy consumption (SEC)’ (expressed in kWh/(m2.a)) means a coefficient to express the energy consumed for ventilation per m2 heated floor area of a dwelling or building, calculated for RVUs in accordance with Annex VIII;
„sistem za rekuperacijo toplote (HRS)“ pomeni del dvosmerne prezračevalne enote, opremljene z izmenjevalnikom toplote, ki je zasnovan za transfer toplote iz (onesnaženega) odvodnega zraka v (sveži) dovodni zrak;
‘sound power level (LWA)’ means the casing-radiated A-weighted sound power level expressed in decibels (dB) with reference to the sound power of one picowatt (1pW), transmitted by the air at reference airflow;
„toplotni izkoristek stanovanjskega HRS (ηt)“ pomeni razmerje med pridobljeno temperaturo dovodnega zraka in izgubljeno temperaturo odvodnega zraka, ki sta odvisni od zunanje temperature, merjeno v suhih pogojih sistema HRS in običajnih pogojih zraka z uravnoteženim masnim pretokom, pri referenčni stopnji pretoka, ter razliko med notranjo in zunanjo temperaturo 13 K ter brez korekcije za pridobljeno toploto od motorjev ventilatorja;
‘multi-speed drive’ means a fan motor that can be operated at three or more fixed speeds plus zero (‘off’);
„stopnja notranjega puščanja“ pomeni delež odvodnega zraka v dovodnem zraku prezračevalnih enot s sistemom HRS, ki je posledica puščanja med odvodnim in dovodnim zračnim tokom v ohišju, ko enota deluje z referenčnim pretokom zraka, merjenim v kanalih;
‘variable speed drive (VSD)’ means an electronic controller, integrated or functioning as one system or as a separate delivery with the motor and the fan, which continuously adapts the electrical power supplied to the motor in order to control the flow rate;
preskus za SPE se opravi pri 100 Pa in za NSPE pri 250 Pa;
‘heat recovery system (HRS)’ means the part of a bidirectional ventilation unit equipped with a heat exchanger designed to transfer the heat contained in the (contaminated) exhaust air to the (fresh) supply air;
„prenos“ pomeni odstotek odvodnega zraka, ki se glede na referenčni pretok vrne v dovodni zrak za regenerativni izmenjevalnik toplote;
‘thermal efficiency of a residential HRS (ηt)’ means the ratio between supply air temperature gain and exhaust air temperature loss, both relative to the outdoor temperature, measured under dry conditions of the HRS, and standard air conditions, with balanced mass flow, at reference flow rate, an indoor-outdoor temperature difference of 13 K, no correction for thermal heat gain from fan motors;
„stopnja zunanjega puščanja“ pomeni delež puščanja referenčnega pretoka zraka iz ohišja enote v okoliški zrak ali obratno, pri tlačnem preskusu;
‘internal leakage rate’ means the fraction of extract air present in the supply air of ventilation units with HRS as a result of leakage between extract and supply airflows inside the casing when the unit is operated at reference air volume flow, measured at the ducts;
preskus za SPE se opravi pri 250 Pa in za NSPE pri 400 Pa, pri podtlaku in nadtlaku;
the test shall be performed for RVUs at 100 Pa, and for NRVUs at 250 Pa;
„mešanje“ pomeni neposredno vračanje ali kratek stik zračnih tokov med odprtinami za izpuh in zajem zraka pri notranjih in zunanjih priključkih, zaradi česar ne prispevajo k učinkovitemu prezračevanju prostorov v stavbi, ko enota deluje z referenčno stopnjo pretoka zraka;
‘carry over’ means the percentage of the exhaust air which is returned to the supply air for a regenerative heat exchanger according to the reference flow;
„stopnja mešanja“ pomeni delež odvodnega zračnega toka, ki je del skupnega referenčnega pretoka zraka, ki se vrača v obtok med odprtinami za odvod in zajem zraka pri notranjih in zunanjih priključkih, zaradi česar ne prispeva k učinkovitemu prezračevanju prostorov v stavbi, ko enota deluje z referenčnim pretokom zraka (merjenim na razdalji 1 m od notranjega dovodnega kanala), od katerega se odšteje stopnja notranjega puščanja;
‘external leakage rate’ means the leakage fraction of the reference air volume flow to or from the inside of the casing of a unit to or from the surrounding air when it is subjected to a pressure test;
„efektivna vhodna moč“ (izražena v W) pomeni električno vhodno moč pri referenčni stopnji pretoka in ustrezni zunanji skupni tlačni razliki ter vključuje električne potrebe ventilatorjev, krmilja (vključno z daljinskimi upravljalniki) in toplotne črpalke (če je vgrajena);
the test shall be performed at 250 Pa for RVUs and at 400 Pa for NRVUs, for both under and over pressure;
„specifična vhodna moč (SPI)“ (izražena v W/(m3/h)) pomeni razmerje med efektivno vhodno močjo (v W) in referenčno stopnjo pretoka (v m3/h);
‘mixing’ means the immediate recirculation or short-circuiting of airflows between discharge and intake ports at both the indoor and outdoor terminals so that they do not contribute to the effective ventilation of a building space, when the unit is operated at reference air volume rate;
„diagram stopnja pretoka/tlak“ pomeni sklop krivulj, ki prikazujejo stopnjo pretoka (vodoravna os) in tlačno razliko v enosmerni SPE ali dovodni strani dvosmerne SPE, kjer vsaka krivulja predstavlja eno hitrost ventilatorja z vsaj osmimi enako oddaljenimi točkami preskusa, število krivulj pa je podano s številom ločenih možnosti za hitrost ventilatorja (ena, dve ali tri) ali pa, v primeru pogona ventilatorja s spremenljivo hitrostjo, vključuje vsaj najmanjšo, največjo in ustrezno srednjo krivuljo, ki je blizu referenčnemu pretoku zraka, in tlačno razliko za preskušanje SPI;
‘mixing rate’ means the fraction of extract airflow, as part of the total reference air volume, that recirculates between discharge and intake ports at both the indoor and outdoor terminals and thus does not contribute to the effective ventilation of a building space, when the unit is operated at reference air volume (measured at 1 m distance from the indoor supply duct), less the internal leakage rate;
„referenčna stopnja pretoka“ (izražena v m3/s) pomeni vrednost na abscisni osi do točke na krivulji diagrama stopnja pretoka/tlak, ki je na referenčni točki ali najbliže referenčni točki na 70 % vsaj največje stopnje pretoka in 50 Pa za enote s kanalskim razvodom ter na najnižjem tlaku za enote brez kanalskega razvoda.
‘effective power input’ (expressed in W) means the electric power input at reference flow rate and corresponding external total pressure difference and includes the electrical demand for fans, controls (including remote controls) and the heat pump (if integrated);
Pri dvosmernih prezračevalnih enotah se referenčna stopnja pretoka zraka nanaša na izhod odvodnega zraka;
‘specific power input (SPI)’ (expressed in W/(m3/h)) means the ratio between the effective power input (in W) and the reference flow rate (in m3/h);
„regulacijski faktor (CTRL)“ pomeni korekcijski faktor za izračun SEC glede na vrsto krmiljenja, ki je del prezračevalne enote v skladu z opisom iz tabele 1 v Prilogi VIII;
‘flow rate/pressure diagram’ means a set of curves for flow rate (horizontal axis) and pressure difference of a unidirectional RVU or the supply side of a bidirectional RVU, where each curve represents one fan speed with at least eight equidistant test-points and the number of curves is given by the number of discrete fan speed options (one, two or three) or, in the case of a variable fan speed drive, includes at least a minimum, maximum and appropriate intermediate curve close to the reference air volume and pressure difference for SPI testing;
„regulacijski parameter“ pomeni izmerljiv parameter ali skupino izmerljivih parametrov, ki naj bi bili reprezentativni za potrebe po prezračevanju, na primer stopnjo relativne vlažnosti (RV), ogljikov dioksid (CO2), hlapne organske spojine (HOS) ali druge pline, zaznavanje prisotnosti, gibanja ali zasedenosti na podlagi infrardeče telesne toplote ali odboja ultrazvočnih valov, električnih signalov zaradi človekovega upravljanja luči ali opreme;
‘reference flow rate’ (expressed in m3/s) is the abscissa value to a point on a curve in the flow rate/pressure diagram which is on or closest to a reference point at 70 % at least of the maximum flow rate and 50 Pa for ducted units and at a minimum pressure for non-ducted units.
„ročna regulacija“ pomeni vsako vrsto regulacije, ki ni regulacija glede na potrebo;