natgillin/translations-raw huggingface dataset:
the installations of restoration service providers connected to their distribution systems; and
Osim mjera navedenih u člancima od 18. do 21., svaki OPS može utvrditi količinu netirane potrošnje koju OPS treba ručno isključiti, izravno ili neizravno putem ODS-ova, ako je to nužno za sprečavanje širenja ili pogoršavanja poremećenog pogona.
By 18 December 2018 each TSO shall notify the SGUs identified pursuant to Article 23(4) and restoration service providers directly connected to its transmission system of the measures that are to be implemented on their installations, including the deadlines for implementation pursuant to point (g) of Article 23(4).
Ako se potrošnja izravno isključuje, OPS bez odgađanja obavješćuje relevantne ODS-ove.
When provided for in national legislation, the TSO shall notify directly the SGUs identified pursuant to Article 23(4) and restoration service providers and DSOs connected to distribution systems and shall inform the concerned DSO of this notification.
OPS aktivira plan hitnog rasterećenja netirane potrošnje iz stavka 1. kako bi:
Where a TSO notifies a DSO in accordance with paragraph 2, the DSO shall notify in turn, without delay, the SGUs, restoration service providers and DSOs connected to its distribution system of the measures of the restoration plan which they have to implement on their respective installations, including the deadlines for implementation, pursuant to point (g) of Article 23(4).
riješio situacije preopterećenja ili podnapona ili
Each notified DSO, SGUs and restoration service provider shall:
riješio situacije u kojima je zatražena pomoć u pogledu djelatne snage u skladu s člankom 21., ali je nedostatna da bi se u njegovu regulacijskom području održala dostatnost za razdoblje dan unaprijed ili za unutardnevno razdoblje u skladu s člankom 107.
implement the measures notified no later than 12 months from the date of notification;
Uredbe (EU) 2017/1485, što dovodi do rizika pogoršavanja frekvencije u sinkronom području.
confirm the implementation of the measures to the notifying system operator, who shall, when different from the TSO, notify the TSO; and
OPS obavješćuje ODS-ove o količini netirane potrošnje utvrđenoj u skladu sa stavkom 1. koju se treba isključiti na njihovim distribucijskim sustavima.
Article 25
Svaki ODS bez nepotrebnog odgađanja isključuje količinu netirane potrošnje navedenu u zahtjevu.
Activation of the restoration plan
U roku od 30 dana od incidenta OPS mora sastaviti izvješće koje sadržava detaljno obrazloženje, opis provedbe mjere i učinke te mjere te ga podnijeti mjerodavnom regulatornom tijelu u skladu s člankom 37.
Each TSO shall activate the procedures of its restoration plan in coordination with the DSOs and SGUs identified pursuant to Article 23(4) and with restoration service providers in the following cases:
Direktive 2009/72/EZ.
when the system is in the emergency state in accordance with the criteria in Article 18(3) of Regulation (EU) 2017/1485, once the system is stabilised following activation of the measures of the system defence plan; or
POGLAVLJE III.
when the system is in the blackout state in accordance with the criteria in Article 18(4) of Regulation (EU) 2017/1485.
PLAN PONOVNE USPOSTAVE SUSTAVA
During system restoration, each TSO shall identify and monitor:
Članak 23.
the extent and borders of the synchronised region or synchronised regions to which its control area belongs;
Izrada plana ponovne uspostave sustava
the TSOs with which it shares a synchronised region or synchronised regions; and
Do 18. prosinca 2018. svaki OPS mora izraditi plan ponovne uspostave sustava u dogovoru s relevantnim ODS-ovima, ZKM-ovima, nacionalnim regulatornim tijelima ili subjektima iz članka 4. stavka 3., susjednim OPS-ovima i ostalim OPS-ovima na tom sinkronom području.
the available active power reserves in its control area.
Pri izradi plana ponovne uspostave sustava svaki OPS mora uzeti u obzir barem sljedeće elemente:
Each DSO and SGU identified pursuant to Article 23(4), as well as each restoration service provider shall execute without undue delay the restoration plan instructions issued by the TSO, pursuant to point (b) of Article 23(3) in accordance with the restoration plan procedures.
ponašanje i sposobnosti opterećenja i proizvodnje;
Each TSO shall activate those procedures of its restoration plan that have a significant cross-border impact in coordination with the impacted TSOs.
posebne potrebe ZKM-ova visokog prioriteta navedenih u stavku 4. i
Re-energisation
karakteristike svoje mreže i povezanih mreža ODS-ova.
Article 26
Plan ponovne uspostave sustava mora sadržavati barem sljedeće odredbe:
Re-energisation procedure
uvjete pod kojima se aktivira plan ponovne uspostave sustava, kako su propisani u članku 25.;
The re-energisation procedure of the restoration plan shall contain a set of measures allowing the TSO to apply:
naloge iz plana ponovne uspostave sustava koje OPS treba izdati i
a top-down re-energisation strategy; and
mjere koje podliježu dogovoru ili koordinaciji u stvarnom vremenu s utvrđenim stranama.
a bottom-up re-energisation strategy.
Konkretno, plan ponovne uspostave sustava mora sadržavati sljedeće elemente:
Regarding the bottom-up re-energisation strategy, the re-energisation procedure shall contain at least measures for:
popis ZKM-ova odgovornih za provedbu mjera na svojim postrojenjima koje proizlaze iz obveznih zahtjeva iz uredaba (EU) 2016/631, (EU) 2016/1388 i (EU) 2016/1447 ili nacionalnog zakonodavstva i popis mjera koje moraju provesti ti ZKM-ovi;
managing voltage and frequency deviations due to re-energisation;
popis ZKM-ova visokog prioriteta te uvjeta za njihovo isključenje i ponovno stavljanje pod napon;
monitoring and managing island operation; and
popis stanica koje su ključne za postupke njegova plana ponovne uspostave sustava;
resynchronising island operation areas.
broj izvora energije u OPS-ovom regulacijskom području nužnih za ponovno stavljanje njegova sustava pod napon u skladu sa strategijom za ponovno stavljanje pod napon koja uključuje i sposobnost crnog starta, sposobnost brzog ponovnog stavljanja pod napon (u radu na vlastitu potrošnju) i sposobnost otočnog pogona i
Article 27
rokove primjene svih navedenih mjera.
Activation of the re-energisation procedure
Plan ponovne uspostave sustava mora uključivati barem sljedeće tehničke i organizacijske mjere navedene u Poglavlju III:
When activating the re-energisation procedure, each TSO shall set up the strategy to be applied, taking into account:
postupak za ponovno stavljanje pod napon u skladu s Odjeljkom 2.;
the availability of power sources capable of re-energisation in its control area;
postupak za upravljanje frekvencijom u skladu s Odjeljkom 3. i
the expected duration and risks of possible re-energisation strategies;
postupak za resinkronizaciju u skladu s Odjeljkom 4.
the conditions of the power systems;
Mjere uključene u plan ponovne uspostave sustava moraju ispunjavati sljedeće uvjete:
the conditions of the directly connected systems, including at least the status of interconnectors;
njihov utjecaj na korisnike sustava mora biti najmanji mogući;
the high priority significant grid users listed pursuant to Article 23(4); and
tim se mjerama ne smije uzrokovati prelazak međusobno povezanih prijenosnih sustava u poremećeni pogon ili raspad sustava.
the possibility to combine top-down and bottom-up re-energisation strategies.
Članak 24.
When applying a top-down re-energisation strategy, each TSO shall manage the connection of load and generation with the aim to regulate the frequency towards the nominal frequency with a maximum tolerance of the maximum steady-state frequency deviation.
Provedba plana ponovne uspostave sustava
Each TSO shall apply the conditions for connection of load and generation defined by the frequency leader, where appointed in accordance with Article 29.
Do 18. prosinca 2019. svaki OPS mora provesti mjere plana ponovne uspostave sustava koje je potrebno provesti na prijenosnom sustavu.
When applying a bottom-up re-energisation strategy, each TSO shall manage the connection of load and generation with the aim to regulate the frequency towards the target frequency established in accordance with point (c) of Article 28(3).
postrojenjima ODS-ova u skladu s člankom 23. stavkom 4. i
During re-energisation, the TSO shall, after consultation with DSOs, establish and notify the amount of netted demand to be reconnected on distribution networks.
postrojenjima ZKM-ova utvrđenih u skladu s člankom 23. stavkom 4. priključenima na njihove distribucijske sustave i
Each DSO shall reconnect the notified amount of netted demand, while respecting the block loading and taking into account the automatic re-connection of load and generation in its network.
postrojenjima pružatelja usluge uravnoteženja sustava priključenima na njihove distribucijske sustave i
Each TSO shall inform its neighbouring TSOs on its capability to support a top-down re-energisation strategy.
Do 18. prosinca 2018. svaki OPS mora obavijestiti ZKM-ove utvrđene u skladu s člankom 23. stavkom 4. i pružatelje usluge ponovne uspostave sustava izravno priključene na njegov prijenosni sustav o mjerama koje je potrebno provesti na njihovim postrojenjima, uključujući rokove za njihovu provedbu u skladu s člankom 23. stavkom 4. točkom (g).
For the activation of a top-down re-energisation strategy, the TSO shall request neighbouring TSOs to support the re-energisation.
Ako je to predviđeno nacionalnim zakonodavstvom, OPS mora izravno obavijestiti ZKM-ove utvrđene u skladu s člankom 23. stavkom 4. i pružatelje usluge ponovne uspostave sustava i ODS-ove priključene na distribucijske sustave te o toj obavijesti izvijestiti predmetni ODS.
This support may consist in assistance for active power, in accordance with paragraphs 3 to 5 of Article 21.
Ako OPS obavijesti ODS-a u skladu sa stavkom 2., ODS bez nepotrebnog odgađanja obavješćuje ZKM-ove, pružatelje usluge ponovne uspostave sustava i ODS-ove priključene na njegov distribucijski sustav o mjerama plana ponovne uspostave sustava koje moraju provesti na svojim pojedinačnim postrojenjima, uključujući rokove za njihovu provedbu u skladu s člankom 23. stavkom 4. točkom (g).
The requested TSOs shall provide assistance for the re-energisation, unless it would lead their systems to the emergency or blackout states.
Svaki obaviješteni ODS, ZKM i pružatelj usluge ponovne uspostave sustava dužan je:
In this case, the requesting TSO shall use the bottom-up re-energisation strategy.
primijeniti upućene mjere u roku od najviše 12 mjeseci od datuma zaprimanja;
SECTION 3
potvrditi provedbu mjera operatoru sustava koji je zatražio njihovu provedbu koji zatim, ako to nije OPS, informira o tome OPS-a i
Frequency management
Članak 25.
Article 28
Aktiviranje plana ponovne uspostave
Frequency management procedure
Svaki OPS aktivira postupke svojeg plana ponovne uspostave sustava u koordinaciji s ODS-ovima i ZKM-ovima utvrđenim u skladu s člankom 23. stavkom 4. te s pružateljima usluge ponovne uspostave sustava, u sljedećim slučajevima:
The frequency management procedure of the restoration plan shall contain a set of measures aiming at restoring system frequency back to the nominal frequency.
ako je sustav u poremećenom pogonu u skladu s kriterijima iz članka 18. stavka 3.
Each TSO shall activate its frequency management procedure:
Uredbe (EU) 2017/1485 nakon što je sustav stabiliziran nakon aktiviranja mjera plana obrane sustava ili
in preparation of the resynchronisation procedure, when a synchronous area is split in several synchronised regions;
ako je sustav u stanju raspada u skladu s kriterijima u članku 18. stavku 4.
in case of frequency deviation in the synchronous area; or
Uredbe (EU) 2017/1485.
in case of re-energisation.
Tijekom ponovne uspostave sustava, svaki OPS utvrđuje i nadzire:
The frequency management procedure shall include at least:
i. opsegu i granicama sinkronizirane regije ili sinkroniziranih regija kojima njegovo regulacijsko područje pripada;
a list of actions regarding the setting of the load-frequency controller before the appointment of frequency leaders;
OPS-ove s kojima dijeli sinkroniziranu regiju ili sinkronizirane regije i
the appointment of frequency leaders;
raspoložive rezerve djelatne snage u svojem regulacijskom području.
the establishment of target frequency in case of bottom-up re-energisation strategy;
Svaki ODS i ZKM utvrđen u skladu s člankom 23. stavkom 4. te svaki pružatelj usluge ponovne uspostave sustava mora bez nepotrebnog odgađanja provesti naloge iz plana ponovne uspostave sustava koje je OPS izdao u skladu s člankom 23. stavkom 3. točkom (b) u skladu s postupcima plana ponovne uspostave sustava.
frequency management after frequency deviation; and
Ako postupci njegova plana obrane sustava imaju znatan prekogranični utjecaj, OPS aktivira te postupke u koordinaciji sa zahvaćenim OPS-ovima.
frequency management after synchronous area split.
Ponovno stavljanje pod napon
the determination of the amount of load and generation to be reconnected, taking into account the available active power reserves within the synchronised region in order to avoid major frequency deviations.
Članak 26.
Article 29
Postupak za ponovno stavljanje pod napon
Appointment of a frequency leader
Postupak za ponovno stavljanje pod napon u planu obrane sustava sadržava skup mjera kojima se OPS-u omogućuje primjena:
During system restoration, when a synchronous area is split in several synchronised regions, the TSOs of each synchronised region shall appoint a frequency leader, in accordance with paragraph 3.
strategije za ponovno stavljanje pod napon odozgo prema dolje i
During system restoration, when a synchronous area is not split but the system frequency exceeds the frequency limits for the alert state as defined in Article 18(2) of Regulation (EU) 2017/1485, all TSOs of the synchronous area shall appoint a frequency leader, in accordance with paragraph 3.
strategije za ponovno stavljanje pod napon odozdo prema gore.
The TSO with the highest real-time estimated K-factor shall be appointed as the frequency leader, unless the TSOs of the synchronised region, or of the synchronous area, agree to appoint another TSO as the frequency leader.
Kad je riječ o strategiji za ponovno stavljanje pod napon odozdo prema gore, postupak za ponovno stavljanje pod napon sadržava barem sljedeće:
In that case, the TSOs of the synchronised region, or of the synchronous area, shall consider the following criteria:
upravljanje odstupanjima napona i frekvencije nastalim zbog ponovnog stavljanja pod napon;
the amount of available active power reserves and especially frequency restoration reserves;
praćenje otočnog pogona i upravljanje njime i
the capacities available on interconnectors;
resinkronizaciju područja otočnog pogona.
the availability of frequency measurements of TSOs of the synchronised region or of the synchronous area; and
Članak 27.
the availability of measurements on critical elements within the synchronised region or the synchronous area.
Aktiviranje postupka za ponovno stavljanje pod napon
Notwithstanding paragraph 3, where the size of the synchronous area concerned and the real time situation allow it, the TSOs of the synchronous area may appoint a predetermined frequency leader.
Pri aktiviranju postupka za ponovno stavljanje pod napon, svaki OPS priprema strategiju koju treba primijeniti, uzimajući u obzir:
The TSO appointed as frequency leader pursuant to paragraphs 1 and 2 shall inform the other TSOs of the synchronous area of its appointment without delay.
raspoloživost izvora energije u njegovu regulacijskom području sposobnih za provedbu ponovnog stavljanja pod napon;
The appointed frequency leader shall act as such until:
očekivano trajanje i rizike mogućih strategija ponovnog stavljanja pod napon;
another frequency leader is appointed for its synchronised region;
stanja elektroenergetskih sustava;
a new frequency leader is appointed as the result of resynchronisation of its synchronised region with another synchronised region; or
stanja izravno priključenih sustava, uključujući barem stanja interkonekcijskih vodova;
the synchronous area has been completely resynchronised, the system frequency is within the standard frequency range and the LFC operated by each TSO of the synchronous area is back to its normal operating mode in accordance with Article 18(1) of Regulation (EU) 2017/1485.
popis ZKM-ova visokog prioriteta u skladu s člankom 23. stavkom 4. i
Article 30
mogućnost kombiniranja strategija za ponovno stavljanje pod napon odozgo prema dolje i odozdo prema gore.
Frequency management after frequency deviation
Pri primjeni strategije za ponovno stavljanje pod napon odozgo prema dolje svaki OPS upravlja priključenjem opterećenja i proizvodnje u cilju reguliranja frekvencije prema razini nazivne frekvencije s najvećom tolerancijom maksimalnog odstupanja frekvencije u stacionarnom stanju.
During system restoration, when a frequency leader has been appointed pursuant to Article 29(3), the TSOs of the synchronous area, other than the frequency leader, shall as a first measure suspend the manual activation of frequency restoration reserves and replacement reserves.
Svaki OPS primjenjuje uvjete za priključenje opterećenja i proizvodnje koje je utvrdio voditelj frekvencije, kada je imenovan u skladu s člankom 29.
The frequency leader shall establish, after consultation with the other TSOs of the synchronous area, the operating mode to be applied on the LFC operated by each TSO of the synchronous area.
Pri primjeni strategije za ponovno stavljanje pod napon odozdo prema gore svaki OPS upravlja priključenjem opterećenja i proizvodnje u cilju reguliranja frekvencije prema razini ciljane frekvencije definirane u skladu s člankom 28. stavkom 3. točkom (c).
The frequency leader shall manage the manual activation of frequency restoration reserves and replacement reserves within the synchronous area, aiming at regulating the frequency of the synchronous area towards the nominal frequency and taking into account the operational security limits defined pursuant to Article 25 of Regulation (EU) 2017/1485.
Tijekom ponovnog stavljanja pod napon OPS nakon savjetovanja s ODS-ovima određuje količinu netirane potrošnje koju treba ponovno priključiti na distribucijske mreže te obavješćuje o toj količini.
Upon request, each TSO of the synchronous area shall support the frequency leader.
Svaki ODS ponovno priključuje naloženu količinu netirane potrošnje istodobno se pridržavajući ograničenja opterećenja bloka i uzimajući u obzir automatsko ponovno priključivanje opterećenja i proizvodnje u svojoj mreži.
Article 31
Svaki OPS obavješćuje susjedne OPS-ove o svojoj sposobnosti za potporu strategiji za ponovno stavljanje pod napon odozgo prema dolje.
Frequency management after synchronous area split
Za aktiviranje strategije za ponovno stavljanje pod napon odozgo prema dolje, OPS traži od susjednih OPS-ova pomoć za ponovno stavljanje pod napon.
During system restoration, when a frequency leader has been appointed pursuant to Article 29(3), the TSOs of each synchronised region, with the exception of the frequency leader, shall as a first measure suspend the manual activation of frequency restoration reserves and replacement reserves.
Ta pomoć može uključivati pomoć u pogledu djelatne snage u skladu s člankom 21. stavcima od 3. do 5.
The frequency leader shall establish, after consultation with the other TSOs of the synchronised region, the operating mode to be applied on the LFC operated by each TSO of the synchronised region.
OPS-ovi kojima je upućen zahtjev pružaju pomoć u pogledu ponovnog stavljanja pod napon, osim ako bi to uzrokovalo poremećeni pogon ili raspad sustava.
The frequency leader shall manage the manual activation of frequency restoration reserves and replacement reserves within the synchronised region, aiming at regulating the frequency of the synchronised region towards the target frequency established by the resynchronisation leader, if any, pursuant to point (a) of Article 34(1) and taking into account the operational security limits set out pursuant to Article 25 of Regulation (EU) 2017/1485.
U tom slučaju OPS koji upućuje zahtjev primjenjuje strategiju za ponovno stavljanje pod napon odozdo prema gore.
When no resynchronisation leader is appointed for the synchronised region, the frequency leader shall aim at regulating the frequency towards the nominal frequency.
ODJELJAK 3.
Upon request, each TSO of the synchronised region shall support the frequency leader.
Upravljanje frekvencijom
SECTION 4
Članak 28.
Resynchronisation
Postupak za upravljanje frekvencijom
Article 32
Postupak za upravljanje frekvencijom u planu obrane sustava sadržava skup mjera za ponovnu uspostavu frekvencije sustava na razinu nazivne frekvencije.
Resynchronisation procedure
Svaki OPS aktivira svoj postupak za upravljanje frekvencijom:
The resynchronisation procedure of the restoration plan shall include, at least:
kao predradnju prije resinkronizacije, kada je sinkrono područje podijeljeno na više sinkroniziranih regija;
the appointment of a resynchronisation leader;
u slučaju odstupanja frekvencije u sinkronom području ili
the measures allowing the TSO to apply a resynchronisation strategy; and
u slučaju ponovnog stavljanja pod napon.
the maximum limits for phase angle, frequency and voltage differences for connecting lines.
Postupak za upravljanje frekvencijom uključuje najmanje:
Article 33
popis mjera o uspostavljanju regulacije frekvencije i snage razmjene prije imenovanja voditelja frekvencije;
Appointment of a resynchronisation leader
imenovanje voditelja frekvencije;
During system restoration, when two synchronised regions can be resynchronised without endangering the operational security of the transmission systems, the frequency leaders of these synchronised regions shall appoint a resynchronisation leader in consultation with at least the TSO(s) identified as the potential resynchronisation leader and in accordance with paragraph 2.
utvrđivanje ciljanih frekvencija za strategiju za ponovno stavljanje pod napon odozdo prema gore;
Each frequency leader shall inform without delay the TSOs from its synchronised region of the appointed resynchronisation leader.
upravljanje frekvencijom nakon odstupanja frekvencije; i
For each pair of synchronised regions to be resynchronised, the resynchronisation leader shall be the TSO that:
upravljanje frekvencijom nakon podjele sinkronog područja i
has in operation at least one substation equipped with a parallel switching device on the border between the two synchronised regions to be resynchronised;
određivanje količine opterećenja i proizvodnje za ponovno priključivanje, uzimajući u obzir raspoložive rezerve djelatne snage u sinkroniziranoj regiji kako bi se izbjegla veća odstupanja frekvencije.
has access to the frequency measurements from both synchronised regions;
Članak 29.
has access to the voltage measurements on the substations between which potential resynchronisation points are located; and
Imenovanje voditelja frekvencije
is able to control the voltage of potential resynchronisation points.
Tijekom ponovne uspostave sustava, ako je sinkrono područje podijeljeno na više sinkroniziranih regija, voditelji frekvencije svake sinkronizirane regije imenuju voditelja frekvencije u skladu sa stavkom 3.
Where more than one TSO fulfils the criteria under paragraph 2, the TSO with the highest number of potential resynchronisation points between the two synchronised regions shall be appointed as the resynchronisation leader, unless the frequency leaders of the two synchronised regions agree to appoint another TSO as resynchronisation leader.
Tijekom ponovne uspostave sustava, ako sinkrono područje nije podijeljeno, ali frekvencija sustava premašuje granične vrijednosti frekvencije za ugroženi normalni pogon kako je definirano u članku 18. stavku 2.
The appointed resynchronisation leader shall act as such until:
Uredbe (EU) 2017/1485, svi OPS-ovi sinkronog područja imenuju voditelja frekvencije u skladu sa stavkom 3.