natgillin/translations-raw huggingface dataset:
The technique is mainly used for SOX, HCl and/or HF control
Koncept izgaranja s niskom razinom emisija NOX u dizelskim motorima
See applicability in BAT 29
Recirkulacija ispušnih plinova (EGR)
Table 16
Nije primjenjivo na četverotaktne motore.
BAT-associated emission levels (BAT-AELs) for dust emissions to air from the combustion of HFO and/or gas oil in boilers
Primjenjivo u okviru ograničenja povezanih s dostupnosti vode.
Existing plant [114]
Primjenjivost može biti ograničena zbog nepostojanja paketa za naknadnu ugradnju.
Existing plant [115]
Naknadna ugradnja u postojeće uređaje za loženje može biti ograničena dostupnošću raspoloživog prostora.
Unless otherwise stated, the BAT conclusions presented in this section are generally applicable to the combustion of HFO and/or gas oil in reciprocating engines.
NRT 33.
As regards HFO- and/or gas-oil-fired engines, secondary abatement techniques for NOX, SO2 and dust may not be applicable to engines in islands that are part of a small isolated system [118] or a micro isolated system [119], due to technical, economic and logistical/infrastructure constraints, pending their interconnection to the mainland electricity grid or access to a natural gas supply.
Za sprečavanje ili smanjenje emisija CO i hlapljivih organskih spojeva u zrak iz izgaranja HFO-a i/ili plinskog ulja u stapnim motorima NRT je upotreba jedne od tehnika navedenih u nastavku ili njihove kombinacije.
The BAT-AELs for such engines shall therefore only apply in small isolated system and micro isolated system as from 1 January 2025 for new engines, and as from 1 January 2030 for existing engines.
Oksidacijski katalizatori
BAT 31.
Primjenjivost može biti ograničena udjelom sumpora u gorivu.
In order to increase the energy efficiency of HFO and/or gas oil combustion in reciprocating engines, BAT is to use an appropriate combination of the techniques given in BAT 12 and below.
Tablica 18.
Combined cycle
Razine emisija povezane s NRT-ima za emisije NOX u zrak iz izgaranja HFO-a i/ili plinskog ulja u stapnim motorima
See description in Section 8.2
postojeći uređaj [124]
Generally applicable to new units operated ≥ 1500 h/yr.
postojeći uređaj [125] [126]
Applicable to existing units within the constraints associated with the steam cycle design and the space availability.
Za postojeće uređaje za loženje u kojima izgara samo HFO i koji rade ≥ 1500 h/god. i nove uređaje za loženje u kojima izgara samo HFO;
Not applicable to existing units operated < 1500 h/yr
indikativna vrijednost godišnje prosječne razine emisije CO općenito iznosi 50–175 mg/Nm3,
Table 17
indikativna vrijednost prosječne vrijednosti tijekom razdoblja uzorkovanja za razine emisije ukupnih HOS-ova općenito iznosi 10–40 mg/Nm3.
BAT-associated energy efficiency levels (BAT-AEELs) for the combustion of HFO and/or gas oil in reciprocating engines
NRT 34.
BAT-AEELs [120]
Za sprečavanje ili smanjenje emisija SOX, HCl i HF u zrak iz izgaranja HFO-a i/ili plinskog ulja u stapnim motorima NRT je upotreba jedne od tehnika navedenih u nastavku ili njihove kombinacije.
HFO- and/or gas-oil-fired reciprocating engine — single cycle
Vidjeti opise u odjeljku 8.4.
HFO- and/or gas-oil-fired reciprocating engine — combined cycle
Mogu postojati tehnička ograničenja kod postojećih uređaja za loženje.
No BAT-AEEL
Nije primjenjivo na uređaje za loženje koji rade < 500 h/god.
NOX, CO and volatile organic compound emissions to air
Tablica 19.
BAT 32.
Razine emisija povezane s NRT-ima za emisije SO2 u zrak iz izgaranja HFO-a i/ili plinskog ulja u stapnim motorima
In order to prevent or reduce NOX emissions to air from the combustion of HFO and/or gas oil in reciprocating engines, BAT is to use one or a combination of the techniques given below.
postojeći uređaj [128]
Low-NOX combustion concept in diesel engines
postojeći uređaj [129]
Exhaust-gas recirculation (EGR)
NRT 35.
Not applicable to four-stroke engines
Za sprečavanje ili smanjenje emisija čestica i metala vezanih na čestice u zrak iz izgaranja HFO-a i/ili plinskog ulja u stapnim motorima NRT je upotreba jedne od tehnika navedenih u nastavku ili njihove kombinacije.
Applicable within the constraints of water availability.
Vidjeti opise u odjeljku 8.5.
The applicability may be limited where no retrofit package is available
Nije primjenjivo na uređaje za loženje koji rade < 500 h/god.
Retrofitting existing combustion plants may be constrained by the availability of sufficient space
Tablica 20.
BAT 33.
Razine emisija povezane s NRT-ima za emisije čestica u zrak iz izgaranja HFO-a i/ili plinskog ulja u stapnim motorima
In order to prevent or reduce emissions of CO and volatile organic compounds to air from the combustion of HFO and/or gas oil in reciprocating engines, BAT is to use one or both of the techniques given below.
postojeći uređaj [131]
Oxidation catalysts
postojeći uređaj [132]
The applicability may be limited by the sulphur content of the fuel
Ako nije drukčije navedeno, zaključci o NRT-ima navedeni u ovom odjeljku općenito su primjenjivi na izgaranje plinskog ulja u plinskim turbinama.
Table 18
NRT 36.
BAT-associated emission levels (BAT-AELs) for NOX emissions to air from the combustion of HFO and/or gas oil in reciprocating engines
Za povećanje energetske učinkovitosti izgaranja plinskog ulja u plinskim turbinama NRT je upotreba prikladne kombinacije tehnika navedenih u NRT 12. i u nastavku.
Existing plant [124]
Vidjeti opis u odjeljku 8.2.
Existing plant [125] [126]
Tablica 21.
As an indication, for existing combustion plants burning only HFO and operated ≥ 1500 h/yr or new combustion plants burning only HFO,
Razine energetske učinkovitosti povezane s NRT-ima za izgaranje plinskog ulja u plinskim turbinama
the yearly average CO emission levels will generally be 50–175 mg/Nm3,
Razine energetske učinkovitosti povezane s NRT-ima [133]
the average over the sampling period for TVOC emission levels will generally be 10–40 mg/Nm3.
Plinska turbina otvorenog ciklusa na plinsko ulje
BAT 34.
Plinska turbina kombiniranog ciklusa na plinsko ulje
In order to prevent or reduce SOX, HCl and HF emissions to air from the combustion of HFO and/or gas oil in reciprocating engines, BAT is to use one or a combination of the techniques given below.
NRT 37.
See descriptions in Section 8.4
Za sprečavanje ili smanjenje emisija NOX u zrak iz izgaranja plinskog ulja u plinskim turbinama NRT je upotreba jedne od tehnika navedenih u nastavku ili njihove kombinacije.
There may be technical restrictions in the case of existing combustion plants
Vidjeti opis u odjeljku 8.3.
Not applicable to combustion plants operated < 500 h/yr
Primjenjivost može biti ograničena zbog dostupnosti vode.
Table 19
Primjenjivo samo na modele turbina za koje su plamenici s niskom razinom emisija NOX dostupni na tržištu.
BAT-associated emission levels (BAT-AELs) for SO2 emissions to air from the combustion of HFO and/or gas oil in reciprocating engines
NRT 38.
Existing plant [128]
Za sprečavanje ili smanjenje emisija CO u zrak iz izgaranja plinskog ulja u plinskim turbinama NRT je upotreba jedne od tehnika navedenih u nastavku ili njihove kombinacije.
Existing plant [129]
Nije primjenjivo na uređaje za loženje koji rade < 500 h/god.
BAT 35.
Indikativna vrijednost razina emisija NOX u zrak iz izgaranja plinskog ulja u plinskim turbinama s dvojnim gorivom za izvanredne (hitne) slučajeve koje rade < 500 h/god. općenito iznosi 145–250 mg/Nm3 kao dnevna srednja vrijednost ili srednja vrijednost tijekom razdoblja uzorkovanja
In order to prevent or reduce dust and particulate-bound metal emissions from the combustion of HFO and/or gas oil in reciprocating engines, BAT is to use one or a combination of the techniques given below.
Emisije SOX i čestica u zrak
See descriptions in Section 8.5
NRT 39.
Not applicable to combustion plants operated < 500 h/yr
Za sprečavanje ili smanjenje emisija SOX i čestica u zrak iz izgaranja plinskog ulja u plinskim turbinama NRT je upotreba tehnike navedene u nastavku.
Table 20
Vidjeti opis u odjeljku 8.4.
BAT-associated emission levels (BAT-AELs) for dust emissions to air from the combustion of HFO and/or gas oil in reciprocating engines
Tablica 22.
Existing plant [131]
Razine emisija povezane s NRT-ima za emisije SO2 i čestica u zrak iz izgaranja plinskog ulja u plinskim turbinama, uključujući plinske turbine s dvojnim gorivom
Existing plant [132]
Vrsta uređaja za loženje
Unless stated otherwise, the BAT conclusions presented in this section are generally applicable to the combustion of gas oil in gas turbines.
godišnja srednja vrijednost [135]
BAT 36.
dnevna srednja vrijednost ili srednja vrijednost tijekom razdoblja uzorkovanja [136]
In order to increase the energy efficiency of gas oil combustion in gas turbines, BAT is to use an appropriate combination of the techniques given in BAT 12 and below.
Novi i postojeći uređaji
See description in Section 8.2
ZAKLJUČCI O NRT-ima ZA IZGARANJE PLINOVITIH GORIVA
Table 21
Zaključci o NRT-ima za izgaranje prirodnog plina
BAT-associated energy efficiency levels (BAT-AEELs) for gas-oil-fired gas turbines
Ako nije drukčije navedeno, zaključci o NRT-ima navedeni u ovom odjeljku općenito su primjenjivi na izgaranje prirodnog plina.
BAT-AEELs [133]
Primjenjuju se uz opće zaključke o NRT-ima navedene u odjeljku 1.
Gas-oil-fired open-cycle gas turbine
NRT 40.
Gas-oil-fired combined cycle gas turbine
Za povećanje energetske učinkovitosti izgaranja prirodnog plina NRT je upotreba prikladne kombinacije tehnika navedenih u NRT 12. i u nastavku.
BAT 37.
Općenito primjenjivo na nove plinske turbine i motore osim ako rade < 1500 h/god.
In order to prevent or reduce NOX emissions to air from the combustion of gas oil in gas turbines, BAT is to use one or a combination of the techniques given below.
Primjenjivo na postojeće plinske turbine i motore u okviru ograničenja povezanih s dizajnom parnog ciklusa i raspoloživim prostorom.
See description in Section 8.3
Nije primjenjivo na postojeće plinske turbine i motore koji rade < 1500 h/god.
The applicability may be limited due to water availability
Nije primjenjivo na plinske turbine za mehaničke pogone koje rade u diskontinuiranom režimu uz veće varijacije opterećenja i česta uključivanja i isključivanja.
Only applicable to turbine models for which low-NOX burners are available on the market
Nije primjenjivo na kotlove.
BAT 38.
Tablica 23.
In order to prevent or reduce CO emissions to air from the combustion of gas oil in gas turbines, BAT is to use one or a combination of the techniques given below.
Razine energetske učinkovitosti povezane s NRT-ima za izgaranje prirodnog plina
Not applicable to combustion plants operated < 500 h/yr.
Razine energetske učinkovitosti povezane s NRT-ima [137] [138]
As an indication, the emission level for NOX emissions to air from the combustion of gas oil in dual fuel gas turbines for emergency use operated < 500 h/yr will generally be 145–250 mg/Nm3 as a daily average or average over the sampling period.
neto ukupno učinkovito iskorištavanje goriva (%) [139] [140]
SOX and dust emissions to air
neto učinkovitost mehaničke energije (%) [140] [141]
BAT 39.
Plinski motor
In order to prevent or reduce SOX and dust emissions to air from the combustion of gas oil in gas turbines, BAT is to use the technique given below.
Nema razine energetske učinkovitosti povezane s NRT-om
See description in Section 8.4
Kotao na plin
Table 22
Plinska turbina otvorenog ciklusa snage ≥ 50 MWth
BAT-associated emission levels for SO2 and dust emissions to air from the combustion of gas oil in gas turbines, including dual fuel gas turbines
Plinska turbina kombiniranog ciklusa (CCGT)
Type of combustion plant
CCGT, 50–600 MWth
Yearly average [135]
CCGT, ≥ 600 MWth
Daily average or average over the sampling period [136]
CHP CCGT, 50–600 MWth
New and existing plants
CHP CCGT, ≥ 600 MWth
BAT CONCLUSIONS FOR THE COMBUSTION OF GASEOUS FUELS
Emisije NOX, CO, NMHOS-a i CH4 u zrak
BAT conclusions for the combustion of natural gas
NRT 41.
They apply in addition to the general BAT conclusions given in Section 1.
Stupnjevani dovod zraka i/ili goriva
They do not apply to combustion plants on offshore platforms; these are covered by Section.
Vidjeti opise u odjeljku 8.3.
4.3.
Stupnjevani dovod zraka često je povezan s plamenicima s niskom razinom emisija NOX.
BAT 40.
Ova se tehnika često upotrebljava u kombinaciji s drugim tehnikama; može se upotrebljavati zasebno u uređajima za loženje koji rade < 500 h/god.
In order to increase the energy efficiency of natural gas combustion, BAT is to use an appropriate combination of the techniques given in BAT 12 and below.
Smanjenje temperature zraka za izgaranje
Generally applicable to new gas turbines and engines except when operated < 1500 h/yr.
Općenito primjenjivo u okviru ograničenja povezanih s potrebama postupka.
Applicable to existing gas turbines and engines within the constraints associated with the steam cycle design and the space availability.
Selektivna nekatalitička redukcija (SNCR)
Not applicable to existing gas turbines and engines operated < 1500 h/yr.
Nije općenito primjenjivo na uređaje za loženje snage < 100 MWth.
Not applicable to mechanical drive gas turbines operated in discontinuous mode with extended load variations and frequent start-ups and shutdowns.
NRT 42.
Not applicable to boilers
Za sprečavanje ili smanjenje emisija NOX u zrak iz izgaranja prirodnog plina u plinskim turbinama NRT je upotreba jedne od tehnika navedenih u nastavku ili njihove kombinacije.
Table 23
Suhi plamenici s niskom razinom emisija NOX (DLN)
BAT-associated energy efficiency levels (BAT-AEELs) for the combustion of natural gas
Primjenjivost može biti ograničena u slučaju turbina za koje nije dostupan paket za naknadnu ugradnju ili u koje su ugrađeni sustavi za dodavanje vode/pare.
BAT-AEELs [137] [138]
Idejno rješenje s malim opterećenjem
Net total fuel utilisation (%) [139] [140]
Prilagodba opreme za kontrolu procesa i povezane opreme kako bi se održala dobra učinkovitost izgaranja kada potražnja za energijom varira, npr. poboljšanjem kapaciteta za regulaciju dotoka zraka ili podjelom procesa izgaranja na međusobno odvojene faze izgaranja.
Net mechanical energy efficiency (%) [140] [141]
Primjenjivost može biti ograničena dizajnom plinske turbine.
Gas engine
Općenito primjenjivo na dodatno zagrijavanje za generatore pare sa sustavom za iskorištavanje otpadne topline u slučaju uređaja za loženje s plinskim turbinama s kombiniranim ciklusom.
No BAT-AEEL.
Nije primjenjivo na uređaje za loženje koji rade < 500 h/god.
Gas-fired boiler
Nije općenito primjenjivo na uređaje za loženje snage < 100 MWth.
Open cycle gas turbine, ≥ 50 MWth
Naknadna ugradnja u postojeće uređaje za loženje može biti ograničena dostupnošću raspoloživog prostora.
Combined cycle gas turbine (CCGT)
NRT 43.
CCGT, 50–600 MWth
Za sprečavanje ili smanjenje emisija NOX u zrak iz izgaranja prirodnog plina u motorima NRT je upotreba jedne od tehnika navedenih u nastavku ili njihove kombinacije.
CCGT, ≥ 600 MWth
Koncept siromašne gorive smjese
CHP CCGT, 50–600 MWth
Općenito se upotrebljava u kombinaciji sa SCR-om.
CHP CCGT, ≥ 600 MWth
Primjenjivo samo na nove plinske motore.
NOX, CO, NMVOC and CH4 emissions to air
Napredni koncept siromašne gorive smjese
BAT 41.
Primjenjivo samo na nove motore s paljenjem pomoću svjećica.
In order to prevent or reduce NOX emissions to air from the combustion of natural gas in boilers, BAT is to use one or a combination of the techniques given below.
NRT 44.
Air and/or fuel staging
Za sprečavanje ili smanjenje emisija CO u zrak iz izgaranja prirodnog plina NRT je osiguravanje optimiziranog izgaranja i/ili upotreba oksidacijskih katalizatora.
See descriptions in Section 8.3.
Vidjeti opise u odjeljku 8.3.
Air staging is often associated with low-NOX burners
Tablica 24.
This technique is often used in combination with other techniques or may be used alone for combustion plants operated < 500 h/yr
Razine emisija povezane s NRT-ima za emisije NOX u zrak iz izgaranja prirodnog plina u plinskim turbinama
Reduction of the combustion air temperature
Razine emisija povezane s NRT-ima (mg/Nm3) [143] [144]
Generally applicable within the constraints associated with the process needs
godišnja srednja vrijednost [145] [146]
Selective non–catalytic reduction (SNCR)
Plinske turbine otvorenog ciklusa (OCGT-i) [147] [148]Novi OCGT
Not generally applicable to combustion plants of < 100 MWth.
Postojeći OCGT (osim turbina koje se upotrebljavaju za mehanički pogon) – Sve osim uređaja koji rade < 500 h/god.
BAT 42.
Plinske turbine s kombiniranim ciklusom (CCGT-i) [147] [150]Novi CCGT
In order to prevent or reduce NOX emissions to air from the combustion of natural gas in gas turbines, BAT is to use one or a combination of the techniques given below.
Postojeći CCGT s neto ukupnim učinkovitim iskorištavanjem goriva od < 75 %
Dry low-NOX burners (DLN)
Postojeći CCGT s neto ukupnim učinkovitim iskorištavanjem goriva od ≥ 75 %
The applicability may be limited in the case of turbines where a retrofit package is not available or when water/steam addition systems are installed
Postojeći CCGT s neto ukupnim učinkovitim iskorištavanjem goriva od < 75 %
Low-load design concept
Postojeći CCGT s neto ukupnim učinkovitim iskorištavanjem goriva od ≥ 75 %
Adaptation of the process control and related equipment to maintain good combustion efficiency when the demand in energy varies, e.g. by improving the inlet airflow control capability or by splitting the combustion process into decoupled combustion stages
Plinske turbine s otvorenim i kombiniranim ciklusom
The applicability may be limited by the gas turbine design
Plinska turbina puštena u rad najkasnije 27. studenoga 2003. ili postojeća plinska turbina za izvanredne (hitne) slučajeve koja radi < 500 h/god.
Generally applicable to supplementary firing for heat recovery steam generators (HRSGs) in the case of combined-cycle gas turbine (CCGT) combustion plants
Nema razine emisija povezane s NRT-om
Not applicable in the case of combustion plants operated < 500 h/yr.
Postojeća plinska turbina koja se upotrebljava za mehanički pogon – Sve osim uređaja koji rade < 500 h/god.
Not generally applicable to existing combustion plants of < 100 MWth.
Indikativna vrijednost godišnje prosječne razine emisije CO za svaku od vrsta postojećih uređaja za loženje koji rade ≥ 1500 h/god. i za sve vrste novih uređaja za loženje općenito iznosi kako slijedi:
Retrofitting existing combustion plants may be constrained by the availability of sufficient space.
novi OCGT snage ≥ 50 MWth: < 5–40 mg/Nm3.
BAT 43.
Za uređaje čija je neto električna učinkovitost (EE) viša od 39 % može se primijeniti faktor korekcije na gornju granicu tog raspona, koji odgovara [gornja granica] × EE/39, gdje je EE neto električna učinkovitost ili neto učinkovitost mehaničke energije uređaja utvrđena na temelju osnovnih uvjeta opterećenja po ISO-u,
In order to prevent or reduce NOX emissions to air from the combustion of natural gas in engines, BAT is to use one or a combination of the techniques given below.
novi CCGT snage ≥ 50 MWth: < 5–30 mg/Nm3.
Lean-burn concept
Za uređaje čija je neto električna učinkovitost (EE) viša od 55 % može se primijeniti faktor korekcije na gornju granicu raspona koji odgovara [gornja granica] × EE/55, gdje je EE neto električna učinkovitost uređaja utvrđena na temelju osnovnih uvjeta opterećenja po ISO-u,
Generally used in combination with SCR
postojeći CCGT snage ≥ 50 MWth: < 5–30 mg/Nm3.
Only applicable to new gas-fired engines
Gornja će granica ovog raspona općenito biti 50 mg/Nm3 za uređaje koji rade s malim opterećenjem,
Advanced lean-burn concept
postojeće plinske turbine snage ≥ 50 MWth koje se upotrebljavaju za mehanički pogon: < 5–40 mg/Nm3.
Only applicable to new spark plug ignited engines
Gornja će granica ovog raspona općenito biti 50 mg/Nm3 za uređaje koji rade s malim opterećenjem.
BAT 44.
Za plinske turbine opremljene suhim plamenicima s niskom razinom emisija NOX (DLN) te indikativne razine odgovaraju učinkovitom radu DLN-a.
In order to prevent or reduce CO emissions to air from the combustion of natural gas, BAT is to ensure optimised combustion and/or to use oxidation catalysts.
Tablica 25.
See descriptions in Section 8.3.
Razine emisija povezane s NRT-ima za emisije NOX u zrak iz izgaranja prirodnog plina u kotlovima i motorima
Table 24
godišnja srednja vrijednost [158]
BAT-associated emission levels (BAT-AELs) for NOX emissions to air from the combustion of natural gas in gas turbines
postojeći uređaj [159]
BAT-AELs (mg/Nm3) [143] [144]
postojeći uređaj [160]
Yearly average [145] [146]
Motor [161]
Open-cycle gas turbines (OCGTs) [147] [148]New OCGT
< 5–40 mg/Nm3 za postojeće kotlove koji rade ≥ 1500 h/god.,
Existing OCGT (excluding turbines for mechanical drive applications) — All but plants operated < 500 h/yr
< 5–15 mg/Nm3 za nove kotlove,
Combined-cycle gas turbines (CCGTs) [147] [150]New CCGT
30–100 mg/Nm3 za postojeće motore koji rade ≥ 1500 h/god. i za nove motore.
Existing CCGT with a net total fuel utilisation of < 75 %
NRT 45.
Existing CCGT with a net total fuel utilisation of ≥ 75 %
Za smanjenje emisija nemetanskih hlapljivih organskih spojeva (NMHOS-i) i metana (CH4) u zrak iz izgaranja prirodnog plina u plinskim motorima sa siromašnom gorivom smjesom s paljenjem pomoću svjećica NRT je osiguravanje optimiziranog izgaranja i/ili upotreba oksidacijskih katalizatora.
Existing CCGT with a net total fuel utilisation of < 75 %
Oksidacijski katalizatori nisu učinkoviti u smanjenju emisija zasićenih ugljikovodika koji sadržavaju manje od četiri atoma ugljika.
Existing CCGT with a net total fuel utilisation of ≥ 75 %
Tablica 26.
Open- and combined-cycle gas turbines
Razine emisija povezane s NRT-ima za emisije formaldehida i CH4 u zrak iz izgaranja prirodnog plina u plinskim motorima sa siromašnom gorivom smjesom s paljenjem pomoću svjećica
Gas turbine put into operation no later than 27 November 2003, or existing gas turbine for emergency use and operated < 500 h/yr
novi ili postojeći uređaj
No BAT-AEL
postojeći uređaj
Existing gas turbine for mechanical drive applications — All but plants operated < 500 h/yr
Zaključci o NRT-ima za izgaranje procesnih plinova iz industrije željeza i čelika
New OCGT of ≥ 50 MWth: < 5–40 mg/Nm3.
NRT 46.
For plants with a net electrical efficiency (EE) greater than 39 %, a correction factor may be applied to the higher end of this range, corresponding to [higher end] × EE/39, where EE is the net electrical energy efficiency or net mechanical energy efficiency of the plant determined at ISO baseload conditions.
Za povećanje energetske učinkovitosti izgaranja procesnih plinova iz industrije željeza i čelika NRT je upotreba prikladne kombinacije tehnika navedenih u NRT 12. i u nastavku.
Existing OCGT of ≥ 50 MWth (excluding turbines for mechanical drive applications): < 5–40 mg/Nm3.
Sustav upravljanja procesnim plinovima
The higher end of this range will generally be 80 mg/Nm3 in the case of existing plants that cannot be fitted with dry techniques for NOX reduction, or 50 mg/Nm3 for plants that operate at low load.
Primjenjivo samo na integrirane čeličane.
New CCGT of ≥ 50 MWth: < 5–30 mg/Nm3.
Tablica 27.
For plants with a net electrical efficiency (EE) greater than 55 %, a correction factor may be applied to the higher end of the range, corresponding to [higher end] × EE/55, where EE is the net electrical energy efficiency of the plant determined at ISO baseload conditions.
Razine energetske učinkovitosti povezane s NRT-ima za izgaranje procesnih plinova iz industrije željeza i čelika u kotlovima
Existing CCGT of ≥ 50 MWth: < 5–30 mg/Nm3.
Razine energetske učinkovitosti povezane s NRT-ima [165] [166]
The higher end of this range will generally be 50 mg/Nm3 for plants that operate at low load.
neto ukupno učinkovito iskorištavanje goriva (%) [167]
Existing gas turbines of ≥ 50 MWth for mechanical drive applications: < 5–40 mg/Nm3.
Postojeći plinski kotao koji upotrebljava više vrsta goriva
The higher end of the range will generally be 50 mg/Nm3 when plants operate at low load.
Novi plinski kotao koji upotrebljava više vrsta goriva [168]
In the case of a gas turbine equipped with DLN burners, these indicative levels correspond to when the DLN operation is effective.
Tablica 28.