natgillin/translations-raw huggingface dataset:
system defence plan procedures, including at least:
granične vrijednosti pogonskih veličina utvrđene u skladu s člankom 25.
frequency deviation management procedure in accordance with Article 18;
Uredbe (EU) 2017/1485;
voltage deviation management procedure in accordance with Article 19;
ponašanje i sposobnosti tereta i proizvodnje unutar sinkronog područja;
power flow management procedure in accordance with Article 20;
posebne potrebe ZKM-ova visokog prioriteta navedene u skladu sa stavkom 4. točkom (d) i
assistance for active power procedure in accordance with Article 21; and
karakteristike svojeg prijenosnog sustava i povezanih sustava ODS-ova.
manual demand disconnection procedure in accordance with Article 22.
Plan obrane sustava mora sadržavati barem sljedeće odredbe:
The measures contained in the system defence plan shall comply with the following principles:
uvjete pod kojima se aktivira plan obrane sustava, u skladu s člankom 13.;
their impact on the system users shall be minimal;
naloge OPS-a za plan obrane sustava i
they shall be economically efficient;
mjere koje ovise o dogovoru ili koordinaciji s utvrđenim stranama u stvarnom vremenu.
only those measures that are necessary shall be activated; and
Konkretno, plan obrane sustava mora uključivati sljedeće:
they shall not lead the TSO's transmission system or the interconnected transmission systems into emergency state or blackout state.
popis mjera koje OPS mora provesti na svojim postrojenjima;
Article 12
popis mjera koje ODS-ovi moraju provesti i popis ODS-ova odgovornih za provedbu tih mjera na svojim postrojenjima;
Implementation of the system defence plan
popis ZKM-ova odgovornih za provedbu mjera na svojim postrojenjima koje proizlaze iz obveznih zahtjeva iz uredaba (EU) 2016/631, (EU) 2016/1388 i (EU) 2016/1447 ili nacionalnog zakonodavstva i popis mjera koje moraju provesti ti ZKM-ovi;
By 18 December 2019 each TSO shall implement those measures of its system defence plan that are to be implemented on the transmission system.
popis ZKM-ova visokog prioriteta te uvjeta za njihovo isključivanje i
It shall maintain the implemented measures henceforth.
rokove primjene svake mjere navedene u planu obrane sustava.
By 18 December 2018 each TSO shall notify the transmission connected DSOs of the measures, including the deadlines for implementation, which are to be implemented on:
Plan obrane sustava mora sadržavati barem sljedeće tehničke i organizacijske mjere utvrđene u Odjeljku 2.
the DSO's installations pursuant to Article 11(4); or
Poglavlja II.:
the installations of SGUs identified pursuant to Article 11(4) connected to their distribution systems; or
planovi djelovanja sustavnih zaštita koji uključuju barem:
the installations of defence service providers connected to their distribution systems; or
i. plan za automatsko djelovanje podfrekvencijske zaštite u skladu s člankom 15.;
the installations of DSOs connected to their distribution systems.
plan za automatsko djelovanje nadfrekvencijske zaštite u skladu s člankom 16. i
By 18 December 2018 each TSO shall notify the SGUs identified pursuant to point (c) of Article 11(4) or the defence service providers directly connected to its transmission system of the measures which are to be implemented on their installations, including the deadlines for the implementation.
plan za automatsko djelovanje zaštite od sloma napona u skladu s člankom 17.;
When provided for in national legislation, the TSO shall notify directly SGUs identified pursuant to point (c) of Article 11(4), defence service providers or DSOs connected to distribution systems of the measures which are to be implemented on their installations, including the deadlines for their implementation.
postupci plana obrane sustava koji uključuju barem:
It shall inform the concerned DSO of this notification.
i. postupak za upravljanje odstupanjem frekvencije u skladu s člankom 18.;
Where a TSO notifies a DSO in accordance with paragraph 2, the DSO shall notify in turn, without delay, the SGUs, the defence service providers and the DSOs connected to its distribution system of the measures of the system defence plan that they have to implement on their respective installations, including the deadlines for their implementation.
postupak za upravljanje odstupanjem napona u skladu s člankom 19.;
Each notified DSO, SGU and defence service provider shall:
postupak za upravljanje tokom snage u skladu s člankom 20.;
implement the measures notified pursuant to this Article no later than 12 months from the date of notification;
postupak za pomaganje u pogledu djelatne snage u skladu s člankom 21. i
confirm the implementation of the measures to the notifying system operator, who shall, when different from the TSO, notify the confirmation to the TSO; and
v. plan hitnog rasterećenja u skladu s člankom 22.
maintain the measures implemented on its installations.
Mjere koje sadržava plan obrane sustava moraju biti dosljedne sljedećim načelima:
Article 13
njihov utjecaj na korisnike sustava mora biti najmanji mogući;
Activation of the system defence plan
moraju biti ekonomski učinkovite;
Each TSO shall activate the procedures of its system defence plan pursuant to point (b) of Article 11(5) in coordination with DSOs and SGUs identified pursuant to Article 11(4) and with defence service providers.
aktiviraju se samo mjere koje su nužne i
In addition to the automatically activated schemes of the system defence plan, pursuant to point (a) of Article 11(5), each TSO shall activate a procedure of the system defence plan when:
tim se mjerama ne smije uzrokovati prelazak prijenosnog sustava OPS-a ili međusobno povezanih prijenosnih sustava u poremećeni pogon ili raspad sustava.
the system is in emergency state in accordance with the criteria set out in Article 18(3) of Regulation (EU) 2017/1485 and there are no remedial actions available to restore the system to the normal state; or
Članak 12.
based on the operational security analysis, the operational security of the transmission system requires the activation of a measure of the system defence plan pursuant to Article 11(5) in addition to the available remedial actions.
Provedba plana obrane sustava
Each DSO and SGU identified pursuant to Article 11(4), as well as each defence service provider shall execute without undue delay the system defence plan instructions issued by the TSO pursuant to point (c) of Article 11(3), in accordance with the system defence plan procedures provided for in point (b) of Article 11(5).
Do 18. prosinca 2019. svaki OPS mora provesti mjere plana obrane sustava koje je potrebno provesti na prijenosnom sustavu.
Each TSO shall activate procedures of its system defence plan referred to in point (b) of Article 11(5) having a significant cross-border impact in coordination with the impacted TSOs.
Provedene mjere dužan je održavati na snazi.
Article 14
Do 18. prosinca 2018. svaki OPS mora obavijestiti ODS-ove priključene na prijenosni sustav o mjerama, uključujući rokove za njihovu provedbu, koje je potrebno provesti na:
Inter-TSO assistance and coordination in emergency state
postrojenjima ODS-ova u skladu s člankom 11. stavkom 4. ili
Upon request from a TSO in emergency state, each TSO shall provide through interconnectors any possible assistance to the requesting TSO, provided this does not cause its transmission system or the interconnected transmission systems to enter into emergency or blackout state.
postrojenjima ZKM-ova utvrđenih u skladu s člankom 11. stavkom 4. priključenima na njihove distribucijske sustave ili
When the assistance needs to be provided through direct current interconnectors, it may consist in carrying out the following actions, taking into account the technical characteristics and capability of HVDC system:
postrojenjima pružatelja usluge uravnoteženja sustava priključenima na njihove distribucijske sustave ili
manual regulation actions of the transmitted active power to help the TSO in emergency state to bring power flows within operational security limits or frequency of neighbouring synchronous area within system frequency limits for alert state defined pursuant to Article 18(2) of Regulation (EU) 2017/1485;
postrojenjima ODS-ova priključenima na njihove distribucijske sustave
automatic control functions of the transmitted active power based on the signals and criteria set out in Article 13 of Regulation (EU) 2016/1447;
Do 18. prosinca 2018. svaki OPS mora obavijestiti ZKM-ove utvrđene u skladu s člankom 11. stavkom 4. točkom (c) ili pružatelje usluge obrane sustava izravno priključene na njegov prijenosni sustav o mjerama koje je potrebno provesti na njihovim postrojenjima, uključujući rokove za njihovu provedbu.
automatic frequency control pursuant to Articles 15 to 18 of Regulation (EU) 2016/1447 in case of islanded operation;
Ako je to predviđeno nacionalnim zakonodavstvom, OPS mora izravno obavijestiti ZKM-ove utvrđene u skladu s člankom 11. stavkom 4. točkom (c), pružatelje usluge obrane sustava ili ODS-ove priključene na distribucijske sustave o mjerama koje je potrebno provesti na njihovim postrojenjima, uključujući rokove za njihovu provedbu.
voltage and reactive power control pursuant to Article 24 of Regulation (EU) 2016/1447, and
OPS o toj obavijesti izvješćuje predmetnog ODS-a.
any other appropriate action.
Ako OPS obavijesti ODS-a u skladu sa stavkom 2., ODS bez odgađanja obavješćuje ZKM-ove, pružatelje usluge obrane sustava ili ODS-ove priključene na njegove distribucijske sustave o mjerama plana obrane sustava koje moraju provesti na svojim pojedinačnim postrojenjima, uključujući rokove za njihovu provedbu.
Each TSO may proceed to a manual disconnection of any transmission system element having a significant cross-border impact, including an interconnector, subject to the following requirements:
Svaki obaviješteni ODS, ZKM i pružatelj usluge obrane sustava dužan je:
the TSO shall coordinate with neighbouring TSOs; and
primijeniti mjere upućene u skladu s ovim člankom najkasnije 12 mjeseci od datuma zaprimanja;
this action shall not lead the remaining interconnected transmission system into emergency state or blackout state.
potvrditi provedbu mjera operatoru sustava koji je zatražio njihovu provedbu koji zatim, ako taj operator nije OPS, upućuje tu potvrdu OPS-u i
Notwithstanding paragraph 3, a TSO may manually disconnect any transmission system element having a significant cross-border impact, including an interconnector, without coordination, in exceptional circumstances implying a violation of the operational security limits, to prevent endangering personnel safety or damaging equipment.
održavati mjere provedene na njegovim postrojenjima.
Within 30 days of the incident, the TSO shall prepare a report at least in English containing a detailed explanation of the rationale, implementation and impact of this action and submit it to the relevant regulatory authority in accordance with Article 37 of Directive 2009/72/EC and neighbouring TSOs, and make it available to the significantly affected system users.
Članak 13.
SECTION 2
Aktiviranje plana obrane sustava
Measures of the System Defence Plan
Svaki OPS aktivira postupke svojeg plana obrane sustava u skladu s člankom 11. stavkom 5. točkom (b) u koordinaciji s ODS-ovima i ZKM-ovima utvrđenima u skladu s člankom 11. stavkom 4. te s pružateljima usluge obrane sustava.
Article 15
Osim automatski aktiviranih sastavnih planova iz plana obrane sustava, u skladu s člankom 11. stavkom 5. točkom (a), svaki OPS aktivira postupak plana obrane sustava:
Automatic under-frequency control scheme
ako je sustav u poremećenom pogonu u skladu s kriterijima navedenim u članku 18. stavku 3.
The scheme for the automatic control of under-frequency of the system defence plan shall include a scheme for the automatic low frequency demand disconnection and the settings of the limited frequency sensitive mode-underfrequency in the TSO load frequency control (LFC) area.
Uredbe (EU) 2017/1485 i nema raspoloživih korektivnih mjera za ponovnu uspostavu normalnog pogona ili
In the design of its system defence plan, each TSO shall provide for the activation of the limited frequency sensitive mode-underfrequency prior to the activation of the scheme for the automatic low frequency demand disconnection, where the rate of change of frequency allows it.
ako, na temelju analize pogonske sigurnosti, stanje pogonske sigurnosti prijenosnog sustava zahtijeva aktiviranje mjere plana obrane sustava u skladu s člankom 11. stavkom 5. zajedno s dostupnim korektivnim mjerama.
Prior to the activation of the automatic low frequency demand disconnection scheme, each TSO and DSO identified pursuant to Article 11(4) shall foresee that energy storage units acting as load connected to its system:
Svaki ODS i ZKM utvrđen u skladu s člankom 11. stavkom 4. te svaki pružatelj usluge obrane sustava bez nepotrebnog odgađanja provode naloge iz plana obrane sustava koje je izdao OPS na temelju članka 11. stavka 3. točke (c), u skladu s postupcima plana obrane sustava utvrđenima u članku 11. stavku 5. točki (b).
automatically switch to generation mode within the time limit and at an active power set-point established by the TSO in the system defence plan; or
Ako OPS aktivira postupke svojega plana obrane sustava u skladu s člankom 11. stavkom 5. točkom (b) koji imaju znatan prekogranični utjecaj, OPS ih aktivira u koordinaciji sa zahvaćenim OPS-ovima.
when the energy storage unit is not capable of switching within the time limit established by the TSO in the system defence plan, automatically disconnect the energy storage unit acting as load.
Članak 14.
Each TSO shall establish in its system defence plan the frequency thresholds at which the automatic switching or disconnection of energy storage units shall occur.
Međusobna pomoć i koordinacija OPS-ova u poremećenom pogonu
These frequency thresholds shall be lower or equal to the system frequency limit defined for the emergency state in Article 18(3) of Regulation (EU) 2017/1485 and higher than the frequency limit for demand disconnection starting mandatory level laid down in the Annex.
Na zahtjev OPS-a u poremećenom pogonu svaki OPS putem interkonekcijskih vodova pruža svu moguću pomoć OPS-u koji je uputio zahtjev, pod uvjetom da se time ne uzrokuje prelazak njegova prijenosnog sustava ili međusobno povezanih prijenosnih sustava u poremećeni pogon ili raspad sustava.
Each TSO shall design the scheme for the automatic low frequency demand disconnection in accordance with the parameters for shedding load in real-time laid down in the Annex.
Ako je pomoć nužno pružiti putem interkonekcijskih vodova istosmjerne struje, uzimajući u obzir tehničke karakteristike i sposobnosti ISVN sustava, pomoć može obuhvaćati sljedeće mjere:
The scheme shall include the disconnection of demand at different frequencies, from a ‘starting mandatory level’ to a ‘final mandatory level’, within an implementation range whilst respecting a minimum number and maximum size of steps.
ručnu regulaciju prenesene djelatne snage čime se OPS-u u poremećenom pogonu pomaže u ponovnom vraćanju tokova snage unutar graničnih vrijednosti pogonskih veličina ili u vraćanju frekvencije susjednog sinkronog područja unutar graničnih vrijednosti frekvencije sustava za ugroženi normalni pogon utvrđen u skladu s člankom 18. stavkom 2.
The implementation range shall define the maximum admissible deviation of netted demand to be disconnected from the target netted demand to be disconnected at a given frequency, calculated through a linear interpolation between starting and final mandatory levels.
Uredbe (EU) 2017/1485;
The implementation range shall not allow the disconnection of less netted demand than the amount of netted demand to be disconnected at the starting mandatory level.
automatske regulacijske mjere za prenesenu djelatnu snagu na temelju signala i kriterija iz članka 13.
A step cannot be considered as such if no netted demand is disconnected when this step is reached.
Uredbe (EU) 2016/1447;
Each TSO or DSO shall install the relays necessary for low frequency demand disconnection taking into account at least load behaviour and dispersed generation.
automatsku regulaciju frekvencije u skladu s člancima od 15. do 18.
When implementing the scheme for the automatic low frequency demand disconnection pursuant to the notification under Article 12(2), each TSO or DSO shall:
Uredbe (EU) 2016/1447 u slučaju otočnog pogona;
avoid setting an intentional time delay in addition to the operating time of the relays and circuit breakers;
regulaciju napona i jalove snage u skladu s člankom 24.
minimise the disconnection of power generating modules, especially those providing inertia; and
Uredbe (EU) 2016/1447 i
limit the risk that the scheme leads to power flow deviations and voltage deviations outside operational security limits.
sve druge odgovarajuće mjere.
If a DSO cannot fulfil the requirements under points (b) and (c), it shall notify the TSO and propose which requirement shall apply.
Svaki OPS može poduzeti ručno isključenje bilo kojeg elementa prijenosnog sustava koji ima znatan prekogranični utjecaj, uključujući interkonekcijski vod, pod sljedećim uvjetima:
The TSO, in consultation with the DSO shall establish the applicable requirements based on a joint cost-benefit analysis.
OPS mora koordinirati djelovanje sa susjednim OPS-ovima i
The scheme for the automatic low frequency demand disconnection of the system defence plan may provide for netted demand disconnection based on frequency gradient provided that:
tom se mjerom ne smije uzrokovati prelazak preostalih međusobno povezanih prijenosnih sustava u poremećeni pogon ili raspad sustava.
it is activated only:
Neovisno o stavku 3., kako bi spriječio ugrožavanje sigurnosti osoblja ili oštećenje opreme, u iznimnim okolnostima u kojima može doći do narušavanja graničnih vrijednosti pogonskih veličina OPS može ručno isključiti svaki element prijenosnog sustava koji ima znatan prekogranični utjecaj, uključujući interkonekcijski vod, bez prethodne koordinacije sa susjednim OPS-ovima.
when the frequency deviation is higher than the maximum steady state frequency deviation and the frequency gradient is higher than the one produced by the reference incident;
U roku od 30 dana od incidenta OPS mora sastaviti izvješće barem na engleskom jeziku koje sadržava detaljno obrazloženje, opis provedbe mjere i učinke te mjere, podnijeti ga mjerodavnom regulatornom tijelu u skladu s člankom 37.
until the frequency reaches the frequency of the demand disconnection starting mandatory level;
Direktive 2009/72/EZ, kao i susjednim OPS-ovima, te ga staviti na raspolaganje znatno zahvaćenim korisnicima sustava.
it complies with the Annex; and
ODJELJAK 2.
it is necessary and justified in order to maintain efficiently the operational security.
Mjere plana obrane sustava
In case the scheme for the automatic low frequency demand disconnection of the system defence plan includes netted demand disconnection based on frequency gradient, as described in paragraph 8, the TSO shall submit, within 30 days of the implementation, a report containing a detailed explanation of the rationale, implementation and impact of this measure to the national regulatory authority.
Članak 15.
A TSO may include in the scheme for automatic low frequency demand disconnection of its system defence plan additional steps for netted demand disconnection below the final mandatory level of demand disconnection set out in the Annex.
Plan za automatsko djelovanje podfrekvencijske zaštite
Each TSO shall be entitled to implement additional system protection schemes that are triggered by a frequency smaller or equal to the frequency of the final mandatory level of demand disconnection and which aim at a faster restoration process.
Plan podfrekvencijskog rasterećenja u planu obrane sustava uključuje plan za automatski isklop potrošnje pri pojavi podfrekvencije i postavke za ograničen frekvencijski osjetljiv način rada – podfrekvencijski, u OPS-ovu regulacijskom području frekvencije i snage razmjene (dalje u tekstu: LFC područje).
The TSO shall ensure that such additional schemes do not further deteriorate frequency.
Pri izradi plana obrane sustava svaki OPS u planu propisuje aktiviranje ograničenog frekvencijski osjetljivog načina rada – podfrekvencijskog prije aktiviranja plana podfrekvencijskog rasterećenja, ako brzina promjene frekvencije to dopušta.
Article 16
Prije aktiviranja plana podfrekvencijskog rasterećenja svaki OPS i ODS utvrđen u skladu s člankom 11. stavkom 4. pretpostavlja za uređaje za pohranjivanje energije u funkciji opterećenja priključenog na njegov sustav:
Automatic over-frequency control scheme
da se ti uređaji automatski prebacuju na proizvodnju unutar zadanog vremena i na razini postavnih vrijednosti djelatne snage koju je OPS utvrdio u planu obrane sustava ili
The scheme for automatic over-frequency control of the system defence plan shall lead to an automatic decrease of the total active power injected in each LFC area.
da se, u slučaju da neki uređaj za pohranjivanje energije u funkciji opterećenja nije sposoban za prebacivanje na proizvodnju unutar zadanog vremena koje je OPS utvrdio u planu obrane sustava, taj uređaj automatski isključuje.
In consultation with the other TSOs of its synchronous area, each TSO shall set out the following parameters of its scheme for automatic over-frequency control:
Svaki OPS u svojem planu obrane sustava utvrđuje frekvencijske pragove za automatsko prebacivanje ili isključenje uređaja za pohranjivanje energije.
the frequency thresholds for its activation; and
Ti frekvencijski pragovi ne smiju biti viši od graničnih vrijednosti frekvencije sustava utvrđenih za poremećeni pogon u članku 18. stavku 3.
the reduction ratio of injection of active power.
Uredbe (EU) 2017/1485 te moraju biti viši od graničnih vrijednosti frekvencije za početnu obveznu razinu isklopa potrošnje navedenu u Prilogu.
Each TSO shall design its automatic over-frequency control scheme taking into account the capabilities of the power generating modules concerning the limited frequency sensitive mode — overfrequency and of the energy storage units, in its LFC area.
Svaki OPS izrađuje plan podfrekvencijskog rasterećenja u skladu s parametrima rasterećenja u stvarnom vremenu navedenim u Prilogu.
If the limited frequency sensitive mode — overfrequency does not exist or is not sufficient to fulfil the requirements set out in points (a) and (b) of paragraph 2, each TSO shall set up in addition a step-wise linear disconnection of generation in its LFC area.
U planu je nužno predvidjeti isklop potrošnje na različitim frekvencijama unutar raspona primjene, od početne obvezne razine do završne obvezne razine, istodobno se pridržavajući minimalnog i maksimalnog broja razreda.
The TSO shall establish the maximum size of the steps for disconnection of power generating modules and/or of HVDC systems in consultation with the other TSOs of its synchronous area.
Rasponom primjene definira se maksimalno dopušteno odstupanje netirane potrošnje koja se treba isključiti od ciljane netirane potrošnje koja se treba isključiti na određenoj frekvenciji, izračunanoj pomoću linearne interpolacije početnih i završnih obveznih razina.
Article 17
Zbog raspona primjene ne smije se dopustiti isklop manje količine netirane potrošnje od količine koja se treba isključiti na početnoj obveznoj razini.
Automatic scheme against voltage collapse
Razred se ne može smatrati razredom ako nikakva netirana potrošnja nije isključena kad je taj razred dosegnut.
The automatic scheme against voltage collapse of the system defence plan may include one or more of the following schemes, depending on the results of a TSO's assessment of system security:
Svaki OPS i ODS mora ugraditi releje potrebne za isklop potrošnje pri pojavi podfrekvencije uzimajući u obzir barem ponašanje opterećenja i raspodjelu proizvodnje.
a scheme for low voltage demand disconnection according to Article 19(2) of Regulation (EU) 2016/1388;
Pri uvođenju plana podfrekvencijskog rasterećenja u skladu s obavijesti iz članka 12. stavka 2. svaki OPS i ODS:
a blocking scheme for on load tap changer according to Article 19(3) of Regulation (EU) 2016/1388; and
izbjegava postavljanje namjerne odgode kojom se produljuje operativno vrijeme releja i prekidača;