natgillin/translations-raw huggingface dataset:
Furthermore, temperature differences between the set temperatures and panel temperatures were much higher in heating conditions compared to cooling conditions.
Osim toga, temperaturne razlike između zadanih temperatura i temperatura ploča bile su mnogo više u uvjetima grijanja nego u slučaju hlađenja.
The influence of panels operating in heating mode was therefore assessed in the course of this study.
Stoga je u okviru ovog istraživanja ispitan i utjecaj panela korištenih u procesu grijanja.
Maximum indoor air temperature differences between the highest and the lowest temperature sensors, measured during the day in a typical heating working week, were observed early in the morning, around 6 a.m. (Figure 5) when the heating system started to operate.
Maksimalne temperaturne razlike između najviše i najniže pozicioniranih senzora, izmjerene tijekom dana u tipičnom radnom tjednu u sezoni grijanja, zabilježene su oko 6 sati ujutro (slika 5.) kada bi sustav grijanja počeo raditi.
After 8 a.m., the system was rarely activated and the indoor air temperature differences were increasingly reduced, and thus quite uniform indoor air temperatures were registered.
Sustav se rijetko aktivirao nakon 8 sati ujutro i temperaturne razlike u unutarnjim prostorima su se sve više smanjivale, pa su tako zabilježene poprilično jednolične unutarnje temperature zraka.
The ceiling temperatures, with ceiling panels activated (heating mode), were recorded with the professional IR camera Flir SC640.
Temperature stropa u slučaju korištenja stropnih panela (postupak grijanja) zabilježene su pomoću profesionalne kamere s infracrvenim zračenjem tipa Flir SC640.
Thermographic images showed the expected temperature range of the heated panel surface and the concrete slab (Figure 6).
Termografske slike pokazale su očekivani temperaturni raspon zagrijanih površina panela i betonske ploče (slika 6.).
The temperature analysis was performed for the worst-case scenario: panels operating at full heating power (in the morning) and with the highest inlet water temperature (38.6 °C).
Analiza temperature obavljena je za najgori scenarij: kada paneli rade pri punoj snazi grijanja (ujutro) te pri najvišoj ulaznoj temperaturi vode (38,6 °C).
The average temperature, based on measured surface temperatures recorded with the IR camera, which included the entire ceiling surface (60 % panels, 40 % concrete slab), amounted to 27.7 °C.
Prosječna temperatura bazirana na izmjerenim površinskim temperaturama zabilježenima pomoću kamere s infracrvenim zračenjem iznosila je 27,7 °C, a obuhvaćena je čitava površina stropa (60 % panela, 40 % betonske ploče).
The floor temperature measurements revealed floor temperatures of 22 °C, which resulted in a warm ceiling radiant temperature asymmetry of less than 7K, thus corresponding to Category C according to SIST EN ISO 7730 [19].
Mjerenjem temperature poda dobivena je vrijednost od 22 °C, što je dovelo do asimetrije u isijavanju topline na strop za manje od 7 K, a to odgovara kategoriji C prema normi SIST EN ISO 7730 [19].
Figure 6. a) screenshot of thermographic recording of activated ceiling panels in heating mode; b) photo of the same section
Slika 6. a) Ekranski prikaz termografskog snimanja aktiviranih stropnih panela u postupku grijanja i b) fotografija istog dijela stropa
Operational performance of ceiling panels
Radna učinkovitost stropnih panela
The thermal response of the ceiling panels managing system and of the panels themselves was very good.
Toplinski odziv sustava za upravljanje stropnim panelima, isto kao i odziv samih panela, bio je jako dobar.
The panels reacted well to air temperature oscillations and provided the necessary heat or cold (according to heating/cooling mode) to the rooms.
Paneli su dobro reagirali na oscilacije temperature zraka i u prostorije su unosili potrebnu toplinu ili hladnoću (ovisno o tome je li korišten sustav grijanja ili hlađenja).
The impacts on indoor air temperatures can, for instance, occur due to the occupants opening the windows, additional internal gains caused by devices, or due to solar gains, etc. An example of the relationship between the measured indoor air temperature (blue line), pre-set cooling temperature (violet line), and cooling capacity of panels (green line) is shown in Figure 7.
Na unutarnju temperaturu zraka može na primjer utjecati otvaranje prozora, dodatni unutarnji dobici uslijed djelovanja uređaja, solarni dobici itd. Na slici 7. daje se primjer odnosa između izmjerene unutarnje temperature zraka (plava linija), unaprijed podešene temperature hlađenja (ljubičasta linija) i kapaciteta hlađenja panela (zelena linija).
By opening the window in the morning, the occupants could increase the air exchange rate between indoor and outdoor air and consequently lower the indoor air temperature.
Ako ujutro otvore prozor, korisnici mogu povećati razmjenu unutarnjeg i vanjskog zraka te bitno smanjiti temperaturu unutarnjeg zraka.
Two typical situations can be
Tablica 4.
Temperature T [°C] at:
Temperatura T [°C] pri:
Temperature difference, max [K]
Maksimalna temperaturna razlika [K]
Temperature difference, average [K]
Prosječna temperaturna razlika [K]
seen in Figure 7: on 23rd April, the indoor air temperature was low enough (below the set temperature), and consequently the panels did not need to cool; on 24th April, the windows were not opened and the indoor air temperature exceeded the temperature set for cooling and, hence, the system started to cool.
Na slici 7. vidimo dvije tipične situacije: 23. travnja unutarnja temperatura zraka bila je dovoljno niska (spustila se ispod zadane temperature) pa zato paneli nisu trebali hladiti; 24. travnja prozori nisu bili otvarani pa je unutarnja temperatura zraka bila viša od temperature na koju je bilo podešeno hlađenje, pa je stoga sustav počeo hladiti.
Thermal response of ceiling panel system to indoor air temperature oscillations due to window opening observed over two days during cooling season
Toplinski odziv sustava stropnih ploča na oscilacije unutarnje temperature zraka zbog otvaranja prozora, zabilježeno tijekom dva dana za vrijeme sezone hlađenja
Heating and cooling energy consumption at pilot offices
Potrošnja toplinske i rashladne energije u piloturedima
The heating/cooling ceiling panels of each office were equipped with calorimeters measuring the amount of energy delivered for the heating or cooling of a particular office.
Stropni paneli za grijanje i hlađenje, koji su se nalazili u svakom od analiziranih ureda, bili su opremljeni kalorimetrima za mjerenje energije potrebne za grijanje tj. hlađenje uredskih prostorija.
The supporting mechanical ventilation system was designed to provide tempered air and thereby a part of the energy to the offices.
U prostorijama se nalazio i dodatni ventilacijski sustav za temperiranje zraka, pa je i na taj način dobiven dio energije potrebne za urede.
The mechanical ventilation system inlets and outlets, provided in each room, were therefore equipped with electronic volume regulators and temperature sensors measuring the air temperature and air volume delivered to and extracted from the rooms.
Ulazi u sustav i izlazi iz sustava za mehaničku ventilaciju, instalirani u svakoj prostoriji, bili su opremljeni elektronskim regulatorima volumena i temperaturnim senzorima za mjerenje temperature i volumena zraka koji se unosio u prostorije, tj. izbacivao iz prostorija.
In 2013, the total energy consumption for heating and cooling all four offices amounted to less than 4900 kWh/a. The consumed energy, calculated per area unit of the analysed office area, was 24 kWh/m2 for heating, and 21 kWh/m2 for cooling.
U 2013. godini ukupna je potrošnja energije za grijanje i hlađenje sva četiri ureda iznosila manje od 4900 kWh/a. Potrošnja analiziranih ureda iskazana po jedinici površine iznosila je 24 kWh/m2 za grijanje, tj. 21 kWh/m2 za hlađenje.
The monthly consumption of energy for tempering the offices in 2013 is presented in Figure 8.
Mjesečna potrošnja energije potrebne za temperiranje uredskih prostorija u 2013. godini prikazana je na slici 8.
As the offices were not identical, differing primarily in their equipment and occupancy, the investigation continued by assessing the consumption of heating and cooling energy in individual offices (Figure 9).
Kako uredi nisu bili jednaki, tj. razlikovali su se najviše po opremi i namjeni, u nastavku istraživanja mjerena je i potrošnja toplinske i rashladne energije u svakom uredu (slika 9.).
This assessment was conducted considering the internal gains, which were based on the evaluation of recorded presence of employees, their estimated time of presence in the rooms, and their mainly sedentary
Ocjena o tome dobivena je uzimajući u obzir interne dobitke koji su se bazirali na ocjeni zabilježene prisutnosti zaposlenika, njihovog vremena boravka u prostorijama te njihovim aktivnostima
activities [19], as well as on the electricity consumption measurements (see Table 5).
koje su uglavnom bile sjedilačke [19], isto kao i na mjerenjima potrošnje električne energije (tablica 5.).
Internal gains per area unit of pilot offices in 2013
Interni dobici po m2 pilot-ureda u 2013.
Heating and cooling energy released to pilot offices in 2013
Energija potrebna za grijanje i hlađenje pilot-ureda u 2013.
Monthly presentation of heating and cooling energy consumption in 2013 per area unit of individual offices
Mjesečni prikaz potrošnje energije za grijanje i hlađenje ureda u 2013., po jedinici površine
Observed periods
Promatrana razdoblja
Internal gains [kWh/m2]
Interni dobici [kWh/m2]
Heating period Cooling period
Razdoblje grijanja 20,5
Građevinar 2/2016
Razdoblje hlađenja 13,2
Once all planned measures and data have been included, the calculated energy losses were almost 60 kWh/m2a (71 % transmission, 29 % ventilation losses), while the energy gains were calculated as 35 kWh/m2a (35 % solar, 65 % internal gains).
Nakon uključivanja svih planiranih mjera i podataka, izračunani gubici energije iznosili su gotovo 60 kWh/m2a (71 % prijenos, 29 % ventilacijski gubici), a izračunani dobici energije iznosili su 35 kWh/m2a (35 % solarni a 65 % interni dobici).
The total heating energy consumption after the retrofit was therefore estimated at 25 kWh/m2a.
Stoga je procijenjeno da ukupna potrošnja energije grijanja nakon obnove iznosi 25 kWh/m2a.
The energy consumption before the retrofit was not measured.
Potrošnja energije nije mjerena prije obnove.
It was calculated for the heating period only.
Ta je potrošnja izračunana samo za razdoblje grijanja.
There was natural ventilation in the offices and the airtightness level was poor.
U uredima se koristila prirodna ventilacija a stupanj zrakopropusnosti nije bio zadovoljavajući.
The measured air exchange rate between the indoor and outdoor areas was 13 h-1 at the pressure difference of 50 Pa. As a consequence, the ventilation heat losses were huge.
Izmjerena stopa izmjene unutarnjeg i vanjskog zraka iznosila je 13 h-1 pri razlici tlaka od 50 Pa. Stoga su gubici topline uslijed prolaska zraka bili golemi.
Considering this, the calculated results for heating energy consumption of the old offices amounted to approximately 143 kWh/m2a.
S obzirom na takvo stanje, izračunana potrošnja energije grijanja u dotadašnjim neobnovljenim uredima iznosila je otprilike 143 kWh/m2a.
The analysis and comprehensive study of one-year measurements in the retrofitted pilot offices equipped with radiant ceiling panels providing heat and cold to the rooms was conducted.
Obavljena je analiza i opsežno istraživanje u okviru kojih su provedena jednogodišnja mjerenja potrošnje energije u obnovljenim pilot-uredima opremljenima isijavajućim stropnim panelima za grijanje i hlađenje analiziranih prostorija.
The complete operation of the system was monitored, and subsequently evaluated.
Ukupan rad sustava je praćen i naknadno analiziran.
Indoor air temperatures, as related to energy released by the ceiling panel system, supported by the ventilation system, were studied.
Analizirane su temperature unutarnjeg zraka u odnosu na energiju generiranu kroz sustav stropnih panela, uz koji je dodatno korišten i ventilacijski sustav.
The efficiency of the radiant heating/cooling ceiling panels (supported by ventilation), installed in the scope of the retrofitting concept adopted for the offices, was confirmed by the analysis results.
Učinkovitost stropnih isijavajućih toplinskih i rashladnih panela (podržanih ventilacijom), instaliranih prema koncepciji obnove koja je usvojena za te urede, potvrđena je kroz rezultate analize.
The daily indoor air temperature oscillations in the rooms, as well as the maximum vertical temperature differences in both the cooling and heating modes, were within the highest comfort range.
Dnevne oscilacije unutarnje temperature zraka u analiziranim prostorijama, isto kao i maksimalne vertikalne temperaturne razlike u postupcima grijanja i hlađenja bile su u skladu s najstrožim zahtjevima udobnosti.
The maximum working day air temperature oscillations were 1.4 K in the heating season and 1.7 K in the cooling season.
Maksimalne oscilacije temperatura zraka u radnom danu iznosile su 1,4 K u sezoni grijanja, a 1,7 K u sezoni hlađenja.
The highest measured vertical temperature difference, measured at noon, was 1.3 K in the typical heating week, whereas the highest measured vertical air temperature difference in the cooling week was 0.6K.
Najviša izmjerena vertikalna temperaturna razlika, određena u podne, iznosila je 1,3 K u tipičnom tjednu grijanja, dok je najveća izmjerena vertikalna temperaturna razlika iznosila 0,6 K u tjednu kada se koristilo hlađenje.
The results of the air temperature differences in the pilot offices equipped with ceiling panels confirmed that the highest category results have been achieved in meeting local thermal criteria for vertical air temperature difference (Category A), both for cooling and heating [19].
Temperaturne razlike dobivene u pilot-uredima koji su opremljen sa stropnim panelima potvrđuju da su postignuti najbolji rezultati u udovoljavanju lokalnim toplinskim kriterijima za vertikalnu razliku u temperaturi zraka (kategorija A), i to kako za grijanje tako i za hlađenje [19].
The heated ceiling temperatures were observed and analysed since people are highly sensitive to radiant asymmetry caused by
Mjerene su i analizirane temperature grijanog stropa jer je ustanovljeno da su korisnici prostora izuzetno osjetljivi na
e.g. warm ceiling.
asimetrično isijavanje koje dolazi primjericer. iz toplog stropa.
The results confirmed compliance with local thermal criteria not only for cooling but also for heating: it may be expected that the radiant temperature asymmetry corresponds to Category C, or better [19].
Rezultati potvrđuju usklađenost s lokalnim toplinskim kriterijima i za grijanje i za hlađenje: može se očekivati da asimetrija isijavanja odgovora kategoriji C ili višoj [19].
It was established that the activity of occupants and some events can also influence operation of the ceiling panels.
Utvrđeno je da aktivnost korisnika prostora i neki događaji također utječu na rad stropnih panela.
On the other hand, the measured values indicated that the radiant ceiling heating/cooling system was fully able to respond quickly and effectively cope with temperature oscillations.
S druge strane, izmjerene vrijednosti pokazuju da se isijavajući stropni toplinski i rashladni sustav može u potpunosti, i to brzo i djelotvorno, suočavati s oscilacijama temperature.
Nevertheless, the frequency, intensity and duration of these events are important.
Međutim, tu je ipak značajna učestalost, intenzitet i trajanje tih događaja.
Further research is needed to define with a higher accuracy which impacts can be compensated, and where the limits of the system are.
Potrebna su stoga dodatna istraživanja da bi se točnije odredilo koji se utjecaji mogu kompenzirati i gdje su granice analiziranog sustava.
Considering the restrictions of the retrofitting measures, the energy needs for tempering the pilot offices were at a very satisfactory level.
S obzirom na ograničenja mjera korištenih za obnovu analiziranih prostorija, može se ustvrditi da je potrošnja energije za temperiranje pilot-ureda bila vrlo zadovoljavajuća.
With 24 kWh/m2a of energy consumption for heating, and 21 kWh/m2a for cooling, the retrofitted pilot offices can be defined as very low-energy offices.
Sa 24 kWh/ m2a potrošnje energije za grijanje te sa 21 kWh/m2a za hlađenje, obnovljeni pilot-uredi svakako ulaze u kategoriju energetski vrlo učinkovitih radnih prostora.
Since large ceilingmounted radiant surfaces use the principle of small temperature differences for heating and cooling, the energy for tempering the indoor environment can be provided quite efficiently.
Kako širokoplošni stropni sustavi rade prema načelu male temperaturne razlike tijekom grijanja i hlađenja, energija potrebna za temperiranje unutarnjih prostora može se koristiti vrlo učinkovito.
Based on experimental and measuring methods, this study proves that the radiant ceiling panels in the retrofitting concept used are operating well in Ljubljana weather conditions.
Utemeljeno na eksperimentalnim i mjernim metodama, ovo istraživanje dokazuje da isijavajući stropni paneli bazirani na korištenom konceptu obnove dobro funkcioniraju u klimatskim uvjetima koji prevladavaju u Ljubljani.
Combined with a ventilation system and good solar protection, they provide a highly satisfactory thermal comfort.
Potpomognuti ventilacijskim sustavom i dobrom zaštitom od sunca, ti paneli nude izuzetno zadovoljavajuću razinu toplinske ugode.
The comprehensive analyses carried out in the scope of this experimental study confirm adequacy of the use of the radiant ceiling panels for both cooling and heating.
Opsežne analize provedene u sklopu ovog eksperimentalnog rada potvrđuju prikladnost upotrebe isijavajućih stropnih panela i za hlađenje i za grijanje.
On the one hand, the study partly justifies generalization of the above presented technical concept while underlying, on the other hand, the necessity for further verifications in a wider spectrum of weather conditions.
S jedne strane, ovo istraživanje djelomično podržava opću primjenu prikazane tehničke koncepcije a, s druge strane, autori ipak upozoravaju na potrebu dodatnih provjera u širem spektru klimatskih uvjeta.
Acknowledgements
Zahvale
The authors would like to thank the European Commission for financial support provided through the EU project Resourceand Cost-Effective Integration of Renewables in Existing High-Rise Buildings, 7FP, 2008-2012, which contributed to the realisation of the pilot demonstration at ZAG.
Autori zahvaljuju Europskoj komisiji na financijskoj podršci dobivenoj u sklopu projekta Europske unije pod nazivom: COST EFFECTIVE, Financijski učinkovita integracija obnovljivih izvora energije u postojeće zgrade, FP7, 2008-2012, što je pridonijelo realizaciji ovog pilot-projekta u ZAG-ovoj zgradi.
Instructions for authors
Upute autorima
Građevinar is a monthly journal that features research and professional papers and other contributions and articles from the field of civil engineering and other related fields.
GRAĐEVINAR je časopis koji objavljuje znanstvene i stručne radove te ostale priloge iz građevinarstva i s njim povezanih područja.
The journal is also the official bulletin of the Croatian Association of Civil Engineers.
Časopis je također i društveno glasilo svih udruga u sastavu Hrvatskoga saveza građevinskih inženjera.
DOCUMENT PREPARATION GUIDELINES
PRIPREMA RADOVA
Template for papers
Predložak za radove
The paper title must be brief (no more than six words), informative and clearly descriptive of the theme treated in the paper.
Naslov članka mora biti koncizan (preporučljivo je najviše 6 riječi), informativan i jasno izražavati sadržaj.
The paper must be devoid of interrogatory or exclamatory sentences, and the authors should restrain from formulating a particular thesis.
U naslovu ne smije biti upitnih ni uskličnih rečenica niti izricanja posebnih teza.
The categorized articles must be preceded by an abstract in which the author will briefly describe the theme treated, procedures applied, and results obtained.
Kategorizirani članci moraju imati sažetak u kojem se ukratko opisuje o čemu se u članku govori, kakvi su postupci primijenjeni i do kojih se rezultata došlo.
The abstract will range from 500 to 520 characters in size.
Sažetak može imati 500 do 520 slovnih znakova.
Below the abstract, the author must formulate 5 to 7 key words that describe main points of the paper.
Uz sažetak treba posebno navesti 5 do 7 ključnih riječi koje ističu glavne pojmove iz članka.
Text must prepared be on A4 paper format with 25mm margins in 10pt Arial font using 1.35 line spacing.
Tekst rada treba pisati na A4 formatu stranice s marginama od 25 mm u 10 point Arial font koristeći 1.35 razmak između redova.
It should be positioned in one column and aligned to both left and right margin (justify).
Tekst je potrebno pisati u jednom stupcu te koristiti obostrano poravnanje teksta.
This format is suitable for the reviewer or language editor notes.
Ovako pripremljen tekst olakšati će postupak lektoriranja i recenzije.
First page should contain a paper title, names of authors (5 authors max.), authors' affiliations, paper abstract and keywords.
Na prvoj stranici rad treba sadržavati naslov, imena autora (maks. pet autora), adresu ustanove ili tvrtke autora, sažetak rada te ključne riječi.
Chapter headings should be aligned to the left and formatted in 12pt Arial bold.
Naslovi poglavlja trebaju imati lijevo poravnanje i pisati ih u 12 pt Arial bold.
Figures (drawings, charts, photographs etc.) can be black-and-white or in colour in JPG, TIFF or BMP file format with a resolution of 300dpi.
Likovni prilozi (dijagrami, crteži, fotografije itd.) mogu biti crno-bijeli ili u boji, u formatima JPG, TIFF ili BMP te razlučivosti 300 dpi.
Vector graphic produced with AutoCAD or similar software should be converted to a popular vector format (wmf, emf, svg) or to JPG, TIFF or BMP raster format with size fitted to article format.
Vektorske grafike rađene AutoCAD-om ili nekim drugim alatom treba priložiti u vektorskom formatu (wmf, emf, svg) ili pretvoriti u JPG, TIFF ili BMP format te ih uklopiti u sadržaj teksta.
Photographs, if any, should be prepared in adequate resolution (300 dpi).
Fotografije, ako ih ima u tekstu, trebaju biti kvalitetno priređene.
Every figure or table should be numbered, titled and positioned in the article.
Svi likovni prilozi i tablice moraju imati naslov, biti numerirani i pozicionirani u članku.
The reference must be presented in chronological order, in the order it is referred to in the text.
Naslov časopisa, knjige ili zbornika konferencije potrebno je pisati u italic formi.
For citations in the text please use square brackets and numbers: [1], [2].
Za navod u tekstu koristiti uglate zagrade i brojeve, kao npr: [1], [2].
The first citation in the text should correspond with the first name on the reference list.
Literaturu treba svrstati onim redom kojim se navodi u tekstu, tj. prvi navod u tekstu treba biti usklađen s prvim navodom u poglavlju Literatura.
Popp, K., Kruse, H., Kaiser, I.: Vehicle-Track Dynamics in the Mid Frequency Range, Vehicle System Dynamics, 31, pp. 423-464, 1999.
Ivšić, T., Bačić, M., Librić, L.: Procjene nosivosti i slijeganja bušenih pilota u mekim tlima, GRAĐEVINAR 65 (2013) 10, pp. 901-918.
Schwager, T., Poschel, T.: Rigid Body Dynamics of Railway Ballast (Chapter), System Dynamics and Long-Term Behaviour of Railway Vehicles, Track and Subgrade, eds.
Schwager, T., Poschel, T.: Rigid Body Dynamics of Railway Ballast (Chapter), System Dynamics and Long-Term Behaviour of Railway Vehicles, Track and Subgrade, (ur.
K. Popp & W. Schiehlen, Springer-Verlag, Berlin and New York, pp. 451-470, 2002.
Popp, K., Schiehlen, W.), Springer-Verlag, Berlin and New York, pp.451-470, 2002.
Person, A.: Personal communication, 20 November 2008, Position of Person in Company, Name of Company or University, City, Country.
Prezime, A.: Osobna komunikacija, 20. studenoga 2008., Pozicija osobe u tvrtki, Naziv tvrtke ili sveučilišta, Grad, Država.
APS-The street level power supply, www.transport.alstom.com , dd.mm.yyyy.
APS-The street level power supply, www.transport.alstom.com
SCIENTIFIC AND PROFESSIONAL PAPERS
ZNANSTVENI I STRUČNI ČLANCI