Three (3) criteria must be met by both sources for it to be considered synchronized or in-sync.
The phased difference between the sources must be less than 5 degrees.
The frequency difference must be less than 0.2Hz,
The voltage difference must be less than 5%.
Note: These parameters are displayed. The controller waits for the sources to become in-sync.
Reference: Page 26 of Group 5 Controller Manual 381333-126
For further questions, you may send your inquiry to technicalsupport@ascopower.com or Contact 1.800.800.ASCO (2726).
Published for:ASCO Power Technologies USA