The connections from S1 and S2 on the current transformer to I+, and I- on the back of the meter might be reversed, ensure that the wiring of the meter is correct as per the user manual
Incase of using a stand alone CTs, ensure the P2 is facing the load
Ensure that the meter has been programmed (e.g CT ratio , System Type)
S1 and S2 connections may still have the link in, (Please remove this while power is OFF)
Please note that this relates to all Meters from the Power Logic PM5000 range.
Released for:Schneider Electric Ireland