It depends on the UPS technology. For Off-Line UPS it is unaffordable to back-up such inrush current. The UPS will go into Fault Mode and shutdown immediately (unless the UPS is already oversized). For Line-Interactive, it applies the same, unless the waveform is pure sine wave. Because all On-Line models deliver pure sine wave, they can also work with APFC with no problem.