EBO system processes data from third party LonWorks devices according definition by Device Template which is imported to a Building Operation Server (ES/AS-P).
In case SNVTs types visible in EBO don't match with SNVTs in TAC Vista database after conversion procedure was done, there must be discrepancy in XIF files which have been imported in advance.
Check up Network Variable index numbers for particular SNVTs which do not match after conversion against XIF files.
Make XIF file correction manually following LonMark org Technical Resource guide
http;//www.lonmark.org/technical_resources/resource_files/1500/snvt.pdf
Released for:Schneider Electric Ireland