Yes, if fire protection is required in your planning, SHERPA goods lifts doors can be delivered compliant with EN 81-58. Depending on the requirements, various performance criteria such as space enclosure (E), thermal insulation (I) and radiation (W) with corresponding classification times can be selected for the shaft doors.
As standard, our shaft end doors have an approval according to EN81-58 with the classification E120, EI05, EW30 or E120, EI15, EW60. This means that the goods lift can be installed in a fire-resistant shaft on site according to DIN 4102 (EN 13401-1). The steel shaft is attached to the on-site fire-resistant shaft using brackets. In front of the inspection hatch, a separate inspection hatch must be installed in the fire-resistant shaft on site in accordance with the fire protection regulations, which ensures both the fire protection requirement and the accessibility to the inspection hatch. Detailed information is available on page 13 of our planning guide.