The SpeeTube heating hoses Ø10 and Ø12 mm are connected to the distributor using PushFit couplings.
There are three types of PushFit couplings: single, double (splitter) and repair couplings. The couplings are 3/4” euroconus fittings.
The PushFit splitter allows for two heating hose groups to be connected to a single distributor group. Two groups connected to a single splitter must be of equal length.
The diameter of the supply and return lines to the central heating boiler or district heating:
distributors for up to 7 groups: minimum Ø 15 mm, connection ½".
distributors for 8 or more groups: minimum Ø 20 mm, connection¾".
The diameter of the supply and return lines to the heat pump or LTHW: ask the supplier for the specific system specifications.
Please note: WARP Systems cannot connect the system to the primary heating source. This must always be done by a certified plumber.