The simplest means of protecting power factor capacitors from the harmful effects of harmonics is to use “detuned PF capacitors”. These capacitors include a series connected reactor that increases the capacitor impedance (ohms) at typical harmonic frequencies. For three phase systems, the best protection is typically achieved with 7% detuning, where the ohms of the reactor equal 7% of the capacitor ohms.