The APR Control can protect against the problems related to clogged filters, which will, for example, cause airflow across the evaporator coil to be reduced causing a drop in suction pressure which will eventually result in coil frosting. The APR will maintain suction pressure by modulating refrigerant flow reducing capacity at the evaporator. Proper and regular equipment maintenance will eliminate this problem.