Issue:
After upgrading to SU v2.2.0.1, event log shows multiple bypass events, even on UPS systems that do not support bypass
Product Line:
SU application module for Network Management Card 3 devices
Cause:
This is caused by an NMC firmware bug
Resolution:
This issue has been addressed in SU v2.2.1.1. To resolve, please update to at least v2.2.1.1 (attached to this article), or search apc.com for the latest firmware version.
Released for:APC Norway