E9 means that the valve cannot close. So it is not an error in the thermostat itself, but rather a message that there is something wrong in the installation.
Possible sources of the error could be incorrect installation, the wrong adapter, or dirt in the valve. If necessary, get help with troubleshooting from a heating installer.