Yes, an independent third party test was conducted to evaluate the use of harmonic filters on bypass systems. The concern is to ensure the series inductor does not provide too excessive of a line voltage drop to prevent proper operation of the bypass control contactors. A 75 HP NEMA design A motor and drive package with a bypass option was tested. Extensive testing showed that the voltage drop across the 480/120 volt control power transformer being caused by the series reactor was approximately 10% at full load which was well within the contactor coils dropout rating. The bypass circuit worked very well and the results concluded that a harmonic filter can be used with a standard drive/bypass configuration without any special system modifications.