The depth is measured from the surface of the ground to the top of the pipe, which would provide the required one foot of earth coverage for the entire pipe, as required by Sections 313.5 and 718.2 of the 2024 Uniform Plumbing Code. 2. It is the opinion of this committee that the clearances would be measured edge to edge.