Not recommended. Please consider using an NOC module. The service port does not support Rapid Spanning Tree Protocol and as a result the connection of each of these ports to a SCADA can result in an excessive amount of broadcast or ARP traffic.
We recommend using the NOC option module for SCADA in HSBY applications.
Released for:Schneider Electric Canada