# Experimental Acoustic Evaluation of an Auditorium

Authors: Marina Dana Ţopa; Norbert Toma; Botond Sandor Kirei; Ioana Sărăcuţ; Angelo Farina
Journal: Advances in Acoustics and Vibration
 (2012)

---

## Abstract

The paper presents a case history: the acoustical analysis of a rectangular auditorium. The following acoustical parameters were evaluated: early decay time, reverberation time, clarity, definition, and center time. The excitation signal was linear sweep sine and additional analysis was carried out: peak-to-noise ratio, reverberation time for empty and occupied room, standard deviation of acoustical parameters, diffusion, and just noticeable differences analysis. Conclusions about room’s destination and modeling were drawn in the end.


---

## Body

## 1. Introduction

Nowadays, the most important events (conferences, concerts) take place in enclosed spaces, where the sound waves are reflected from the walls, ceiling, and floor, giving birth to the reverberation phenomenon [1–3]. This phenomenon can be evaluated subjectively as pleasant (in a concert hall, it can contribute to spatial sensation for music listeners) or irritating (in a conference hall, it could be a factor of unintelligibility of speech).An objective classification is achieved with acoustical parameters extracted from the impulse response of the room [4–7]. Thus, accurate impulse response measurements, already regulated by ISO 3382 standard, are desired for the assessment of acoustical properties. In our work, we chose to measure the impulse response using a linear sweep sine as excitation and compute the acoustical parameters with professional software.The paper is dedicated to the acoustic evaluation of an auditorium. The acoustical parameters of the room were computed in several points. The destination of the room was provided by the analysis altogether with information about the minimum measurement points.The paper is organized as follows. Section2 presents the objective acoustical parameters used to evaluate the properties of a room as well as the relation between objective and subjective (perceptual) parameters. Section 3 describes the equipment used to evaluate the acoustics as well as the software for processing the measured samples. Section 4 is dedicated to the estimation of acoustical properties of the analyzed auditorium. The last section presents the final conclusions altogether with the comments related to the acoustical properties of the auditorium.


## 2. Evaluated Acoustical Parameters

### 2.1. Objective Parameters

The acoustical parameter evaluation is based upon the measurement of the impulse responseh(t) and the computation of the energy decay curve (EDC) [4]:
(1)EDC(t)=∫t∞h2(τ)dτ.The EDC is the graphical representation of the decay of the sound pressure level in a room with respect to time, after the sound source has stopped. It is possible to measure this decay either after the actual cutoff of a continuous sound source in the room or derived from the reverse-time integrated squared impulse response of the room. EDC for each octave band is obtained by a backward integration of the squared impulse response. The impulse response is the temporal evolution of the sound pressure observed at a point in a room as a result of the emission of a Dirac impulse at another point in the room. It is impossible in practice to create and radiate true Dirac delta functions, but short transient sounds (e.g., from gunshots) can offer close enough approximations for practical measurement. An alternative measurement technique, however, is to use a deterministic, wide-band signal like a sine sweep and transform the measured response back to an impulse response. Several quantities that can be obtained from measured impulse responses are correlated with particular subjective aspects of the acoustical character of an auditorium [4].The reverberation time(RT) is the basic indicator of acoustical behavior and is the time required for the EDC to decay by 60 dB. It can be evaluated on a smaller dynamic range than 60 dB and then extrapolated to a 60 dB decay time. It is then labeled accordingly. Thus, if RT is derived from the average slope of the decay in the range between 5 dB and 25 dB below the initial level, it is accordingly labeled  T20. If the range is between 5 dB and 35 dB, then the corresponding time is labeled T30 [4].If the RT is measured in an unoccupied room, then to obtain the value for the occupied one, the following correction should be made [8]:
(2)RTo=RT-DT,
where RTo is the estimated RT when the enclosure is occupied and DT is the Schultz diffusion time, that is, the estimated change in RT values from the equations (see Table 1) [8].Table 1
Schultz’s estimated change in RT values.
Frequency (Hz)
DT (s)
125
0.510 RT–0.708
250
0.605 RT–0.867
500
0.668 RT–0.929
1000
0.696 RT–0.935
2000
0.694 RT–0.889
4000
0.652 RT–0.752Barron [9] lists a range of recommended occupied reverberation times suited to different types of music or speech (Table 2).Table 2
Recommended occupied reverberation times.
Type of music (speech)
Recommended RT (s)
Organ music
>2.5
Romantic classical music
1.8–2.2
Early classical music
1.6–1.8
Opera
1.3–1.8
Chamber music
1.4–1.7
Drama theatre
0.7–1.0In Table2, the value quoted for the RT refers to the mid-frequency value, averaged at 500 and 1000 Hz. The “optimal” reverberation time depends on the type and style of the music [1, 10].The early decay time(EDT) is defined as the reverberation time computed by the slope of the decay in the range between 0 and –10 dB on the EDC [3]. The slope is evaluated by a linear regression line fitted over the appropriate portion of the decay curve [4]. The EDT is strongly influenced by early reflections, thus depends on the measuring position and the room’s geometry. The associated subjective sensation of reverberation (perceived reverberation) is strongly correlated with EDT. The EDT is expected to have the same value as the reverberation time for a room exhibiting perfectly linear decay.Clarity index
(
C
t
e
) is an early-to-late arriving sound energy rati
(3)Cte=10·lg[∫0teh2(t)·dt∫te∞h2(t)·dt],
where te is the early time limit, specified to be either 50 ms or 80 ms; C80 is usually considered relevant for music, C50 for speech. The value for C80 is obtained as the average of the 500 Hz, 1000 Hz, and 2000 Hz values. It can range from small positive numbers for a dead room to small negative values for very reverberant spaces. Generally, the optimal value of C80 for orchestral music is between 0 to −3 dB and for singers it is between 1 and 5 dB [11].Definition
(
D
50
) measures the early to total sound energy ratio. D50 is mostly used for the speech case:
(4)D50=∫050msh2(t)·dt∫0∞h2(t)·dt[%].
It is evaluated in the 4 octave frequency (500 Hz, 1000 Hz, 2000 Hz, 4000 Hz) and should have values above 50% for good speech intelligibility [12].The center time
(
T
s
) corresponds to the center of gravity of the squared impulse response:
(5)Ts=∫0∞t·h2(t)·dt∫0∞h2(t)·dt[s].Ts avoids the discrete division of the impulse response into early and late periods [4]. For speech, the desirable Ts is in the range of 60 ms–80 ms in the 4 relevant octave bands (500 Hz, 1000 Hz, 2000 Hz, and 4000 Hz). For music, the desirable Ts is in the range of 70 ms–150 ms in the 1000 Hz octave band [12].


### 2.2. Relation between Objective and Subjective Parameters

Subjective studies of the acoustic characteristics of auditoria have shown that several quantities that can be obtained from measured impulse responses are correlated with particular subjective aspects of the acoustic character of an auditorium. While the reverberation time is a fundamental description of the acoustic character of an auditorium, the other quantities provide additional information on the acoustic conditions in the auditorium. Albeit dozens of additional acoustical descriptors have been defined, here only the parameters that have been found to be subjectively important and that can be obtained directly from integrating impulse responses are considered [4]. The just noticeable difference (JND) is the smallest change in a parameter that is necessary for a human to detect a difference. Table 3 presents the analyzed parameters and the associated JND values [4]. These values are computed at the midrange frequency (average at 500 Hz and 1000 Hz).Table 3
Acoustical parameters and their JND values.
Subjective listener aspect
Acoustical parameter
Just noticeable difference (JND)
Perceived reverberance
EDT
5%
Perceived clarity of sound
ClarityC80
1 dB
DefinitionD50
5%
T
s
10 ms


## 2.1. Objective Parameters

The acoustical parameter evaluation is based upon the measurement of the impulse responseh(t) and the computation of the energy decay curve (EDC) [4]:
(1)EDC(t)=∫t∞h2(τ)dτ.The EDC is the graphical representation of the decay of the sound pressure level in a room with respect to time, after the sound source has stopped. It is possible to measure this decay either after the actual cutoff of a continuous sound source in the room or derived from the reverse-time integrated squared impulse response of the room. EDC for each octave band is obtained by a backward integration of the squared impulse response. The impulse response is the temporal evolution of the sound pressure observed at a point in a room as a result of the emission of a Dirac impulse at another point in the room. It is impossible in practice to create and radiate true Dirac delta functions, but short transient sounds (e.g., from gunshots) can offer close enough approximations for practical measurement. An alternative measurement technique, however, is to use a deterministic, wide-band signal like a sine sweep and transform the measured response back to an impulse response. Several quantities that can be obtained from measured impulse responses are correlated with particular subjective aspects of the acoustical character of an auditorium [4].The reverberation time(RT) is the basic indicator of acoustical behavior and is the time required for the EDC to decay by 60 dB. It can be evaluated on a smaller dynamic range than 60 dB and then extrapolated to a 60 dB decay time. It is then labeled accordingly. Thus, if RT is derived from the average slope of the decay in the range between 5 dB and 25 dB below the initial level, it is accordingly labeled  T20. If the range is between 5 dB and 35 dB, then the corresponding time is labeled T30 [4].If the RT is measured in an unoccupied room, then to obtain the value for the occupied one, the following correction should be made [8]:
(2)RTo=RT-DT,
where RTo is the estimated RT when the enclosure is occupied and DT is the Schultz diffusion time, that is, the estimated change in RT values from the equations (see Table 1) [8].Table 1
Schultz’s estimated change in RT values.
Frequency (Hz)
DT (s)
125
0.510 RT–0.708
250
0.605 RT–0.867
500
0.668 RT–0.929
1000
0.696 RT–0.935
2000
0.694 RT–0.889
4000
0.652 RT–0.752Barron [9] lists a range of recommended occupied reverberation times suited to different types of music or speech (Table 2).Table 2
Recommended occupied reverberation times.
Type of music (speech)
Recommended RT (s)
Organ music
>2.5
Romantic classical music
1.8–2.2
Early classical music
1.6–1.8
Opera
1.3–1.8
Chamber music
1.4–1.7
Drama theatre
0.7–1.0In Table2, the value quoted for the RT refers to the mid-frequency value, averaged at 500 and 1000 Hz. The “optimal” reverberation time depends on the type and style of the music [1, 10].The early decay time(EDT) is defined as the reverberation time computed by the slope of the decay in the range between 0 and –10 dB on the EDC [3]. The slope is evaluated by a linear regression line fitted over the appropriate portion of the decay curve [4]. The EDT is strongly influenced by early reflections, thus depends on the measuring position and the room’s geometry. The associated subjective sensation of reverberation (perceived reverberation) is strongly correlated with EDT. The EDT is expected to have the same value as the reverberation time for a room exhibiting perfectly linear decay.Clarity index
(
C
t
e
) is an early-to-late arriving sound energy rati
(3)Cte=10·lg[∫0teh2(t)·dt∫te∞h2(t)·dt],
where te is the early time limit, specified to be either 50 ms or 80 ms; C80 is usually considered relevant for music, C50 for speech. The value for C80 is obtained as the average of the 500 Hz, 1000 Hz, and 2000 Hz values. It can range from small positive numbers for a dead room to small negative values for very reverberant spaces. Generally, the optimal value of C80 for orchestral music is between 0 to −3 dB and for singers it is between 1 and 5 dB [11].Definition
(
D
50
) measures the early to total sound energy ratio. D50 is mostly used for the speech case:
(4)D50=∫050msh2(t)·dt∫0∞h2(t)·dt[%].
It is evaluated in the 4 octave frequency (500 Hz, 1000 Hz, 2000 Hz, 4000 Hz) and should have values above 50% for good speech intelligibility [12].The center time
(
T
s
) corresponds to the center of gravity of the squared impulse response:
(5)Ts=∫0∞t·h2(t)·dt∫0∞h2(t)·dt[s].Ts avoids the discrete division of the impulse response into early and late periods [4]. For speech, the desirable Ts is in the range of 60 ms–80 ms in the 4 relevant octave bands (500 Hz, 1000 Hz, 2000 Hz, and 4000 Hz). For music, the desirable Ts is in the range of 70 ms–150 ms in the 1000 Hz octave band [12].


## 2.2. Relation between Objective and Subjective Parameters

Subjective studies of the acoustic characteristics of auditoria have shown that several quantities that can be obtained from measured impulse responses are correlated with particular subjective aspects of the acoustic character of an auditorium. While the reverberation time is a fundamental description of the acoustic character of an auditorium, the other quantities provide additional information on the acoustic conditions in the auditorium. Albeit dozens of additional acoustical descriptors have been defined, here only the parameters that have been found to be subjectively important and that can be obtained directly from integrating impulse responses are considered [4]. The just noticeable difference (JND) is the smallest change in a parameter that is necessary for a human to detect a difference. Table 3 presents the analyzed parameters and the associated JND values [4]. These values are computed at the midrange frequency (average at 500 Hz and 1000 Hz).Table 3
Acoustical parameters and their JND values.
Subjective listener aspect
Acoustical parameter
Just noticeable difference (JND)
Perceived reverberance
EDT
5%
Perceived clarity of sound
ClarityC80
1 dB
DefinitionD50
5%
T
s
10 ms


## 3. Measurement Setup and Software

The acoustical parameter evaluation requires the following steps:(i)
Measure the room impulse responseh(t)—in our experiments the following equipments were used.
(a)
an omnidirectional microphone (PCB 130D20), having a diaphragm diameter of 7 mm (according to the ISO 3382, the microphone should have a maximum diaphragm diameter of 13 mm);(b)
a B&K omnidirectional sound source type 4295 (dodecahedron loudspeaker);(c)
a B&K audio power amplifier, rated at 100 W RMS, stereo, type 2716-C;(d)
a laptop, incorporating a Soundmax Integrated Digital Audio sound card from Analog Devices.(ii)
Measure the RT using the Delta Ohm HD 2010 sound lever meter/real-time spectrum analyzer, with the associated Delta Log 5 software that measures the RT values in octave frequency bands.(iii)
Estimation of the acoustical parameters—the processing of measurements was done with the B&K Dirac software.


## 4. The Evaluation of Acoustical Parameters in the Auditorium

### 4.1. The Evaluated Points and Setups

The analyzed room is an auditorium of the Technical University of Cluj Napoca (Romania), with the volume of approximately 1326 m3, the walls are covered with absorbing materials as wood and plexiglass. The auditorium plan is presented in Figure 1. The furniture consists of wooden benches and seats; there are about 300 seats in the hall. The room was newly arranged as an auditorium; previously it was a sport room, so the acoustics had to be checked and if possible improved.Figure 1
The plan of the auditorium.The impulse response measurements were performed using the instruments listed in the previous section and a 2.97 s linear sweep sine signal was applied. The advantages of the omnidirectional loudspeaker sound source measuring method are the omnidirectionality corresponding with ISO 3382 standard and good repeatability as well as ecological efficacy. The loudspeaker was placed at 1.50 m height above the floor in two positions: S1 and S2, indicated in Figure1 by white large circles. The RT was also evaluated using a phonometer. The measurements were done in 15 spots pointed out by small white circles in Figure 1. The microphone was placed at a height of 1.2 m above the floor in the audience seat locations to respect the ISO 3382. In every spot, 5 measurements were made with both source positions and the resulting values are means of the measurements. The data processing was executed with the programs Dirac and Delta Log 5 (for phonometer).


### 4.2. Peak-to-Noise Ratio Analysis

The Peak-to-noise ratio (PNR) is defined as the difference between the maximum peak impulse response level and the root mean square (RMS) noise level, in dB. It reflects the decay range, which according toISO 3382should be at least 35 dB or 45 dB for accurate determination of T20 or T30, respectively. Next to a visual inspection of the impulse response, the PNR can be used to judge the quality of a recording. Table 4 presents the PNR values for the analyzed samples for two source position.Table 4
Standard deviation of PNR (a) the source situated in S1 and (b) the source situated in S2.
(a)
Frequency (Hz)
Average value PNR (dB)
Standard deviation PNR (dB)
125
44
2
250
49
2
500
52
2
1000
54
3
2000
59
3
4000
60
1
(b)
Frequency (Hz)
Average value PNR (dB)
Standard deviation PNR (dB)
125
42
2
250
49
1
500
52
2
1000
53
3
2000
58
2
4000
60
1The average value of the PNR at 125 Hz is below 45 dB, value imposed by the ISO 3382 standard forT30measurements. But due to the fact that the parameters are significant for frequencies above 500 Hz and for these frequencies PNR exceeds 50 dB, the acoustical evaluation of the room may be accomplished.


### 4.3. The Standard Deviation of Acoustical Parameters

The standard deviation of reverberation time was determined to provide a measure of accuracy and the spatial variance of the reverberation time. Their values are presented in Tables5 and 6, using the omnidirectional loudspeaker or the phonometer. It is remarkable that the values of standard deviation from Tables 5 and 6 never exceed 1 JND, being around 2% at 500 Hz and 1000 Hz.Table 5
Standard deviation of reverberation time measured with an omnidirectional loudspeaker (a) the source situated in S1 and (b) the source situated in S2.
(a)
Frequency(Hz)
Average value RT (s)
Standard deviation RT (s)
125
2.949
0.148
250
3.017
0.095
500
2.19
0.034
1000
1.944
0.042
2000
1.776
0.035
4000
1.498
0.035
(b)
Freq(Hz)
Average value RT (s)
Standard deviation RT (s)
125
2.975
0.163
250
3.026
0.137
500
2.187
0.048
1000
1.949
0.044
2000
1.771
0.025
4000
1.475
0.023Table 6
Standard deviation of reverberation time measured with the HD 2010 SLM for the source situated in S1.
Freq(Hz)
Average value RT (s)
Standard deviation RT (s)
125
3.048
0.158
250
3.028
0.088
500
2.144
0.039
1000
1.945
0.028
2000
1.829
0.022
4000
1.569
0.017The standard deviation analysis for the other acoustical parameters for the same frequencies, 500 Hz and 1000 Hz, is presented in Tables7, 8, 9, 10, 11, 12, 13, and 14. The 0.00 value from Tables 9, 11, and 12 denotes a standard deviation below 0.01. None of the measured values from Tables 7–14 exceeds 1 JND.Table 7
Standard deviation of EDT for the source situated in S1.
f (Hz)
Standard deviation EDT (s)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.002
0.014
0.008
0.028
0.003
0.012
0.012
0.017
0.007
0.004
0.005
0.009
0.008
0.009
0.004
1000
0.001
0.002
0.008
0.081
0.006
0.005
0.008
0.014
0.007
0.003
0.001
0.02
0.005
0.005
0.009Table 8
Standard deviation of EDT for the source situated in S2.
f (Hz)
Standard deviation EDT (s)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.005
0.011
0.005
0.004
0.002
0.006
0.005
0.009
0.008
0.006
0.005
0.006
0.005
0.007
0.009
1000
0.004
0.007
0.003
0.007
0.015
0.006
0.015
0.015
0.006
0.008
0.01
0.007
0.01
0.004
0.014Table 9
Standard deviation ofC80 for the source situated in S1.
f (Hz)
Standard deviationC80 (dB)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.01
0.02
0.01
0.03
0.03
0.02
0.01
0.07
0.02
0.01
0.01
0.02
0.01
0.02
0.01
1000
0.01
0.01
0.02
0.08
0.01
0.02
0.03
0.05
0.05
0.05
0.04
0.02
0.04
0.00
0.04Table 10
Standard deviation ofC80 for the source situated in S2.
f (Hz)
Standard deviationC80 (dB)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.01
0.03
0.01
0.02
0.01
0.01
0.04
0.04
0.02
0.03
0.01
0.03
0.08
0.03
0.02
1000
0.02
0.02
0.01
0.03
0.01
0.01
0.09
0.05
0.03
0.03
0.03
0.03
0.02
0.04
0.03Table 11
Standard deviation ofD50 for the source situated in S1.
f (Hz)
Standard deviationD50 (%)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.00
0.00
0.00
0.01
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
1000
0.00
0.00
0.00
0.01
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00Table 12
Standard deviation ofD50 for the source situated in S2.
f (Hz)
Standard deviationD50 (%)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
1000
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00Table 13
Standard deviation ofTs for the source situated in S1.
f (Hz)
Standard deviationTs (ms)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.1
0.5
0.2
1
0
0.3
0.4
0.3
0.2
0.1
0.3
0.2
0.3
0.2
0.1
1000
0.1
0.1
0.2
1.8
0.1
0.2
0.2
0.3
0.5
0.4
0.1
0.9
0.1
0.2
0.3Table 14
Standard deviation ofTs for the source situated in S2.
f (Hz)
Standard deviationTs (ms)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.3
0.3
0.1
0.1
0.1
0.1
0.2
0.6
0.1
0.4
0.3
0.2
0.1
0.5
0.2
1000
0.1
0.2
0.1
0.5
0.5
0.1
0.4
1.1
0.2
0.4
0.4
0.4
0.4
0.4
0.2


### 4.4. Estimation of the Reverberation Time in the Occupied Room

Using relation (2) one can estimate the occupied reverberation time: RTo=1.59 s independently of the source position or evaluation equipment. The value of RT places the auditorium in the category of rooms which are designed to opera and chamber music events. It is generally considered tolerable, if not favorable, to have an increase of the RT in the low frequency range (below 500 Hz). On the other hand, there are several concert halls with RTs which do not increase at low frequencies or which even have a slightly decreasing RT and are considered to be excellent from an acoustical point of view [1]. For speech, a decrease of RT is desirable in this frequency range [9, 12]. Due to the increased values of reverberation time at low frequencies (below 500 Hz), a “warmth” sensation for music will appear in this auditorium.


### 4.5. Diffusion Analysis

The diffuseness or directedness of enclosures is indicated byEDT/T30 ratio at mid frequencies. For the audience, a lack of diffusion may be heard as poor balance and blend between the various sections [9]. In a highly diffuse hall, where the decay is completely linear, the EDT/T30 ratio tends to have a value close to 1, that means that EDT and RT are almost equal [9, 13]. The mean value of EDT/T30 gives a global evaluation of the diffuseness or directedness. Good diffuseness is obtained when the mean EDT/T30 ratio takes values between 0.8 and 1.1 [13]. In the case of the auditorium, the mean EDT/T30 ratio for S1 is 0.9973 s and for S2 is 1.0160 s (almost ideal values).Particularly, using the microphone positions dependentEDT/T30 ratio, one can determine prominent directional or diffuse locations. Regarding to the spatial variation of EDT (Figure 2), a general conclusion can be made: where the EDT has maximal values, the locations are diffuse (the EDT/T30 values are close to 1.1), whereas minimal values indicate a directional sound field. This assertion can be made due to the relative constant spatial RT. Tables 15 and 16 present EDT/T30 ratios for both source positions. From the tables one can conclude that the auditorium is diffuse and does not have excessively directional spots (the ratio is above 0.8). Three excessively diffuse locations were found for the S1 source position (12, 13, and 15) and for S2 position a single location was identified.Table 15
EDT
/
T
30 ratio for the source situated in S1.
Microphoneposition
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
EDT/T30
0.91
0.85
0.83
0.98
0.93
0.91
1.03
0.92
1.02
1.04
1.04
1.13
1.14
1.09
1.14Table 16
EDT
/
T
30 ratio for the source situated in S2.
Microphoneposition
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
EDT/T30
0.94
0.85
1.01
0.90
0.98
1.10
1.00
1.09
1.04
1.01
1.00
1.06
1.08
1.08
1.10Measured acoustical parameters in the microphone positions and their JND values (indicated by error bars) for (a) the S1 source position and (b) the S2 source position.
(a)
(b)In a directed design in which early sound is reflected into the audience, where a sagging decay is obtained, theEDT/T30 ratio tends to be lower than 1. Ballooning decay indicates an EDT/T30 ratio that exceeds 1, so the enclosure is described as excessively diffuse [13, 14]. Figure 3(a) presents the decay curve for the 2nd microphone position, where EDT<T30 reveals a sagging decay. Figure 3(b) indicates the decay of the 13th microphone position where EDT>T30 exposes a ballooning decay at 500 Hz. The slope of the EDT is presented by a parallel dashed line to the decay curve.Decay curves for (a) the 2nd microphone position and (b) the 13th microphone position.
(a)
(b)


### 4.6. JND Analysis

Accurate evaluation of acoustical parameters can be achieved with the examination of spatial variations as well as their JND values. It is a useful way to model the room acoustics using reverberators. Reverberators are spatial effect generators [15]. Because we cannot build a reverberator for every point in the measured space, one have to try to reduce the implementation complexity using the JND terms.Let us recall Figure2 to illustrate the acoustical parameters and their JND values for mid-frequency range (average 500 Hz and 1000 Hz) and also two offset values marked with error bars, one with the measured values +JND, the other is the measured value −JND. This plots make it easy to understand if the spatial variation of the parameter is significant or not as well as their perceptually aspects. The EDT and Ts are correlated, whereas EDT is inverse correlated with  C80; similar results were found in [9, 13]. The sensitivity of the acoustical parameters to the source positions at mid frequencies are observed by comparing the two columns of Figure 2. (i)
ForT30, one cannot found any locations where the variations exceed 1 JND for the two excitation locations;(ii)
EDT has a variation that exceeds 1 JND for the following locations: 1, 3, 4, 5, 6, 8, 12, and 13;(iii)
C80 has a variation that exceeds 1 JND for the following locations: 2, 9, and 12;(iv)
D50 has a variation that exceeds 1 JND for the following locations: 1, 2, 3, 4, and 9;(v)
Ts has a variation that exceeds 1 JND for the following locations: 1, 2, 6, 8, 9, and 14.For the auditorium, the center time is the most sensitive acoustical parameter and the clarity is the least sensitive with respect to the excitation source position.An enhanced evaluation and analyses are obtained by pairing of acoustical parameters based on perceived reverberation and clarity. One can try to identify a number of regions in the room where EDT and clarity are the same (the variation of the acoustical parameters not exceeding 1 JND) (Figure2). This can be achieved separately for S1 and S2 or together for the two source positions.Considering the source placed in S1, one can find 11 regions with the same subjective reverberation and clarity sensation. To model these acoustical features, 11 reverberators are necessary instead of 15 (the total number of considered measuring positions); this means a reduction of 26.66%.If the source is placed in S2, we obtained 9 regions with the same subjective reverberation and clarity sensation. In this case, the acoustical modeling will require 9 reverberators instead of 15, that is, a reduction of 40%.If we want to consider the source placed to S1 or S2, we obtained 12 regions, so a reduction of the necessary reverberators is of 20%.One can observe that the reduction in this last case is lower than in the previous cases. This is due to the huge acoustical differences between samples of regions, for instance, the samples situated at the front of the hall with respect to the end ones.


## 4.1. The Evaluated Points and Setups

The analyzed room is an auditorium of the Technical University of Cluj Napoca (Romania), with the volume of approximately 1326 m3, the walls are covered with absorbing materials as wood and plexiglass. The auditorium plan is presented in Figure 1. The furniture consists of wooden benches and seats; there are about 300 seats in the hall. The room was newly arranged as an auditorium; previously it was a sport room, so the acoustics had to be checked and if possible improved.Figure 1
The plan of the auditorium.The impulse response measurements were performed using the instruments listed in the previous section and a 2.97 s linear sweep sine signal was applied. The advantages of the omnidirectional loudspeaker sound source measuring method are the omnidirectionality corresponding with ISO 3382 standard and good repeatability as well as ecological efficacy. The loudspeaker was placed at 1.50 m height above the floor in two positions: S1 and S2, indicated in Figure1 by white large circles. The RT was also evaluated using a phonometer. The measurements were done in 15 spots pointed out by small white circles in Figure 1. The microphone was placed at a height of 1.2 m above the floor in the audience seat locations to respect the ISO 3382. In every spot, 5 measurements were made with both source positions and the resulting values are means of the measurements. The data processing was executed with the programs Dirac and Delta Log 5 (for phonometer).


## 4.2. Peak-to-Noise Ratio Analysis

The Peak-to-noise ratio (PNR) is defined as the difference between the maximum peak impulse response level and the root mean square (RMS) noise level, in dB. It reflects the decay range, which according toISO 3382should be at least 35 dB or 45 dB for accurate determination of T20 or T30, respectively. Next to a visual inspection of the impulse response, the PNR can be used to judge the quality of a recording. Table 4 presents the PNR values for the analyzed samples for two source position.Table 4
Standard deviation of PNR (a) the source situated in S1 and (b) the source situated in S2.
(a)
Frequency (Hz)
Average value PNR (dB)
Standard deviation PNR (dB)
125
44
2
250
49
2
500
52
2
1000
54
3
2000
59
3
4000
60
1
(b)
Frequency (Hz)
Average value PNR (dB)
Standard deviation PNR (dB)
125
42
2
250
49
1
500
52
2
1000
53
3
2000
58
2
4000
60
1The average value of the PNR at 125 Hz is below 45 dB, value imposed by the ISO 3382 standard forT30measurements. But due to the fact that the parameters are significant for frequencies above 500 Hz and for these frequencies PNR exceeds 50 dB, the acoustical evaluation of the room may be accomplished.


## 4.3. The Standard Deviation of Acoustical Parameters

The standard deviation of reverberation time was determined to provide a measure of accuracy and the spatial variance of the reverberation time. Their values are presented in Tables5 and 6, using the omnidirectional loudspeaker or the phonometer. It is remarkable that the values of standard deviation from Tables 5 and 6 never exceed 1 JND, being around 2% at 500 Hz and 1000 Hz.Table 5
Standard deviation of reverberation time measured with an omnidirectional loudspeaker (a) the source situated in S1 and (b) the source situated in S2.
(a)
Frequency(Hz)
Average value RT (s)
Standard deviation RT (s)
125
2.949
0.148
250
3.017
0.095
500
2.19
0.034
1000
1.944
0.042
2000
1.776
0.035
4000
1.498
0.035
(b)
Freq(Hz)
Average value RT (s)
Standard deviation RT (s)
125
2.975
0.163
250
3.026
0.137
500
2.187
0.048
1000
1.949
0.044
2000
1.771
0.025
4000
1.475
0.023Table 6
Standard deviation of reverberation time measured with the HD 2010 SLM for the source situated in S1.
Freq(Hz)
Average value RT (s)
Standard deviation RT (s)
125
3.048
0.158
250
3.028
0.088
500
2.144
0.039
1000
1.945
0.028
2000
1.829
0.022
4000
1.569
0.017The standard deviation analysis for the other acoustical parameters for the same frequencies, 500 Hz and 1000 Hz, is presented in Tables7, 8, 9, 10, 11, 12, 13, and 14. The 0.00 value from Tables 9, 11, and 12 denotes a standard deviation below 0.01. None of the measured values from Tables 7–14 exceeds 1 JND.Table 7
Standard deviation of EDT for the source situated in S1.
f (Hz)
Standard deviation EDT (s)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.002
0.014
0.008
0.028
0.003
0.012
0.012
0.017
0.007
0.004
0.005
0.009
0.008
0.009
0.004
1000
0.001
0.002
0.008
0.081
0.006
0.005
0.008
0.014
0.007
0.003
0.001
0.02
0.005
0.005
0.009Table 8
Standard deviation of EDT for the source situated in S2.
f (Hz)
Standard deviation EDT (s)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.005
0.011
0.005
0.004
0.002
0.006
0.005
0.009
0.008
0.006
0.005
0.006
0.005
0.007
0.009
1000
0.004
0.007
0.003
0.007
0.015
0.006
0.015
0.015
0.006
0.008
0.01
0.007
0.01
0.004
0.014Table 9
Standard deviation ofC80 for the source situated in S1.
f (Hz)
Standard deviationC80 (dB)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.01
0.02
0.01
0.03
0.03
0.02
0.01
0.07
0.02
0.01
0.01
0.02
0.01
0.02
0.01
1000
0.01
0.01
0.02
0.08
0.01
0.02
0.03
0.05
0.05
0.05
0.04
0.02
0.04
0.00
0.04Table 10
Standard deviation ofC80 for the source situated in S2.
f (Hz)
Standard deviationC80 (dB)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.01
0.03
0.01
0.02
0.01
0.01
0.04
0.04
0.02
0.03
0.01
0.03
0.08
0.03
0.02
1000
0.02
0.02
0.01
0.03
0.01
0.01
0.09
0.05
0.03
0.03
0.03
0.03
0.02
0.04
0.03Table 11
Standard deviation ofD50 for the source situated in S1.
f (Hz)
Standard deviationD50 (%)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.00
0.00
0.00
0.01
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
1000
0.00
0.00
0.00
0.01
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00Table 12
Standard deviation ofD50 for the source situated in S2.
f (Hz)
Standard deviationD50 (%)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
1000
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00
0.00Table 13
Standard deviation ofTs for the source situated in S1.
f (Hz)
Standard deviationTs (ms)—S1
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.1
0.5
0.2
1
0
0.3
0.4
0.3
0.2
0.1
0.3
0.2
0.3
0.2
0.1
1000
0.1
0.1
0.2
1.8
0.1
0.2
0.2
0.3
0.5
0.4
0.1
0.9
0.1
0.2
0.3Table 14
Standard deviation ofTs for the source situated in S2.
f (Hz)
Standard deviationTs (ms)—S2
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
500
0.3
0.3
0.1
0.1
0.1
0.1
0.2
0.6
0.1
0.4
0.3
0.2
0.1
0.5
0.2
1000
0.1
0.2
0.1
0.5
0.5
0.1
0.4
1.1
0.2
0.4
0.4
0.4
0.4
0.4
0.2


## 4.4. Estimation of the Reverberation Time in the Occupied Room

Using relation (2) one can estimate the occupied reverberation time: RTo=1.59 s independently of the source position or evaluation equipment. The value of RT places the auditorium in the category of rooms which are designed to opera and chamber music events. It is generally considered tolerable, if not favorable, to have an increase of the RT in the low frequency range (below 500 Hz). On the other hand, there are several concert halls with RTs which do not increase at low frequencies or which even have a slightly decreasing RT and are considered to be excellent from an acoustical point of view [1]. For speech, a decrease of RT is desirable in this frequency range [9, 12]. Due to the increased values of reverberation time at low frequencies (below 500 Hz), a “warmth” sensation for music will appear in this auditorium.


## 4.5. Diffusion Analysis

The diffuseness or directedness of enclosures is indicated byEDT/T30 ratio at mid frequencies. For the audience, a lack of diffusion may be heard as poor balance and blend between the various sections [9]. In a highly diffuse hall, where the decay is completely linear, the EDT/T30 ratio tends to have a value close to 1, that means that EDT and RT are almost equal [9, 13]. The mean value of EDT/T30 gives a global evaluation of the diffuseness or directedness. Good diffuseness is obtained when the mean EDT/T30 ratio takes values between 0.8 and 1.1 [13]. In the case of the auditorium, the mean EDT/T30 ratio for S1 is 0.9973 s and for S2 is 1.0160 s (almost ideal values).Particularly, using the microphone positions dependentEDT/T30 ratio, one can determine prominent directional or diffuse locations. Regarding to the spatial variation of EDT (Figure 2), a general conclusion can be made: where the EDT has maximal values, the locations are diffuse (the EDT/T30 values are close to 1.1), whereas minimal values indicate a directional sound field. This assertion can be made due to the relative constant spatial RT. Tables 15 and 16 present EDT/T30 ratios for both source positions. From the tables one can conclude that the auditorium is diffuse and does not have excessively directional spots (the ratio is above 0.8). Three excessively diffuse locations were found for the S1 source position (12, 13, and 15) and for S2 position a single location was identified.Table 15
EDT
/
T
30 ratio for the source situated in S1.
Microphoneposition
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
EDT/T30
0.91
0.85
0.83
0.98
0.93
0.91
1.03
0.92
1.02
1.04
1.04
1.13
1.14
1.09
1.14Table 16
EDT
/
T
30 ratio for the source situated in S2.
Microphoneposition
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
EDT/T30
0.94
0.85
1.01
0.90
0.98
1.10
1.00
1.09
1.04
1.01
1.00
1.06
1.08
1.08
1.10Measured acoustical parameters in the microphone positions and their JND values (indicated by error bars) for (a) the S1 source position and (b) the S2 source position.
(a)
(b)In a directed design in which early sound is reflected into the audience, where a sagging decay is obtained, theEDT/T30 ratio tends to be lower than 1. Ballooning decay indicates an EDT/T30 ratio that exceeds 1, so the enclosure is described as excessively diffuse [13, 14]. Figure 3(a) presents the decay curve for the 2nd microphone position, where EDT<T30 reveals a sagging decay. Figure 3(b) indicates the decay of the 13th microphone position where EDT>T30 exposes a ballooning decay at 500 Hz. The slope of the EDT is presented by a parallel dashed line to the decay curve.Decay curves for (a) the 2nd microphone position and (b) the 13th microphone position.
(a)
(b)


## 4.6. JND Analysis

Accurate evaluation of acoustical parameters can be achieved with the examination of spatial variations as well as their JND values. It is a useful way to model the room acoustics using reverberators. Reverberators are spatial effect generators [15]. Because we cannot build a reverberator for every point in the measured space, one have to try to reduce the implementation complexity using the JND terms.Let us recall Figure2 to illustrate the acoustical parameters and their JND values for mid-frequency range (average 500 Hz and 1000 Hz) and also two offset values marked with error bars, one with the measured values +JND, the other is the measured value −JND. This plots make it easy to understand if the spatial variation of the parameter is significant or not as well as their perceptually aspects. The EDT and Ts are correlated, whereas EDT is inverse correlated with  C80; similar results were found in [9, 13]. The sensitivity of the acoustical parameters to the source positions at mid frequencies are observed by comparing the two columns of Figure 2. (i)
ForT30, one cannot found any locations where the variations exceed 1 JND for the two excitation locations;(ii)
EDT has a variation that exceeds 1 JND for the following locations: 1, 3, 4, 5, 6, 8, 12, and 13;(iii)
C80 has a variation that exceeds 1 JND for the following locations: 2, 9, and 12;(iv)
D50 has a variation that exceeds 1 JND for the following locations: 1, 2, 3, 4, and 9;(v)
Ts has a variation that exceeds 1 JND for the following locations: 1, 2, 6, 8, 9, and 14.For the auditorium, the center time is the most sensitive acoustical parameter and the clarity is the least sensitive with respect to the excitation source position.An enhanced evaluation and analyses are obtained by pairing of acoustical parameters based on perceived reverberation and clarity. One can try to identify a number of regions in the room where EDT and clarity are the same (the variation of the acoustical parameters not exceeding 1 JND) (Figure2). This can be achieved separately for S1 and S2 or together for the two source positions.Considering the source placed in S1, one can find 11 regions with the same subjective reverberation and clarity sensation. To model these acoustical features, 11 reverberators are necessary instead of 15 (the total number of considered measuring positions); this means a reduction of 26.66%.If the source is placed in S2, we obtained 9 regions with the same subjective reverberation and clarity sensation. In this case, the acoustical modeling will require 9 reverberators instead of 15, that is, a reduction of 40%.If we want to consider the source placed to S1 or S2, we obtained 12 regions, so a reduction of the necessary reverberators is of 20%.One can observe that the reduction in this last case is lower than in the previous cases. This is due to the huge acoustical differences between samples of regions, for instance, the samples situated at the front of the hall with respect to the end ones.


## 5. Conclusions

The paper presents the acoustical evaluation of an auditorium using an omnidirectional loudspeaker for sound source and linear sweep sine signal for excitation. The hall was evaluated for 2 source positions. For the evaluation of the reverberation time, a phonometer was also used for one source position. We did not detect important differences between the reverberation times determined in the 2 source positions with the omnidirectional loudspeaker and with the phonometer. We made 5 measurements in each spot to check the repeatability. Notable standard deviation differences were not found.Taking into account the values of the reverberation time, the possible destination of the room is for opera and chamber music events. The auditorium has poor acoustical properties for speech events (like lectures, courses). At the same time, the hall has many diffuse locations.Using 2 subjective criteria (the perceived reverberation and clarity), a number of 11 and 9 perceptively identical locations were found for individual source position and 12 locations if the sources are considered together. This fact indicates the possibility of acoustical model optimization.



---

*Source: 868247-2012-09-23.xml*