# Case Study on Incentive Mechanism of Energy Efficiency Retrofit in Coal-Fueled Power Plant in China

Authors: Donghai Yuan; Xujing Guo; Yuan Cao; Liansheng He; Jinggang Wang; Beidou Xi; Junqi Li; Wenlin Ma; Mingshun Zhang
Journal: The Scientific World Journal
 (2012)

---

## Abstract

An ordinary steam turbine retrofit project is selected as a case study; through the retrofit, the project activities will generate emission reductions within the power grid for about 92,463 tCO2e per annum. The internal rate of return (IRR) of the project is only −0.41% without the revenue of carbon credits, for example, CERs, which is much lower than the benchmark value of 8%. Only when the unit price of carbon credit reaches  125 CNY/tCO2, the IRR could reach the benchmark and an effective carbon tax needs to increase the price of carbon to 243 CNY/tce in order to make the project financially feasible. Design of incentive mechanism will help these low efficiency enterprises  improve efficiency and reduce CO2 emissions, which can provide the power plants sufficient incentive to implement energy efficiency retrofit project in existing coal-fuel power generation-units, and we hope it will make a good demonstration for the other low efficiency coal-fueled power generation units in China.


---

## Body

## 1. Introduction

With the rapid development of industrialization and urbanization, the global climate-change issue has become an important factor to affect the world economic order, political regime and international relations, as well as to determine the key of the world’s energy future [1, 2]. Global climate change is closely related to energy, a variety of greenhouse gases (GHG) that cause climate change. Carbon dioxide (CO2) contribution rate is more than 50%, and 70% of human activities’ CO2 emissions are from the burning of fossil fuels [3]. At present, China is one of the countries with the most CO2 emissions in the word, and CO2 emissions are still growing rapidly. The main reasons for CO2 emissions of China are as follow: (1) The existing energy resource characteristics of primary energy consumption are dominated by coal, and thermal power accounts for about 70% of the total power generation; (2) the rate of energy-intensive industries and products is high [4].In the 12th Five-Year Plan, China has shown its intention to shift from a policy of maximizing growth to balance growth with social harmony and environmental sustainability [5]. But the dominant position of coal in the energy consumption will continue in a long period; by 2020, the GDP goal is quadrupling, and then the total installed capacity will reach 900–950 million kilowatts, generating capacity will reach 4.2 trillion kWh, of which thermal power installed capacity still contains about 70%. How to coordinate the relationship between the rapid development with CO2 emissions is a severe challenge for the power industry.Today, there are lots of low efficiency power plants in China, which is urgent to implement the steam turbine retrofit, and these power plants have the great potential to reduce CO2 emissions. Because the development among different regions and industries in China is very uneven, the enterprises cannot afford the high cost of the steam turbine retrofit by themselves [6]. The introduction of an incentive mechanism to help these low efficiency enterprises to improve efficiency and reduce CO2 emissions has been practically significant [7]. In this study, a steam turbine retrofit project in China is selected for a case study to find an effective GHG emission reduction mechanism for this project type, which can provide the power plants sufficient incentive to implement energy efficiency retrofit project in existing coal fuel-power generation-units, and we want to make a good demonstration for the other low efficiency coal-fuel power generation-units in China.


## 2. Description of the Project Activity

### 2.1. Site Description

Panshan Power Plant is located in the southeast of the Ji County, Tianjin City (117°16′58′′E, 39°59′26′′N). The mean annual temperature in Ji County is 10-11°C, and the mean annual precipitation is approximately 700 mm, of which three-quarters are distributed from July to September. Figure1 is the location of Panshan Power Plant.Figure 1
The map of the project location–Panshan Power Plant.


### 2.2. Description of the Project

Steam Turbine Retrofit Project of Tianjin Panshan Power Plant (hereafter refers to as the project) involves retrofitting supercritical steam turbine. The steam turbine with rated power of 500 MW (hereafter refers to as PAT, project activity turbine), which was designed in the early 1970s and introduced from Russia, has been put into commercial operation since April 16th 1996. The technical lifetime of the power unit is 24 years. Designed as a super critical turbine set, the technological level of the PAT is relatively higher than the subcritical turbine sets that are commonly used and regarded as a good practice currently in current China. So up to 2009 (the year of retrofit action), the remaining life is 11 years, more than 8 years. The principal specifications of the steam turbine are shown below (Table1).Table 1
The principal specifications of the steam turbine.
Item
Designed value
Manufacturer
Leningrad metal factory of Russia (designed in the beginning of 1970s)
Type of turbine
Supercritical,  once reheated, single shaft, 4 cylinder and 4 steam exhaust, condensing turbine
Rated power
500 MW
Rated main steam flow
1528.8 t/h
Main steam pressure
23.54 MPa
Main steam temperature
540°C
Reheated steam pressure
3.51 MPa
Reheated steam temperature
540°C
Exhausted steam pressure
4.27/5.44 kPa
Number of blade stage
54
Net heat rate
8146 kJ/kWh
Lifetime
24 yearsThe main target of the project is retrofitting the low pressure cylinder to reduce the coal consumption of the power generation, in particular, by promoting the performance of the low pressure cylinder. The components, including rotor, blades, diaphragm and its set, inner cylinder, and shaft butt seal of the low pressure cylinder, are retrofitted. Steam seal installed in the surrounding bend of the first stage of high-pressure cylinder, steam seal of each turbine stage, and shaft butt seal of high-cylinder and medium-cylinder will also be altered (Figure2).Figure 2
Profile of turbine.The current practice with low efficiency would be continued in the absence of the proposed project. By adopting retrofit measures, the proposed project will not only reduce GHG emissions, but also contributes to sustainable development for local communities by the means of:(1) reducing the emissions of SO2, NOx, and coal ash due to the reduction of standard coal consumption; (2) improving the energy efficiency of power plant and promoting development of manufacturing industry. The project is expected to give a lead on turbine retrofit of supercritical power plants in China.


## 2.1. Site Description

Panshan Power Plant is located in the southeast of the Ji County, Tianjin City (117°16′58′′E, 39°59′26′′N). The mean annual temperature in Ji County is 10-11°C, and the mean annual precipitation is approximately 700 mm, of which three-quarters are distributed from July to September. Figure1 is the location of Panshan Power Plant.Figure 1
The map of the project location–Panshan Power Plant.


## 2.2. Description of the Project

Steam Turbine Retrofit Project of Tianjin Panshan Power Plant (hereafter refers to as the project) involves retrofitting supercritical steam turbine. The steam turbine with rated power of 500 MW (hereafter refers to as PAT, project activity turbine), which was designed in the early 1970s and introduced from Russia, has been put into commercial operation since April 16th 1996. The technical lifetime of the power unit is 24 years. Designed as a super critical turbine set, the technological level of the PAT is relatively higher than the subcritical turbine sets that are commonly used and regarded as a good practice currently in current China. So up to 2009 (the year of retrofit action), the remaining life is 11 years, more than 8 years. The principal specifications of the steam turbine are shown below (Table1).Table 1
The principal specifications of the steam turbine.
Item
Designed value
Manufacturer
Leningrad metal factory of Russia (designed in the beginning of 1970s)
Type of turbine
Supercritical,  once reheated, single shaft, 4 cylinder and 4 steam exhaust, condensing turbine
Rated power
500 MW
Rated main steam flow
1528.8 t/h
Main steam pressure
23.54 MPa
Main steam temperature
540°C
Reheated steam pressure
3.51 MPa
Reheated steam temperature
540°C
Exhausted steam pressure
4.27/5.44 kPa
Number of blade stage
54
Net heat rate
8146 kJ/kWh
Lifetime
24 yearsThe main target of the project is retrofitting the low pressure cylinder to reduce the coal consumption of the power generation, in particular, by promoting the performance of the low pressure cylinder. The components, including rotor, blades, diaphragm and its set, inner cylinder, and shaft butt seal of the low pressure cylinder, are retrofitted. Steam seal installed in the surrounding bend of the first stage of high-pressure cylinder, steam seal of each turbine stage, and shaft butt seal of high-cylinder and medium-cylinder will also be altered (Figure2).Figure 2
Profile of turbine.The current practice with low efficiency would be continued in the absence of the proposed project. By adopting retrofit measures, the proposed project will not only reduce GHG emissions, but also contributes to sustainable development for local communities by the means of:(1) reducing the emissions of SO2, NOx, and coal ash due to the reduction of standard coal consumption; (2) improving the energy efficiency of power plant and promoting development of manufacturing industry. The project is expected to give a lead on turbine retrofit of supercritical power plants in China.


## 3. Performance Assessment

### 3.1. Emission Reductions

To evaluate the effect of GHG emission reduction by the project with a quantitative way, the approved CDM methodology AM0062 in Unit Nation Framework Convention on Climate Change (UNFCCC) is applied to this study on the project in the following steps: calculate the baseline emissions, the project emissions, and the emission reductions [8].


#### 3.1.1. Calculate the Baseline Emissions

(
1
) Determine baseline emission for the scenario of project electricity generation. Electricity generation in the project power plant will displace in the baseline scenario less efficient electricity generation in the project plant and can, in addition, displace electricity to the grid, if the quantity of electricity generation is increased as a result of the project. The calculation of baseline emissions is therefore based on different emission factors for different quantities of electricity generated. In China the annual power generation is determined by the annual dispatch order from grid company where the PAT connects to, thus it is assumed that annual power generation dispatch will be according to the original capacity of PAT. In this case, the annual power generation after retrofit unlikely exceeds the historical average level. Therefore the emission reduction is only relevant to the efficiencies of PAT before and after the retrofit.To evaluate the emission reduction due to the retrofit, the follow case from AM0062 [9] is selected in a future analysis: the quantity of electricity generated in the project turbine (EGPJ,y) is lower or the same as the historic average annual generation level (EGAVR). Baseline emissions are calculated as:
(1)BEy=EGPJ,y*EFBL,y,
where BEy= baseline emissions in year “y” (tCO2/yr), EGPJ,y= quantity of electricity supplied by the project turbine to the grid in year “y” (MWh/yr), adjusted for changes in efficiency, EFBL,y= baseline emission factor of the project turbine in year y (tCO2/MWh).(
2
) Determine Baseline Emission factor.  The project turbine is steam turbine and the fuel is fired in a boiler, so its emission factor is calculated as follows [10]:
(2)EFBL,y=3.61000×EFFF,BL×FCPJ,y×NCVFF,PJηBL,y×HIPJ,y,
where EFBL,y= baseline emission factor of the Project turbine in year “y” (tCO2/MWh), EFFF,BL= CO2 emission factor of the fossil fuel used in the Project turbine prior to the implementation of the Project (tCO2/TJ), NCVFF,PJ= net calorific value (NCV) of fossil fuel used in the Project turbine during year y (TJ/tonne of fuel).η
BL
,
y
=energy efficiency of the turbine without retrofitting estimated using the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems,” determined the efficiency based on measurements and used a conservative value, based on performance tests before the implementing the project following national/international standards, at discrete loads within the operating range or over the entire rated capacity,  FCPJ,y= Actual fuel consumption by project in year “y” (tonne of fuel), HIPJ,y=Heat input to the steam turbine in year “y” (TJ). In case of multicylinder steam turbines, this is the sum of the heat input at the inlet of first stage and the heat inputs in the re-heaters of steam between various cylinders (e.g., high-pressure, medium pressure, and low-pressure cylinders).


#### 3.1.2. Calculate the Project Emissions

The CO2 emissions from fossil fuel consumption in the project (PEy) should be calculated using the latest approved version of the “tool to calculate project or leakage CO2 emissions from fossil fuel combustion,” where the process j  in the tool corresponds to the combustion of fossil fuels in the project for electricity generation in the project power plants [11]:
(3)PEFC,j,y=∑iFCi,j,y×COEFi,y,
where PEFC,j,y=are the CO2 emissions from fossil fuel combustion in process j during the year y, FCi,j,y= is the quantity of fuel type i combusted in process j during the year y (mass or volume unit/yr), COEFi,y=  is the CO2 emission coefficient of fuel type i in year y (tCO2/mass or volume unit), i= are the fuel types combusted in process j during the year y.The CO2 emission coefficient COEFi,y can be calculated using one of two options proposed in the “tool to calculate project or leakage CO2  emissions from fossil fuel combustion”.Depending on the availability of data on the fossil fuel type i, the CO2 emission coefficient COEFi,y is calculated based on net calorific value and CO2 emission factor of the fuel type i:
(4)COEFi,y=NCVi,y×EFCO2,i,y
where COEFi,y= is the CO2 emission coefficient of fuel type i in year y (tCO2/mass or volume unit), NCVi,y= is the weighted average net calorific value of the fuel type i in year y (GJ/mass or volume unit). EFCO2,i,y= is the weighted average CO2 emission factor of fuel type i in year y (tCO2/GJ), i= are the fuel types combusted in process j during the year y.


#### 3.1.3. Calculate the Emission Reductions

(
1
) Emission reductions are calculated as follows:
(5)ERy=BEy-PEy,
whereERy= emissions reductions in year y (tCO2e/yr), BEy= baseline emissions in year y (tCO2e/yr), PEy= project emissions in year y (tCO2e/yr).(
2
) Data and parameters which are available at validation. Because the regional specific value is not available, the Intergovernmental Panel on Climate Change (IPCC) default value of the CO2 emission factor of coal was selected. Choose the CO2 emission factor corresponding to the applicable fuel type. IPCC default values may be used. CO2 emission factor of the fossil fuel used in the Project turbine prior to the implementation the Project (EFFF,BL) = 89.5 tCO2/TJ of fuel [12].Use the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems.”  Depending upon the option selected from the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems.” Energy efficiency of the turbine without retrofitting in a year y(ηBL,y) = 39.553% (from Efficiency Test Report of the PAT prior to the retrofit).(
3
) Ex-ante calculation of emission reductions. In order to estimate the emission reductions generated by the project, the following assumptions are brought into account.(
4
) Calculate the baseline emissions:
(6)EFBL,y=3.61000×EFFF,BL×FCPJ,y×NCVFF,PJηBL,y×HIPJ,y=3.61000×89.5×(322.5956×2,632,000)×0.0293060.39553×2,632,000×8738.92=0.88126tCO2eMMh,BEy=EGPJ,y*EFBL,y=2,632,000*0.88126=2,319,482tCO2e.(5) Calculate the project emissions:
(7)PEy=FCcoal,y×NCVcoal,y×EFCO2,coal,y=1,080,643.24ton×0.023026TJ/ton×89.5tCO2e/TJ=2,227,019tCO2e.(6) Calculate the emission reductions:
(8)ERy=BEy-PEy=2,319,482-2,227,019=92,463tCO2e.


#### 3.1.4. Summary of the Ex-Ante Estimation of Emission Reductions

It is expected that the project activities will generate emission reductions within the power grid for about 92,463 tCO2e per annum over an 8-year fixed crediting period from 01/01/2012 to 31/12/2019. And the total emission reductions will come to 739,704 tCO2e.


### 3.2. Investment Analysis

#### 3.2.1. Determine the Suitable Financial Indicator for the Project Type

Financial indicator of internal rate of return (IRR) is the most suitable for such power retrofit project and decision making context. According to Trial Implementation Methods for Economic Assessment of technology retrofit Project in Power Engineering, the benchmark of IRR of power retrofit project is set at 8% [13]. The financial attractiveness of this project will be determined by comparing the IRR after tax (without Certified Emission Reductions (CERs)) with its benchmark applied in power retrofit project of China power industry, which is a standard recommended by the industry experts and is widely used at present in China. If the IRR after tax (without CERs) is less than 8%, the project is considered not being financially attractive in the absence of CDM revenues, and is therefore considered to be additional.


#### 3.2.2. Calculation and Comparison of Financial Indicators

The key parameters of the project are showed in Tables2 and 3.Table 2
The key parameters of the project.
Item
Value
Unit
Data source
Electricity supplied to the grid in year y (EGPJ, y)
2,632,000
MWh
Feasibility study report of the project (FSR)
Standard coal consumption after retrofit
322.5956
kg/MWh
Efficiency test report
Net calorific value of standard coal
29,306
MJ/ton
Efficiency test report
Net calorific value of fossil coal
23,026
MJ/ton
Calculated
Annual consumption of fossil coal
1,080,643.24
ton
Calculated
Average net heat consumption of turbine after retrofit
8738.92
kJ/kWh
Efficiency test reportTable 3
The key parameters of the proposed project.
Item
Value
Unit
Data source
Rated continuous power
500
MW
FSR
Total investment
100,000,000
RMB
FSR
Equity proportion
100
%
FSR
Incremental annual power generation
0
MWh
FSR
Profit loss due to the retrofitting
24,730,000
RMB
FSR
Annual operation hours
5600
h
FSR
Power consumption rate (for self-use)
6
%
FSR
Standard coal consumption for power generation before retrofit (designed in FSR)
316
g/KWh
FSR
Decrease of standard coal consumption after retrofit (designed in FSR)
13
g/KWh
FSR, P51
Standard coal price (without VAT)
389
RMB/ton
FSR
Electricity tariff (without VAT)
341.2
RMB/MWh
FSR
New added O and M cost
−11,675,000
RMB/year
FSR
Of which fuel cost saving due to retrofit
−14,175,000
RMB/year
FSR
New added repair cost
2,500,000
RMB/year
FSR
Income tax
25
%
FSR
Value added tax (VAT)
17
%
FSR
Town building maintenance tax
7 (of VAT)
%
FSR
Surcharge for education
3 (of VAT)
%
FSR
Project operating period
11
Years
FSR
Rate of residual value of the fixed assets
3 (out of total investment)
%
FSR
Depreciation period
11
Years
FSR
Amount of CERs
92,463
tCO2e/year
ER calculation sheetThe financial analysis results are shown in Table4. As shown in this table, without carbon credits, the IRR is −0.41%, which is much lower than the benchmark rate of 8%. This therefore indicates that in comparison to other alternative investments, the project without carbon credits is not financially attractive to a rational investor.Table 4
The financial indicators of the project.
Financial indicators
Rate
IRR (after tax) without CERs
−0.41%
Benchmark
8%
IRR with CERs
8.27%


#### 3.2.3. Sensitivity Analysis

The sensitivity analysis is conducted to check whether, under reasonable variations of the sensitive factors in the critical assumptions, the results from the analysis remain unaltered. After overall checking of the IRR calculation sheet, five factors have been selected for the sensitivity analysis, which are the total investment, annual operation hours, electricity tariff, standard coal price, and the decrease of standard coal consumption.Assuming the five factors within a fluctuation range from −20% to 20%, the IRR (after tax) of the project (without income from selling CERs) varies to a different extent, as shown in Table5.Table 5
The sensitivity analysis of the project within a fluctuation range from −20% to 20%.
Fluctuation range
−20%
−10%
0
10%
20%
Total investment
2.34%
0.87%
−0.41%
−1.55%
−2.57%
Annual operation hours
−3.64%
−1.98%
−0.41%
1.08%
2.50%
Electricity tariff
−0.41%
−0.41%
−0.41%
−0.41%
−0.41%
Standard coal price
−3.64%
−1.98%
−0.41%
1.08%
2.50%
Decrease of standard coal consumption
−3.64%
−1.98%
−0.41%
1.08%
2.50%As shown in the sensitivity analysis, even the varying range of the uncertain factors reaches ±20%, the IRR (after tax) could not reach the benchmark. The conclusion that the project is definitely not financially attractive would not be influenced.As above, the internal rate of return (IRR) of the project is only −0.41% without the revenue of carbon credits for example, CERs, which is much lower than the benchmark value of 8%. In addition, only when the unit price of carbon credit comes to 125 CNY/tCO2, the IRR could reach the benchmark and become financially feasible. Therefore the GHG emission reduction cost of such retrofit project is 125 CNY/tCO2.


### 3.3. Design of Incentive Mechanism

#### 3.3.1. Incentive from Carbon Tax

Carbon tax is a Pigovian tax levied on the carbon content of fuels [14], which is a form of carbon pricing. Carbon is present in every hydrocarbon fuel (coal, petroleum, and natural gas) and is released as CO2, when they are burnt [15].In this case study, it is assumed that government levies the carbon tax on coal consumption in the power sector. It means that the carbon tax will be a part of the fuel cost in operating the power plant, being of the same effect of raising the price of coal. According to the sensitive analysis, an effective carbon tax needs to increase the price of coal by 243 CNY/tce, so as to make the project financially feasible. Then the cost of carbon tax should be 90 CNY/tCO2 (1tce leads to GHG emission of 2.77 tCO2).


#### 3.3.2. Incentive from Carbon Market (Credit Trading)

Emissions trading or cap-and-trade is a market-based approach used to control pollution by providing economic incentives for achieving reductions in the emissions of pollutants. For GHG the largest is the European Union Emission Trading Scheme (ETS), whose purpose is to avoid dangerous climate change [16]. In the carbon market created by ETS, GHG emission reduction credits are a kind of eligible unit, generated from the project that is implemented by entity outside the ETS. As analyzed above, the price of carbon credits in the market for example, CERs must be not less than 125 CNY/tCO2 to make the project financially attractive.


#### 3.3.3. Incentives Combined with Encouraging Dispatch Plan

Since the electricity tariff is determined by the government in China, which is fixed unless the new tariff policy approved by the government, most of the coal fuel power plants resist carbon tax in practice. A very high cost of carbon tax is not very likely to occur in China. On the other hand, given the experience of the EU ETS, the credit price is of high volatility in the market [17]. Thus, there is always uncertainty about the credit price to make the investment decisions of this kind of retrofit. To mitigate the shortage of carbon tax and carbon market, the encouraging dispatch plan is expected to enhance the effect from above mechanisms.Given the sensitivity analysis, the annual operation hours of the PAT are a very crucial factor to the IRR. The annual operation hours of a power plant are normally determined by power dispatch arrangement of grid company. In this section, the effect of encouraging dispatch plan is an analysis together with carbon tax and credit price in an ETS. Clearly, the more annual operation hours of the PAT, the higher IRR appears in the Project (Table6). Thus, the necessary cost of either carbon tax and credit cost in ETS will decrease by incorporating with such encourage to dispatch plan.Table 6
The necessary cost of carbon tax and credit price with/without encouraging dispatch plan.
Dispatch plan
Necessary cost of Carbon tax
Necessary cost of credit price
The dispatch electricity generation does not change
90 CNY/tCO2
125 CNY/tCO2
Dispatched electricity generation increased by 20%
50 CNY/tCO2
85 CNY/tCO2


## 3.1. Emission Reductions

To evaluate the effect of GHG emission reduction by the project with a quantitative way, the approved CDM methodology AM0062 in Unit Nation Framework Convention on Climate Change (UNFCCC) is applied to this study on the project in the following steps: calculate the baseline emissions, the project emissions, and the emission reductions [8].


### 3.1.1. Calculate the Baseline Emissions

(
1
) Determine baseline emission for the scenario of project electricity generation. Electricity generation in the project power plant will displace in the baseline scenario less efficient electricity generation in the project plant and can, in addition, displace electricity to the grid, if the quantity of electricity generation is increased as a result of the project. The calculation of baseline emissions is therefore based on different emission factors for different quantities of electricity generated. In China the annual power generation is determined by the annual dispatch order from grid company where the PAT connects to, thus it is assumed that annual power generation dispatch will be according to the original capacity of PAT. In this case, the annual power generation after retrofit unlikely exceeds the historical average level. Therefore the emission reduction is only relevant to the efficiencies of PAT before and after the retrofit.To evaluate the emission reduction due to the retrofit, the follow case from AM0062 [9] is selected in a future analysis: the quantity of electricity generated in the project turbine (EGPJ,y) is lower or the same as the historic average annual generation level (EGAVR). Baseline emissions are calculated as:
(1)BEy=EGPJ,y*EFBL,y,
where BEy= baseline emissions in year “y” (tCO2/yr), EGPJ,y= quantity of electricity supplied by the project turbine to the grid in year “y” (MWh/yr), adjusted for changes in efficiency, EFBL,y= baseline emission factor of the project turbine in year y (tCO2/MWh).(
2
) Determine Baseline Emission factor.  The project turbine is steam turbine and the fuel is fired in a boiler, so its emission factor is calculated as follows [10]:
(2)EFBL,y=3.61000×EFFF,BL×FCPJ,y×NCVFF,PJηBL,y×HIPJ,y,
where EFBL,y= baseline emission factor of the Project turbine in year “y” (tCO2/MWh), EFFF,BL= CO2 emission factor of the fossil fuel used in the Project turbine prior to the implementation of the Project (tCO2/TJ), NCVFF,PJ= net calorific value (NCV) of fossil fuel used in the Project turbine during year y (TJ/tonne of fuel).η
BL
,
y
=energy efficiency of the turbine without retrofitting estimated using the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems,” determined the efficiency based on measurements and used a conservative value, based on performance tests before the implementing the project following national/international standards, at discrete loads within the operating range or over the entire rated capacity,  FCPJ,y= Actual fuel consumption by project in year “y” (tonne of fuel), HIPJ,y=Heat input to the steam turbine in year “y” (TJ). In case of multicylinder steam turbines, this is the sum of the heat input at the inlet of first stage and the heat inputs in the re-heaters of steam between various cylinders (e.g., high-pressure, medium pressure, and low-pressure cylinders).


### 3.1.2. Calculate the Project Emissions

The CO2 emissions from fossil fuel consumption in the project (PEy) should be calculated using the latest approved version of the “tool to calculate project or leakage CO2 emissions from fossil fuel combustion,” where the process j  in the tool corresponds to the combustion of fossil fuels in the project for electricity generation in the project power plants [11]:
(3)PEFC,j,y=∑iFCi,j,y×COEFi,y,
where PEFC,j,y=are the CO2 emissions from fossil fuel combustion in process j during the year y, FCi,j,y= is the quantity of fuel type i combusted in process j during the year y (mass or volume unit/yr), COEFi,y=  is the CO2 emission coefficient of fuel type i in year y (tCO2/mass or volume unit), i= are the fuel types combusted in process j during the year y.The CO2 emission coefficient COEFi,y can be calculated using one of two options proposed in the “tool to calculate project or leakage CO2  emissions from fossil fuel combustion”.Depending on the availability of data on the fossil fuel type i, the CO2 emission coefficient COEFi,y is calculated based on net calorific value and CO2 emission factor of the fuel type i:
(4)COEFi,y=NCVi,y×EFCO2,i,y
where COEFi,y= is the CO2 emission coefficient of fuel type i in year y (tCO2/mass or volume unit), NCVi,y= is the weighted average net calorific value of the fuel type i in year y (GJ/mass or volume unit). EFCO2,i,y= is the weighted average CO2 emission factor of fuel type i in year y (tCO2/GJ), i= are the fuel types combusted in process j during the year y.


### 3.1.3. Calculate the Emission Reductions

(
1
) Emission reductions are calculated as follows:
(5)ERy=BEy-PEy,
whereERy= emissions reductions in year y (tCO2e/yr), BEy= baseline emissions in year y (tCO2e/yr), PEy= project emissions in year y (tCO2e/yr).(
2
) Data and parameters which are available at validation. Because the regional specific value is not available, the Intergovernmental Panel on Climate Change (IPCC) default value of the CO2 emission factor of coal was selected. Choose the CO2 emission factor corresponding to the applicable fuel type. IPCC default values may be used. CO2 emission factor of the fossil fuel used in the Project turbine prior to the implementation the Project (EFFF,BL) = 89.5 tCO2/TJ of fuel [12].Use the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems.”  Depending upon the option selected from the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems.” Energy efficiency of the turbine without retrofitting in a year y(ηBL,y) = 39.553% (from Efficiency Test Report of the PAT prior to the retrofit).(
3
) Ex-ante calculation of emission reductions. In order to estimate the emission reductions generated by the project, the following assumptions are brought into account.(
4
) Calculate the baseline emissions:
(6)EFBL,y=3.61000×EFFF,BL×FCPJ,y×NCVFF,PJηBL,y×HIPJ,y=3.61000×89.5×(322.5956×2,632,000)×0.0293060.39553×2,632,000×8738.92=0.88126tCO2eMMh,BEy=EGPJ,y*EFBL,y=2,632,000*0.88126=2,319,482tCO2e.(5) Calculate the project emissions:
(7)PEy=FCcoal,y×NCVcoal,y×EFCO2,coal,y=1,080,643.24ton×0.023026TJ/ton×89.5tCO2e/TJ=2,227,019tCO2e.(6) Calculate the emission reductions:
(8)ERy=BEy-PEy=2,319,482-2,227,019=92,463tCO2e.


### 3.1.4. Summary of the Ex-Ante Estimation of Emission Reductions

It is expected that the project activities will generate emission reductions within the power grid for about 92,463 tCO2e per annum over an 8-year fixed crediting period from 01/01/2012 to 31/12/2019. And the total emission reductions will come to 739,704 tCO2e.


## 3.1.1. Calculate the Baseline Emissions

(
1
) Determine baseline emission for the scenario of project electricity generation. Electricity generation in the project power plant will displace in the baseline scenario less efficient electricity generation in the project plant and can, in addition, displace electricity to the grid, if the quantity of electricity generation is increased as a result of the project. The calculation of baseline emissions is therefore based on different emission factors for different quantities of electricity generated. In China the annual power generation is determined by the annual dispatch order from grid company where the PAT connects to, thus it is assumed that annual power generation dispatch will be according to the original capacity of PAT. In this case, the annual power generation after retrofit unlikely exceeds the historical average level. Therefore the emission reduction is only relevant to the efficiencies of PAT before and after the retrofit.To evaluate the emission reduction due to the retrofit, the follow case from AM0062 [9] is selected in a future analysis: the quantity of electricity generated in the project turbine (EGPJ,y) is lower or the same as the historic average annual generation level (EGAVR). Baseline emissions are calculated as:
(1)BEy=EGPJ,y*EFBL,y,
where BEy= baseline emissions in year “y” (tCO2/yr), EGPJ,y= quantity of electricity supplied by the project turbine to the grid in year “y” (MWh/yr), adjusted for changes in efficiency, EFBL,y= baseline emission factor of the project turbine in year y (tCO2/MWh).(
2
) Determine Baseline Emission factor.  The project turbine is steam turbine and the fuel is fired in a boiler, so its emission factor is calculated as follows [10]:
(2)EFBL,y=3.61000×EFFF,BL×FCPJ,y×NCVFF,PJηBL,y×HIPJ,y,
where EFBL,y= baseline emission factor of the Project turbine in year “y” (tCO2/MWh), EFFF,BL= CO2 emission factor of the fossil fuel used in the Project turbine prior to the implementation of the Project (tCO2/TJ), NCVFF,PJ= net calorific value (NCV) of fossil fuel used in the Project turbine during year y (TJ/tonne of fuel).η
BL
,
y
=energy efficiency of the turbine without retrofitting estimated using the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems,” determined the efficiency based on measurements and used a conservative value, based on performance tests before the implementing the project following national/international standards, at discrete loads within the operating range or over the entire rated capacity,  FCPJ,y= Actual fuel consumption by project in year “y” (tonne of fuel), HIPJ,y=Heat input to the steam turbine in year “y” (TJ). In case of multicylinder steam turbines, this is the sum of the heat input at the inlet of first stage and the heat inputs in the re-heaters of steam between various cylinders (e.g., high-pressure, medium pressure, and low-pressure cylinders).


## 3.1.2. Calculate the Project Emissions

The CO2 emissions from fossil fuel consumption in the project (PEy) should be calculated using the latest approved version of the “tool to calculate project or leakage CO2 emissions from fossil fuel combustion,” where the process j  in the tool corresponds to the combustion of fossil fuels in the project for electricity generation in the project power plants [11]:
(3)PEFC,j,y=∑iFCi,j,y×COEFi,y,
where PEFC,j,y=are the CO2 emissions from fossil fuel combustion in process j during the year y, FCi,j,y= is the quantity of fuel type i combusted in process j during the year y (mass or volume unit/yr), COEFi,y=  is the CO2 emission coefficient of fuel type i in year y (tCO2/mass or volume unit), i= are the fuel types combusted in process j during the year y.The CO2 emission coefficient COEFi,y can be calculated using one of two options proposed in the “tool to calculate project or leakage CO2  emissions from fossil fuel combustion”.Depending on the availability of data on the fossil fuel type i, the CO2 emission coefficient COEFi,y is calculated based on net calorific value and CO2 emission factor of the fuel type i:
(4)COEFi,y=NCVi,y×EFCO2,i,y
where COEFi,y= is the CO2 emission coefficient of fuel type i in year y (tCO2/mass or volume unit), NCVi,y= is the weighted average net calorific value of the fuel type i in year y (GJ/mass or volume unit). EFCO2,i,y= is the weighted average CO2 emission factor of fuel type i in year y (tCO2/GJ), i= are the fuel types combusted in process j during the year y.


## 3.1.3. Calculate the Emission Reductions

(
1
) Emission reductions are calculated as follows:
(5)ERy=BEy-PEy,
whereERy= emissions reductions in year y (tCO2e/yr), BEy= baseline emissions in year y (tCO2e/yr), PEy= project emissions in year y (tCO2e/yr).(
2
) Data and parameters which are available at validation. Because the regional specific value is not available, the Intergovernmental Panel on Climate Change (IPCC) default value of the CO2 emission factor of coal was selected. Choose the CO2 emission factor corresponding to the applicable fuel type. IPCC default values may be used. CO2 emission factor of the fossil fuel used in the Project turbine prior to the implementation the Project (EFFF,BL) = 89.5 tCO2/TJ of fuel [12].Use the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems.”  Depending upon the option selected from the latest version of approved “tool to determine the baseline efficiency of thermal or electric energy generation systems.” Energy efficiency of the turbine without retrofitting in a year y(ηBL,y) = 39.553% (from Efficiency Test Report of the PAT prior to the retrofit).(
3
) Ex-ante calculation of emission reductions. In order to estimate the emission reductions generated by the project, the following assumptions are brought into account.(
4
) Calculate the baseline emissions:
(6)EFBL,y=3.61000×EFFF,BL×FCPJ,y×NCVFF,PJηBL,y×HIPJ,y=3.61000×89.5×(322.5956×2,632,000)×0.0293060.39553×2,632,000×8738.92=0.88126tCO2eMMh,BEy=EGPJ,y*EFBL,y=2,632,000*0.88126=2,319,482tCO2e.(5) Calculate the project emissions:
(7)PEy=FCcoal,y×NCVcoal,y×EFCO2,coal,y=1,080,643.24ton×0.023026TJ/ton×89.5tCO2e/TJ=2,227,019tCO2e.(6) Calculate the emission reductions:
(8)ERy=BEy-PEy=2,319,482-2,227,019=92,463tCO2e.


## 3.1.4. Summary of the Ex-Ante Estimation of Emission Reductions

It is expected that the project activities will generate emission reductions within the power grid for about 92,463 tCO2e per annum over an 8-year fixed crediting period from 01/01/2012 to 31/12/2019. And the total emission reductions will come to 739,704 tCO2e.


## 3.2. Investment Analysis

### 3.2.1. Determine the Suitable Financial Indicator for the Project Type

Financial indicator of internal rate of return (IRR) is the most suitable for such power retrofit project and decision making context. According to Trial Implementation Methods for Economic Assessment of technology retrofit Project in Power Engineering, the benchmark of IRR of power retrofit project is set at 8% [13]. The financial attractiveness of this project will be determined by comparing the IRR after tax (without Certified Emission Reductions (CERs)) with its benchmark applied in power retrofit project of China power industry, which is a standard recommended by the industry experts and is widely used at present in China. If the IRR after tax (without CERs) is less than 8%, the project is considered not being financially attractive in the absence of CDM revenues, and is therefore considered to be additional.


### 3.2.2. Calculation and Comparison of Financial Indicators

The key parameters of the project are showed in Tables2 and 3.Table 2
The key parameters of the project.
Item
Value
Unit
Data source
Electricity supplied to the grid in year y (EGPJ, y)
2,632,000
MWh
Feasibility study report of the project (FSR)
Standard coal consumption after retrofit
322.5956
kg/MWh
Efficiency test report
Net calorific value of standard coal
29,306
MJ/ton
Efficiency test report
Net calorific value of fossil coal
23,026
MJ/ton
Calculated
Annual consumption of fossil coal
1,080,643.24
ton
Calculated
Average net heat consumption of turbine after retrofit
8738.92
kJ/kWh
Efficiency test reportTable 3
The key parameters of the proposed project.
Item
Value
Unit
Data source
Rated continuous power
500
MW
FSR
Total investment
100,000,000
RMB
FSR
Equity proportion
100
%
FSR
Incremental annual power generation
0
MWh
FSR
Profit loss due to the retrofitting
24,730,000
RMB
FSR
Annual operation hours
5600
h
FSR
Power consumption rate (for self-use)
6
%
FSR
Standard coal consumption for power generation before retrofit (designed in FSR)
316
g/KWh
FSR
Decrease of standard coal consumption after retrofit (designed in FSR)
13
g/KWh
FSR, P51
Standard coal price (without VAT)
389
RMB/ton
FSR
Electricity tariff (without VAT)
341.2
RMB/MWh
FSR
New added O and M cost
−11,675,000
RMB/year
FSR
Of which fuel cost saving due to retrofit
−14,175,000
RMB/year
FSR
New added repair cost
2,500,000
RMB/year
FSR
Income tax
25
%
FSR
Value added tax (VAT)
17
%
FSR
Town building maintenance tax
7 (of VAT)
%
FSR
Surcharge for education
3 (of VAT)
%
FSR
Project operating period
11
Years
FSR
Rate of residual value of the fixed assets
3 (out of total investment)
%
FSR
Depreciation period
11
Years
FSR
Amount of CERs
92,463
tCO2e/year
ER calculation sheetThe financial analysis results are shown in Table4. As shown in this table, without carbon credits, the IRR is −0.41%, which is much lower than the benchmark rate of 8%. This therefore indicates that in comparison to other alternative investments, the project without carbon credits is not financially attractive to a rational investor.Table 4
The financial indicators of the project.
Financial indicators
Rate
IRR (after tax) without CERs
−0.41%
Benchmark
8%
IRR with CERs
8.27%


### 3.2.3. Sensitivity Analysis

The sensitivity analysis is conducted to check whether, under reasonable variations of the sensitive factors in the critical assumptions, the results from the analysis remain unaltered. After overall checking of the IRR calculation sheet, five factors have been selected for the sensitivity analysis, which are the total investment, annual operation hours, electricity tariff, standard coal price, and the decrease of standard coal consumption.Assuming the five factors within a fluctuation range from −20% to 20%, the IRR (after tax) of the project (without income from selling CERs) varies to a different extent, as shown in Table5.Table 5
The sensitivity analysis of the project within a fluctuation range from −20% to 20%.
Fluctuation range
−20%
−10%
0
10%
20%
Total investment
2.34%
0.87%
−0.41%
−1.55%
−2.57%
Annual operation hours
−3.64%
−1.98%
−0.41%
1.08%
2.50%
Electricity tariff
−0.41%
−0.41%
−0.41%
−0.41%
−0.41%
Standard coal price
−3.64%
−1.98%
−0.41%
1.08%
2.50%
Decrease of standard coal consumption
−3.64%
−1.98%
−0.41%
1.08%
2.50%As shown in the sensitivity analysis, even the varying range of the uncertain factors reaches ±20%, the IRR (after tax) could not reach the benchmark. The conclusion that the project is definitely not financially attractive would not be influenced.As above, the internal rate of return (IRR) of the project is only −0.41% without the revenue of carbon credits for example, CERs, which is much lower than the benchmark value of 8%. In addition, only when the unit price of carbon credit comes to 125 CNY/tCO2, the IRR could reach the benchmark and become financially feasible. Therefore the GHG emission reduction cost of such retrofit project is 125 CNY/tCO2.


## 3.2.1. Determine the Suitable Financial Indicator for the Project Type

Financial indicator of internal rate of return (IRR) is the most suitable for such power retrofit project and decision making context. According to Trial Implementation Methods for Economic Assessment of technology retrofit Project in Power Engineering, the benchmark of IRR of power retrofit project is set at 8% [13]. The financial attractiveness of this project will be determined by comparing the IRR after tax (without Certified Emission Reductions (CERs)) with its benchmark applied in power retrofit project of China power industry, which is a standard recommended by the industry experts and is widely used at present in China. If the IRR after tax (without CERs) is less than 8%, the project is considered not being financially attractive in the absence of CDM revenues, and is therefore considered to be additional.


## 3.2.2. Calculation and Comparison of Financial Indicators

The key parameters of the project are showed in Tables2 and 3.Table 2
The key parameters of the project.
Item
Value
Unit
Data source
Electricity supplied to the grid in year y (EGPJ, y)
2,632,000
MWh
Feasibility study report of the project (FSR)
Standard coal consumption after retrofit
322.5956
kg/MWh
Efficiency test report
Net calorific value of standard coal
29,306
MJ/ton
Efficiency test report
Net calorific value of fossil coal
23,026
MJ/ton
Calculated
Annual consumption of fossil coal
1,080,643.24
ton
Calculated
Average net heat consumption of turbine after retrofit
8738.92
kJ/kWh
Efficiency test reportTable 3
The key parameters of the proposed project.
Item
Value
Unit
Data source
Rated continuous power
500
MW
FSR
Total investment
100,000,000
RMB
FSR
Equity proportion
100
%
FSR
Incremental annual power generation
0
MWh
FSR
Profit loss due to the retrofitting
24,730,000
RMB
FSR
Annual operation hours
5600
h
FSR
Power consumption rate (for self-use)
6
%
FSR
Standard coal consumption for power generation before retrofit (designed in FSR)
316
g/KWh
FSR
Decrease of standard coal consumption after retrofit (designed in FSR)
13
g/KWh
FSR, P51
Standard coal price (without VAT)
389
RMB/ton
FSR
Electricity tariff (without VAT)
341.2
RMB/MWh
FSR
New added O and M cost
−11,675,000
RMB/year
FSR
Of which fuel cost saving due to retrofit
−14,175,000
RMB/year
FSR
New added repair cost
2,500,000
RMB/year
FSR
Income tax
25
%
FSR
Value added tax (VAT)
17
%
FSR
Town building maintenance tax
7 (of VAT)
%
FSR
Surcharge for education
3 (of VAT)
%
FSR
Project operating period
11
Years
FSR
Rate of residual value of the fixed assets
3 (out of total investment)
%
FSR
Depreciation period
11
Years
FSR
Amount of CERs
92,463
tCO2e/year
ER calculation sheetThe financial analysis results are shown in Table4. As shown in this table, without carbon credits, the IRR is −0.41%, which is much lower than the benchmark rate of 8%. This therefore indicates that in comparison to other alternative investments, the project without carbon credits is not financially attractive to a rational investor.Table 4
The financial indicators of the project.
Financial indicators
Rate
IRR (after tax) without CERs
−0.41%
Benchmark
8%
IRR with CERs
8.27%


## 3.2.3. Sensitivity Analysis

The sensitivity analysis is conducted to check whether, under reasonable variations of the sensitive factors in the critical assumptions, the results from the analysis remain unaltered. After overall checking of the IRR calculation sheet, five factors have been selected for the sensitivity analysis, which are the total investment, annual operation hours, electricity tariff, standard coal price, and the decrease of standard coal consumption.Assuming the five factors within a fluctuation range from −20% to 20%, the IRR (after tax) of the project (without income from selling CERs) varies to a different extent, as shown in Table5.Table 5
The sensitivity analysis of the project within a fluctuation range from −20% to 20%.
Fluctuation range
−20%
−10%
0
10%
20%
Total investment
2.34%
0.87%
−0.41%
−1.55%
−2.57%
Annual operation hours
−3.64%
−1.98%
−0.41%
1.08%
2.50%
Electricity tariff
−0.41%
−0.41%
−0.41%
−0.41%
−0.41%
Standard coal price
−3.64%
−1.98%
−0.41%
1.08%
2.50%
Decrease of standard coal consumption
−3.64%
−1.98%
−0.41%
1.08%
2.50%As shown in the sensitivity analysis, even the varying range of the uncertain factors reaches ±20%, the IRR (after tax) could not reach the benchmark. The conclusion that the project is definitely not financially attractive would not be influenced.As above, the internal rate of return (IRR) of the project is only −0.41% without the revenue of carbon credits for example, CERs, which is much lower than the benchmark value of 8%. In addition, only when the unit price of carbon credit comes to 125 CNY/tCO2, the IRR could reach the benchmark and become financially feasible. Therefore the GHG emission reduction cost of such retrofit project is 125 CNY/tCO2.


## 3.3. Design of Incentive Mechanism

### 3.3.1. Incentive from Carbon Tax

Carbon tax is a Pigovian tax levied on the carbon content of fuels [14], which is a form of carbon pricing. Carbon is present in every hydrocarbon fuel (coal, petroleum, and natural gas) and is released as CO2, when they are burnt [15].In this case study, it is assumed that government levies the carbon tax on coal consumption in the power sector. It means that the carbon tax will be a part of the fuel cost in operating the power plant, being of the same effect of raising the price of coal. According to the sensitive analysis, an effective carbon tax needs to increase the price of coal by 243 CNY/tce, so as to make the project financially feasible. Then the cost of carbon tax should be 90 CNY/tCO2 (1tce leads to GHG emission of 2.77 tCO2).


### 3.3.2. Incentive from Carbon Market (Credit Trading)

Emissions trading or cap-and-trade is a market-based approach used to control pollution by providing economic incentives for achieving reductions in the emissions of pollutants. For GHG the largest is the European Union Emission Trading Scheme (ETS), whose purpose is to avoid dangerous climate change [16]. In the carbon market created by ETS, GHG emission reduction credits are a kind of eligible unit, generated from the project that is implemented by entity outside the ETS. As analyzed above, the price of carbon credits in the market for example, CERs must be not less than 125 CNY/tCO2 to make the project financially attractive.


### 3.3.3. Incentives Combined with Encouraging Dispatch Plan

Since the electricity tariff is determined by the government in China, which is fixed unless the new tariff policy approved by the government, most of the coal fuel power plants resist carbon tax in practice. A very high cost of carbon tax is not very likely to occur in China. On the other hand, given the experience of the EU ETS, the credit price is of high volatility in the market [17]. Thus, there is always uncertainty about the credit price to make the investment decisions of this kind of retrofit. To mitigate the shortage of carbon tax and carbon market, the encouraging dispatch plan is expected to enhance the effect from above mechanisms.Given the sensitivity analysis, the annual operation hours of the PAT are a very crucial factor to the IRR. The annual operation hours of a power plant are normally determined by power dispatch arrangement of grid company. In this section, the effect of encouraging dispatch plan is an analysis together with carbon tax and credit price in an ETS. Clearly, the more annual operation hours of the PAT, the higher IRR appears in the Project (Table6). Thus, the necessary cost of either carbon tax and credit cost in ETS will decrease by incorporating with such encourage to dispatch plan.Table 6
The necessary cost of carbon tax and credit price with/without encouraging dispatch plan.
Dispatch plan
Necessary cost of Carbon tax
Necessary cost of credit price
The dispatch electricity generation does not change
90 CNY/tCO2
125 CNY/tCO2
Dispatched electricity generation increased by 20%
50 CNY/tCO2
85 CNY/tCO2


## 3.3.1. Incentive from Carbon Tax

Carbon tax is a Pigovian tax levied on the carbon content of fuels [14], which is a form of carbon pricing. Carbon is present in every hydrocarbon fuel (coal, petroleum, and natural gas) and is released as CO2, when they are burnt [15].In this case study, it is assumed that government levies the carbon tax on coal consumption in the power sector. It means that the carbon tax will be a part of the fuel cost in operating the power plant, being of the same effect of raising the price of coal. According to the sensitive analysis, an effective carbon tax needs to increase the price of coal by 243 CNY/tce, so as to make the project financially feasible. Then the cost of carbon tax should be 90 CNY/tCO2 (1tce leads to GHG emission of 2.77 tCO2).


## 3.3.2. Incentive from Carbon Market (Credit Trading)

Emissions trading or cap-and-trade is a market-based approach used to control pollution by providing economic incentives for achieving reductions in the emissions of pollutants. For GHG the largest is the European Union Emission Trading Scheme (ETS), whose purpose is to avoid dangerous climate change [16]. In the carbon market created by ETS, GHG emission reduction credits are a kind of eligible unit, generated from the project that is implemented by entity outside the ETS. As analyzed above, the price of carbon credits in the market for example, CERs must be not less than 125 CNY/tCO2 to make the project financially attractive.


## 3.3.3. Incentives Combined with Encouraging Dispatch Plan

Since the electricity tariff is determined by the government in China, which is fixed unless the new tariff policy approved by the government, most of the coal fuel power plants resist carbon tax in practice. A very high cost of carbon tax is not very likely to occur in China. On the other hand, given the experience of the EU ETS, the credit price is of high volatility in the market [17]. Thus, there is always uncertainty about the credit price to make the investment decisions of this kind of retrofit. To mitigate the shortage of carbon tax and carbon market, the encouraging dispatch plan is expected to enhance the effect from above mechanisms.Given the sensitivity analysis, the annual operation hours of the PAT are a very crucial factor to the IRR. The annual operation hours of a power plant are normally determined by power dispatch arrangement of grid company. In this section, the effect of encouraging dispatch plan is an analysis together with carbon tax and credit price in an ETS. Clearly, the more annual operation hours of the PAT, the higher IRR appears in the Project (Table6). Thus, the necessary cost of either carbon tax and credit cost in ETS will decrease by incorporating with such encourage to dispatch plan.Table 6
The necessary cost of carbon tax and credit price with/without encouraging dispatch plan.
Dispatch plan
Necessary cost of Carbon tax
Necessary cost of credit price
The dispatch electricity generation does not change
90 CNY/tCO2
125 CNY/tCO2
Dispatched electricity generation increased by 20%
50 CNY/tCO2
85 CNY/tCO2


## 4. Conclusions

This study presented the emission reductions of an ordinary thermal power plant after a steam turbine retrofit project with an incentive mechanism of carbon tax and carbon market (ETS). In particular, the most cost-efficient method is the combination of this mechanism made by central authorities with encouraging dispatch plan by grid company. The results presented within this paper indicate that the project will make a good demonstration for the other low efficiency thermal power plants in China.



---

*Source: 841636-2012-12-16.xml*