# Control Strategy of Constant-Speed Air-Conditioners Based on Virtual State of Charging Priority

Authors: Yanbo Che; Zheng Li; Wei He; Yuancheng Zhao; Ruiping Zhang
Journal: Mathematical Problems in Engineering
 (2019)

---

## Abstract

As typical thermostatically controlled loads (TCL) driven by constant-speed compressor, constant-speed air-conditioners play important roles in demand-side response for their abilities of energy conversion and storage. Their great potential for load regulation can be incorporated into power system scheduling through demand response. In view of their operating characteristics, a virtual energy storage (VES) model of thermostatically controlled loads with electrical and thermal parameters is established. This model is discretized and linearized to simplify calculation. By analyzing the control function and constraints of the VES model, the control strategy of VES of constant-speed air-conditioners load with virtual charging state priority is proposed. Example analysis shows that this strategy can solve and alleviate power shortage problem of the system by participating in demand response, which provides methodological support for constant-speed compressor temperature-control load to participate in the system operation.


---

## Body

## 1. Introduction

With the development of advanced measurement techniques [1], power system stakeholders are becoming pluralistic, the interaction between power generation and load response is becoming more visible, and with emerging technologies, it is easy to resolve the problem of energy shortage [2]. Demand response plays a key role in power management; once the load curve is derived, it is easy to track the power shortage, shave the peak, and fill the valley by defining user attractive schemes. The implementation of internet + smart energy strategies [3] has a great significance in relation to sale electricity reform and the construction of smart cities. Demand response can be varied by price signals and incentive measures. To control demand response by price signals, demand elasticity is used to encourage users to adjust their load in accordance with price changes. Demand response is controlled by the incentive measures; relevant policies are used to encourage users to transfer control rights through corresponding policies, so as to achieve the goal of minimum cost.Air-conditioner load operation is characterized as short time, large proportion, and high peak value. Without the improvement, it will increase the peaking pressure of the power grid and lead to imbalance of supply and demand. Allowing resident users to transfer control of air conditioning resources is the most efficient way to solve the problem of power shortage and energy consumption through, while modeling air-conditioning resources is the key to fully exploit the scheduling margin and effectively implement direct load control of demand response [4].At present, two modeling methods for TCLs are commonly accepted: equivalent thermal parameter (ETP) based on circuit simulation [5, 6] and calculation based on cold and heat load [7]. Reference [8] proposed state sequence algorithm to suppress the energy fluctuation of the tie-line by controlling the start-stop state of the thermostatically controlled loads. The specific characteristics of household load are fully considered and then a load model, taking account of users’ behavior, is established in [9]. Reference [10] uses a thermal comfort model to estimate a residential comfort level and build a dispatching system for large-scale TCL-based load. Reference [11] establishes a thermodynamic model of air-conditioner load based on the double-coupled partial differential equation and proposes the concept of VES. Reference [12] compares three control methods, (i) including air-conditioner load (ii) changing compressor start-stop valve setting and (iii) duty cycle control. But it lacks quantitative evaluation of their corresponding capacity.By guaranteeing the basic comfort requirements of users [13, 14], air-conditioning can be equivalent to VES devices. Reference [15] establishes a VES model based on air-conditioner load thermodynamic model and human thermal comfort model, which proves the potential and feasibility of applying air-conditioner load VES on demand response. Reference [16] proposed an optimal allocation model of energy-efficient power plants considering user comfort level. Its logic provides solid theoretical support for the deep participation of thermostatically controlled loads in demand-side response. Reference [17] presents a VES model of electric heating load and proposes a control strategy of electric heating load based on virtual state of charge priority table, which provides good technical support for this paper.This paper presents analysis of constant-speed air-conditioning. A VES model based on first-order thermodynamic model is proposed, which reflects the load electrothermal conversion of constant-speed air-conditioning and fulfill the potential of demand-side response. Based on the VES model, a VSOC prior to VES control strategy for constant-speed air-conditioning load is established. Simulation results validate the proposed control strategy of constant-speed air-conditioning in demand-side response and can play a major role in power management to balance the load curve.


## 2. VES Model of Constant-Speed Air-Conditioning

With the rapid increase in electricity demand, an energy-stored constant-speed air-conditioning becomes a load with great potential to vary a demand response [18] according to proposed strategy. By adopting reasonable control methods to simulate demand response, constant-speed air-conditioners can quickly respond to grid side dispatch, reduce load demand during the peak hours, and alleviate the shortage of power supply to some extent. Compared to investment on expanding the capacity of power plants, cost on demand-side response controlling and the influence of participants on reasonable comfort level is lower [19].


### 2.1. Operational Characteristics

Constant-speed air-conditioner mainly consists of the refrigeration system [20], the ventilation system, and the electrical system. Its core operating principle is “inverse Carnot cycle”; detailed processes are shown in Figure 1.Figure 1
Schematic diagram of constant-speed air-conditioner.The constant-speed air-conditioner usually adopts compressor driven by single-phase asynchronous motor, which means the speed in stable operation is determined by grid frequency. In order to maintain a specific indoor temperature, the compressor needs to be continuously on and off, which is called start-stop regulation.Referring to experimental results in [21], constant-speed air-conditioner is a constant power load within the allowable threshold range of power grid operation. In terms of dynamic characteristics, voltage flicker and frequency fluctuation of power grid will affect the processes of starting the cooling, constant temperature operation, and shutdown of air-conditioner directly, which will lead to dissatisfaction of users’ comfort level and damage of air-conditioner. Frequent start-up and shutdown of constant-speed air-conditioner should be avoided because it will increase the wear of moving parts of air-conditioner machinery and bring greater peak impact and energy loss to power grid.


### 2.2. Equivalent Thermal Parameter Model

Based on the ETP modeling method [15], this paper establishes an equivalent thermal parameter model for room thermal energy conversion, which hereinafter referred to as the ETP model.Considering the differences among solid temperature, gas temperature, heat capacity, and thermal resistance of exterior and interior walls, the classical third-order state-space thermodynamic model comprehensively analyzes the energy transfer process between the environment and the room. Neglecting the difference between inner and outer walls, the widely used second-order thermodynamic model [22] can be obtained by considering the practical application and calculating speed. When the temperature changes smoothly, there is no obvious difference between the temperature of gas and solid in the room. In order to enhance the practicability of the model, the second-order ETP model can be reduced to the first-order ETP model, as shown in Figure 2, where Pelectrical represents the refrigeration or heating rate, KW.Figure 2
First-order ETP model.Except for special instructions, this paper takes heating as an example, so hereinafter referred to as heating rate.Tin and Tout denote the temperature in and outside of room in °C, respectively. Ca represents the heat capacity of the gas J/°C; R1 represents the heat transfer resistance of the energy between the room and the external environment °C/W. Ce denotes the equivalent heat capacity in the room. According to Kirchhoff’s theorem, the state space equation of the first-order ETP model is(1)Tin·=1R1CeTout-Tin+PelectricalCeTin· is the rate of temperature change. Formula (1) can be transformed into(2)Tin-ToutR1+CedTindt=PelectricalThe physical meaning of each part of (2) is analyzed as follows: (Tin-Tout)/R1 indicates the heat loss caused by the temperature difference between the room and the external environment, R1 reacts to the extent to which heat loss is hindered, CedTin/dt represents the thermal power required for room heating, and Ce represents the amount of energy required for temperature changes.


### 2.3. VES Model

#### 2.3.1. Thermal Parameter Section

The response potential of demand-side resources mainly depends on the response time interval. Considering the different response time of demand-side resources, the virtual thermal storage parameter model in Figure3 can be obtained by equivalently changing Figure 2.Figure 3
Thermal parameters part of the VES model.In Figure3, Tint represents the indoor temperature at time t in °C; S represents the switch state, with 0 disconnected and 1 controlled. The action from the closed state to disconnected or controlled state can be regarded as the beginning of the discharging stage, and the reverse action can be regarded as the beginning of the charging stage.P e l e c t r i c a l represents the external charging power supplied in VES and it depends on the type of constant-speed air-conditioner. Ce represents the core part of energy storage in the VES thermal parameter model, mainly used in changing room temperature and its energy storage capacity mainly depends on the temperature limit of the TCL and the current temperature. Pleakage=(Tint-Tout)/R1 represents the leakage current in the virtual thermal storage parameter model, mainly depending on the energy loss caused by temperature difference.The power before the transfer of VES control is set as the base powerPbase. When the TCL participating in the demand response, Pelectrical, increases, the VES can be considered to be in charging state and vice versa in discharging state. Charging and discharging power can be expressed as(3)Pdisc=St-11-StPelectrical-PbasePchar=St1-St-1Pelectrical-PbaseP c h a r is charging power and Pdisc is discharging power. S(t) represents the switching state at t time. The charging and discharging capacity of VES is derived from the change of state rather than the persistence of state like that of batteries.LetTin(t0)=C, and from formula (2), we have(4)Tint=Toutt+SR1Pelectricalt-Toutt+SR1Pelectricalt-Ce-t/R1CeFrom formula (4), the charging and discharging time is(5)ton/off=R1Celn⁡C-Toutt-SR1PelectricaltTint-Toutt-SR1PelectricaltIn addition to the inherent room parameters, the charging and discharging time depend on internal and external temperatures, the state of switch function, and electric power. The energy of VES load is stored in capacitorCe, and by using the relationship between temperature and power in the ETP model, the maximum charge capacity of VES is(6)Qcapacity=CeTmax-TminBased on the principle of energy conservation, the charge capacity at timet is (7)Qt=Qt0+∫t0tPCeξdξwhere PCe(t) represents the power flowing into the capacitor Ce.Substituting (4) into the above formula, we have(8)Qt=CeTint0+Ce∫t0tTinξdξ=CeTint0+Ce∫t0tToutt+SR1Pelectricalt-Toutt+SR1Pelectricalt-Ce-t/R1CedξThe United States Advanced Battery Consortium (USABC) defines State of Charge (SOC) in “electric vehicle battery laboratory manual” as the ratio of the remaining battery capacity to the rated capacity under the same conditions at a certain discharge rate. Following its definition, Virtual State of Charge (VSOC) is proposed as the ratio of residual energy to rated capacity under the same charging and discharging power. Therefore, VSOC represents the response capability of VES at the current stage.(9)VSOC=QtQcapacity


#### 2.3.2. Electrical Parameter Part

Assume that the external power grid is stable; the constant-speed air-conditioner works at a fixed speed and controls room temperature by starting and stopping the compressor. Fully considering the startup characteristics, electric power can be expressed as(10)Pelectrical=ημSFact·PFac_ratedδtt≤εηSFact·PFac_ratedt>εwhere η denotes the energy efficiency ratio, which depends on the type of air-conditioner; μ denotes the impact power multiple, which mainly depends on the parameters of air-conditioning; PFac_rated denotes the rated power in KW; δ(t) denotes the impact at a certain time as a unit impulse function; ε denotes the value approaching 0, lim⁡(ε)=0; and SFac(t) is like Sh(t), which indicates the switching state, but it needs to distinguish refrigeration and heating conditions.In conclusion, the structure of the VES model is shown in Figure4. Solid lines with arrows indicate the direction of energy flow, and dashed lines with arrows indicate the direction of signal flow.Figure 4
VES model.


## 2.1. Operational Characteristics

Constant-speed air-conditioner mainly consists of the refrigeration system [20], the ventilation system, and the electrical system. Its core operating principle is “inverse Carnot cycle”; detailed processes are shown in Figure 1.Figure 1
Schematic diagram of constant-speed air-conditioner.The constant-speed air-conditioner usually adopts compressor driven by single-phase asynchronous motor, which means the speed in stable operation is determined by grid frequency. In order to maintain a specific indoor temperature, the compressor needs to be continuously on and off, which is called start-stop regulation.Referring to experimental results in [21], constant-speed air-conditioner is a constant power load within the allowable threshold range of power grid operation. In terms of dynamic characteristics, voltage flicker and frequency fluctuation of power grid will affect the processes of starting the cooling, constant temperature operation, and shutdown of air-conditioner directly, which will lead to dissatisfaction of users’ comfort level and damage of air-conditioner. Frequent start-up and shutdown of constant-speed air-conditioner should be avoided because it will increase the wear of moving parts of air-conditioner machinery and bring greater peak impact and energy loss to power grid.


## 2.2. Equivalent Thermal Parameter Model

Based on the ETP modeling method [15], this paper establishes an equivalent thermal parameter model for room thermal energy conversion, which hereinafter referred to as the ETP model.Considering the differences among solid temperature, gas temperature, heat capacity, and thermal resistance of exterior and interior walls, the classical third-order state-space thermodynamic model comprehensively analyzes the energy transfer process between the environment and the room. Neglecting the difference between inner and outer walls, the widely used second-order thermodynamic model [22] can be obtained by considering the practical application and calculating speed. When the temperature changes smoothly, there is no obvious difference between the temperature of gas and solid in the room. In order to enhance the practicability of the model, the second-order ETP model can be reduced to the first-order ETP model, as shown in Figure 2, where Pelectrical represents the refrigeration or heating rate, KW.Figure 2
First-order ETP model.Except for special instructions, this paper takes heating as an example, so hereinafter referred to as heating rate.Tin and Tout denote the temperature in and outside of room in °C, respectively. Ca represents the heat capacity of the gas J/°C; R1 represents the heat transfer resistance of the energy between the room and the external environment °C/W. Ce denotes the equivalent heat capacity in the room. According to Kirchhoff’s theorem, the state space equation of the first-order ETP model is(1)Tin·=1R1CeTout-Tin+PelectricalCeTin· is the rate of temperature change. Formula (1) can be transformed into(2)Tin-ToutR1+CedTindt=PelectricalThe physical meaning of each part of (2) is analyzed as follows: (Tin-Tout)/R1 indicates the heat loss caused by the temperature difference between the room and the external environment, R1 reacts to the extent to which heat loss is hindered, CedTin/dt represents the thermal power required for room heating, and Ce represents the amount of energy required for temperature changes.


## 2.3. VES Model

### 2.3.1. Thermal Parameter Section

The response potential of demand-side resources mainly depends on the response time interval. Considering the different response time of demand-side resources, the virtual thermal storage parameter model in Figure3 can be obtained by equivalently changing Figure 2.Figure 3
Thermal parameters part of the VES model.In Figure3, Tint represents the indoor temperature at time t in °C; S represents the switch state, with 0 disconnected and 1 controlled. The action from the closed state to disconnected or controlled state can be regarded as the beginning of the discharging stage, and the reverse action can be regarded as the beginning of the charging stage.P e l e c t r i c a l represents the external charging power supplied in VES and it depends on the type of constant-speed air-conditioner. Ce represents the core part of energy storage in the VES thermal parameter model, mainly used in changing room temperature and its energy storage capacity mainly depends on the temperature limit of the TCL and the current temperature. Pleakage=(Tint-Tout)/R1 represents the leakage current in the virtual thermal storage parameter model, mainly depending on the energy loss caused by temperature difference.The power before the transfer of VES control is set as the base powerPbase. When the TCL participating in the demand response, Pelectrical, increases, the VES can be considered to be in charging state and vice versa in discharging state. Charging and discharging power can be expressed as(3)Pdisc=St-11-StPelectrical-PbasePchar=St1-St-1Pelectrical-PbaseP c h a r is charging power and Pdisc is discharging power. S(t) represents the switching state at t time. The charging and discharging capacity of VES is derived from the change of state rather than the persistence of state like that of batteries.LetTin(t0)=C, and from formula (2), we have(4)Tint=Toutt+SR1Pelectricalt-Toutt+SR1Pelectricalt-Ce-t/R1CeFrom formula (4), the charging and discharging time is(5)ton/off=R1Celn⁡C-Toutt-SR1PelectricaltTint-Toutt-SR1PelectricaltIn addition to the inherent room parameters, the charging and discharging time depend on internal and external temperatures, the state of switch function, and electric power. The energy of VES load is stored in capacitorCe, and by using the relationship between temperature and power in the ETP model, the maximum charge capacity of VES is(6)Qcapacity=CeTmax-TminBased on the principle of energy conservation, the charge capacity at timet is (7)Qt=Qt0+∫t0tPCeξdξwhere PCe(t) represents the power flowing into the capacitor Ce.Substituting (4) into the above formula, we have(8)Qt=CeTint0+Ce∫t0tTinξdξ=CeTint0+Ce∫t0tToutt+SR1Pelectricalt-Toutt+SR1Pelectricalt-Ce-t/R1CedξThe United States Advanced Battery Consortium (USABC) defines State of Charge (SOC) in “electric vehicle battery laboratory manual” as the ratio of the remaining battery capacity to the rated capacity under the same conditions at a certain discharge rate. Following its definition, Virtual State of Charge (VSOC) is proposed as the ratio of residual energy to rated capacity under the same charging and discharging power. Therefore, VSOC represents the response capability of VES at the current stage.(9)VSOC=QtQcapacity


### 2.3.2. Electrical Parameter Part

Assume that the external power grid is stable; the constant-speed air-conditioner works at a fixed speed and controls room temperature by starting and stopping the compressor. Fully considering the startup characteristics, electric power can be expressed as(10)Pelectrical=ημSFact·PFac_ratedδtt≤εηSFact·PFac_ratedt>εwhere η denotes the energy efficiency ratio, which depends on the type of air-conditioner; μ denotes the impact power multiple, which mainly depends on the parameters of air-conditioning; PFac_rated denotes the rated power in KW; δ(t) denotes the impact at a certain time as a unit impulse function; ε denotes the value approaching 0, lim⁡(ε)=0; and SFac(t) is like Sh(t), which indicates the switching state, but it needs to distinguish refrigeration and heating conditions.In conclusion, the structure of the VES model is shown in Figure4. Solid lines with arrows indicate the direction of energy flow, and dashed lines with arrows indicate the direction of signal flow.Figure 4
VES model.


## 2.3.1. Thermal Parameter Section

The response potential of demand-side resources mainly depends on the response time interval. Considering the different response time of demand-side resources, the virtual thermal storage parameter model in Figure3 can be obtained by equivalently changing Figure 2.Figure 3
Thermal parameters part of the VES model.In Figure3, Tint represents the indoor temperature at time t in °C; S represents the switch state, with 0 disconnected and 1 controlled. The action from the closed state to disconnected or controlled state can be regarded as the beginning of the discharging stage, and the reverse action can be regarded as the beginning of the charging stage.P e l e c t r i c a l represents the external charging power supplied in VES and it depends on the type of constant-speed air-conditioner. Ce represents the core part of energy storage in the VES thermal parameter model, mainly used in changing room temperature and its energy storage capacity mainly depends on the temperature limit of the TCL and the current temperature. Pleakage=(Tint-Tout)/R1 represents the leakage current in the virtual thermal storage parameter model, mainly depending on the energy loss caused by temperature difference.The power before the transfer of VES control is set as the base powerPbase. When the TCL participating in the demand response, Pelectrical, increases, the VES can be considered to be in charging state and vice versa in discharging state. Charging and discharging power can be expressed as(3)Pdisc=St-11-StPelectrical-PbasePchar=St1-St-1Pelectrical-PbaseP c h a r is charging power and Pdisc is discharging power. S(t) represents the switching state at t time. The charging and discharging capacity of VES is derived from the change of state rather than the persistence of state like that of batteries.LetTin(t0)=C, and from formula (2), we have(4)Tint=Toutt+SR1Pelectricalt-Toutt+SR1Pelectricalt-Ce-t/R1CeFrom formula (4), the charging and discharging time is(5)ton/off=R1Celn⁡C-Toutt-SR1PelectricaltTint-Toutt-SR1PelectricaltIn addition to the inherent room parameters, the charging and discharging time depend on internal and external temperatures, the state of switch function, and electric power. The energy of VES load is stored in capacitorCe, and by using the relationship between temperature and power in the ETP model, the maximum charge capacity of VES is(6)Qcapacity=CeTmax-TminBased on the principle of energy conservation, the charge capacity at timet is (7)Qt=Qt0+∫t0tPCeξdξwhere PCe(t) represents the power flowing into the capacitor Ce.Substituting (4) into the above formula, we have(8)Qt=CeTint0+Ce∫t0tTinξdξ=CeTint0+Ce∫t0tToutt+SR1Pelectricalt-Toutt+SR1Pelectricalt-Ce-t/R1CedξThe United States Advanced Battery Consortium (USABC) defines State of Charge (SOC) in “electric vehicle battery laboratory manual” as the ratio of the remaining battery capacity to the rated capacity under the same conditions at a certain discharge rate. Following its definition, Virtual State of Charge (VSOC) is proposed as the ratio of residual energy to rated capacity under the same charging and discharging power. Therefore, VSOC represents the response capability of VES at the current stage.(9)VSOC=QtQcapacity


## 2.3.2. Electrical Parameter Part

Assume that the external power grid is stable; the constant-speed air-conditioner works at a fixed speed and controls room temperature by starting and stopping the compressor. Fully considering the startup characteristics, electric power can be expressed as(10)Pelectrical=ημSFact·PFac_ratedδtt≤εηSFact·PFac_ratedt>εwhere η denotes the energy efficiency ratio, which depends on the type of air-conditioner; μ denotes the impact power multiple, which mainly depends on the parameters of air-conditioning; PFac_rated denotes the rated power in KW; δ(t) denotes the impact at a certain time as a unit impulse function; ε denotes the value approaching 0, lim⁡(ε)=0; and SFac(t) is like Sh(t), which indicates the switching state, but it needs to distinguish refrigeration and heating conditions.In conclusion, the structure of the VES model is shown in Figure4. Solid lines with arrows indicate the direction of energy flow, and dashed lines with arrows indicate the direction of signal flow.Figure 4
VES model.


## 3. Preprocessing Based on Policy Model

Advanced measurement system [23] records data such as user power consumption at a specific time interval and can transmit data to the data center system through the communication network in a specific time period, which provides a hardware basis for demand response.The communication capacity of advanced measurement systems supporting demand response is limited. In order to prevent communication data congestion and improve communication timeliness, it is necessary to discretize and linearize the original VES model.


### 3.1. Operational characteristics

In the process of demand response, constant-speed air-conditioner is intermittent, andPelectrical is the discrete variable. Tin(t), as a continuous variable, has relatively larger demand of traffic flow. Formula (4) cannot describe Tin(t) in actual data transmission. Therefore, it is necessary to discretize the VES model.Assuming the time step isΔt, the solution of (2) can be obtained(11)Tint+1=Toutt+1+SR1Pelectrical-Toutt+1+SR1Pelectrical-Tinte-Δt/R1Cewhere Tint denotes the temperature inside the room at time t in °C; Tint+1 denotes the temperature inside the room at timet+1 in °C; Toutt denotes the temperature outside the room at timet in °C; Toutt+1 denotes the temperature outside the room at timet+1 in °C; and S denotes that the switch function is 0 or 1 according to the operating conditions. Δt denotes the communication time interval.


### 3.2. Model Linearization

Temperature change is a slow process. When the response time of participating demand side is shorter, the external environment is considered as no change, i.e.,Toutt=Toutt+1. Setting the room temperature range to [Tmin,Tmax], control cycle of Pelectrical to tcyc, where the time with electric power input is ton, and the time without electric power input is toff. From the iterative calculation of Tmin and Tmax with the formula (11)(12)Tmax=Tout+R1Pelectrical1-e-tonΔt/R1Ce+Tmine-tonΔt/R1CeTmin=Tout1-e-toffΔt/R1Ce+Tmaxe-toffΔt/R1Cetcyc=ton+toffSolve (12) to obtain the charging and discharging time as(13)toff=R1CeΔtln⁡Tmax-ToutTmin-Toutton=R1CeΔtln⁡Tmin-Tout-R1PelectricalTmax-Tout-R1PelectricalWith the ratio of time intervalΔt to total switching timeton and toff, the temperature change of each iteration is described as(14)Tint+1=Tint+ΔttonTmax-Tmins=1Tint+1=Tint-ΔttoffTmax-Tmins=0taking the air-conditioner heating as an example to verify the rationality of linearization. The simulation parameters areR1=0.1208°C/W; Ce=3599.3J/°C [24]; Pelectrical =400W; Tmin =23°C; Tmax =26°C; Δt=1min; Tout≡ 0°C; and Tino=18°C, and the simulation results of MATLAB platform are shown in Figure 5. The solid line represents the temperature changes with time from the first-order ETP model and the dotted line represents the result shown in the linearized ETP model. By conducting comparative analysis of the temperature rise process from 18°C to 26°C and the heat preservation process from 23°C to 26°C, the results show that the linearization effect is better in the shorter temperature range and the part near the temperature limit is better.Figure 5
Comparison of temperature curves between linearized model and original ETP model.The correlation coefficientsR for the two curves are calculated as(15)RX,Y=CovX,YDX·DYwhereR(X,Y) denotes the correlation coefficient of X and Y; the closer the correlation coefficient is to 1, the greater the correlation between the two curves is, and the less the influence of substitution is; Cov(X,Y) denotes the covariance of X and Y; D(X), D(Y) denotes the standard deviation of X and Y.Within 300 minutes, the overall correlation coefficient isR=0.99856 between the linearized ETP model and the first-order ETP model. Generally speaking, the VES load below the minimum temperature does not participate in the demand response. The correlation coefficient of the heating process part and the normal working part isR=0.99919. It is considered that the linearization processing has a good fitting effect with the original model and will not have any greater impact on the relevant results.


## 3.1. Operational characteristics

In the process of demand response, constant-speed air-conditioner is intermittent, andPelectrical is the discrete variable. Tin(t), as a continuous variable, has relatively larger demand of traffic flow. Formula (4) cannot describe Tin(t) in actual data transmission. Therefore, it is necessary to discretize the VES model.Assuming the time step isΔt, the solution of (2) can be obtained(11)Tint+1=Toutt+1+SR1Pelectrical-Toutt+1+SR1Pelectrical-Tinte-Δt/R1Cewhere Tint denotes the temperature inside the room at time t in °C; Tint+1 denotes the temperature inside the room at timet+1 in °C; Toutt denotes the temperature outside the room at timet in °C; Toutt+1 denotes the temperature outside the room at timet+1 in °C; and S denotes that the switch function is 0 or 1 according to the operating conditions. Δt denotes the communication time interval.


## 3.2. Model Linearization

Temperature change is a slow process. When the response time of participating demand side is shorter, the external environment is considered as no change, i.e.,Toutt=Toutt+1. Setting the room temperature range to [Tmin,Tmax], control cycle of Pelectrical to tcyc, where the time with electric power input is ton, and the time without electric power input is toff. From the iterative calculation of Tmin and Tmax with the formula (11)(12)Tmax=Tout+R1Pelectrical1-e-tonΔt/R1Ce+Tmine-tonΔt/R1CeTmin=Tout1-e-toffΔt/R1Ce+Tmaxe-toffΔt/R1Cetcyc=ton+toffSolve (12) to obtain the charging and discharging time as(13)toff=R1CeΔtln⁡Tmax-ToutTmin-Toutton=R1CeΔtln⁡Tmin-Tout-R1PelectricalTmax-Tout-R1PelectricalWith the ratio of time intervalΔt to total switching timeton and toff, the temperature change of each iteration is described as(14)Tint+1=Tint+ΔttonTmax-Tmins=1Tint+1=Tint-ΔttoffTmax-Tmins=0taking the air-conditioner heating as an example to verify the rationality of linearization. The simulation parameters areR1=0.1208°C/W; Ce=3599.3J/°C [24]; Pelectrical =400W; Tmin =23°C; Tmax =26°C; Δt=1min; Tout≡ 0°C; and Tino=18°C, and the simulation results of MATLAB platform are shown in Figure 5. The solid line represents the temperature changes with time from the first-order ETP model and the dotted line represents the result shown in the linearized ETP model. By conducting comparative analysis of the temperature rise process from 18°C to 26°C and the heat preservation process from 23°C to 26°C, the results show that the linearization effect is better in the shorter temperature range and the part near the temperature limit is better.Figure 5
Comparison of temperature curves between linearized model and original ETP model.The correlation coefficientsR for the two curves are calculated as(15)RX,Y=CovX,YDX·DYwhereR(X,Y) denotes the correlation coefficient of X and Y; the closer the correlation coefficient is to 1, the greater the correlation between the two curves is, and the less the influence of substitution is; Cov(X,Y) denotes the covariance of X and Y; D(X), D(Y) denotes the standard deviation of X and Y.Within 300 minutes, the overall correlation coefficient isR=0.99856 between the linearized ETP model and the first-order ETP model. Generally speaking, the VES load below the minimum temperature does not participate in the demand response. The correlation coefficient of the heating process part and the normal working part isR=0.99919. It is considered that the linearization processing has a good fitting effect with the original model and will not have any greater impact on the relevant results.


## 4. VSOC Priority VES Control Strategy

VSOC prioritized VES control strategy is to select the one with higher VSOC to participate in demand response for the same type of VES equipment.


### 4.1. Control Model of Constant-Speed Air-Conditioning

Community users are involved in demand response. Assuming that the external environment does not change during the response period, the energy consumption only occurs when the room temperature and the external temperature change. Communication data refresh interval isΔt.The change of the switch determines the working state of the VES model, and the switch function must highlight the state changes at different times. Setting switch functionSFac=1 as charging and SFac=0 as discharging, then the VES of a constant-speed air-conditioner at a certain time t is(16)PjFac_disct=SFacjt-11-SFacjtPjFac_rated(17)PjFac_chart=μSFacjt1-SFacjt-1·PjFac_ratedδtt≤εSFacjt1-SFacjt-1·PjFac_ratedt>εSubscripts Fac_disc and Fac_char denote discharging power and charging power of constant-speed air-conditioner, respectively. Superscript j denotes thej-th VES unit, and PjFac_rated denotes rated power of thejth constant-speed air-conditioner.μ is the multiple of impact power, and δ(t) is a unit impulse function.The charging process of constant-speed air-conditioner VES is divided into two stages. At the beginning, an impact power withμ times of rated power lasts a very short time period, which then quickly falls to the rated power. Due to the impact power, it is necessary to limit the number of times in relation to start-stop loads per unit of time and start-stops during a single-load control period strictly.At a certain momentt, VSOCjFac of thejth constant-speed air-conditioner or virtual energy storage unit is(18)VSOCFacjt=QFactQFac_capacity=CejTjFact-TjFac_minCejTjFac_max-TjFac_min=TjFact-TjFac_minTjFac_max-TjFac_minAt a certain moment t, thejth constant-speed air-conditioner VES VSOCjFac is(19)VSOCjFact+1=Δt-∑0iεjSjFacttjFac_on_max-1-SjFacttjFac_off_max+VSOCjFactwhere i represents the i-th constant-speed air-conditioner in the start-up sequence, ti represents the time point of the i-th start-up, and k represents the number of constant-speed air-conditioners needed to start-up during the time interval Δt.To reduce the impact power of constant-speed air-conditioning in demand response and prevent the maloperation of relay protection device due to the superposition of power peaks caused by start-up, two constraints are added to (19).(20)tjFac_offtjFac_off_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minj1-tjFac_ontjFac_on_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minjThe first one indicates that the interval between start times of every two air-conditioners should be greater thanεi during the demand response process; the second one indicates the restriction to duration that the air-conditioner started within the time interval bearing the impact power.Figure6 represents the relationships among linearized temperature curve, VSOC curve, and electric power and thermal power. The shaded part indicates that the VES equipment not reaching the steady-state temperature is not considered. For thejth VES of air-conditioner at time t, Tj(t) denotes the temperature; tjFac_off denotes the remaining discharge time; tjFac_off_max denotes the maximum discharge time; tjFac_on_max denotes the maximum charge time; and tjFac_on denotes the remaining charge time.Figure 6
Relation diagram of linearized temperature curve, VSOC curve, and thermal power.Using triangle similarity principle, the virtual charge state of VES in constant-speed air-conditioner can be expressed by the ratio of the difference between the current temperature and limit value. The essence of discretization and linearization of the VES model is to describe electrical parameters with thermal parameters, i.e., to complete the conversion of electrical parameters to thermal parameters in the time domain.Charging and discharging time is an important constraint index. On the one hand, it can prevent the VES unit of air-conditioner from overcharged or overdischarged maintaining the temperature fluctuation of air-conditioner within the set range. On the other hand, it can keep the state of equipment during communication time interval to avoid affecting the control accuracy and bringing unnecessary network side fluctuation.(21)tjFac_offtjFac_off_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minj1-tjFac_ontjFac_on_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minjFurther simplification is available:(22)tFac_offj=VSOCjFacttFac_off_maxjtFac_onj=1-VSOCjFacttFac_on_maxjTo sum up, taking discharge as an example, the control model of VES for constant-speed air-conditioning is established.(23)PjFac_disct=SFacjt-11-SFacjtPjFac_ratedVSOCjFact+1=Δt-∑0iεjSjFacttjFac_on_max-1-SjFacttjFac_off_max+VSOCjFacttFac_offj=VSOCjFacttFac_off_maxj


### 4.2. Control Strategy and Algorithms Analysis

The main idea of the control strategy for constant-speed air-conditioners is to control the on-off state of VES in the light of their VSOCs. The VES equipment with higher VSOC will be turned off in priority. The VSOC value is in the range of 0-1. Its main objective function is to satisfy the power vacancy within the communication time interval, and the marginal limitation is the discharge time is longer than the communication time interval. In addition, it is necessary to satisfy the relevant constraints in the control model and ensure that the power peak is as small as possible. Specific control functions are shown as formulas.(24)Pst≤min⁡∑APtFac_discjnPst-∑APtFac_discjn≤min⁡∑∁QAPtFac_discjn0≤VSOCFactjn≤1tjnFac_off≥Δttjni+1-tjni≥εjnk<Δtmini∈0,k⁡εiAmong them,Pst represents the power vacancy at time t; Q is the set in which air-conditioners are arranged according to their VSOCs from large to small; jn is the element of Q sets, and n represents the position of j in the new set, A denotes the controlled set arranged from large to small according to VSOC; and CQA denotes the complement set of A whose complete set is Q. The new restriction condition expresses the priority of controlled virtual energy storage discharge and then supplements the power vacancy based on the size of VSOC.Using MATLAB as the simulation platform, major program implementation steps include refreshing data status, dealing with VSOC overlimit problem, generating control queueQ based on VSOCs, calculating whether the power vacancy is met, generating startup queue based on impact power, processing related startup queue, and iteratively updating VES status.


## 4.1. Control Model of Constant-Speed Air-Conditioning

Community users are involved in demand response. Assuming that the external environment does not change during the response period, the energy consumption only occurs when the room temperature and the external temperature change. Communication data refresh interval isΔt.The change of the switch determines the working state of the VES model, and the switch function must highlight the state changes at different times. Setting switch functionSFac=1 as charging and SFac=0 as discharging, then the VES of a constant-speed air-conditioner at a certain time t is(16)PjFac_disct=SFacjt-11-SFacjtPjFac_rated(17)PjFac_chart=μSFacjt1-SFacjt-1·PjFac_ratedδtt≤εSFacjt1-SFacjt-1·PjFac_ratedt>εSubscripts Fac_disc and Fac_char denote discharging power and charging power of constant-speed air-conditioner, respectively. Superscript j denotes thej-th VES unit, and PjFac_rated denotes rated power of thejth constant-speed air-conditioner.μ is the multiple of impact power, and δ(t) is a unit impulse function.The charging process of constant-speed air-conditioner VES is divided into two stages. At the beginning, an impact power withμ times of rated power lasts a very short time period, which then quickly falls to the rated power. Due to the impact power, it is necessary to limit the number of times in relation to start-stop loads per unit of time and start-stops during a single-load control period strictly.At a certain momentt, VSOCjFac of thejth constant-speed air-conditioner or virtual energy storage unit is(18)VSOCFacjt=QFactQFac_capacity=CejTjFact-TjFac_minCejTjFac_max-TjFac_min=TjFact-TjFac_minTjFac_max-TjFac_minAt a certain moment t, thejth constant-speed air-conditioner VES VSOCjFac is(19)VSOCjFact+1=Δt-∑0iεjSjFacttjFac_on_max-1-SjFacttjFac_off_max+VSOCjFactwhere i represents the i-th constant-speed air-conditioner in the start-up sequence, ti represents the time point of the i-th start-up, and k represents the number of constant-speed air-conditioners needed to start-up during the time interval Δt.To reduce the impact power of constant-speed air-conditioning in demand response and prevent the maloperation of relay protection device due to the superposition of power peaks caused by start-up, two constraints are added to (19).(20)tjFac_offtjFac_off_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minj1-tjFac_ontjFac_on_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minjThe first one indicates that the interval between start times of every two air-conditioners should be greater thanεi during the demand response process; the second one indicates the restriction to duration that the air-conditioner started within the time interval bearing the impact power.Figure6 represents the relationships among linearized temperature curve, VSOC curve, and electric power and thermal power. The shaded part indicates that the VES equipment not reaching the steady-state temperature is not considered. For thejth VES of air-conditioner at time t, Tj(t) denotes the temperature; tjFac_off denotes the remaining discharge time; tjFac_off_max denotes the maximum discharge time; tjFac_on_max denotes the maximum charge time; and tjFac_on denotes the remaining charge time.Figure 6
Relation diagram of linearized temperature curve, VSOC curve, and thermal power.Using triangle similarity principle, the virtual charge state of VES in constant-speed air-conditioner can be expressed by the ratio of the difference between the current temperature and limit value. The essence of discretization and linearization of the VES model is to describe electrical parameters with thermal parameters, i.e., to complete the conversion of electrical parameters to thermal parameters in the time domain.Charging and discharging time is an important constraint index. On the one hand, it can prevent the VES unit of air-conditioner from overcharged or overdischarged maintaining the temperature fluctuation of air-conditioner within the set range. On the other hand, it can keep the state of equipment during communication time interval to avoid affecting the control accuracy and bringing unnecessary network side fluctuation.(21)tjFac_offtjFac_off_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minj1-tjFac_ontjFac_on_max=VSOCFacjt-VSOCFac_minjVSOCFac_maxj-VSOCFac_minjFurther simplification is available:(22)tFac_offj=VSOCjFacttFac_off_maxjtFac_onj=1-VSOCjFacttFac_on_maxjTo sum up, taking discharge as an example, the control model of VES for constant-speed air-conditioning is established.(23)PjFac_disct=SFacjt-11-SFacjtPjFac_ratedVSOCjFact+1=Δt-∑0iεjSjFacttjFac_on_max-1-SjFacttjFac_off_max+VSOCjFacttFac_offj=VSOCjFacttFac_off_maxj


## 4.2. Control Strategy and Algorithms Analysis

The main idea of the control strategy for constant-speed air-conditioners is to control the on-off state of VES in the light of their VSOCs. The VES equipment with higher VSOC will be turned off in priority. The VSOC value is in the range of 0-1. Its main objective function is to satisfy the power vacancy within the communication time interval, and the marginal limitation is the discharge time is longer than the communication time interval. In addition, it is necessary to satisfy the relevant constraints in the control model and ensure that the power peak is as small as possible. Specific control functions are shown as formulas.(24)Pst≤min⁡∑APtFac_discjnPst-∑APtFac_discjn≤min⁡∑∁QAPtFac_discjn0≤VSOCFactjn≤1tjnFac_off≥Δttjni+1-tjni≥εjnk<Δtmini∈0,k⁡εiAmong them,Pst represents the power vacancy at time t; Q is the set in which air-conditioners are arranged according to their VSOCs from large to small; jn is the element of Q sets, and n represents the position of j in the new set, A denotes the controlled set arranged from large to small according to VSOC; and CQA denotes the complement set of A whose complete set is Q. The new restriction condition expresses the priority of controlled virtual energy storage discharge and then supplements the power vacancy based on the size of VSOC.Using MATLAB as the simulation platform, major program implementation steps include refreshing data status, dealing with VSOC overlimit problem, generating control queueQ based on VSOCs, calculating whether the power vacancy is met, generating startup queue based on impact power, processing related startup queue, and iteratively updating VES status.


## 5. Example Analysis

### 5.1. Algorithmic Case

The parameters of the example are as follows. There are 100 constant-speed air-conditioners whose initial VSOCs are uniformly distributed within[0,1], switching functions are 0-1 integer distributed, and time intervals are 1 minute. The rated power is 2~3kW uniformly distributed; the maximum charging time and discharge time are 10~15min and 20~30min uniformly distributed; the minimum temperature and maximum temperature of protocol are 24~25°C and 27~28°C uniformly distributed; the impact coefficient is 2~3 uniformly distributed; and the starting current duration is 3~5s uniformly distributed. The maximum response potential was 128.25 kW.Assume that the shortage power is 30 kW and the protocol control period is 120 minutes, the related control results are shown in Figure7.Figure 7
Power change and VSOC change chart in 120 minutes after optimization.
(a)
Response power change diagram (b)
VSOC change chart of 100 constant-speed air-conditioner with VESThrough reasonable dispatch during the protocol control period, the air conditioning load response power basically meets the shortage power, thus reducing the coincidence rate of the power system and making the power load operation more stable.


### 5.2. Analysis of Control Strategy Parameters of VSOC Priority Constant-Speed Air-Conditioners

Based on the example analyzed before, the influences of different power shortages and communication time intervals in the control strategy are discussed in this section.


#### 5.2.1. Tracking Effect of VSOC Priority Constant-Speed Air-Conditioners Control Strategy

Assuming that the maximum power vacancy of demand-side response is 50 KW and the minimum is 10 KW sinusoidal curve, the control time is set to 120 minutes.Figure8 shows the tracking effect. As indicated in Figure 8, the response power is in the capacity range, and the VSOC priority constant-speed air-conditioning control strategy can track the shortage power well. Power fluctuation and burr are mainly produced by the demand response of constant-speed air-conditioning.Figure 8
Tracking effect of VSOC priority constant-speed air-conditioning control strategy.


#### 5.2.2. Influence of Power Deviancy on Control Effect

40 kW, 100 kW, 130 kW, and 150 kW are selected to analyze the control effect in the range of response power capacity and over the range of capacity. Results of control effect are shown in Figures9 and 10.Figure 9
VES control effect of 40 kW and 100 kW power deficiency constant-speed air-conditioners.
(a) (b)Figure 10
130 kW and 150 kW power shortage constant-speed air-conditioners VES control effect.
(a) (b)When the gap power slightly exceeds the range, the initial response power will fluctuate massively, and the VSOC of its VES will oscillate at the bottom. After a period of adjustment, the response power can barely meet the power gap. With the gradual increase of the gap power, the response power will keep oscillating violently, and the VSOC state of VES will keep hovering at the bottom. As a result, the excessive response will lead to the violent oscillation of the response power. This will not only cause the failure to achieve response effect, but also pose greater threat by increasing the power oscillation in the distribution network.


#### 5.2.3. Influence of Communication Time Interval on Control Effect

The communication time interval determines the refresh rate of the VES data, which will affect the control results. Figure11 shows the control effect of VES in constant-speed air-conditioning with time interval of 2 minutes and 5 minutes, respectively. The whole process lasts 60 minutes. In order to achieve these results, the response power should be selected in the capacity range and the gap power of constant-speed air-conditioning should be set as 60 KW.Figure 11
(a) and (b) show the control effect of VES in constant-speed air-conditioning with time intervals of 2 minutes and 5 minutes, respectively.
(a) (b)Communication time interval has a significant influence on VES of constant-speed air-conditioning. With the increasing of time interval, the constant-speed air-conditioning control strategy will gradually lose control over VES. The obvious power shortage will occur when the time interval is 5 minutes and the gap power is 60 KW. With the fluctuation range of power over 80%, the maximum power vacancy can reach up to 50%.


## 5.1. Algorithmic Case

The parameters of the example are as follows. There are 100 constant-speed air-conditioners whose initial VSOCs are uniformly distributed within[0,1], switching functions are 0-1 integer distributed, and time intervals are 1 minute. The rated power is 2~3kW uniformly distributed; the maximum charging time and discharge time are 10~15min and 20~30min uniformly distributed; the minimum temperature and maximum temperature of protocol are 24~25°C and 27~28°C uniformly distributed; the impact coefficient is 2~3 uniformly distributed; and the starting current duration is 3~5s uniformly distributed. The maximum response potential was 128.25 kW.Assume that the shortage power is 30 kW and the protocol control period is 120 minutes, the related control results are shown in Figure7.Figure 7
Power change and VSOC change chart in 120 minutes after optimization.
(a)
Response power change diagram (b)
VSOC change chart of 100 constant-speed air-conditioner with VESThrough reasonable dispatch during the protocol control period, the air conditioning load response power basically meets the shortage power, thus reducing the coincidence rate of the power system and making the power load operation more stable.


## 5.2. Analysis of Control Strategy Parameters of VSOC Priority Constant-Speed Air-Conditioners

Based on the example analyzed before, the influences of different power shortages and communication time intervals in the control strategy are discussed in this section.


### 5.2.1. Tracking Effect of VSOC Priority Constant-Speed Air-Conditioners Control Strategy

Assuming that the maximum power vacancy of demand-side response is 50 KW and the minimum is 10 KW sinusoidal curve, the control time is set to 120 minutes.Figure8 shows the tracking effect. As indicated in Figure 8, the response power is in the capacity range, and the VSOC priority constant-speed air-conditioning control strategy can track the shortage power well. Power fluctuation and burr are mainly produced by the demand response of constant-speed air-conditioning.Figure 8
Tracking effect of VSOC priority constant-speed air-conditioning control strategy.


### 5.2.2. Influence of Power Deviancy on Control Effect

40 kW, 100 kW, 130 kW, and 150 kW are selected to analyze the control effect in the range of response power capacity and over the range of capacity. Results of control effect are shown in Figures9 and 10.Figure 9
VES control effect of 40 kW and 100 kW power deficiency constant-speed air-conditioners.
(a) (b)Figure 10
130 kW and 150 kW power shortage constant-speed air-conditioners VES control effect.
(a) (b)When the gap power slightly exceeds the range, the initial response power will fluctuate massively, and the VSOC of its VES will oscillate at the bottom. After a period of adjustment, the response power can barely meet the power gap. With the gradual increase of the gap power, the response power will keep oscillating violently, and the VSOC state of VES will keep hovering at the bottom. As a result, the excessive response will lead to the violent oscillation of the response power. This will not only cause the failure to achieve response effect, but also pose greater threat by increasing the power oscillation in the distribution network.


### 5.2.3. Influence of Communication Time Interval on Control Effect

The communication time interval determines the refresh rate of the VES data, which will affect the control results. Figure11 shows the control effect of VES in constant-speed air-conditioning with time interval of 2 minutes and 5 minutes, respectively. The whole process lasts 60 minutes. In order to achieve these results, the response power should be selected in the capacity range and the gap power of constant-speed air-conditioning should be set as 60 KW.Figure 11
(a) and (b) show the control effect of VES in constant-speed air-conditioning with time intervals of 2 minutes and 5 minutes, respectively.
(a) (b)Communication time interval has a significant influence on VES of constant-speed air-conditioning. With the increasing of time interval, the constant-speed air-conditioning control strategy will gradually lose control over VES. The obvious power shortage will occur when the time interval is 5 minutes and the gap power is 60 KW. With the fluctuation range of power over 80%, the maximum power vacancy can reach up to 50%.


## 5.2.1. Tracking Effect of VSOC Priority Constant-Speed Air-Conditioners Control Strategy

Assuming that the maximum power vacancy of demand-side response is 50 KW and the minimum is 10 KW sinusoidal curve, the control time is set to 120 minutes.Figure8 shows the tracking effect. As indicated in Figure 8, the response power is in the capacity range, and the VSOC priority constant-speed air-conditioning control strategy can track the shortage power well. Power fluctuation and burr are mainly produced by the demand response of constant-speed air-conditioning.Figure 8
Tracking effect of VSOC priority constant-speed air-conditioning control strategy.


## 5.2.2. Influence of Power Deviancy on Control Effect

40 kW, 100 kW, 130 kW, and 150 kW are selected to analyze the control effect in the range of response power capacity and over the range of capacity. Results of control effect are shown in Figures9 and 10.Figure 9
VES control effect of 40 kW and 100 kW power deficiency constant-speed air-conditioners.
(a) (b)Figure 10
130 kW and 150 kW power shortage constant-speed air-conditioners VES control effect.
(a) (b)When the gap power slightly exceeds the range, the initial response power will fluctuate massively, and the VSOC of its VES will oscillate at the bottom. After a period of adjustment, the response power can barely meet the power gap. With the gradual increase of the gap power, the response power will keep oscillating violently, and the VSOC state of VES will keep hovering at the bottom. As a result, the excessive response will lead to the violent oscillation of the response power. This will not only cause the failure to achieve response effect, but also pose greater threat by increasing the power oscillation in the distribution network.


## 5.2.3. Influence of Communication Time Interval on Control Effect

The communication time interval determines the refresh rate of the VES data, which will affect the control results. Figure11 shows the control effect of VES in constant-speed air-conditioning with time interval of 2 minutes and 5 minutes, respectively. The whole process lasts 60 minutes. In order to achieve these results, the response power should be selected in the capacity range and the gap power of constant-speed air-conditioning should be set as 60 KW.Figure 11
(a) and (b) show the control effect of VES in constant-speed air-conditioning with time intervals of 2 minutes and 5 minutes, respectively.
(a) (b)Communication time interval has a significant influence on VES of constant-speed air-conditioning. With the increasing of time interval, the constant-speed air-conditioning control strategy will gradually lose control over VES. The obvious power shortage will occur when the time interval is 5 minutes and the gap power is 60 KW. With the fluctuation range of power over 80%, the maximum power vacancy can reach up to 50%.


## 6. Conclusion

This paper proposed a VSOC prioritized virtual-energy-storage control strategy based on the VES model of thermostatically controlled loads for constant-speed air-conditioner. Relevant examples show that when the load resources of constant-speed air-conditioners effectively participate in the dispatch, the power shortage problem of the power system can be resolved and alleviated; consequently, the power efficiency of the system is significantly improved.The simulation results prove the availability of VSOC prioritized virtual-energy-storage control model, which provides methodological support for demand-side of constant-speed air-conditioning loads to participate in power system operation. At the same time, it provides a control basis for other constant-speed compressor-typed TCL to participate in demand response. This is of great significance for the development of new energy absorption and intelligent power consumption, and it is expected to promote the progress of energy conservation and emission reduction.The response power of VSOC prioritized constant-speed air-conditioner control strategy is limited by VES state and impact power duration. A stable power response can be achieved in a short time, but the control results in the long term still need further optimization. To overcome this shortcoming, it is the focus of future work studying the mechanism of the insufficient or excessive response of constant-speed compressor-typed TCLs in response process and optimizing the control effect of long-term VES.



---

*Source: 3095182-2019-07-01.xml*