An air conditioner comprising: an outdoor unit comprising a compressor, an outdoor heat exchanger, and a main expansion device, wherein a refrigerant is circulated by a refrigerant pipe configured to connect the compressor, the outdoor heat exchanger, and the main expansion device to each other; an indoor unit comprising an indoor heat exchanger; and a connection pipe (171, 172) configured to connect the outdoor unit to the indoor unit, wherein the refrigerant pipe comprises a suction pipe that is configured to guide suction of the refrigerant to the compressor and a discharge pipe that guides discharge of the refrigerant compressed in the compressor, wherein the refrigerant pipe is made of a stainless steel material, characterized in that the air conditioner has refrigeration capacity of 7kW to 11kW, a mixed refrigerant containing 50% or more of an R32 is used as the refrigerant, the refrigerant pipe is made of a ductile stainless steel material having an austenite matrix structure of 99% or more and a delta ferrite matrix structure of 1% or less on the basis of a grain area, wherein the ductile stainless steel material comprises, percent by weight, C: 0.03% or less, Si: more than 0 and less than 1.7%, Mn: 1.5 to 3.5%, Cr: 15.0 to 18.0%, Ni: 7.0 to 9.0%, Cu: 1.0 to 4.0%, Mo: 0.03% or less, P: 0.04% or less, S: 0.04% or less, and N: 0.03% or less, an average grain diameter of the austenite matrix structure is 30 μm to 60 μm, and the suction pipe has an outer diameter of 12.70 mm and an inner diameter of 12.04 mm, and the discharge pipe has an outer diameter of any one of 7.94 mm, 9.52 mm and 12.70 mm, wherein the discharge pipe has an inner diameter of 7.54 mm or less, when the discharge pipe has the outer diameter of 7.94 mm, wherein the discharge pipe has an inner diameter of 9.04 mm or less, when the discharge pipe has the outer diameter of 9.52 mm, and wherein the discharge pipe has an inner diameter of 12.04 mm or less, when the discharge pipe has the outer diameter of 12.70 mm. an outdoor unit comprising a compressor, an outdoor heat exchanger, and a main expansion device, wherein a refrigerant is circulated by a refrigerant pipe configured to connect the compressor, the outdoor heat exchanger, and the main expansion device to each other; an indoor unit comprising an indoor heat exchanger; and a connection pipe (171, 172) configured to connect the outdoor unit to the indoor unit, wherein the refrigerant pipe comprises a suction pipe that is configured to guide suction of the refrigerant to the compressor and a discharge pipe that guides discharge of the refrigerant compressed in the compressor, wherein the refrigerant pipe is made of a stainless steel material, characterized in that the air conditioner has refrigeration capacity of 7kW to 11kW, a mixed refrigerant containing 50% or more of an R32 is used as the refrigerant, the refrigerant pipe is made of a ductile stainless steel material having an austenite matrix structure of 99% or more and a delta ferrite matrix structure of 1% or less on the basis of a grain area, wherein the ductile stainless steel material comprises, percent by weight, C: 0.03% or less, Si: more than 0 and less than 1.7%, Mn: 1.5 to 3.5%, Cr: 15.0 to 18.0%, Ni: 7.0 to 9.0%, Cu: 1.0 to 4.0%, Mo: 0.03% or less, P: 0.04% or less, S: 0.04% or less, and N: 0.03% or less, C: 0.03% or less, Si: more than 0 and less than 1.7%, Mn: 1.5 to 3.5%, Cr: 15.0 to 18.0%, Ni: 7.0 to 9.0%, Cu: 1.0 to 4.0%, Mo: 0.03% or less, P: 0.04% or less, S: 0.04% or less, and N: 0.03% or less, an average grain diameter of the austenite matrix structure is 30 μm to 60 μm, and the suction pipe has an outer diameter of 12.70 mm and an inner diameter of 12.04 mm, and the discharge pipe has an outer diameter of any one of 7.94 mm, 9.52 mm and 12.70 mm, wherein the discharge pipe has an inner diameter of 7.54 mm or less, when the discharge pipe has the outer diameter of 7.94 mm, wherein the discharge pipe has an inner diameter of 9.04 mm or less, when the discharge pipe has the outer diameter of 9.52 mm, and wherein the discharge pipe has an inner diameter of 12.04 mm or less, when the discharge pipe has the outer diameter of 12.70 mm.