TEXT: Arrived on call for no heat and thermostat issue. Found furnace in rollout lockout. Cycled unit after resetting and didn't see any flame issues present. Took reading on everything. Also found coil plugged causing a high limit issue. Recommended customer on replacing unit over coil due to age.