Abstract:
A method and composition for controlling the formation and deposition of scale imparting compounds in an aqueous system is disclosed. A treatment comprising a sulfonated polymer and a polymaleic acid is effective in controlling the formation and deposition of such compounds.

Description:
This is a continuation-in-part of application Ser. No. 08/215,982 filed Mar. 22, 1994 now abandoned. 
    
    
     FIELD OF THE INVENTION 
     The present invention pertains to a composition and method of utilization of same to control the formation and deposition of scale imparting compounds in water systems such as cooling, boiler and gas scrubbing systems. 
     BACKGROUND OF THE INVENTION 
     The problems associated with scale formation have troubled water systems for years. Scale tends to accumulate on internal walls of various water systems, such as boiler and cooling systems, and thereby materially lessens the operational efficiency of the system. 
     Deposits in lines, heat exchange equipment, etc., may originate from several causes. For example, precipitation of calcium carbonate, calcium sulfate and calcium phosphate in the water systems leads to an accumulation of these scale imparting compounds along or around the metal surfaces which contact the flowing water circulating through the system. In this manner, heat transfer functions of the particular system are severely impeded. 
     Typically, in cooling water systems, the formation of calcium sulfate, calcium phosphate and calcium carbonate, among others, has proven deleterious to the overall efficiency of the cooling water system. Recently, due to the popularity of cooling treatments using high levels of orthophosphate to promote passivation of the metal surfaces in contact with the system water, it has become critically important to control calcium phosphate crystallization so that relatively high levels of orthophosphate may be maintained in the system to achieve the desired passivation without resulting in fouling or impeded heat transfer functions which would normally be caused by calcium phosphate deposition. 
     Although steam generating systems are somewhat different from cooling water systems, they share a common problem in regard to deposit formation. 
     As detailed in the Betz Handbook of Industrial Water Conditioning, 8th Edition, 1980, Betz Laboratories, Inc., Trevose, Pa. pages 85-96, the formation of scale and sludge deposits on boiler heating surfaces is a serious problem encountered in steam generation. Although current industrial steam producing systems make use of sophisticated external treatments of the boiler feedwater, e.g., coagulation, filtration, softening of water prior to its feed into the boiler system, these operations are only moderately effective. In all cases, external treatment does not in itself provide adequate treatment since mud, sludge, silts and hardness-imparting ions escape the treatment, and eventually are introduced into the steam generating system. 
     In addition to the problems caused by mud, sludge or silts, the industry has also had to contend with boiler scale. Although external treatment is utilized specifically in an attempt to remove calcium and magnesium from the feedwater, scale formation due to residual hardness, i.e., calcium and magnesium salts, is always experienced. Accordingly, internal treatment, i.e., treatment of the water fed to the system, is necessary to prevent, reduce and/or retard formation of the scale imparting compounds and their resultant deposition. The carbonates of magnesium and calcium are not the only problem compounds as regards to scale, but also waters having high contents of phosphate, sulfate and silicate ions either occurring naturally or added for other purposes cause problems since calcium and magnesium, and any iron or copper present, react with each and deposit as boiler scale. As is obvious, the deposition of scale on the structural parts of a steam generating system causes poorer circulation and lower heat transfer capacity, resulting accordingly in an overall loss in efficiency. 
     Polymaleic acid is known to be a calcium carbonate inhibitor. One of the problems with polymaleic acid is that when it is added to aqueous solutions to prevent calcium carbonate precipitation, it tends to precipitate out with calcium. This reduces the concentration of polymaleic acid (PMA) and also can cause fouling with calcium:PMA deposits. 
    
    
     DETAILED DESCRIPTION OF THE INVENTION 
     In accordance with the invention, it has been surprisingly discovered that a combination of polymaleic acid and a sulfonated acrylic acid copolymer is effective in controlling the formation of mineral deposits in various water systems. The addition of sulfonated acrylic acid copolymer, e.g., acrylic acid/allyl hydroxypropyl sulfonate ether (AA/AHPSE, or Polymer A) prevents PMA from precipitating out with the calcium. Also, the addition of the copolymer improved the calcium carbonate scale controllability of PMA. It is expected that any sulfonated polymer (copolymer, terpolymer, etc.) would provide the same benefit to PMA. Also, other polymaleic acid polymers would also be expected to be improved with sulfonated copolymers. Furthermore, it is anticipated that other copolymers, such as acrylic acid/2-acrylamido-2-methylpropylsulfonic acid or 2-acrylamido-2-methylsulfonic acid and PMA would provide the same benefits to PMA, namely preventing PMA from precipitating out with calcium, and improving calcium carbonate scale controllability of PMA. 
     The following data indicate the precipitation of PMA with soluble calcium in aqueous solutions: 
     
         ______________________________________  Turbidity (NTU) at ppm active treatmentTreatment    0      10     15   20   25   30   35   40______________________________________PMA      0.2    0.6    0.8  1.2  1.5  2.2  2.6  2.9______________________________________ 
    
     The increasing turbidity indicates precipitation of calcium: PMA. The tests were conducted under the following conditions: 500 ppm Ca as CaCO 3 , pH 9.0 and 158° F. The pH was controlled with 0.01M sodium borate. The turbidity was measured according to standard procedures. 
     The improvement in the calcium tolerance of PMA with AA/AHPSE copolymer is demonstrated with a similar test. A 0.01M CaCl 2 .2H 2  O solution was titrated with 0.01M NaOH. The higher the pH where precipitation first occurs indicates a more calcium tolerant treatment. The tests were conducted at 120° F. The pHs were measured with a Corning pH meter equipped with a Thomas Ag/AgCl combination electrode. The pH at which precipitation occurred was the first detectable increase in absorbance detected with a Brinkman PC 600 colorimeter. The initial pH of the solutions with the treatments was pre-adjusted to a pH of 4. The following data were generated: 
     
                       TABLE 1______________________________________                               pH at which pre-Test Treat-  ppm              ppm   cipitation was firstNo.  ment    active  Treatment                         active                               detected______________________________________1    PMA     100     --       --    8.3-8.52    PMA     100     --       --    8.4-8.63    PMA     100     AA/AHPSE 100   no precipitation to                               pH 9.9 where ti-                               tration was                               stopped______________________________________ 
    
     Recirculator tests are used to simulate heat transfer conditions in cooling systems. The recirculator test units have been used to demonstrate the improved inhibition of calcium carbonate deposits with PMA and AA/AHPSE blends. These units have a volume of approximately 11 liters and use a pump to generate water flow past the outside of an admiralty brass metal tube that contains a heater. The units have a temperature control device to maintain a desired sump temperature. The pH is maintained by the controlled addition of CO 2  to the system. Two makeup solutions are fed simultaneously to the units in order to maintain the specified water composition. The system volume is controlled by an overflow port. One makeup solution contains calcium chloride and magnesium sulfate while the other makeup tank contains sodium bicarbonate and sodium silicate. 
     Three recirculator tests were completed with the following physical characteristics: 
     pH 8.5 
     120° F. sump temperature 
     308 watts on the heater (at 13,000 BTU/HR/FT 2  heat flux) 
     2.8 ft/sec water velocity past the heated metal tubes 
     1.4 day retention time for 75% depletion 
     The composition of the test water in these tests was: 600 ppm Ca as CaCO 3 , 150 ppm Mg as CaCO 3 , 210 ppm M alk as CaCO 3 , 425 ppm Cl, 447 ppm SO 4 , 244 ppm Na and 51 ppm SiO 2 . 
     The following table illustrates the treatments and the results of the 7 day tests. All of the tests contain 3 ppm tolyltriazole to control admiralty brass corrosion. 
     
                       TABLE 2______________________________________      Tube          Sump      SumpTreatment  Condition     Turbidity Deposits______________________________________21 ppm active      Complete tube was                    None      DepositsAA/AHPSE   covered with a          found on      deposit                 sump floor21 ppm active      Complete tube was                    Very slight                              NonePMA        covered with a      deposit11 ppm active      Isolated areas of                    None      NonePMA and 10 ppm      very slight depositsactive AA/ on tubeAHPSE______________________________________ 
    
     Admiralty tubes were used purely for exemplary purposes: other types of metal would also be protected from deposition with the blend. Other sulfonated polymers would also be expected to work in place of AA/AHPSE. For example, the following calcium carbonate beaker tests were completed with other sulfonated polymers: 
     
                       TABLE 3______________________________________                      PercentTreatment                  Inhibition______________________________________12 ppm active PMA and 50 ppm active                      50.5copolymer of acrylic acid andCH.sub.2 CH(CO)O(CH.sub.2).sub.3 SO.sub.3 Na12 ppm active PMA and 50 ppm active                      57.7AA/AHPSE12 ppm active PMA and 50 ppm active                      40.7acrylic acid/allyl hydroxypropyl sulfonateether copolymer (Polymer B)12 ppm active PMA and 50 ppm active                      39.0sulfonated styrene/maleic anhydride copolymerControl (no treatment)     0.0______________________________________ 
    
     Note: The proprietary polymers A, B and C tested each have differing mole ratios of acrylic acid to sulfonate ether, and differing molecular weights. 
     The conditions of this calcium carbonate beaker test were as follows: pH 9, 135° F., 600 ppm Ca as CaCO 3 , 505 ppm Malk as CaCO 3 , 18 hour duration. The percent inhibition is calculated as 100 × (ppm Ca of treated--ppm of control solution)/(ppm Ca of stock solution--ppm Ca of control solution). 
     The effectiveness of a sulfonated polymer in providing improved calcium carbonate deposit control of PMA would not have been expected. For example, polyacrylic acid is also a known calcium carbonate inhibitor. The calcium carbonate inhibiting properties of blends of polyacrylate and ANAHPSE (or similar sulfonated copolymers) are not superior to straight polyacrylate at equal total actives. The following calcium carbonate inhibition data demonstrate this: 
     
                       TABLE 4______________________________________                      PercentTreatment                  Inhibition______________________________________2 ppm active polyacrylic acid                      651 ppm active polyacrylic acid and 1 ppm active                      62Polymer C (acrylic acid/allyl hydroxypropylsulfonate ether)Control (no treatment)     0______________________________________ 
    
     The conditions of this calcium carbonate beaker test were: pH 9, 70° C., 1102 ppm Ca as CaCO 3 , 1170 ppm CO 3  as CaCO 3  and 17 hour duration. 
     While this invention has been described with respect to particular embodiments thereof, it is apparent that numerous other forms and modifications of this invention will be obvious to those skilled in the art. The appended claims and this invention generally should be construed to cover all such obvious forms and modifications which are within the true spirit and scope of the present invention.