Document:

Unassociated Document

Exhibit 4.8.5 - Electronic Catalogue (1,3,4,5) - 42CE

  

  

  

	

	 	
Carrier China

Carrier is affiliated to United Technologies. United Technologies ranks 126 in world’s 500 tops (2006), its business extends to architectural industry and aerospace industry around the world.

 

In 1902, Professor Carrier invented first set of scientific air-conditioning system. Since then, carrier’s complete series products and system resolution have become first choice of many world-renowned buildings.

 

In 2007, carrier’s sales revenue reaches 14.6 billion US dollars, leading in the whole industry. Its distributors’ network covers over 170 countries. Carrier is now world’s biggest HVAC manufacturer.

 

Carrier China has 11 companies, 40 sales service offices and 2,500 employees.

 

As the world-class factory, Carrier Yileng has several advanced production lines of units and compressors, covering main units of commercial and residential central air-conditioning systems and air terminal products. The various products can meet diversifying demands from different customers.

Content

	
Model Index Cooling Capacity

	
1

	  	  
	
Features of units

	
2

	  	  
	
Technical Specification

	
4

	  	  
	
Performance Data

	
6

	  	  
	
Noise Test

	
31

	  	  
	
Selection Method

	
32

	  	  
	
Unit Dimension

	
33

	  	  
	
Fan Performance

	
36

	  	  
	
Wiring Diagram

	
37

	  	  
	
Installation& Maintenance Manual

	
38

  

  

  

Model Index

 

 

	
·

	
Digit No. 1, 2

	  
	  	
Product Series

	  
	  	
42 Fan Coil Unit

	  
	  	  	  
	
·

	
Digit No. 3, 4

	  
	  	
CE: Horizontal Ceiling Fan Coil Unit

	  
	  	  	  
	
·

	
Digit No. 5, 6, 7

	  
	  	
Unit Size: ( Air Volume= Unit size x 170 m3/h

	  
	  	
002: 2x170=340 m3/h

	  
	  	
003: 3x170=510 m3/h

	  
	  	  	  
	
·

	
Digit No. 8, 9

	  
	  	
Coil Rows

	
Digit No. 10

	  	
20 : 2 Rows Cooling

	
Static Pressure

	  	
30: 3 Rows Cooing

	
0: 12 Pa Standard

	  	
21: 2 Rows Cooling+1 Row Heating

	
3: 30 Pa Normal

	  	
31: 3 Rows Cooling+1 Row Heating

	
5: 50 High Static

	  	  	  
	  	  	  
	
·

	
Digit No. 11

	  
	  	
Drain Pan

	
Digit No. 12

	  	
A: Standard Drain Pan

	
Unit Connection Direction

	  	
B: Long Drain Pan

	
( Differs by facing the outlet)

	  	
C: Stainless Steel Drain Pan

	
L: Left

	  	
D: Long Stainless Steel Drain Pan

	
R: Right

	  	  	  

Air Volume

340~2380 M3/h

  

01

  

Features of Units

 

Carrier 42 CE Fan Coil Unit is an energy saving product evolved from latest advanced technology. The unit combines advanced technology of low noise fan, efficient air condition manufacturing process and ingenious coil and fin design. Based on previous 42CM fan coil units, 42 CE has been developed to be an ultra-tranquil, high efficiency and easy to install and compact construction fan coil units, which are the replacement of 42 CM.  The fan coil Units has the following features:

Ultra-tranquil

The units use the latest wide wheel width design and low speed forward-curved blades, together with best match with motor, and a good muffler insulation materials. The units achieve the best level of noise through generally reducing it by 2~5dB(A) comparing to similar units.

High Efficiency

The Units adopt the latest lanced sine wave fin coils with folded collar, advanced machinery pipe-expanding process, which make the aluminum foil bond onto copper tubing best. The lanced sine wave fin provides a best channel to assure efficient heat transfer. Extra wide coil wheel provides a uniform heat transfer wind speed environment, which makes better heat transfer, so that with only 2 rows for the fan coil units, the input power cooling capacity of them  surpasses that of similar units with 3 rows at home and abroad.

 

 

Ultra Thin

 

The Unit height is only 220mm, which saves the installation space and meets all kinds of installation requirement

  

2

  

 

	 	
Flexible Selection

	 	 
	  	
To meet specifics and limitations of installation, Carrier offers drain pans of different length for customers’ options:

	  	  
	  	
· 42CE standard drain pan——— reduces the installation space, especially suitable for narrow installation space.

	  	
· 42Ce long drain pan—— extended length to collect

	  	
· Possible sweating from field installed valve accessories 350mm external drain pan available to meet a variety of application.

	  	  
	  	
This series of fan coil unit have been improved in the following aspects, besides it has the above features:

	  	  
	  	
· The closed terminal posts replace the original open structure; and apply the metal soft tube to the motor wiring, which make sure a safer and more reliable performance

	 	 
	  	
· It adopts new type fiberglass as muffler and insulation material, which makes sure not only the smooth and beautiful appearance, but also the excellent performance. Even tested in the worst condensation environment, the good insulation performance of the unit can meet the international standards and requirements.

	 	 
	  	
· The arc metal impeller manufactured by latest process technology ensure a more reliable application in high temperature space.

	 	 
	  	
· The unit drain pan and drain pan insulation board are manufactured by integrated mold process, which not only makes a easier process and beautiful appearance, but also avoids the disadvantage of water leakage of welded drain pan.

	  	  
	  	
Note: Mark between left side and right side of the unit by facing the positive air outlet.

	  	

	

	 	 	 
	  	
Electrical two-way Valve

	
LCD Thermostat

	  	  	  
	

	

	

	 	 	 
	
UV Germicidal Lamp

	
Three-speed temperature controller

	
Remote Controller

 

  

3

  

Technical Specification

2 Rows Single Fan Coil /2+1 Rows Combine Fan Coil

	
Specification

	
002

	
003

	
004

	
005

	
00

	
008

	
Rated Air Flow

	
High

	
370

	
550

	
750

	
900

	
1060

	
1430

	
Medium

	
290

	
440

	
590

	
720

	
820

	
1115

	
Low

	
215

	
325

	
450

	
540

	
610

	
830

	
Cooling Capacity

	
1900

	
2820

	
3740

	
4500

	
5230

	
7300

	
Heating Capacity

	
3280

	
4700

	
6260

	
7500

	
8720

	
11500

	
Input Power

	
12 Pa

	
33

	
46

	
60

	
82

	
94

	
134

	
30 pa

	
40

	
54

	
72

	
92

	
112

	
156

	
50 pa

	
49

	
65

	
84

	
105

	
122

	
184

	
Noise Level

	
12 pa

	
37

	
38

	
40

	
43

	
45

	
46

	
30 pa

	
39

	
41

	
43

	
46

	
47

	
47.5

	
50 pa

	
41

	
43

	
45

	
47

	
49

	
50

	
Water Flow

	
6

	
8

	
11

	
13

	
15

	
21.5

	
Water Pressure Drop

	
10

	
16

	
26

	
30

	
40

	
38

	
Fan

	
Type

	  	  	  	  	  	  
	
Motor

	
Type

	  	  	  	  	  	  
	
Coil

	
Entrance and Return Water

	  	  	
2

	  	  	  
	
Condensation Water

	  	  	
1 MPa

	  	  	  
	
Connection Pipe

	
Entrance and Return Water

	  	  	
3/4

	  	  	  
	  	  	  	
3/4

	  	  	  
	  	
13

	
14 5

	
1 5

	
17 8

	
19

	
2 5

	
Optional Accessories

	
Thermostat(Remote Controller,Four Control, and so on)Two/Three Valve,Return Air Cap

Note: 1. the data in the table is the performance in high speed with relevant static pressure.

	 	
2.

	
Cooling Capacity is under the cooling conditions: Cooling water entering temperature: 7oC, temperature difference between entrance and exit is 5oC, Air temperature DB=27oC, WB=19.5.  Heating Capacity is under the heating conditions: Heating water entering temperature: 60 oC, air temperature DB=21oC.

	 	
3.

	
The heating capacity in the table is based on single row coil performance. The heating capacity of combined row coil can be calculated according to the model selection.

	 	
4.

	
The noise level is measured in front of or under the unit by 1 meter in the anechoic chamber.

  

4

  

 

Technical Specification

3 Rows Single Fan Coil /3+1 Rows Combined Fan Coil

 

	
Specification

	
002

	
003

	
004

	
005

	
00

	
008

	00100	  012	0084
	
Rate Air Flow

	
High

	
340

	
510

	
680

	
850

	
1020

	
1360

	
1700

	
2040

	
2380

	
Medium

	
265

	
405

	
535

	
680

	
790

	
1060

	
1360

	
1595

	
1904

	
Low

	
195

	
305

	
405

	
510

	
585

	
790

	
1020

	
1180

	
1428

	
Cooling Capacity

	
2300

	
3200

	
4250

	
4720

	
5900

	
8150

	
9460

	
11600

	
13000

	
Heating Capacity

	
3905

	
5330

	
7080

	
7870

	
9840

	
13570

	
15490

	
18640

	
21290

	
Input Power

	
12 Pa

	
32

	
46

	
58

	
76

	
91

	
130

	
150

	
180

	
208

	
30 pa

	
41

	
52

	
65

	
87

	
106

	
150

	
172

	
210

	
250

	
50 pa

	
48

	
63

	
82

	
100

	
118

	
174

	
205

	
236

	
290

	
Noise Level

	
12 pa

	
37

	
38

	
40

	
43

	
45

	
46

	
48

	
49

	
51

	
30 pa

	
39

	
41

	
43

	
46

	
47

	
47.5

	
49

	
51

	
52

	
50 pa

	
41

	
43

	
45

	
47

	
49

	
50

	
51

	
51

	
52

	
Water Flow

	
6.6

	
9

	
12.3

	
13.8

	
17

	
23.5

	
27

	
33

	
37

	
Water Pressure Drop

	
14

	
25

	
20

	
24

	
35

	
35

	
40

	
40

	
47

	
Fan

	
Type

	  	  	  	  	  	  	  	  	  
	
Motor

	
Type

	  	  	  	  	  	  	  	  	  
	
Coil

	
Row

	  	  	  	  	
3 2

	
 

	  	  	  
	
Usage pressure

	  	  	  	  	
1 MPa

	
 

	  	  	  
	
Connection Pipe

	
Entrance and return water

	  	  	  	  	
3/4

	
 

 

	  	  	  
	
Condensation water

	  	  	  	  	
3/4

	
 

 

	  	  	  
	  	
1413

	
15

	
14 577

	
19115

	
205

	
17283

	
31 19

	
35 3

	
24155

	
Optional Accessories

	
Thermostat(Remote Controller,Four Control, and so on)Two/Three Valve,Return Air Cap

Note: 1. the data in the table is the performance in high speed with relevant static pressure.

	 	
2.

	
Cooling Capacity is under the cooling conditions: Cooling water entering temperature: 7oC, temperature difference between entrance and exit is 5oC, Air temperature DB=27oC, WB=19.5.  Heating Capacity is under the heating conditions: Heating water entering temperature: 60 oC, air temperature DB=21oC.

	 	
3.

	
The heating capacity in the table is based on single row coil performance. The heating capacity of combined row coil can be calculated according to the model selection.

	 	
4.

	
The noise level is measured in front of or under the unit by 1 meter in the anechoic chamber.

  

5

  

Performance Data

 

	
2 Rows Cooing Capacity

	
(W)

 

	
Model

	
Entering 

Water 

Temp.

oC

	
Water 

Flow

I/min

	
Water 

Pressure

Drop

kpa

	
Entering Air TemperatureoC

	
17.0WB

	
18.0WB

	
19.0WB

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
002

	
5

	
4.5

	
7

	
1564

	
1289

	
11692

	
11299

	
181692

	
1400

	
1821

	
1309

	
1821

	
1400

	
6

	
10

	
1821

	
1441

	
1979

	
1451

	
1979

	
1563

	
2128

	
1461

	
2128

	
1573

	
7.5

	
14

	
1999

	
1532

	
2177

	
1563

	
2177

	
1674

	
2335

	
1583

	
2335

	
1685

	
9

	
19

	
2138

	
1603

	
2326

	
1644

	
2326

	
1745

	
2494

	
1664

	
2494

	
1766

	
6

	
4.5

	
7

	
1425

	
1238

	
1831

	
1248

	
1564

	
1350

	
1692

	
1248

	
1692

	
1360

	
6

	
10

	
1672

	
1370

	
1821

	
1380

	
1821

	
1492

	
1979

	
1400

	
1979

	
1502

	
7.5

	
14

	
1841

	
1451

	
1999

	
1471

	
1999

	
1583

	
2177

	
1502

	
2177

	
1603

	
9

	
19

	
1969

	
1512

	
2138

	
1542

	
2138

	
1654

	
2326

	
1573

	
2326

	
1674

	
7

	
4.5

	
7

	
1296

	
1187

	
1425

	
1187

	
1425

	
1299

	
1564

	
1208

	
1564

	
1299

	
6

	
10

	
1524

	
1299

	
1672

	
1309

	
1672

	
1421

	
1821

	
1329

	
1821

	
1441

	
7.5

	
14

	
1672

	
1370

	
1841

	
1390

	
1841

	
1502

	
1999

	
1421

	
1999

	
1522

	
9

	
19

	
1781

	
1421

	
1969

	
1451

	
1969

	
1563

	
2138

	
1471

	
2138

	
1583

	
8

	
4.5

	
7

	
1178

	
1147

	
1296

	
1147

	
1296

	
1248

	
1425

	
1157

	
1425

	
1248

	
6

	
10

	
1366

	
1228

	
1524

	
1238

	
1524

	
1350

	
1672

	
1258

	
1672

	
1370

	
7.5

	
14

	
1504

	
1279

	
1672

	
1309

	
1672

	
1421

	
1841

	
1329

	
1841

	
1441

	
9

	
19

	
1613

	
1319

	
1781

	
1360

	
1781

	
1461

	
1969

	
1390

	
1969

	
1502

	
9

	
4.5

	
7

	
1039

	
1066

	
1178

	
1106

	
1178

	
1115

	
1296

	
1106

	
1296

	
1218

	
6

	
10

	
1217

	
1147

	
1366

	
1177

	
1366

	
1279

	
1524

	
1187

	
1524

	
1299

	
7.5

	
14

	
1336

	
1187

	
1504

	
1228

	
1504

	
1319

	
1672

	
1248

	
1672

	
1329

	
9

	
19

	
1425

	
1218

	
1613

	
1258

	
1613

	
1360

	
1781

	
1299

	
1781

	
1400

	
10

	
4.5

	
7

	
910

	
862

	
1039

	
973

	
1039

	
987

	
1178

	
1076

	
1178

	
1167

	
6

	
10

	
1059

	
1003

	
1217

	
1015

	
1217

	
1208

	
1366

	
1137

	
1366

	
1228

	
7.5

	
14

	
1178

	
1096

	
1336

	
1126

	
1336

	
1238

	
1504

	
1167

	
1504

	
1279

	
9

	
19

	
1257

	
1106

	
1425

	
1167

	
1425

	
1258

	
1613

	
1208

	
1613

	
1299

	
003

	
5

	
6

	
9

	
2406

	
1996

	
2608

	
2007

	
2608

	
2164

	
2810

	
2017

	
2810

	
2174

	
8

	
16

	
2699

	
2153

	
2941

	
2174

	
2941

	
2331

	
3164

	
2205

	
3164

	
2362

	
10

	
25

	
2911

	
2247

	
3164

	
2289

	
3164

	
2446

	
3396

	
2310

	
3396

	
2467

	
12

	
34

	
3073

	
2320

	
3315

	
2362

	
3315

	
3502

	
3578

	
2394

	
3578

	
2550

	
6

	
6

	
9

	
2214

	
1913

	
2406

	
1892

	
2406

	
2080

	
2608

	
1944

	
2608

	
2090

	
8

	
16

	
2476

	
2038

	
2699

	
2070

	
2699

	
2226

	
2941

	
2090

	
2941

	
2247

	
10

	
25

	
2668

	
2132

	
2911

	
2164

	
2911

	
2320

	
3164

	
2205

	
3164

	
2341

	
12

	
34

	
2810

	
2185

	
3073

	
2226

	
3073

	
2394

	
3315

	
2268

	
3315

	
2435

	
7

	
6

	
9

	
2011

	
1819

	
2214

	
1850

	
2214

	
1996

	
2305

	
1861

	
2406

	
2007

	
8

	
16

	
2254

	
1934

	
2476

	
1955

	
2476

	
2111

	
2699

	
1996

	
2699

	
2143

	
10

	
25

	
2436

	
1996

	
2668

	
2038

	
2668

	
2205

	
2608

	
2080

	
2911

	
2237

	
12

	
34

	
2547

	
2038

	
2810

	
2090

	
2810

	
2247

	
3073

	
2143

	
3073

	
2299

	
8

	
6

	
9

	
1809

	
1746

	
2011

	
1766

	
2011

	
1923

	
2214

	
1787

	
2214

	
1934

	
8

	
16

	
2032

	
1819

	
2254

	
1861

	
2254

	
2007

	
2476

	
1881

	
2476

	
2038

	
10

	
25

	
2183

	
1871

	
2436

	
1923

	
2436

	
2070

	
2668

	
1955

	
2668

	
2101

	
12

	
34

	
2305

	
1913

	
2547

	
1955

	
2547

	
2111

	
2810

	
2007

	
2810

	
2164

	
9

	
6

	
9

	
1607

	
1662

	
1809

	
1693

	
1809

	
1850

	
2011

	
1704

	
2011

	
1861

	
8

	
16

	
1809

	
1714

	
2032

	
1746

	
2032

	
1892

	
2254

	
1787

	
2254

	
1934

	
10

	
25

	
1941

	
1735

	
2183

	
1798

	
2183

	
1944

	
2436

	
1840

	
2436

	
1986

	
12

	
34

	
2042

	
1766

	
2305

	
1819

	
2305

	
1965

	
2547

	
1881

	
2547

	
2017

	
10

	
6

	
9

	
1415

	
1463

	
1607

	
1620

	
1607

	
1662

	
1809

	
1631

	
1809

	
1787

	
8

	
16

	
1577

	
1610

	
1809

	
1641

	
1809

	
1787

	
2032

	
1672

	
2032

	
1819

	
10

	
25

	
1708

	
1610

	
1941

	
1662

	
1941

	
1808

	
2183

	
1714

	
2183

	
1861

	
12

	
34

	
1789

	
1620

	
2042

	
1672

	
2042

	
1819

	
2305

	
1746

	
2305

	
1881

 

Note:1. DB-Dry Bulb oC,WB-Wet Bulb oC。

	 	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

6

  

 

Performance Data

	
2 Rows Cooing Capacity

	
(W)

 

	
Model

	
Entering 

Water  

Temp.

oC

	
Water 

Flow

I/min

	
Water 

Pressure 

Drop

kpa

	
Entering Air TemperatureoC

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
002

	
5

	
4.5

	
7

	
1890

	
1360

	
1949

	
1309

	
1949

	
1400

	
2088

	
1319

	
2088

	
1400

	
2207

	
1400

	
6

	
10

	
2197

	
1522

	
2276

	
1471

	
2276

	
1583

	
2424

	
1492

	
2424

	
1593

	
2583

	
1593

	
7.5

	
14

	
2424

	
1644

	
2514

	
1593

	
2514

	
1695

	
2672

	
1603

	
2672

	
1715

	
2840

	
1725

	
9

	
19

	
2613

	
1725

	
2682

	
1674

	
2682

	
2811

	
2850

	
1695

	
2850

	
1806

	
3038

	
1816

	
6

	
4.5

	
7

	
1761

	
1309

	
1821

	
1258

	
1821

	
1360

	
1949

	
1258

	
1949

	
1360

	
2088

	
1360

	
6

	
10

	
2048

	
1461

	
2128

	
1421

	
2128

	
1512

	
2276

	
1431

	
2276

	
1522

	
2424

	
1532

	
7.5

	
14

	
2256

	
1563

	
2335

	
1522

	
2335

	
1624

	
2514

	
1532

	
2514

	
1644

	
2672

	
1644

	
9

	
19

	
2405

	
1644

	
2494

	
1593

	
2494

	
1695

	
2682

	
1613

	
2682

	
1715

	
2850

	
1735

	
7

	
4.5

	
7

	
1623

	
1258

	
1692

	
1218

	
1692

	
1309

	
1821

	
1218

	
1821

	
1309

	
1949

	
1309

	
6

	
10

	
1900

	
1390

	
1979

	
1350

	
1979

	
1451

	
2128

	
1360

	
2128

	
1451

	
2276

	
1461

	
7.5

	
14

	
2098

	
1492

	
2177

	
1441

	
2177

	
1542

	
2335

	
1461

	
2335

	
1563

	
2514

	
1573

	
9

	
19

	
2236

	
1542

	
2326

	
1512

	
2326

	
1603

	
2494

	
1532

	
2494

	
1624

	
2682

	
1654

	
8

	
4.5

	
7

	
1494

	
1208

	
1564

	
1167

	
1564

	
1258

	
1692

	
1167

	
1692

	
1258

	
1821

	
1258

	
6

	
10

	
1752

	
1319

	
1821

	
1289

	
1821

	
1380

	
1979

	
1299

	
1979

	
1390

	
2128

	
1400

	
7.5

	
14

	
1920

	
1400

	
1999

	
1360

	
1999

	
1461

	
2177

	
1380

	
2177

	
1471

	
2335

	
1502

	
9

	
19

	
2048

	
1451

	
2138

	
1421

	
2138

	
1522

	
2326

	
1441

	
2326

	
1542

	
2494

	
1573

	
9

	
4.5

	
7

	
1366

	
1167

	
1425

	
1116

	
1425

	
1218

	
1564

	
1116

	
1564

	
1218

	
1692

	
1218

	
6

	
10

	
1603

	
1248

	
1672

	
1218

	
1672

	
1309

	
1821

	
1228

	
1821

	
1319

	
1979

	
1329

	
7.5

	
14

	
1761

	
1319

	
1841

	
1289

	
1841

	
1380

	
1999

	
1309

	
1999

	
1400

	
2177

	
1421

	
9

	
19

	
1880

	
1370

	
1969

	
1329

	
1969

	
1431

	
2138

	
1360

	
2138

	
1451

	
2326

	
1471

	
10

	
4.5

	
7

	
1227

	
1116

	
1296

	
1076

	
1296

	
1167

	
1425

	
1076

	
1425

	
1167

	
1564

	
1167

	
6

	
10

	
1435

	
1187

	
1524

	
1147

	
1524

	
1248

	
1672

	
1167

	
1672

	
1258

	
1821

	
1279

	
7.5

	
14

	
1583

	
1238

	
1672

	
1208

	
1672

	
1299

	
1841

	
1228

	
1841

	
1319

	
1999

	
1350

	
9

	
19

	
1692

	
1279

	
1781

	
1238

	
1781

	
1329

	
1969

	
1279

	
1969

	
1370

	
2138

	
1390

	
003

	
5

	
6

	
9

	
2911

	
2101

	
3012

	
2028

	
3012

	
2174

	
3204

	
2038

	
3204

	
2174

	
3416

	
2174

	
8

	
16

	
3265

	
2289

	
3386

	
2216

	
3386

	
2373

	
3608

	
2226

	
3608

	
2383

	
3831

	
2383

	
10

	
25

	
3528

	
2404

	
3649

	
2331

	
3649

	
2488

	
3891

	
2362

	
3891

	
2509

	
4124

	
2519

	
12

	
34

	
3699

	
2488

	
3831

	
2414

	
3831

	
2582

	
4094

	
2446

	
4094

	
2603

	
4336

	
2613

	
6

	
6

	
9

	
2719

	
2017

	
2810

	
1944

	
2810

	
2090

	
3012

	
1955

	
3012

	
2101

	
3204

	
2101

	
8

	
16

	
3042

	
2174

	
3164

	
2111

	
3164

	
2258

	
3386

	
2132

	
3386

	
2268

	
3608

	
2289

	
10

	
25

	
3275

	
2289

	
3396

	
2226

	
3396

	
2373

	
3649

	
2247

	
3649

	
2394

	
3891

	
2404

	
12

	
34

	
3447

	
2362

	
3578

	
2299

	
3578

	
2456

	
3831

	
2331

	
3831

	
2477

	
4094

	
2509

	
7

	
6

	
9

	
2517

	
1944

	
2608

	
1871

	
2608

	
2017

	
2810

	
1881

	
2810

	
2017

	
3012

	
2028

	
8

	
16

	
2820

	
2080

	
2941

	
2017

	
2941

	
2164

	
3164

	
2028

	
3164

	
2174

	
3386

	
2185

	
10

	
25

	
3032

	
2164

	
3164

	
2101

	
3164

	
2258

	
3396

	
2143

	
3396

	
2289

	
3649

	
2299

	
12

	
34

	
3194

	
2237

	
3315

	
2174

	
3315

	
2320

	
3578

	
2216

	
3578

	
2362

	
3831

	
2383

	
8

	
6

	
9

	
2315

	
1861

	
2406

	
1798

	
2406

	
1934

	
2608

	
1798

	
2608

	
1944

	
2810

	
1944

	
8

	
16

	
2598

	
1965

	
2699

	
1913

	
2699

	
2059

	
2941

	
1934

	
2941

	
2080

	
3164

	
2090

	
10

	
25

	
2800

	
2059

	
2911

	
1996

	
2911

	
2143

	
3164

	
2028

	
3164

	
2164

	
3396

	
2185

	
12

	
34

	
2941

	
2101

	
3073

	
2059

	
3073

	
2205

	
3315

	
2090

	
3315

	
2237

	
3578

	
2258

	
9

	
6

	
9

	
2102

	
1787

	
2214

	
1714

	
2214

	
1861

	
2406

	
1725

	
2406

	
1871

	
2608

	
1871

	
8

	
16

	
2375

	
1871

	
2476

	
1808

	
2476

	
1955

	
2699

	
1840

	
2699

	
1986

	
2941

	
1996

	
10

	
25

	
2547

	
1934

	
2668

	
1881

	
2668

	
2017

	
2911

	
1913

	
2911

	
2059

	
3164

	
2080

	
12

	
34

	
2678

	
1965

	
2810

	
1923

	
2810

	
2070

	
3073

	
1965

	
3073

	
2101

	
3315

	
2143

	
10

	
6

	
9

	
1900

	
1714

	
2011

	
1641

	
2011

	
1787

	
2214

	
1651

	
2214

	
1798

	
2406

	
1798

	
8

	
16

	
2143

	
1777

	
2254

	
1714

	
2254

	
1861

	
2476

	
1735

	
2476

	
1881

	
2699

	
1892

	
10

	
25

	
2305

	
1808

	
2436

	
1766

	
2436

	
1892

	
2668

	
1798

	
2668

	
1934

	
2911

	
1965

	
12

	
34

	
2426

	
1840

	
2547

	
1798

	
2547

	
1934

	
2810

	
1850

	
2810

	
2080

	
3073

	
2017

 

Note:1. DB-Dry Bulb oC,WB-Wet Bulb oC。

	 	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

7

  

Performance Data

	
2 Rows Cooing Capacity

	
(W)

 

	
Model

	
Entering Water 

Temp.

oC

	
Water 

Flow

I/min

	
Water 

Pressure 

Drop

kpa

	
Entering Air TemperatureoC

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
002

	
5

	
4.5

	
7

	
1890

	
1360

	
1949

	
1309

	
1949

	
1400

	
2088

	
1319

	
2088

	
1400

	
2207

	
1400

	
6

	
10

	
2197

	
1522

	
2276

	
1471

	
2276

	
1583

	
2424

	
1492

	
2424

	
1593

	
2583

	
1593

	
7.5

	
14

	
2424

	
1644

	
2514

	
1593

	
2514

	
1695

	
2672

	
1603

	
2672

	
1715

	
2840

	
1725

	
9

	
19

	
2613

	
1725

	
2682

	
1674

	
2682

	
2811

	
2850

	
1695

	
2850

	
1806

	
3038

	
1816

	
6

	
4.5

	
7

	
1761

	
1309

	
1821

	
1258

	
1821

	
1360

	
1949

	
1258

	
1949

	
1360

	
2088

	
1360

	
6

	
10

	
2048

	
1461

	
2128

	
1421

	
2128

	
1512

	
2276

	
1431

	
2276

	
1522

	
2424

	
1532

	
7.5

	
14

	
2256

	
1563

	
2335

	
1522

	
2335

	
1624

	
2514

	
1532

	
2514

	
1644

	
2672

	
1644

	
9

	
19

	
2405

	
1644

	
2494

	
1593

	
2494

	
1695

	
2682

	
1613

	
2682

	
1715

	
2850

	
1735

	
7

	
4.5

	
7

	
1623

	
1258

	
1692

	
1218

	
1692

	
1309

	
1821

	
1218

	
1821

	
1309

	
1949

	
1309

	
6

	
10

	
1900

	
1390

	
1979

	
1350

	
1979

	
1451

	
2128

	
1360

	
2128

	
1451

	
2276

	
1461

	
7.5

	
14

	
2098

	
1492

	
2177

	
1441

	
2177

	
1542

	
2335

	
1461

	
2335

	
1563

	
2514

	
1573

	
9

	
19

	
2236

	
1542

	
2326

	
1512

	
2326

	
1603

	
2494

	
1532

	
2494

	
1624

	
2682

	
1654

	
8

	
4.5

	
7

	
1494

	
1208

	
1564

	
1167

	
1564

	
1258

	
1692

	
1167

	
1692

	
1258

	
1821

	
1258

	
6

	
10

	
1752

	
1319

	
1821

	
1289

	
1821

	
1380

	
1979

	
1299

	
1979

	
1390

	
2128

	
1400

	
7.5

	
14

	
1920

	
1400

	
1999

	
1360

	
1999

	
1461

	
2177

	
1380

	
2177

	
1471

	
2335

	
1502

	
9

	
19

	
2048

	
1451

	
2138

	
1421

	
2138

	
1522

	
2326

	
1441

	
2326

	
1542

	
2494

	
1573

	
9

	
4.5

	
7

	
1366

	
1167

	
1425

	
1116

	
1425

	
1218

	
1564

	
1116

	
1564

	
1218

	
1692

	
1218

	
6

	
10

	
1603

	
1248

	
1672

	
1218

	
1672

	
1309

	
1821

	
1228

	
1821

	
1319

	
1979

	
1329

	
7.5

	
14

	
1761

	
1319

	
1841

	
1289

	
1841

	
1380

	
1999

	
1309

	
1999

	
1400

	
2177

	
1421

	
9

	
19

	
1880

	
1370

	
1969

	
1329

	
1969

	
1431

	
2138

	
1360

	
2138

	
1451

	
2326

	
1471

	
10

	
4.5

	
7

	
1227

	
1116

	
1296

	
1076

	
1296

	
1167

	
1425

	
1076

	
1425

	
1167

	
1564

	
1167

	
6

	
10

	
1435

	
1187

	
1524

	
1147

	
1524

	
1248

	
1672

	
1167

	
1672

	
1258

	
1821

	
1279

	
7.5

	
14

	
1583

	
1238

	
1672

	
1208

	
1672

	
1299

	
1841

	
1228

	
1841

	
1319

	
1999

	
1350

	
9

	
19

	
1692

	
1279

	
1781

	
1238

	
1781

	
1329

	
1969

	
1279

	
1969

	
1370

	
2138

	
1390

	
003

	
5

	
6

	
9

	
2911

	
2101

	
3012

	
2028

	
3012

	
2174

	
3204

	
2038

	
3204

	
2174

	
3416

	
2174

	
8

	
16

	
3265

	
2289

	
3386

	
2216

	
3386

	
2373

	
3608

	
2226

	
3608

	
2383

	
3831

	
2383

	
10

	
25

	
3528

	
2404

	
3649

	
2331

	
3649

	
2488

	
3891

	
2362

	
3891

	
2509

	
4124

	
2519

	
12

	
34

	
3699

	
2488

	
3831

	
2414

	
3831

	
2582

	
4094

	
2446

	
4094

	
2603

	
4336

	
2613

	
6

	
6

	
9

	
2719

	
2017

	
2810

	
1944

	
2810

	
2090

	
3012

	
1955

	
3012

	
2101

	
3204

	
2101

	
8

	
16

	
3042

	
2174

	
3164

	
2111

	
3164

	
2258

	
3386

	
2132

	
3386

	
2268

	
3608

	
2289

	
10

	
25

	
3275

	
2289

	
3396

	
2226

	
3396

	
2373

	
3649

	
2247

	
3649

	
2394

	
3891

	
2404

	
12

	
34

	
3447

	
2362

	
3578

	
2299

	
3578

	
2456

	
3831

	
2331

	
3831

	
2477

	
4094

	
2509

	
7

	
6

	
9

	
2517

	
1944

	
2608

	
1871

	
2608

	
2017

	
2810

	
1881

	
2810

	
2017

	
3012

	
2028

	
8

	
16

	
2820

	
2080

	
2941

	
2017

	
2941

	
2164

	
3164

	
2028

	
3164

	
2174

	
3386

	
2185

	
10

	
25

	
3032

	
2164

	
3164

	
2101

	
3164

	
2258

	
3396

	
2143

	
3396

	
2289

	
3649

	
2299

	
12

	
34

	
3194

	
2237

	
3315

	
2174

	
3315

	
2320

	
3578

	
2216

	
3578

	
2362

	
3831

	
2383

	
8

	
6

	
9

	
2315

	
1861

	
2406

	
1798

	
2406

	
1934

	
2608

	
1798

	
2608

	
1944

	
2810

	
1944

	
8

	
16

	
2598

	
1965

	
2699

	
1913

	
2699

	
2059

	
2941

	
1934

	
2941

	
2080

	
3164

	
2090

	
10

	
25

	
2800

	
2059

	
2911

	
1996

	
2911

	
2143

	
3164

	
2028

	
3164

	
2164

	
3396

	
2185

	
12

	
34

	
2941

	
2101

	
3073

	
2059

	
3073

	
2205

	
3315

	
2090

	
3315

	
2237

	
3578

	
2258

	
9

	
6

	
9

	
2102

	
1787

	
2214

	
1714

	
2214

	
1861

	
2406

	
1725

	
2406

	
1871

	
2608

	
1871

	
8

	
16

	
2375

	
1871

	
2476

	
1808

	
2476

	
1955

	
2699

	
1840

	
2699

	
1986

	
2941

	
1996

	
10

	
25

	
2547

	
1934

	
2668

	
1881

	
2668

	
2017

	
2911

	
1913

	
2911

	
2059

	
3164

	
2080

	
12

	
34

	
2678

	
1965

	
2810

	
1923

	
2810

	
2070

	
3073

	
1965

	
3073

	
2101

	
3315

	
2143

	
10

	
6

	
9

	
1900

	
1714

	
2011

	
1641

	
2011

	
1787

	
2214

	
1651

	
2214

	
1798

	
2406

	
1798

	
8

	
16

	
2143

	
1777

	
2254

	
1714

	
2254

	
1861

	
2476

	
1735

	
2476

	
1881

	
2699

	
1892

	
10

	
25

	
2305

	
1808

	
2436

	
1766

	
2436

	
1892

	
2668

	
1798

	
2668

	
1934

	
2911

	
1965

	
12

	
34

	
2426

	
1840

	
2547

	
1798

	
2547

	
1934

	
2810

	
1850

	
2810

	
2080

	
3073

	
2017

 

Note:1. DB-Dry Bulb oC,WB-Wet Bulb oC。

	 	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

8

  

Performance Data

   

	
2 Rows Cooling Capacity

	
(W)

	
Model

	
Entering

	
Water

	
Water

	
Entering Air Temperature°C

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
°C

	  	
Kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
004

	
5

	
8

	
19

	
3850

	
2710

	
3980

	
2620

	
3980

	
2800

	
4240

	
2630

	
4240

	
2810

	
4510

	
2800

	
11

	
26

	
4450

	
3010

	
4610

	
2920

	
4610

	
3130

	
4910

	
2940

	
4910

	
3140

	
5220

	
3150

	
14

	
31

	
4860

	
3220

	
5040

	
3130

	
5040

	
3340

	
5370

	
3150

	
5370

	
3360

	
5710

	
3370

	
17

	
37

	
5160

	
3360

	
5350

	
3270

	
5350

	
3490

	
5700

	
3300

	
5700

	
3510

	
6060

	
3540

	
6

	
8

	
19

	
3580

	
2610

	
3720

	
2510

	
3720

	
2710

	
3980

	
2502

	
3980

	
2710

	
4240

	
2710

	
11

	
26

	
4140

	
2880

	
4300

	
2790

	
4300

	
2990

	
4610

	
2810

	
4610

	
3010

	
4910

	
3020

	
14

	
31

	
4540

	
3060

	
4700

	
2980

	
4700

	
3170

	
5040

	
3000

	
5040

	
3210

	
5370

	
3220

	
17

	
37

	
4810

	
3190

	
4990

	
3100

	
4990

	
3310

	
5350

	
3140

	
5350

	
3350

	
5700

	
3370

	
7

	
8

	
19

	
3310

	
2510

	
3450

	
2420

	
3450

	
2610

	
3720

	
2430

	
3720

	
2620

	
3980

	
2620

	
11

	
26

	
3840

	
2740

	
3990

	
2660

	
3990

	
2860

	
4300

	
2690

	
4300

	
2870

	
4610

	
2900

	
14

	
31

	
4200

	
2910

	
4360

	
2830

	
4360

	
3020

	
4700

	
2860

	
4700

	
3060

	
5040

	
3080

	
17

	
37

	
4450

	
3010

	
4630

	
2940

	
4630

	
3140

	
4990

	
2980

	
4990

	
3170

	
5350

	
3210

	
8

	
8

	
19

	
3060

	
2420

	
3190

	
2330

	
3190

	
2510

	
3450

	
2340

	
3450

	
2520

	
3720

	
2520

	
11

	
26

	
3540

	
2620

	
3690

	
2540

	
3690

	
2720

	
3990

	
2560

	
3990

	
2741

	
4300

	
2770

	
14

	
31

	
3860

	
2740

	
4020

	
2670

	
4020

	
2870

	
4360

	
2710

	
4360

	
2910

	
4700

	
2930

	
17

	
37

	
4090

	
2840

	
4280

	
2770

	
4280

	
2970

	
4630

	
2810

	
4630

	
3010

	
4990

	
3050

	
9

	
8

	
19

	
2790

	
2330

	
2920

	
2230

	
2920

	
2430

	
3190

	
2240

	
3190

	
2430

	
3450

	
2430

	
11

	
26

	
3220

	
2480

	
3370

	
2410

	
3370

	
2590

	
3690

	
2430

	
3690

	
2620

	
3990

	
2640

	
14

	
31

	
3520

	
2590

	
3690

	
2510

	
3690

	
2710

	
4020

	
2560

	
4020

	
2760

	
4360

	
2780

	
17

	
37

	
3740

	
2660

	
3920

	
2611

	
3920

	
2790

	
4280

	
2650

	
4280

	
2840

	
4630

	
2880

	
10

	
8

	
19

	
2520

	
2240

	
2650

	
2150

	
2650

	
2340

	
2920

	
2160

	
2920

	
2340

	
3190

	
2350

	
11

	
26

	
2920

	
2350

	
3070

	
2270

	
3070

	
2470

	
3370

	
2310

	
3370

	
2490

	
3690

	
2510

	
14

	
31

	
3190

	
2430

	
3360

	
2360

	
3360

	
2550

	
3690

	
2420

	
3690

	
2590

	
4020

	
2640

	
17

	
37

	
3380

	
2490

	
3560

	
2430

	
3560

	
2620

	
3920

	
2490

	
3920

	
2670

	
4280

	
2720

	
005

	
5

	
11

	
22

	
4685

	
3542

	
4849

	
3429

	
4849

	
3666

	
5172

	
3445

	
5172

	
3682

	
5495

	
3677

	
13

	
30

	
5219

	
3824

	
5403

	
3711

	
5403

	
3969

	
5760

	
3732

	
5760

	
3985

	
6122

	
3995

	
17

	
40

	
5595

	
4021

	
5794

	
3908

	
5794

	
4171

	
6181

	
3940

	
6181

	
4192

	
6573

	
4214

	
20

	
55

	
5882

	
4165

	
6086

	
4046

	
6086

	
4315

	
6492

	
4084

	
6492

	
4341

	
6899

	
4373

	
6

	
11

	
22

	
4363

	
3407

	
4527

	
3289

	
4527

	
3536

	
4849

	
3296

	
4849

	
3542

	
5172

	
3542

	
13

	
30

	
4857

	
3657

	
5041

	
3539

	
5041

	
3797

	
5403

	
3571

	
5403

	
3824

	
5760

	
3834

	
17

	
40

	
5218

	
3827

	
5407

	
3720

	
5407

	
3967

	
5794

	
3752

	
5794

	
4010

	
6181

	
4026

	
20

	
55

	
5476

	
3955

	
5684

	
3843

	
5684

	
4106

	
6086

	
3891

	
6086

	
4143

	
6492

	
4175

	
7

	
11

	
22

	
4040

	
3273

	
4199

	
3155

	
4199

	
3402

	
4527

	
3176

	
4527

	
3413

	
4849

	
3418

	
13

	
30

	
4500

	
3480

	
4679

	
3378

	
4679

	
3630

	
5041

	
3410

	
5041

	
3647

	
5403

	
3673

	
17

	
40

	
4831

	
3634

	
5020

	
3538

	
5020

	
3779

	
5407

	
3570

	
5407

	
3822

	
5794

	
3849

	
20

	
55

	
5069

	
3735

	
5272

	
3644

	
5272

	
3896

	
5684

	
3692

	
5684

	
3934

	
6086

	
3977

	
8

	
11

	
22

	
3718

	
3144

	
3881

	
3031

	
3881

	
3267

	
4199

	
3047

	
4199

	
3284

	
4527

	
3284

	
13

	
30

	
4143

	
3319

	
4321

	
3217

	
4321

	
3459

	
4679

	
3249

	
4679

	
3481

	
5041

	
3512

	
17

	
40

	
4440

	
3436

	
4628

	
3344

	
4628

	
3586

	
5020

	
3393

	
5020

	
3634

	
5407

	
3666

	
20

	
55

	
4662

	
3526

	
4871

	
3435

	
4871

	
3737

	
5272

	
3489

	
5272

	
3730

	
5684

	
3778

	
9

	
11

	
22

	
3395

	
3020

	
3554

	
2896

	
3554

	
3149

	
3881

	
2918

	
3881

	
3154

	
4199

	
3160

	
13

	
30

	
3781

	
3147

	
3959

	
3056

	
3959

	
3292

	
4321

	
3082

	
4321

	
3324

	
4679

	
3357

	
17

	
40

	
4053

	
3242

	
4246

	
3185

	
4246

	
3398

	
4628

	
3205

	
4628

	
3446

	
5020

	
3484

	
20

	
55

	
4261

	
3306

	
4464

	
3237

	
4464

	
3473

	
4871

	
3290

	
4871

	
3526

	
5272

	
3574

	
10

	
11

	
22

	
3067

	
2896

	
3231

	
2778

	
3231

	
3025

	
3554

	
2805

	
3554

	
3036

	
3881

	
3052

	
13

	
30

	
3423

	
2980

	
3602

	
2889

	
3602

	
3131

	
3959

	
2932

	
3959

	
3163

	
4321

	
3190

	
17

	
40

	
3671

	
3044

	
3864

	
2958

	
3864

	
3200

	
4246

	
3028

	
4246

	
3253

	
4628

	
3301

	
20

	
55

	
3849

	
3097

	
4057

	
3022

	
4057

	
3252

	
4464

	
3091

	
4464

	
3317

	
4871

	
3381

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

9

  

 

Performance Data

  

	
2 Rows Cooling Capacity

	
(W)

	
Model

	
Entering

	
Water Flow

	
Water

	
Entering Air Temperature°C

	 	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
°C

	  	
Kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
006

	
5

	
12

	
28

	
4630

	
3947

	
5010

	
3968

	
5010

	
4278

	
5400

	
4000

	
5400

	
4289

	
15

	
40

	
5020

	
4139

	
5440

	
4193

	
5440

	
4503

	
5860

	
4225

	
5860

	
4524

	
18

	
52

	
5310

	
4278

	
5760

	
4342

	
5760

	
4652

	
6200

	
4396

	
6200

	
4706

	
21

	
65

	
5540

	
4396

	
6000

	
4449

	
6000

	
4781

	
6470

	
4513

	
6470

	
4824

	
6

	
12

	
28

	
4240

	
3765

	
4630

	
3807

	
4630

	
4107

	
5010

	
3829

	
5010

	
4128

	
15

	
40

	
4610

	
3936

	
5020

	
3989

	
5020

	
4289

	
5440

	
4032

	
5440

	
4332

	
18

	
52

	
4870

	
4053

	
5310

	
4118

	
5310

	
4428

	
5760

	
4182

	
5760

	
4481

	
21

	
65

	
5080

	
4139

	
5540

	
4214

	
5540

	
4524

	
6000

	
4278

	
6000

	
4588

	
7

	
12

	
28

	
3860

	
3604

	
4240

	
3647

	
4240

	
3947

	
4630

	
3668

	
4630

	
3968

	
15

	
40

	
4190

	
3733

	
4610

	
3786

	
4610

	
4096

	
5020

	
3840

	
5020

	
4128

	
18

	
52

	
4430

	
3818

	
4870

	
3893

	
4870

	
4193

	
5310

	
3957

	
5310

	
4257

	
21

	
65

	
4620

	
3882

	
5080

	
3968

	
5080

	
4267

	
5540

	
4043

	
5540

	
4342

	
8

	
12

	
28

	
3480

	
3444

	
3860

	
3487

	
3860

	
3786

	
4240

	
3508

	
4240

	
3807

	
15

	
40

	
3770

	
3519

	
4190

	
3583

	
4190

	
3882

	
4610

	
3647

	
4610

	
3936

	
18

	
52

	
3990

	
3583

	
4430

	
3668

	
4430

	
3957

	
4870

	
3743

	
4870

	
4032

	
21

	
65

	
4150

	
3615

	
4620

	
3722

	
4620

	
4021

	
5080

	
3807

	
5080

	
4096

	
9

	
12

	
28

	
3080

	
3283

	
3480

	
3326

	
3480

	
3636

	
3860

	
3358

	
3860

	
3658

	
15

	
40

	
3350

	
3326

	
3770

	
3380

	
3770

	
3679

	
4190

	
3444

	
4190

	
3733

	
18

	
52

	
3550

	
3348

	
3990

	
3433

	
3990

	
3722

	
4430

	
3519

	
4430

	
3797

	
21

	
65

	
3700

	
3358

	
4150

	
3465

	
4150

	
3754

	
4620

	
3572

	
4620

	
3840

	
10

	
12

	
28

	
2700

	
2888

	
3080

	
3176

	
3080

	
3294

	
3480

	
3209

	
3480

	
3508

	
15

	
40

	
2930

	
3112

	
3350

	
3187

	
3350

	
3465

	
3770

	
3262

	
3770

	
3529

	
18

	
52

	
3110

	
3166

	
3550

	
3198

	
3550

	
3487

	
3990

	
3294

	
3990

	
3572

	
21

	
65

	
3230

	
3187

	
3700

	
3219

	
3700

	
3487

	
4150

	
3326

	
4150

	
3594

	
008

	
5

	
15

	
28

	
6264

	
5467

	
6787

	
5519

	
6787

	
5948

	
7319

	
5551

	
7319

	
5969

	
21.5

	
38

	
7005

	
5864

	
7585

	
5937

	
7585

	
6366

	
8165

	
5990

	
8165

	
6418

	
27

	
50

	
7481

	
6094

	
8098

	
6188

	
8098

	
6627

	
8735

	
6272

	
8735

	
6700

	
32

	
65

	
7813

	
6230

	
8469

	
6355

	
8469

	
6794

	
9115

	
6439

	
9115

	
6878

	
6

	
15

	
28

	
5751

	
5237

	
6264

	
5289

	
6264

	
5718

	
6787

	
5321

	
6787

	
5739

	
21.5

	
38

	
6426

	
5540

	
7005

	
5624

	
7005

	
6063

	
7585

	
5697

	
7585

	
6125

	
27

	
50

	
6853

	
5739

	
7481

	
5843

	
7481

	
6272

	
8098

	
5948

	
8098

	
6355

	
32

	
65

	
7167

	
5864

	
7813

	
5990

	
7813

	
6418

	
8469

	
6094

	
8469

	
6512

	
7

	
15

	
28

	
5228

	
5007

	
5751

	
5059

	
5751

	
5488

	
6264

	
5101

	
6264

	
5509

	
21.5

	
38

	
5836

	
5237

	
6426

	
5341

	
6426

	
5749

	
7005

	
5425

	
7005

	
5822

	
27

	
50

	
6235

	
5383

	
6853

	
5509

	
6853

	
5916

	
7481

	
5613

	
7481

	
6021

	
32

	
65

	
6511

	
5488

	
7167

	
5613

	
7167

	
6031

	
7813

	
5739

	
7813

	
6146

	
8

	
15

	
28

	
4696

	
4777

	
5228

	
4829

	
5228

	
5150

	
5751

	
4871

	
5751

	
5289

	
21.5

	
38

	
5247

	
4934

	
5836

	
5028

	
5836

	
5446

	
6426

	
5132

	
6426

	
5530

	
27

	
50

	
5618

	
5017

	
6235

	
5164

	
6235

	
5571

	
6853

	
5279

	
6853

	
5676

	
32

	
65

	
5855

	
5080

	
6511

	
5237

	
6511

	
5645

	
7167

	
5383

	
7167

	
5770

	
9

	
15

	
28

	
4182

	
4558

	
4696

	
4620

	
4696

	
4639

	
5228

	
4672

	
5228

	
5070

	
21.5

	
38

	
4667

	
4620

	
5247

	
4725

	
5247

	
5132

	
5836

	
4840

	
5836

	
5226

	
27

	
50

	
4990

	
4652

	
5618

	
4819

	
5618

	
5206

	
6235

	
4944

	
6235

	
5341

	
32

	
65

	
5209

	
4683

	
5855

	
4861

	
5855

	
5247

	
6511

	
5017

	
6511

	
5394

	
10

	
15

	
28

	
3660

	
3616

	
4182

	
4108

	
4182

	
4157

	
4696

	
4453

	
4696

	
4569

	
21.5

	
38

	
4087

	
3971

	
4667

	
4422

	
4667

	
4527

	
5247

	
4547

	
5247

	
4923

	
27

	
50

	
4363

	
4265

	
4990

	
4463

	
4990

	
4829

	
5618

	
4610

	
5618

	
4986

	
32

	
65

	
4553

	
4275

	
5209

	
4474

	
5209

	
4840

	
5855

	
4652

	
5855

	
5007

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

10

  

Performance Data

  

	
2 Rows Cooking Capacity

	
(W)

	
Model

	
Entering

	
Water

	
Water

	
Entering Air Temperature°C

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	20.0WB	21.0WB	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
°C

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
006

	
5

	
12

	
28

	
5590

	
4150

	
5790

	
4021

	
5790

	
4299

	
6180

	
4043

	
6180

	
4321

	
6560

	
4321

	
15

	
40

	
6070

	
4396

	
6280

	
4267

	
6280

	
4556

	
6700

	
4289

	
6700

	
4578

	
7120

	
4588

	
18

	
52

	
6420

	
4567

	
6640

	
4439

	
6640

	
4738

	
7090

	
4481

	
7090

	
4759

	
7540

	
4791

	
21

	
65

	
6700

	
4706

	
6920

	
4567

	
6920

	
4866

	
7390

	
4610

	
7390

	
4898

	
7850

	
4930

	
6

	
12

	
28

	
5210

	
3989

	
5400

	
3861

	
5400

	
4139

	
5790

	
3882

	
5790

	
4150

	
6180

	
4150

	
15

	
40

	
5650

	
4203

	
5860

	
4064

	
5860

	
4364

	
6280

	
4107

	
6280

	
4396

	
6700

	
4406

	
18

	
52

	
5980

	
4353

	
6200

	
4225

	
6200

	
4513

	
6640

	
4267

	
6640

	
4556

	
7090

	
4578

	
21

	
65

	
6230

	
4471

	
6470

	
4342

	
6470

	
4642

	
6920

	
4396

	
6920

	
4674

	
7390

	
4717

	
7

	
12

	
28

	
4830

	
3829

	
5010

	
3690

	
5010

	
3979

	
5400

	
3722

	
5400

	
3989

	
5790

	
4000

	
15

	
40

	
5230

	
4000

	
5440

	
3882

	
5440

	
4171

	
5860

	
3914

	
5860

	
4193

	
6280

	
4214

	
18

	
52

	
5540

	
4128

	
5760

	
4021

	
5760

	
4299

	
6200

	
4053

	
6200

	
4342

	
6640

	
4374

	
21

	
65

	
5770

	
4225

	
6000

	
4118

	
6000

	
4406

	
6470

	
4171

	
6470

	
4449

	
6920

	
4492

	
8

	
12

	
28

	
4430

	
3668

	
4630

	
3540

	
4630

	
3818

	
5010

	
3561

	
5010

	
3840

	
5400

	
3840

	
15

	
40

	
4810

	
3807

	
5020

	
3690

	
5020

	
3979

	
5440

	
3733

	
5440

	
4000

	
5860

	
4032

	
18

	
52

	
5090

	
3914

	
5310

	
3807

	
5310

	
4075

	
5760

	
3861

	
5760

	
4128

	
6200

	
4171

	
21

	
65

	
5310

	
3989

	
5540

	
3882

	
5540

	
4267

	
6000

	
3947

	
6000

	
4214

	
6470

	
4267

	
9

	
12

	
28

	
4050

	
3519

	
4240

	
3380

	
4240

	
3668

	
4630

	
3412

	
4630

	
3679

	
5010

	
3690

	
15

	
40

	
4400

	
3615

	
4610

	
3508

	
4610

	
3786

	
5020

	
3540

	
5020

	
3818

	
5440

	
3861

	
18

	
52

	
4650

	
3690

	
4870

	
3658

	
4870

	
3872

	
5310

	
3647

	
5310

	
3914

	
5760

	
3968

	
21

	
65

	
4850

	
3743

	
5080

	
3658

	
5080

	
3936

	
5540

	
3722

	
5540

	
3989

	
6000

	
4043

	
10

	
12

	
28

	
3660

	
3369

	
3860

	
3230

	
3860

	
3519

	
4240

	
3273

	
4240

	
3540

	
4630

	
3561

	
15

	
40

	
3980

	
3422

	
4190

	
3326

	
4190

	
3594

	
4610

	
3369

	
4610

	
3636

	
5020

	
3668

	
18

	
52

	
4210

	
3465

	
4430

	
3369

	
4430

	
3647

	
4870

	
3444

	
4870

	
3711

	
5310

	
3754

	
21

	
65

	
4380

	
3508

	
4620

	
3422

	
4620

	
3679

	
5080

	
3497

	
5080

	
3754

	
5540

	
3829

	
008

	
5

	
15

	
28

	
7576

	
5791

	
7842

	
5592

	
7842

	
5990

	
8355

	
5613

	
8355

	
6010

	
8878

	
6010

	
21.5

	
38

	
8469

	
6240

	
8754

	
6052

	
8754

	
6470

	
9344

	
6094

	
9344

	
6491

	
9923

	
6512

	
27

	
50

	
9039

	
6512

	
9353

	
6335

	
9353

	
6763

	
9980

	
6397

	
9980

	
6805

	
10598

	
6847

	
32

	
65

	
9439

	
6700

	
9771

	
6533

	
9771

	
6951

	
10427

	
6606

	
10427

	
7014

	
11074

	
7056

	
6

	
15

	
28

	
7053

	
5540

	
7319

	
5362

	
7319

	
5760

	
7842

	
5383

	
7842

	
5770

	
8355

	
5791

	
21.5

	
38

	
7880

	
5948

	
8165

	
5760

	
8165

	
6178

	
8754

	
5822

	
8754

	
6209

	
9344

	
6251

	
27

	
50

	
8412

	
6188

	
8735

	
6021

	
8735

	
6429

	
9353

	
6094

	
9353

	
6491

	
9980

	
6533

	
32

	
65

	
8792

	
6345

	
9115

	
6188

	
9115

	
6606

	
9771

	
6272

	
9771

	
6669

	
10427

	
6721

	
7

	
15

	
28

	
6530

	
5321

	
6787

	
5143

	
6787

	
5530

	
7319

	
5164

	
7319

	
5551

	
7842

	
5575

	
21.5

	
38

	
7300

	
5655

	
7585

	
5488

	
7585

	
5885

	
8165

	
5540

	
8165

	
5937

	
8754

	
5969

	
27

	
50

	
7794

	
5864

	
8098

	
5697

	
8098

	
6105

	
8735

	
5791

	
8735

	
6178

	
9353

	
6220

	
32

	
65

	
8136

	
5990

	
8469

	
5843

	
8469

	
6251

	
9115

	
5948

	
9115

	
6335

	
9771

	
6397

	
8

	
15

	
28

	
6007

	
5101

	
6264

	
4923

	
6264

	
5310

	
6787

	
4944

	
6787

	
5341

	
7319

	
5352

	
21.5

	
38

	
6711

	
5362

	
7005

	
5206

	
7005

	
5592

	
7585

	
5279

	
7585

	
5655

	
8165

	
5697

	
27

	
50

	
7176

	
5530

	
7481

	
5383

	
7481

	
5770

	
8098

	
5467

	
8098

	
5864

	
8735

	
5916

	
32

	
65

	
7500

	
5645

	
7813

	
5509

	
7813

	
5885

	
8469

	
5603

	
8469

	
5979

	
9115

	
6063

	
9

	
15

	
28

	
5485

	
5206

	
5751

	
4704

	
5751

	
5091

	
6264

	
4746

	
6264

	
5122

	
6787

	
5143

	
21.5

	
38

	
6121

	
5080

	
6426

	
4923

	
6426

	
5310

	
7005

	
4997

	
7005

	
5373

	
7585

	
5436

	
27

	
50

	
6540

	
5206

	
6853

	
5070

	
6853

	
5446

	
7481

	
5164

	
7481

	
5530

	
8098

	
5613

	
32

	
65

	
6844

	
5279

	
7167

	
5153

	
7167

	
5530

	
7813

	
5279

	
7813

	
5645

	
8469

	
5739

	
10

	
15

	
28

	
4962

	
4683

	
5228

	
4495

	
5228

	
4892

	
5751

	
4537

	
5751

	
4913

	
6264

	
4934

	
21.5

	
38

	
5551

	
4787

	
5836

	
4641

	
5836

	
5017

	
6426

	
4725

	
6426

	
5091

	
7005

	
5153

	
27

	
50

	
5922

	
4861

	
6235

	
4746

	
6235

	
5101

	
6853

	
4850

	
6853

	
5216

	
7481

	
5300

	
32

	
65

	
6188

	
4913

	
6511

	
4798

	
6511

	
5164

	
7167

	
4934

	
7167

	
5289

	
7813

	
5394

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

11

  

 

Performance Data

  

	
2 Rows Cooling Capacity

	
(W)

	
Model

	
Entering

	
Water

	
Water

	
Entering Air Temperature°C

	  	
Water

	
Flow

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	
I/min

	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
°C

	 	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
010

	
5

	
19

	
24

	
7443

	
6483

	
8062

	
6545

	
8062

	
7058

	
8690

	
6587

	
8690

	
7079

	
24

	
32

	
7967

	
6660

	
8624

	
6744

	
8624

	
7225

	
9280

	
6796

	
9280

	
7288

	
31

	
50

	
8281

	
6734

	
8966

	
6838

	
8966

	
7330

	
9671

	
6932

	
9671

	
7413

	
37

	
68

	
8509

	
6776

	
9223

	
6911

	
9223

	
7382

	
9928

	
6995

	
9928

	
7476

	
6

	
19

	
24

	
6834

	
6211

	
7443

	
6274

	
7443

	
6786

	
8062

	
6315

	
8062

	
6807

	
24

	
32

	
7310

	
6295

	
7967

	
6389

	
7967

	
6891

	
8624

	
6472

	
8624

	
6953

	
31

	
50

	
7586

	
6347

	
8281

	
6462

	
8281

	
6932

	
8966

	
6577

	
8966

	
7026

	
37

	
68

	
7805

	
6378

	
8500

	
6514

	
8500

	
6974

	
9223

	
6629

	
9223

	
7079

	
7

	
19

	
24

	
6206

	
5939

	
6825

	
6002

	
6825

	
6504

	
7434

	
6044

	
7434

	
6535

	
24

	
32

	
6634

	
5960

	
7301

	
6064

	
7301

	
6535

	
7957

	
6159

	
7957

	
6608

	
31

	
50

	
6891

	
6012

	
7577

	
6085

	
7577

	
6587

	
8271

	
6200

	
8271

	
6650

	
37

	
68

	
7072

	
6054

	
7786

	
6106

	
7786

	
6608

	
8490

	
6221

	
8490

	
6671

	
8

	
19

	
24

	
5578

	
5667

	
6206

	
5730

	
6206

	
6221

	
6825

	
5782

	
6825

	
6274

	
24

	
32

	
5968

	
5709

	
6634

	
5772

	
6634

	
6253

	
7310

	
5824

	
7310

	
6315

	
31

	
50

	
6215

	
5730

	
6901

	
5814

	
6901

	
6274

	
7586

	
5845

	
7586

	
6357

	
37

	
68

	
6377

	
5751

	
7091

	
5834

	
7091

	
6295

	
7805

	
5866

	
6853

	
6378

	
9

	
19

	
24

	
4531

	
4935

	
5092

	
5008

	
5092

	
5448

	
5673

	
5061

	
5673

	
5489

	
24

	
32

	
5311

	
5249

	
5968

	
5364

	
5968

	
5834

	
6644

	
5500

	
6644

	
5939

	
31

	
50

	
5521

	
5270

	
6215

	
5385

	
6215

	
5855

	
6901

	
5521

	
6901

	
5960

	
37

	
68

	
5673

	
5280

	
6377

	
5395

	
6377

	
5876

	
7091

	
5542

	
7091

	
5970

	
10

	
19

	
24

	
4350

	
4580

	
4969

	
4810

	
4969

	
5186

	
5578

	
4988

	
5578

	
5353

	
24

	
32

	
4645

	
4611

	
5302

	
4831

	
5302

	
5228

	
5958

	
5019

	
5958

	
5395

	
31

	
50

	
4835

	
4632

	
5530

	
4852

	
5530

	
5249

	
6225

	
5040

	
6225

	
5416

	
37

	
68

	
4950

	
4642

	
5673

	
4862

	
5673

	
5259

	
6377

	
5061

	
6377

	
5437

	
012

	
5

	
24

	
32

	
9045

	
7655

	
9799

	
7727

	
9799

	
8316

	
10544

	
7789

	
10544

	
8357

	
30

	
40

	
9599

	
7882

	
10401

	
7985

	
10401

	
8564

	
11194

	
8078

	
11194

	
8647

	
36

	
60

	
10000

	
7985

	
10831

	
8171

	
10831

	
8750

	
11662

	
8264

	
11662

	
8843

	
42

	
82

	
10287

	
8161

	
11156

	
8285

	
11156

	
8864

	
12006

	
8409

	
12006

	
8977

	
6

	
24

	
32

	
8290

	
7293

	
9045

	
7376

	
9045

	
7954

	
9799

	
7448

	
9799

	
8016

	
30

	
40

	
8797

	
7469

	
9599

	
7583

	
9599

	
8161

	
10401

	
7686

	
10401

	
8275

	
36

	
60

	
9160

	
7593

	
10000

	
7727

	
10000

	
8285

	
10831

	
7841

	
10831

	
8399

	
42

	
82

	
9427

	
7665

	
10287

	
7820

	
10287

	
8388

	
11156

	
7954

	
11156

	
8502

	
7

	
24

	
32

	
7536

	
6932

	
8290

	
7025

	
8290

	
7603

	
9045

	
7097

	
9045

	
7665

	
30

	
40

	
7994

	
7056

	
8797

	
7180

	
8797

	
7748

	
9599

	
7293

	
9599

	
7841

	
36

	
60

	
8329

	
7128

	
9160

	
7283

	
9160

	
7830

	
10000

	
7417

	
10000

	
7965

	
42

	
82

	
8577

	
7180

	
9427

	
7355

	
9427

	
7903

	
10287

	
7510

	
10287

	
8037

	
8

	
24

	
32

	
6772

	
6580

	
7536

	
6684

	
7536

	
7252

	
8290

	
6766

	
8290

	
7314

	
30

	
40

	
7202

	
6632

	
7994

	
6777

	
7994

	
7324

	
8797

	
6901

	
8797

	
7438

	
36

	
60

	
7498

	
6663

	
8329

	
6839

	
8329

	
7376

	
9160

	
6994

	
9160

	
7521

	
42

	
82

	
7717

	
6684

	
8577

	
6870

	
8577

	
7417

	
9427

	
7056

	
9427

	
7572

	
9

	
24

	
32

	
6017

	
5888

	
6772

	
6343

	
6772

	
6594

	
7536

	
6436

	
7536

	
6983

	
30

	
40

	
6399

	
6188

	
7202

	
6364

	
7202

	
6973

	
7994

	
6508

	
7994

	
7045

	
36

	
60

	
6667

	
6209

	
7498

	
6384

	
7498

	
7014

	
8329

	
6560

	
8329

	
7066

	
42

	
82

	
6867

	
6240

	
7717

	
6395

	
7717

	
7056

	
8577

	
6580

	
8577

	
7087

	
10

	
24

	
32

	
5272

	
5123

	
6017

	
5899

	
6017

	
5930

	
6772

	
6116

	
6772

	
6591

	
30

	
40

	
5597

	
5397

	
6399

	
5919

	
6399

	
6232

	
7202

	
6198

	
7202

	
6611

	
36

	
60

	
5836

	
5795

	
6667

	
5961

	
6667

	
6477

	
7498

	
6250

	
7498

	
6632

	
42

	
82

	
5998

	
5930

	
6867

	
6012

	
6867

	
6508

	
7717

	
6291

	
7717

	
6653

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

12

  

 

Performance Data

 

	
2 Rows Cooling Capacity

	
(W)

    

	
Model

	
Entering

	
Water

	
Water

	
Entering Air Temperature°C

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	20.0WB	21.0WB	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
°C

	  	
Kpa

	
T.H.

	
S.H.

	
T.H.

	
S.H.

	
T.H.

	
S.H.

	
T.H.

	
S.H.

	
T.H.

	
S.H.

	
T.H.

	
S.H.

	  	  	  	  	
9004

	
6870

	
9318

	
6640

	
9318

	
7110

	
9928

	
6660

	
9928

	
7131

	
10546

	
7131

	
010

	
5

	
24

	
32

	
9633

	
7089

	
9956

	
6870

	
9956

	
7351

	
10622

	
6922

	
10622

	
7371

	
11279

	
7392

	
31

	
50

	
10013

	
7204

	
10356

	
7006

	
10356

	
7476

	
11051

	
7068

	
11051

	
7528

	
11736

	
7570

	
37

	
68

	
10356

	
7288

	
10642

	
7100

	
10642

	
7560

	
11355

	
7183

	
11355

	
7622

	
12060

	
7675

	
6

	
19

	
24

	
8386

	
6577

	
8700

	
6368

	
8700

	
6838

	
9318

	
6389

	
9318

	
6849

	
9928

	
6870

	
24

	
32

	
8966

	
6755

	
9290

	
6545

	
9290

	
7016

	
9956

	
6608

	
9956

	
7047

	
10632

	
7100

	
31

	
50

	
9318

	
6838

	
9671

	
6660

	
9671

	
7110

	
10356

	
6734

	
10356

	
7173

	
11051

	
7225

	
37

	
68

	
9575

	
6901

	
9918

	
6723

	
9918

	
7183

	
10642

	
6817

	
10642

	
7246

	
11355

	
7309

	
7

	
19

	
24

	
7757

	
6305

	
8062

	
6096

	
8062

	
6556

	
8690

	
6127

	
8690

	
6577

	
9309

	
6608

	
24

	
32

	
8300

	
6420

	
8624

	
6232

	
8624

	
6681

	
9280

	
6284

	
9280

	
6734

	
9947

	
6776

	
31

	
50

	
8624

	
6472

	
8957

	
6295

	
8957

	
6744

	
9661

	
6399

	
9661

	
6817

	
10346

	
6870

	
37

	
68

	
8843

	
6493

	
9195

	
6336

	
9195

	
6776

	
9899

	
6451

	
9899

	
6870

	
10613

	
6943

	
8

	
19

	
24

	
7139

	
6054

	
7443

	
5834

	
7443

	
6295

	
8062

	
5866

	
8062

	
6336

	
8690

	
6347

	
24

	
32

	
7634

	
6085

	
7967

	
5908

	
7967

	
6347

	
8624

	
5991

	
8624

	
6420

	
9280

	
6472

	
31

	
50

	
7948

	
6117

	
8281

	
5949

	
8281

	
6378

	
8966

	
6044

	
8966

	
6483

	
9671

	
6535

	
37

	
68

	
8167

	
6138

	
8500

	
5991

	
8500

	
6399

	
9214

	
6085

	
9214

	
6504

	
9918

	
6587

	
9

	
19

	
24

	
5949

	
5636

	
6235

	
5092

	
6235

	
5510

	
6796

	
5144

	
6796

	
5552

	
7358

	
5573

	
24

	
32

	
6967

	
5772

	
7310

	
5594

	
7310

	
6033

	
7967

	
5678

	
7967

	
6106

	
8633

	
6180

	
31

	
50

	
7243

	
5793

	
7586

	
5615

	
7586

	
6054

	
8281

	
5709

	
8281

	
6117

	
8966

	
6211

	
37

	
68

	
7453

	
5814

	
7805

	
5625

	
7805

	
6064

	
8509

	
5740

	
8509

	
6138

	
9223

	
6242

	
10

	
19

	
24

	
5901

	
5353

	
6215

	
5144

	
6215

	
5552

	
6834

	
5280

	
6834

	
5657

	
7443

	
5793

	
24

	
32

	
6311

	
5374

	
6634

	
5176

	
6634

	
5584

	
7301

	
5322

	
7301

	
5699

	
7957

	
5824

	
31

	
50

	
6568

	
5385

	
6910

	
5197

	
6910

	
5604

	
7596

	
5343

	
7596

	
5730

	
8290

	
5845

	
37

	
68

	
6739

	
5395

	
7091

	
5218

	
7091

	
5615

	
7805

	
5364

	
7805

	
5751

	
8509

	
5866

	
012

	
5

	
24

	
32

	
10917

	
8099

	
11299

	
7841

	
11299

	
8399

	
12053

	
7882

	
12053

	
8419

	
12808

	
8430

	
30

	
40

	
11595

	
8453

	
11996

	
8151

	
11996

	
8698

	
12798

	
8337

	
12798

	
8337

	
13601

	
8781

	
36

	
60

	
12073

	
8605

	
12493

	
8357

	
12493

	
8915

	
13333

	
8430

	
13333

	
8977

	
14164

	
9018

	
42

	
82

	
12426

	
8750

	
12865

	
8502

	
12865

	
9060

	
13715

	
8595

	
13715

	
9132

	
14575

	
9194

	
6

	
24

	
32

	
10162

	
7748

	
10544

	
7510

	
10544

	
8047

	
11299

	
7562

	
11299

	
8089

	
12053

	
8099

	
30

	
40

	
10793

	
8006

	
11194

	
7758

	
11194

	
8316

	
11996

	
7830

	
11996

	
8357

	
12798

	
8409

	
36

	
60

	
11242

	
8171

	
11662

	
7944

	
11662

	
8492

	
12493

	
8027

	
12493

	
8564

	
13333

	
8616

	
42

	
82

	
11576

	
8285

	
12006

	
8078

	
12006

	
8616

	
12865

	
8171

	
12865

	
8698

	
13715

	
8771

	
7

	
24

	
32

	
9417

	
7417

	
9799

	
7056

	
9799

	
7717

	
10544

	
7221

	
10544

	
7748

	
11299

	
7789

	
30

	
40

	
10000

	
7614

	
10401

	
7386

	
10401

	
7934

	
11194

	
7459

	
11194

	
7985

	
11996

	
8037

	
36

	
60

	
10411

	
7748

	
10831

	
7531

	
10831

	
8058

	
11662

	
7634

	
11662

	
8151

	
12493

	
8213

	
42

	
82

	
10716

	
7830

	
11156

	
7645

	
11156

	
8161

	
12006

	
7748

	
12006

	
8264

	
12865

	
8347

	
8

	
24

	
32

	
8663

	
7076

	
9045

	
6849

	
9045

	
7376

	
9799

	
6911

	
9799

	
7428

	
10544

	
7438

	
30

	
40

	
9198

	
7221

	
9599

	
7004

	
9599

	
7531

	
10401

	
7097

	
10401

	
7614

	
11194

	
7676

	
36

	
60

	
9580

	
7314

	
10000

	
7107

	
10000

	
7645

	
10831

	
7231

	
10831

	
7820

	
12006

	
7934

	
42

	
82

	
9866

	
7386

	
10287

	
7200

	
10287

	
7717

	
11156

	
7324

	
11156

	
7820

	
12006

	
7934

	
9

	
24

	
32

	
7908

	
6756

	
8290

	
6529

	
8290

	
7056

	
9045

	
6580

	
9045

	
7097

	
9799

	
7149

	
30

	
40

	
8395

	
6839

	
8797

	
6632

	
8797

	
7149

	
9599

	
6725

	
9599

	
7231

	
10401

	
7304

	
36

	
60

	
8739

	
6880

	
9160

	
6704

	
9160

	
7211

	
10000

	
6828

	
10000

	
7324

	
10831

	
7428

	
42

	
82

	
9007

	
6921

	
9427

	
6756

	
9427

	
7242

	
10287

	
6901

	
10287

	
7386

	
11156

	
7500

	
10

	
24

	
32

	
7154

	
6426

	
7536

	
6198

	
7536

	
6725

	
8290

	
6271

	
9245

	
6787

	
9045

	
6839

	
30

	
40

	
7593

	
6436

	
7994

	
6250

	
7994

	
6756

	
8797

	
6353

	
8797

	
6859

	
9599

	
6942

	
36

	
60

	
7908

	
6457

	
8329

	
6281

	
8329

	
6777

	
9160

	
6426

	
9160

	
6911

	
10000

	
7014

	
42

	
82

	
8138

	
6457

	
8577

	
6312

	
8577

	
6787

	
9427

	
6467

	
9427

	
6942

	
10287

	
7076

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

13

  

 

Performance Data

  

	
2 Rows Cooling Capacity

	
(W)

	Model	
Entering

	
Water Flow

	
Water

	
Entering Air Temperature°C

	 	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
°C

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
014

	
5

	
27

	
26

	
10640

	
9580

	
11530

	
9660

	
11530

	
10408

	
12410

	
9741

	
12410

	
10454

	
33

	
38

	
11050

	
9603

	
11970

	
9775

	
11970

	
10477

	
12880

	
9890

	
12880

	
10580

	
39

	
52

	
11340

	
9626

	
12280

	
9844

	
12280

	
10546

	
13220

	
9959

	
13220

	
10661

	
45

	
72

	
11530

	
9729

	
12500

	
9867

	
12500

	
10557

	
13450

	
10017

	
13450

	
10695

	
6

	
27

	
26

	
9750

	
9085

	
10640

	
9223

	
10640

	
9948

	
11530

	
9315

	
11530

	
10028

	
33

	
38

	
10100

	
9108

	
11020

	
9258

	
11020

	
9959

	
11950

	
9384

	
11950

	
10097

	
39

	
52

	
10380

	
9120

	
11330

	
9304

	
11330

	
9982

	
12270

	
9442

	
12270

	
10120

	
45

	
72

	
10570

	
9131

	
11530

	
9315

	
11530

	
9994

	
12500

	
9476

	
12500

	
10132

	
7

	
27

	
26

	
8870

	
8464

	
9760

	
8671

	
9760

	
9315

	
10650

	
8878

	
10650

	
9476

	
33

	
38

	
9200

	
8510

	
10120

	
8717

	
10120

	
9361

	
11040

	
8924

	
11040

	
9522

	
39

	
52

	
9440

	
8533

	
10380

	
8740

	
10380

	
9396

	
11330

	
8936

	
11330

	
9557

	
45

	
72

	
9620

	
8556

	
10570

	
8763

	
10570

	
9419

	
11530

	
8947

	
11530

	
9580

	
8

	
27

	
26

	
7970

	
7832

	
8870

	
8073

	
8870

	
8717

	
9760

	
8315

	
9760

	
8924

	
33

	
38

	
8290

	
7901

	
9200

	
8119

	
9200

	
8740

	
10120

	
8338

	
10120

	
8970

	
39

	
52

	
8500

	
7935

	
9440

	
8154

	
9440

	
8775

	
10380

	
8384

	
10380

	
8993

	
45

	
72

	
8650

	
7958

	
9610

	
8177

	
9610

	
8832

	
10560

	
8407

	
10560

	
9016

	
9

	
27

	
26

	
7080

	
7245

	
7970

	
7475

	
7970

	
8119

	
8870

	
7740

	
8870

	
8338

	
33

	
38

	
7370

	
7303

	
8290

	
7556

	
8290

	
8177

	
9200

	
7786

	
9200

	
8395

	
39

	
52

	
7560

	
7337

	
8500

	
7590

	
8500

	
8211

	
9440

	
7820

	
9440

	
8418

	
45

	
72

	
7700

	
7372

	
8650

	
7625

	
8650

	
8246

	
9620

	
7855

	
9620

	
8453

	
10

	
27

	
26

	
6200

	
6670

	
7080

	
6912

	
7080

	
7360

	
7970

	
7222

	
7970

	
7774

	
33

	
38

	
6450

	
6716

	
7370

	
6958

	
7370

	
7590

	
8300

	
7245

	
8300

	
7820

	
39

	
52

	
6620

	
6728

	
7560

	
7015

	
7560

	
7625

	
8500

	
7280

	
8500

	
7855

	
45

	
72

	
6730

	
6739

	
7710

	
7038

	
7710

	
7636

	
8660

	
7303

	
8660

	
7866

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor

T.H.: Total Heat Capacity

S.H: Sensible Heat Capacity

Speed Correction Table

  

	
Model

	
Cooling Capacity

	
Heating Capacity

	
Medium Speed

	
Low Speed

	
Medium

Speed

	
Low

Speed

	
T.H

	
S.H

	
T.H.

	
S,H

	
002

	
0.85

	
0.83

	
0.70

	
0.66

	
0.84

	
0.72

	
003

	
0.86

	
0.84

	
0.71

	
0.67

	
0.85

	
0.73

	
004

	
0.87

	
0.85

	
0.74

	
0.70

	
0.86

	
0.74

	
005

	
0.87

	
0.85

	
0.73

	
0.70

	
0.86

	
0.74

	
006

	
0.89

	
0.87

	
0.75

	
0.70

	
0.87

	
0.75

	
008

	
0.86

	
0.84

	
0.73

	
0.69

	
0.86

	
0.74

	
010

	
0.89

	
0.87

	
0.75

	
0.70

	
0.86

	
0.74

	
012

	
0.88

	
0.86

	
0.75

	
0.70

	
0.87

	
0.75

	
014

	
0.89

	
0.87

	
0.75

	
0.69

	
0.87

	
0.75

  

  

14

  

  

Performance Data

  

	
2 Rows Cooling Capacity

	
(W)

   

	
Model

	
Entering

	
Water

	
Water

	
Entering Air Temperature°C

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
°C

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
014

	
5

	
27

	
26

	
12850

	
10132

	
13300

	
9810

	
13300

	
10511

	
14180

	
9867

	
14180

	
10534

	
15070

	
10546

	
33

	
38

	
13350

	
10350

	
13810

	
9971

	
13800

	
10649

	
14730

	
9948

	
14730

	
10707

	
15660

	
10741

	
39

	
52

	
13690

	
10373

	
14160

	
10074

	
14160

	
10741

	
15120

	
10155

	
15120

	
10822

	
16060

	
10868

	
45

	
72

	
13930

	
10419

	
14420

	
10132

	
14420

	
10799

	
15370

	
10235

	
15370

	
10879

	
16340

	
10960

	
6

	
27

	
26

	
11960

	
9695

	
12400

	
9396

	
12400

	
10063

	
13290

	
9453

	
13290

	
10120

	
14180

	
10132

	
33

	
38

	
12400

	
9775

	
12860

	
9476

	
12860

	
10155

	
13780

	
9557

	
13780

	
10201

	
14700

	
10270

	
39

	
52

	
12740

	
9844

	
13210

	
9568

	
13210

	
10224

	
14150

	
9672

	
14150

	
10316

	
15110

	
10373

	
45

	
72

	
12980

	
9879

	
13460

	
9626

	
13460

	
10270

	
14420

	
9741

	
14420

	
10362

	
15370

	
10454

	
7

	
27

	
26

	
11090

	
9281

	
11540

	
8832

	
11540

	
9660

	
12410

	
9039

	
12410

	
9695

	
13300

	
9752

	
33

	
38

	
11510

	
9315

	
11970

	
9039

	
11970

	
9695

	
12880

	
9120

	
12880

	
9764

	
13800

	
9833

	
39

	
52

	
11800

	
9327

	
12270

	
9074

	
12270

	
9706

	
13210

	
9200

	
13210

	
9821

	
14160

	
9890

	
45

	
72

	
12020

	
9338

	
12510

	
9108

	
12510

	
9729

	
13460

	
9235

	
13460

	
9856

	
14430

	
9948

	
8

	
27

	
26

	
10200

	
8706

	
10650

	
8510

	
10650

	
9120

	
11530

	
8648

	
11530

	
9223

	
12410

	
9315

	
33

	
38

	
10590

	
8740

	
11050

	
8533

	
11050

	
9154

	
11970

	
8683

	
11970

	
9258

	
12880

	
9396

	
39

	
52

	
10860

	
8775

	
11330

	
8556

	
11330

	
9177

	
12270

	
8706

	
12270

	
9292

	
13210

	
9442

	
45

	
72

	
11060

	
8798

	
11530

	
8579

	
11530

	
9200

	
12500

	
8729

	
12500

	
9315

	
13450

	
9453

	
9

	
27

	
26

	
9310

	
8165

	
9260

	
7993

	
9260

	
8533

	
10650

	
8165

	
10650

	
8694

	
11530

	
8855

	
33

	
38

	
9670

	
8188

	
10130

	
8027

	
10130

	
8579

	
11050

	
8200

	
11050

	
8740

	
11980

	
8901

	
39

	
52

	
9910

	
8223

	
10380

	
8050

	
10380

	
8602

	
11340

	
8223

	
11340

	
8786

	
12280

	
8924

	
45

	
72

	
10100

	
8257

	
10570

	
8062

	
10570

	
8637

	
11530

	
8234

	
11530

	
8809

	
12510

	
8947

	
10

	
27

	
26

	
8420

	
7590

	
8870

	
7441

	
8870

	
8004

	
9750

	
7625

	
9750

	
8200

	
10640

	
8487

	
33

	
38

	
8750

	
7648

	
9210

	
7475

	
9210

	
8050

	
10130

	
7671

	
10130

	
8223

	
11060

	
8395

	
39

	
52

	
8970

	
7682

	
9450

	
7510

	
9450

	
8073

	
10390

	
7705

	
10390

	
8257

	
11340

	
8430

	
45

	
72

	
9130

	
7705

	
9620

	
7533

	
9620

	
8096

	
10580

	
7717

	
10580

	
8280

	
11540

	
8441

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

15

  

Performance Data

  

	
3 Rows Cooling Capacity

	
(W)

	
Model

	
Entering

	
Water Flow

	
Water

	
Entering Air  Temperature°C

	  	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
°C

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
002

	
5

	
5

	
10

	
1893

	
1409

	
2048

	
1420

	
2048

	
1531

	
2204

	
1431

	
2204

	
1531

	
6.6

	
14

	
2204

	
1575

	
2396

	
1587

	
2396

	
1709

	
2576

	
1598

	
2576

	
1720

	
8.4

	
19

	
2420

	
1675

	
2635

	
1709

	
2635

	
1831

	
2827

	
1731

	
2827

	
1842

	
10

	
25

	
2588

	
1753

	
2815

	
1797

	
2815

	
1908

	
3019

	
1820

	
3019

	
1931

	
6

	
5

	
10

	
1725

	
1354

	
2216

	
1365

	
1893

	
1476

	
2048

	
1365

	
2048

	
1487

	
6.6

	
14

	
2024

	
1498

	
2204

	
1509

	
2204

	
1631

	
2396

	
1531

	
2396

	
1642

	
8.4

	
19

	
2228

	
1587

	
2420

	
1609

	
2420

	
1731

	
2635

	
1642

	
2635

	
1753

	
10

	
25

	
2384

	
1653

	
2588

	
1686

	
2588

	
1808

	
2815

	
1720

	
2815

	
1831

	
7

	
5

	
10

	
1569

	
1298

	
1725

	
1298

	
1725

	
1420

	
1893

	
1320

	
1893

	
1420

	
6.6

	
14

	
1845

	
1420

	
2024

	
1431

	
2024

	
1553

	
2204

	
1453

	
2204

	
1575

	
8.4

	
19

	
2024

	
1498

	
2228

	
1520

	
2228

	
1642

	
2420

	
1553

	
2420

	
1664

	
10

	
25

	
2156

	
1553

	
2384

	
1587

	
2384

	
1709

	
2588

	
1609

	
2588

	
1731

	
8

	
5

	
10

	
1426

	
1254

	
1569

	
1254

	
1569

	
1365

	
1725

	
1265

	
1725

	
1365

	
6.6

	
14

	
1653

	
1342

	
1845

	
1354

	
1845

	
1476

	
2024

	
1376

	
2024

	
1498

	
8.4

	
19

	
1821

	
1398

	
2024

	
1431

	
2024

	
1553

	
2228

	
1453

	
2228

	
1575

	
10

	
25

	
1953

	
1442

	
2156

	
1487

	
2156

	
1598

	
2384

	
1520

	
2384

	
1642

	
9

	
5

	
10

	
1258

	
1165

	
1426

	
1209

	
1426

	
1320

	
1569

	
1209

	
1569

	
1331

	
6.6

	
14

	
1473

	
1254

	
1653

	
1287

	
1653

	
1398

	
1845

	
1298

	
1845

	
1420

	
8.4

	
19

	
1617

	
1298

	
1821

	
1342

	
1821

	
1442

	
2024

	
1365

	
2024

	
1453

	
10

	
25

	
1725

	
1331

	
1953

	
1376

	
1953

	
1487

	
2156

	
1420

	
2156

	
1531

	
10

	
5

	
10

	
1102

	
1021

	
1258

	
1165

	
1258

	
1165

	
1426

	
1176

	
1426

	
1276

	
6.6

	
14

	
1282

	
1176

	
1473

	
1109

	
1473

	
1320

	
1653

	
1243

	
1653

	
1342

	
8.4

	
19

	
1426

	
1198

	
1617

	
1232

	
1617

	
1354

	
1821

	
1276

	
1821

	
1398

	
10

	
25

	
1521

	
1209

	
1725

	
1276

	
1725

	
1376

	
1953

	
1320

	
1953

	
1420

	
003

	
5

	
7

	
15

	
2730

	
2073

	
2959

	
2084

	
2959

	
2247

	
3189

	
2095

	
3189

	
2258

	
9

	
25

	
3062

	
2236

	
3338

	
2258

	
3338

	
2421

	
3590

	
2290

	
3590

	
2453

	
11

	
34

	
3303

	
2334

	
3590

	
2377

	
3590

	
2540

	
3854

	
2399

	
3854

	
2562

	
13.6

	
42

	
3487

	
2410

	
3762

	
2453

	
3762

	
3636

	
4060

	
2486

	
4060

	
2648

	
6

	
7

	
15

	
2512

	
1986

	
2730

	
1965

	
2730

	
2160

	
2959

	
2019

	
2959

	
2171

	
9

	
25

	
2810

	
2117

	
3062

	
2149

	
3062

	
2312

	
3338

	
2171

	
3338

	
2334

	
11

	
34

	
3028

	
2214

	
3303

	
2247

	
3303

	
2410

	
3590

	
2290

	
3590

	
2431

	
13.6

	
42

	
3189

	
2269

	
3487

	
2312

	
3487

	
2486

	
3762

	
2355

	
3762

	
2529

	
7

	
7

	
15

	
2282

	
1889

	
2512

	
1921

	
2512

	
2073

	
2615

	
1932

	
2730

	
2084

	
9

	
25

	
2558

	
2008

	
2810

	
2030

	
2810

	
2193

	
3062

	
2073

	
3062

	
2225

	
11

	
34

	
2764

	
2073

	
3028

	
2117

	
3028

	
2290

	
2959

	
2160

	
3303

	
2323

	
13.6

	
42

	
2890

	
2117

	
3189

	
2171

	
3189

	
2334

	
3487

	
2225

	
3487

	
2388

	
8

	
7

	
15

	
2053

	
1813

	
2282

	
1834

	
2282

	
1997

	
2512

	
1856

	
2512

	
2008

	
9

	
25

	
2305

	
1889

	
2558

	
1932

	
2558

	
2084

	
2810

	
1954

	
2810

	
2117

	
11

	
34

	
2477

	
1943

	
2764

	
1997

	
2764

	
2149

	
3028

	
2030

	
3028

	
2182

	
13.6

	
42

	
2615

	
1986

	
2890

	
2030

	
2890

	
2193

	
3189

	
2084

	
3189

	
2247

	
9

	
7

	
15

	
1824

	
1726

	
2053

	
1758

	
2053

	
1921

	
2282

	
1769

	
2282

	
1932

	
9

	
25

	
2053

	
1780

	
2305

	
1813

	
2305

	
1965

	
2558

	
1856

	
2558

	
2008

	
11

	
34

	
2202

	
1802

	
2477

	
1867

	
2477

	
2019

	
2764

	
1910

	
2764

	
2062

	
13.6

	
42

	
2317

	
1834

	
2615

	
1889

	
2615

	
2041

	
2890

	
1954

	
2890

	
2095

	
10

	
7

	
15

	
1606

	
1520

	
1824

	
1682

	
1824

	
1726

	
2053

	
1693

	
2053

	
1856

	
9

	
25

	
1789

	
1672

	
2053

	
1704

	
2053

	
1856

	
2305

	
1737

	
2305

	
1889

	
11

	
34

	
1938

	
1672

	
2202

	
1726

	
2202

	
1878

	
2477

	
1780

	
2477

	
1932

	
13.6

	
42

	
2030

	
1682

	
2317

	
1737

	
2317

	
1889

	
2615

	
1813

	
2615

	
1954

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

16

  

   

Performance Data

  

	
3 Rows Cooling Capacity

	
(W)

   

	
Model

	
Entering

	
Water

	
Water

	
Entering Air Temperature°C

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
°C

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
002

	
5

	
5

	
10

	
2288

	
1487

	
2360

	
1431

	
2360

	
1531

	
2528

	
1442

	
2528

	
1531

	
2671

	
1531

	
6.6

	
14

	
2659

	
1664

	
2755

	
1609

	
2755

	
1731

	
2935

	
1631

	
2935

	
1742

	
3127

	
1742

	
8.4

	
19

	
2935

	
1797

	
3043

	
1742

	
3043

	
1853

	
3234

	
1753

	
3234

	
1875

	
3438

	
1886

	
10

	
25

	
3163

	
1886

	
3246

	
1831

	
3246

	
3073

	
3450

	
1853

	
3450

	
1975

	
3678

	
1986

	
6

	
5

	
10

	
2132

	
1431

	
2204

	
1376

	
2204

	
1487

	
2360

	
1376

	
2360

	
1487

	
2528

	
1487

	
6.6

	
14

	
2480

	
1598

	
2576

	
1553

	
2576

	
1653

	
2755

	
1564

	
2755

	
1664

	
2935

	
1675

	
8.4

	
19

	
2731

	
1709

	
2827

	
1664

	
2827

	
1775

	
3043

	
1675

	
3043

	
1797

	
3234

	
1797

	
10

	
25

	
2911

	
1797

	
3019

	
1742

	
3019

	
1853

	
3246

	
1764

	
3246

	
1875

	
3450

	
1897

	
7

	
5

	
10

	
1965

	
1376

	
2048

	
1331

	
2048

	
1431

	
2204

	
1331

	
2204

	
1431

	
2360

	
1431

	
6.6

	
14

	
2300

	
1520

	
2396

	
1476

	
2396

	
1587

	
2576

	
1487

	
2576

	
1587

	
2755

	
1598

	
8.4

	
19

	
2540

	
1631

	
2635

	
1575

	
2635

	
1686

	
2827

	
1598

	
2827

	
1709

	
3043

	
1720

	
10

	
25

	
2707

	
1686

	
2815

	
1653

	
2815

	
1753

	
3019

	
1675

	
3019

	
1775

	
3246

	
1808

	
8

	
5

	
10

	
1809

	
1320

	
1893

	
1276

	
1893

	
1376

	
2048

	
1276

	
2048

	
1376

	
2204

	
1376

	
6.6

	
14

	
2120

	
1442

	
2204

	
1409

	
2204

	
1509

	
2396

	
1420

	
2396

	
1520

	
2576

	
1531

	
8.4

	
19

	
2324

	
1531

	
2420

	
1487

	
2420

	
1598

	
2635

	
1509

	
2635

	
1609

	
2827

	
1642

	
10

	
25

	
2480

	
1587

	
2588

	
1553

	
2588

	
1664

	
2815

	
1575

	
2815

	
1686

	
3019

	
1720

	
9

	
5

	
10

	
1653

	
1276

	
1725

	
1220

	
1725

	
1331

	
1893

	
1220

	
1893

	
1331

	
2048

	
1331

	
6.6

	
14

	
1941

	
1365

	
2024

	
1331

	
2024

	
1431

	
2204

	
1342

	
2204

	
1442

	
2396

	
1453

	
8.4

	
19

	
2132

	
1442

	
2228

	
1409

	
2228

	
1509

	
2420

	
1431

	
2420

	
1531

	
2635

	
1553

	
10

	
25

	
2276

	
1498

	
2384

	
1453

	
2384

	
1564

	
2588

	
1487

	
2588

	
1587

	
2815

	
1609

	
10

	
5

	
10

	
1485

	
1220

	
1569

	
1176

	
1569

	
1276

	
1725

	
1176

	
1725

	
1276

	
1893

	
1276

	
6.6

	
14

	
1737

	
1298

	
1845

	
1254

	
1845

	
1365

	
2024

	
1276

	
2024

	
1376

	
2204

	
1398

	
8.4

	
19

	
1917

	
1354

	
2024

	
1320

	
2024

	
1420

	
2228

	
1342

	
2228

	
1442

	
2420

	
1476

	
10

	
25

	
2048

	
1398

	
2156

	
1354

	
2156

	
1453

	
2384

	
1398

	
2384

	
1498

	
2588

	
1520

	
003

	
5

	
7

	
15

	
3303

	
2182

	
3418

	
2106

	
3418

	
2258

	
3636

	
2117

	
3636

	
2258

	
3877

	
2258

	
9

	
25

	
3705

	
2377

	
3842

	
2301

	
3842

	
2464

	
4095

	
2312

	
4095

	
2475

	
4347

	
2475

	
11

	
34

	
4003

	
2496

	
4141

	
2421

	
4141

	
2583

	
4416

	
2453

	
4416

	
2605

	
4680

	
2616

	
13.6

	
42

	
4198

	
2583

	
4347

	
2507

	
4347

	
2681

	
4645

	
2540

	
4645

	
2703

	
4920

	
2714

	
6

	
7

	
15

	
3085

	
2095

	
3189

	
2019

	
3189

	
2171

	
3418

	
2030

	
3418

	
2182

	
3636

	
2182

	
9

	
25

	
3452

	
2258

	
3590

	
2193

	
3590

	
2345

	
3842

	
2214

	
3842

	
2355

	
4095

	
2377

	
11

	
34

	
3716

	
2377

	
3854

	
2312

	
3854

	
2464

	
4141

	
2334

	
4141

	
2486

	
4416

	
2496

	
13.6

	
42

	
3911

	
2453

	
4060

	
2388

	
4060

	
2551

	
4347

	
2421

	
4347

	
2572

	
4645

	
2605

	
7

	
7

	
15

	
2856

	
2019

	
2959

	
1943

	
2959

	
2095

	
3189

	
1954

	
3189

	
2095

	
3418

	
2106

	
9

	
25

	
3200

	
2160

	
3338

	
2095

	
3338

	
2247

	
3590

	
2106

	
3590

	
2258

	
3842

	
2269

	
11

	
34

	
3441

	
2247

	
3590

	
2182

	
3590

	
2345

	
3854

	
2225

	
3854

	
2377

	
4141

	
2388

	
13.6

	
42

	
3624

	
2323

	
3762

	
2258

	
3762

	
2410

	
4060

	
2301

	
4060

	
2453

	
4347

	
2475

	
8

	
7

	
15

	
2627

	
1932

	
2730

	
1867

	
2730

	
2008

	
2959

	
1867

	
2959

	
2019

	
3189

	
2019

	
9

	
25

	
2948

	
2041

	
3062

	
1986

	
3062

	
2138

	
3338

	
2008

	
3338

	
2160

	
3590

	
2171

	
11

	
34

	
3177

	
2138

	
3303

	
2073

	
3303

	
2225

	
3590

	
2106

	
3590

	
2247

	
3854

	
2269

	
13.6

	
42

	
3338

	
2182

	
3487

	
2138

	
3487

	
2290

	
3762

	
2171

	
3762

	
2323

	
4060

	
2345

	
9

	
7

	
15

	
2386

	
1856

	
2512

	
1780

	
2512

	
1932

	
2730

	
1791

	
2730

	
1943

	
2959

	
1943

	
9

	
25

	
2695

	
1943

	
2810

	
1878

	
2810

	
2030

	
3062

	
1910

	
3062

	
2062

	
3338

	
2073

	
11

	
34

	
2890

	
2008

	
3028

	
1954

	
3028

	
2095

	
3303

	
1986

	
3303

	
2138

	
3590

	
2160

	
13.6

	
42

	
3039

	
2041

	
3189

	
1997

	
3189

	
2149

	
3487

	
2041

	
3487

	
2182

	
3762

	
2225

	
10

	
7

	
15

	
2156

	
1780

	
2282

	
1704

	
2282

	
1856

	
2512

	
1715

	
2512

	
1867

	
2730

	
1867

	
9

	
25

	
2432

	
1845

	
2558

	
1780

	
2558

	
1932

	
2810

	
1802

	
2810

	
1954

	
3062

	
1965

	
11

	
34

	
2615

	
1878

	
2764

	
1834

	
2764

	
1965

	
3028

	
1867

	
3028

	
2008

	
3303

	
2041

	
13.6

	
42

	
2753

	
1910

	
2890

	
1867

	
2890

	
2008

	
3189

	
1921

	
3189

	
2160

	
3487

	
2095

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

 

  

17

  

Performance Data

  

	
3 Rows Cooling Capacity

	
(W)

	
Model

	
Entering

	
Water

	
Water Flow

	
Entering Air Temperature°C

	  	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
°C

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
004

	
5

	
9

	
11

	
3531

	
2795

	
3818

	
2817

	
3818

	
3034

	
4117

	
2839

	
4117

	
3045

	
12.3

	
20

	
4084

	
3089

	
4416

	
3121

	
4416

	
3350

	
4759

	
3154

	
4759

	
3382

	
15.6

	
29

	
4449

	
3274

	
4826

	
3328

	
4826

	
3567

	
5202

	
3361

	
5202

	
3600

	
19

	
38

	
4737

	
3415

	
5124

	
3469

	
5124

	
3709

	
5523

	
3513

	
5523

	
3752

	
6

	
9

	
11

	
2900

	
2697

	
3531

	
2708

	
3531

	
2936

	
3818

	
2719

	
3918

	
2936

	
12.3

	
20

	
3619

	
2936

	
4084

	
2969

	
4084

	
3198

	
4416

	
3013

	
4416

	
3230

	
15.6

	
29

	
4084

	
3100

	
4449

	
3154

	
4449

	
3393

	
4826

	
3198

	
4826

	
3426

	
19

	
38

	
4339

	
3208

	
4737

	
3274

	
4737

	
3513

	
5124

	
3328

	
5124

	
3567

	
7

	
9

	
11

	
2933

	
2578

	
3232

	
2610

	
3232

	
2817

	
3531

	
2621

	
3531

	
2839

	
12.3

	
20

	
3398

	
2784

	
3730

	
2817

	
3730

	
3045

	
4084

	
2860

	
4084

	
3089

	
15.6

	
29

	
3719

	
2904

	
4084

	
2969

	
4084

	
3198

	
4449

	
3024

	
4449

	
3252

	
19

	
38

	
3940

	
3013

	
4339

	
3078

	
4339

	
3306

	
4737

	
3132

	
4737

	
3361

	
8

	
9

	
11

	
2634

	
2480

	
2933

	
2501

	
2933

	
2719

	
3232

	
2512

	
3232

	
2730

	
12.3

	
20

	
3066

	
2632

	
3398

	
2686

	
3398

	
2893

	
3730

	
2719

	
3730

	
2936

	
15.6

	
29

	
3342

	
2730

	
3719

	
2795

	
3719

	
3024

	
4084

	
2860

	
4084

	
3078

	
19

	
38

	
3553

	
2795

	
3940

	
2882

	
3940

	
3100

	
4339

	
2947

	
4339

	
3176

	
9

	
9

	
11

	
2357

	
2317

	
2634

	
2404

	
2634

	
2588

	
2833

	
2414

	
2933

	
2632

	
12.3

	
20

	
2712

	
2469

	
3066

	
2534

	
3066

	
2741

	
3398

	
2567

	
3398

	
2784

	
15.6

	
29

	
2977

	
2545

	
3342

	
2621

	
3342

	
2839

	
3719

	
2686

	
3719

	
2893

	
19

	
38

	
3154

	
2578

	
3553

	
2686

	
3553

	
2893

	
3940

	
2762

	
3940

	
2969

	
10

	
9

	
11

	
2059

	
2023

	
2357

	
2317

	
2357

	
2317

	
2634

	
2327

	
2634

	
2545

	
12.3

	
20

	
2380

	
2317

	
2712

	
2382

	
2712

	
2588

	
3066

	
2425

	
3066

	
2643

	
15.6

	
29

	
2601

	
2338

	
2977

	
2425

	
2977

	
2643

	
3342

	
2501

	
3342

	
2708

	
19

	
38

	
2756

	
2360

	
3154

	
2469

	
3154

	
2686

	
3553

	
2567

	
3553

	
2773

	
005

	
5

	
11.5

	
17

	
4071

	
3384

	
4404

	
3405

	
4404

	
3670

	
4748

	
3432

	
4748

	
3681

	
13.8

	
24

	
4533

	
3624

	
4907

	
3667

	
4907

	
3938

	
5287

	
3700

	
5287

	
3964

	
17

	
34

	
4854

	
3785

	
5265

	
3844

	
5265

	
4119

	
5671

	
3887

	
5671

	
4163

	
21

	
45

	
5109

	
3913

	
5530

	
3967

	
5530

	
4253

	
5962

	
4021

	
5962

	
4296

	
6

	
11.5

	
17

	
3574

	
3243

	
4071

	
3270

	
4071

	
3535

	
4404

	
3287

	
4450

	
3546

	
13.8

	
24

	
4102

	
3446

	
4533

	
3489

	
4533

	
3754

	
4907

	
3532

	
4907

	
3792

	
17

	
34

	
4454

	
3585

	
4854

	
3644

	
4854

	
3919

	
5265

	
3698

	
5265

	
3963

	
21

	
45

	
4682

	
3681

	
5109

	
3751

	
5109

	
4027

	
5530

	
3811

	
5530

	
4086

	
7

	
11.5

	
17

	
3389

	
3102

	
3728

	
3140

	
3728

	
3394

	
4071

	
3156

	
4071

	
3416

	
13.8

	
24

	
3778

	
3268

	
4153

	
3311

	
4153

	
3581

	
4533

	
3360

	
4533

	
3619

	
17

	
34

	
4053

	
3369

	
4454

	
3439

	
4454

	
3704

	
4854

	
3499

	
4854

	
3763

	
21

	
45

	
4256

	
3454

	
4682

	
3530

	
4682

	
3795

	
5109

	
3595

	
5109

	
3859

	
8

	
11.5

	
17

	
3051

	
2972

	
3389

	
3005

	
3389

	
3264

	
3728

	
3021

	
3728

	
3281

	
13.8

	
24

	
3403

	
3084

	
3778

	
3143

	
3778

	
3397

	
4153

	
3192

	
4153

	
3446

	
17

	
34

	
3647

	
3164

	
4053

	
3240

	
4053

	
3499

	
4454

	
3310

	
4454

	
3563

	
21

	
45

	
3829

	
3212

	
4256

	
3309

	
4256

	
3568

	
4682

	
3384

	
4682

	
3643

	
9

	
11.5

	
17

	
2712

	
2811

	
3051

	
2875

	
3051

	
3124

	
3343

	
2897

	
3389

	
3156

	
13.8

	
24

	
3018

	
2906

	
3403

	
2965

	
3403

	
3219

	
3778

	
3014

	
3778

	
3268

	
17

	
34

	
3247

	
2953

	
3647

	
3034

	
3647

	
3288

	
4053

	
3110

	
4053

	
3353

	
21

	
45

	
3408

	
2975

	
3829

	
3082

	
3829

	
3331

	
4256

	
3174

	
4256

	
3411

	
10

	
11.5

	
17

	
2374

	
2465

	
2712

	
2756

	
2712

	
2817

	
3051

	
2777

	
3051

	
3037

	
13.8

	
24

	
2644

	
2722

	
3018

	
2792

	
3018

	
3035

	
3403

	
2852

	
3403

	
3095

	
17

	
34

	
2841

	
2760

	
3247

	
2819

	
3247

	
3072

	
3647

	
2905

	
3647

	
3148

	
21

	
45

	
2976

	
2782

	
3408

	
2851

	
3408

	
3093

	
3829

	
2953

	
3829

	
3190

 

Note:1. DB-Dry Bulb °C,WB-Wet Bulb °C。

2. Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

  

18

  

 

Performance Data

	
3 Rows Cooling Capacity

	
(W)

	
Model

	

Entering

	

Water

	

Water

	
Entering Air TemperatureoC

	  	

Water

	

Flow

	

Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	

Temp.

	
I/min

	

Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
9

	
11

	
4261

	
2947

	
4405

	
2849

	
4405

	
3045

	
4693

	
2860

	
4693

	
3056

	
4992

	
3045

	  	
5

	
12.3

	
20

	
4925

	
3274

	
5102

	
3176

	
5102

	
3404

	
5434

	
3198

	
5434

	
3415

	
5777

	
3426

	  	  	
15.6

	
29

	
5379

	
3502

	
5578

	
3404

	
5578

	
3633

	
5943

	
3426

	
5943

	
3654

	
6320

	
3665

	  	  	
19

	
38

	
5711

	
3654

	
5921

	
3556

	
5921

	
3796

	
6309

	
3589

	
6309

	
3817

	
6707

	
3850

	  	  	
9

	
11

	
3962

	
2839

	
4117

	
2730

	
4117

	
2947

	
4405

	
2721

	
4405

	
2947

	
4693

	
2947

	  	
6

	
12.3

	
20

	
4582

	
3132

	
4759

	
3034

	
4759

	
3252

	
5102

	
3056

	
5102

	
3274

	
5434

	
3285

	  	  	
15.6

	
29

	
5025

	
3328

	
5202

	
3241

	
5202

	
3448

	
5578

	
3263

	
5578

	
3491

	
5943

	
3502

	  	  	
19

	
38

	
5324

	
3469

	
5523

	
3372

	
5523

	
3600

	
5921

	
3415

	
5921

	
3643

	
6309

	
3665

	  	  	
9

	
11

	
3663

	
2730

	
3818

	
2632

	
3818

	
2839

	
4117

	
2643

	
4117

	
2849

	
4405

	
2849

	  	
7

	
12.3

	
20

	
4250

	
2980

	
4416

	
2893

	
4416

	
3111

	
4759

	
2926

	
4759

	
3121

	
5102

	
3154

	  	  	
15.6

	
29

	
4648

	
3165

	
4826

	
3078

	
4826

	
3285

	
5202

	
3111

	
5202

	
3328

	
5578

	
3350

	
004

	  	
19

	
38

	
4925

	
3274

	
5124

	
3198

	
5124

	
3415

	
5523

	
3241

	
5523

	
3448

	
5921

	
3491

	  	  	
9

	
11

	
3387

	
2632

	
3531

	
2534

	
3531

	
2730

	
3818

	
2545

	
3818

	
2741

	
4117

	
2741

	  	
8

	
12.3

	
20

	
3918

	
2849

	
4084

	
2762

	
4084

	
2958

	
4416

	
2784

	
4416

	
2981

	
4759

	
3013

	  	  	
15.6

	
29

	
4272

	
2980

	
4449

	
2904

	
4449

	
3121

	
4826

	
2947

	
4826

	
3165

	
5202

	
3187

	  	  	
19

	
38

	
4527

	
3089

	
4737

	
3013

	
4737

	
3230

	
5124

	
3056

	
5124

	
3274

	
5523

	
3317

	  	  	
9

	
11

	
3088

	
2534

	
3232

	
2425

	
3232

	
2643

	
3531

	
2436

	
3531

	
2643

	
3818

	
2643

	  	
9

	
12.3

	
20

	
3564

	
2697

	
3730

	
2621

	
3730

	
2817

	
4084

	
2643

	
4084

	
2849

	
4416

	
2871

	  	  	
15.6

	
29

	
3896

	
2817

	
4084

	
2730

	
4084

	
2947

	
4449

	
2784

	
4449

	
3002

	
4826

	
3024

	  	  	
19

	
38

	
4139

	
2893

	
4339

	
2840

	
4339

	
3034

	
4737

	
2882

	
4737

	
3089

	
5124

	
3132

	  	  	
9

	
11

	
2789

	
2436

	
2933

	
2338

	
2933

	
2545

	
3232

	
2349

	
3232

	
2545

	
3531

	
2556

	  	
10

	
12.3

	
20

	
3232

	
2556

	
3398

	
2469

	
3398

	
2686

	
3730

	
2512

	
3730

	
2708

	
4084

	
2730

	  	  	
15.6

	
29

	
3531

	
2643

	
3719

	
2567

	
3719

	
2773

	
4084

	
2632

	
4084

	
2817

	
4449

	
2871

	  	  	
19

	
38

	
3741

	
2708

	
3940

	
2643

	
3940

	
2849

	
4339

	
2708

	
4339

	
2904

	
4737

	
2958

	  	  	
11.5

	
17

	
4915

	
3562

	
5086

	
3449

	
5086

	
3687

	
5425

	
3465

	
5425

	
3703

	
5763

	
3698

	  	
5

	
13.8

	
24

	
5475

	
3846

	
5667

	
3732

	
5667

	
3991

	
6042

	
3754

	
6042

	
4008

	
6422

	
4018

	  	  	
17

	
34

	
5869

	
4044

	
6077

	
3930

	
6077

	
4195

	
6483

	
3963

	
6483

	
4216

	
6894

	
4238

	  	  	
21

	
45

	
6170

	
4189

	
6383

	
4070

	
6383

	
4339

	
6810

	
4107

	
6810

	
4366

	
7236

	
4399

	  	  	
11.5

	
17

	
4576

	
3427

	
4748

	
3308

	
4748

	
3557

	
5086

	
3315

	
5086

	
3562

	
5425

	
3562

	  	
6

	
13.8

	
24

	
5095

	
3678

	
5287

	
3559

	
5287

	
3819

	
5667

	
3592

	
5667

	
3846

	
6042

	
3856

	  	  	
17

	
34

	
5473

	
3849

	
5671

	
3741

	
5671

	
3990

	
6077

	
3774

	
6077

	
4033

	
6483

	
4049

	  	  	
21

	
45

	
5743

	
3978

	
5962

	
3865

	
5962

	
4129

	
6383

	
3913

	
6383

	
4167

	
6810

	
4199

	  	  	
11.5

	
17

	
4238

	
3292

	
4404

	
3173

	
4404

	
3421

	
4748

	
3195

	
4748

	
3432

	
5086

	
3438

	  	
7

	
13.8

	
24

	
4720

	
3500

	
4907

	
3397

	
4907

	
3651

	
5287

	
3430

	
5287

	
3667

	
5667

	
3694

	  	  	
17

	
34

	
5068

	
3655

	
5265

	
3558

	
5265

	
3801

	
5671

	
3590

	
5671

	
3844

	
6077

	
3871

	
005

	  	
21

	
45

	
5317

	
3757

	
5530

	
3665

	
5530

	
3919

	
5962

	
3713

	
5962

	
3957

	
6383

	
4000

	  	  	
11.5

	
17

	
3899

	
3162

	
4071

	
3048

	
4071

	
3286

	
4404

	
3065

	
4404

	
3302

	
4748

	
3302

	  	
8

	
13.8

	
24

	
4345

	
3338

	
4533

	
3235

	
4533

	
3479

	
4907

	
3268

	
4907

	
3501

	
5287

	
3532

	  	  	
17

	
34

	
4657

	
3456

	
4854

	
3364

	
4854

	
3606

	
5265

	
3412

	
5265

	
3655

	
5671

	
3688

	  	  	
21

	
45

	
4890

	
3546

	
5109

	
3454

	
5109

	
3758

	
5530

	
3509

	
5530

	
3751

	
5962

	
3800

	  	  	
11.5

	
17

	
3561

	
3037

	
3728

	
2913

	
3728

	
3167

	
4071

	
2935

	
4071

	
3172

	
4404

	
3178

	  	
9

	
13.8

	
24

	
3966

	
3165

	
4153

	
3073

	
4153

	
3311

	
4533

	
3100

	
4533

	
3343

	
4907

	
3376

	  	  	
17

	
34

	
4251

	
3261

	
4454

	
3203

	
4454

	
3418

	
4854

	
3223

	
4854

	
3466

	
5265

	
3504

	  	  	
21

	
45

	
4469

	
3325

	
4682

	
3255

	
4682

	
3493

	
5109

	
3309

	
5109

	
3546

	
5530

	
3595

	  	  	
11.5

	
17

	
3217

	
2913

	
3389

	
2794

	
3389

	
3042

	
3728

	
2821

	
3728

	
3053

	
4071

	
3070

	  	
10

	
13.8

	
24

	
3591

	
2998

	
3778

	
2906

	
3778

	
3149

	
4153

	
2949

	
4153

	
3181

	
4533

	
3208

	  	  	
17

	
34

	
3850

	
3061

	
4053

	
2975

	
4053

	
3218

	
4454

	
3045

	
4454

	
3272

	
4854

	
3320

	  	  	
21

	
45

	
4037

	
3115

	
4256

	
3039

	
4256

	
3271

	
4682

	
3109

	
4682

	
3336

	
5109

	
3401

 

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	 	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

19

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water Flow

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
13.5

	
25

	
5223

	
4065

	
5652

	
4087

	
5652

	
4406

	
6092

	
4120

	
6092

	
4417

	  	
5

	
17

	
35

	
5663

	
4263

	
6137

	
4318

	
6137

	
4638

	
6611

	
4351

	
6611

	
4660

	  	  	
20

	
42

	
5990

	
4406

	
6498

	
4473

	
6498

	
4792

	
6994

	
4528

	
6994

	
4847

	  	  	
24

	
52

	
6250

	
4528

	
6769

	
4583

	
6769

	
4924

	
7299

	
4649

	
7299

	
4968

	  	  	
13.5

	
25

	
4783

	
3878

	
5223

	
3922

	
5223

	
4230

	
5652

	
3944

	
5652

	
4252

	  	
6

	
17

	
35

	
5201

	
4054

	
5663

	
4109

	
5663

	
4417

	
6137

	
4153

	
6137

	
4461

	  	  	
20

	
42

	
5494

	
4175

	
5990

	
4241

	
5990

	
4561

	
6498

	
4307

	
6498

	
4616

	  	  	
24

	
52

	
5731

	
4263

	
6250

	
4340

	
6250

	
4660

	
6769

	
4406

	
6769

	
4726

	  	  	
13.5

	
25

	
4354

	
3712

	
4783

	
3756

	
4783

	
4065

	
5223

	
3779

	
5223

	
4087

	  	
7

	
17

	
35

	
4727

	
3845

	
5201

	
3900

	
5201

	
4219

	
5663

	
3955

	
5663

	
4252

	  	  	
20

	
42

	
4998

	
3933

	
5494

	
4010

	
5494

	
4318

	
5990

	
4076

	
5990

	
4384

	
006

	  	
24

	
52

	
5212

	
3999

	
5731

	
4087

	
5731

	
4395

	
6250

	
4164

	
6250

	
4473

	  	  	
13.5

	
25

	
3926

	
3547

	
4354

	
3591

	
4354

	
3900

	
4783

	
3613

	
4783

	
3922

	  	
8

	
17

	
35

	
4253

	
3624

	
4727

	
3690

	
4727

	
3999

	
5201

	
3756

	
5201

	
4054

	  	  	
20

	
42

	
4501

	
3690

	
4998

	
3779

	
4998

	
4076

	
5494

	
3856

	
5494

	
4153

	  	  	
24

	
52

	
4682

	
3723

	
5212

	
3834

	
5212

	
4142

	
5731

	
3922

	
5731

	
4219

	  	  	
13.5

	
25

	
3475

	
3382

	
3926

	
3426

	
3926

	
3745

	
4354

	
3459

	
4354

	
3767

	  	
9

	
17

	
35

	
3779

	
3426

	
4253

	
3481

	
4253

	
3790

	
4727

	
3547

	
4727

	
3845

	  	  	
20

	
42

	
4005

	
3448

	
4501

	
3536

	
4501

	
3834

	
4998

	
3624

	
4998

	
3911

	  	  	
24

	
52

	
4174

	
3459

	
4682

	
3569

	
4682

	
3867

	
5212

	
3679

	
5212

	
3955

	  	  	
13.5

	
25

	
3046

	
2974

	
3475

	
3272

	
3475

	
3393

	
3926

	
3305

	
3926

	
3613

	  	
10

	
17

	
35

	
3305

	
3206

	
3779

	
3283

	
3779

	
3569

	
4253

	
3360

	
4253

	
3635

	  	  	
20

	
42

	
3508

	
3261

	
4005

	
3294

	
4005

	
3591

	
4501

	
3393

	
4501

	
3679

	  	  	
24

	
52

	
3644

	
3283

	
4174

	
3316

	
4174

	
3591

	
4682

	
3426

	
4682

	
3701

	  	  	
16

	
22

	
6993

	
5713

	
7577

	
5768

	
7577

	
6216

	
8171

	
5801

	
8171

	
6238

	  	
5

	
23.5

	
35

	
7821

	
6128

	
8468

	
6205

	
8468

	
6653

	
9116

	
6260

	
9116

	
6707

	  	  	
29

	
50

	
8352

	
6369

	
9041

	
6467

	
9041

	
6926

	
9752

	
6555

	
9752

	
7002

	  	  	
35

	
65

	
8723

	
6511

	
9455

	
6642

	
9455

	
7101

	
10177

	
6729

	
10177

	
7188

	  	  	
16

	
22

	
6420

	
5473

	
6993

	
5528

	
6993

	
5976

	
7577

	
5560

	
7577

	
5997

	  	
6

	
23.5

	
35

	
7174

	
5790

	
7821

	
5877

	
7821

	
6336

	
8468

	
5954

	
8468

	
6402

	  	  	
29

	
50

	
7651

	
5997

	
8352

	
6107

	
8352

	
6555

	
9041

	
6216

	
9041

	
6642

	  	  	
35

	
65

	
8001

	
6128

	
8723

	
6260

	
8723

	
6707

	
9455

	
6369

	
9455

	
6806

	  	  	
16

	
22

	
5837

	
5233

	
6420

	
5287

	
6420

	
5735

	
6993

	
5331

	
6993

	
5757

	  	
7

	
23.5

	
35

	
6516

	
5473

	
7174

	
5582

	
7174

	
6008

	
7821

	
5670

	
7821

	
6085

	  	  	
29

	
50

	
6961

	
5626

	
7651

	
5757

	
7651

	
6183

	
8352

	
5866

	
8352

	
6292

	
008

	  	
35

	
65

	
7269

	
5735

	
8001

	
5866

	
8001

	
6303

	
8723

	
5997

	
8723

	
6423

	  	  	
16

	
22

	
5242

	
4992

	
5837

	
5047

	
5837

	
5484

	
6420

	
5091

	
6420

	
5528

	  	
8

	
23.5

	
35

	
5858

	
5156

	
6516

	
5255

	
6516

	
5692

	
7174

	
5364

	
7174

	
5779

	  	  	
29

	
50

	
6272

	
5244

	
6961

	
5397

	
6961

	
5823

	
7651

	
5517

	
7651

	
5932

	  	  	
35

	
65

	
6537

	
5309

	
7269

	
5473

	
7269

	
5899

	
8001

	
5626

	
8001

	
6030

	  	  	
16

	
22

	
4669

	
4763

	
5242

	
4829

	
5242

	
5255

	
5837

	
4883

	
5837

	
5298

	  	
9

	
23.5

	
35

	
5210

	
4829

	
5858

	
4938

	
5858

	
5364

	
6516

	
5058

	
6516

	
5462

	  	  	
29

	
50

	
5571

	
4861

	
6272

	
5036

	
6272

	
5440

	
6961

	
5167

	
6961

	
5582

	  	  	
35

	
65

	
5815

	
4894

	
6537

	
5080

	
6537

	
5484

	
7269

	
5244

	
7269

	
5637

	  	  	
16

	
22

	
4086

	
4206

	
4669

	
4599

	
4669

	
4807

	
5242

	
4654

	
5242

	
5080

	  	
10

	
23.5

	
35

	
4563

	
4381

	
5210

	
4621

	
5210

	
5036

	
5858

	
4752

	
5858

	
5145

	  	  	
29

	
50

	
4871

	
4457

	
5571

	
4665

	
5571

	
5047

	
6272

	
4818

	
6272

	
5211

	  	  	
35

	
65

	
5083

	
4468

	
5815

	
4676

	
5815

	
5058

	
6537

	
4861

	
6537

	
5233

 

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	 	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

20

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
13.5

	
25

	
6306

	
4274

	
6532

	
4142

	
6532

	
4428

	
6972

	
4164

	
6972

	
4450

	
7400

	
4450

	  	
5

	
17

	
35

	
6848

	
4528

	
7085

	
4395

	
7085

	
4693

	
7558

	
4417

	
7558

	
4715

	
8032

	
4726

	  	  	
20

	
42

	
7242

	
4704

	
7491

	
4572

	
7491

	
4880

	
7998

	
4616

	
7998

	
4902

	
8506

	
4935

	  	  	
24

	
52

	
7558

	
4847

	
7807

	
4704

	
7807

	
5012

	
8337

	
4748

	
8337

	
5045

	
8856

	
5078

	  	  	
13.5

	
25

	
5877

	
4109

	
6092

	
3977

	
6092

	
4263

	
6532

	
3999

	
6532

	
4274

	
6972

	
4274

	  	
6

	
17

	
35

	
6374

	
4329

	
6611

	
4186

	
6611

	
4495

	
7085

	
4230

	
7085

	
4528

	
7558

	
4539

	  	  	
20

	
42

	
6746

	
4484

	
6994

	
4351

	
6994

	
4649

	
7491

	
4395

	
7491

	
4693

	
7998

	
4715

	  	  	
24

	
52

	
7028

	
4605

	
7299

	
4473

	
7299

	
4781

	
7807

	
4528

	
7807

	
4814

	
8337

	
4858

	  	  	
13.5

	
25

	
5449

	
3944

	
5652

	
3801

	
5652

	
4098

	
6092

	
3834

	
6092

	
4109

	
6532

	
4120

	  	
7

	
17

	
35

	
5900

	
4120

	
6137

	
3999

	
6137

	
4296

	
6611

	
4032

	
6611

	
4318

	
7085

	
4340

	  	  	
20

	
42

	
6250

	
4252

	
6498

	
4142

	
6498

	
4428

	
6994

	
4175

	
6994

	
4473

	
7491

	
4506

	
006

	  	
24

	
52

	
6509

	
4351

	
6769

	
4241

	
6769

	
4539

	
7299

	
4296

	
7299

	
4583

	
7807

	
4627

	  	  	
13.5

	
25

	
4998

	
3779

	
5223

	
3646

	
5223

	
3933

	
5652

	
3668

	
5652

	
3955

	
6092

	
3955

	  	
8

	
17

	
35

	
5426

	
3922

	
5663

	
3801

	
5663

	
4098

	
6137

	
3845

	
6137

	
4120

	
6611

	
4153

	  	  	
20

	
42

	
5742

	
4032

	
5990

	
3922

	
5990

	
4197

	
6498

	
3977

	
6498

	
4252

	
6994

	
4296

	  	  	
24

	
52

	
5990

	
4109

	
6250

	
3999

	
6250

	
4395

	
6769

	
4065

	
6769

	
4340

	
7299

	
4395

	  	  	
13.5

	
25

	
4569

	
3624

	
4783

	
3481

	
4783

	
3779

	
5223

	
3514

	
5223

	
3790

	
5652

	
3801

	  	
9

	
17

	
35

	
4964

	
3723

	
5201

	
3613

	
5201

	
3900

	
5663

	
3646

	
5663

	
3933

	
6137

	
3977

	  	  	
20

	
42

	
5246

	
3801

	
5494

	
3767

	
5494

	
3988

	
5990

	
3756

	
5990

	
4032

	
6498

	
4087

	  	  	
24

	
52

	
5471

	
3856

	
5731

	
3767

	
5731

	
4054

	
6250

	
3834

	
6250

	
4109

	
6769

	
4164

	  	  	
13.5

	
25

	
4129

	
3470

	
4354

	
3327

	
4354

	
3624

	
4783

	
3371

	
4783

	
3646

	
5223

	
3668

	  	
10

	
17

	
35

	
4490

	
3525

	
4727

	
3426

	
4727

	
3701

	
5201

	
3470

	
5201

	
3745

	
5663

	
3779

	  	  	
20

	
42

	
4749

	
3569

	
4998

	
3470

	
4998

	
3756

	
5494

	
3547

	
5494

	
3823

	
5990

	
3867

	  	  	
24

	
52

	
4941

	
3613

	
5212

	
3525

	
5212

	
3790

	
5731

	
3602

	
5731

	
3867

	
6250

	
3944

	  	  	
16

	
22

	
8458

	
6052

	
8755

	
5844

	
8755

	
6260

	
9328

	
5866

	
9328

	
6281

	
9912

	
6281

	  	
5

	
23.5

	
35

	
9455

	
6522

	
9774

	
6325

	
9774

	
6762

	
10432

	
6369

	
10432

	
6784

	
11079

	
6806

	  	  	
29

	
50

	
10092

	
6806

	
10442

	
6620

	
10442

	
7068

	
11143

	
6686

	
11143

	
7112

	
11832

	
7155

	  	  	
35

	
65

	
10538

	
7002

	
10909

	
6828

	
10909

	
7265

	
11641

	
6904

	
11641

	
7330

	
12363

	
7374

	  	  	
16

	
22

	
7874

	
5790

	
8171

	
5604

	
8171

	
6019

	
8755

	
5626

	
8755

	
6030

	
9328

	
6052

	  	
6

	
23.5

	
35

	
8797

	
6216

	
9116

	
6019

	
9116

	
6456

	
9774

	
6085

	
9774

	
6489

	
10432

	
6533

	  	  	
29

	
50

	
9392

	
6467

	
9752

	
6292

	
9752

	
6718

	
10442

	
6369

	
10442

	
6784

	
11143

	
6828

	  	  	
35

	
65

	
9816

	
6631

	
10177

	
6467

	
10177

	
6904

	
10909

	
6555

	
10909

	
6970

	
11641

	
7024

	  	  	
16

	
22

	
7290

	
5560

	
7577

	
5375

	
7577

	
5779

	
8171

	
5397

	
8171

	
5801

	
8755

	
5826

	  	
7

	
23.5

	
35

	
8150

	
5910

	
8468

	
5735

	
8468

	
6150

	
9116

	
5790

	
9116

	
6205

	
9774

	
6238

	  	  	
29

	
50

	
8702

	
6128

	
9041

	
5954

	
9041

	
6380

	
9752

	
6052

	
9752

	
6456

	
10442

	
6500

	
008

	  	
35

	
65

	
9084

	
6260

	
9455

	
6107

	
9455

	
6533

	
10177

	
6216

	
10177

	
6620

	
10909

	
6686

	  	  	
16

	
22

	
6707

	
5331

	
6993

	
5145

	
6993

	
5550

	
7577

	
5167

	
7577

	
5582

	
8171

	
5593

	  	
8

	
23.5

	
35

	
7492

	
5604

	
7821

	
5440

	
7821

	
5844

	
8468

	
5517

	
8468

	
5910

	
9116

	
5954

	  	  	
29

	
50

	
8012

	
5779

	
8352

	
5626

	
8352

	
6030

	
9041

	
5713

	
9041

	
6128

	
9752

	
6183

	  	  	
35

	
65

	
8373

	
5899

	
8723

	
5757

	
8723

	
6150

	
9455

	
5855

	
9455

	
6249

	
10177

	
6336

	  	  	
16

	
22

	
6123

	
5440

	
6420

	
4916

	
6420

	
5320

	
6993

	
4960

	
6993

	
5353

	
7577

	
5375

	  	
9

	
23.5

	
35

	
6834

	
5309

	
7174

	
5145

	
7174

	
5550

	
7821

	
5222

	
7821

	
5615

	
8468

	
5681

	  	  	
29

	
50

	
7301

	
5440

	
7651

	
5298

	
7651

	
5692

	
8352

	
5397

	
8352

	
5779

	
9041

	
5866

	  	  	
35

	
65

	
7641

	
5517

	
8001

	
5386

	
8001

	
5779

	
8723

	
5517

	
8723

	
5899

	
9455

	
5997

	  	  	
16

	
22

	
5539

	
4894

	
5837

	
4697

	
5837

	
5113

	
6420

	
4741

	
6420

	
5134

	
6993

	
5156

	  	
10

	
23.5

	
35

	
6197

	
5003

	
6516

	
4850

	
6516

	
5244

	
7174

	
4938

	
7174

	
5320

	
7821

	
5386

	  	  	
29

	
50

	
6611

	
5080

	
6961

	
4960

	
6961

	
5331

	
7651

	
5069

	
7651

	
5451

	
8352

	
5539

	  	  	
35

	
65

	
6908

	
5134

	
7269

	
5014

	
7269

	
5397

	
8001

	
5156

	
8001

	
5528

	
8723

	
5637

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	
  

	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

21

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water Flow

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	  	  	
22

	
31

	
8484

	
7018

	
9189

	
7086

	
9189

	
7640

	
9905

	
7131

	
9905

	
7663

	  	
5

	
27

	
40

	
9080

	
7210

	
9829

	
7301

	
9829

	
7822

	
10577

	
7357

	
10577

	
7889

	  	  	
35

	
60

	
9438

	
7290

	
10219

	
7403

	
10219

	
7935

	
11022

	
7505

	
11022

	
8025

	  	  	
42

	
82

	
9699

	
7335

	
10512

	
7482

	
10512

	
7991

	
11315

	
7573

	
11315

	
8093

	  	  	
22

	
31

	
7789

	
6724

	
8484

	
6792

	
8484

	
7346

	
9189

	
6837

	
9189

	
7369

	  	
6

	
27

	
40

	
8332

	
6814

	
9080

	
6916

	
9080

	
7459

	
9829

	
7007

	
9829

	
7527

	  	  	
35

	
60

	
8646

	
6871

	
9438

	
6995

	
9438

	
7505

	
10219

	
7120

	
10219

	
7607

	  	  	
42

	
82

	
8896

	
6905

	
9688

	
7052

	
9688

	
7550

	
10512

	
7176

	
10512

	
7663

	  	  	
22

	
31

	
7073

	
6429

	
7778

	
6497

	
7778

	
7041

	
8473

	
6543

	
8473

	
7075

	  	
7

	
27

	
40

	
7561

	
6452

	
8321

	
6565

	
8321

	
7075

	
9069

	
6667

	
9069

	
7154

	  	  	
35

	
60

	
7854

	
6509

	
8636

	
6588

	
8636

	
7131

	
9427

	
6712

	
9427

	
7199

	
010

	  	
42

	
82

	
8061

	
6554

	
8874

	
6610

	
8874

	
7154

	
9677

	
6735

	
9677

	
7222

	  	  	
22

	
31

	
6357

	
6135

	
7073

	
6203

	
7073

	
6735

	
7778

	
6260

	
7778

	
6792

	  	
8

	
27

	
40

	
6802

	
6180

	
7561

	
6248

	
7561

	
6769

	
8332

	
6305

	
8332

	
6837

	  	  	
35

	
60

	
7084

	
6203

	
7865

	
6293

	
7865

	
6792

	
8646

	
6327

	
8646

	
6882

	  	  	
42

	
82

	
7269

	
6226

	
8082

	
6316

	
8082

	
6814

	
8896

	
6350

	
7811

	
6905

	  	  	
22

	
31

	
5164

	
5343

	
5804

	
5422

	
5804

	
5897

	
6466

	
5479

	
6466

	
5943

	  	
9

	
27

	
40

	
6054

	
5682

	
6802

	
5807

	
6802

	
6316

	
7572

	
5954

	
7572

	
6429

	  	  	
35

	
60

	
6292

	
5705

	
7084

	
5829

	
7084

	
6339

	
7865

	
5977

	
7865

	
6452

	  	  	
42

	
82

	
6466

	
5716

	
7269

	
5841

	
7269

	
6361

	
8082

	
5999

	
8082

	
6463

	  	  	
22

	
31

	
4958

	
4958

	
5663

	
5207

	
5663

	
5614

	
6357

	
5399

	
6357

	
5795

	  	
10

	
27

	
40

	
5294

	
4992

	
6043

	
5229

	
6043

	
5660

	
6791

	
5433

	
6791

	
5841

	  	  	
35

	
60

	
5511

	
5014

	
6303

	
5252

	
6303

	
5682

	
7095

	
5456

	
7095

	
5863

	  	  	
42

	
82

	
5641

	
5026

	
6466

	
5263

	
6466

	
5694

	
7269

	
5479

	
7269

	
5886

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	
  

	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

22

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water Flow

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
27

	
32

	
10492

	
8325

	
11367

	
8404

	
11367

	
9044

	
12232

	
8471

	
12232

	
9089

	  	
5

	
33

	
40

	
11135

	
8572

	
12065

	
8684

	
12065

	
9314

	
12985

	
8786

	
12985

	
9403

	  	  	
40

	
60

	
11600

	
8684

	
12564

	
8887

	
12564

	
9516

	
13528

	
8988

	
13528

	
9617

	  	  	
47

	
82

	
11932

	
8875

	
12941

	
9010

	
12941

	
9639

	
13927

	
9145

	
13927

	
9763

	  	  	
27

	
32

	
9617

	
7932

	
10492

	
8022

	
10492

	
8651

	
11367

	
8100

	
11367

	
8718

	  	
6

	
33

	
40

	
10204

	
8123

	
11135

	
8246

	
11135

	
8875

	
12065

	
8359

	
12065

	
8999

	  	  	
40

	
60

	
10625

	
8258

	
11600

	
8404

	
11600

	
9010

	
12564

	
8527

	
12564

	
9134

	  	  	
47

	
82

	
10935

	
8336

	
11932

	
8505

	
11932

	
9123

	
12941

	
8651

	
12941

	
9246

	  	  	
27

	
32

	
8742

	
7539

	
9617

	
7640

	
9617

	
8269

	
10492

	
7718

	
10492

	
8336

	  	
7

	
33

	
40

	
9273

	
7673

	
10204

	
7808

	
10204

	
8426

	
11135

	
7932

	
11135

	
8527

	  	  	
40

	
60

	
9661

	
7752

	
10625

	
7920

	
10625

	
8516

	
11600

	
8067

	
11600

	
8662

	
012

	  	
47

	
82

	
9949

	
7808

	
10935

	
7999

	
10935

	
8595

	
11932

	
8168

	
11932

	
8741

	  	  	
27

	
32

	
7855

	
7157

	
8742

	
7269

	
8742

	
7887

	
9617

	
7359

	
9617

	
7954

	  	
8

	
33

	
40

	
8354

	
7213

	
9273

	
7370

	
9273

	
7965

	
10204

	
7505

	
10204

	
8089

	  	  	
40

	
60

	
8697

	
7246

	
9661

	
7437

	
9661

	
8022

	
10625

	
7606

	
10625

	
8179

	  	  	
47

	
82

	
8952

	
7269

	
9949

	
7471

	
9949

	
8067

	
10935

	
7673

	
10935

	
8235

	  	  	
27

	
32

	
6980

	
6718

	
7855

	
6898

	
7855

	
7516

	
8742

	
6999

	
8742

	
7595

	  	
9

	
33

	
40

	
7423

	
6730

	
8354

	
6921

	
8354

	
7583

	
9273

	
7078

	
9273

	
7662

	  	  	
40

	
60

	
7733

	
6752

	
8697

	
6943

	
8697

	
7628

	
9661

	
7134

	
9661

	
7685

	  	  	
47

	
82

	
7966

	
6786

	
8952

	
6954

	
8952

	
7673

	
9949

	
7157

	
9949

	
7707

	  	  	
27

	
32

	
6116

	
6202

	
6980

	
6415

	
6980

	
6954

	
7855

	
6651

	
7855

	
7168

	  	
10

	
33

	
40

	
6492

	
6269

	
7423

	
6438

	
7423

	
6988

	
8354

	
6741

	
8354

	
7190

	  	  	
40

	
60

	
6769

	
6303

	
7733

	
6482

	
7733

	
7044

	
8697

	
6797

	
8697

	
7213

	  	  	
47

	
82

	
6958

	
6449

	
7966

	
6539

	
7966

	
7078

	
8952

	
6842

	
8952

	
7235

 

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	
  

	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

23

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
22

	
31

	
10263

	
7437

	
10621

	
7188

	
10621

	
7697

	
11315

	
7210

	
11315

	
7720

	
12020

	
7720

	  	
5

	
27

	
40

	
10979

	
7674

	
11348

	
7437

	
11348

	
7957

	
12107

	
7493

	
12107

	
7980

	
12856

	
8003

	  	  	
35

	
60

	
11413

	
7799

	
11803

	
7584

	
11803

	
8093

	
12595

	
7652

	
12595

	
8150

	
13376

	
8195

	  	  	
42

	
82

	
11803

	
7889

	
12129

	
7686

	
12129

	
8184

	
12942

	
7776

	
12942

	
8252

	
13745

	
8308

	  	  	
22

	
31

	
9558

	
7120

	
9916

	
6893

	
9916

	
7403

	
10621

	
6916

	
10621

	
7414

	
11315

	
7437

	  	
6

	
27

	
40

	
10219

	
7312

	
10588

	
7086

	
10588

	
7595

	
11348

	
7154

	
11348

	
7629

	
12118

	
7686

	  	  	
35

	
60

	
10621

	
7403

	
11022

	
7210

	
11022

	
7697

	
11803

	
7290

	
11803

	
7765

	
12595

	
7822

	  	  	
42

	
82

	
10914

	
7471

	
11304

	
7278

	
11304

	
7776

	
12129

	
7380

	
12129

	
7844

	
12942

	
7912

	  	  	
22

	
31

	
8842

	
6825

	
9189

	
6599

	
9189

	
7097

	
9905

	
6633

	
9905

	
7120

	
10610

	
7154

	  	
7

	
27

	
40

	
9460

	
6950

	
9829

	
6746

	
9829

	
7233

	
10577

	
6803

	
10577

	
7290

	
11337

	
7335

	  	  	
35

	
60

	
9829

	
7007

	
10209

	
6814

	
10209

	
7301

	
11011

	
6927

	
11011

	
7380

	
11792

	
7437

	
010

	  	
42

	
82

	
10078

	
7029

	
10480

	
6859

	
10480

	
7335

	
11283

	
6984

	
11283

	
7437

	
12096

	
7516

	  	  	
22

	
31

	
8136

	
6554

	
8484

	
6316

	
8484

	
6814

	
9189

	
6350

	
9189

	
6859

	
9905

	
6871

	  	
8

	
27

	
40

	
8701

	
6588

	
9080

	
6395

	
9080

	
6871

	
9829

	
6486

	
9829

	
6950

	
10577

	
7007

	  	  	
35

	
60

	
9059

	
6622

	
9438

	
6441

	
9438

	
6905

	
10219

	
6543

	
10219

	
7018

	
11022

	
7075

	  	  	
42

	
82

	
9308

	
6644

	
9688

	
6486

	
9688

	
6927

	
10501

	
6588

	
10501

	
7041

	
11304

	
7131

	  	  	
22

	
31

	
6780

	
6101

	
7106

	
5512

	
7106

	
5965

	
7746

	
5569

	
7746

	
6011

	
8386

	
6033

	  	
9

	
27

	
40

	
7941

	
6248

	
8332

	
6056

	
8332

	
6531

	
9080

	
6146

	
9080

	
6610

	
9840

	
6690

	  	  	
35

	
60

	
8256

	
6271

	
8646

	
6078

	
8646

	
6554

	
9438

	
6180

	
9438

	
6622

	
10219

	
6724

	  	  	
42

	
82

	
8494

	
6293

	
8896

	
6090

	
8896

	
6565

	
9699

	
6214

	
9699

	
6644

	
10512

	
6758

	  	  	
22

	
31

	
6726

	
5795

	
7084

	
5569

	
7084

	
6011

	
7789

	
5716

	
7789

	
6124

	
8484

	
6271

	  	
10

	
27

	
40

	
7193

	
5818

	
7561

	
5603

	
7561

	
6044

	
8321

	
5761

	
8321

	
6169

	
9069

	
6305

	  	  	
35

	
60

	
7486

	
5829

	
7876

	
5626

	
7876

	
6067

	
8657

	
5784

	
8657

	
6203

	
9449

	
6327

	  	  	
42

	
82

	
7681

	
5841

	
8082

	
5648

	
8082

	
6078

	
8896

	
5807

	
8896

	
6226

	
9699

	
6350

 

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	
  

	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

24

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
27

	
32

	
12664

	
8808

	
13107

	
8527

	
13107

	
9134

	
13982

	
8572

	
13982

	
9156

	
14857

	
9168

	  	
5

	
33

	
40

	
13450

	
9193

	
13916

	
8864

	
13916

	
9460

	
14846

	
9066

	
14846

	
9066

	
15777

	
9550

	  	  	
40

	
60

	
14004

	
9359

	
14492

	
9089

	
14492

	
9696

	
15467

	
9168

	
15467

	
9763

	
16431

	
9808

	  	  	
47

	
82

	
14414

	
9516

	
14924

	
9246

	
14924

	
9853

	
15910

	
9347

	
15910

	
9932

	
16907

	
9999

	  	  	
27

	
32

	
11788

	
8426

	
12232

	
8168

	
12232

	
8752

	
13107

	
8224

	
13107

	
8797

	
13982

	
8808

	  	
6

	
33

	
40

	
12520

	
8707

	
12985

	
8437

	
12985

	
9044

	
13916

	
8516

	
13916

	
9089

	
14846

	
9145

	  	  	
40

	
60

	
13040

	
8887

	
13528

	
8640

	
13528

	
9235

	
14492

	
8729

	
14492

	
9314

	
15467

	
9370

	  	  	
47

	
82

	
13428

	
9010

	
13927

	
8786

	
13927

	
9370

	
14924

	
8887

	
14924

	
9460

	
15910

	
9538

	  	  	
27

	
32

	
10924

	
8067

	
11367

	
7673

	
11367

	
8392

	
12232

	
7853

	
12232

	
8426

	
13107

	
8471

	  	
7

	
33

	
40

	
11600

	
8280

	
12065

	
8033

	
12065

	
8628

	
12985

	
8111

	
12985

	
8684

	
13916

	
8741

	  	  	
40

	
60

	
12076

	
8426

	
12564

	
8190

	
12564

	
8763

	
13528

	
8302

	
13528

	
8864

	
14492

	
8932

	
012

	  	
47

	
82

	
12431

	
8516

	
12941

	
8314

	
12941

	
8875

	
13927

	
8426

	
13927

	
8988

	
14924

	
9078

	  	  	
27

	
32

	
10049

	
7696

	
10492

	
7449

	
10492

	
8022

	
11367

	
7516

	
11367

	
8078

	
12232

	
8089

	  	
8

	
33

	
40

	
10669

	
7853

	
11135

	
7617

	
11135

	
8190

	
12065

	
7718

	
12065

	
8280

	
12985

	
8347

	  	  	
40

	
60

	
11113

	
7954

	
11600

	
7729

	
11600

	
8314

	
12564

	
7864

	
12564

	
8505

	
13927

	
8628

	  	  	
47

	
82

	
11445

	
8033

	
11932

	
7831

	
11932

	
8392

	
12941

	
7965

	
12941

	
8505

	
13927

	
8628

	  	  	
27

	
32

	
9174

	
7348

	
9617

	
7100

	
9617

	
7673

	
10492

	
7157

	
10492

	
7718

	
11367

	
7774

	  	
9

	
33

	
40

	
9739

	
7437

	
10204

	
7213

	
10204

	
7774

	
11135

	
7314

	
11135

	
7864

	
12065

	
7943

	  	  	
40

	
60

	
10138

	
7482

	
10625

	
7291

	
10625

	
7842

	
11600

	
7426

	
11600

	
7965

	
12564

	
8078

	  	  	
47

	
82

	
10448

	
7527

	
10935

	
7348

	
10935

	
7876

	
11932

	
7505

	
11932

	
8033

	
12941

	
8156

	  	  	
27

	
32

	
8298

	
6988

	
8742

	
6741

	
8742

	
7314

	
9617

	
6819

	
10725

	
7381

	
10492

	
7437

	  	
10

	
33

	
40

	
8808

	
6999

	
9273

	
6797

	
9273

	
7348

	
10204

	
6909

	
10204

	
7460

	
11135

	
7550

	  	  	
40

	
60

	
9174

	
7022

	
9661

	
6831

	
9661

	
7370

	
10625

	
6988

	
10625

	
7516

	
11600

	
7628

	  	  	
47

	
82

	
9440

	
7022

	
9949

	
6864

	
9949

	
7381

	
10935

	
7033

	
10935

	
7550

	
11932

	
7696

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	
  

	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

25

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water Flow

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
I/min

	
Pressure

	
17.0WB

	
18.0WB

	
19.0WB

	  	
Temp.

	  	
Drop

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
30

	
32

	
12017

	
10038

	
13023

	
10123

	
13023

	
10906

	
14017

	
10207

	
14017

	
10954

	  	
5

	
37

	
47

	
12480

	
10062

	
13520

	
10243

	
13520

	
10978

	
14547

	
10364

	
14547

	
11087

	  	  	
44

	
61

	
12808

	
10086

	
13870

	
10315

	
13870

	
11050

	
14931

	
10436

	
14931

	
11171

	  	  	
51

	
76

	
13023

	
10195

	
14118

	
10339

	
14118

	
11062

	
15191

	
10496

	
15191

	
11207

	  	  	
30

	
32

	
11012

	
9520

	
12017

	
9665

	
12017

	
10424

	
13023

	
9761

	
13023

	
10508

	  	
6

	
37

	
47

	
11407

	
9544

	
12447

	
9701

	
12447

	
10436

	
13497

	
9833

	
13497

	
10580

	  	  	
44

	
61

	
11724

	
9556

	
12797

	
9749

	
12797

	
10460

	
13858

	
9894

	
13858

	
10605

	  	  	
51

	
76

	
11938

	
9568

	
13023

	
9761

	
13023

	
10472

	
14118

	
9930

	
14118

	
10617

	  	  	
30

	
32

	
10018

	
8869

	
11023

	
9086

	
11023

	
9761

	
12029

	
9303

	
12029

	
9930

	  	
7

	
37

	
47

	
10391

	
8917

	
11430

	
9134

	
11430

	
9809

	
12469

	
9351

	
12469

	
9978

	  	  	
44

	
61

	
10662

	
8942

	
11724

	
9158

	
11724

	
9845

	
12797

	
9363

	
12797

	
10014

	
014

	  	
51

	
76

	
10865

	
8966

	
11938

	
9183

	
11938

	
9869

	
13023

	
9375

	
13023

	
10038

	  	  	
30

	
32

	
9002

	
8206

	
10018

	
8460

	
10018

	
9134

	
11023

	
8713

	
11023

	
9351

	  	
8

	
37

	
47

	
9363

	
8279

	
10391

	
8508

	
10391

	
9158

	
11430

	
8737

	
11430

	
9399

	  	  	
44

	
61

	
9600

	
8315

	
10662

	
8544

	
10662

	
9195

	
11724

	
8785

	
11724

	
9424

	  	  	
51

	
76

	
9770

	
8339

	
10854

	
8568

	
10854

	
9255

	
11927

	
8809

	
11927

	
9448

	  	  	
30

	
32

	
7997

	
7592

	
9002

	
7833

	
9002

	
8508

	
10018

	
8110

	
10018

	
8737

	  	
9

	
37

	
47

	
8324

	
7652

	
9363

	
7917

	
9363

	
8568

	
10391

	
8158

	
10391

	
8797

	  	  	
44

	
61

	
8539

	
7688

	
9600

	
7953

	
9600

	
8604

	
10662

	
8194

	
10662

	
8821

	  	  	
51

	
76

	
8697

	
7724

	
9770

	
7990

	
9770

	
8640

	
10865

	
8231

	
10865

	
8857

	  	  	
30

	
32

	
7003

	
6989

	
7997

	
7242

	
7997

	
7712

	
9002

	
7568

	
9002

	
8146

	  	
10

	
37

	
47

	
7285

	
7038

	
8324

	
7291

	
8324

	
7953

	
9374

	
7592

	
9374

	
8194

	  	  	
44

	
61

	
7477

	
7050

	
8539

	
7351

	
8539

	
7990

	
9600

	
7628

	
9600

	
8231

	  	  	
51

	
76

	
7601

	
7062

	
8708

	
7375

	
8708

	
8002

	
9781

	
7652

	
9781

	
8243

 

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	
  

	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

26

  

Performance Data

	
3 Rows Cooling Capacity

	
(W)

 

	
Model

	
Entering

	
Water

	
Water

	
Entering Air TemperatureoC

	  	
Water

	
Flow

	
Pressure

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	  	
Temp.

	
I/min

	
Drop

	
27.0DB

	
27.0DB

	
28.0DB

	
28.0DB

	
29.0DB

	
30.0DB

	  	
oC

	  	
kpa

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	
T.H

	
S.H

	  	  	
30

	
32

	
14513

	
10617

	
15022

	
10279

	
15022

	
11014

	
16016

	
10339

	
16016

	
11038

	
17021

	
11050

	  	
5

	
37

	
47

	
15078

	
10846

	
15598

	
10448

	
15586

	
11159

	
16637

	
10424

	
16637

	
11219

	
17687

	
11255

	  	  	
44

	
61

	
15462

	
10870

	
15993

	
10556

	
15993

	
11255

	
17077

	
10641

	
17077

	
11340

	
18139

	
11388

	  	  	
51

	
76

	
15733

	
10918

	
16287

	
10617

	
16287

	
11316

	
17360

	
10725

	
17360

	
11400

	
18455

	
11484

	  	  	
30

	
32

	
13508

	
10159

	
14005

	
9845

	
14005

	
10544

	
15010

	
9906

	
15010

	
10605

	
16016

	
10617

	  	
6

	
37

	
47

	
14005

	
10243

	
14525

	
9930

	
14525

	
10641

	
15564

	
10014

	
15564

	
10689

	
16603

	
10761

	  	  	
44

	
61

	
14389

	
10315

	
14920

	
10026

	
14920

	
10713

	
15982

	
10135

	
15982

	
10809

	
17066

	
10870

	  	  	
51

	
76

	
14660

	
10351

	
15202

	
10086

	
15202

	
10761

	
16287

	
10207

	
16287

	
10858

	
17360

	
10954

	  	  	
30

	
32

	
12526

	
9725

	
13034

	
9255

	
13034

	
10123

	
14017

	
9472

	
14017

	
10159

	
15022

	
10219

	  	
7

	
37

	
47

	
13000

	
9761

	
13520

	
9472

	
13520

	
10159

	
14547

	
9556

	
14547

	
10231

	
15586

	
10303

	  	  	
44

	
61

	
13328

	
9773

	
13858

	
9508

	
13858

	
10171

	
14920

	
9640

	
14920

	
10291

	
15993

	
10364

	
014

	  	
51

	
76

	
13576

	
9785

	
14129

	
9544

	
14129

	
10195

	
15202

	
9677

	
15202

	
10327

	
16298

	
10424

	  	  	
30

	
32

	
11520

	
9122

	
12029

	
8917

	
12029

	
9556

	
13023

	
9062

	
13023

	
9665

	
14017

	
9761

	  	
8

	
37

	
47

	
11961

	
9158

	
12480

	
8942

	
12480

	
9592

	
13520

	
9098

	
13520

	
9701

	
14547

	
9845

	  	  	
44

	
61

	
12266

	
9195

	
12797

	
8966

	
12797

	
9616

	
13858

	
9122

	
13858

	
9737

	
14920

	
9894

	  	  	
51

	
76

	
12492

	
9219

	
13023

	
8990

	
13023

	
9640

	
14118

	
9146

	
14118

	
9761

	
15191

	
9906

	  	  	
30

	
32

	
10515

	
8556

	
10459

	
8375

	
10459

	
8942

	
12029

	
8556

	
12029

	
9110

	
13023

	
9279

	  	
9

	
37

	
47

	
10922

	
8580

	
11441

	
8411

	
11441

	
8990

	
12480

	
8592

	
12480

	
9158

	
13531

	
9327

	  	  	
44

	
61

	
11193

	
8616

	
11724

	
8435

	
11724

	
9014

	
12808

	
8616

	
12808

	
9207

	
13870

	
9351

	  	  	
51

	
76

	
11407

	
8652

	
11938

	
8447

	
11938

	
9050

	
13023

	
8628

	
13023

	
9231

	
14129

	
9375

	  	  	
30

	
32

	
9510

	
7953

	
10018

	
7797

	
10018

	
8387

	
11012

	
7990

	
11012

	
8592

	
12017

	
8893

	  	
10

	
37

	
47

	
9883

	
8014

	
10402

	
7833

	
10402

	
8435

	
11441

	
8038

	
11441

	
8616

	
12492

	
8797

	  	  	
44

	
61

	
10131

	
8050

	
10673

	
7869

	
10673

	
8460

	
11735

	
8074

	
11735

	
8652

	
12808

	
8833

	  	  	
51

	
76

	
10312

	
8074

	
10865

	
7893

	
10865

	
8484

	
11950

	
8086

	
11950

	
8676

	
13034

	
8845

 

	
Note:1.

	
DB-Dry Bulb °C,WB-Wet Bulb °C。

	
  

	
2.

	
Data in the table for the unit is obtained at high speed, the data at medium or low speed can be obtained by the data in the table multiplying by the corresponding correction factor (see page P14)

  

  

27

  

 

Performance Data

1 Row Cooling Capacity

	
Model

	
Water Flow

	
Water

	
Entering Air TemperatureoC

	  	
I/min

	
Pressure

	
21.0DB

	  	  	
Drop

	
Entering Water TemperatureoC

	  	  	
kappa

	
40

	
45

	
50

	
55

	
60

	
65

	
70

	
75

	
80

	  	
4

	
5

	
1055

	
1403

	
1714

	
2036

	
2371

	
2695

	
3030

	
3365

	
7413

	
002

	
6

	
10

	
1118

	
1502

	
1838

	
2186

	
2534

	
2893

	
3240

	
3601

	
3961

	  	
8

	
17

	
1167

	
1552

	
1912

	
2272

	
2633

	
3005

	
3365

	
3738

	
4111

	  	
10

	
25

	
1204

	
1590

	
1950

	
2334

	
2707

	
3079

	
3452

	
3837

	
4222

	  	
4

	
8

	
1316

	
1740

	
2151

	
2562

	
2974

	
3397

	
3821

	
4232

	
4667

	
003

	
6

	
17

	
1399

	
1881

	
2316

	
2762

	
3209

	
3656

	
4114

	
4561

	
5019

	  	
8

	
29

	
1470

	
1940

	
2422

	
2880

	
3351

	
3841

	
4291

	
4761

	
5231

	  	
10

	
44

	
1505

	
1998

	
2468

	
2963

	
3445

	
3926

	
4408

	
4890

	
5383

	  	
4

	
12

	
1529

	
2038

	
2537

	
3024

	
3523

	
4021

	
4531

	
5030

	
5539

	
004

	
6

	
25

	
1631

	
2220

	
2741

	
3273

	
3817

	
4350

	
4893

	
5437

	
5981

	  	
8

	
41

	
1710

	
2277

	
2865

	
3421

	
3976

	
4543

	
5108

	
5686

	
6253

	  	
10

	
62

	
1767

	
2356

	
2922

	
3523

	
4100

	
4678

	
5267

	
5856

	
6434

	  	
4

	
12

	
1934

	
2551

	
3210

	
3752

	
4363

	
4975

	
5587

	
6205

	
6822

	
005

	
6

	
25

	
2067

	
2771

	
3417

	
4063

	
4727

	
5379

	
6043

	
6707

	
7376

	  	
8

	
41

	
2171

	
2858

	
3573

	
4254

	
4935

	
5628

	
6320

	
7018

	
7717

	  	
10

	
62

	
2240

	
2956

	
3654

	
4381

	
5091

	
5795

	
6516

	
7238

	
7948

	  	
8

	
5

	
2326

	
3047

	
3861

	
4454

	
5175

	
5896

	
6606

	
7339

	
8060

	
006

	
12

	
10

	
2489

	
3303

	
4070

	
4826

	
5606

	
6373

	
7152

	
7932

	
8722

	  	
16

	
16

	
2617

	
3419

	
4256

	
5059

	
5862

	
6676

	
7490

	
8304

	
9129

	  	
20

	
24

	
2698

	
3536

	
4361

	
5210

	
6048

	
6873

	
7722

	
8571

	
9409

	  	
8

	
10

	
2941

	
3884

	
4827

	
5758

	
6701

	
7655

	
8608

	
9563

	
10517

	
008

	
12

	
20

	
3135

	
4225

	
5225

	
6235

	
7258

	
8279

	
9313

	
10347

	
11380

	  	
16

	
35

	
3305

	
4361

	
5475

	
6530

	
7598

	
8666

	
9744

	
10823

	
11914

	  	
20

	
52

	
3407

	
4509

	
5588

	
6734

	
7825

	
8927

	
10040

	
11153

	
12277

	  	
10

	
15

	
3288

	
4351

	
5402

	
6453

	
7505

	
8579

	
9631

	
10716

	
11623

	
010

	
14

	
28

	
3509

	
4727

	
5856

	
6985

	
8136

	
9277

	
10439

	
11512

	
12730

	  	
18

	
44

	
3653

	
4837

	
6077

	
7251

	
8502

	
9619

	
10826

	
12010

	
13229

	  	
22

	
58

	
3764

	
4981

	
6199

	
7472

	
8679

	
9909

	
11070

	
12376

	
13616

	  	
8

	
17

	
3955

	
5300

	
6622

	
7968

	
9301

	
10646

	
12003

	
13359

	
14715

	
012

	
12

	
36

	
4184

	
5760

	
7197

	
8646

	
10094

	
11554

	
13014

	
14486

	
15957

	  	
16

	
60

	
4415

	
5932

	
7542

	
9059

	
10577

	
12106

	
13635

	
15176

	
16612

	  	
20

	
90

	
4576

	
6139

	
7680

	
9347

	
10911

	
12485

	
14072

	
15658

	
17257

	  	
10

	
25

	
4594

	
6164

	
7699

	
9188

	
10816

	
12258

	
13840

	
15386

	
16863

	
014

	
14

	
47

	
4815

	
6629

	
8292

	
9955

	
11630

	
13305

	
15003

	
16689

	
18387

	  	
18

	
68

	
5082

	
6838

	
8688

	
10444

	
12095

	
13956

	
15724

	
17445

	
19155

	  	
22

	
98

	
5268

	
7071

	
8850

	
10758

	
12560

	
14375

	
15038

	
18026

	
19900

 

The heating capacity in the table is based on fan running at high speed and entering air dry bulb temperature at 21oC. The heating capacity when fan runs at medium and low speed can be obtained through the value in the table multiplying by correction coefficient. (Please refer to P 28 for formula, and see page 14 for correction coefficient.)

 

When the entering air dry bulb temperature is not 21°C, the heating capacity correction method is as below:

 

	
If:  Fan Coil Type

Water Flow Rate

Entering Water Temperature

Entering Air Temperature

	
006

18  I/min

60oC

18oCDB

	

 

Explanation :Check the table and obtains:When the unit type is 006, The entering water temperature is 60 o C, water flow rate 18l/min, and entering air temperature is 21 o C,  the heating capacity is  8980W。

 

The heating capacity difference on each 1 o C difference is: 

 

8980/ (60-21) =230W/ o C

 

When the entering air temperature is 18 o C ,the heating capacity after correction is:230 × (60-18) = 9660W

  

28

  

 

Performance Data

2 Rows Cooling Capacity

	  	  	Water	
Entering Air Temperature°C

	  	  	
Pressure

	
21.0DB

	  	
Water Flow

	
Drop

	
Entering Water Temperature°C

	
Model

	
I/min

	
kpa

	
40

	
45

	
50

	
55

	
60

	
65

	
70

	
75

	
80

	
 

 

002

	
4.5

	
7

	
1499

	
1892

	
2294

	
2676

	
3079

	
3471

	
3874

	
4256

	
4658

	
6

	
10

	
1590

	
2012

	
2435

	
2857

	
3280

	
3703

	
4115

	
4538

	
4960

	
7.5

	
14

	
1660

	
2093

	
2535

	
2968

	
3421

	
3853

	
4286

	
4729

	
5161

	
9

	
19

	
1710

	
2163

	
2606

	
3069

	
3511

	
3964

	
4407

	
4870

	
5312

	
 

 

003

	
6

	
9

	
2173

	
2749

	
3315

	
3891

	
4468

	
5044

	
5610

	
6186

	
6752

	
8

	
16

	
2294

	
2891

	
3487

	
4104

	
4700

	
5306

	
5913

	
6509

	
7116

	
10

	
25

	
2375

	
3002

	
3618

	
4245

	
4862

	
5488

	
6125

	
6752

	
7368

	
12

	
34

	
2436

	
3083

	
3720

	
4356

	
4993

	
5640

	
6277

	
6914

	
7560

	
 

 

004

	
8

	
19

	
2844

	
3594

	
4354

	
5094

	
5844

	
6594

	
7344

	
8084

	
8844

	
11

	
26

	
3039

	
3828

	
4636

	
5425

	
6233

	
7032

	
7831

	
8629

	
9428

	
14

	
31

	
3156

	
4003

	
4841

	
5668

	
6506

	
7324

	
8464

	
8990

	
9827

	
17

	
37

	
3263

	
4120

	
4987

	
5844

	
6691

	
7558

	
8415

	
9272

	
10139

	
 

 

005

	
11

	
22

	
3474

	
4387

	
5309

	
6218

	
7141

	
8054

	
8967

	
9880

	
10798

	
13

	
30

	
3652

	
4614

	
5582

	
6534

	
7502

	
8464

	
9427

	
10384

	
11352

	
17

	
40

	
3775

	
4777

	
5780

	
6772

	
7769

	
8756

	
9905

	
10746

	
11753

	
20

	
55

	
3884

	
4901

	
5933

	
6950

	
7967

	
8989

	
10016

	
11033

	
12060

	
 

 

006

	
12

	
28

	
4080

	
5150

	
6230

	
7300

	
8390

	
9460

	
10530

	
11610

	
12680

	
15

	
40

	
4240

	
5370

	
6490

	
7600

	
8720

	
9840

	
10960

	
12070

	
13200

	
18

	
52

	
4370

	
5520

	
6680

	
7830

	
8980

	
10130

	
11280

	
12430

	
13600

	
21

	
65

	
4480

	
5650

	
6840

	
8010

	
9190

	
10360

	
11550

	
12720

	
13900

	
 

 

008

	
15

	
28

	
5305

	
6699

	
8092

	
9495

	
10889

	
12291

	
13676

	
15079

	
16472

	
21.5

	
38

	
5602

	
7076

	
8227

	
10025

	
11500

	
12975

	
14449

	
15924

	
17398

	
27

	
50

	
5799

	
7337

	
8866

	
10394

	
11923

	
13451

	
14989

	
16508

	
18037

	
32

	
65

	
5961

	
7526

	
9090

	
10664

	
12237

	
13802

	
15375

	
16940

	
18513

	
 

 

010

	
19

	
28

	
6663

	
8414

	
9594

	
11936

	
13687

	
15448

	
17190

	
18951

	
20702

	
24

	
38

	
6729

	
8509

	
9890

	
12060

	
13830

	
15601

	
17381

	
19151

	
20921

	
31

	
58

	
6796

	
8595

	
10385

	
12174

	
13973

	
15762

	
17561

	
19341

	
21131

	
37

	
78

	
6863

	
8662

	
10470

	
12279

	
14087

	
15896

	
17704

	
19513

	
21321

	
 

 

012

	
24

	
14

	
8126

	
10271

	
12406

	
14541

	
16667

	
18812

	
20947

	
23082

	
25228

	
30

	
22

	
8403

	
10607

	
12821

	
15036

	
17250

	
19454

	
21669

	
23883

	
26088

	
36

	
33

	
8610

	
10874

	
13138

	
15401

	
17675

	
19939

	
22203

	
24476

	
26740

	
42

	
45

	
8768

	
11082

	
13395

	
15708

	
18011

	
20324

	
22628

	
24970

	
27244

	
 

 

014

	
27

	
18

	
9240

	
11680

	
14110

	
16540

	
18960

	
21400

	
23830

	
26260

	
28710

	
33

	
27

	
9350

	
11800

	
14260

	
16730

	
19190

	
21640

	
24110

	
26570

	
29020

	
39

	
39

	
9430

	
11910

	
14390

	
16870

	
19370

	
21850

	
24330

	
26820

	
29300

	
45

	
52

	
9600

	
12140

	
14670

	
17210

	
19730

	
22270

	
24790

	
27360

	
29850

The heating capacity in the table is based on fan running at high speed and entering air dry bulb temperature at 21°C. The heating capacity when fan runs at medium and low speed can be obtained through the value in the table multiplying by correction coefficient. (Please refer to P 28 for formula, and see page 14 for correction coefficient.)

	

	  

 

  

30

  

 

Performance Data

 

3 Row Heating Capacity

	  	  	
Water

	

Entering Air Temperature°C

	  	
 

	
Pressure

	
21.0DB

	
 

	

Water Flow

	
Drop

	

Entering Air Temperature°C

	Model	I/min	kpa	
40

	
45

	
50

	
55

	
60

	
65

	
70

	
75

	  
	
 

 

002

	
5

	
10

	
1785

	
2252

	
2731

	
3186

	
3666

	
4133

	
4612

	
5067

	
5546

	
6.6

	
14

	
1893

	
2396

	
2899

	
3402

	
3905

	
4408

	
4899

	
5403

	
5906

	
8.4

	
19

	
1977

	
2492

	
3019

	
3534

	
4073

	
4588

	
5103

	
5630

	
6145

	
10

	
25

	
2036

	
2576

	
3103

	
3654

	
4181

	
4720

	
5247

	
5798

	
6325

	
 

 

003

	
7

	
15

	
2466

	
3120

	
3762

	
4416

	
5070

	
5723

	
6366

	
7019

	
7662

	
9

	
25

	
2604

	
3280

	
3957

	
4657

	
5333

	
6022

	
6710

	
7386

	
8075

	
11

	
34

	
2695

	
3406

	
4106

	
4817

	
5517

	
6228

	
6951

	
7662

	
8361

	
13.6

	
42

	
2764

	
3498

	
4221

	
4943

	
5666

	
6400

	
7123

	
7845

	
8579

	
 

 

004

	
9

	
11

	
3232

	
4084

	
4947

	
5788

	
6641

	
7493

	
8345

	
9186

	
10049

	
12.3

	
20

	
3453

	
4350

	
5268

	
6165

	
7083

	
7991

	
8898

	
9806

	
10714

	
15.6

	
29

	
3586

	
4549

	
5501

	
6441

	
7393

	
8323

	
9618

	
10215

	
11167

	
19

	
38

	
3708

	
4682

	
5667

	
6641

	
7604

	
8589

	
9562

	
10536

	
11521

	
 

 

005

	
11.5

	
17

	
3643

	
4601

	
5569

	
6522

	
7490

	
8447

	
9405

	
10363

	
11326

	
13.8

	
24

	
3830

	
4840

	
5855

	
6854

	
7868

	
8878

	
9888

	
10892

	
11907

	
17

	
34

	
3960

	
5011

	
6062

	
7103

	
8149

	
9184

	
10389

	
11271

	
12327

	
21

	
45

	
4074

	
5141

	
6223

	
7290

	
8357

	
9428

	
10506

	
11572

	
12649

	
 

 

006

	
13.5

	
25

	
4603

	
5810

	
7028

	
8235

	
9465

	
10672

	
11879

	
13097

	
14304

	
17

	
35

	
4783

	
6058

	
7321

	
8574

	
9837

	
11101

	
12364

	
13616

	
14891

	
20

	
42

	
4930

	
6227

	
7536

	
8833

	
10130

	
11428

	
12725

	
14022

	
15342

	
24

	
52

	
5054

	
6374

	
7716

	
9036

	
10367

	
11687

	
13030

	
14350

	
15681

	
 

 

008

	
16

	
22

	
6261

	
7906

	
9551

	
11206

	
12851

	
14507

	
16141

	
17796

	
19441

	
23.5

	
35

	
6611

	
8352

	
9710

	
11832

	
13573

	
15313

	
17053

	
18794

	
20534

	
29

	
50

	
6845

	
8659

	
10463

	
12267

	
14071

	
15876

	
17690

	
19484

	
21288

	
35

	
65

	
7036

	
8882

	
10729

	
12586

	
14443

	
16289

	
18146

	
19993

	
21850

	
 

 

010

	
22

	
31

	
7461

	
9422

	
10744

	
13366

	
15327

	
17299

	
19249

	
21221

	
23182

	
27

	
40

	
7536

	
9529

	
11074

	
13504

	
15487

	
17469

	
19462

	
21445

	
23427

	
35

	
60

	
7610

	
9625

	
11628

	
13632

	
15647

	
17650

	
19665

	
21658

	
23662

	
42

	
82

	
7685

	
9699

	
11724

	
13749

	
15775

	
17800

	
19825

	
21850

	
23875

	
 

 

012

	
27

	
32

	
8782

	
11101

	
13408

	
15716

	
18013

	
20331

	
22639

	
24947

	
27265

	
33

	
40

	
9081

	
11464

	
13857

	
16250

	
18643

	
21026

	
23419

	
25812

	
28195

	
40

	
60

	
9306

	
11752

	
14199

	
16645

	
19103

	
21549

	
23996

	
26453

	
28900

	
47

	
82

	
9477

	
11977

	
14477

	
16977

	
19466

	
21966

	
24455

	
26987

	
29445

	
 

 

014

	
30

	
32

	
10253

	
12961

	
15657

	
18354

	
21039

	
23747

	
26443

	
29140

	
31858

	
37

	
47

	
10375

	
13094

	
15824

	
18565

	
21294

	
24013

	
26754

	
29484

	
32202

	
44

	
61

	
10464

	
13216

	
15968

	
18720

	
21494

	
24246

	
26998

	
29761

	
32513

	
51

	
76

	
10653

	
13471

	
16279

	
19097

	
21893

	
24712

	
27508

	
30360

	
33123

 

The heating capacity in the table is based on fan running at high speed and entering air dry bulb temperature at 21°C. The heating capacity when fan runs at medium and low speed can be obtained through the value in the table multiplying by correction coefficient. (Please refer to P 28 for formula, and see page 14 for correction coefficient.)

 

Noise

Test Techincal

 

Test environment is the anechoic chamber with the background noise is less than 20dB (A).

	
  

	
Vertical Unit      

	

	Horizontal Unit      	

 

  

31

  

  

Selection Method

Technical Specification

Selection of the cooling unit is to match the design sensible heat load with the unit

Sensible heat load. Under most circumstances, the coil has enough potential heat capacity to meet the design requirement. If using the outdoor air, the corresponding load correction and formula is as below:

	
Water Temperature

	 	
Total Heat Capacity (W) x0.86 

	 	
Air Temperature

	 	
 Sensible Heat Capacity (W) ×0.86

	Rise (°C) =	 	
60×Water Flow rate (l/min)

	 	Rise (°CDB) =	 	
0.29×Air Flow Rate (m3/h)

 

Selection Example:

 

	
  

	
●

	
When the fan runs at high speed, select (Cooling)

The Fan Coil is selected when it runs at high speed, to make sure it is the smallest type of unit.

1. Confirm the operation requirement (Refer to Selection Guide)

	 	
If:    

	
Indoor sensible heat cooling load o2330W,          Indoor Total heat cooling load ⋯3140W

	
 

	
Inlet Air Temperatureooo27°CDB,19.5°CWB

	
 

	

Inlet Water Temperature ooo 7°C                        Air Flow Rate oooooo 660m3/h

 

2. Confirm the Unit specification, water volume, and pressure drop

Under the condition of inlet air temperature 19.5oWB, and inlet water temperature 7o, refer to the cooling capacity data table to obtain the unit sensible heat capacity, that equal to or more than required value. Get the sensible heat cooling load is 2510W, total heat cooling load is 3224W. Then refer to the left front line, and the model of unit should be 004 type. The water flow rate is 8 l/min, and the pressure drop on the water side is 19kPa. When the fan runs at other speed, the cooling capacity can be obtained by speed correction table of VS. Please refer to the cooling capacity table for VS value.

     

	
  

	
●

	
When the fan runs at medium speed, select (Cooling)

The Fan always runs at medium or low speed, so type of unit can be selected at medium speed under average cooling load. It is allowed to run at high speed at unusual condition or peak load to increase the unit capacity:

1. Confirm the operation requirement (Refer to Selection Gu ide)

If: Average Indoor S.H. cooling load --1480W,    Average Indoor T. H. cooling load---1980 W

Average Inlet Air Temperature ------- 27°CDB,19.5°CWB

Average Inlet Water Temperature ---- 7°C          Average Air Flow Rate ---------- 340m3/h

2. Confirm the Unit specification.

According to the technical specification, the air flow rate at medium speed is 430 m3/h, which is closest to the required air flow rate from the example. So the model of unit should be 003 Type.

3. Get the VS value in the cooling capacity table from the cooling speed correction table.

The unit of 003 Type, Sensible Heat multiplies 0.84, total heat multiplies 0.86.

4. Confirm the correction sensible heat and total heat, through average design load divided by correction:

	  	
1480

	
  = 1762 (Corrected S.H Load)

	
1980

	
  = 2302 (Corrected T.H Load)

	  	
0.84

	
0.86

 

5. Confirm the Unit specification, water volume, and pressure drop

Replace the given load with the above corrected load. Under the condition of 27°CDB,   19.5°CWB, and inlet water temperature 7o, refer to the cooling capacity data table to obtain the unit sensible heat capacity, that equal to or more than required value. Get the sensible heat cooling load is 1944W, total heat cooling load is 2517W. The model of unit should be 004 type. The water flow rate is 6 l/min, and the pressure drop on the water side is 9kPa.

	
  

	
●

	
heating (Use the unit selected according to cooling capacity)

1. Confirm the Operation Specification

If: the unit selected according to cooling capacity--- 004 Type           Water Flow Rate----14 l/min

Indoor Heating Load------ 5820W                                                     Entering Air Temperature--21°CDB

2.     Confirmed the required water temperature

Check the Heating Specification at high speed of fan, the unit of 004 type is 8 l/min with heating load of 5844W and inlet water temperature 60°C.

  

32

  

 

Unit Dimension

Technical Specification

Chilled Water Fan Coil Unit

	
Model

	
Dimension

	  	
A

	
B

	
C

	
D

	
E

	
F

	
H

	
J

	
K

	
M

	
N

	
002

	
690

	
770

	
550

	
520

	
35

	
480

	
550

	
72

	
400

	
10

	
6

	  	  	  	  	  	  	  	  	  	  	  	  
	
003

	
770

	
890

	
630

	
600

	
75

	
480

	
630

	
112

	
400

	
12

	
6

	  	  	  	  	  	  	  	  	  	  	  	  
	
004

	
890

	
970

	
750

	
720

	
75

	
600

	
750

	
72

	
600

	
14

	
6

	  	  	  	  	  	  	  	  	  	  	  	  
	
005

	
970

	
1090

	
830

	
800

	
55

	
720

	
830

	
112

	
600

	
16

	
8

	  	  	  	  	  	  	  	  	  	  	  	  
	
006

	
1090

	
1410

	
950

	
920

	
55

	
840

	
950

	
72

	
800

	
18

	
8

	  	  	  	  	  	  	  	  	  	  	  	  
	
008

	
1410

	
1530

	
1270

	
1240

	
95

	
1080

	
1270

	
32

	
1200

	
26

	
10

	  	  	  	  	  	  	  	  	  	  	  	  
	
010

	
1530

	
1770

	
1390

	
1360

	
95

	
1200

	
1390

	
92

	
1200

	
28

	
10

	  	  	  	  	  	  	  	  	  	  	  	  
	
012

	
1770

	
2010

	
1630

	
1600

	
95

	
1440

	
1630

	
112

	
1400

	
32

	
12

	  	  	  	  	  	  	  	  	  	  	  	  
	
014

	
2010

	
2250

	
1870

	
1840

	
95

	
1680

	
1870

	
132

	
1600

	
36

	
14

Note: B is the Long Drain Pan Dimension

   

  

33

  

   

Unit Dimension

Technical Specification

Combined Rows Fan Coil Unit

	
Model

	
Dimension

	  	
A

	
B

	
C

	
D

	
E

	
F

	
H

	
J

	
K

	
M

	
N

	
002

	
690

	
770

	
550

	
520

	
35

	
480

	
550

	
72

	
400

	
10

	
6

	  	  	  	  	  	  	  	  	  	  	  	  
	
003

	
770

	
890

	
630

	
600

	
75

	
480

	
630

	
112

	
400

	
12

	
6

	  	  	  	  	  	  	  	  	  	  	  	  
	
004

	
890

	
970

	
750

	
720

	
75

	
600

	
750

	
72

	
600

	
14

	
6

	  	  	  	  	  	  	  	  	  	  	  	  
	
005

	
970

	
1090

	
830

	
800

	
55

	
720

	
830

	
112

	
600

	
16

	
8

	  	  	  	  	  	  	  	  	  	  	  	  
	
006

	
1090

	
1410

	
950

	
920

	
55

	
840

	
950

	
72

	
800

	
18

	
8

	  	  	  	  	  	  	  	  	  	  	  	  
	
008

	
1410

	
1530

	
1270

	
1240

	
95

	
1080

	
1270

	
32

	
1200

	
26

	
10

	  	  	  	  	  	  	  	  	  	  	  	  
	
010

	
1530

	
1770

	
1390

	
1360

	
95

	
1200

	
1390

	
92

	
1200

	
28

	
10

	  	  	  	  	  	  	  	  	  	  	  	  
	
012

	
1170

	
2010

	
1630

	
1600

	
95

	
1440

	
1630

	
112

	
1400

	
32

	
12

	  	  	  	  	  	  	  	  	  	  	  	  
	
014

	
2010

	
2250

	
1870

	
1840

	
95

	
1680

	
1870

	
132

	
1600

	
36

	
14

Note: B is the Long Drain Pan Dimension

 

  

34

  

 

Unit Dimension

Technical Specification

42CE

Return Air Box

	  	
Dimension

	
Part No.

	
A

	
B

	
C

	
D

	
E

	
F

	
Used

in Model

	
42CE402900

	
554

	
47

	
2

	
400

	
524

	
520

	
42CE002

	 	 	 	 	 	 	 	 
	
42CE403900

	
634

	
87

	
2

	
400

	
604

	
600

	
42CE003

	 	 	 	 	 	 	 	 
	
42CE404900

	
754

	
47

	
3

	
600

	
724

	
720

	
42CE004

	 	 	 	 	 	 	 	 
	
42CE405900

	
834

	
87

	
3

	
600

	
804

	
800

	
42CE005

	 	 	 	 	 	 	 	 
	
42CE406900

	
954

	
47

	
4

	
800

	
924

	
920

	
42CE006

	 	 	 	 	 	 	 	 
	
42CE408900

	
1274

	
107

	
5

	
1000

	
1244

	
1240

	
42CE008

	 	 	 	 	 	 	 	 
	
42CE410900

	
1394

	
67

	
6

	
1200

	
1364

	
1360

	
42CE010

	 	 	 	 	 	 	 	 
	
42CE412900

	
1634

	
87

	
7

	
1400

	
1604

	
1600

	
42CE012

	 	 	 	 	 	 	 	 
	
42CE414900

	
1874

	
107

	
8

	
1600

	
1844

	
1840

	
42CE014

	
Note:   

	
1.

	
Return air cap can be intake air from the bottom or the back.

	
  

	
2.

	
It can be modified as requirement of the Bottom or the Back intake air in the field.

	
  

	
3.

	
The Return air cap doesn’t include the filter; please add a filter in the return air duct on installation.

 

 

  

35

  

 

Fan Performance

Technical Specification

    

	
2/ (2+1) Row Standard Unit

 

	
3/ (3+1) Row Standard Unit

 

	  	  
	
2/ (2+1) Row Static Unit

 

	
3/ (3+1) Row Static Unit

 

	  	  
	
2/ (2+1) Row High Static Unit

 

	
3/ (3+1) Row High Static Unit

 

 

  

36

  

  

Wiring Diagram

Technical Specification

    

  

Power Supply:220V-1Ph-50Hz

	
Model 42CE

	
002

	
003

	
004

	
005

	
006

	
008

	
010

	
012

	
014

	  	
2 Rows Standard Unit

	
33

	
46

	
60

	
82

	
94

	
134

	  	  	  
	
Unit

	
2 Rows 30Pa Unit

	
40

	
54

	
72

	
92

	
112

	
156

	  	  	  
	
Input

	
2 Rows 50Pa Unit

	
49

	
65

	
84

	
105

	
122

	
184

	  	  	  
	
Power

	
3 Rows Standard Unit

	
32

	
46

	
58

	
76

	
91

	
130

	
150

	
180

	
208

	
(W)

	
3 Rows 30Pa Unit

	
41

	
52

	
65

	
87

	
106

	
150

	
172

	
210

	
250

	  	
3 Rows 50Pa Unit

	
48

	
63

	
82

	
100

	
118

	
174

	
205

	
236

	
290

	  	
2 Rows Standard Unit

	
0.15

	
0.22

	
0.27

	
0.37

	
0.43

	
0.61

	  	  	  
	  	
2 Rows 30Pa Unit

	
0.18

	
0.25

	
0.33

	
0.42

	
0.51

	
0.71

	  	  	  
	
Current(A)

	
2 Rows 50Pa Unit

	
0.22

	
0.30

	
0.38

	
0.48

	
0.55

	
0.84

	  	  	  
	  	
3 Rows Standard Unit

	
0.15

	
0.22

	
0.26

	
0.35

	
0.41

	
0.59

	
0.68

	
0.82

	
0.95

	  	
3 Rows 30Pa Unit

	
0.19

	
0.24

	
0.30

	
0.40

	
0.48

	
0.68

	
0.78

	
0.96

	
1.14

	  	
3 Rows 50Pa Unit

	
0.22

	
0.29

	
0.37

	
0.46

	
0.54

	
0.79

	
0.93

	
1.07

	
1.32

	 	
Note:

	
The data of Combines Rows (2+1) equal to the 2 Rows Unit

The data of Combines Rows (3+1) equal to the 3 Rows Unit

  

  

37

  

  

Installation and Maintenance Instructions

	
1.

	
Application Scope

This series of unit applies to 50Hz/220V AC Power, the ambient temperature of -30o~+65o,while no more than 4000 meters above sea level

	
2.

	
Unit Installation

For the horizontal unit, the upper level of it should be kept flat, while for the vertical unit, the level of it should be adjusted by adjusting bolts. For the Ceiling installed unit, the repair checkpoints should be kept for repair use. If the building is still under construction, the checkpoints should be protected against trash invasion.

	
3.

	
Pipelines Disposition and Anti-sweat Measurement

 When installing the inlet and outlet pipe, the pipe end must be tight with pipe pliers, and both ends should be installed with valves. The highest point of the pipe should be installed with air deflation valve, while the lowest point should be installed with water outlet valve. The condensation water pipe requires a certain slope in order to successfully discharge condensate. On valves, inlet and outlet pipe, and condensation pipes, the strict measures should be taken to preserve heat and anti- sweat.

	
4.

	
Electrical Wiring

Connect the wiring in strict accordance with the wiring diagram of the unit. Note: The power wiring should be connected with the yellow wiring in the diagram.

The grounding bolt in the terminal box of the unit is available to be connected with grounding system during installation.

Do not install two or more units parallel in the same switch; otherwise it will lead to loop current during the normal operation of the unit, even the damage to the motor.

A fully enclosed ball bearing is used for motor bearing, unnecessarily adding the lubricating oil.

	
5.

	
Water Supply Requirement

It is prohibited to supply steam or hot water above 100o. For 2 row fan coil unit, the temperature of heat water should not exceed 65o. If the temperature is over 65o, the water supply should be dematerialized water; otherwise it will lead to corrosion of the pipe, and then affect the heat transfer.

The maximum water flow rate should not surpass the sample range, and the water should be clean.

	
6.

	
Anti-freezing Measures

When the environment temperature is below 0o, stop the operation of the circulation pump, the water in the pipes will freeze, which will lead to the cracking of the coil of units and pipes. So the following measures should be taken:

	
1)

	
Operate the circulation pump continuously.

	
2)

	
Input the anti-freezing solution with appropriate concentration.

	
7.

	
Operation and Maintenance

Before operation, open the air inflation valve of the unit to release all air in the pipe, and then close it when the water flows out.

Clean the filter once a month, and clean the coil according to the fouling regularly, which will ensure the heat transfer efficiency.

 

  

38

  

	
Carrier, as a world-class manufacturer, has the responsibility to protect environmental

resources in the following six aspects:

	
Welcome the visit to:

	 	
www .carrier .com.cn

 

  

   

Carrier China Sales

Shanghai (86-21) 2306 3000        Beijing (86-10) 6583 2008     Guangzhou (86-20) 3820 1818

Suzhou (86-512) 6288 8120         Wuhan    (86-27) 8551 0493      Chongqing (86-23) 6382 4732

 Xi’an (86-29) 8762 0258

Carrier China Service Business

  

Hotline   (86) 800-820-2969/79    (86) 400-820-2969/79

Carrier China Totaline Parts Business

  

Hotline (86) 800-820-6010

 

In order to meet the requirements of customer better and product innovation, Carrier reserves the right to change any product specifications without notice.

Copyright, Carrier China

T-42CE-0810-06

产品制造公司:上海一冷开利空调设备有限公司通惠空调设备厂

成都开利爱得瑞空调设备有限公司Unassociated Document

Exhibit 4.8.6 - Electronic Catalogue (1,3,4,5) - 42CV

  

  

  

Carrier China

 

Carrier is affiliated to United Technologies. United Technologies ranks 120 in world’s 500 tops (2005), its business extends to architectural industry and aerospace industry around the world.

In 1902, Professor Carrier invented first set of scientific air-conditioning system. Since then, carrier’s complete series products and system resolution have become first choice of many world-renowned buildings.

Carrier’s sales revenue reaches 14.6 billion US dollars, leading in the whole industry. Its distributors’ network covers over 170 countries. Carrier is now world’s biggest HVAC manufacturer.

Carrier China has 13 companies, more than 40 sales service offices with over 2,500 employees.

As the world-class factory, Carrier China has several advanced production lines of units and compressors, covering main units of commercial and residential central air-conditioning systems and air terminal products. The various products can meet diversifying demands from different customers.

Contents

	
Type No.

	  	
1

	
Air Flow

	  	1
	
Unit Characteristics

	  	
2

	
Technical Specification

	  	
4

	
External Dimensions

	  	
5

	
Performance Data

	  	
6

	
Purchase Guideline

	  	
16

	
Fan Performance

	  	
18

	
Electrical Data

	  	
19

	 	 	 
	
Acoustic Noise Test

	  	
20

	
Supply Line

	  	20
	 	 	 
	
Installation and Maintenance Instructions

	
  

	
21

 

  

  

  

	
Type No.

 

•  Page1, 2

Product Series

42:fan coil unit

•  Page 3, 4

Type Letter Label

CL:Crouching exposed fan coil unit

VL:Vertical exposed fan coil unit

VM: Vertical concealed fan coil unit

VP: Vertical concealed fan coil unit (high static pressure type)

CW: High static pressure type fan coil unit

CH:high static pressure type fan coil unit (combined coil)

•  Page 5, 6, 7

Unit specification (air flow= unit specification X I70m3/h)

002: 340m3/h

003: 510m3/h

•  Page8

Unit connection direction

L: Left

R: Right

	
Air Flow

 

340~2040m3/h

 

  

1

  

	
Unit Characteristics

 

	

Carrier fan coil units are used for semi-concentrated air conditioning systems. Due to load varying characteristics, advanced design, full product range and superior performance, they are widely used in hotels, apartments, office buildings, etc.

•  Eight Types: with air flow from 340~2550m3/h,cooling capacity from 1920~11510W。

•  Vertical type and crouching type

•  Exposed installation and concealed installation

•  Left or right connector

• Single or combined coils (single or double line water supply and return system)

Low floor occupying

 

The fan coil unit is very thin. It is possible to be installed in any place.

Fast installation

 

One person can install the unit because of its compact size, excellent balance and easy cable connection.

 

Beautiful outlook

 

Balanced structure and smooth outline

 

High efficiency

 

Copper tubes are used for high heat transfer efficiency. Hyperbolic slit fin type heat exchanger and mechanical pipe expanding ensure close contact between copper tubes and fins.

 

Electricity saving

 

Three adjustable fan speeds with permanent capacitor motor make it possible to save electricity.

Easy maintenance

 

Concentrated heating and cooling units with high capacity and easy adjusting functions keep a low maintenance expense. As equipped with condensed water tray, drainage devices and self-cooling motor, it is easy for maintenance with least failures.

 

Low noise

 

The reasonable fan design together with low motor rotational speed and noise absorbent and heat insulating materials, 42C/V Series fan coil units create a quiet and comfortable working and living environment.

Note: left and right are judged when facing the unit.

	
 

 

  

2

  

	

	  	
Full Range           Excellent Performance

	  	  
	  	

	  	  
	  	
• 42CE Crouching Concealed Type (See detail in 42CE sample)

	  	  
	  	
This type is high compact, and can be hidden in ceiling. It's an ideal product for hotel, apartment, office building, etc.

	  	  
	  	

	  	  
	  	
• 42VM Vertical concealed installation type

	  	  
	  	
42VP Concealed installation, high static pressure fan coil unit

	  	  
	  	
Special designed types of high stand, edge lining and stand 2VM,42VP,suitable for outside window installation with only a thickness of 232mm.  42VM and VP types are ideal for in-wall installation or decoration board with a notch. There are 8 specifications for each of these two types with sound performance and easy maintenance.

	  	  
	  	

	  	  
	  	
• 42CL Crouching Exposed Installation Type

	  	  
	  	
It is ideal for hosting in ceilings of all buildings without floor occupying, and particularly appropriate for renovation of old buildings with low pipeline consumption and low cost. Outer shell is protected by durable stoving varnish with colors matching indoor decorations.

	  	  
	  	

	  	  
	  	
• 42VL Vertical Exposed Installation Type

	  	  
	
  

	
Beautiful appearance of this unit can be directly placed on the floor of indoors, with colors matching indoor decorations. Removable entire assembling panel facilitates periodic inside unit inspection. Equipped with speed adjustment switch.

 

  

3

  

	
Technical Specification

CL/VL/VM/VP

	
Type

	
002

	
003

	
004

	
006

	
008

	
010

	
012

	
Rated air flow

m3/h

	
High Speed

	
340

	
510

	
680

	
1020

	
1360

	
1700

	
2040

	
Medium Speed

	
230

	
350

	
470

	
750

	
940

	
1200

	
1500

	
Low Speed

	
150

	
230

	
320

	
480

	
640

	
800

	
960

	
Cooling Capacity W

	
-

	
1920

	
2790

	
3840

	
5230

	
7680

	
8720

	
10470

	
Heat Capacity W

	
-

	
3260

	
4650

	
6400

	
8720

	
12790

	
14530

	
17450

	
Input Power W

	
VL/VM/CL

	
31

	
35

	
50

	
87

	
100

	
160

	
174

	
VP

	
35

	
77

	
87

	
134

	
174

	
210

	
268

	
Noise Value dB (A)

	
VL/VM/CL

	
37

	
39

	
39

	
47

	
43

	
47

	
50

	
VP

	
40

	
42

	
42.5

	
49.5

	
47

	
50

	
53

	
Water Volume l/min

	
-

	
5.5

	
8

	
11

	
15

	
22

	
25

	
30

	
Water Pressure Drop kPa

	
-

	
8

	
17

	
18

	
27

	
36

	
45

	
22

	
Air conditioner fan

	
Form

	
Centrifugal, multi-blade forward fan

	
Quantity

	
1

	
1

	
2

	
2

	
4

	
4

	
4

	
Motor

	
Form

	
Permanent capacitor motor

	
Quantity

	
1

	
1

	
1

	
1

	
2

	
2

	
2

	
Form

	
copper tubes, Hyperbolic slit fins

	
coil

	
working pressure

	
1.5MPa

	
connecting pipe

	
supply and return water

	
3/4" internal thread 3/4" FPT

	
condensation water

	
3/4" external thread 3/4" MPT

	
net weight

	
VL

	
19

	
21

	
23.5

	
28

	
38

	
38

	
40

	
CL

	
19.5

	
21.5

	
24.5

	
30

	
41

	
41

	
50

	
VM/VP

	
14

	
15

	
18

	
22

	
32

	
32

	
39

	
optional accessories

	
VL

	  
	
CL/VM/VP

	  	  	  	
Temperature control switch

	  	  	  

	
Note:

	
1. Cooling capacity value measured is when entering water temperature is 7 ° C, inlet and outlet temperature difference 5 ° C, air DB = 27 ° C and WB = 19.5 ° C. Heating capacity valued measured is when hot  entering water temperature is 60°C and air DB = 21°C.

2. Rated air flow, Cooling Capacity and heat capacity when residual pressures of VL, CL, VM are 0 and when residual pressure of VP is 30.

3. Performance data in the chart is high speed air flow. Refer to noise test method at page 20.

  

4

  

	
External Dimension

42VL

 

 

	
42VL

	
Dimensions

	
A

	
B

	
C

	
002

	
924

	
549

	
524

	
003

	
1044

	
669

	
644

	
004

	
1164

	
789

	
764

	
006

	
1404

	
1029

	
1004

	
008

	
1764

	
1389

	
1364

	
010

	
1764

	
1389

	
1364

	
012

	
2244

	
1869

	
1844

 

42CL

 

 

	
42CL

	
Dimensions

	
A

	
B

	
002

	
924

	
549

	
003

	
1044

	
669

	
004

	
1164

	
789

	
006

	
1404

	
1029

	
008

	
1764

	
1389

	
010

	
1764

	
1389

	
012

	
2244

	
1869

 

42VM/VP

 

	
42

	
Dimensions

	
VM/VP

	
A

	
B

	
C

	
D

	
E

	
002

	
574

	
524

	
549

	
360

	
10

	
003

	
694

	
644

	
669

	
4480

	
12

	
004

	
814

	
764

	
789

	
600

	
14

	
006

	
1054

	
1004

	
1029

	
840

	
18

	
008

	
1414

	
1364

	
1389

	
1200

	
24

	
010

	
1414

	
1364

	
1389

	
1200

	
24

	
012

	
1894

	
1844

	
1869

	
1688

	
32

 

  

5

  

	
Performance Data

	
Cooling Capacity

	
(W)   

	  	
Inlet

	  	
Water

	  
	  	
Water

	
Water

	
Pressure

	
Inlet Air Temp

	Type	
Temp

	
Volume

	
Drop

	
17.0WB

	
18.0WB

	
19.0WB

	
 

	
°C

	
l/min

	
kPa

	
24.0DB

	
25.0DB

	
26.0DB

	
26.0DB

	
27.0DB

	  	  	  	  	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
002

	
5

	
4

	
5

	
1580

	
1270

	
1710

	
1280

	
1710

	
1380

	
1840

	
1290

	
1840

	
1380

	
5.5

	
8

	
1840

	
1420

	
2000

	
1430

	
2000

	
1540

	
2150

	
1440

	
2150

	
1550

	
7

	
13

	
2020

	
1510

	
2200

	
1540

	
2200

	
1650

	
2360

	
1560

	
2360

	
1660

	
8.5

	
17

	
2160

	
1580

	
2350

	
1620

	
2350

	
1720

	
2520

	
1640

	
2520

	
1740

	
6

	
4

	
5

	
1440

	
1220

	
1650

	
1230

	
1580

	
1330

	
1710

	
1230

	
1710

	
1340

	
5.5

	
8

	
1690

	
1350

	
1840

	
1360

	
1840

	
1470

	
2000

	
1380

	
2000

	
1480

	
7

	
13

	
1860

	
1430

	
2020

	
1450

	
2020

	
560

	
2200

	
1480

	
2200

	
1580

	
8.5

	
17

	
1990

	
1490

	
2160

	
1520

	
2160

	
1630

	
2350

	
1550

	
2350

	
1650

	
7

	
4

	
5

	
1310

	
1170

	
1440

	
1170

	
1440

	
1280

	
1580

	
1190

	
1580

	
1280

	
5.5

	
8

	
1540

	
1280

	
1690

	
1290

	
1690

	
1400

	
1840

	
1310

	
1840

	
1420

	
7

	
13

	
1690

	
1350

	
1860

	
1370

	
1680

	
1480

	
2020

	
1400

	
2020

	
1500

	
8.5

	
17

	
1800

	
1400

	
1990

	
1430

	
1990

	
1540

	
2160

	
1450

	
2160

	
1560

	
8

	
4

	
5

	
1190

	
1130

	
1310

	
1130

	
1310

	
1230

	
1440

	
1140

	
1440

	
1230

	
5.5

	
8

	
1380

	
1210

	
1540

	
1220

	
1540

	
1330

	
1690

	
1240

	
1690

	
1350

	
7

	
13

	
1520

	
1260

	
1690

	
1290

	
1690

	
1400

	
1860

	
1310

	
1860

	
1420

	
8.5

	
17

	
1630

	
1300

	
1800

	
1340

	
1800

	
1440

	
1990

	
1370

	
1990

	
1480

	
9

	
4

	
5

	
1050

	
1050

	
1190

	
1090

	
1190

	
1190

	
1310

	
1090

	
1310

	
1200

	
5.5

	
8

	
1230

	
1130

	
1380

	
1160

	
1380

	
1260

	
1540

	
1170

	
1540

	
1280

	
7

	
13

	
1350

	
1170

	
1520

	
1210

	
1520

	
1300

	
1690

	
1230

	
1690

	
1310

	
8.5

	
17

	
1440

	
1200

	
1630

	
1240

	
1630

	
1340

	
1800

	
1280

	
1800

	
1340

	
10

	
4

	
5

	
920

	
920

	
1050

	
1050

	
1050

	
1050

	
1190

	
1060

	
1190

	
1150

	
5.5

	
8

	
1070

	
1060

	
1230

	
1000

	
1230

	
1190

	
1380

	
1120

	
1380

	
1210

	
7

	
13

	
1190

	
1080

	
1350

	
1110

	
1350

	
1220

	
1520

	
1150

	
1520

	
1260

	
8.5

	
17

	
1270

	
1090

	
1440

	
1150

	
1440

	
1240

	
1630

	
1190

	
1630

	
1280

	
003

	
5

	
6

	
10

	
2380

	
1910

	
2580

	
1920

	
2580

	
2070

	
2780

	
1930

	
2780

	
2080

	
8

	
17

	
2670

	
2060

	
2910

	
2080

	
2910

	
2230

	
3130

	
2110

	
3130

	
2260

	
10

	
26

	
2880

	
2150

	
3130

	
2190

	
3130

	
2340

	
3360

	
2210

	
3360

	
2440

	
12

	
35

	
3040

	
2220

	
3280

	
2260

	
3280

	
3350

	
3540

	
2290

	
3540

	
2240

	
6

	
6

	
10

	
1990

	
1740

	
2190

	
1770

	
2190

	
1910

	
2280

	
1780

	
2380

	
1920

	
8

	
17

	
2230

	
1850

	
2450

	
1870

	
2450

	
2020

	
2670

	
1910

	
2670

	
2050

	
10

	
26

	
2410

	
1910

	
2640

	
1950

	
2640

	
2110

	
2580

	
1990

	
2880

	
2140

	
12

	
35

	
2520

	
1950

	
2780

	
2000

	
2780

	
2150

	
3040

	
2050

	
3040

	
2200

	
7

	
6

	
10

	
1790

	
1670

	
1990

	
1690

	
1990

	
1840

	
2190

	
1710

	
2190

	
1850

	
8

	
17

	
2010

	
1740

	
2230

	
1780

	
2230

	
1920

	
2450

	
1800

	
2450

	
1950

	
10

	
26

	
2160

	
1790

	
2410

	
1840

	
2410

	
1980

	
2640

	
1870

	
2640

	
2010

	
12

	
35

	
2280

	
1830

	
2520

	
1870

	
2520

	
2020

	
2780

	
1920

	
2780

	
2070

	
8

	
6

	
10

	
1590

	
1590

	
1790

	
1620

	
1790

	
1770

	
1990

	
1630

	
1990

	
1780

	
8

	
17

	
2010

	
1740

	
2230

	
1780

	
2230

	
1920

	
2450

	
1800

	
2450

	
1950

	
10

	
26

	
2160

	
1790

	
2410

	
1840

	
2410

	
1980

	
2640

	
1870

	
2640

	
2010

	
12

	
35

	
2280

	
1830

	
2520

	
1870

	
2520

	
2020

	
2780

	
1920

	
2780

	
2070

	
9

	
6

	
10

	
1590

	
1590

	
1790

	
1620

	
1790

	
1770

	
1990

	
1630

	
1990

	
1780

	
8

	
17

	
1790

	
1640

	
2010

	
1670

	
2010

	
1810

	
2230

	
1710

	
2230

	
1850

	
10

	
26

	
1920

	
1660

	
2160

	
1720

	
2160

	
1860

	
2410

	
1760

	
2410

	
1900

	
12

	
35

	
2020

	
1690

	
2280

	
1740

	
2280

	
1880

	
2520

	
1800

	
2520

	
1930

	
10

	
6

	
10

	
1400

	
1400

	
1590

	
1550

	
1590

	
1590

	
1790

	
1560

	
1790

	
1710

	
8

	
17

	
1560

	
1540

	
1790

	
1570

	
1790

	
1710

	
2010

	
1600

	
2010

	
1740

	
10

	
26

	
1690

	
1540

	
1920

	
1590

	
14920

	
1730

	
2160

	
1640

	
2160

	
1780

	
12

	
35

	
1770

	
1550

	
2020

	
1600

	
2020

	
1740

	
2280

	
1670

	
2280

	
1800

	
Note:

	
1. DB - Dry bulb temperature ° C, WB - wet bulb temperature ° C.

	
 

	
2. The displayed cooling capacities in above chart are those at high-speed. Cooling capacities at medium speed and low speed should be values in above chart multiplied by the speed correction factors VS. 

 

  

6

  

 

	
Performance Data

 

	
Cooling Capacity

	
(W)   

	
Type

	
Inlet Water

Temp

°C

	
Water

Volume

l/min

	
Water

Pressure

Drop

kPa

	
Inlet Air Temp

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	
27.0DB

	
27.0DB

	
28.0DB

	
26.0DB

	
27.0DB

	
30.0DB

	  	  	  	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
002

	
5

	
4

	
5

	
1910

	
1340

	
1970

	
1290

	
1970

	
1380

	
2110

	
1300

	
2110

	
1380

	
2230

	
1380

	
5.5

	
8

	
2220

	
1500

	
2300

	
1540

	
2300

	
1560

	
2450

	
1470

	
2450

	
1570

	
2610

	
1570

	
7

	
13

	
2450

	
1620

	
2540

	
1570

	
2540

	
1670

	
2700

	
1580

	
2700

	
1690

	
2870

	
1700

	
8.5

	
17

	
2620

	
1700

	
2710

	
1650

	
2710

	
1770

	
2880

	
1670

	
2880

	
1780

	
3070

	
1790

	
6

	
4

	
5

	
1780

	
1290

	
1840

	
1240

	
1840

	
1340

	
1970

	
1240

	
1970

	
1340

	
2110

	
1340

	
5.5

	
8

	
2070

	
1440

	
2150

	
1400

	
2150

	
1490

	
2300

	
1410

	
2300

	
1500

	
2450

	
1510

	
7

	
13

	
2280

	
1540

	
2360

	
1500

	
2360

	
1600

	
2540

	
1510

	
2540

	
1620

	
2700

	
1620

	
8.5

	
17

	
2430

	
1620

	
2520

	
1570

	
2520

	
1670

	
2710

	
1590

	
2710

	
1690

	
2880

	
1710

	
7

	
4

	
5

	
1640

	
1240

	
1710

	
1200

	
1710

	
1290

	
1840

	
1200

	
1840

	
1290

	
1970

	
1290

	
5.5

	
8

	
1290

	
1370

	
2000

	
1330

	
2000

	
1430

	
2150

	
1340

	
2150

	
1430

	
2300

	
1440

	
7

	
13

	
2120

	
1470

	
2200

	
1420

	
2200

	
1520

	
2360

	
1440

	
2360

	
1540

	
2540

	
1550

	
8.5

	
17

	
2260

	
1520

	
2350

	
1490

	
2350

	
1580

	
2520

	
1510

	
2520

	
1600

	
2710

	
1630

	
8

	
4

	
5

	
1510

	
1190

	
1580

	
1150

	
1580

	
1240

	
1710

	
1150

	
1710

	
1240

	
1840

	
1240

	
5.5

	
8

	
1770

	
1300

	
1840

	
1270

	
1840

	
1360

	
2000

	
1280

	
2000

	
1370

	
2150

	
1380

	
7

	
13

	
1940

	
1380

	
2020

	
1340

	
2020

	
1440

	
2200

	
1360

	
2200

	
1450

	
2360

	
1480

	
8.5

	
17

	
2070

	
143

	
2160

	
1400

	
2160

	
1500

	
2350

	
1420

	
2350

	
1520

	
2520

	
1550

	
9

	
4

	
5

	
1380

	
1150

	
1440

	
1100

	
1440

	
1200

	
1580

	
1100

	
1580

	
1200

	
1710

	
1200

	
5.5

	
8

	
1620

	
1230

	
1690

	
1200

	
1690

	
1290

	
1840

	
1210

	
1840

	
1300

	
2000

	
1310

	
7

	
13

	
1780

	
1300

	
1860

	
1270

	
1860

	
1360

	
2020

	
1290

	
2020

	
1380

	
2200

	
1400

	
8.5

	
17

	
1900

	
1350

	
1990

	
1310

	
1990

	
1410

	
2160

	
1340

	
2160

	
1430

	
2350

	
1450

	
10

	
4

	
5

	
1240

	
1100

	
1310

	
1060

	
1310

	
1150

	
1440

	
1060

	
1440

	
1150

	
1580

	
1150

	
5.5

	
8

	
1450

	
1170

	
1540

	
1130

	
1540

	
1230

	
1690

	
1150

	
1690

	
1240

	
1840

	
1260

	
7

	
13

	
1600

	
1220

	
1690

	
1190

	
1690

	
1280

	
1860

	
1210

	
1860

	
1300

	
2020

	
1330

	
8.5

	
17

	
1710

	
1260

	
1800

	
1220

	
1800

	
1310

	
1990

	
1260

	
1990

	
1350

	
2160

	
1370

	
003

	
5

	
6

	
10

	
2880

	
2010

	
2980

	
1940

	
2980

	
2080

	
3170

	
1950

	
3170

	
2080

	
3380

	
2080

	
8

	
17

	
3230

	
2190

	
3350

	
2120

	
3350

	
2270

	
3570

	
2130

	
3570

	
2280

	
3790

	
2280

	
10

	
26

	
3490

	
2300

	
3610

	
2230

	
3610

	
2380

	
3850

	
2260

	
3850

	
2400

	
4080

	
2410

	
12

	
35

	
3660

	
2380

	
3790

	
2310

	
3790

	
2470

	
4050

	
2340

	
4050

	
2490

	
4290

	
2500

	
6

	
6

	
10

	
2690

	
1930

	
2780

	
1860

	
2780

	
2000

	
2980

	
1870

	
2980

	
2010

	
3170

	
2010

	
8

	
17

	
3010

	
2080

	
3130

	
2020

	
3130

	
2160

	
3350

	
2040

	
3350

	
2170

	
3570

	
2190

	
10

	
26

	
3240

	
2190

	
3360

	
2130

	
3360

	
2270

	
3610

	
2150

	
3610

	
2290

	
3850

	
2300

	
12

	
35

	
3410

	
2260

	
3540

	
2200

	
3540

	
2350

	
3790

	
2230

	
3790

	
2370

	
4050

	
2400

	
7

	
6

	
10

	
2490

	
1860

	
2580

	
1790

	
2580

	
1930

	
2780

	
1800

	
2780

	
1930

	
2980

	
1940

	
8

	
17

	
2790

	
1990

	
2910

	
1930

	
2910

	
2070

	
3130

	
1940

	
3130

	
2080

	
3350

	
2090

	
10

	
26

	
3000

	
2070

	
3130

	
2010

	
3130

	
2160

	
3360

	
2050

	
3360

	
2190

	
3610

	
2200

	
12

	
35

	
3160

	
2140

	
3280

	
2080

	
3280

	
2220

	
3540

	
2120

	
3540

	
2260

	
3790

	
2280

	
8

	
6

	
10

	
2290

	
1780

	
2380

	
1720

	
2380

	
1850

	
2580

	
1720

	
2580

	
1860

	
2780

	
1860

	
8

	
17

	
2570

	
1880

	
2670

	
1830

	
2670

	
1970

	
2910

	
1850

	
2910

	
1990

	
3130

	
2000

	
10

	
26

	
2770

	
1970

	
2880

	
1910

	
2880

	
2050

	
3130

	
19440

	
3130

	
2080

	
3360

	
2090

	
12

	
35

	
2910

	
2010

	
3040

	
1970

	
3040

	
2110

	
3270

	
2000

	
3280

	
2140

	
3540

	
2160

	
9

	
6

	
10

	
2080

	
1710

	
2190

	
1640

	
2190

	
1780

	
2380

	
1650

	
2380

	
1790

	
2580

	
1790

	
8

	
17

	
2350

	
1790

	
2450

	
1730

	
2450

	
1870

	
2670

	
1760

	
2670

	
1900

	
2910

	
1910

	
10

	
26

	
2520

	
1850

	
2640

	
1800

	
2640

	
1930

	
2880

	
1830

	
2880

	
1970

	
3130

	
1990

	
12

	
35

	
2650

	
1880

	
2780

	
1840

	
2780

	
1980

	
3040

	
1880

	
3040

	
2010

	
3280

	
2050

	
10

	
6

	
10

	
1880

	
1640

	
1990

	
1570

	
1990

	
1710

	
2190

	
1580

	
2190

	
1720

	
2380

	
1720

	
8

	
17

	
2120

	
1700

	
2230

	
1640

	
2230

	
1780

	
2450

	
1660

	
2450

	
1800

	
2670

	
1810

	
10

	
26

	
2280

	
1730

	
2410

	
1690

	
2410

	
1810

	
2640

	
1720

	
2640

	
1850

	
2880

	
1880

	
12

	
35

	
2400

	
1760

	
2520

	
1720

	
2520

	
1850

	
2780

	
1770

	
2780

	
1990

	
3040

	
1930

Speed correction factor VS

	
Type

	
Medium Speed

	
Low Speed

	
Total Heat

	
Sensible Heat

	
Total Heat

	
Sensible Heat

	
002

	
0.85

	
0.83

	
0.70

	
0.66

	
003

	
0.86

	
0.84

	
0.71

	
0.67

 

  

7

  

	
Performance Data

	
Cooling Capacity

	
(W)   

	
Type

	
Inlet Water Temp

°C

	
Water Volume

l/min

	
Water Pressure Drop kPa

	
Inlet Air Temp

	
17.0WB

	
18.0WB

	
19.0WB

	
24.0DB

	
25.0DB

	
226.0DB

	
26.0DB

	
27.0DB

	  	  	  	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
004

	
5

	
8

	
13

	
3190

	
2570

	
3450

	
2590

	
3450

	
2790

	
3920

	
2610

	
3720

	
2800

	
11

	
18

	
3690

	
2840

	
3990

	
2870

	
3990

	
3080

	
4300

	
2900

	
4300

	
3110

	
14

	
20

	
4020

	
3010

	
4360

	
3060

	
4360

	
3280

	
4800

	
3090

	
4800

	
3310

	
17

	
31

	
4280

	
3140

	
4630

	
3190

	
4630

	
3410

	
4990

	
3230

	
4990

	
3450

	
6

	
8

	
13

	
2620

	
2480

	
3190

	
2490

	
3190

	
2700

	
3450

	
2500

	
3540

	
2700

	
11

	
18

	
3270

	
2700

	
3690

	
2730

	
3690

	
2940

	
3990

	
2770

	
3990

	
2970

	
14

	
20

	
3690

	
2850

	
4020

	
2900

	
4020

	
3120

	
4360

	
2940

	
4360

	
3150

	
17

	
31

	
3920

	
2950

	
4280

	
3010

	
4280

	
3230

	
4630

	
3060

	
4630

	
3280

	
7

	
8

	
13

	
2650

	
2370

	
2920

	
2400

	
2920

	
2590

	
3190

	
2410

	
3190

	
2610

	
11

	
18

	
3070

	
2560

	
3370

	
2590

	
3370

	
2800

	
3690

	
2630

	
3690

	
2840

	
14

	
20

	
3360

	
2670

	
3690

	
2730

	
3690

	
2940

	
4020

	
2780

	
4020

	
2990

	
17

	
31

	
3560

	
2770

	
3920

	
2730

	
3920

	
3040

	
4280

	
2880

	
4280

	
3090

	
8

	
8

	
13

	
2380

	
2280

	
2650

	
2300

	
2650

	
2500

	
2920

	
2310

	
2920

	
2510

	
11

	
18

	
2770

	
2420

	
3070

	
2470

	
3070

	
2660

	
3370

	
2500

	
3370

	
2700

	
14

	
20

	
3020

	
2510

	
3360

	
2570

	
3360

	
2780

	
3690

	
2630

	
3690

	
2830

	
17

	
31

	
3210

	
2570

	
3560

	
2650

	
3560

	
2850

	
3920

	
2710

	
3920

	
2920

	
9

	
8

	
13

	
2130

	
2130

	
2380

	
2210

	
2380

	
2380

	
2650

	
2220

	
2650

	
2420

	
11

	
18

	
2450

	
2270

	
2770

	
2330

	
2770

	
2520

	
3070

	
2360

	
3070

	
2560

	
14

	
20

	
2690

	
2340

	
3020

	
2410

	
3020

	
2610

	
3360

	
2470

	
3360

	
2660

	
17

	
31

	
2850

	
2370

	
3210

	
2470

	
3210

	
2660

	
3560

	
2540

	
3560

	
2730

	
10

	
8

	
13

	
1860

	
1860

	
2130

	
2130

	
2130

	
2130

	
2380

	
2140

	
2380

	
2340

	
11

	
18

	
2150

	
2130

	
2450

	
2190

	
2450

	
2380

	
2770

	
2230

	
2770

	
2430

	
14

	
20

	
2350

	
2150

	
2690

	
2230

	
2690

	
2430

	
3020

	
2300

	
3020

	
2490

	
17

	
31

	
2490

	
2170

	
2850

	
2270

	
2850

	
2470

	
3210

	
2360

	
3210

	
2550

	
006

	
5

	
12

	
18

	
4630

	
3690

	
5010

	
3710

	
5010

	
4000

	
5400

	
3740

	
5400

	
4010

	
15

	
27

	
5020

	
3870

	
5440

	
3920

	
5440

	
4310

	
5860

	
3950

	
5860

	
4230

	
18

	
37

	
5310

	
4000

	
5760

	
4060

	
5760

	
4350

	
6200

	
4110

	
6200

	
4400

	
21

	
57

	
5540

	
4110

	
5000

	
4150

	
5000

	
4470

	
6470

	
4220

	
6470

	
4510

	
6

	
12

	
18

	
4240

	
3520

	
4630

	
3560

	
4630

	
3840

	
5010

	
3580

	
5010

	
3860

	
15

	
27

	
4610

	
3680

	
5020

	
3730

	
5020

	
4010

	
5440

	
3770

	
5440

	
4050

	
18

	
37

	
4870

	
3890

	
5310

	
3850

	
5310

	
4140

	
5760

	
3910

	
5760

	
4190

	
21

	
57

	
5080

	
3870

	
5540

	
3940

	
5540

	
4230

	
6000

	
4000

	
6000

	
4290

	
7

	
12

	
18

	
3860

	
3370

	
4240

	
3410

	
4240

	
3690

	
4630

	
3430

	
4630

	
3710

	
15

	
27

	
4190

	
3490

	
4610

	
3540

	
4610

	
3830

	
5020

	
3590

	
5020

	
3860

	
18

	
37

	
4430

	
3570

	
4870

	
3640

	
4870

	
3920

	
5310

	
3700

	
5310

	
3980

	
21

	
57

	
4620

	
3630

	
5080

	
3710

	
5080

	
3990

	
5540

	
3780

	
5540

	
4060

	
8

	
12

	
18

	
3480

	
3220

	
3860

	
3260

	
3860

	
3540

	
4240

	
3280

	
4240

	
3560

	
15

	
27

	
3770

	
3290

	
4190

	
3350

	
4190

	
3630

	
4610

	
3410

	
4610

	
3680

	
18

	
37

	
3990

	
3350

	
4430

	
3430

	
4430

	
3700

	
4870

	
3500

	
4870

	
3770

	
21

	
57

	
4150

	
3380

	
4620

	
3480

	
4620

	
3760

	
5080

	
3560

	
5080

	
3830

	
9

	
12

	
18

	
3080

	
3070

	
3480

	
3110

	
3480

	
3400

	
3860

	
3140

	
3860

	
3420

	
15

	
27

	
3350

	
3110

	
3770

	
3160

	
3770

	
3440

	
4190

	
3220

	
4190

	
3490

	
18

	
37

	
3550

	
3130

	
3990

	
3210

	
3990

	
3480

	
4430

	
3290

	
4430

	
3550

	
21

	
57

	
3700

	
3140

	
4150

	
3240

	
4150

	
3510

	
4620

	
3340

	
4620

	
3590

	
10

	
12

	
18

	
2700

	
2700

	
3080

	
2970

	
3080

	
3080

	
3480

	
3000

	
3480

	
3280

	
15

	
27

	
2930

	
2910

	
3350

	
2980

	
3350

	
3240

	
3770

	
3050

	
3770

	
3300

	
18

	
37

	
3110

	
2960

	
3550

	
2990

	
3550

	
3260

	
3990

	
3080

	
3990

	
3340

	
21

	
57

	
3230

	
2980

	
3700

	
3010

	
3700

	
3260

	
4150

	
3110

	
4150

	
3360

	
Note:

	
1. DB - Dry bulb temperature ° C, WB - wet bulb temperature ° C.

	
 

	
2. The displayed cooling capacities in above chart are those at high-speed. Cooling capacities at medium speed and low speed should be values in above chart multiplied by the speed correction factors VS. 

 

  

8

  

	
Performance Data

	
Cooling Capacity

	
(W)   

	
Type

	
Inlet Water Temp

°C

	
Water Volume

l/min

	
Water Pressure Drop kPa

	
Inlet Air Temp

	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	
27.0DB

	
27.0DB

	
28.0DB

	
26.0DB

	
27.0DB

	
30.0DB

	  	  	  	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
004

	
5

	
8

	
13

	
3850

	
2710

	
3980

	
2620

	
3980

	
2800

	
4240

	
2630

	
4240

	
2810

	
4510

	
2800

	
11

	
18

	
4450

	
3010

	
4610

	
2920

	
4610

	
3130

	
4910

	
2940

	
4910

	
3140

	
5220

	
3150

	
14

	
20

	
4860

	
3220

	
5040

	
3130

	
5040

	
3340

	
5370

	
3150

	
5370

	
3360

	
5710

	
3370

	
17

	
31

	
5160

	
3360

	
5350

	
3270

	
5350

	
3490

	
5700

	
3300

	
5700

	
3510

	
6060

	
3540

	
6

	
8

	
13

	
3580

	
2610

	
3720

	
2510

	
3720

	
2710

	
3980

	
2502

	
3980

	
2710

	
4240

	
2710

	
11

	
18

	
4140

	
2880

	
4300

	
2790

	
4300

	
2990

	
4610

	
2810

	
4610

	
3010

	
4910

	
3020

	
14

	
20

	
4540

	
3060

	
4800

	
2980

	
4700

	
3170

	
5040

	
3000

	
5040

	
3210

	
5370

	
3220

	
17

	
31

	
4810

	
3190

	
4990

	
3100

	
4990

	
3310

	
5350

	
3140

	
5350

	
3350

	
5700

	
3370

	
7

	
8

	
13

	
3310

	
2510

	
3450

	
2420

	
3450

	
2610

	
3720

	
2430

	
3720

	
2620

	
3980

	
2620

	
11

	
18

	
3840

	
2740

	
3390

	
2660

	
3990

	
2860

	
4300

	
2690

	
4300

	
2870

	
4610

	
2900

	
14

	
20

	
4200

	
2910

	
4360

	
2830

	
4360

	
3020

	
4800

	
2860

	
4800

	
3060

	
5040

	
3080

	
17

	
31

	
4450

	
3010

	
4630

	
2940

	
4630

	
3140

	
4990

	
2980

	
4990

	
3170

	
5350

	
3210

	
8

	
8

	
13

	
3060

	
2420

	
3190

	
2330

	
3190

	
2510

	
3450

	
2340

	
3450

	
2520

	
3720

	
2520

	
11

	
18

	
3540

	
2620

	
3690

	
2540

	
3690

	
2720

	
3990

	
2560

	
3990

	
2741

	
4300

	
2770

	
14

	
20

	
3860

	
2740

	
4020

	
2670

	
4020

	
2870

	
4360

	
2710

	
4360

	
2910

	
4700

	
2930

	
17

	
31

	
4090

	
2840

	
4280

	
2770

	
4280

	
2970

	
4630

	
2810

	
4630

	
3010

	
4990

	
3050

	
9

	
8

	
13

	
2790

	
2330

	
2920

	
2230

	
2920

	
2460

	
3190

	
2240

	
3190

	
2430

	
3450

	
2430

	
11

	
18

	
3220

	
2480

	
3370

	
2410

	
3370

	
2590

	
3690

	
2430

	
3690

	
2620

	
3990

	
2640

	
14

	
20

	
3520

	
2590

	
3690

	
2510

	
3690

	
2710

	
4020

	
2560

	
4020

	
2760

	
4360

	
2780

	
17

	
31

	
3740

	
2660

	
3920

	
2611

	
3920

	
2760

	
4280

	
2650

	
4280

	
2840

	
4630

	
2880

	
10

	
8

	
13

	
2520

	
2240

	
2650

	
2150

	
2650

	
2340

	
2920

	
2160

	
2920

	
2340

	
3190

	
2350

	
11

	
18

	
2920

	
2350

	
3070

	
2270

	
3070

	
2470

	
3370

	
2310

	
3370

	
2490

	
3690

	
2510

	
14

	
20

	
3190

	
2430

	
3360

	
2360

	
3360

	
2550

	
3690

	
2420

	
3690

	
2590

	
4020

	
2640

	
17

	
31

	
3380

	
2490

	
3560

	
2430

	
3560

	
2620

	
3920

	
2490

	
3920

	
2670

	
4280

	
2720

	
006

	
5

	
12

	
18

	
5590

	
3770

	
5790

	
3760

	
5790

	
4020

	
6180

	
3780

	
6180

	
4040

	
6560

	
4040

	
15

	
27

	
6070

	
4110

	
6280

	
3990

	
6280

	
4260

	
6700

	
4010

	
6700

	
4280

	
7120

	
4290

	
18

	
37

	
6420

	
4280

	
6640

	
4150

	
6640

	
4430

	
7090

	
4190

	
7090

	
4450

	
7540

	
4480

	
21

	
57

	
6700

	
4400

	
6920

	
4270

	
6920

	
4550

	
7390

	
4310

	
7390

	
4580

	
7850

	
4610

	
6

	
12

	
18

	
5210

	
3730

	
5400

	
3610

	
5400

	
3870

	
5790

	
3630

	
5790

	
3880

	
6180

	
3880

	
15

	
27

	
5650

	
3930

	
5860

	
3800

	
5860

	
4080

	
6280

	
3840

	
6280

	
4110

	
6700

	
4120

	
18

	
37

	
5980

	
4070

	
6200

	
3950

	
6200

	
4220

	
6640

	
3990

	
6640

	
4260

	
7090

	
4280

	
21

	
57

	
6230

	
4180

	
6470

	
4060

	
6470

	
4340

	
6920

	
4110

	
6920

	
4370

	
7390

	
4410

	
7

	
12

	
18

	
4830

	
3580

	
5010

	
3450

	
5010

	
3720

	
5400

	
3480

	
5400

	
3730

	
5790

	
3740

	
15

	
27

	
5230

	
3740

	
5440

	
3630

	
5440

	
3900

	
5860

	
3660

	
5860

	
3920

	
6280

	
3940

	
18

	
37

	
5540

	
3860

	
5760

	
3760

	
5760

	
4020

	
6200

	
3790

	
6200

	
4060

	
6640

	
4090

	
21

	
57

	
55770

	
3950

	
6000

	
3850

	
6000

	
4120

	
6470

	
3900

	
6470

	
4160

	
6920

	
4200

	
8

	
12

	
18

	
4430

	
3430

	
4630

	
3310

	
4630

	
3470

	
5010

	
3330

	
5010

	
3590

	
6400

	
3590

	
15

	
27

	
4810

	
3560

	
5020

	
3450

	
5020

	
3720

	
5440

	
3490

	
5440

	
3740

	
5860

	
3770

	
18

	
37

	
5090

	
36960

	
5310

	
3560

	
5310

	
38910

	
5760

	
3610

	
5760

	
3860

	
6200

	
3900

	
21

	
57

	
5310

	
3730

	
5540

	
3630

	
5540

	
39890

	
6000

	
3690

	
6000

	
3940

	
6470

	
3990

	
9

	
12

	
18

	
4050

	
3290

	
4240

	
3160

	
4240

	
3430

	
4630

	
3190

	
4630

	
3440

	
5010

	
3450

	
15

	
27

	
4400

	
3380

	
4610

	
3280

	
4610

	
3540

	
5020

	
3310

	
5020

	
3570

	
6440

	
3610

	
18

	
37

	
4650

	
3450

	
4870

	
3420

	
4870

	
3620

	
5310

	
3410

	
5310

	
3660

	
5760

	
3710

	
21

	
57

	
4850

	
3500

	
5080

	
340

	
5080

	
3680

	
5540

	
3480

	
5540

	
3730

	
6000

	
3780

	
10

	
12

	
18

	
3660

	
3150

	
3860

	
3020

	
3860

	
3290

	
4240

	
3060

	
4240

	
3310

	
4630

	
3330

	
15

	
27

	
3980

	
3200

	
4190

	
3110

	
4190

	
3360

	
4610

	
3150

	
4610

	
3400

	
5020

	
3430

	
18

	
37

	
4210

	
3240

	
4430

	
3150

	
4430

	
3410

	
4870

	
3220

	
4870

	
3470

	
5310

	
3510

	
21

	
57

	
4380

	
3280

	
4620

	
3200

	
4620

	
3440

	
5080

	
3270

	
5080

	
3510

	
5540

	
3580

Speed correction factor VS

	
Type

	
Medium Speed

	
Low Speed

	
Total Heat

	
Sensible Heat

	
Total Heat

	
Sensible Heat

	
004

	
0.87

	
0.85

	
0.74

	
0.70

	
006

	
0.89

	
0.87

	
0.74

	
0.70

 

  

9

  

	
Performance Data

	
Cooling Capacity

	
(W)   

	
Type

	
Inlet

Water

Temp

°C

	
Water

Volume

l/min

	
Water

Pressure

Drop

kPa

	
Inlet Air Temp

	
17.0WB

	
18.0WB

	
19.0WB

	
24.0DB

	
225.0DB

	
226.0DB

	
226.0DB

	
27.0DB

	  	  	  	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
008

	
5

	
16

	
20

	
6590

	
5230

	
7140

	
5280

	
7140

	
5690

	
7700

	
5310

	
7700

	
5710

	
22

	
36

	
7370

	
5610

	
7980

	
5680

	
7980

	
6090

	
8590

	
5730

	
8590

	
6140

	
28

	
55

	
7870

	
5830

	
8520

	
5920

	
8520

	
6340

	
9190

	
6000

	
9190

	
6410

	
34

	
79

	
8220

	
5960

	
8910

	
6080

	
8910

	
6500

	
9590

	
6160

	
6590

	
6580

	
6

	
16

	
20

	
6050

	
5010

	
6590

	
5060

	
6590

	
5470

	
7140

	
5090

	
7140

	
5490

	
22

	
36

	
6760

	
5300

	
7370

	
5380

	
7370

	
5800

	
7980

	
5450

	
7980

	
5860

	
28

	
55

	
7210

	
5490

	
7870

	
590

	
7870

	
6000

	
8520

	
5690

	
8520

	
6080

	
34

	
79

	
7540

	
5610

	
8220

	
5730

	
8220

	
6140

	
8910

	
5830

	
8910

	
6230

	
7

	
16

	
20

	
5500

	
4790

	
6050

	
4840

	
6050

	
5250

	
6590

	
4880

	
6590

	
5270

	
22

	
36

	
6140

	
5010

	
6760

	
5110

	
6760

	
5500

	
7370

	
5190

	
7370

	
5570

	
28

	
55

	
6560

	
5150

	
7210

	
5270

	
7210

	
5660

	
7870

	
5370

	
7870

	
5760

	
34

	
79

	
6850

	
5250

	
7540

	
5370

	
7540

	
5770

	
8220

	
5490

	
8220

	
5880

	
8

	
16

	
20

	
4940

	
4570

	
5500

	
4620

	
5500

	
5020

	
6050

	
4660

	
6050

	
5060

	
22

	
36

	
5520

	
4720

	
6140

	
4810

	
6140

	
5210

	
6760

	
4910

	
6760

	
5290

	
28

	
55

	
5910

	
4800

	
6560

	
4940

	
6560

	
5330

	
7210

	
5050

	
7210

	
5430

	
34

	
79

	
6160

	
4860

	
6850

	
5010

	
6850

	
5400

	
7540

	
5150

	
7540

	
5520

	
9

	
16

	
20

	
4400

	
4360

	
4940

	
4420

	
4940

	
4810

	
5500

	
4470

	
5500

	
4850

	
22

	
36

	
4910

	
4420

	
5520

	
4520

	
5520

	
4910

	
6140

	
4630

	
6140

	
5000

	
28

	
55

	
5250

	
4450

	
5910

	
4610

	
5910

	
4980

	
6560

	
4730

	
6560

	
5110

	
34

	
79

	
5480

	
4480

	
6160

	
4650

	
6160

	
5020

	
6850

	
4800

	
6850

	
5160

	
10

	
16

	
20

	
3850

	
3850

	
4400

	
4210

	
4400

	
4400

	
4940

	
4260

	
4940

	
4650

	
22

	
36

	
4300

	
4010

	
4910

	
4230

	
4910

	
4610

	
5520

	
4350

	
5520

	
4710

	
28

	
55

	
4590

	
4080

	
5250

	
4270

	
5250

	
4620

	
5910

	
4410

	
5910

	
4770

	
34

	
79

	
4790

	
4090

	
5480

	
4280

	
5480

	
4630

	
6160

	
4450

	
6160

	
4790

	
010

	
5

	
19

	
28

	
7820

	
6200

	
8470

	
62660

	
8470

	
6750

	
9130

	
6300

	
9130

	
6770

	
25

	
45

	
8370

	
6370

	
9060

	
6450

	
9060

	
6910

	
9750

	
6500

	
9750

	
6970

	
31

	
67

	
8700

	
6440

	
9420

	
6540

	
98420

	
7010

	
10160

	
6630

	
10160

	
7090

	
37

	
90

	
8740

	
6480

	
9690

	
6610

	
9690

	
7060

	
10430

	
6690

	
10430

	
7150

	
6

	
19

	
28

	
7180

	
5940

	
7820

	
6000

	
7820

	
6490

	
8470

	
6040

	
8470

	
6510

	
25

	
45

	
7680

	
6020

	
8370

	
6110

	
8370

	
6590

	
9060

	
6190

	
9060

	
6650

	
31

	
67

	
7970

	
6070

	
8700

	
6180

	
8700

	
6630

	
9420

	
6290

	
9420

	
6720

	
37

	
90

	
8200

	
6100

	
8930

	
6230

	
8930

	
66670

	
99690

	
6340

	
9690

	
6770

	
7

	
19

	
28

	
6520

	
5680

	
7170

	
5740

	
7170

	
6220

	
7810

	
5780

	
7810

	
6250

	
25

	
45

	
6970

	
5700

	
7670

	
5800

	
7670

	
6250

	
8360

	
5890

	
8360

	
6320

	
31

	
67

	
7240

	
5750

	
7960

	
5820

	
7960

	
6300

	
8690

	
5930

	
8690

	
6360

	
37

	
90

	
7430

	
5790

	
8180

	
5840

	
8180

	
6320

	
8920

	
5920

	
8920

	
6380

	
8

	
19

	
38

	
5860

	
5420

	
6520

	
5480

	
6520

	
5950

	
7170

	
5530

	
5050

	
6000

	
25

	
45

	
6270

	
5460

	
6970

	
5520

	
6970

	
5980

	
7680

	
5570

	
7680

	
6040

	
31

	
67

	
6530

	
5480

	
7250

	
5560

	
7250

	
6000

	
7970

	
5590

	
7970

	
6080

	
37

	
90

	
6700

	
5500

	
7450

	
5580

	
7450

	
6020

	
8200

	
5610

	
7200

	
6100

	
9

	
19

	
38

	
4760

	
4720

	
5350

	
4790

	
5350

	
5210

	
5960

	
4840

	
5960

	
5250

	
25

	
45

	
5580

	
5020

	
6270

	
5130

	
6270

	
5580

	
6980

	
5260

	
6980

	
5680

	
31

	
67

	
5800

	
5040

	
6530

	
5150

	
6530

	
5600

	
7250

	
5280

	
7250

	
5700

	
37

	
90

	
5960

	
5050

	
66700

	
5160

	
6700

	
5620

	
7450

	
5300

	
7450

	
5710

	
10

	
19

	
38

	
4570

	
4380

	
5220

	
4600

	
5220

	
4960

	
5860

	
4770

	
5860

	
5120

	
25

	
45

	
4880

	
4410

	
5570

	
4620

	
5570

	
5000

	
6260

	
4800

	
6260

	
5160

	
31

	
67

	
5080

	
4430

	
5810

	
4640

	
5810

	
5020

	
66540

	
4820

	
6540

	
5180

	
37

	
90

	
5200

	
4440

	
5960

	
4650

	
5960

	
5030

	
6700

	
4840

	
6700

	
5200

	
Note:

	
1. DB - Dry bulb temperature ° C, WB - wet bulb temperature ° C.

	
 

	
2. The displayed cooling capacities in above chart are those at high-speed. Cooling capacities at medium speed and low speed should be values in above chart multiplied by the speed correction factors VS. 

 

  

10

  

	
Performance Data

	
Cooling Capacity

	
(W)   

	
Type

	
Inlet

Water

Temp

°C

	
Water

Volume

l/min

	
Water

Pressure

Drop

kPa

	  	
Inlet Air Temp

	  
	
19.5WB

	
20.0WB

	
21.0WB

	
22.0WB

	
27.0DB

	
27.0DB

	
28.0DB

	
26.0DB

	
27.0DB

	
30.0DB

	  	  	  	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
008

	
5

	
16

	
20

	
7970

	
5540

	
8250

	
5350

	
8250

	
5730

	
5790

	
5537

	
8790

	
5350

	
9340

	
5750

	
22

	
36

	
8910

	
5970

	
9210

	
5790

	
9210

	
6190

	
980

	
5830

	
9830

	
6210

	
10440

	
6230

	
28

	
55

	
9510

	
6230

	
9840

	
6060

	
9840

	
6470

	
10500

	
6120

	
10500

	
6540

	
11150

	
6550

	
34

	
79

	
9930

	
6410

	
10280

	
6250

	
10280

	
6650

	
10970

	
6320

	
10970

	
6710

	
11650

	
6750

	
6

	
16

	
20

	
7420

	
5300

	
7700

	
5130

	
7700

	
5510

	
8250

	
5150

	
7250

	
5520

	
8790

	
5540

	
22

	
36

	
8290

	
5690

	
8590

	
5510

	
8590

	
5910

	
9210

	
5570

	
9210

	
5940

	
9830

	
5980

	
28

	
55

	
8850

	
5920

	
9190

	
5760

	
9190

	
6150

	
9840

	
5830

	
9840

	
6210

	
10500

	
6250

	
34

	
79

	
9250

	
6070

	
9590

	
5920

	
9590

	
6320

	
10280

	
6000

	
10280

	
6380

	
10970

	
6430

	
7

	
16

	
20

	
6870

	
5090

	
7140

	
4920

	
7140

	
5290

	
7700

	
4940

	
7700

	
5310

	
8250

	
5333

	
22

	
36

	
6780

	
5410

	
7980

	
5250

	
7980

	
5630

	
8590

	
5300

	
8590

	
5680

	
9210

	
5710

	
28

	
55

	
8200

	
5610

	
8520

	
5450

	
8520

	
5840

	
9190

	
5540

	
9190

	
5910

	
9840

	
5950

	
34

	
79

	
8560

	
5730

	
8910

	
5590

	
8910

	
5980

	
9590

	
5690

	
9590

	
60660

	
10280

	
6120

	
8

	
16

	
20

	
6320

	
4880

	
6590

	
4710

	
6590

	
5080

	
7140

	
4730

	
7140

	
5110

	
7700

	
5120

	
22

	
36

	
7060

	
5130

	
7370

	
4980

	
7370

	
5350

	
7980

	
5050

	
7980

	
5410

	
8590

	
5450

	
28

	
55

	
7550

	
5290

	
7870

	
5150

	
7870

	
5520

	
8520

	
5230

	
8520

	
5610

	
9190

	
5660

	
34

	
79

	
7890

	
5400

	
8220

	
5270

	
8220

	
5630

	
8910

	
5360

	
8910

	
5720

	
9590

	
5800

	
9

	
16

	
20

	
5770

	
4980

	
6050

	
4500

	
6050

	
4870

	
6590

	
4540

	
6590

	
4900

	
7140

	
4920

	
22

	
36

	
6440

	
4960

	
6760

	
4710

	
6760

	
5080

	
7370

	
4780

	
7370

	
5140

	
7980

	
5200

	
28

	
55

	
6880

	
4980

	
7210

	
4850

	
72101

	
5210

	
7870

	
4940

	
7870

	
5290

	
8520

	
5370

	
34

	
79

	
7200

	
5050

	
7540

	
4930

	
7540

	
5290

	
8220

	
5050

	
8220

	
5400

	
8910

	
5490

	
10

	
16

	
20

	
5220

	
4480

	
5500

	
4300

	
5500

	
4680

	
6050

	
4340

	
6050

	
4700

	
6590

	
4720

	
22

	
36

	
5840

	
4580

	
6140

	
4440

	
6140

	
4800

	
6760

	
4520

	
6760

	
4870

	
7370

	
4930

	
28

	
55

	
6230

	
4650

	
6560

	
4540

	
6560

	
4880

	
7210

	
4640

	
7210

	
4990

	
7870

	
5070

	
34

	
79

	
6510

	
4700

	
6850

	
4590

	
6850

	
4940

	
7540

	
4720

	
7540

	
5060

	
8220

	
5160

Speed correction factor VS

	
Type

	
Medium Speed

	
Low Speed

	
Total Heat

	
Sensible Heat

	
Total Heat

	
Sensible Heat

	
008

	
0.86

	
0.84

	
0.73

	
0.69

	
010

	
0.86

	
0.84

	
0.73

	
0.69

  

11

  

	
Performance Data

	
Cooling Capacity

	
(W)   

	
Type

	
Inlet

Water

Temp

°C

	
Water

Volume

l/min

	
Water

Pressure

Drop

kPa

	
Inlet Air Temp

	
17.0WB

	
18.0WB

	
19.0WB

	
24.0DB

	
225.0DB

	
226.0DB

	
26.0DB

	
27.0DB

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
012

	
5

	
24

	
14

	
9470

	
7410

	
10260

	
7480

	
10260

	
8050

	
11040

	
7540

	
11040

	
8090

	
30

	
22

	
10050

	
7630

	
10890

	
7730

	
10890

	
8290

	
11720

	
7820

	
11720

	
8370

	
36

	
33

	
10470

	
7730

	
11340

	
7910

	
11340

	
8470

	
12210

	
8000

	
12210

	
8560

	
42

	
45

	
10770

	
7900

	
11680

	
8020

	
11680

	
8580

	
12570

	
8140

	
12570

	
8690

	
6

	
24

	
14

	
8680

	
7060

	
9470

	
7140

	
9470

	
7700

	
10260

	
7210

	
10260

	
7760

	
30

	
22

	
9210

	
7230

	
10050

	
73440

	
10050

	
7900

	
10890

	
7440

	
10890

	
8010

	
36

	
33

	
9590

	
7350

	
10470

	
7480

	
10470

	
8020

	
11340

	
7590

	
11340

	
8130

	
42

	
45

	
9870

	
7420

	
10770

	
7570

	
10770

	
8120

	
11680

	
7700

	
11680

	
8230

	
7

	
24

	
14

	
7890

	
6710

	
8680

	
6800

	
8680

	
7360

	
9470

	
6870

	
9470

	
7420

	
30

	
22

	
8370

	
6830

	
9210

	
6950

	
9210

	
7500

	
10050

	
7060

	
10050

	
7590

	
36

	
33

	
8720

	
6900

	
9590

	
7050

	
9590

	
7580

	
10470

	
7180

	
10470

	
7710

	
42

	
45

	
8980

	
6950

	
9870

	
7120

	
9870

	
7650

	
10770

	
7270

	
10770

	
7780

	
8

	
24

	
14

	
7090

	
6370

	
7890

	
6470

	
7890

	
7020

	
8680

	
6550

	
8680

	
7080

	
30

	
22

	
7540

	
6420

	
8370

	
6560

	
8370

	
7090

	
7210

	
6680

	
9210

	
7200

	
36

	
33

	
7850

	
6450

	
8720

	
6620

	
8720

	
7140

	
9590

	
6770

	
9590

	
7280

	
42

	
45

	
8080

	
6470

	
8980

	
6650

	
8980

	
7180

	
9870

	
6830

	
9870

	
7330

	
9

	
24

	
14

	
6300

	
5980

	
7090

	
6140

	
7090

	
6690

	
7890

	
6230

	
7890

	
6760

	
30

	
22

	
6700

	
5990

	
7540

	
6160

	
7540

	
6750

	
8370

	
6300

	
8370

	
6820

	
36

	
33

	
6980

	
6010

	
7850

	
6180

	
7850

	
6790

	
8720

	
6350

	
8720

	
6840

	
42

	
45

	
7190

	
6040

	
8080

	
6190

	
8080

	
6830

	
8980

	
6370

	
89980

	
6860

	
10

	
24

	
14

	
5520

	
5520

	
6300

	
5710

	
6300

	
6190

	
7090

	
5920

	
7090

	
6380

	
30

	
22

	
5860

	
5580

	
6700

	
5730

	
6700

	
6220

	
7540

	
6000

	
7540

	
6400

	
36

	
33

	
6110

	
5610

	
6980

	
5770

	
6980

	
6270

	
7850

	
6050

	
7850

	
6420

	
42

	
45

	
6280

	
5740

	
7190

	
5820

	
7190

	
6300

	
8080

	
6090

	
8080

	
6440

	
014

	
5

	
27

	
18

	
10640

	
8330

	
11530

	
7400

	
11530

	
9050

	
12410

	
8470

	
12410

	
9090

	
33

	
27

	
11050

	
8350

	
11970

	
8500

	
11970

	
9110

	
12880

	
8600

	
12880

	
9200

	
39

	
39

	
11340

	
8370

	
12280

	
8560

	
12280

	
9170

	
13220

	
8660

	
13220

	
9270

	
45

	
52

	
11530

	
8460

	
12500

	
8580

	
12500

	
9180

	
13450

	
8710

	
13450

	
9300

	
6

	
27

	
18

	
9750

	
7900

	
10640

	
8020

	
10640

	
8650

	
11530

	
8100

	
11530

	
8720

	
33

	
27

	
11050

	
8350

	
11970

	
8500

	
1190

	
9110

	
12880

	
8600

	
12880

	
9200

	
39

	
39

	
11340

	
8370

	
12280

	
8560

	
12280

	
9170

	
13220

	
8660

	
13220

	
9270

	
45

	
52

	
11530

	
8460

	
12500

	
8580

	
12500

	
9180

	
13450

	
8710

	
13450

	
9300

	
7

	
27

	
18

	
8870

	
7360

	
9760

	
7540

	
9760

	
8100

	
10650

	
7720

	
10650

	
8240

	
33

	
27

	
9200

	
7400

	
10120

	
7580

	
10120

	
8140

	
11040

	
7760

	
11040

	
8280

	
39

	
39

	
9440

	
7420

	
10380

	
7600

	
10380

	
8170

	
11330

	
7770

	
11330

	
8310

	
45

	
52

	
9620

	
7440

	
10570

	
7620

	
10570

	
8190

	
11530

	
7780

	
11530

	
8330

	
8

	
27

	
18

	
7970

	
6810

	
8870

	
7020

	
8870

	
7580

	
9860

	
7230

	
9860

	
7760

	
33

	
27

	
8290

	
6870

	
9200

	
7060

	
9200

	
7600

	
10120

	
7250

	
10120

	
7800

	
39

	
39

	
8500

	
6900

	
9440

	
7090

	
9440

	
7630

	
10380

	
7290

	
10380

	
7820

	
45

	
52

	
8650

	
6920

	
9610

	
7110

	
9610

	
7680

	
10560

	
7310

	
10560

	
7840

	
9

	
27

	
18

	
7080

	
6300

	
7970

	
6500

	
7970

	
7060

	
8870

	
6730

	
8870

	
7250

	
33

	
27

	
7370

	
6250

	
8290

	
6570

	
8290

	
7110

	
9200

	
6770

	
9200

	
7300

	
39

	
39

	
7560

	
6380

	
8500

	
6600

	
8500

	
7140

	
9440

	
6800

	
9440

	
7320

	
45

	
52

	
7700

	
6410

	
8650

	
6630

	
8650

	
7170

	
9620

	
6830

	
9620

	
7350

	
10

	
27

	
18

	
6200

	
5800

	
7080

	
6010

	
7080

	
6400

	
7970

	
6280

	
7970

	
6760

	
33

	
27

	
6450

	
5840

	
7370

	
6050

	
7370

	
6630

	
8300

	
6300

	
8300

	
6800

	
39

	
39

	
6620

	
5850

	
7560

	
6100

	
7560

	
6630

	
8500

	
6330

	
8500

	
6830

	
45

	
52

	
6730

	
5860

	
7710

	
6120

	
7710

	
6640

	
8660

	
6350

	
8660

	
6840

	
Note:

	
1. DB - Dry bulb temperature ° C, WB - wet bulb temperature ° C.

	
 

	
2. The displayed cooling capacities in above chart are those at high-speed. Cooling capacities at medium speed and low speed should be values in above chart multiplied by the speed correction factors VS. 

 

  

12

  

	
Performance Data

	
Cooling Capacity

	
(W)   

	
Type

	
Inlet

Water

Temp

°C

 

	
Water

Volume

l/min

 

	
Water

Pressure

Drop

kPa

 

	
Inlet Air Temp

	
19.5WB

	
20.0WB

	
28.0DB

	
22.0WB

	
27.0DB

	
21.0WB

	
27.0DB

	
26.0DB

	
27.0DB

	
30.0DB

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
Total

Heat

	
Sensible

Heat

	
012

	
5

	
24

	
14

	
11430

	
7840

	
11830

	
7590

	
11830

	
8130

	
12620

	
7630

	
12620

	
8150

	
13410

	
8160

	
30

	
22

	
12140

	
8183

	
12560

	
7890

	
12560

	
8420

	
13400

	
8070

	
13400

	
8070

	
14240

	
8500

	
36

	
33

	
12640

	
8330

	
13080

	
8090

	
13080

	
8630

	
13960

	
8160

	
13960

	
8690

	
14830

	
8730

	
42

	
45

	
13010

	
8470

	
13470

	
8230

	
13470

	
8770

	
14360

	
8320

	
14360

	
8840

	
15260

	
8900

	
6

	
24

	
14

	
10640

	
7500

	
11040

	
7270

	
11040

	
7790

	
11830

	
7320

	
11830

	
7830

	
12620

	
7840

	
30

	
22

	
11300

	
7750

	
11720

	
7510

	
11720

	
8050

	
12560

	
7580

	
12560

	
8090

	
13400

	
8140

	
36

	
33

	
11770

	
7910

	
12210

	
7690

	
12210

	
8220

	
13080

	
7770

	
13080

	
8290

	
13960

	
8340

	
42

	
45

	
12120

	
8020

	
12570

	
7820

	
12570

	
8340

	
13470

	
7910

	
13470

	
8420

	
14360

	
8490

	
7

	
24

	
14

	
9860

	
7180

	
10260

	
6830

	
10260

	
7470

	
11040

	
6990

	
11040

	
7500

	
11830

	
7540

	
30

	
22

	
10470

	
7370

	
10890

	
7150

	
10890

	
7680

	
11720

	
7220

	
11720

	
7730

	
12560

	
7780

	
36

	
33

	
10900

	
7500

	
11340

	
7290

	
113470

	
7800

	
12210

	
7390

	
12210

	
7890

	
13080

	
7950

	
42

	
45

	
11220

	
7580

	
11680

	
7400

	
11680

	
7900

	
12570

	
7500

	
12570

	
8000

	
113470

	
8080

	
8

	
24

	
14

	
9070

	
6850

	
9470

	
6630

	
9470

	
7140

	
10260

	
6690

	
10260

	
7190

	
11040

	
7200

	
30

	
22

	
9630

	
6990

	
10050

	
6780

	
10050

	
7290

	
10890

	
6870

	
10890

	
7670

	
11720

	
7430

	
36

	
33

	
10030

	
7080

	
10470

	
6880

	
10470

	
7400

	
11340

	
7000

	
11340

	
7570

	
12570

	
7680

	
42

	
45

	
10330

	
7150

	
10770

	
6970

	
10770

	
7470

	
11680

	
7090

	
11680

	
7570

	
12570

	
7680

	
9

	
24

	
17

	
8280

	
6540

	
8680

	
6320

	
8680

	
6830

	
9470

	
6370

	
9470

	
6870

	
10260

	
6920

	
30

	
22

	
8790

	
6620

	
9210

	
6420

	
9210

	
6920

	
10050

	
6510

	
10050

	
7000

	
10890

	
7070

	
36

	
33

	
9150

	
6660

	
9590

	
6490

	
9590

	
6980

	
10470

	
6610

	
10470

	
7090

	
11340

	
7190

	
42

	
45

	
9430

	
6700

	
9870

	
6540

	
9870

	
7010

	
10770

	
6680

	
10770

	
7150

	
11670

	
7260

	
10

	
24

	
14

	
7490

	
6220

	
8790

	
6000

	
8790

	
6510

	
8680

	
6070

	
8680

	
6570

	
9470

	
6620

	
30

	
22

	
7950

	
6230

	
8370

	
6050

	
8370

	
6540

	
9210

	
6150

	
9210

	
6640

	
10050

	
6720

	
36

	
33

	
8280

	
6250

	
8720

	
6080

	
8720

	
6560

	
9590

	
6220

	
9590

	
6690

	
10470

	
6790

	
42

	
45

	
8520

	
6250

	
8980

	
6110

	
8980

	
6570

	
9870

	
6260

	
9870

	
6720

	
10770

	
6850

	
014

	
5

	
27

	
18

	
12850

	
8810

	
13300

	
8530

	
13300

	
9140

	
14180

	
8580

	
14180

	
9160

	
15070

	
9170

	
33

	
27

	
16650

	
9000

	
13810

	
8670

	
13810

	
9260

	
14730

	
8650

	
14730

	
9310

	
15660

	
9340

	
39

	
39

	
13690

	
9020

	
14160

	
8760

	
14160

	
9340

	
15120

	
8830

	
15120

	
9410

	
16060

	
9450

	
45

	
52

	
13930

	
9060

	
14420

	
8810

	
14420

	
9390

	
15370

	
8900

	
15370

	
9460

	
16340

	
9530

	
6

	
27

	
18

	
11960

	
8430

	
12400

	
8170

	
12400

	
8750

	
13290

	
8220

	
13290

	
8800

	
14180

	
8810

	
33

	
27

	
12400

	
8500

	
12860

	
8240

	
12860

	
8830

	
13780

	
8310

	
13780

	
8870

	
14700

	
8930

	
39

	
39

	
12740

	
8560

	
13210

	
8320

	
13210

	
8890

	
14150

	
7410

	
14150

	
8940

	
15110

	
9020

	
45

	
52

	
12980

	
8590

	
13460

	
8370

	
13460

	
8930

	
14420

	
8470

	
14420

	
9010

	
15370

	
9090

	
7

	
27

	
18

	
11090

	
8070

	
11540

	
7680

	
11540

	
8400

	
12410

	
7860

	
12410

	
8430

	
13300

	
8480

	
33

	
27

	
11510

	
8100

	
11970

	
7860

	
11970

	
8430

	
12880

	
7930

	
12880

	
8490

	
13900

	
8550

	
39

	
39

	
11800

	
8110

	
12270

	
7890

	
12270

	
8440

	
13210

	
8000

	
13210

	
8540

	
14160

	
8900

	
45

	
52

	
12020

	
8120

	
12510

	
7920

	
12510

	
8460

	
13460

	
8030

	
13460

	
8570

	
14430

	
8650

	
8

	
27

	
18

	
10200

	
78570

	
10650

	
7400

	
10650

	
7930

	
11530

	
7520

	
11530

	
8020

	
12410

	
8100

	
33

	
27

	
10590

	
7600

	
11050

	
7420

	
11050

	
7960

	
11970

	
7550

	
11970

	
8050

	
12880

	
8170

	
39

	
39

	
10860

	
7630

	
11330

	
7440

	
11330

	
7980

	
12270

	
7570

	
12270

	
8080

	
13210

	
8210

	
45

	
52

	
11060

	
7650

	
11530

	
7460

	
11530

	
8000

	
12500

	
7590

	
12500

	
8100

	
13450

	
8220

	
9

	
27

	
18

	
9310

	
7100

	
9260

	
650

	
9260

	
7420

	
10650

	
7100

	
10650

	
7560

	
11530

	
7700

	
33

	
27

	
9670

	
7120

	
10130

	
66980

	
10130

	
7460

	
11050

	
7130

	
11050

	
7600

	
11980

	
7740

	
39

	
39

	
9910

	
7150

	
10380

	
7000

	
10380

	
7480

	
11340

	
7150

	
11340

	
7640

	
12280

	
7760

	
45

	
52

	
10100

	
7180

	
10570

	
7010

	
10570

	
7510

	
11530

	
7160

	
11530

	
7660

	
12510

	
7780

	
10

	
27

	
18

	
8420

	
6600

	
8870

	
6470

	
8870

	
6960

	
9750

	
6630

	
9750

	
7130

	
10640

	
7380

	
33

	
27

	
8750

	
6650

	
9210

	
6500

	
9210

	
7000

	
10130

	
6670

	
10130

	
7150

	
11060

	
7300

	
39

	
39

	
8970

	
6680

	
9450

	
6530

	
9450

	
7020

	
10390

	
6700

	
10390

	
7180

	
11340

	
7330

	
45

	
52

	
9130

	
6700

	
9620

	
6550

	
9620

	
7040

	
10580

	
6710

	
10580

	
7200

	
11540

	
7340

Speed correction factor VS

	
Type

	
Medium Speed

	
Low Speed

	
Total Heat

	
Sensible Heat

	
Total Heat

	
Sensible Heat

	
012

	
0.89

	
0.87

	
0.73

	
0.69

	
014

	
0.89

	
0.87

	
0.73

	
0.69

  

13

  

	
Performance Data

	
Heat Capacity

	
(W)   

	
Type

	
Water

Volume

l/min

	
Water

Pressure

Drop

kPa

	
Inlet Air Temp

	
Inlet Water Temp

	
21.0DB

	
40

	
45

	
50

	
55

	
60

	
65

	
70

	
78

	
80

	
002

	
4

	
5

	
1490

	
1880

	
2280

	
2660

	
3060

	
3450

	
3850

	
4230

	
4630

	
5.5

	
8

	
1580

	
2000

	
2420

	
2840

	
3260

	
3680

	
4090

	
4510

	
4930

	
7

	
13

	
1650

	
2080

	
2520

	
2950

	
3400

	
3830

	
4260

	
4700

	
5130

	
8.5

	
17

	
1700

	
2150

	
2590

	
3050

	
3490

	
3940

	
4380

	
4840

	
5280

	
003

	
6

	
10

	
2150

	
2720

	
3280

	
3850

	
4420

	
4990

	
5550

	
6120

	
6680

	
8

	
17

	
2270

	
2860

	
3450

	
4060

	
4650

	
4250

	
5850

	
6440

	
7040

	
10

	
26

	
2350

	
2970

	
3580

	
4200

	
4810

	
5430

	
6060

	
6680

	
7290

	
12

	
34

	
1410

	
3050

	
3680

	
4310

	
4940

	
5580

	
6210

	
6840

	
7480

	
004

	
8

	
13

	
2920

	
3690

	
4470

	
5230

	
6000

	
6770

	
7540

	
8300

	
9080

	
11

	
18

	
3120

	
3930

	
4760

	
5570

	
6400

	
7220

	
8040

	
8860

	
9680

	
14

	
20

	
3240

	
4110

	
4970

	
5820

	
6680

	
7520

	
8390

	
9230

	
10090

	
17

	
31

	
3350

	
4230

	
5120

	
6000

	
6870

	
7760

	
8640

	
9520

	
10410

	
006

	
12

	
18

	
4080

	
5150

	
6230

	
7300

	
8390

	
9460

	
10530

	
11610

	
12680

	
15

	
27

	
4240

	
5370

	
6490

	
7600

	
8720

	
9840

	
10960

	
12070

	
13200

	
18

	
37

	
4370

	
5520

	
6680

	
7830

	
8980

	
10130

	
11280

	
12430

	
13600

	
21

	
57

	
4480

	
5650

	
6840

	
8010

	
9190

	
10360

	
11550

	
12720

	
13900

	
008

	
16

	
20

	
5900

	
7450

	
9000

	
10560

	
12110

	
13670

	
15210

	
16770

	
18320

	
22

	
36

	
6230

	
7870

	
9150

	
11150

	
12790

	
14430

	
16070

	
17710

	
19350

	
28

	
55

	
6450

	
8160

	
9860

	
11560

	
13260

	
14960

	
16670

	
18360

	
20060

	
34

	
79

	
6630

	
8370

	
10110

	
11860

	
13610

	
15350

	
17100

	
18840

	
20590

	
010

	
19

	
28

	
7000

	
8840

	
10080

	
12540

	
14380

	
16230

	
18060

	
19910

	
21750

	
25

	
45

	
7070

	
8940

	
10390

	
12670

	
14530

	
16390

	
18260

	
20120

	
21980

	
31

	
67

	
7140

	
9030

	
10910

	
12790

	
14680

	
16560

	
18450

	
20320

	
22200

	
37

	
90

	
7210

	
9100

	
11000

	
12900

	
14800

	
16700

	
18600

	
20500

	
22400

	
012

	
24

	
14

	
8220

	
10390

	
12550

	
14710

	
16860

	
19030

	
21190

	
23350

	
25520

	
30

	
22

	
8500

	
10730

	
12970

	
15210

	
17450

	
19680

	
21920

	
24160

	
26390

	
36

	
33

	
8710

	
11000

	
13290

	
15580

	
17880

	
20170

	
22460

	
24760

	
27050

	
42

	
45

	
8870

	
11210

	
13550

	
15890

	
18220

	
20560

	
22890

	
25260

	
27560

	
014

	
27

	
18

	
9240

	
11680

	
14110

	
16540

	
18960

	
21400

	
23830

	
26260

	
28710

	
33

	
27

	
9350

	
11800

	
14260

	
16730

	
19190

	
21400

	
24110

	
26570

	
29020

	
39

	
39

	
9430

	
11910

	
14390

	
16870

	
19370

	
21850

	
24330

	
26820

	
29300

	
45

	
52

	
9600

	
12140

	
14670

	
17210

	
19730

	
22270

	
24890

	
28360

	
29850

 

  

14

  

	
Performance Data

Heating Capacity

The displayed heating capacities in above chart are those at high-speed when inlet air dry-bulb temperature at 21°C DB. Heating capacities at medium speed and low speed should be values in above chart multiplied by the speed correction factors VS.

When inlet air dry-bulb temperature at 21°C, heat capacity correction methods are as follow:

Given that:

	
Air conditioner type

	
006

	
Water volume

	
18 l/min

	
Inlet water temp

	
60°C

	
Inlet air temp

	
18°C DB

Solution: look-up the chart: take model 006 as example, when inlet water temperature is 60° C, water flow 18 l / min, inlet air temperature 21°C, the heating capacity is 8980W:

Every difference of 1°C, its heating capacity variation is:

8980/(60-21 ) =230W/°C

When inlet air temperature is at 18°C, modified heating capacity is:

230X (60-18) = 9660W

Speed correction factor VS

	
Type

	
Medium

Speed

	
Low

Speed

	
002

	
0.84

	
0.72

	
003

	
0.85

	
0.73

	
004

	
0.86

	
0.74

	
006

	
0.87

	
0.75

	
008

	
0.86

	
0.74

	
010

	
0.86

	
0.74

	
012

	
0.87

	
0.75

	
014

	
0.87

	
0.75

 

  

15

  

	
Purchase Guideline

When select cooling unit is to match designed warm-up load with sensible heat load. In most cases, the coil has enough latent heat capacity, which can meet the design requirements. If air is used, the corresponding calculation formula should be changed:

	  	
Total heat capacity (W) x 0.86

	 
	
Water temp rise (°C) =

	
60 X water flow (l/min)

	 
	  	  	 
	  	
Sensible heat capacity (W) x 0.86

	 
	
Air temp rise (°C DB) =

	
0.29 X air flow (m3/h)

	 

Choose according to air conditioner fan at high speed (cooling)

Fan coil unit is often selected according to air conditioner fan at high speed for the smallest unit type.

1. Determine working requirements (see selection guide)

	
Given that: indoor sensible heat cooling load

	
2330W

	
Inlet air temp

	
27°C DB, 19.5°C WB

	
Air flow

	
660m3/h

	
Total indoor heat cooling load

	
3140W

	
Inlet water temp

	
7°C

2. Determine unit specification, water volume and pressure drop

	 	
  

	
Check cooling capacity indicator when inlet air temp at 19.5°C WB, inlet water temp at 7°C WB. The sensible heat capacity should be the same or above the value needed. For the 004 type, it reads warm-up heat cooling load 2510W, total heat and cooling load of 3310W, water flow 8 l / min and the water pressure drop 13kPa. Cooling capacities at other speeds can be obtained by the speed correction factor Vs. Vs value should be checked in the chart of cooling capacity.

Choose according to air conditioner fan at medium speed (cooling)

The units usually operate at medium or low speed. So units can be selected under condition of average cooling load at medium speed.  And it permits to run at high speed with unusual or peak load to increase unit capacity.

1. Determine working requirements

Given that:

	
Average designed indoor sensible heat cooling load 

	
2330W

	
Inlet air temp

	
27°C DB, 19.5°C WB

	
Average designed air flow

	
340m3/h

	
Average designed indoor total heat cooling load

	
3140W.

	
Inlet water temp

	
7°C

2. Testing unit specifications

	 	
  

	
According to technical data sheet, medium speed air flow is 350m3/h, which is the closest to the required air volume in calculation. So 003 is selected.

 

  

16

  

	
Purchase Guideline

	
  

	
3.

	
According to cooling capacity correction sheet, find cooling capacity correction factor with test unit running at medium speed.

 Type 003 unit, multiplied by 0.84 with sensible heat capacity, or multiplied by 0.86 with total heat capacity.

	
  

	
4.

	
In order to determine modified sensible heat capacity and total heat, we use correction factor to divide average designed cooling load.

	
1480

	  	
=1760(W)(modified sensible heat load) 0.84

	
0.84

	
  

	
1980

	  	
=2302 (W)(modified total heat load)

	
0.86

	
  

5. Finally, determine water flow and pressure drop.

	
  

	
Use above modified load instead of the given load, at 27°C DB, 19.5°C WB and 7°C water temperature, to check cooling capacity performance chart.  The sensible heat and total heat load of selected unit should be the same or above modified load. According to the chart, for type 003, it reads that sensible heat is 1860W, total heat 2490W, water flow 6 l / min, pressure drop 10 kPa.

Heating (units selected by cooling function)

Units selected by cooling function are sufficient for heating. Heating capacity is determined when water flow is at the same level.  That is to use inlet water temperature to meet the indoor heating load.

1. Determine working requirements

	
Given that: type selected according to cooling load

	
Type 004

	
Indoor heating load

	
5820W

	
Water flow

	
8 l/min

	
Inlet water temp

	
21°C DB

2. Determine water temperature needed

	 	
  

	
Check hot water heating performance chart, the 8 l/min inlet water temperature of 004 type unit is 60°C when air conditioner fan runs at high speed with heating capacity of 6000W.

 

  

17

  

	
Fan Performance

Standard Unit

High Static Pressure Unit

The technical data in this chart is measured when the unit runs at high speed in dry air with air filter and air return grille uninstalled.

  

18

  

	
Electrical Data

Electrical Wiring Diagram

 

Total unit consumption power (motor input power)

	
Type Specification

	
002

	
003

	
004

	
006

	
008

	
010

	
012

	
Power

(W)

	
VL/CL/VM

	
31

	
35

	
50

	
87

	
100

	
160

	
174

	
VP

	
35

	
77

	
87

	
134

	
174

	
210

	
268

	
Electric Current

(A)

	
VL/CL/VM

	
0.14

	
0.16

	
0.23

	
0.42

	
0.47

	
0.76

	
0.83

	
VP

	
0.16

	
0.34

	
0.42

	
0.60

	
0.84

	
1.00

	
1.25

 

Unit Output Power

	
Type Specification

	
002

	
003

	
004

	
006

	
008

	
010

	
012

	
Power

(W)

	
VL/CL/VM

	
8

	
12

	
16

	
40

	
16x2

	
40 X 2

	
40 X 2

	
VP

	
12

	
28

	
40

	
53

	
40 X 2

	
53 X 2

	
53 X 2

 

Note: The above is the data with high motor speed.

  

19

  

	
Noise Test

Test environment is an anechoic chamber with background noise less than 50db (A).

	
Supply Line

	
Type Specification

	
42CL, VM, Vp

	
42VL

	
002

	
003

	
004

	
006

	
008

	
010

	
012

	
002

	
003

	
004

	
006

	
008

	
010

	
012

	
Units

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
Air Filter

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
Speed Adjusting Switch

	
●

	
●

	
●

	
●

	
●

	
●

	
●

	
○

	
○

	
○

	
○

	
○

	
○

	
○

	
Temperature control switch

	
●

	
●

	
●

	
●

	
●

	
●

	
●

	  	  	  	  	  	  	  

 

	
Note:

	
○Accessories with unit.

● Optional accessories. Orders for optional accessories should be indicated in purchasing contract.

  

20

  

	
Installation and Maintenance Instructions

 

1. Scope of Application

 

The unit uses50HZ/220VAC power, with ambient temperature of-30°C—+65°C,altitude not exceeding 4000m.

 

2. Unit Installation

 

Crouching units should be kept at horizontal level and vertical unit level should be adjusted by adjusting the bolts. Checkpoints for repairments should be considered when concealed type units are installed. Installed units should be covered against dust in process of renovation or decoration.

 

Pipeline Configuration and Anti-frost Measures

 

When install outlet water pipes, pipe clamp should be used to hold pipe end tightly. Valves should be installed on inlet and outlet water pipes. The highest point of the pipeline should be installed air release valve, the lowest point water release valve.

 

Condensation water requires a slope for successful discharge.

 

Strict anti-dew measures should be taken at valves of inlet and outlet water pipes and condensing water pipes.

 

4. Electrical Connection

 

In strict accordance with wiring diagram on the unit Note: Middle power line must be connected to the yellow line shown in the diagram. Grounding bolt inside the terminal box of unit is used for grounding connection protection system.

 

Do not put two or more (including two) units in connection in parallel; otherwise it will affect loop current in normal operation of the unit. Motor may be damaged.

 

Motor shaft bearing uses enclosed ball bearing motor, free from lubricant.

 

5. Water Supply Requirements

 

Prohibit the use of steam and hot water above 100 ° C. For double tube unit, hot water temperature should not exceed 65 ° C. If water above 65 ° C is used, softened water must be used; otherwise it will affect heat transfer effects because of corrosion.

 

Maximum water flows of all types of units do not exceed sample range. Water must be clean.

 

6. Anti-freezing Measures

 

If stop the operation of circulation pumps when the external temperature is below 0 ° C, the water in pipeline will freeze, causing cracks of coil units and pipe. So following measures must be taken:

	
  

	
1)

	
Continuous operation of circulation pump:

	
  

	
2)

	
Input antifreeze solution with appropriate concentration:

 

7. Maintenance

 

When start unit, first turn on air release valve to remove air and turn off air release valve when there is water flowing out.

 

The filter should be cleaned once a month or so. For coil unit, clean it periodically to ensure heat exchange efficiency.

  

21

  

Carrier, as a world-class manufacturer, takes following six responsibilities for environment protection:

	

	  	  
	  	  
	  	
Welcome to visit Carrier website

	  	
www.carrier.com.cn

	  	  
	
  

	  

 

Carrier China Sales Offices

	
Shanghai(86-21) 2306 3000

	
Beijing(86-10) 6583 2008

	
Guangzhou(86-20) 3820 1818

	
Suzhou(86-512)6511 0233

	
Chongqing(86-23)6382 4732

	
Xi'an(86-29)8762 0258

 

Carrier China Service Center

	
Service Hotline(86) 800-820-2969/79

	
(86) 400-820-2969/79

 

Carrier China“Totaline”Spare Parts Business

Spare Parts Inquiry(86)800-820-6010

 

	

	  
	
In order to meet customers in a better way with our product improvements and innovations, we reserve the modifying rights to samples without prior notice

	
All rights reserved. Carrier China

Source: [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}, [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}]]