Document:

Unassociated Document

Exhibit 4.8.64 -Design Drawings - Components in Distribution Box

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	  	
Lighting Distribution Box

	  	
Ampere(A)

	  	  	  
	
1

	
11MX(1st Floor)

	
XSAII-18

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-11MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
8

	
MX11-1~8

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX11-9~10

	
Schneider

	
2

	
12MX(1st Floor)

	
XSAII-24

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-12MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
12

	
MX12-1~12

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX12-13~14

	
Schneider

	
3

	
13MX(1st Floor)

	
XSAII-24

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-13MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
15

	
MX13-1~15

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX13-16~17

	
Schneider

	
4

	
14MX(1st Floor)

	
XSAII-24

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-14MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
15

	
MX14-1~15

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX14-16~17

	
Schneider

	
5

	
15MX(1st Floor)

	
XSAII-18

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-15MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
8

	
MX15-1~8

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX15-9~10

	
Schneider

	
6

	
16MX(Half Floor)

	
XSAII-24

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-16MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
14

	
MX16-1~14

	
Schneider

 

	
SUNTEC

	
Page 1 of 8

	
   

 

  

 

  

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX16-15~16

	
Schneider

	
7

	
21MX(2nd Floor)

	
XSAII-24

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-21MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
10

	
MX21-1~10

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
5

	
MX21-11~15

	
Schneider

	
8

	
22MX(2nd Floor)

	
XSAII-24

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-22MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
MX22-1~3

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
10

	
MX22-4~13

	
Schneider

	
9

	
23MX(2nd Floor)

	
XSAII-24

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-23MX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
14

	
MX23-1~14

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX23-15~16

	
Schneider

	
10

	
11MHX (1st Floor Evacuation)

	
XSAII-72

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-11MHX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
17

	
MHX11-1~17

	
Schneider

	
11

	
21MHX(2nd FloorEvacuation)

	
XSAII-72

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-21MHX

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
10

	
MHX21-1~10

	
Schneider

	  	
Power Supply Box

	  	  	  	  	  
	
1

	
11DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-11DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
11DX-1~5

	
Schneider

 

	
SUNTEC

	
Page 2 of 8

	
   

 

  

 

  

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	  	
Leakage Protection Breaker

	
DPNVigiC32

	
32+30mA

	
1

	
11DX-6

	
Schneider

	
2

	
12DX(1st Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-12DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
12DX-1~5

	
Schneider

	
3

	
13DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-13DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
13DX-1~5

	
Schneider

	
4

	
14DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-14DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
14DX-1~5

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C20/1P

	
20

	
1

	
14DX-6

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
1

	
14DX-7

	
Schneider

	
5

	
15DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-15DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
6

	
15DX-1~6

	
Schneider

	
6

	
16DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-16DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
16DX-1~5

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
4

	
16DX-6~9

	
Schneider

	
7

	
17DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
32

	
1

	
D-17DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
16DX-1~5

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
16DX-6~7

	
Schneider

	
8

	
18DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

 

	
SUNTEC

	
Page 3 of 8

	
   

 

  

 

  

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-18DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
3

	
16DX-1~3

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
16DX-4~5

	
Schneider

	
8

	
19DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-18DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
18DX-1~5

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
18DX-6~8

	
Schneider

	
9

	
110DX(1st Floor)

	
XSAII-12(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-110DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
3

	
110DX-1~3

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
110DX-4~6

	
Schneider

	
10

	
111DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-111DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
4

	
111DX-1~4

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
111DX-5~7

	
Schneider

	
11

	
112DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-112DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
112DX-1~5

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
1

	
112DX-6

	
Schneider

	
12

	
113DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-113DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
113DX-1~5

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
4

	
113DX-6~9

	
Schneider

	
14

	
114DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

 

	
SUNTEC

	
Page 4 of 8

	
   

 

  

 

  

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-114DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
1

	
114DX-1

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
4

	
114DX-2~5

	
Schneider

	
15

	
115DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-115DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
7

	
115DX-1~7

	
Schneider

	
16

	
116DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-116DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC32

	
32+30mA

	
3

	
116DX-1~3

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C63/1P

	
63

	
2

	
116DX-4~5

	
Schneider

	
17

	
117DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-117DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
3

	
117DX-1~3

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
117DX-4~5

	
Schneider

	
18

	
21DX(2nd Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-21DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
6

	
21DX-1~6

	
Schneider

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
21DX-7~8

	
Schneider

	
19

	
22DX(2nd Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-22DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
6

	
22DX-1~6

	
Schneider

	
20

	
23DX(2nd Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-23DX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
6

	
23DX-1~5

	
Schneider

 

	
SUNTEC

	
Page 5 of 8

	
   

 

  

 

  

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
23DX-6~7

	
Schneider

	  	
Power Supply Box

	  	  	  	  	  
	
1

	
11EX(1st Floor)

	
XSAII-84(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-11EX

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/16/4+VigiC65ELE

	
16+30mA

	
5

	
11EX-1~5

	
Schneider

	
2

	
12EX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-12EX

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
7

	
11EX-1~7

	
Schneider

	
3

	
13EX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-13EX

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
9

	
11EX-1~9

	
Schneider

	
4

	
14EX(1st Floor)

	
XSAII-48(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-14EX

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/16/4+VigiC65ELE

	
16+30mA

	
6

	
14EX-1~6

	
Schneider

	
6

	
15EX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-15EX

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
7

	
15EX-1~7

	
Schneider

	
7

	
16EX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-16EX

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
9

	
16EX-1~9

	
Schneider

	
8

	
17EX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-17EX

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/D10/3P

	
10

	
7

	
17EX-1~7

	
Schneider

	
9

	
21EX(2nd Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality

 

	
SUNTEC

	
Page 6 of 8

	
   

 

  

 

  

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-21EX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC32

	
32+30mA

	
7

	
21EX-1~7

	
Schneider

	
10

	
22EX(2nd Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-22EX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
10

	
22EX-1~10

	
Schneider

	
11

	
23EX(2nd Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-23EX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
8

	
23EX-1~8

	
Schneider

	
12

	
24EX(2nd Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality

	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-24EX

	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
6

	
24EX-1~6

	
Schneider

	  	
Maintenance Power Box (1st Floor)

	  	  	  	  	  
	
1

	
Maintenance Power Box

	
Non-Standard

	  	
4

	  	
High Quality

	  	
11JX、12JX、13JX、14JX

	  	  	  	  	  
	  	
Circuit Breaker

	
C65H/63/D63/3P

	
63

	
16

	
Incoming Line

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
16

	  	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
48

	  	
Schneider

	
1

	
Maintenance Power Box (Trench)

	
Non-Standard

	  	
6

	  	
High Quality

	  	
01JX、02JX、03JX、04JX、05JX、06JX

	  	  	  	  	  
	  	
Circuit Breaker

	
C65H/63/D63/3P

	
63

	
16

	
Incoming Line

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
16

	  	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
48

	  	
Schneider

 

	
SUNTEC

	
Page 7 of 8

	
   

 

  

 

  

 

List of Components in Distribution Box

	
Owner Name: Shenyang Sunshine

	
P554

	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10

	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand

	
1

	
Maintenance Power Box (Half Floor)

	
Non-Standard

	  	
6

	  	
High Quality

	  	
21JX、22JX、23JX、24JX、25JX、26JX

	  	  	  	  	  
	  	
Circuit Breaker

	
C65H/63/D63/3P

	
63

	
16

	
Incoming Line

	
Schneider

	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
16

	  	
Schneider

	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
48

	  	
Schneider

	
1

	
Socket Box (Seed Proliferation)

	
Non-Standard

	  	
8

	  	  
	  	
Socket

	  	  	  	  	
Schneider

	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  

 

	
SUNTEC

	
Page 8 of 8Unassociated Document

Exhibit 4.8.65 -Design Drawings - Electrical Distribution Box

 

List of Electrical Distribution Box

	
Serial

No.

	
Name of Electrical

Distribution Box

	
Construction 

Range

	
Drawing Name

	
Drawing No.

	
Specific 

Position

	
Notes

	
1

	
Switching Cabinet 11KHX

	
From low-voltage distribution cabinet P114 in workshop, to K32、K33、PJ32-1、PJ33-1.

	
Distribution System Drawing of AC Switching Cabinet 11KHX

	
E.07-061305-1-6/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
2

	
Switching Cabinet 12KHX

	
From low-voltage distribution cabinet P114 in workshop, to K13、K22、PJ13-1、PJ22-1.

	
Distribution System Drawing of AC Switching Cabinet 12KHX

	
E.07-061305-1-10/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
3

	
Air Conditioning Cabinet 11KX

	
From low-voltage distribution cabinet P113 in workshop, to K3X、K31、K34、PJ31-1、PJ34-1.

	
Distribution System Drawing of Air Conditioning Cabinet 11KX

	
E.07-061305-1-7/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
4

	
Air Conditioning Cabinet 12KX

	
From low-voltage distribution cabinet P113 in workshop, to K71、K61、K62、PJ71-1、PJ61-1.

	
Distribution System Drawing of Air Conditioning Cabinet 12KX

	
E.07-061305-1-8/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
5

	
Air Conditioning Cabinet 13KX

	
From low-voltage distribution cabinet P113 in workshop, to K41、K51、K52、PJ41-1、PJ41-2、PJ41-3、PJ41-4、PJ51-1.

	
Distribution System Drawing of Air Conditioning Cabinet 13KX

	
E.07-061305-1-9/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
6

	
Air Conditioning Cabinet 14KX

	
From low-voltage distribution cabinet P113 in workshop, to K1X、K11、K12、K14、PBJ11-1、PJ11-1、PJ12-1、PJ14-1.

	
Distribution System Drawing of Air Conditioning Cabinet 14KX

	
E.07-061305-1-11/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
7

	
Air Conditioning Cabinet 15KX

	
From low-voltage distribution cabinet P113 in workshop, to K2X-1、K21、K23、PBJ11-1、PJ21-1、PJ23-1.

	
Distribution System Drawing of Air Conditioning Cabinet 15KX

	
E.07-061305-1-12/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
8

	
Air Conditioning Cabinet 16KX

	
From low-voltage distribution cabinet P113 in workshop, to K15-1、K2X-2-1、K24、K25、PJ15-1、PJ24-1、PJ25-1.

	
Distribution System Drawing of Air Conditioning Cabinet 16KX

	
E.07-061305-1-13/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

  

Page 1 of 10

  

 

	
9

	
Second-Class Load Power Cabinet 11ELX

	
From low-voltage distribution cabinet P111 in workshop, to transfer pump in injection water and purifying water room

	
Distribution System Drawing of Second-Class Load Power Cabinet 11~22ELX

	
E.07-061305-1-5/22

	
11-F-1-07/Control Room/E.07-061305-1-20/22

	
Non Purifying Area

	
10

	
Second-Class Load Power Cabinet 12ELX

	
From low-voltage distribution cabinet P111 in workshop, to transfer pump in injection water and purifying water room

	
Distribution System Drawing of Second-Class Load Power Cabinet 11~22ELX

	
E.07-061305-1-5/22

	
11-F-1-07/Control Room/E.07-061305-1-20/22

	
Non Purifying Area

	
11

	
Second-Class Load Power Cabinet 13ELX

	
From low-voltage distribution cabinet P111 in workshop, to transfer pump in injection water and purifying water room

	
Distribution System Drawing of Second-Class Load Power Cabinet 11~22ELX

	
E.07-061305-1-5/22

	
11-F-1-07/Control Room/E.07-061305-1-20/22

	
Non Purifying Area

	
12

	
Second-Class Load Power Cabinet 21ELX

	
From low-voltage distribution cabinet P111 in workshop, to exhaust fan P73-1、P73-2、P73-3

	
Distribution System Drawing of Second-Class Load Power Cabinet 11~22ELX

	
E.07-061305-1-5/22

	
14-F-2-10/Protein Analysis Room/E.07-061305-1-22/22

	
Purifying Area

	
13

	
Second-Class Load Power Cabinet 22ELX

	
From low-voltage distribution cabinet P112 in workshop, to air compressor and dryer in AC machine room

	
Distribution System Drawing of Second-Class Load Power Cabinet 11~22ELX

	
E.07-061305-1-5/22

	
13-F-2-01/2nd Floor AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
14

	
Power Supply Box 110DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point in light testing and labeling room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
9-E-1-17/Light Testing and labeling/E.07-061305-1-20/22

	
Purifying Area

	
15

	
Power Supply Box 111DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point of room (plan drawing) around 111DX

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
9-C-1-26/Temporary Storage of Inner Packing Materials/E.07-061305-1-20/22

	
Purifying Area

	
16

	
Power Supply Box 112DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point of room (plan drawing) around 112DX

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
9-C-1-19/People Air Lock/E.07-061305-1-20/22

	
Purifying Area

	
17

	
Power Supply Box 113DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point in external packing room and code room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
10-E-1-29/External Packing/E.07-061305-1-20/22

	
Purifying Area

  

Page 2 of 10

  

 

 

	
18

	
Power Supply Box 114DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point in shipping area and cushion room of refrigerator

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
10-F-1-23/Shipping Area/E.07-061305-1-20/22

	
Purifying Area

	
19

	
Power Supply Box 115DX

	
Form power cabinet 13LX, to power consumption point in original solution storage, measuring and sampling room, and material purifying room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
10-D-1-04/People Air Lock/E.07-061305-1-20/22

	
Purifying Area

	
20

	
Power Supply Box 116DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point in maintenance room and work clothes cleaning room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
11-E-1-29/Maintenance Room/E.07-061305-1-20/22

	
Purifying Area

	
21

	
Power Supply Box 117DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption points of two cleaning rooms

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
5-E-1-10/Material Purifying/E.07-061305-1-20/22

	
Purifying Area

	
22

	
Power Supply Box 21DX

	
From low-voltage distribution cabinet P15 in workshop, to power consumption point in air conditioning machine room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
12-F-2-01/Pilot Production in Preservation/E.07-061305-1-20/22

	
Purifying Area

	
23

	
Maintenance Box 01JX

	
From power supply box 117DX, to maintenance box in trench

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
Power Plane Drawing of Trench/E.07-061305-1-19/22

	
Non Purifying Area

	
24

	
Maintenance Box 02JX

	
From power supply box 117DX, to maintenance box in trench

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
Power Plane Drawing of Trench /E.07-061305-1-19/22

	
Non Purifying Area

	
25

	
Maintenance Box 03JX

	
From power supply box 117DX, to maintenance box in trench

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
Power Plane Drawing of Trench /E.07-061305-1-19/22

	
Non Purifying Area

	
26

	
Maintenance Box 04JX

	
From power supply box 113DX, to maintenance box in trench

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
Power Plane Drawing of Trench /E.07-061305-1-19/22

	
Non Purifying Area

  

Page 3 of 10

  

 

	
27

	
Maintenance Box 05JX

	
From power supply box 113DX, to maintenance box in trench

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
Power Plane Drawing of Trench /E.07-061305-1-19/22

	
Non Purifying Area

	
28

	
Maintenance Box 06JX

	
From power supply box 113DX, to maintenance box in trench

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
Power Plane Drawing of Trench /E.07-061305-1-19/22

	
Non Purifying Area

	
29

	
Maintenance Box 11JX

	
From power supply box 116DX, to maintenance box in maintenance room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
11-E-1-29/Maintenance Room/E.07-061305-1-20/22

	
Non Purifying Area

	
30

	
Maintenance Box 12JX

	
From power supply box 116DX, to maintenance box in maintenance room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
11-E-1-29/ Maintenance Room/E.07-061305-1-20/22

	
Non Purifying Area

	
31

	
Maintenance Box 13JX

	
From power supply box 116DX, to maintenance box in maintenance room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
11-E-1-29/ Maintenance Room/E.07-061305-1-20/22

	
Non Purifying Area

	
32

	
Maintenance Box 14JX

	
From power supply box 116DX, to maintenance box in maintenance room

	
Distribution System Drawing of Power Supply Box 110~21DX

	
E.07-061305-1-15/22

	
11-E-1-29/ Maintenance Room/E.07-061305-1-20/22

	
Non Purifying Area

	
33

	
Maintenance Box 21JX

	
From low-voltage distribution cabinet P13 in workshop, to maintenance box on 1st floor ceiling

	  	  	
Power Plan Drawing of 1st Floor Ceiling/E.07-061305-1-21/22

	
Non Purifying Area

	
34

	
Maintenance Box 22JX

	
From low-voltage distribution cabinet P13 in workshop, to maintenance box on 1st floor ceiling

	  	  	
Power Plane Drawing of 1st Floor Ceiling/E.07-061305-1-21/22

	
Non Purifying Area

	
35

	
Maintenance Box 23JX

	
From low-voltage distribution cabinet P13 in workshop, to maintenance box on 1st floor ceiling

	  	  	
Power Plane Drawing of 1st Floor Ceiling/E.07-061305-1-21/22

	
Non Purifying Area

  

Page 4 of 10

  

 

	
36

	
Maintenance Box 24JX

	
From low-voltage distribution cabinet P13 in workshop, to maintenance box on 1st floor ceiling

	  	  	
Power Plane Drawing of 1st Floor Ceiling/E.07-061305-1-21/22

	
Non Purifying Area

	
37

	
Maintenance Box 25JX

	
From low-voltage distribution cabinet P15 in workshop, to maintenance box on 1st floor ceiling

	  	  	
Power Plane Drawing of 1st Floor Ceiling/E.07-061305-1-21/22

	
Non Purifying Area

	
38

	
Maintenance Box 26JX

	
From low-voltage distribution cabinet P15 in workshop, to maintenance box on 1st floor ceiling

	  	  	
Power Plane Drawing of 1st Floor Ceiling/E.07-061305-1-21/22

	
Non Purifying Area

	
39

	
Lighting Switching Box 11MHX

	
From low-voltage distribution cabinet P115 in workshop, to power consumption point of escape lighting  in 1st floor passage

	
Distribution System Drawing of Lighting Box (Yi I)

	
E.07-061305-2-1/8

	
10-C-1-07/Measuring and Sampling Room/E.07-061305-2-3/8

	
Purifying Area

	
40

	
Lighting Switching Box 21MHX

	
From low-voltage distribution cabinet P115 in workshop, to power consumption point of escape lighting  in 2nd floor passage

	
Distribution System Drawing of Lighting Box (Yi I)

	
E.07-061305-2-1/8

	
12-F-2-13/2nd Floor Passage/E.07-061305-2-4/8

	
Purifying Area

	
41

	
Trench Lighting Box DGMX

	
From low-voltage distribution cabinet P115 in workshop, to power consumption point of lighting  in trench

	
Distribution System Drawing of Lighting Box (Yi I)

	
E.07-061305-2-1/8

	
10-E-1-29/External Packing/E.07-061305-1-20/22

	
Non Purifying Area

	
42

	
Lighting Box 11MX

	
From low-voltage distribution cabinet P115 in workshop, to power consumption point of lighting  in room around 11MX

	
Distribution System Drawing of Lighting Box (Yi I)

	
E.07-061305-2-1/8

	
11-F-1-13/Central Control Room/E.07-061305-2-6/8

	
Purifying Area

	
43

	
Lighting Box 12MX

	
From low-voltage distribution cabinet P115 in workshop, to power consumption point of lighting  in room around 12MX

	
Distribution System Drawing of Lighting Box (Yi I)

	
E.07-061305-2-1/8

	
9-E-1-27/Aluminum-Plastic External Packing Sterilization /E.07-061305-2-6/8

	
Purifying Area

	
44

	
Lighting Box 13MX

	
From low-voltage distribution cabinet P116 in workshop, to power consumption point of lighting  in room around 13MX

	
Distribution System Drawing of Lighting Box (Yi I)

	
E.07-061305-2-1/8

	
1-C-1-06/Storage after Sterilization/E.07-061305-2-6/8

	
Purifying Area

  

Page 5 of 10

  

 

	
45

	
Lighting Box 14MX

	
From low-voltage distribution cabinet P116 in workshop, to power consumption point of lighting  in room around 14MX

	
Distribution System Drawing of Lighting Box (Yi II)

	
E.07-061305-2-1/8

	
5-C-1-06/Storage after Sterilization/E.07-061305-2-6/8

	
Purifying Area

	
46

	
Lighting Box 15MX

	
From low-voltage distribution cabinet P116 in workshop, to power consumption point of lighting  in room around 15MX

	
Distribution System Drawing of Lighting Box (Yi II)

	
E.07-061305-2-2/8

	
10-F-1-12/Warehouse Management /E.07-061305-2-6/8

	
Purifying Area

	
47

	
Lighting Box 16MX

	
From low-voltage distribution cabinet P116 in workshop, to power consumption point of lighting  in room around 16MX

	
Distribution System Drawing of Lighting Box (Yi II)

	
E.07-061305-2-2/8

	
Ante-room by Stair/E.07-061305-2-6/8

	
Purifying Area

	
48

	
Lighting Box 21MX

	
From low-voltage distribution cabinet P116 in workshop, to power consumption point of lighting  in room around 21MX

	
Distribution System Drawing of Lighting Box (Yi II)

	
E.07-061305-2-2/8

	
13-F-2-03/Pilot Production in Preservation/E.07-061305-2-8/8

	
Purifying Area

	
49

	
Lighting Box 22MX

	
From low-voltage distribution cabinet P116 in workshop, to power consumption point of lighting  in room around 22MX

	
Distribution System Drawing of Lighting Box (Yi II)

	
E.07-061305-2-2/8

	
14-F-2-14/ storage room/E.07-061305-2-8/8

	
Purifying Area

	
50

	
Lighting Box 23MX

	
From low-voltage distribution cabinet P116 in workshop, to power consumption point of lighting  in room around 23MX

	
Distribution System Drawing of Lighting Box (Yi II)

	
E.07-061305-2-2/8

	
13-F-2-01/AC Machine Room/E.07-061305-2-8/8

	
Purifying Area

	
51

	
Power Supply Box 11DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in seed proliferation room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
3-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
52

	
Power Supply Box 12DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in control room and buffer solution preparation room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
1-C-1-13/Control Room/E.07-061305-1-20/22

	
Purifying Area

	
53

	
Power Supply Box 13DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in culture medium preparation room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
1-C-1-14/Culture Medium Preparation/E.07-061305-1-20/22

	
Purifying Area

  

Page 6 of 10

  

 

	
54

	
Power Supply Box 14DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in purifying room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
4-C-1-05/People Air Brake/E.07-061305-1-20/22

	
Purifying Area

	
55

	
Power Supply Box 15DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in seed proliferation room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
7-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
56

	
Power Supply Box 16DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in control room and buffer solution preparation room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
5-C-1-13/Control Room/E.07-061305-1-20/22

	
Purifying Area

	
57

	
Power Supply Box 17DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in purifying room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
8-C-1-05/People Air Brake/E.07-061305-1-20/22

	
Purifying Area

	
58

	
Power Supply Box 18DX

	
From low-voltage distribution cabinet P13 in workshop, to power consumption point in culture medium preparation room

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
5-C-1-14/Culture Medium Preparation/E.07-061305-1-20/22

	
Purifying Area

	
59

	
Power Supply Box 19DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point of lighting in work clothes cleaning room of clean area

	
Distribution System Drawing of Power Supply Box 11~19DX

	
E.07-061305-1-14/22

	
11-D-1-25/Work Clothes Cleaning in Clean Area/E.07-061305-1-20/22

	
Purifying Area

	
60

	
Power Supply Box 22DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption point in preserved pilot production room and machine room

	
Distribution System Drawing of Power Supply Box 22~23DX

	
E.07-061305-1-16/22

	
12-F-2-03/Pilot Production in Preparation/E.07-061305-1-20/22

	
Purifying Area

	
61

	
Power Supply Box 23DX

	
From low-voltage distribution cabinet P14 in workshop, to power consumption points of 3 process technology rooms

	
Distribution System Drawing of Power Supply Box 22~23DX

	
E.07-061305-1-16/22

	
12-F-2-09/Process Technology Room/E.07-061305-1-20/22

	
Purifying Area

	
62

	
Second-Class Load Power Cabinet 11EX

	
From low-voltage distribution cabinet P110 in workshop, to power consumption point in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
3-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

  

Page 7 of 10

  

 

	
63

	
Second-Class Load Power Cabinet 12EX

	
From low-voltage distribution cabinet P110 in workshop, to power consumption point in culture medium preparation room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
1-C-1-14/Culture Medium Preparation/E.07-061305-1-20/22

	
Purifying Area

	
64

	
Second-Class Load Power Cabinet 13EX

	
From low-voltage distribution cabinet P110 in workshop, to power consumption point in cell culture room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
2-C-1-03/Cell Culture Room/E.07-061305-1-20/22

	
Purifying Area

	
65

	
Second-Class Load Power Cabinet 14EX

	
From low-voltage distribution cabinet P110 in workshop, to power consumption point in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
7-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
66

	
Second-Class Load Power Cabinet 15EX

	
From low-voltage distribution cabinet P110 in workshop, to power consumption point in culture medium preparation room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
5-C-1-14/Culture Medium Preparation/E.07-061305-1-20/22

	
Purifying Area

	
67

	
Second-Class Load Power Cabinet 16EX

	
From low-voltage distribution cabinet P110 in workshop, to power consumption point in cell culture room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
6-C-1-03/Cell Culture Room/E.07-061305-1-20/22

	
Purifying Area

	
68

	
Second-Class Load Power Cabinet 17EX

	
From low-voltage distribution cabinet P111 in workshop, to power consumption point in room around 17EX

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
9-B-1-31/Storage/E.07-061305-1-20/22

	
Purifying Area

	
69

	
Second-Class Load Power Cabinet 21EX

	
From low-voltage distribution cabinet P111 in workshop, to power consumption point in balance room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
14-F-2-05/Balance Room/E.07-061305-1-22/22

	
Purifying Area

	
70

	
Second-Class Load Power Cabinet 22EX

	
From low-voltage distribution cabinet P111 in workshop, to power consumption point in physical and chemical analysis room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
14-F-2-13/Physical and Chemical Analysis Room/E.07-061305-1-22/22

	
Purifying Area

	
71

	
Second-Class Load Power Cabinet 23EX

	
From low-voltage distribution cabinet P111 in workshop, to power consumption point in sterilization room and preparation room

	
Distribution System Drawing of Second-Class Load Power Box 11~23ELX

	
E.07-061305-1-17/22

	
14-F-2-16/Sterilization/E.07-061305-1-22/22

	
Purifying Area

  

Page 8 of 10

  

 

 

	
72

	
Second-Class Load Power Cabinet 24EX

	
From low-voltage distribution cabinet P111 in workshop, to power consumption point in culture room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
14-D-2-21/Material Air Brake/E.07-061305-1-22/22

	
Purifying Area

	
73

	
Power Auto Switching Box 21HX

	
From low-voltage distribution cabinet P17 in workshop, to power consumption point in distribution room and maintenance room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
14-F-2-03/Distribution Room/E.07-061305-1-22/22

	
Non Purifying Area

	
74

	
Socket Box 11CX

	
From power supply box 11EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
3-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
75

	
Socket Box 12CX

	
From power supply box 11EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
3-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
76

	
Socket Box 13CX

	
From power supply box 11EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
3-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
77

	
Socket Box 14CX

	
From power supply box 11EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
3-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
78

	
Socket Box 15CX

	
From power supply box 14EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
7-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
79

	
Socket Box 16CX

	
From power supply box 14EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
7-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
80

	
Socket Box 17CX

	
From power supply box 14EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
7-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

  

Page 9 of 10

  

 

 

	
81

	
Socket Box 18CX

	
From power supply box 14EX, to socket box in seed proliferation room

	
Distribution System Drawing of Second-Class Load Power Box 24X Switching Box 21HX

	
E.07-061305-1-18/22

	
7-B-1-03/Seed Proliferation/E.07-061305-1-20/22

	
Purifying Area

	
82

	
Power Cabinet 11LX

	
From low-voltage distribution cabinet P15 in workshop, to power consumption point in control room of 1st floor

	
Distribution System Drawing of Power Cabinet 11~21LX and Switching Cabinet 11HX

	
E.07-061305-1-4/22

	
11-F-1-07/Control Room/E.07-061305-1-20/22

	
Non Purifying Area

	
83

	
Power Cabinet 12LX

	
From low-voltage distribution cabinet P15 in workshop, to power consumption point in chilled water room and circulating water room

	
Distribution System Drawing of Power Cabinet 11~21LX and Switching Cabinet 11HX

	
E.07-061305-1-4/22

	
11-F-1-10/Chilled Water and Circulating Water/E.07-061305-1-20/22

	
Non Purifying Area

	
84

	
Power Cabinet 13LX

	
From low-voltage distribution cabinet P15 in workshop, to power consumption point in normal temperature storehouse

	
Distribution System Drawing of Power Cabinet 11~21LX and Switching Cabinet 11HX

	
E.07-061305-1-4/22

	
10-F-1-12/Warehouse Management/E.07-061305-1-22/22

	
Non Purifying Area

	
85

	
Power Cabinet 21LX

	
From low-voltage distribution cabinet P15 in workshop, to power consumption point for air compressor and dryer of AC machine room

	
Distribution System Drawing of Power Cabinet 11~21LX and Switching Cabinet 11HX

	
E.07-061305-1-4/22

	
13-F-2-01/2nd AC Machine Room/E.07-061305-1-22/22

	
Non Purifying Area

	
86

	
Power Switching Box 11HX

	
From low-voltage distribution cabinet P17 in workshop, to power consumption point for smoke exhaust fan PY11, PY21, PY31, PY41, PY71, PB53, PB63

	
Distribution System Drawing of Power Cabinet 11~21LX and Switching Cabinet 11HX

	
E.07-061305-1-4/22

	
11-F-1-13/2nd AC Machine Room/E.07-061305-1-20/22

	
Non Purifying Area

	  	  	  	  	  	  	  

 

  

Page 10 of 10

Source: [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}, [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}]]