Document:

Unassociated Document

Exhibit 4.8.66 -Design Drawings - Power Consumption – Workshop

	
Bill of Power Consumption in Production Workshop

	
Serial No.

	
Description

	
Unit(KW)

	
Calculating Power(KW)

	
Calculating Current after Compensation

	
Cable Type

	
Remarks

	
A

	
Gross Installed Capacity of Workshop Power

	
1831

	
999

	
1597.75

	
ZR-YJV22-1.0,3x300+1x150

	
Compliance with Actual Needs

	
1

	
Power Supply Box11DX

	
15

	
11

	
20.89

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
2

	
Power Supply Box12DX

	
18

	
13

	
24.69

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
3

	
Power Supply Box13DX

	
13

	
9

	
17.09

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs

	
4

	
Maintanence Box21,22JX

	
20

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
5

	
Power Supply Box15DX

	
15

	
11

	
20.89

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
6

	
Power Supply Box16DX

	
18

	
13

	
24.69

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
7

	
Maintanence Box23,24JX

	
20

	
16

	
30.39

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
8

	
Power Supply Box18DX

	
13

	
9

	
17.09

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs

	
9

	
Power Supply Box19DX

	
28

	
21

	
39.88

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
10

	
Power Supply Box110DX

	
7

	
7

	
13.29

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs

	
11

	
Power Supply Box111DX

	
20

	
15

	
28.49

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
12

	
Power Supply Box112DX

	
12

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
13

	
Power Supply Box113DX

	
77

	
49

	
93.06

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs

	
14

	
Power Supply Box114DX

	
20

	
15

	
28.49

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
15

	
Power Supply Box116DX

	
54

	
19

	
36.09

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
16

	
Power Supply Box117DX

	
14

	
11

	
20.89

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
17

	
Power Supply Box21DX

	
20

	
15

	
28.49

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
18

	
Power Supply Box22DX

	
18

	
14

	
26.59

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
19

	
Power Supply Box23DX

	
22

	
12

	
22.79

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
20

	
Power Cabinet11LX

	
38

	
32

	
60.78

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs

	
21

	
Power Cabinet12LX

	
115

	
97

	
184.23

	
ZR-YJV22-1.0,3x95+2x50

	
Compliance with Actual Needs

	
22

	
Power Cabinet13LX

	
35

	
26

	
49.38

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
23

	
Power Cabinet21LX

	
103

	
87

	
165.23

	
ZR-YJV22-1.0,3x95+2x50

	
Compliance with Actual Needs

	
24

	
Maintanence Box25,26JX

	
20

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
25

	
CIP Washing Unit

	
28.5

	
28.5

	
54.13

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs

	
26

	
CIP Washing Unit

	
15.5

	
15.5

	
29.44

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
27

	
Cleaning Machine of Instruments

	
10.65

	
10.65

	
20.23

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
28

	
Sterilizing Cabinet

	
9

	
8

	
15.19

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
29

	
Sterilizing Cabinet

	
9

	
8

	
15.19

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
30

	
Cleaning Machine

	
10.65

	
15.5

	
29.44

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
31

	
Cleaning Machine

	
10.65

	
15.5

	
29.44

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
32

	
Sterilizing Cabinet

	
11.5

	
10.35

	
19.66

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
33

	
Drying Box

	
20

	
18

	
34.19

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
34

	
Elevator

	
7.5

	
7.5

	
14.24

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

  

第 1 页,共 3 页

 

 

 

Bill of Power Consumption in Production Workshop

	
35

	
Switching Cabinet11HX

	
46

	
46

	
87.36

	
ZR-YJV22-1.0,3x50+2x25

	
Compliance with Actual Needs

	
36

	
Switching Cabinet21HX

	
10

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
37

	
Freezing Machine

	
189

	
189

	
358.96

	
ZR-YJV22-1.0,3x240+2x120

	
Compliance with Actual Needs

	
38

	
Freezing Machine

	
189

	
189

	
358.96

	
ZR-YJV22-1.0,3x240+2x120

	
Compliance with Actual Needs

	
39

	
Freezing Machine

	
98

	
98

	
186.12

	
ZR-YJV22-1.0,3x150+2x70

	
Compliance with Actual Needs

	
40

	
Process Second-Class Load

	
442

	  	  	  	  
	
B

	
Gross Capacity of Second-Class Load in Process

	
442

	
276

	
530.82

	
ZR-YJV22-1.0,3x150+1x70

	
Compliance with Actual Needs

	
1

	
Power Supply Box11EX

	
24

	
18

	
34.18

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
2

	
Power Supply Box12EX

	
27

	
20

	
37.98

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
3

	
Power Supply Box13EX

	
33

	
25

	
47.48

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
4

	
Power Supply Box14EX

	
24

	
20

	
37.98

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
5

	
Power Supply Box15EX

	
27

	
20

	
37.98

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
6

	
Power Supply Box16EX

	
33

	
25

	
47.48

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
7

	
Power Supply Box17EX

	
16

	
14

	
26.59

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
8

	
Power Supply Box21EX

	
24

	
18

	
34.18

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs

	
9

	
Power Supply Box22EX

	
33

	
25

	
47.48

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
10

	
Power Supply Box23EX

	
22

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
11

	
Power Supply Box24EX

	
12

	
12

	
22.79

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
12

	
Power Cabinet11~13ELX

	
21

	
17

	
32.29

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
13

	
Power Cabinet21ELX

	
2

	
2

	
3.8

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs

	
14

	
Power Cabinet22ELX

	
23

	
23

	
43.68

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
15

	
Tunnel Oven

	
33

	
33

	
62.67

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs

	
16

	
Capping Machine

	
10

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
17

	
Power Supply Box14DX

	
22

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
18

	
Power Supply Box17DX

	
22

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
19

	
HPLC

	
17

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
20

	
HPLC

	
17

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
C

	
Gross Capacity of Air Conditioning Load in Workshop

	
316

	
253

	
480.51

	
ZR-YJV22-1.0,3x240+2x120

	
Compliance with Actual Needs

	
1

	
Power Cabinet11KX

	
26

	
26

	
49.38

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs

	
2

	
Power Cabinet12KX

	
33

	
33

	
62.67

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs

	
3

	
Power Cabinet13KX

	
30

	
30

	
56.98

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs

	
4

	
Power Cabinet14KX

	
48

	
48

	
91.16

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs

	
5

	
Power Cabinet15KX

	
41

	
41

	
77.87

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs

	
6

	
Power Cabinet16KX

	
40

	
40

	
75.97

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs

	
7

	
Power Cabinet11KHX

	
30

	
30

	
56.98

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs

	
8

	
Power Cabinet12KHX

	
68

	
68

	
129.15

	
ZR-YJV22-1.0,3x70+2x35

	
Compliance with Actual Needs

  

第 2 页,共 3 页

 

 

 

Bill of Power Consumption in Production Workshop

	
D

	
Gross Capacity of Lighting Load in Workshop

	
122

	
104

	
185.9

	
ZR-YJV22-1.0,3x185+1x95

	
Compliance with Actual Needs

	
1

	
Lighting Box11MHX

	
9

	
9

	
16.09

	
NH-VV-1.0,5x6

	
Compliance with Actual Needs

	
2

	
Lighting Box21MHX

	
6

	
6

	
10.73

	
NH-VV-1.0,5x4

	
Compliance with Actual Needs

	
3

	
Lighting BoxDGMX

	
11

	
11

	
19.66

	
ZR-VV-1.0,5x6

	
Compliance with Actual Needs

	
4

	
Lighting Box11MX

	
5

	
5

	
8.94

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs

	
5

	
Lighting Box12MX

	
9

	
9

	
16.09

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs

	
6

	
Lighting Box13MX

	
12

	
12

	
21.15

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs

	
7

	
Lighting Box14MX

	
12

	
12

	
21.15

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs

	
8

	
Lighting Box15MX

	
8

	
8

	
14.3

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs

	
9

	
Lighting Box16MX

	
7

	
7

	
12.51

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs

	
10

	
Lighting Box21MX

	
16

	
16

	
28.6

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs

	
11

	
Lighting Box22MX

	
16

	
16

	
28.6

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs

	
12

	
Lighting Box23MX

	
11

	
11

	
19.66

	
ZR-VV-1.0,5x6

	
Compliance with Actual Needs

	
E

	
Gross Capacity of Second-Class Load in Workshop

	
614

	
425

	
807.17

	
ZR-YJV22-1.0,3x240+1x120

	
Compliance with Actual Needs

	
1

	
Switching Cabinet11HX

	
46

	
46

	
87.36

	
ZR-YJV22-1.0,3x50+2x25

	
Compliance with Actual Needs

	
2

	
Switching Cabinet21HX

	
10

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs

	
3

	
Lighting Box11MHX

	
9

	
9

	
16.09

	
NH-VV-1.0,5x6

	
Compliance with Actual Needs

	
4

	
Lighting Box21MHX

	
6

	
6

	
10.73

	
NH-VV-1.0,5x4

	
Compliance with Actual Needs

	
5

	
Power Cabinet11KHX

	
30

	
30

	
56.98

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs

	
6

	
Power Cabinet12KHX

	
68

	
68

	
129.15

	
ZR-YJV22-1.0,3x70+2x35

	
Compliance with Actual Needs

	
7

	
Process Second-Class Load

	
445

	  	  	  	  
	  	  	  	  	  	  	  
	
Note: Gross Capacity of Whole Workshop =A+C+D+E-445=1831+316+122+614-445=2883 KW

	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  

 

  

第 3 页,共 3 页Unassociated Document

Exhibit 4.8.67 -Design Drawings -Room Parameters

 

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

 

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of

Lamps &

lanterns

	
Current Qty of

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	  	
1st Floor

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
11-F-1-01

	
Foyer, Lobby

	  	  	  	  	  	  	
11

	
4

	  	  	  	  	  	  	  
	
11-F-1-02

	
Stair

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
11-F-1-03

	
Lady’s Room

	  	  	  	  	  	  	
3

	  	  	  	  	  	  	  	  
	
11-F-1-04

	
Gentlemen’s Room

	  	  	  	  	  	  	
3

	  	  	  	  	  	  	  	  
	
11-F-1-05

	
Ante-Room

	  	  	  	  	  	  	
3

	  	  	  	  	  	  	  	  
	
11-F-1-06

	
Steam Decompression

	  	  	  	  	  	  	
2

	  	  	  	  	  	  	  	  
	
11-F-1-07

	
Control Room

	  	  	  	  	  	  	
1

	
1

	  	  	  	  	
2

	  	  
	
11-F-1-08

	
Purifying Water, Injection Water

	  	  	  	  	  	  	
18

	  	  	  	  	  	  	
18

	
18

	
11-F-1-09

	
Stair

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
11-F-1-10

	
Chilled Water, Circulating Water, Compressed Air

	  	  	  	  	  	  	
12

	  	  	  	  	  	  	
12

	
12

	
11-F-1-11

	
Emergency Door

	  	  	  	  	  	  	
1

	  	  	  	  	  	  	
1

	
1

	
11-F-1-12

	
Gas Cylinder Room

	
12

	
4.9

	
58.8

	  	
200

	
588

	
4

	  	  	  	  	  	  	
3

	
4

	
11-F-1-13

	
Central Control Room

	
4.4

	
3.8

	
16.72

	  	
150

	
125.4

	
3

	
1

	  	  	  	  	
6

	
4

	
4

	
11-F-1-14

	
Changing Shoes

	
6.2

	
3.5

	
21.7

	  	
150

	
162.8

	
1

	
1

	  	  	  	  	  	
2

	
2

	
11-F-1-15

	
Changing Clothes

	
12

	
3.5

	
42

	  	
150

	
315

	
3

	
2

	  	  	  	  	  	
4

	
5

	
11-F-1-16

	
Changing Clothes

	
11

	
4.2

	
46.2

	  	
150

	
346.5

	
4

	
2

	  	  	  	  	  	
4

	
6

	
11-F-1-17

	
Changing Clothes

	
4.6

	
3.5

	
16.1

	  	
150

	
120.8

	
1

	
1

	  	  	  	  	
1

	
1

	
2

	
11-F-1-18

	
Changing Clothes

	
4.6

	
4.2

	
19.32

	  	
150

	
144.9

	
1

	
1

	  	  	  	  	
1

	
1

	
2

	
11-F-1-19

	  	
4.3

	
2

	
8.6

	  	
150

	
64.5

	  	
1

	  	  	  	  	  	
1

	
1

	
11-D-1-20

	
People Air Brake

	
2.6

	
1.8

	
4.68

	  	
200

	
46.8

	  	
1

	  	  	  	  	
1

	
1

	
1

	
SUNTEC

	
1 /12

	
2009-3-5

 

  

  

  

 

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
11-C-1-21

	
People Air Brake

	
2.7

	
1.8

	
4.86

	  	
200

	
48.6

	  	
1

	  	  	  	  	
1

	
1

	
1

	
11-C-1-22

	
Work Clothes Storage in Clean Area

	
6

	
3

	
18

	  	
200

	
180

	
1

	
1

	  	  	  	  	
3

	
2

	
2

	
11-C-1-23

	
Exit Air Brake

	
1.7

	
1.5

	
2.55

	  	
200

	
25.5

	  	
1

	  	  	  	  	  	
1

	
1

	
11-D-1-24

	
Exit Air Brake

	
1.7

	
1.5

	
2.55

	  	
200

	
25.5

	  	
1

	  	  	  	  	  	
1

	
1

	
11-D-1-25

	
Work Clothes Cleaning in Clean Area

	
6

	
5

	
30

	  	
200

	
300

	
4

	
2

	  	  	  	  	
7

	
6

	
6

	
11-E-1-26

	
Hygiene Instruments Cleaning

	
2

	
1.8

	
3.6

	  	
150

	
27

	
1

	  	  	  	  	  	  	
1

	
1

	
11-E-1-27

	
Hygiene Instruments Storage

	
2

	
2

	
4

	  	
150

	
30

	
1

	  	  	  	  	  	  	
1

	
1

	
11-E-1-28

	
Work Clothes Cleaning in General Area

	
6.5

	
2.7

	
17.55

	  	
150

	
131.6

	
2

	  	  	  	  	  	
6

	
2

	
2

	
11-E-1-29

	
Maintenance Room

	
8.2

	
2.7

	
22.14

	  	
150

	
166.1

	
3

	  	  	  	  	  	  	
3

	
3

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
10-E-1-01

	
Liquid Nitrogen

	
2.7

	
1.9

	
5.13

	  	
150

	
38.48

	
1

	  	  	  	  	  	  	
1

	
1

	
10-E-1-02

	
Seed Bank

	
2.7

	
2.2

	
5.94

	  	
150

	
44.55

	
1

	  	  	  	  	  	  	
1

	
1

	
10-F-1-03

	
Normal Temperature Storehouse

	
28

	
21

	
588

	  	
200

	
5880

	
36

	
12

	  	  	  	  	  	
48

	
48

	
10-D-1-04

	
People Air Brake

	
2.6

	
1.7

	
4.42

	  	
200

	
44.2

	
1

	  	  	  	  	  	
1

	
1

	
1

	
10-D-1-05

	
Material Purifying

	
3.6

	
2.2

	
7.92

	  	
200

	
79.2

	
1

	  	  	  	  	  	
1

	
1

	
1

	
10-C-1-06

	
People Air Brake

	
4

	
1.7

	
6.8

	  	
200

	
68

	
1

	  	  	  	  	  	
1

	
1

	
1

	
10-C-1-07

	
Weighting & Sampling Room

	
4

	
3.4

	
13.6

	  	
300

	
204

	  	  	
1

	
1

	  	  	
3

	
2

	
2

	
10-F-1-08

	
Original Solution Bank

	
7.6

	
3.7

	
28.12

	  	
200

	
281.2

	  	  	
1

	
1

	  	  	
10

	
2

	
2

	
10-F-1-09

	
Refrigerator for Special Packing Products

	
12

	
7.6

	
91.2

	  	  	  	  	  	  	  	  	  	  	  	  
	
10-F-1-10

	
Refrigerator for Raw Materials

	
7.6

	
4.3

	
32.68

	  	  	  	  	  	  	  	  	  	  	  	  
	
10-F-1-11

	
Buffering

	
7.6

	
2.8

	
21.28

	  	
150

	
159.6

	
1

	
1

	  	  	  	  	  	
2

	
2

	
SUNTEC

	
2 /12

	
2009-3-5

  

  

  

 

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
10-F-1-12

	
Warehouse Management

	
7.6

	
3.5

	
26.6

	  	
150

	
199.5

	
1

	
1

	  	  	  	  	
4

	
2

	
2

	
10-F-1-13

	
Relay

	
11

	
5.9

	
64.9

	  	
150

	
486.8

	  	  	
4

	
2

	  	  	  	
6

	
6

	
10-F-1-14

	
Outer Packing Removal Area

	
5.9

	
3.2

	
18.88

	  	
150

	
141.6

	
1

	
1

	  	  	  	  	  	
2

	
2

	
10-F-1-15

	
Buffering

	
2

	
1.8

	
3.6

	  	
150

	
27

	
1

	  	  	  	  	  	  	
1

	
1

	
10-F-1-16

	
Hygiene Instruments

	
2

	
1.7

	
3.4

	  	
150

	
25.5

	  	  	  	  	  	  	  	  	  
	
10-F-1-17

	
Bathroom

	
2

	
1.9

	
3.8

	  	
150

	
28.5

	  	  	  	  	  	  	  	  	  
	
10-F-1-18

	
Dangerous Cargo Warehouse

	
5.6

	
5.9

	
33.04

	  	
200

	
330.4

	
4

	
4

	  	  	  	  	  	
4

	
4

	
10-F-1-19

	
No.1 Stair

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
10-F-1-20

	  	
2.5

	
2.5

	
6.25

	  	  	  	  	  	  	  	  	  	  	  	  
	
10-F-1-23

	
Shipping Area

	
10

	
8.5

	
85

	  	
150

	
637.5

	
8

	  	  	  	  	  	
3

	
8

	
8

	
10-F-1-24

	
Buffering

	
3.7

	
2.9

	
10.73

	  	
150

	
80.48

	
1

	  	  	  	  	  	  	
1

	
1

	
10-F-1-25

	
Refrigerator

	
4.8

	
3.7

	
17.76

	  	  	  	  	  	  	  	  	  	  	  	  
	
10-F-1-26

	
Auxiliary Machine

	
3.7

	
2

	
7.4

	  	
150

	
55.5

	
1

	  	  	  	  	  	  	
1

	
1

	
10-F-1-27

	
Refrigerator for Finished Products

	
10

	
6.8

	
68

	  	  	  	  	  	  	  	  	  	  	  	  
	
10-F-1-28

	
Refrigerator for Finished Products

	
9.5

	
9.2

	
87.4

	  	  	  	  	  	  	  	  	  	  	  	  
	
10-F-1-29

	
Outer Packing

	
9.5

	
9

	
85.5

	  	
300

	
1283

	  	  	
10

	
5

	  	  	
8

	
15

	
15

	
10-F-1-30

	
Coding Room

	
7.9

	
4

	
31.6

	  	
200

	
316

	  	  	
2

	
1

	  	  	
4

	
3

	
4

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
9-D-1-01

	
Material Air Brake

	
2.4

	
1.9

	
4.56

	  	
200

	
45.6

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-02

	
Material Air Brake

	
2.5

	
1.9

	
4.75

	  	
200

	
47.5

	  	
1

	  	  	  	  	  	
1

	
1

	
9-D-1-03

	
People Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	
1

	
1

	
1

	
SUNTEC

	
3 /12

	
2009-3-5

 

  

  

  

 

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

 

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
9-C-1-04

	
People Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	
1

	
1

	
1

	
9-B-1-05

	
Material Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	  	
1

	
1

	
9-B-1-06

	
People Air Brake

	
2.7

	
2.1

	
5.67

	  	
200

	
56.7

	  	
1

	  	  	  	  	
1

	
1

	
1

	
9-B-1-07

	
Storage

	
2.8

	
2.6

	
7.28

	  	
200

	
72.8

	  	
1

	  	  	  	  	
1

	
1

	
1

	
9-B-1-08

	
Solution Dosing

	
3.7

	
3

	
11.1

	  	
300

	
166.5

	  	  	
1

	
1

	  	  	  	
2

	
2

	
9-B-1-09

	
Exit Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-10

	
Exit Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	  	
1

	
1

	
9-D-1-11

	
Exit Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	  	
1

	
1

	
9-B-1-12

	
Filling and Capping of Vials

	
7.9

	
5

	
39.5

	  	
300

	
592.5

	  	  	
6

	
2

	  	  	
3

	
8

	
8

	
9-B-1-13

	
Exit Air Brake

	
1.9

	
1.6

	
3.04

	  	
200

	
30.4

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-14

	
Exit Air Brake

	
1.6

	
1.6

	
2.56

	  	
200

	
25.6

	  	
1

	  	  	  	  	  	
1

	
1

	
9-D-1-15

	
Walkway

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
9-D-1-16

	
Air Brake

	
1.9

	
1.7

	
3.23

	  	
200

	
32.3

	  	
1

	  	  	  	  	  	
1

	
1

	
9-E-1-17

	
Light Testing, Labeling

	
10

	
4

	
40

	  	
300

	
600

	
6

	
2

	  	  	  	  	
6

	
8

	
8

	
9-D-1-17

	
Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-18

	
Cleaning and Sterilization of Vials

	
6.2

	
5.4

	
33.48

	  	
300

	
502.2

	  	  	  	  	
4

	
2

	
4

	
6

	
6

	
9-C-1-19

	
People Air Brake

	
2.7

	
1.8

	
4.86

	  	
200

	
48.6

	  	
1

	  	  	  	  	
1

	
1

	
1

	
9-C-1-20

	
Material Air Brake

	
2.7

	
1.8

	
4.86

	  	
200

	
48.6

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-21

	
Cleaning Tools Storage

	
5.1

	
2.7

	
13.77

	  	
200

	
137.7

	
2

	  	  	  	  	  	
2

	
1

	
2

	
9-C-1-22

	
Exit Air Brake

	
1.8

	
1.8

	
3.24

	  	
200

	
32.4

	  	
1

	  	  	  	  	  	
1

	
1

	
9-D-1-23

	
Washing

	
5.2

	
3.6

	
18.72

	  	
200

	
187.2

	
2

	  	  	  	  	  	
2

	
2

	
2

	
SUNTEC

	
4 /12

	
2009-3-5

 

  

  

  

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
9-C-1-24

	
Exit Air Brake

	
5.2

	
1.7

	
8.84

	  	
200

	
88.4

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-25

	
Clean Walkway in Area C

	  	  	
0

	  	  	  	  	  	  	  	  	  	  	  	  
	
9-C-1-26

	
Temporary Storage of Inner Packing Materials

	
10

	
1.9

	
19

	  	
200

	
190

	
2

	
1

	  	  	  	  	
2

	
3

	
3

	
9-E-1-27

	
Aluminum-Plastic Packing

	
10

	
6

	
60

	  	
300

	
900

	  	  	
8

	
4

	  	  	
5

	
12

	
12

	
9-C-1-28

	
Labeling, Light Testing

	
8

	
6

	
48

	  	
300

	
720

	  	  	
5

	
3

	  	  	
5

	
8

	
8

	
9-C-1-29

	
Exit Air Brake

	
1.75

	
1.7

	
2.975

	  	
200

	
29.75

	  	
1

	  	  	  	  	  	
1

	
1

	
9-B-1-30

	
People Air Brake

	
2

	
1.9

	
3.8

	  	
200

	
38

	  	
1

	  	  	  	  	
1

	
1

	
1

	
9-B-1-31

	
Storage

	
1.9

	
1.9

	
3.61

	  	
200

	
36.1

	  	
1

	  	  	  	  	  	
1

	
1

	
9-B-1-32

	
Pre-Filling Syringe Filling

	
5.5

	
4.2

	
23.1

	  	
300

	
346.5

	  	  	
3

	
1

	  	  	
4

	
4

	
4

	
9-B-1-33

	
Material Air Brake

	
1.9

	
1.9

	
3.61

	  	
200

	
36.1

	  	
1

	  	  	  	  	  	
1

	
1

	
9-B-1-34

	
People Air Brake

	
1.9

	
1.9

	
3.61

	  	
200

	
36.1

	  	
1

	  	  	  	  	
1

	
1

	
1

	
9-B-1-35

	
Solution Dosing

	
4.2

	
3.9

	
16.38

	  	
300

	
245.7

	  	  	  	  	
1

	
1

	
3

	
2

	
2

	
9-B-1-36

	
Exit Air Brake

	
3.9

	
1.7

	
6.63

	  	
200

	
66.3

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-37

	
Exit Air Brake

	
3

	
1.7

	
5.1

	  	
200

	
51

	  	
1

	  	  	  	  	  	
1

	
1

	
9-C-1-38

	
Preparation of Buffering Solution

	
6

	
3

	
18

	  	
300

	
270

	  	  	
2

	
1

	  	  	
3

	
3

	
3

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
8-C-1-01

	
People Air Brake

	
1.8

	
1.8

	
3.24

	  	
200

	
32.4

	  	
1

	  	  	  	  	
1

	
1

	
1

	
8-C-1-02

	
Material Air Brake

	
3.6

	
1.9

	
6.84

	  	
200

	
68.4

	  	
1

	  	  	  	  	  	
1

	
1

	
8-C-1-03

	
Ultrafiltration

	
7.3

	
6.4

	
46.72

	  	
300

	
700.8

	  	  	  	  	
5

	
2

	
4

	
7

	
7

	
8-C-1-04

	
Material Air Brake

	
2.5

	
1.9

	
4.75

	  	
200

	
47.5

	  	
1

	  	  	  	  	  	
1

	
1

	
8-C-1-05

	
People Air Brake

	
2.1

	
1.9

	
3.99

	  	
200

	
39.9

	  	
1

	  	  	  	  	
1

	
1

	
1

	
SUNTEC

	
5 /12

	
2009-3-5

 

  

  

  

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
8-C-1-06

	
Purification

	
11.6

	
3.5

	
40.6

	  	
300

	
609

	  	  	  	  	
6

	
2

	
8

	
8

	
8

	
8-B-1-07

	
People Air Brake

	
2.5

	
2

	
5

	  	
200

	
50

	  	
1

	  	  	  	  	
1

	
1

	
1

	
8-B-1-08

	
Original Solution

	
3.7

	
3.6

	
13.32

	  	
300

	
199.8

	  	  	
1

	
1

	  	  	
4

	
2

	
2

	
8-B-1-09

	
Exit Air Brake

	
1.8

	
1.7

	
3.06

	  	
200

	
30.6

	  	
1

	  	  	  	  	  	
1

	
1

	
8-C-1-10

	
Exit Air Brake

	
1.8

	
1.7

	
3.06

	  	
200

	
30.6

	  	
1

	  	  	  	  	  	
1

	
1

	
8-D-1-11

	
Exit Walkway in Area D

	  	  	
0

	  	  	  	  	  	  	  	  	  	  	  	  
	
8-D-1-12

	
Air Brake

	
2.6

	
2.4

	
6.24

	  	
200

	
62.4

	  	
1

	  	  	  	  	  	
1

	
1

	
8-E-1-13

	
Hygiene Instruments Cleaning

	
2.6

	
2

	
5.2

	  	
150

	
39

	
1

	  	  	  	  	  	  	
1

	
1

	
8-E-1-14

	
Hygiene Instruments Storage

	
2.6

	
2

	
5.2

	  	
150

	
39

	
1

	  	  	  	  	  	  	
1

	
1

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
7-B-1-01

	
People Air Brake

	
2.3

	
2

	
4.6

	  	
200

	
46

	  	
1

	  	  	  	  	
1

	
1

	
1

	
7-B-1-02

	
Material Air Brake

	
2.3

	
2

	
4.6

	  	
200

	
46

	  	
1

	  	  	  	  	  	
1

	
1

	
7-B-1-03

	
Seed Proliferation

	
17

	
4.3

	
73.1

	  	
300

	
1097

	  	  	  	  	
7

	
3

	
10

	
10

	
10

	
7-B-1-04

	
Exit Air Brake

	
3

	
2.1

	
6.3

	  	
200

	
63

	  	
1

	  	  	  	  	  	
1

	
1

	
7-C-1-05

	
Exit Air Brake

	
2.6

	
2.1

	
5.46

	  	
200

	
54.6

	  	
1

	  	  	  	  	  	
1

	
1

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
6-C-1-01

	
Material Air Brake

	
5.3

	
1.9

	
10.07

	  	
200

	
100.7

	  	
1

	  	  	  	  	  	
1

	
1

	
6-C-1-02

	
People Air Brake

	
5.3

	
1.9

	
10.07

	  	
200

	
100.7

	  	
1

	  	  	  	  	
1

	
1

	
1

	
6-C-1-03

	
Cell Culture Room

	  	  	
0

	  	
300

	
0

	  	  	  	  	
19

	
5

	
52

	
24

	
24

	
6-C-1-04

	
Cold Room

	
19

	
4.9

	
93.1

	  	
300

	
1397

	  	  	  	  	
12

	
4

	  	
16

	
16

	
6-C-1-05

	
Exit Air Brake

	
1.9

	
1.8

	
3.42

	  	
200

	
34.2

	  	  	  	  	  	  	  	  	  

	
SUNTEC

	
6 /12

	
2009-3-5

  

  

  

 

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
5-D-1-01

	
People Air Brake

	
3.5

	
1.9

	
6.65

	  	
200

	
66.5

	  	
1

	  	  	  	  	
1

	
1

	
1

	
5-D-1-02

	
Material Air Brake

	
3.5

	
1.9

	
6.65

	  	
200

	
66.5

	  	
1

	  	  	  	  	  	
1

	
1

	
5-C-1-03

	
People Air Brake

	
4.1

	
1.9

	
7.79

	  	
200

	
77.9

	  	
1

	  	  	  	  	
1

	
1

	
1

	
5-C-1-04

	
Material Air Brake

	
4.1

	
1.9

	
7.79

	  	
200

	
77.9

	  	
1

	  	  	  	  	  	
1

	
1

	
5-C-1-05

	
Clean Walkway in Area C

	  	  	
0

	  	  	  	  	  	  	  	  	  	  	  	  
	
5-C-1-06

	
Storage after Sterilization

	
7.2

	
4.1

	
29.52

	  	
200

	
295.2

	
3

	
1

	  	  	  	  	
2

	
4

	
4

	
5-C-1-07

	
Sterilization

	
7.2

	
5.1

	
36.72

	  	
300

	
550.8

	  	  	
3

	
1

	  	  	
2

	
4

	
4

	
5-C-1-08

	
Storage

	
7.2

	
4.7

	
33.84

	  	
200

	
338.4

	
3

	
1

	  	  	  	  	
2

	
4

	
4

	
5-D-1-09

	
Washing

	
8

	
7.6

	
60.8

	  	
200

	
608

	  	  	
6

	
2

	  	  	
4

	
8

	
8

	
5-D-1-10

	
Material Purifying

	
2.6

	
2.5

	
6.5

	  	
200

	
65

	
1

	  	  	  	  	  	  	
1

	
1

	
5-D-1-11

	
Exit Air Brake

	
2.2

	
1.9

	
4.18

	  	
200

	
41.8

	  	
1

	  	  	  	  	  	
1

	
1

	
5-C-1-12

	
Buffering Solution Dosing室

	
7.2

	
5.3

	
38.16

	  	
300

	
572.4

	  	  	
4

	
2

	  	  	
6

	
6

	
6

	
5-C-1-13

	
Control Room

	
5.3

	
3.5

	
18.55

	  	
200

	
185.5

	  	  	
1

	
1

	  	  	
4

	
2

	
2

	
5-C-1-14

	
Preparation of Culture Medium

	
10.1

	
5.3

	
53.53

	  	
300

	
803

	  	  	
6

	
2

	  	  	
7

	
8

	
8

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
4-C-1-01

	
People Air Brake

	
2.4

	
1.8

	
4.32

	  	
200

	
43.2

	  	
1

	  	  	  	  	
1

	
1

	
1

	
4-C-1-02

	
Material Air Brake

	
3.4

	
1.9

	
6.46

	  	
200

	
64.6

	  	
1

	  	  	  	  	  	
1

	
1

	
4-C-1-03

	
Ultrafiltration

	
7.4

	
2.6

	
19.24

	  	
300

	
288.6

	  	  	  	  	
5

	
2

	
5

	
7

	
7

	
4-C-1-04

	
Material Air Brake

	
2.8

	
1.9

	
5.32

	  	
200

	
53.2

	  	
1

	  	  	  	  	  	
1

	
1

	
4-C-1-05

	
People Air Brake

	
2.4

	
2

	
4.8

	  	
200

	
48

	  	
1

	  	  	  	  	
1

	
1

	
1

	
SUNTEC

	
7 /12

	
2009-3-5

  

  

  

 

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
4-C-1-06

	
Purification

	
12

	
3.5

	
42

	  	
300

	
630

	  	  	
6

	
2

	  	  	
8

	
8

	
8

	
4-B-1-07

	
People Air Brake

	
2.4

	
1.9

	
4.56

	  	
200

	
45.6

	  	
1

	  	  	  	  	  	
1

	
1

	
4-B-1-08

	
Original Solution

	
3.7

	
3.5

	
12.95

	  	
300

	
194.3

	  	  	
1

	
1

	  	  	
4

	
2

	
2

	
4-B-1-09

	
Exit Air Brake

	
1.8

	
1.7

	
3.06

	  	
200

	
30.6

	  	
1

	  	  	  	  	  	
1

	
1

	
4-C-1-10

	
Exit Air Brake

	
1.8

	
1.8

	
3.24

	  	
200

	
32.4

	  	
1

	  	  	  	  	  	
1

	
1

	
4-D-1-11

	
Walkway in Area D

	  	  	
0

	  	  	  	  	  	  	  	  	  	  	  	  
	
4-D-1-12

	
Air Brake

	
2.4

	
2.4

	
5.76

	  	
200

	
57.6

	  	
1

	  	  	  	  	  	
1

	
1

	
4-E-1-13

	
Hygiene Instruments Cleaning

	
2.4

	
1.9

	
4.56

	  	
150

	
34.2

	
1

	  	  	  	  	  	  	
1

	
1

	
4-E-1-14

	
Hygiene Instruments Storage

	
2.4

	
1.9

	
4.56

	  	
150

	
34.2

	
1

	  	  	  	  	  	  	
1

	
1

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
3-B-1-01

	
People Air Brake

	
2.1

	
2

	
4.2

	  	
200

	
42

	  	
1

	  	  	  	  	  	
1

	
1

	
3-B-1-02

	
Material Air Brake

	
2.5

	
2

	
5

	  	
200

	
50

	  	
1

	  	  	  	  	  	
1

	
1

	
3-B-1-03

	
Seed Proliferation

	
17

	
4.7

	
79.9

	  	
300

	
1199

	  	  	  	  	
7

	
3

	
10

	
10

	
10

	
3-B-1-04

	
Exit Air Brake

	
2.8

	
1.7

	
4.76

	  	
200

	
47.6

	  	
1

	  	  	  	  	  	
1

	
1

	
3-B-1-05

	
Exit Air Brake

	
2.7

	
1.7

	
4.59

	  	
200

	
45.9

	  	
1

	  	  	  	  	  	
1

	
1

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
2-C-1-01

	
Material Air Brake

	
5.4

	
1.9

	
10.26

	  	
200

	
102.6

	  	
1

	  	  	  	  	  	
1

	
1

	
2-C-1-02

	
People Air Brake

	
5.4

	
2.2

	
11.88

	  	
200

	
118.8

	  	
1

	  	  	  	  	
1

	
1

	
1

	
2-C-1-03

	
Cell Culture Room

	  	  	
0

	  	
300

	
0

	  	  	  	  	
19

	
5

	
48

	  	  
	
2-C-1-04

	
Cold Room

	
19

	
4.9

	
93.1

	  	
300

	
1397

	  	  	  	  	
12

	
4

	  	
16

	
14

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  

	
SUNTEC

	
8 /12

	
2009-3-5

  

  

  

  

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
1-D-1-01

	
People Air Brake

	
3.5

	
1.9

	
6.65

	  	
200

	
66.5

	  	
1

	  	  	  	  	
1

	
1

	
1

	
1-D-1-02

	
Material Air Brake

	
3.5

	
2.3

	
8.05

	  	
200

	
80.5

	  	
1

	  	  	  	  	  	
1

	
1

	
1-C-1-03

	
People Air Brake

	
3.5

	
1.9

	
6.65

	  	
200

	
66.5

	  	
1

	  	  	  	  	
1

	
1

	
1

	
1-C-1-04

	
Material Air Brake

	
3.5

	
2.3

	
8.05

	  	
200

	
80.5

	  	
1

	  	  	  	  	  	
1

	
1

	
1-C-1-05

	
Clean Walkway in Area C

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
1-C-1-06

	
Storage after Sterilization

	
6.8

	
3.8

	
25.84

	  	
200

	
258.4

	
3

	
1

	  	  	  	  	
2

	
4

	
4

	
1-C-1-07

	
Sterilization

	
6.8

	
4.3

	
29.24

	  	
300

	
438.6

	  	  	
3

	
1

	  	  	
2

	
4

	
4

	
1-C-1-08

	
Storage

	
6.8

	
4.8

	
32.64

	  	
200

	
326.4

	
3

	
1

	  	  	  	  	
2

	
4

	
4

	
1-D-1-09

	
Washing

	
8

	
6.8

	
54.4

	  	
200

	
544

	  	  	
6

	
2

	  	  	
4

	
8

	
8

	
1-E-1-10

	
Material Purifying

	
2.5

	
2.4

	
6

	  	
200

	
60

	
1

	  	  	  	  	  	  	
1

	
1

	
1-C-1-11

	
Exit Air Brake

	
2.5

	
1.9

	
4.75

	  	
200

	
47.5

	  	
1

	  	  	  	  	  	
1

	
1

	
1-C-1-12

	
Preparation of Buffering Solution

	
6.2

	
5.4

	
33.48

	  	
300

	
502.2

	  	  	
4

	
2

	  	  	
6

	
6

	
6

	
1-C-1-13

	
Control Room

	
5.4

	
3.2

	
17.28

	  	
200

	
172.8

	  	  	
1

	
1

	  	  	
4

	
2

	
2

	
1-C-1-14

	
Preparation of Culture Medium

	
11

	
5.3

	
58.3

	  	
300

	
874.5

	  	  	
6

	
2

	  	  	
7

	
8

	
8

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	  	
2nd Floor

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
12-F-2-01

	
Pilot Production in Preservation

	
18.6

	
16.5

	
306.9

	  	
300

	
4604

	  	  	
33

	
9

	  	  	  	
42

	
42

	
12-F-2-03

	
Pilot Production in Preservation

	
18.6

	
16.5

	
306.9

	  	
300

	
4604

	  	  	
33

	
9

	  	  	  	
42

	
42

	
12-F-2-04

	
Instrument Room

	
6

	
3.6

	
21.6

	  	
200

	
216

	
3

	
1

	  	  	  	  	
3

	
4

	
4

	
12-F-2-05

	
Instrument Room

	
7.1

	
3.6

	
25.56

	  	
200

	
255.6

	
3

	
1

	  	  	  	  	
4

	
4

	
4

	
12-F-2-06

	
Instrument Room

	
5.3

	
3.6

	
19.08

	  	
200

	
190.8

	
3

	
1

	  	  	  	  	
3

	
4

	
4

	
SUNTEC

	
9 /12

	
2009-3-5

  

  

  

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
12-F-2-07

	
Process Technology Room

	
10.2

	
10

	
102

	  	
200

	
1020

	  	  	
12

	
4

	  	  	
11

	
25

	
16

	
12-F-2-08

	
Process Technology Room

	
8.3

	
4

	
33.2

	  	
200

	
332

	
6

	
2

	  	  	  	  	
6

	
8

	
8

	
12-F-2-09

	
Process Technology Room

	
8.3

	
5.8

	
48.14

	  	
200

	
481.4

	
10

	
2

	  	  	  	  	
6

	
12

	
12

	
12-F-2-11

	
Anteroom for Washroom

	  	  	  	  	  	  	  	  	
3

	  	  	  	  	
3

	
3

	
12-F-2-12

	
Anteroom for Washroom

	  	  	  	  	  	  	  	  	
3

	  	  	  	  	
3

	
3

	
12-F-2-13

	
Clean Walkway

	  	  	  	  	  	  	  	  	  	  	  	  	  	
35

	
54

	
12-F-2-14

	
Drinking Room

	
4.8

	
2.4

	
11.52

	  	
200

	
115.2

	
2

	  	  	  	  	  	  	
1

	
2

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
14-F-2-01

	
Changing Clothes

	
5

	
2.4

	
12

	  	
200

	
120

	
2

	  	  	  	  	  	
1

	
1

	
2

	
14-F-2-02

	
Changing Clothes

	
5

	
2.4

	
12

	  	
200

	
120

	
2

	  	  	  	  	  	
1

	
1

	
2

	
14-F-2-03

	
Process Technology Room

	
6.8

	
2.4

	
16.32

	  	
200

	
163.2

	  	  	
3

	  	  	  	
6

	
3

	
3

	
14-F-2-04

	
Samples Keeping Room of Raw & Supplementary Materials

	
6.8

	
3.5

	
23.8

	  	
300

	
357

	  	  	  	  	
3

	  	
4

	
3

	
3

	
14-F-2-05

	
Balance Room

	
5.15

	
4.85

	
24.9775

	  	
200

	
249.8

	  	  	
3

	
1

	  	  	
3

	
4

	
4

	
14-F-2-06

	
Reagent Room

	
4.8

	
4.2

	
20.16

	  	
200

	
201.6

	  	  	
3

	
1

	  	  	
3

	
4

	
4

	
14-F-2-07

	
Samples Keeping Room of Products

	
6.8

	
5

	
34

	  	  	  	  	  	  	  	  	  	  	  	  
	
14-F-2-08

	
Clean Walkway

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	
20

	
14-F-2-09

	
Laboratory

	
10.2

	
7.4

	
75.48

	  	
300

	
1132

	  	  	  	  	
8

	
4

	
8

	
12

	
12

	
14-F-2-10

	
Protein Analysis Room

	
10.2

	
7.2

	
73.44

	  	
300

	
1102

	  	  	  	  	
8

	
4

	
5

	
12

	
12

	
14-F-2-11

	
Storage Room

	
4.5

	
6.5

	
29.25

	  	
200

	
292.5

	
4

	  	  	  	  	  	
3

	
4

	
4

	
14-F-2-12

	
Gas Chromatography Room

	
4.5

	
3.6

	
16.2

	  	
200

	
162

	
2

	  	  	  	  	  	
3

	
2

	
2

	
14-F-2-13

	
Physic and Chemistry Analysis Room

	
10.2

	
7.55

	
77.01

	  	
300

	
1155

	  	  	
8

	
4

	  	  	
6

	
12

	
12

	
SUNTEC

	
10 /12

	
2009-3-5

  

  

  

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
14-F-2-14

	
Activity Analysis Room

	
10.2

	
7.2

	
73.44

	  	
300

	
1102

	  	  	
8

	
4

	  	  	
6

	
12

	
12

	
14-F-2-15

	
Preparation Room

	
10.2

	
3.4

	
34.68

	  	
200

	
346.8

	  	  	
2

	
2

	  	  	
2

	
5

	
4

	
14-F-2-16

	
Sterilization

	
7.75

	
4.1

	
31.775

	  	
300

	
476.6

	  	  	
4

	
2

	  	  	
5

	
6

	
6

	
14-F-2-17

	
Rinse

	
7.75

	
6

	
46.5

	  	
300

	
697.5

	  	  	
6

	
3

	  	  	
4

	
9

	
9

	
14-B-2-18

	
Clean-room for Sterile Examination

	
6

	
4

	
24

	  	
300

	
360

	  	  	
3

	
1

	  	  	
5

	
4

	
4

	
14-C-2-19

	
Walkway

	  	  	  	  	  	  	
2

	
2

	  	  	  	  	  	
3

	
4

	
14-C-2-20

	
Material Air Brake

	
2.55

	
2

	
5.1

	  	
200

	
51

	  	
1

	  	  	  	  	  	
1

	
1

	
14-D-2-21

	
Material Air Brake

	
2.4

	
2

	
4.8

	  	
200

	
48

	  	
1

	  	  	  	  	  	
1

	
1

	
14-C-2-22

	
People Air Brake

	
2.3

	
2

	
4.6

	  	
200

	
46

	  	
1

	  	  	  	  	
1

	
1

	
1

	
14-D-2-23

	
People Air Brake

	
2.28

	
2

	
4.56

	  	
200

	
45.6

	  	
1

	  	  	  	  	
1

	
1

	
1

	
14-F-2-24

	
Culture Room

	
6

	
5.2

	
31.2

	  	
300

	
468

	  	  	
4

	
2

	  	  	
6

	
6

	
6

	
14-F-2-25

	
Activity Detection Room

	
10

	
3.6

	
36

	  	
300

	
540

	  	  	  	  	
3

	
2

	
4

	
5

	
5

	
14-C-2-26

	
Instrument Storage

	
4.1

	
3.2

	
13.12

	  	
200

	
131.2

	
2

	  	  	  	  	  	
2

	
1

	
1

	
14-C-2-27

	
Clean-room for Microbial Limit Testing

	
4

	
3.75

	
15

	  	
300

	
225

	  	  	
3

	
1

	  	  	
4

	
2

	
4

	
14-C-2-28

	
Enter Air Brake

	
2.1

	
1.7

	
3.57

	  	
200

	
35.7

	  	
1

	  	  	  	  	  	
1

	
1

	
14-B-2-29

	
Enter Air Brake

	
1.85

	
1.7

	
3.145

	  	
200

	
31.45

	  	
1

	  	  	  	  	  	
1

	
1

	
14-B-2-30

	
Exit Air Brake

	
1.85

	
1.8

	
3.33

	  	
200

	
33.3

	  	
1

	  	  	  	  	  	
1

	
1

	
14-C-2-31

	
Exit Air Brake

	
2

	
1.9

	
3.8

	  	
200

	
38

	  	
1

	  	  	  	  	  	
1

	
1

	
14-D-2-32

	
Exit Air Brake

	
1.8

	
1.8

	
3.24

	  	
200

	
32.4

	  	
1

	  	  	  	  	  	
1

	
1

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
13-F-2-01

	
Air Conditioning Machine Room

	  	  	  	  	  	  	  	  	  	  	  	  	  	
86

	
86

	
SUNTEC

	
11 /12

	
2009-3-5

  

  

  

	  	
Parameter List of Major Rooms

	

	
Date:

	
2009-3-5

	
Project Name: Production Workshop of Sunshine

	
by:

	
Wei Xiangjun

	
Doc. No.: P558

	
No.

	
Room Name

	
Length

	
Width

	
Area

	
Height

	  	  	
2X28

	
2X28E

	
3X28

	
3X28E

	
4X28

	
4X28E

	
Socket

	
Original Qty of 

Lamps & 

lanterns

	
Current Qty of 

Lamps & lanterns

	
Lux

	
W

	
A

	
B

	
m2

	
m

	  	  	  	  	  	  	  	  	  
	
13-F-2-02

	
Maintenance Room

	
9.7

	
7.1

	
68.87

	  	  	  	
9

	  	  	  	  	  	
9

	
9

	
9

	
13-F-2-03

	
Distribution Room

	
9.7

	
7.1

	
68.87

	  	  	  	
12

	  	  	  	  	  	
4

	
9

	
12

	
13-F-2-04

	
Relay

	
0

	
0

	
0

	  	  	  	
6

	
2

	  	  	  	  	  	
8

	
8

	  	
 

Note: The table lists electric parameters of major rooms (illuminance, quantity of lamps and lanterns, and quantity of sockets), mainly according to requirements for clean-rooms and relevant provisions. The construction drawings have been through an in-depth secondary design on the basis of the drawings from design institute.

	  
	  	  
	  	  	  	  	  	  	  	  	
240

	
130

	
222

	
85

	
119

	
43

	
457

	
897

	
941

 

	
SUNTEC

	
12 /12

	
2009-3-5

Source: [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}, [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}]]