Document:

Unassociated Document

Exhibit 4.8.13 - Electronic Catalogue (6) – NBG125-80-160-167

   

	
Description

	
Value

	

	
Product Name:

	
NBG 125-80-160/167 A-F-A BAQE

	
Product No:

	
95106014

	
EAN No:

	
5700836555440

	  	  
	
Technology:

	  
	
Pump speed data

	
2945 rpm

	
Real calculated flow rate

	
200.1 m3/H

	
pump lift

	
28.5 m

	
Real blade diameter

	
167mm

	
Shaft seal

	
BAQE

	
Shaft diameter

	
32mm

	
Curve tolerance

	
ISO 9906 Annex A

	
Edition of pump

	
A

	  	  
	
Material

	  
	
pump body

	
cast iron

	  	
EN-GJL-250 DIN W. – Nr.

	  	
A48-40 B ASTM

	
blade

	
Cast iron

	  	
EN-GJL-250 DIN W. – Nr.

	  	
A48-40 B ASTM

	
Material Code

	
A

	  	  
	
Install

	  
	
Max Environment temperature

	
40°C

	
Max Operation Pressure

	
16

	
Flange Standard

	
EN1092-2

	
Connection Code

	
F

	
Pump inlet

	
DN 125

	
Pump outlet

	
DN 80

	
Pressure Level

	
PN 16

	
occipital ring

	
occipital ring

	  	  
	
Liquid

	  
	
Temperature of Liquid

	
0...120°C

 

  

  

  

 

	
Electric Data:

	  
	
Motor type

	
180M

	
Number of Motor Poles

	
2

	
Rated Power – P2

	
22kw

	
Frequency of Power

	
50Hz

	
Rated voltage

	
3 x 380-415 D / 660-690 Y V

	
Rated current

	
38 / 21.9A

	
Start-up current

	
720%

	
Cos phi-power factor

	
0, 89

	
Rated speed

	
2950 rpm

	
efficiency of mortar in Full load

	
93%

	
efficiency of mortar in 3/4 load

	
93,2%

	
Encapsulation grade (IEC 34-5)

	
IP55

	
Insulation grade (IEC 85)

	
F

	
Motor protection

	
PTC

	
Motor No

	
83A15430

	
Motor series

	
Domestic

	  	  
	
Other

	  
	
Net Weight

	
197kg

	
Gross Weight

	
211kg

	
Transport volume

	
0.725m3Unassociated Document

Exhibit 4.8.14 - Electronic Catalogue (6) – NBG125-100-160-169

 

	
Description

	
Value

	

	
Product Name:

	
NBG 125-100-160/161 A-F-A BAQE

	
Product No:

	
95105171

	
EAN No:

	
5700836546714

	  	  
	
Technology:

	  
	
Pump speed data

	
2950 rpm

	
Real calculated flow rate

	
279 m3/H

	
pump lift

	
26.4 m

	
Real blade diameter

	
169mm

	
Shaft seal

	
BAQE

	
Shaft diameter

	
32mm

	
Curve tolerance

	
ISO 9906 Annex A

	
Edition of pump

	
A

	  	  
	
Material

	  
	
pump body

	
cast iron

	  	
EN-GJL-250 DIN W. – Nr.

	  	
A48-40 B ASTM

	
blade

	
Cast iron

	  	
EN-GJL-250 DIN W. – Nr.

	  	
A48-30 B ASTM

	
Material Code

	
A

	  	  
	
Install

	  
	
Max Environment temperature

	
40°C

	
Max Operation Pressure

	
16

	
Flange Standard

	
EN1092-2

	
Connection Code

	
F

	
Pump inlet

	
DN 125

	
Pump outlet

	
DN 100

	
Pressure Level

	
PN 16

	
occipital ring

	
occipital ring

	  	  
	
Liquid

	  
	
Temperature of Liquid

	
0...120°C

	  

 

  

  

  

 

	
Electric Data:

	  
	
Motor type

	
MMG200L

	
Number of Motor Poles

	
2

	
Rated Power – P2

	
30kw

	
Frequency of Power

	
50Hz

	
Rated voltage

	
3 x 380-415 D / 660-690 Y V

	
Rated current

	
53.3 / 31A

	
Start-up current

	
720%

	
Cos phi-power factor

	
0, 88

	
Rated speed

	
2950 rpm

	
efficiency of mortar in Full load

	
91,4%

	
efficiency of mortar in 3/4 load

	
92,1%

	
efficiency of mortar in 1/2 load

	
91,3%

	
Encapsulation grade (IEC 34-5)

	
IP55

	
Insulation grade (IEC 85)

	
F

	
Motor protection

	
PTC

	
Motor No

	
83315432

	
Motor series

	
Domestic

	  	  
	
Other

	  
	
Net Weight

	
335kg

	
Gross Weight

	
353kg

	
Transport volume

	
0.725m3Unassociated Document

Exhibit 4.8.15 - Electronic Catalogue (6) – NBG125-80-160-161

 

	
Description

	
Value

	

	
Product Name:

	
NBG 125-80-160/161 A-F-A BAQE

	
Product No:

	
95105153

	
EAN No:

	
5700836546530

	  	  
	
Technology:

	  
	
Pump speed data

	
2940 rpm

	
Real calculated flow rate

	
147 m3/H

	
pump lift

	
29.2 m

	
Real blade diameter

	
161mm

	
Shaft seal

	
BAQE

	
Shaft diameter

	
32mm

	
Curve tolerance

	
ISO 9906 Annex A

	
Edition of pump

	
A

	  	  
	
Material

	  
	
pump body

	
cast iron

	  	
EN-GJL-250 DIN W. – Nr.

	  	
A48-40 B ASTM

	
blade

	
Cast iron

	  	
EN-GJL-250 DIN W. – Nr.

	  	
A48-40 B ASTM

	
Material Code

	
A

	  	  
	
Install

	  
	
Max Environment temperature

	
40°C

	
Max Operation Pressure

	
16

	
Flange Standard

	
EN1092-2

	
Connection Code

	
F

	
Pump inlet

	
DN 125

	
Pump outlet

	
DN 80

	
Pressure Level

	
PN 16

	
occipital ring

	
occipital ring

	  	  
	
Liquid

	  
	
Temperature of Liquid

	
0...120°C

 

  

  

  

 

	
Electric Data:

	  
	
Motor type

	
MMG160L

	
Number of Motor Poles

	
2

	
Rated Power – P2

	
18.5kw

	
Frequency of Power

	
50Hz

	
Rated voltage

	
3 x 380-415 D / 660-690 Y V

	
Rated current

	
33 / 19.2A

	
Start-up current

	
720%

	
Cos phi-power factor

	
0, 90

	
Rated speed

	
2940 rpm

	
efficiency of mortar in Full load

	
90,0%

	
efficiency of mortar in 3/4 load

	
90,8%

	
efficiency of mortar in 1/2 load

	
90,1%

	
Encapsulation grade (IEC 34-5)

	
IP55

	
Insulation grade (IEC 85)

	
F

	
Motor protection

	
PTC

	
Motor No

	
83315428

	
Motor series

	
Domestic

	  	  
	
Other

	  
	
Net Weight

	
215kg

	
Gross Weight

	
228kg

	
Transport volume

	
0.725m3Unassociated Document

Exhibit 4.8.19 - Electronic Catalogue (6) – Selection Explanation for SUNTEC Water Pump

三生水泵选择说明:

 

Specification for Selecting Sunshine’s Water Pump

 

	
1、  

	
LB1~2

 

	
设计院参数:

	
Q:187cmh  Parameters from Designing Institute

 

H:24m

P:18.5kw

	
SUNTEC: 

	
Q:187cmh

H:26.1m

P:18.5kw

 

	
2、 

	
LB3~4

 

	
设计院参数:

	
Q:280cmh Parameters from Designing Institute

 

H:24m

P:30kw

	
SUNTEC: 

	
Q:279cmh

H:26.4m

P:30kw

 

	
3、  

	
L2-2~4

 

	
设计院参数:

	
Q:112~192cmh Parameters from Designing Institute

 

H:34~28m

P:22kw

	
SUNTEC: 

	
Q:147cmh

H:29.2m

P:18.5kw

 

	
4、  

	
L1-3~5

 

	
设计院参数:

	
Q:131~225cmh Parameters from Designing Institute

 

H:29.5~24.5m

P:22kw

	
SUNTEC: 

	
Q:170cmh

H:31.5m

P:22kwUnassociated Document

Exhibit 4.8.21 - Electronic Catalogue (7) - NZP-Series NZP Floor-Mounted Expansion Tank

NZP系列落地膨胀水箱

NZP Series Floor Type Expansion Water Tank

 

产品简介

Product Introduction

 

NZG系列囊式自动给水装置已广泛用于住宅、办公科研、宾馆饭店、医院、影院等民用建筑及工矿企业设施的生活、生产及消防供水系统。NZP系列广泛用于热水供应、热水采暖、小区集中供热及空调系统中的落地膨胀水箱。主要适用于:

NZG series bag type automatic water supply device has been widely used in the living, production and fire control water supply systems of residence, office & scientific research, hotels, hospitals, cinemas and other civilian buildings as well as facilities of industrial and mining enterprises. NZP series are widely used in floor type expansion water tank for hot water supply, hot water heating, central heating and air conditioning system in residential quarters. It is Mainly applicable to:

 

●工业及民用建筑的生产、生活、消防供水系统。

Production, living and fire control water supply system of industrial and civil buildings.

 

●热水供应、热水采暖及空调系统的稳压补水。

Steady pressure water makeup for the hot water supply, hot water heating and air condition system.

 

●作为高层建筑给水系统中的水锤噪音消除设备。

Using as the water hammer noise cancellation device of water supply system in high-rise buildings.

 

●旅游设施及旅游景点的喷泉、林场或农业浇灌系统。

Foundation, forest farm or agricultural irrigation system of tourism facilities and tourist sites.

 

●可用潜水泵、深井泵地下取水,用于生产、生活、消防系统。

Use submersible pump and deep-well pump to get water from under the ground to use for the production, living and fire-fighting system.

 

●农村自来水的理想设备;也可作为建筑施工,流动作业中的临时 供水设备。

Using as the ideal device for supplying tap water in rural areas; also using as the temporary water supply device in mobile operational process of building construction.

  

  

  

 

主要特点

Main Characteristics

 

●罐体内装有无毒橡胶囊,水气不接触保证水质不受外界污染,用于有除氧设施的供热系统中可杜绝氧腐蚀现象的发生。

Nontoxic rubber bags are equipped in the tank shell to prevent contacting with water vapor so as to guarantee that the water quality is free from outside contamination; oxygen corrosion could be prevented when it is used in the heating system where deaerating facility is equipped.

 

●密封性能好,一次冲气可长期使用。

Good sealing performance; and it can be used for a long term after inflating one time.

 

●能自动消除管网中的水锤及噪音。

It can automatically abate the water hammer and noise in pipe network.

 

●可取代生活、消防、采暖及空调系统的高位水箱及水塔,有利于结构抗震和建筑美观。

Take the place of the head tank and water tower in living, fire fighting, heating and air conditioning system and be favorable to structure seismic and beauty-view of architecture.

 

●占地面积小、投资少、安装快、操作维修方便。

Small floor area and investment, quick installation, and easy maintenance and operation.

 

●可按用户要求设定系统压力。

System pressure can be set at customer's request.

 

工作原理

Working Principle

 

现以NZP系列落地式膨胀水箱为例说明其工作原理。NZP系列设备由气压罐、定压补水罐、电控柜、压力控制器、安全阀、压力表、阀门及管道等组成的一个完善的全自动定压补水装置。气压水罐由内、外两室组成,内室(橡胶囊内部)为水室。外室(橡胶囊与设备外壳之间)为充满氮气的气室。

Let’s take the NZP series floor type expansion water tank for example to introduce its working principle. NZP series device is a complete fully automatic constant pressure water makeup device composed of air pressure tank, constant pressure water makeup tank, electrical cabinet, pressure controller, safety valve, pressure gauge, valve and pipeline. Air pressure tank is composed of external and internal chambers, with the internal chamber (inside of rubber bag) as the water chamber while the external chamber (the space between rubber bag and device shell) as the air chamber full of nitrogen gas.

  

  

  

该设备采用系统静压作为膨胀水箱内的设计初始压力水头P1,采用保证系统内热水不汽化的压力作为膨胀水箱内运行终端压力水头P2。初始运行时首先启动补水泵向系统及气压罐内的水室中充水,系统充满后多余的水被挤进胶囊内。 因为水的不可压缩性,随着水量的不断增加,水室的体积也不断的扩大而压缩气室,罐内的压力也不断的升高。当压力达到设计压力时,通过压力控制器使补水泵关闭。 当系统内的水受热膨胀使系统压力升高超过设计压力时,多余的水通过安全阀排至补水箱循环使用,当系统中的水由于泄露或温度下降而体积缩小,系统压力降低时,胶囊中的水被不断压入管网补充系统的压降损失,当系统压力降至设计允许的最低压力时,通过压力控制器使补水泵重新启动向管网及气压罐内补水,如此周而复始的工作,完成了高位膨胀水箱所起到的作用,同时不存在真空或缺水的现象,保证水的流量,压力永不失调。举例:罐体直径为1600mm,罐体个数为1,水泵吸入口径为50mm,水泵数量为2,水泵级数为3级的囊式落地膨胀水箱表示为NZPl.6 x 1-50 x 2 X 3。

This device uses the system static pressure as the designed initial pressure head P1 in expansion water tank and uses the pressure not causing vaporization of hot water in the system as the running terminal pressure water head P2 in the expansion water tank. In initial running, firstly start the make-up water pump to fill water into the system and water chamber in air pressure tank, and then the excess water will be forced into the rubber bag after the system is full of water. The volume of water chamber will keep expanding with the increasing of water volume due to the incompressibility of water, and then the air chamber will be compressed to make the pressure in tank increase continually. The make-up water pump will be closed through the pressure controller when reaching the design pressure. When the water in system expands by heat, which makes the system pressure increase and exceed the design pressure, the excess water will be discharged to make-up water tank through safety valve for recycling; when the volume of water in the system decreases due to water leakage or temperature drop, which makes the system pressure decrease, water in rubber bag will be pressed into pipe network to make up the loss of pressure drop of the system; when the system pressure is dropped to the minimum pressure allowed by the design, the make-up water pump will be re-started through the pressure controller to make up water into the pipe network and air pressure tank; such continuous cycle enables the high expansion water tank to realize its function without causing vacuum or water shortage phenomenon and guarantees the water discharge and never disorder pressure. For example, diameter of tank body 1600mm, quantity of tank 1, water pump suction caliber 50mm, and quantity of water pump 2, so the bag type floor expansion water tank with series 3 pump shall be expressed as NZPl.6 x 1-50 x 2 X 3.

 

  

  

  

使用说明

Instructions for Use

 

●设备使用环境通风良好,电压波动不应超过5%。

The environment for use of the device shall keep good ventilation condition, and the voltage fluctuation shall not exceed 5%.

 

●每年设备运行前,利用电控箱手动开关检查水泵电机、压力控制器的工作性能,然后在关闭给水阀门的情况下检查自动补水、泄水、排水以及压力保护功能,检查合格后方可打开补水阀门,与供热系统连成一体,进入正常运行状态。

Use the hand switch of electrical cabinet to check the working performance of water pump motor and pressure controller prior to running of device every year, then check the automatic water makeup, discharge, drainage and pressure protection function in the case of closing water supply valve, and then open the makeup water valve after the checking is qualified to connect with the heating system to form an unit and enter the normal running status.

 

●每年检查一次水泵,阀门及压力控制器,并定期检查系统的密闭性,防止漏水及锈蚀。

Check the water pump, valve and pressure controller once a year, and periodically check the tightness of the system to prevent water leakage and corrosion.

  

  

  

订货须知

Ordering Instructions

 

●订货时应说明设计给水的最高工作压力及最低压力。

Describe the designed maximum working pressure and minimum pressure of water supply in ordering.

 

●说明是生活用水、生产用水、消防用水或采暖用水。

Clarify it is for domestic water, water of production use, fire demand or heating demand.

 

●用户如有特殊要求,本公司可按用户要求供货(如特殊规格、材料的罐体、水泵等)

The company can supply at the customer’s special request (if any) (such as the tank body, water pump, etc of special specification and material)

 

●本公司对产品有更改的权利,产品今后如有变更恕不另行通知。

The company shall have the right to change the products, and the products shall be subject to change (if any) without further notice.

型号说明

Model Description

  

  

  

落地膨胀水箱 Floor Type Expansion Water Tank

 

单罐双泵装配图 Single Tank Double Pump Assembly Diagram

 

  

  

  

NZG系列自动给水装置技术性能表

Technical Performance Table of NZG Series Automatic Water Supply Device

	
 

型号

Model

	
进水口径

Inlet Diameter

DN2mm

	
出水口径

Outlet

Diameter

	
电机功率

Motor

Power

kW

	
水泵参数

Pump Parameters

	
总容量

 Total

Capacity

m3

	
调节容量

Regulating

Capacity

m3

	
流量

Flow Rate

m3/h

	
扬程

Lift

m(H2O)

	
NZG0.8×1-50×2×4

	
50

	
50

	
4

	
9-16

	
53-42

	
0.90

	
0.40

	
NZG0.8×2-65×2×3

	
65

	
50

	
7.5

	
18-35

	
55-43

	
1.80

	
0.80

	
NZG1.0×1-65×2×3

	
65

	
65

	
7.5

	
18-35

	
55-43

	
1.55

	
0.55

	
NZG1.0×2-65×2×4

	
65

	
65

	
11

	
18-35

	
74-58

	
3.10

	
1.10

	
NZG1.0×1-80×2×4

	
80

	
65

	
22

	
32-65

	
86-68

	
1.55

	
0.55

	
NZG1.0×2-80×2×3

	
80

	
65

	
15

	
32-65

	
64-51

	
3.10

	
1.10

	
NZG1.0×2-80×2×4

	
80

	
65

	
22

	
32-65

	
86-68

	
3.10

	
1.10

	
NZG1.2×1-65×2×3

	
65

	
80

	
7.5

	
18-35

	
53-43

	
2.65

	
0.80

	
NZG1.2×2-65×2×4

	
65

	
80

	
11

	
18-35

	
74-58

	
5.30

	
1.60

	
NZG1.2×1-80×2×3

	
80

	
80

	
15

	
32-65

	
64-51

	
2.65

	
0.80

	
NZG1.2×2-80×2×4

	
80

	
80

	
22

	
32-65

	
86-68

	
5.30

	
1.60

	
NZG1.2×2-100×2×4

	
100

	
80

	
37

	
72-126

	
86-68

	
5.30

	
1.60

	
NZG1.4×1-65×2×3

	
65

	
100

	
7.5

	
18-35

	
55-43

	
3.70

	
1.10

	
NZG1.4×2-65×2×4

	
65

	
100

	
11

	
18-35

	
74-58

	
7.40

	
2.20

	
NZG1.4×1-80×2×3

	
80

	
100

	
15

	
32-65

	
64-51

	
3.70

	
1.10

	
NZG1.4×2-80×2×3

	
80

	
100

	
15

	
32-65

	
64-51

	
7.40

	
2.20

	
NZG1.4×2-100×2×4

	
100

	
100

	
37

	
72-126

	
86-68

	
7.40

	
2.20

	
NZG1.6×2-100×2×5

	
100

	
100

	
45

	
72-126

	
109-85

	
7.40

	
2.20

	
NZG1.6×2-80×2×3

	
80

	
100

	
15

	
32-65

	
64-51

	
11.30

	
4.0

	
NZG1.6×1-100×2×4

	
100

	
100

	
37

	
72-126

	
86-65

	
11.30

	
2.0

	
NZG1.6×2-100×2×3

	
100

	
100

	
30

	
72-126

	
65-51

	
11.30

	
4.0

	
NZG1.6×1-100×2×5

	
100

	
100

	
45

	
72-126

	
109-85

	
11.30

	
2.0

	
NZG2.0×2-100×2×3

	
100

	
100

	
30

	
72-126

	
65-51

	
8.60

	
7.60

	
NZG2.0×1-100×2×3

	
100

	
100

	
30

	
72-126

	
65-51

	
9.30

	
3.80

 

  

  

  

 

NZP系列膨胀水箱技术性能表

Technical Performance Table of NZP Series Expansion Tank

	
 

型号

Model

	
进水口径

Inlet

Diameter

DN2mm

	
出水口径

Outlet

Diameter

	
电机功率

Motor

Power

kW

	
水泵参数

Pump Parameters

	
总容量

 Total

Capacity

m3

	
调节容量

Regulating

Capacity

m3

	
流量

Flow Rate

m3/h

	
扬程

Lift

m(H2O)

	
NZP0.8×1-50×2×3

	
50

	
40

	
3

	
9-16

	
39-31

	
0.5-0.8

	
0.14-0.47

	
NZP0.8×1-50×2×4

	
50

	
50

	
4

	
9-16

	
53-42

	
0.5-0.8

	
0.14-0.47

	
NZP0.8×1-50×2×5

	
50

	
50

	
5.5

	
9-16

	
66-53

	
0.5-0.8

	
0.14-0.47

	
NZP1.0×1-50×2×3

	
50

	
65

	
3

	
9-16

	
39-31

	
0.8-1.6

	
0.24-0.80

	
NZP1.0×1-50×2×4

	
50

	
65

	
4

	
9-16

	
53-42

	
0.8-1.6

	
0.24-0.80

	
NZP1.0×1-50×2×5

	
50

	
65

	
5.5

	
9-16

	
66-53

	
0.8-1.6

	
0.24-0.80

	
NZP1.2×1-50×2×3

	
50

	
80

	
3

	
9-16

	
39-31

	
1.6-2.0

	
0.41-1.36

	
NZP1.2×1-50×2×4

	
50

	
80

	
4

	
9-16

	
53-42

	
1.6-2.0

	
0.41-1.36

	
NZP1.2×1-50×2×5

	
50

	
80

	
5.5

	
9-16

	
66-53

	
1.6-2.0

	
0.41-1.36

	
NZP1.4×1-50×2×3

	
50

	
100

	
3

	
9-16

	
39-31

	
2.0-4.0

	
0.57-1.91

	
NZP1.4×1-50×2×4

	
50

	
100

	
4

	
9-16

	
53-42

	
2.0-4.0

	
0.57-1.91

	
NZP1.4×1-50×2×5

	
50

	
100

	
5.5

	
9-16

	
66-53

	
2.0-4.0

	
0.57-1.91

	
NZP1.4×2-50×2×3

	
50

	
100

	
3

	
9-16

	
39-31

	
5.0-8.0

	
1.14-3.82

	
NZP1.6×1-50×2×3

	
50

	
100

	
4

	
9-16

	
39-31

	
4.0-8.0

	
0.86-2.86

	
NZP1.6×1-50×2×4

	
50

	
100

	
5.5

	
9-16

	
53-42

	
4.0-8.0

	
0.86-2.86

	
NZP1.6×1-50×2×5

	
50

	
100

	
3

	
9-16

	
66-53

	
4.0-8.0

	
0.86-2.86

	
NZP1.6×2-50×2×3

	
50

	
100

	
4

	
9-16

	
39-31

	
8.0-16

	
1.72-5.72

	
NZP1.6×2-50×2×6

	
50

	
100

	
5.5

	
9-16

	
79-63

	
8.0-16

	
1.72-5.72

	
NZP2.0×1-50×2×3

	
50

	
100

	
3

	
9-16

	
39-31

	
8.0-10

	
1.40-3.26

	
NZP2.0×1-50×2×4

	
50

	
100

	
4

	
9-16

	
53-42

	
8.0-10

	
1.40-3.26

	
NZP2.0×1-50×2×5

	
50

	
100

	
5.5

	
9-16

	
66-53

	
8.0-10

	
1.40-3.26

	
NZP2.0×2-50×2×3

	
50

	
100

	
3

	
9-16

	
39-31

	
10-20

	
2.80-6.52

	
NZP2.0×2-50×2×6

	
50

	
100

	
4

	
9-16

	
79-63

	
10-20

	
2.80-6.52

 

  

  

  

 

NZP系列单罐双泵结构参数表

Parameter Table of NZP Series Single Tank Double Pump Structure

	
罐体直径

符号

Diameter

Symbol of

Tank Body

	
Ф800

mm

	
Ф1000

mm

	
Ф1200

mm

	
Ф1400

mm

	
Ф1600

mm

	
Ф2000

mm

	
A

	
1900

	
2050

	
2230

	
2430

	
2580

	
3100

	
A1

	
204

	
204

	
224

	
224

	
244

	
264

	
B

	
840

	
1000

	
1000

	
1200

	
1300

	
1600

	
B2

	
480

	
640

	
640

	
840

	
940

	
1240

	
H

	
2650

	
2870

	
3250

	
3350

	
3680

	
3770

	
H1

	
186

	
223

	
229

	
279

	
278

	
284

	
H2

	
100

	
120

	
140

	
140

	
160

	
160

以下为基础尺寸

Following is the foundation dimension

	
A2

	
150

	
1650

	
1830

	
2030

	
2180

	
2700

	
B1

	
800

	
960

	
960

	
1150

	
1250

	
1550

	
C

	
1040

	
1200

	
1200

	
1400

	
1500

	
1800

	
L

	
2000

	
2150

	
2330

	
2530

	
2680

	
3200

	
L1

	
250

	
H3

	
350

	
H4

	
300

立式膨胀水箱外型尺寸表

External Dimension Table of Vertical Expansion Tank

	
型号

Model

	
DN

mm

	
A

mm

	
B

mm

	
C

mm

	
D

mm

	
E

mm

	
F

mm

	
DN1

mm

	
容积

Capacity

m3

	
NZG600

	
600

	
1770

	
440

	
100

	
150

	
20

	
300

	
50

	
0.32

	
NZG800

	
800

	
2360

	
600

	
100

	
150

	
20

	
400

	
50

	
0.82

	
NZG1000

	
1000

	
2460

	
630

	
120

	
160

	
20

	
500

	
65

	
1.38

	
NZG1200

	
1200

	
2930

	
790

	
120

	
160

	
20

	
600

	
80

	
2.45

	
NZG1400

	
1400

	
3230

	
900

	
130

	
210

	
24

	
700

	
100

	
3.45

	
NZG1500

	
1500

	
3300

	
980

	
130

	
210

	
24

	
750

	
100

	
4.00

	
NZG1600

	
1600

	
3390

	
1050

	
130

	
210

	
24

	
800

	
100

	
5.10

	
NZG1800

	
1800

	
3560

	
1150

	
130

	
250

	
24

	
900

	
100

	
6.10

	
NZG2000

	
2000

	
3725

	
1310

	
130

	
250

	
24

	
1000

	
100

	
8.61

Source: [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}, [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}], [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}], [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}], [{"source": "alea-institute/alea-institute/kl3m-data-edgar-agreements/train-00195-of-00352.parquet"}]]