6/3 NM-B, Non-Metallic, Sheathed Cable, Residential Indoor Wire, Equivalent to Romex (100ft Cut)
Brand: Stock Wire
APPLICATIONS:
Non-metallic sheathed NM-B cable is used in normally dry installations in residential wiring, as branch circuits for outlets, lighting and other residential loads. Its applications are outlined in NEC 2008 and NEC 2011 Article 334. NM-B is rated at 600 volts and although it is rated at a conductor temperature of 90°C dry , its ampacity is limited to 60°C according to the NEC 2008 and NEC 2011. It may be fished through masonry or tile walls, where not exposed or subject to excessive moisture or dampness. NM-B cables are LEAD FREE and RoHS compliant. Equivalent to Romex NM-B.

STANDARDS:
Meets or exceeds all applicable ASTM specifications
UL Standard 83: Thermoplastic Insulated Wires and Cables
UL Standard 719: Non-Metallic Cables
Federal Specification A-A-59544 and requirements of the NEC
Voltage rating - 600 volts

CONSTRUCTION:
Insulation: Color coded polyvinyl chloride (PVC) compound with a nylon covering meeting the required thickness of Type THHN. Conductor insulation is rated 90 degrees Celsius
Ground: Soft, bare copper solid per ASTM B3 and stranded per ASTM B3 and B8
Sheath: 30 mil color coded PVC sheath rated 90C is applied over the completed assembly

SPECIFICATIONS:
Size: 6 AWG
Number of Conductors: 3
PVC Insulation Thickness: 0.76 mm / 0.029 inches
Ground Wire Size: 10 AWG
Nylon Thickness: 0.13 mm / 0.005 inches
Nominal Cable Dimensions: 16.0 mm / 0.62 inches
Weight per foot: 0.357 lbs
Allowable Ampacity: 55 Amps
#6 AWG Residential Wire for Outlets, Switches and Other Loads
Copper (Cu) Conductors
For Dry Locations up to 90 Degrees Celsius or 194 Degrees Farenheit. For Exposed and Concealed Applications
600-Volt Maximum with an Allowable Ampacity of 55 Amps
Equivalent to Romex NM-B - Color of Wire May not be the Same as the Picture Shown.