VORTEX Submersible Pump for Sewage Water VX 15/35-N 10M 1,5Hp 400V Pedrollo
Brand: Pedrollo
Model: VX 15/35-N 10MT
Liquid Type: Sewage Water
Power Supply: Three Phase 400V 50Hz
kW: 1,1
Hp: 1,5
Flow Rate Q L/min: 50 ÷ 500
Head H Metres: 13,5 ÷ 2
Outlet: 1½"
Power Cable: 10 Meter
Float Switch: without
Pump Body: Cast Iron
Impeller: VORTEX Stainless Steel AISI 304 type
Engine Features: Shaft with double seal and oil chamber
VX VORTEX Submersible pump for sewage water
INSTALLATION AND USE Suitable for use in domestic, civil and industrial applications where the water, such as groundwater, surface water and sewage water, contains suspended solids up t50 mm They are suitable for use in applications such as for draining flooded areas such as cellars, underground car parks, car washes, for emptying cesspools and for sewage disposal.
These pumps distinguish themselves for their reliability, which can be best appreciated under automatic operating conditions in fixed installations.
PERFORMANCES Head +15% as compared to previous versions Flow rate +30% as compared to previous versions TECHNICAL CHARACTERISTICS Cast iron pump body subjected to Epoxy Electrocoating Treatment. This treatment guarantees high resistance to oxidation. Stainless steel vortex type impeller. Stainless steel motor shaft. Precision cast stainless steel handle. Double mechanical seals. Float switch equipped with patented tilting system (patented). Supply cable equipped with anti-tear system (patented)
FEATURES Liquid type: sewage water Uses: domestic, civil, industrial APPLICATIONS: drainage, dirty water - slightly solid particles, emptying tanks. Typology: submersible Family: submersible pumps APPLICATION LIMIT: Temperature of the liquid to +40 °C 5 m maximum immersion depth with a sufficiently long power cable SOLIDS PASSAGE: up to Ø 40 mm for VX8-10-15/35 up to 50 mm for VX8-10-15/50 MINIMUM IMMERSION DEPTH FOR CONTINUOUS SERVICE: 290 mm for VX8-10-15/35 320 mm for VX8-10-15/50