Fees
15. (1) Except where a higher fee is prescribed by a municipality under subsection 81 (4) of the Act, the fees payable for the following matters are:  1.

For an application for a certificate of approval for the construction, installation, establishment, enlargement, extension or alteration of a Class 4, 5, 6 or 7 sewage system other than a Class A sewage system

$36.05


2.

For an application for a certificate of approval for the construction, installation, establishment, enlargement, extension or alteration of a Class A sewage system

87.55


3.

For the issuance of each licence under section 80 of the Act

Nil


4.

For the renewal of a licence issued under section 80 of the Act

Nil


5.

For a matter referred to in subsection 82 (2) of the Act

Nil (2) Every parcel of land with respect to which there is an application referred to in clause 82 (2) (a) or (c) of the Act and no application referred to in clause 82 (2) (b) or (d) of the Act, and the subject matter of the application, (a) by the determination of the person to whom the application is made will not affect any sewage system or potential sewage system or require a new sewage system; and (b) is not forwarded to a Director under Part VIII of the Act for review, is exempt from the payment of the fee for the purposes of section 82. R.R.O. 1990, Reg. 358, s. 15. TABLE 1   CLEARANCES FOR CLASS 1, 2 AND 3 SEWAGE SYSTEMS (SUBSECTION 5 (3))  Column 1

Column 2

Column 3

Column 4

Column 5


 

Minimum distance in metres from well with watertight casing to a depth of 6 metres

Minimum distance in metres from spring used as a source of potable water or well other than a well with watertight casing to a depth of 6 metres

Minimum distance in metres from lake, river, pond, stream, reservoir or a spring not used as a source of potable water

Minimum distance in metres from a Property Line


Pit Privy

15

30

15

3


Privy Vault

10

15

10

3


Pail Privy

 

 

 

 


Cesspool

30

60

15

3


Leaching pit

10

15

15

3 R.R.O. 1990, Reg. 358, Table 1. TABLE 2   SEPTIC TANK MINIMUM SIZE REQUIREMENTS FOR RESIDENCES (SUBPARAGRAPH I OF PARAGRAPH 2 OF SUBSECTION 10 (1))  Column 1

Column 2


Number of Bedrooms

Working Capacity In Litres


Two bedrooms or less

2,700


Three bedrooms

3,600


Four or five bedrooms

4,500 R.R.O. 1990, Reg. 358, Table 2. TABLE 3   CLEARANCES FOR CLASS 4, 6 AND 10 SEWAGE SYSTEMS (PARAGRAPH 9 OF SUBSECTION 10 (1), PARAGRAPH 1 OF SUBSECTION 12 (1) AND PARAGRAPH 4 OF SUBSECTION 13.1 (3))  Column 1

Column 2


 

Distance in Metres


Building or structure

1.5


Lake

15


Pond

15


Property Line

3


Reservoir

15


River

15


Spring

15


Stream

15


Well

15 R.R.O. 1990, Reg. 358, Table 3; O. Reg. 370/97, s. 4. TABLE 4   PIPE CLEARANCES FOR CLASS 4 AND 10 SEWAGE SYSTEMS (SUBPARAGRAPH III OF PARAGRAPH 1 OF SUBSECTION 10 (2), SUBPARAGRAPH IX OF PARAGRAPH 5 OF SUBSECTION 10 (3) AND SUBPARAGRAPH II OF PARAGRAPH 14 OF SUBSECTION 13.1 (3))  Column 1

Column 2


 

 

Distance in Metres


1.

Well, other than a well referred to in item 2, or a spring used as a source of potable water

30


2.

Well with watertight casing to a depth of 6 metres

15


3.

Building or structure

5


4.

Property line

3


5.

A spring not used as a source of potable water or a lake, river, pond, stream or reservoir

15 R.R.O. 1990, Reg. 358, Table 4; O. Reg. 370/97, s. 5. TABLE 5   LENGTH OF DISTRIBUTION PIPE IN METRES FOR VARIOUS DESIGN SOIL PERCOLATION TIMES(T) FOR PRIVATE DWELLINGS (PARAGRAPH 1 OF SUBSECTION 10 (3) AND SUBPARAGRAPH I OF PARAGRAPH 1 OF SUBSECTION 12 (2))  Column 1

Column 2

Column 3

Column 4

Column 5

Column 6

Column 7


Number of Bedrooms

T from 1 to 5 min inclusive

T greater than 5 min but not greater than 10 min

T greater than 10 min but not greater than 15 min

T greater than 15 min but not greater than 20 min

T greater than 20 min but not greater than 25 min

T greater than 25 min


2 or less

40

40

70

100

130

5.5T


3

40

60

100

140

180

8T


4

40

80

130

180

230

10T


for each bedroom over 4, add

5

12

20

27

35

1.5T R.R.O. 1990, Reg. 358, Table 5. TABLE 6   MINIMUM AREA OF THE SURFACE OF THE FILTER MEDIUM IN FILTER TYPE LEACHING BEDS FOR PRIVATE DWELLINGS (CLAUSE 10 (4) (D) AND SUBPARAGRAPH III OF PARAGRAPH 3 OF SUBSECTION 12 (2))  Column 1

Column 2


Number of Bedrooms

Minimum Surface Area of the Filter Medium – Square Metres


 

Class 4 Sewage Systems

Class 6 Sewage Systems


2 or less

15

10


3

22

11


4

28

14


For each bedroom over 4 add

4

2 R.R.O. 1990, Reg. 358, Table 6. TABLE 7   CLASSES OF LICENCE (SUBSECTION 14 (1))  Column 1

Column 2


Type of Business

Class of Licence


Construction on site, installing, repairing, servicing, cleaning or emptying sewage systems

1


Storing, hauling or disposing of sewage from a sewage system

2 R.R.O. 1990, Reg. 358, Table 7.