38. (1) No later than 45 days after the end of each quarter, each discharger shall submit a report to the Director containing information relating to the discharger’s plant throughout the quarter as required by subsections (3) to (13). (2) A report under this section shall be submitted both in an electronic format acceptable to the Director and in hard copy generated from the electronic format acceptable to the Director and signed by the discharger. (3) A report under this section shall include all information included in a report given under section 37 during the quarter. (4) Each discharger shall report, for each month in the quarter, the monthly average plant loadings and the highest and lowest daily plant loadings calculated under sections 12 and 13 for each limited parameter and each Schedule 2 assessment parameter. (5) Each discharger shall report, for each day in the quarter, each daily overflow effluent stream loading calculated under section 14 for each Schedule 3 assessment parameter. (6) Each discharger shall report, for each month in the quarter, the monthly average concentrations calculated under section 15 and the highest and lowest analytical results obtained under sections 22 and 23 for each limited parameter in each process effluent monitoring stream at the discharger’s plant. (7) Each discharger shall report, for each month in the quarter, the monthly average concentrations calculated under section 16 and the highest and lowest analytical results obtained under section 29 for each Schedule 2 assessment parameter in each cooling water effluent monitoring stream at the discharger’s plant. (8) Each discharger shall report, for each day in the quarter, the daily concentrations calculated under section 17 and the highest and lowest analytical results obtained under section 30 for each Schedule 3 assessment parameter in each overflow effluent monitoring stream at the discharger’s plant. (9) Each discharger shall report, for each month in the quarter, the monthly average process effluent plant volume and the highest and lowest daily process effluent plant volumes calculated under section 32. (10) Each discharger shall report, for each month in the quarter, the monthly average cooling water effluent plant volume and the highest and lowest daily cooling water effluent plant volumes calculated under section 32. (11) Each discharger shall report, for each day in the quarter, the daily overflow effluent stream volumes calculated under section 31. (12) Each discharger shall report the number of days in each month in the quarter on which process effluent or overflow effluent was discharged from the discharger’s plant. (13) Each discharger shall report, for each month in the quarter, the highest and lowest pH results obtained under section 25 for each process effluent monitoring stream at the discharger’s plant.  O. Reg. 560/94, s. 38. Reports to the Director on Chronic Toxicity Testing

39. (1) Each discharger shall report to the Director the results of all monitoring performed under section 28, together with the date on which each sample was picked up, no later than 60 days after the end of each semi-annual period in which the monitoring was performed. (2) A report under subsection (1) shall include a plot of percentage reduction in growth or reproduction against the logarithm of test concentration and shall include a calculation of the concentration at which a 25 per cent reduction in growth or reproduction would occur.  O. Reg. 560/94, s. 39. PART IX   COMPLIANCE Compliance — Existing and New Plants

40. (1) A discharger for an existing plant with respect to which this Regulation applies need not comply with, (a) Part IV before August 26, 1997; and (b) Parts V and VI before November 24, 1994.  O. Reg. 560/94, s. 40. (2) A discharger for a new plant with respect to which this Regulation applies need not comply with section 19 before August 26, 1997.  O. Reg. 169/96, s. 6 (2).

41. Omitted (revokes other Regulations).  O. Reg. 560/94, s. 41. Schedule 1   Process Effluent Limits and Monitoring Frequency (All existing and new plants)  Item   Column 0.1 Analytical test group   Column 1 Parameter   Column 2 Monitoring frequency   Column 3 Daily concentration limit (mg/L)   Column 4 Monthly average concentration limit 

  1.   2   Total Cyanide   Thrice weekly   2   1 

  2.   8   Total Suspended Solids (TSS)   Thrice weekly   30   15 

  3.   9   Copper   Weekly   0.6   0.3 

  4.   9   Lead   Weekly   0.4   0.2 

  5.   9   Nickel   Weekly   1   0.5 

  6.   9   Zinc   Weekly   1   0.5 

  7.   10   Arsenic   Weekly   1   0.5 O. Reg. 306/17, s. 1. SCHEDULE 2   Cooling Water Effluent Assessment Monitoring (All existing and new Plants) Item   Column 0.1 Analytical test group   Column 1 Parameter   Column 2 Monitoring frequency 

  1.   8   Total Suspended Solids (TSS)   Weekly O. Reg. 306/17, s. 1. Schedule 3   Overflow Effluent Assessment Monitoring (All Existing and New Plants) Item   Column 0.1 Analytical test group   Column 1 Parameter   Column 2 Monitoring frequency 

  1.   2   Total Cyanide   Every eight-hour period 

  2.   8   Total Suspended Solids (TSS)   Every eight-hour period 

  3.   9   Copper   Every eight-hour period 

  4.   9   Lead   Every eight-hour period 

  5.   9   Nickel   Every eight-hour period 

  6.   9   Zinc   Every eight-hour period 

  7.   10.   Arsenic   Every eight-hour period O. Reg. 306/17, s. 1.