Service Stations
 7. Each person responsible for a service station shall ensure that the following rules are complied with in respect of the service station: 1. The service station must be equipped with an operable vapour control system applicable to transfers of gasoline for receipt at the service station. 2. In each calendar year, the vapour control system must operate properly during more than 95 per cent of the time during which gasoline is transferred for receipt at the service station. 3. For the purposes of rule 2, gasoline transfers from cargo tank trucks to which section 8 does not apply are not to be taken into account. 4. A record must be made of the date and duration of any transfer of gasoline for receipt at the service station during, i. a shutdown of the vapour control system that lasts for more than 24 hours, or ii. a malfunction of the vapour control system that permits abnormal discharge of gasoline vapour and lasts for more than 24 hours. 5. Records made under rule 4 must be kept at the service station or at a business office of the owner of the service station for at least two years. 6. The vapour control system must be a vapour balancing system. 7. The vapour recovery adapters at each storage tank at the service station must be accessible to the operator of any cargo tank truck that delivers gasoline to the tank. 8. No person may carry out any work on the vapour control system or be involved in the transfer of gasoline for receipt at the service station unless he or she has received appropriate training in the operation and maintenance of the vapour control system. 9. Records of training given to a person under rule 8 must be made and kept at the service station or at a business office of the owner of the service station for at least two years after the person ceases to carry out the work in respect of which the training was given. 10. Written operating procedures must be prepared sufficient to enable persons working at the service station to operate and maintain the vapour control system in compliance with all requirements of this Regulation, the CCME Code and the CGSB Standard. 11. The address at which records required by this section are kept must be included in the operating procedures. 12. The operating procedures must be available to each person who carries out work on the vapour control system or who is involved in the transfer of gasoline for receipt at the service station. 13. The operating procedures must be followed. 14. Equipment tests and inspections must be carried out as specified in the CGSB
Standard and as specified in the CCME Code. 15. Records of the results of all tests and inspections carried out under rule 14, other than the results of visual inspections, must be made and kept at the service station or at a business office of the owner of the service station for at least two years. 16. Records of abnormalities observed during visual inspections carried out under rule 14 must be made and kept at the service station or at a business office of the owner of the service station for at least two years. 17. Condensed material found in the vapour control system must be collected and removed from the system. 18. All transfers of gasoline from cargo tank trucks to which section 8 applies must be carried out in accordance with the cargo tank truck unloading procedures specified in the CGSB Standard.  O. Reg. 455/94, s. 7. Cargo Tank Trucks