10.3.2.2. Reduction in Performance Level (1) Except as provided in Sentence (2), the performance level of a building or part of a building is reduced where the existing structural floor and roof framing systems and their supporting members are not adequate to support the proposed dead loads and live loads of the new major occupancy that the building is to support. (2) The inadequacy of the existing structural floor or roof framing system and its supporting members to support the proposed dead loads and live loads does not reduce the performance level of the building if the portion of the floor affected by the proposed loads is restricted to the loading it will support and signs stating the restrictions are posted. (3) Except as provided in Section 10.4., the performance level of a building or part of a building is reduced where the early warning and evacuation systems requirements of the building do not meet the early warning and evacuation systems requirements set out in Table 10.3.2.2.A. for the new major occupancy that the building is to support. Table 10.3.2.2.A. For Evaluation of Early Warning/Evacuation Forming Part of Sentence 10.3.2.2.(3)  EW/EVAC Evaluation

Compliance Alternative(1)


Early Warning and Evacuation to be checked against

EARLY WARNING (a) Compliance alternatives as listed may be used.
EVACUATION
(b) Compliance alternatives as listed to access to exit and exit widths, number of exits, door release hardware, and travel distance may be used.


(a) access to exit widths based on occupant load in Subsection 3.3.1. or 9.9.3.;


(b) exit widths based on occupant load in Subsection 3.4.3. or 9.9.3.;


(c) exit signs in Subsection 3.4.5. or 9.9.10.;


(d) lighting of exits, lighting of access to exits and emergency lighting in 


Subsection 3.2.7. or 9.9.11.;


(e) fire alarm system in Subsection 3.2.4. or 9.10.17.;


(f) smoke alarms in 9.10.18.;


(g) travel distance and number of exits in other Parts of the Code;


(h) smoke control measures, and at least one elevator to permit transport of firefighters to all floors in hotels whose floor level is more than 18 m high, measured between grade and floor level of the top storey as per Subsection 3.2.6., and


(i) door release hardware requirements in Articles 3.3.1.12. and 3.4.6.15., and


deficiencies shall be upgraded.


Column 1

2 Note to Table 10.3.2.2.A.: (1)See Tables 11.5.1.1.A., 11.5.1.1.B., 11.5.1.1.C., 11.5.1.1.D/E and 11.5.1.1.F. for compliance alternatives that may be used. (4) Except as provided in Sentence (5), the performance level of an existing building is reduced where a change in use will result in a change of the major occupancy of all or part of an existing building to another major occupancy of a greater hazard index. (5) Except as provided in Sentence (6), if the hazard index of the new major occupancy is greater than the hazard index of the existing major occupancy, the performance level is not reduced where the hazard index of the new major occupancy is not greater than the construction index of the existing building. (6) Small or medium sized existing buildings as determined in Tables 11.2.1.1.B. to N. facing multiple streets may be assigned a hazard index credit of 1, which may be subtracted from the hazard index of the new major occupancy provided (a) the building does not contain a Group B, Division 1, a Group C, or a Group F, Division 1 occupancy, and (b) fire fighting access complying with Articles 3.2.5.1., 3.2.5.2., 3.2.5.3., 3.2.5.4. and 3.2.5.5. or Subsection 9.10.9., or an approved alternative measure is provided from all streets. (7) Except as provided in Sentence (8), the performance level of a building or part of a building is reduced in an existing building constructed of combustible construction where (a) the occupancy is changed to a residential occupancy in all or part of the building, and (b) if the building was new, it would have been required to be constructed of noncombustible construction. (8) A change in the occupancy of a building or part of a building to a residential occupancy does not reduce the performance level of the building or part of the building where (a) the building is sprinklered, and (b) the building does not exceed 6 storeys in building height. (9) The performance level of a building or part of a building is reduced where the new major occupancy in an existing building of multiple occupancy is not separated from adjoining major occupancies by fire separations having fire-resistance ratings conforming to Article 3.1.3.1., Subsection 9.10.9. or Table 10.3.2.2.B. Table 10.3.2.2.B.(1) Additional Upgrading for Multiple Major Occupancies Forming Part of Sentence 10.3.2.2.(9)  New Major Occupancy

Code Requirements

Compliance Alternative


All(2)

Table 3.1.3.1. and Subsection 9.10.9.

For Existing
Buildings

If Sprinklered


Where:

Reduce to

Reduce to


1 h rating required

45 min

30 min


2 h rating required

1.5 h

1 h


3 h rating required

2 h

1.5 h


Column 1

2

3 Notes to Table 10.3.2.2.B.: (1)For buildings with multiple major occupancies only, where there is a change in major occupancy. (2)See Sentence 10.3.2.2.(9). (10) The performance level of a building is reduced where the building after the change of major occupancy will not comply with Articles 3.1.3.1. or 9.10.9.12. (11) The performance level of a building or part of a building is reduced where, after a change of major occupancy (a) the total daily design sanitary sewage flow of the new major occupancy, calculated in accordance with Article 8.2.1.3., exceeds the capacity of any component of a sewage system serving the building, or (b) the type or amount of sanitary sewage which will, under the new major occupancy, be discharged to a sewage system serving the building is prohibited by Article 8.1.3.1. Section 10.4. Compliance Alternatives And Alternative Measures 10.4.1.Compliance Alternatives