jswizzle3737/ontario_laws_and_regs huggingface dataset:
5.14.9.1. This Subsection applies to bowling alleys. Notification
5.14.9.2. The Chief Fire Official shall be notified when bowling alleys are to be resurfaced. Floor finishing
5.14.9.3. Floor finishing operations shall be carried out in accordance with Subsection 5.14.8. Pin refinishing
5.14.9.4. (1) Pin refinishing shall be carried out (a)  in a building
provided for that purpose, or (b)  in a room at or above grade separated from the building
it is located in by a fire separation having a fire-resistance rating not less than 1 h. Smoking prohibited
5.14.9.5. (1) Smoking shall not take place in a room where pin refinishing occurs. (2) Signs prohibiting smoking that meet the requirements of Article 2.4.3.2. shall be conspicuously posted in any place where pin refinishing occurs. Flammable and combustible liquids
5.14.9.6. The storage, handling and use of flammable liquids
and combustible liquids shall meet the requirements of Part 4.
5.14.9.7. (1) During the pin refinishing process, a receptacle that complies with Sentence 2.4.1.3.(3) shall be provided for waste rags and materials used in operations involving flammable finishes or solvents. (2) The contents of each receptacle referred to in Sentence (1) shall be removed daily and disposed of in an approved manner. Subsection 5.14.10. Drycleaning and Dyeing Plants Application
5.14.10.1. (1) Drycleaning plants shall comply with NFPA 32, “Standard for Drycleaning Plants”. (2) Despite Sentence (1) and subject to Article 5.14.10.2., flammable liquids shall not be used for any purpose in drycleaning and dyeing plants. Use and storage of flammable liquids
5.14.10.2. (1) Flammable liquids may be used as a local application to remove spots and stains if the liquids (a)  are stored in containers that have a capacity of not more than 1 L, (b)  do not exceed more than 25 L in aggregate quantity, and (c)  are dispensed from plastic containers that have a capacity of not more than 0.5 L. (2) Despite Sentence (1), existing drycleaning plants and dyeing plants may be approved
if the Chief Fire Official is satisfied that the level of fire safety specified in Sentence (1) is provided. Subsection 5.14.11. Hazardous Extraction Operations Application
5.14.11.1. This subsection applies to hazardous extraction operations. Prohibited locations
5.14.11.2. A hazardous extraction operation shall not be performed (a)  in a basement, or (b)  in a building
containing a residential occupancy. SECTION 5.15 RADIOACTIVE Nuclear substances Subsection 5.15.1. Application Application
5.15.1.1. This Section applies to the storage and handling of any radioactive nuclear substance that is present in a quantity that exceeds the exemption quantity as defined in Section 1 of the Nuclear Substances and Radiation Devices Regulations made under the Nuclear Safety and Control Act (Canada). Subsection 5.15.2. Storage
5.15.2.1. Radioactive nuclear substances and equipment shall be returned to storage after use. Storage
5.15.2.2. Radioactive nuclear substances shall be stored in accordance with the licence requirements and regulations of the Canadian Nuclear Safety Commission. Prohibited combination
5.15.2.3. Radioactive nuclear substances and equipment shall not be stored with flammable or corrosive materials. Subsection 5.15.3. Emergency Procedures Fire emergency procedures
5.15.3.1. (1) Persons using or storing radioactive nuclear substances shall establish fire emergency procedures in consultation with the fire department, including (a)  the location and identification of storage and use areas, (b)  methods to control a fire emergency and to recover radioactive nuclear substances and equipment containing radioactive nuclear substances safely and efficiently, (c)  the names, addresses and telephone numbers of primary and alternative sources of expert radiation safety advice and assistance, and (d)  the location of primary and alternative sources of radiation survey instruments. SECTION 5.16 FUMIGATION AND THERMAL INSECTICIDAL FOGGING Subsection 5.16.1. Application Application
5.16.1.1. (1) This Section applies to the fumigation or thermal fogging of buildings
where this activity creates a fire or explosion hazard, including the fumigation of equipment or commodities within structures, tanks or bins or under tarpaulins. (2) Articles 5.16.2.1. and 5.16.2.2. do not apply to industries that conduct frequent fumigation operations on a routine basis where approved prior to the conducting of the operations. Subsection 5.16.2. Safety Precautions Notification of fire department
5.16.2.1. (1) Except as permitted in Sentence 5.16.1.1.(2), the fire department
shall (a)  be notified in writing at least 24 h before any building is to be closed for fumigation, and (b)  be advised of the chemicals to be used, the proposed date and time of use, the types of respiratory protective devices required and the degree of flammability of the fumigant or fog being used. Notification of adjacent premises
5.16.2.2. Except as permitted in Sentence 5.16.1.1.(2), prior notice shall be given to the occupants of any premises adjacent to that in which fumigation or thermal insecticidal fogging is to take place. Ignition sources
5.16.2.3. Flames and other sources of ignition shall be eliminated in a building
undergoing fumigation or thermal insecticidal fogging. Power supply
5.16.2.4. Electric power supply shall be shut off to the premises undergoing fumigation or thermal insecticidal fogging. Air temperature
5.16.2.5. The air temperature in a building undergoing fumigation or thermal insecticidal fogging shall be kept sufficiently low to prevent the actuation of any sprinkler system. Breathing apparatus
5.16.2.6. Protective breathing apparatus shall be made available at the premises undergoing fumigation or thermal insecticidal fogging for all persons in case of emergency. Restricted entrance
5.16.2.7. (1) No unauthorized person shall be permitted to enter a premises undergoing fumigation or thermal insecticidal fogging until the premises has been ventilated and is safe. (2) Warning signs shall be posted in a conspicuous location near every entrance to the premises being fumigated. (3) One person shall be on duty at each entrance to the premises undergoing fumigation or thermal insecticidal fogging to prevent any unauthorized person from entering until such premises have been ventilated. SECTION 5.17 HOT WORKS Subsection 5.17.1. Application Application
5.17.1.1. This Section applies to hot works that use open flames or produce heat or sparks, including cutting, welding, soldering, brazing, grinding, adhesive bonding, thermal spraying and thawing pipes. Same
5.17.1.2. The installation, operation and maintenance of hot work equipment shall comply with CAN/CSA-W117.2, “Safety in Welding, Cutting and Allied Processes” and meet the requirements of this Section. Subsection 5.17.2. Use and Maintenance of Equipment Fuel gases
5.17.2.1. The operation of acetylene generating systems and the storage and generation of hot work fuel gases shall comply with NFPA 51, “Standard for Design and Installation of Oxygen-Fuel Gas Systems for Welding, Cutting and Allied Processes”. Piping
5.17.2.2. Acetylene gas shall not be piped through copper or high copper content alloy, tubing, piping or fittings. Cylinder storage
5.17.2.3. Cylinders stored inside buildings shall conform to the requirements in Section 5.6. Cylinder caps and valves
5.17.2.4. Gas fuel cylinders, whether full or empty, whose valves are not in a recessed or protected location shall have their caps in place and their valves tightly closed when not in actual use. Damaged equipment
5.17.2.5. Torches, regulators, hoses and other oxyacetylene hot work equipment which have been damaged shall not be used. Equipment inspection
5.17.2.6. (1) Hot work equipment shall be inspected daily or prior to use for defects by personnel in charge of the equipment. (2) Hot work equipment shall be tested monthly for leaks with a leak test solution. (3) Leaks or defects found in hot work equipment shall be repaired prior to use. Equipment not in use
5.17.2.7. Valves shall be closed and lines bled when equipment is not in actual use. Lubrication
5.17.2.8. Oil or grease shall not be used for lubrication of hot work equipment. Subsection 5.17.3. Prevention of Fires Location of operations
5.17.3.1. (1) Hot work operations in buildings shall be carried out in areas that  (a)  are free of combustible and flammable contents, and (b)  have walls, ceilings and floors of noncombustible construction or that are lined with noncombustible materials. (2) When it is not practical to undertake hot work operations in areas described in Sentence (1), combustible and flammable materials shall either be kept at least 11 m from the work area or otherwise protected against ignition by sheet metal, asbestos blankets or other noncombustible material. (3) Any process or activity that produces flammable gases or vapours, combustible dusts or combustible fibres in quantities sufficient to create a fire or explosion hazard shall be interrupted and the hazardous conditions shall be removed before any hot work is carried out. Work adjacent to piping
5.17.3.2. When hot work is to be carried out near piping containing flammable gas, the section of the piping located within 1 m of the torch shall be covered with wet noncombustible insulating material 6 mm thick. Work on containers
5.17.3.3. (1) Hot work shall not be performed on containers, equipment, or piping containing flammable liquids, combustible liquids
or flammable gases unless (a)  they have been cleaned and tested with a listed gas detector, such as one conforming to CSA C22.2 No. 152, “Combustible Gas Detection Instruments”, to ascertain that they are free of explosive vapours, or (b)  safety measures are taken in conformance with good engineering practice. (2) Hot work operations shall not be undertaken on a totally enclosed container. (3) At least one portable extinguisher conforming to Section 6.2 shall be provided in the hot work area. SECTION 5.18 INDUSTRIAL OVENS FOR BAKING AND DRYING PROCESSES Subsection 5.18.1. Application Application
5.18.1.1. This Section applies to industrial baking and drying ovens which during operation contain flammable vapours given off by the products being baked or dried. Subsection 5.18.2. Location Prohibited location
5.18.2.1. Ovens shall not be located in any storey below grade. Subsection 5.18.3. Construction Oven materials
5.18.3.1. Industrial ovens shall be constructed of noncombustible materials with smooth interior surfaces to permit cleaning. Limiting temperature on combustible construction
5.18.3.2. The roof and floor of ovens and heaters and associated ductwork shall have sufficient clearance or be insulated where necessary to prevent the temperature from exceeding 90°C at any combustible part of the building assembly. Explosion vents
5.18.3.3. (1) Explosion vents shall be provided for ovens where fuel or vapour hazards are present. (2) Explosion vents shall be designed in accordance with NFPA 68, “Standard on Explosion Protection by Deflagration Venting”. (3) Existing explosion vents that provide a vent ratio of 0.2 m2 of vent area for each cubic metre of oven volume are deemed to satisfy the vent ratio for the purposes of NFPA 68 in Sentence (1). (4) Openings or access doors equipped with explosion release hardware shall be acceptable as explosion vents. Duct and stack restrictions
5.18.3.4. (1) Ducts, stacks and associated insulation in systems for the removal of flammable vapours shall (a)  be constructed of noncombustible materials, (b)  not pass through firewalls, and (c)  discharge outdoors not less than (i)  1.5 m from unprotected building openings, and (ii)  6 m from air intake openings. Subsection 5.18.4. Ventilation Oven ventilation
5.18.4.1. Ovens in which flammable vapours may be present or through which products of combustion are circulated shall be ventilated in accordance with NFPA 86, “Standard for Ovens and Furnaces”. Fan interlocks
5.18.4.2. (1) In ovens where flammable vapours may be present, interlocks shall be provided to ensure that energy sources and ignition devices are de-activated when (a)  the ventilating fans stop, or (b)  the excess temperature controls are activated. Continuous-process oven interlocks
5.18.4.3. (1) In continuous-process ovens where flammable vapours may be present, interlocks shall be provided to ensure (a)  that ventilating fans are operating before conveyors can be started, and (b)  that the conveyors are stopped when (i)  the ventilating fans stop, or (ii)  the excess temperature controls are activated. Subsection 5.18.5. Maintenance Cleaning of ovens and ductwork
5.18.5.1. (1) Ovens and associated ductwork shall be inspected, cleaned and maintained internally and externally at intervals sufficient to prevent the accumulation of combustible deposits. (2) Access doors or panels shall be provided to permit inspection, cleaning and maintenance of ovens and associated ductwork. (3) Fixed noncombustible ladders, steps or grab rails shall be provided to permit access to the doors or panels required in Sentence (2). Subsection 5.18.6. Fire Protection Portable extinguishers
5.18.6.1. Portable extinguishers shall be provided in conformance with Section 6.2. Standpipe and hose systems
5.18.6.2. A standpipe and hose system shall be installed in conformance with the Building Code and equipped with spray nozzles so that all parts of an oven structure can be reached by a hose stream. Fire access doors
5.18.6.3. Doors or other means of access shall be provided in ovens and associated ductwork so that portable extinguishers or hose streams may be used in all parts of the equipment. Automatic fire protection
5.18.6.4. Ovens containing or processing sufficient combustible materials to sustain a fire shall be protected by an automatic sprinkler system or other fixed extinguishing systems. O. Reg. 213/07, Division B, Part 5; O. Reg. 256/14, ss. 196-255; O. Reg. 33/19, ss. 18-20. PART 6   FIRE PROTECTION EQUIPMENT TABLE OF CONTENTS SECTION 6.1    GENERAL 

  Subsection 6.1.1.   Application 

        

  SECTION 6.2    PORTABLE EXTINGUISHERS 

  Subsection 6.2.1.   General 

  Subsection 6.2.2.   Classification 

  Subsection 6.2.3.   Selection Requirements 

  Subsection 6.2.4.   Installation Requirements 

  Subsection 6.2.5.   Grading of Hazards 

  Subsection 6.2.6.   Distribution 

  Subsection 6.2.7.   Inspection, Testing and Maintenance 

        

  SECTION 6.3    ALARM AND VOICE COMMUNICATION SYSTEMS FOR LIFE SAFETY 

  Subsection 6.3.1.   General 

  Subsection 6.3.2.   Check, Inspect and Test 

  Subsection 6.3.3.   Smoke Alarms — Maintenance and Testing 

  Subsection 6.3.4.   Carbon Monoxide Alarms — Maintenance and Testing 

        

  SECTION 6.4    STANDPIPE AND HOSE SYSTEMS 

  Subsection 6.4.1.   General 

  Subsection 6.4.2.   Maintenance and Inspection of Hose Stations and Equipment 

  Subsection 6.4.3.   Checking, Inspection and Testing 

        

  SECTION 6.5   SPRINKLER SYSTEMS 

  Subsection 6.5.1.   General 

  Subsection 6.5.2.   Sprinkler System Shutdowns 

  Subsection 6.5.3.   Checking 

  Subsection 6.5.4.   Inspection 

  Subsection 6.5.5.   Testing 

  Subsection 6.5.6.   Maintenance 

        

  SECTION 6.6    WATER SUPPLIES FOR FIRE PROTECTION 

  Subsection 6.6.1.   General 

  Subsection 6.6.2.   Tanks 

  Subsection 6.6.3.   Fire Pumps and Reservoirs 

  Subsection 6.6.4.   Hydrants 

  Subsection 6.6.5.   Inspection of Hydrants 

  Subsection 6.6.6.   Uniform Marking of Hydrants 

        

  SECTION 6.7    EMERGENCY POWER SYSTEMS 

  Subsection 6.7.1.   General 

        

  SECTION 6.8    SPECIAL FIRE SUPPRESSION SYSTEMS 

  Subsection 6.8.1.   Installation 

  Subsection 6.8.2.   Inspection and Maintenance 

        

  SECTION 6.9   DECOMMISSIONING 

  Subsection 6.9.1.   General SECTION 6.1 GENERAL Subsection 6.1.1. Application Application
6.1.1.1. This Part applies to installation, checking, inspection,
testing, maintenance and operation of fire protection equipment and life safety systems. Exception
6.1.1.2. Section 6.2 does not apply to dwelling units. SECTION 6.2 PORTABLE EXTINGUISHERS Subsection 6.2.1. General
6.2.1.1. Listed
portable extinguishers shall be installed when replacing or adding new extinguishers. Maintenance
6.2.1.2. Portable extinguishers shall be kept operable and fully charged. Location
6.2.1.3. (1) Portable extinguishers shall be located so that they are easily seen and shall be accessible at all times, except as permitted in Sentences (2) and (3). (2) A lockable, break-front glazed cabinet may be used for security purposes to store portable extinguishers and where portable extinguishers are located in a fire hose cabinet, an approved lockable, scored glass break-front cabinet may be used. (3) In a detention occupancy, portable extinguishers are permitted to be located in secure areas, or in lockable cabinets provided (a)  identical keys for all cabinets are located at all supervisory or security stations, or (b)  electrical remote release devices that are designed to open upon power failure are provided for the cabinets.
6.2.1.4. Portable extinguishers shall be located in or adjacent to corridors or aisles that provide access to exits. Signs
6.2.1.5. The location of portable extinguishers shall be prominently indicated by signs or markings in large
floor areas and in locations where visual obstructions cannot be avoided. Proximity to fire hazards
6.2.1.6. Portable extinguishers in proximity to a fire hazard shall be located so as to be accessible without exposing the operator to undue risk. Corrosive atmosphere
6.2.1.7. Portable extinguishers that are subject to corrosion shall not be installed in a corrosive environment unless they are provided with appropriate corrosion protection. Temperature range requirements
6.2.1.8. (1) Where a portable extinguisher is to be located in an area subject to temperatures outside the range 4°C to 49°C, it shall be (a)  placed in an enclosure where the temperature is maintained within this range, or (b)  of a type labelled for the temperatures to which it will be exposed. Mounting brackets
6.2.1.9. When portable extinguishers are located on vehicles or in areas where they are subject to jarring or vibration, brackets designed to accommodate these effects shall be used. Subsection 6.2.2. Classification Rating of portable extinguishers
6.2.2.1. Portable extinguishers shall be rated and identified in conformance with CAN/ULC-S508, “Standard for the Rating and Fire Testing of Fire Extinguishers”. Subsection 6.2.3. Selection Requirements Multiple ratings
6.2.3.1. Where portable extinguishers have been tested and are rated as being acceptable for fighting more than one class of fire, each class of fire for which they are acceptable shall be designated on each extinguisher. Subsection 6.2.4. Installation Requirements Where portable extinguishers required
6.2.4.1. Portable extinguishers shall be provided to protect every building, each hazardous occupancy inside the building and each hazardous process or operation located outside. Distance above floor
6.2.4.2. Portable extinguishers with a gross weight greater than 18 kg shall be installed so that the top of the extinguisher is not more than 1.1 m above the floor when the extinguisher is not equipped with wheels.
6.2.4.3. Portable extinguishers having a gross weight of 18 kg or less shall be installed so that the top of the extinguisher is not more than 1.5 m above the floor. Operating instructions
6.2.4.4. The operating instructions of portable extinguishers shall face outward when the extinguishers are located in cabinets, in wall recesses or on shelves. Subsection 6.2.5. Grading of Hazards Light hazard occupancy
6.2.5.1. Where the quantity of combustible material present is such that fires of small size may be expected, such as in offices, schoolrooms, churches, assembly halls and telephone exchanges, the occupancy shall be graded as light hazard. Ordinary hazard occupancy
6.2.5.2. Where the quantity of combustible material present is such that fires of moderate size may be expected, such as in mercantile occupancies, display rooms, auto showrooms, parking garages, light manufacturing, warehouses not classified as extra hazard and school shop areas, the occupancy
shall be graded as ordinary hazard. Extra hazard occupancy
6.2.5.3. Where the quantity of combustible material present is such that fires of severe magnitude may be expected, such as in woodworking, auto repair, aircraft servicing, mercantile storage areas, warehouses with high-piled combustibles and processes incorporating flammable liquids or
combustible liquids, the occupancy shall be graded as extra hazard. Subsection 6.2.6. Distribution
6.2.6.1. (1) Portable extinguishers required in Article 6.2.4.1. shall be located in conformance with this Subsection. (2) Despite Sentence (1), in an unoccupied warehouse equipped with a fixed fire protection system, provision shall be made for portable extinguishers to be available for use by responding personnel. (3) The location and number of portable extinguishers required under Sentence (2) shall be approved. Building protection
6.2.6.2. Portable extinguishers that are provided to protect a building
shall be suitable for fighting Class A fires and be available for use at all times. Occupancy protection
6.2.6.3. Portable extinguishers that are provided to protect a hazardous occupancy shall be those required in this Section for fighting Class A fires, Class B fires, Class C fires, Class D fires or Class K fires. Extinguishers for Class A fires
6.2.6.4. Except as required in Article 6.2.6.5., portable extinguishers for Class A fires shall be provided in conformance with Table 6.2.6.A.
6.2.6.5. Where a floor area is less than that shown in Table 6.2.6.A., one portable extinguisher not less than the minimum size permitted shall be provided. TABLE 6.2.6.A. Forming Part of Article 6.2.6.4.  Basic Minimum Extinguisher Rating for Area Specified   Maximum Travel Distance to Extinguisher, m   Maximum Area to be Protected per Extinguisher for Class A Fires, m2 

          Light Hazard Occupancy   Ordinary Hazard Occupancy   Extra Hazard Occupancy 

  2A   25   600   300   Not Acceptable 

  3A   25   900   400   300 

  4A   25   1100   600   400 

  6A   25   1100   900   600 

  10A   25   1100   1100   900 

  20A   25   1100   1100   1100 

  40A   25   1100   1100   1100 Hose stations in lieu of extinguishers
6.2.6.6. Up to one half of the number of portable extinguishers required in Table 6.2.6.A. may be replaced by hose stations. Extinguishers for Class B fires
6.2.6.7. Except as required by Article 6.2.6.9., portable extinguishers for Class B fires shall be provided as required in Table 6.2.6.B.
6.2.6.8. (1) Where up to three portable extinguishers rated for Class B fires
are used to satisfy the extinguisher rating specified in Table 6.2.6.B., the sum of the basic extinguisher ratings shall satisfy the requirements in Table 6.2.6.B. (2) No more than three portable extinguishers shall be used to satisfy the requirements of Table 6.2.6.B. TABLE 6.2.6.B. Forming Part of Article 6.2.6.7.  Grade of Hazard   Basic Minimum Extinguisher Rating per Unit   Maximum Travel Distance to Extinguishers, m 

  Light   5B   9 

  10B   15 

  Ordinary   10B   9 

  20B   15 

  Extra   20B   9 

  40B   15 Extinguishers for flammable and combustible liquids
6.2.6.9. (1) Portable extinguishers for Class B fires shall be provided for
flammable liquid and combustible liquid hazards when flammable liquids or combustible liquids are stored in open containers to a depth greater than 6 mm.  (2) The portable extinguishers shall provide at least one numerical unit of extinguishing potential for Class B fires per 0.1 m2 of surface area of the largest open container within the area, but in no case shall the extinguisher rating be less than that required by Table 6.2.6.B. (3) The distance travelled to reach a portable extinguisher required by Sentence (1) shall not exceed 15 m.
6.2.6.10. (1) Where up to three foam-type portable extinguishers rated for Class B fires are used to satisfy the requirements of Article 6.2.6.9., the sum of the basic extinguisher ratings shall satisfy the requirements in Table 6.2.6.B. (2) No more than three portable extinguishers shall be used to satisfy the requirements of Table 6.2.6.B. Supplementary protection
6.2.6.11. Portable extinguishers shall supplement fixed fire protection in Part 5 in accordance with Article 6.2.6.9. where a flammable liquid or combustible liquid is stored in an open container and where the liquid surface area exceeds 0.4 m2. Extinguishers for commercial cooking equipment
6.2.6.12. (1) Portable extinguishers suitable for Class K fires shall be provided to protect cooking operations. (2) Sentence (1) does not apply to cooking operations protected by wet chemical or dry chemical extinguishers not listed for Class K fires that met the requirements of this Code on December 31, 2014, as it read on that day, unless the extinguishers (a)  become due for an internal examination or hydrostatic test under Subsection 6.2.7., (b)  require recharging due to use, or (c)  become damaged. Extinguishers for Class C fires
6.2.6.13. Portable extinguishers suitable for Class C fires shall be provided in or near service rooms containing electrical equipment. Distribution
6.2.6.14. Distribution of portable extinguishers for Class C fires shall conform to the applicable provisions for the distribution of extinguishers for Class A fires or Class B fires in the vicinity of the electrical equipment.
6.2.6.15. Reference shall be made to Parts 2, 3, 4 and 5 for requirements of portable extinguishers for flammable liquids and combustible liquids, hazardous materials, processes and operations. Extinguishers for combustible metal fires
6.2.6.16. (1) For fires involving combustible metals, extinguishers or extinguishing agents with Class D fire ratings suitable for the combustible metal shall be provided. (2) Extinguishing equipment shall be located not more than 25 m from the Class D fire hazard. Subsection 6.2.7. Inspection, Testing and Maintenance
6.2.7.1. (1) Maintenance and testing of portable extinguishers shall be in conformance with NFPA 10, “Portable Fire Extinguishers”. (2) Portable extinguishers that are inspected in conformance with NFPA 10, “Portable Fire Extinguishers”, are deemed to satisfy the inspection requirements of this Subsection. Examination
6.2.7.2. Portable extinguishers shall be inspected monthly. Defective extinguishers
6.2.7.3. Portable extinguishers having defects shall be repaired and, if necessary, recharged to ensure the extinguishers will operate effectively and safely. Tags
6.2.7.4. (1) Each portable extinguisher shall have a tag securely attached to it showing the maintenance or recharge date, the servicing agency and the signature of the person who performed the service. (2) Sentence (1) does not apply where other approved records are maintained that show the maintenance or recharge date, the servicing agency and the signature of the person who performed the service. Maintenance records
6.2.7.5. A permanent record containing the maintenance date, the examiner’s name and a description of any maintenance work or hydrostatic testing carried out shall be prepared and maintained for each portable extinguisher. Maintenance after use
6.2.7.6. Portable extinguishers shall be replaced or recharged after use in conformance with instructions given on the extinguisher nameplate.
6.2.7.7. Extinguisher shells, cartridges or cylinders that show leakage or permanent distortion in excess of specified limits or that rupture shall be removed from service.
6.2.7.8. Hydrostatic pressure tests shall be conducted at the original test pressure as stated on the nameplate. Test labels
6.2.7.9. (1) Where a portable extinguisher is tested, a label shall be fixed to the extinguisher after testing that indicates the month and year the hydrostatic pressure test
was performed, the test pressure used and the name of the person or agency performing the test. (2) Sentence (1) does not apply where a permanent record of the test is kept and is available to the fire department. SECTION 6.3 ALARM AND VOICE COMMUNICATION SYSTEMS FOR LIFE SAFETY Subsection 6.3.1. General Access
6.3.1.1. Access to fire alarm and voice communication system components requiring inspection
or servicing shall be kept unobstructed. Monitoring
6.3.1.2. (1) Where the Building Code or this Code require a fire alarm system to be monitored to transmit a signal to the fire department, the building owner shall ensure the continuation of the monitoring. (2) Where the fire alarm system monitoring referred to in Sentence (1) is provided by a central station, the building owner shall obtain written documentation from the central station operator that the monitoring service complies with (a)  NFPA 71, “Standard for the Installation, Maintenance, and Use of Signaling Systems for Central Station Service”, or (b)  CAN/ULC-S561, “Installation and Services for Fire Signal Receiving Centres and Systems”. (3) Where a fire alarm system is monitored by a central station to meet the requirements of the Building Code or this Code, the operator of the central station shall provide, upon request by the owner or Chief Fire Official, a document attesting that the monitoring service is in compliance with one of the standards identified in Sentence (2). (4) Despite Article 1.2.1.1. of Division A, where the Building Code or this Code requires a fire alarm system to be monitored and the monitoring is provided by a central station, the operator of the central station shall be responsible for maintaining the monitoring service and associated monitoring equipment in accordance with one of the standards identified in Sentence (2). (5) Where the fire alarm system is monitored by a proprietary signalling system, such system shall be maintained in accordance with Chapter 4 of NFPA 72, “National Fire Alarm and Signaling Code”.
6.3.1.3. (1) If a fire alarm or voice communication system or any part thereof is shut down (a)  the fire department and building occupants shall be notified in accordance with Article 1.1.1.1., and (b)  the supervisory staff shall be notified.
6.3.1.4. Fire alarm and voice communication systems shall be maintained in operating condition. Signal silencing
6.3.1.5. (1) Once activated, a fire alarm system shall not be manually silenced unless it has been confirmed by supervisory staff, in accordance with approved procedures as detailed in the fire safety plan, that no fire emergency exists. (2) Sentence (1) does not apply where a silencing switch is part of an approved
integrated voice communication system and signal silencing takes place to allow fire emergency instructions to be heard. Disconnect switches
6.3.1.6. Disconnect switches for power supplies which serve only fire alarm systems or interconnected smoke alarms shall be in a locked secure area or otherwise secured in an approved manner. Relocating manual pull stations
6.3.1.7. (1) Where
approved, manual pull stations for a fire alarm system in a building may be relocated if there is a high incidence of false alarms in the building. (2) Where the manual pull stations are relocated, alternate approved measures shall be used to maintain the level of life safety. Repairs and alterations to fire alarm systems
6.3.1.8. Repair, replacement and alterations of fire alarm system components shall be in accordance with CAN/ULC-S524, “Standard for the Installation of Fire Alarm Systems”. Subsection 6.3.2. Check, Inspect and Test Obligation to ensure compliance
6.3.2.1. (1) The owner shall ensure that any person performing the annual tests or annual inspections required by this Subsection for fire alarm systems or performing the repairs, replacements or alterations of fire alarm systems referred to in Article 6.3.1.8. is in compliance with the requirements of (a)  Clause 1.2.1.2.(1)(a) of Division C, or (b)  Sentence 1.2.1.2.(2) of Division C. (2) The owner shall ensure that any person performing the annual tests or annual inspections
required by this Subsection for interconnected smoke alarm systems or performing the tests or maintenance for interconnected
smoke alarm systems referred to in Article 6.3.2.6. is in compliance with the requirements of (a)  Clause 1.2.2.2.(1)(a) of Division C, or (b)  Sentence 1.2.2.2.(2) of Division C. Fire alarm systems
6.3.2.2. (1) Except as provided in Sentence (2), a fire alarm system, with or without voice communication capability, shall be inspected and tested in conformance with CAN/ULC-S536, “Inspection and Testing of Fire Alarm Systems”. (2) Despite Clause 5.7.4.1.6. of CAN/ULC-S536, “Inspection and Testing of Fire Alarm Systems”, a UL listed smoke detector sensitivity instrument may be used to conduct annual sensitivity testing of smoke detectors. (3) A description of the fire alarm system as required in Clause 3.6 of CAN/ULC-S536, “Inspection and Testing of Fire Alarm Systems”, shall be kept current and maintained in the building at an approved location. (4) A record of each device, component and circuit of the fire alarm system that is inspected and tested in accordance with Sentence (1) shall (a)  indicate whether the device, component or circuit is in proper working order, and (b)  be kept in accordance with Subsection 1.1.2. (5) Where a fire alarm system is monitored to transmit a signal to the fire department, the owner shall record whether all signals from the tests conducted in Sentence (1), or other events, are received by the monitoring station, and records shall be kept in accordance with Subsection 1.1.2. Central alarm and control facilities
6.3.2.3. The central alarm and control facility shall be checked daily for indication of trouble in the system. Voice communication systems
6.3.2.4. Voice communication systems that are integrated with a fire alarm system shall be tested in conformance with CAN/ULC-S536, “Inspection and Testing of Fire Alarm Systems”.
6.3.2.5. (1) Voice communication systems that are not integrated with a fire alarm system shall be
tested monthly in compliance with Sentences (2) and (3). (2) Loudspeakers described in Sentence (1) shall be tested monthly as an all-call signal to ensure they function as intended. (3) Communication from at least one remote firefighter emergency telephone location to the control unit shall be tested monthly on a rotational basis so that communication from all remote firefighter emergency telephone locations are tested at least once per year. (4) Voice communication systems are not required to be tested in conformance with Sentences (1) and (2) where the systems are regularly used as part of a paging system. Interconnected smoke alarms
6.3.2.6. (1) This Article applies to interconnected smoke alarm systems in all residential occupancies and care occupancies, except in individual dwelling units and in buildings regulated by Section 9.8. (2) Interconnected smoke alarms shall be tested and maintained in operating condition in conformance with CAN/ULC-S552, “Standard for the Maintenance and Testing of Smoke Alarms”, and as required by this Article. (3) The power supply shall be checked weekly. (4) The operability of the interconnected system shall be confirmed monthly, by testing
at least one smoke alarm using its test function, on a rotational basis. (5) Where installed, each manual pull station shall be tested to ensure activation of the interconnected smoke alarms on an annual basis. (6) Written records shall be kept of weekly checks of the power supply for at least six months after they are made, and be available upon request to the Chief Fire Official. (7) Revoked: O. Reg. 33/19, s. 23. Subsection 6.3.3. Smoke Alarms — Maintenance and Testing Application
6.3.3.1. (1) This Subsection applies to smoke alarms in (a)  suites of residential occupancy, (b)  guest suites, (c)  sleeping rooms not within a dwelling unit, and (d)  other occupancies in which smoke alarms are required by the Building Code. Landlord is responsible
6.3.3.2. Despite the definition of owner in Article 1.4.1.2. of Division A, in the case of a rental suite, only the landlord shall be considered to be the owner for the purpose of applying Article 1.2.1.1. of Division A to this Subsection. Duty to maintain in operating condition
6.3.3.3. (1) Smoke alarms shall be maintained in operating condition.  (2) Primary and secondary power supplies that serve smoke alarms shall be maintained in operating condition. (3) If the Building Code requires a visual signalling component that is integral with or connected to a smoke alarm, the visual signalling component shall be maintained in operating condition. Maintenance instructions to be given to tenant
6.3.3.4. The landlord of each rental suite shall give the tenant a copy of the smoke alarm manufacturer’s maintenance instructions or approved
alternative maintenance instructions. Tenant to notify landlord
6.3.3.5. (1) A tenant of a rental suite shall notify the landlord as soon as the tenant becomes aware that (a)  a smoke alarm in the unit is disconnected, (b)  a smoke alarm in the unit is not operating, or (c)  the operation of a smoke alarm in the unit is impaired. Disabling prohibited
6.3.3.6. No person shall disable a smoke alarm. Replacement
6.3.3.7. (1) A smoke alarm shall be replaced within the time frame indicated in the manufacturer’s instructions.
 (2) When a smoke alarm is replaced (a)  in the case of a suite subject to Part 9, the replacement shall not provide a lower level or type of protection than that required by Part 9, (b)  in the case of a suite not subject to Part 9 that was constructed on or after April 6, 1998, the replacement shall not provide a lower level or type of protection than that required by the Building Code in effect at the time of construction of the suite, and (c)  in the case of a suite not subject to Part 9 that was constructed before April 6, 1998, the replacement shall not provide a lower level or type of protection than that required by Article 2.13.2.1. (3) The Chief Fire Official may approve an alternative to a requirement of Sentence (2) if, in the opinion of the Chief Fire Official, the alternative provides fire safety protection equivalent to or greater than the fire safety protection that would be provided by the requirement. Testing
6.3.3.8. (1) This Article applies to rental suites. (2) The landlord shall test smoke alarms
annually and after every change in tenancy. (3) The landlord shall test battery-operated smoke alarms after the battery is replaced. (4) The landlord shall test smoke alarms
that are connected to an electrical circuit after any change is made to the electrical circuit. (5) For the purposes of Sentences (2), (3) and (4), smoke alarms shall be tested by activating the smoke alarm test feature. (6) If the Building Code requires a visual signalling component that is integral with or connected to a smoke alarm, the landlord shall ensure that any test
of the smoke alarm required by Sentences (2) to (4) activates the visible signalling component. Subsection 6.3.4.  Carbon Monoxide Alarms — Maintenance and Testing Application
6.3.4.1. This Subsection applies to carbon monoxide alarms in buildings containing a residential occupancy.  Landlord is responsible
6.3.4.2. Despite the definition of owner in Article 1.4.1.2. of Division A, in the case of a rental suite of residential occupancy, only the landlord shall be considered to be the owner for the purpose of applying Article 1.2.1.1. of Division A to this Subsection. Duty to maintain in operating condition
6.3.4.3. (1) Carbon monoxide alarms shall be maintained in operating condition.  (2) Primary and secondary power supplies that serve carbon monoxide alarms shall be maintained in operating condition. Maintenance instructions to be given to tenant
6.3.4.4. The landlord of each rental suite of residential occupancy shall give the tenant a copy of the carbon monoxide alarm manufacturer’s maintenance instructions or approved
alternative maintenance instructions. Tenant to notify landlord
6.3.4.5. (1) A tenant of a rental suite of residential occupancy shall notify the landlord as soon as the tenant becomes aware that (a)  a carbon monoxide alarm in the unit is disconnected, (b)  a carbon monoxide alarm in the unit is not operating, or (c)  the operation of a carbon monoxide alarm in the unit is impaired. Disabling prohibited
6.3.4.6. No person shall disable a carbon monoxide alarm.  Replacement in certain buildings
6.3.4.7. (1) Subject to Sentence (2), this Article applies to every building that contains a residential occupancy and (a)  a fuel-burning appliance, (b)  a fireplace, or (c)  a storage garage. (2) This Article applies (a)  as of April 15, 2015, in the case of buildings that contain no more than six suites of residential occupancy, and (b)  as of October 15, 2015, in the case of buildings that contain more than six suites of residential occupancy. (3) A carbon monoxide alarm shall be replaced within the time frame indicated in the manufacturer’s instructions. (4) Despite Section 2.16, when a carbon monoxide alarm is replaced in a suite of residential occupancy constructed on or after August 6, 2001, the replacement (a)  shall not provide a lower level or type of carbon monoxide protection than that required by the Building Code as it read on the day the suite was constructed, and (b)  shall comply with CSA-6.19, “Residential Carbon Monoxide Alarming Devices” or UL 2034, “Single and Multiple Station Carbon Monoxide Alarms”. (5) When a carbon monoxide alarm is replaced in a suite of residential occupancy constructed before August 6, 2001, the replacement carbon monoxide alarm shall meet the requirements of Article 2.16.2.1. (6)  The Chief Fire Official
may approve an alternative to a requirement of Sentence (4) or (5) if, in the opinion of the Chief Fire Official, the alternative provides life safety protection equivalent to or greater than the life safety protection that would be provided by the requirement. Testing
6.3.4.8. (1) This Article applies to rental suites of residential occupancy. (2) The landlord shall test carbon monoxide alarms annually and after every change in tenancy. (3) The landlord shall test battery-operated carbon monoxide alarms after the battery is replaced. (4) The landlord shall test carbon monoxide alarms that are connected to an electrical circuit after any change is made to the electrical circuit. (5) For the purposes of Sentences (2), (3) and (4), carbon monoxide alarms shall be tested by activating the carbon monoxide alarm test feature. SECTION 6.4 STANDPIPE AND HOSE SYSTEMS Subsection 6.4.1. General
6.4.1.1. During alteration of a building required to have a standpipe and hose system, the system shall be installed or dismantled progressively so as to provide protection to all floor areas.
6.4.1.2. Standpipe and hose systems shall be maintained in operating condition. Fire department connections
6.4.1.3. (1) Except when in use or being inspected in accordance with Article 6.4.3.7., fire department connections shall be equipped with plugs or caps that are secured wrench-tight. (2) If plugs or caps are missing, the fire department connections shall be examined for obstructions, back-flushed when conditions warrant and the plugs or caps replaced. Out of service requirements
6.4.1.4. (1) If a standpipe system or any part thereof is shut down (a)  the fire department and building occupants shall be notified in accordance with Article 1.1.1.1., and (b)  the supervisory staff shall be notified. Hotels
6.4.1.5. In buildings containing a hotel, a standpipe and hose system shall not be shut down, disconnected or otherwise impaired without notifying the Chief Fire Official in accordance with a schedule identified in the approved
fire safety plan. Inspection, testing and maintenance
6.4.1.6. Compliance with the
inspection, testing and maintenance provisions of NFPA 25, “Standard for the Inspection, Testing and Maintenance of Water-Based Fire Protection Systems”, for standpipe and hose systems is deemed to satisfy the requirements of Articles 6.4.2.1. to 6.4.2.5. and Subsection 6.4.3. Subsection 6.4.2. Maintenance and Inspection of Hose Stations and Equipment Hose stations
6.4.2.1. Hose stations shall be inspected monthly to ensure that the hose is in proper position and that all of the equipment is in place and in operable condition.
6.4.2.2. Standpipe and hose system equipment shall be used for fire protection only.
6.4.2.3. Standpipe hose stations shall be conspicuously identified and unobstructed. Hose valves
6.4.2.4. Hose valves shall be inspected annually to ensure that they are tight so that there is no water leakage into the hose. Hose
6.4.2.5. (1) Standpipe hose shall be unracked, unreeled or unrolled and inspected
at least annually and after use, and any worn hose or gaskets in the couplings at the hose valves and at the nozzle replaced. (2) If the hose is replaced on the rack, reel or storage area, it shall be reracked, rereeled or rerolled so that any folds do not occur at the same position they were previously on the hose. Standpipe identification
6.4.2.6. (1) Except as required in Sentence (2), each hose connection in a standpipe system shall be provided with a legible sign reading: “FIRE HOSE FOR USE BY TRAINED PERSONS ONLY”. (2) Each hose connection in a dry standpipe system with no permanent water supply shall be provided with a legible weatherproof sign reading: “DRY STANDPIPE FOR FIRE DEPARTMENT USE ONLY”. Hose cabinets
6.4.2.7. (1) If a fire hose station is located in a cabinet, an approved
lockable, scored glass break-front cabinet may be used. (2) Hose stations in a major occupancy consisting of detention occupancy may be located in secure areas, or in lockable cabinets where (a)  identical keys for all cabinets are located at all guard stations, or (b)  electrical remote release devices are provided and are connected to an emergency power supply. Subsection 6.4.3. Checking, Inspection and Testing Standpipe systems
6.4.3.1. (1) Standpipe systems that have been modified, extended or are being restored to service after a period of disuse exceeding one year shall be tested
in conformance with Articles 6.4.3.2. to 6.4.3.5. (2) Where standpipes are built in walls or partitions, the tests
shall be made before the standpipes are concealed. Hydrostatic test
6.4.3.2. (1) Standpipe system piping shall be hydrostatically tested for 2 hours at a pressure of not less than (a)  1400 kPa (gauge), or (b)  350 kPa (gauge) in excess of the normal hydrostatic pressure when the normal hydrostatic pressure is in excess of 1050 kPa (gauge). Fire department connections
6.4.3.3. Piping between the fire department connection and the check valve in the inlet pipe to the standpipe shall be hydrostatically tested
in the same manner as the remainder of the system. Underground mains
6.4.3.4. (1) Underground mains and connections shall be hydrostatically tested
for 2 hours at a hydrostatic pressure of 350 kPa (gauge) in excess of the maximum hydrostatic pressure in service, but not less than 1400 kPa (gauge). (2) Leakage during the test shall not exceed 2 L/h per 100 joints for pipe laid with rubber gasketted joints, and 30 mL/h per 25 mm of pipe diameter per joint for pipe laid with caulked lead or lead substitute joints. Flow and pressure tests
6.4.3.5. Flow and pressure tests shall be conducted at the highest and most remote hose valve or hose connection to ensure that the water supply for the standpipe system is provided as originally designed. Dry standpipes
6.4.3.6. (1) Standpipe system piping which normally remains dry shall be hydrostatically tested in accordance with Article 6.4.3.2. at intervals of not more than five years. (2) Water supply pressure and system air pressure for automatic dry standpipe systems shall be checked weekly by using gauges to ensure that the system is maintained at the required operating pressure. Fire department connections