3.5.2.4. (1) Piles or containers with metal shavings, turnings and dusts shall be stored in an area separate from other salvage materials and identified with warning signs. (2) Warning signs required in Sentence (1) shall (a)  be visible from all directions of approach, and (b)  have the name of the metal and the words “COMBUSTIBLE METAL — DO NOT USE WATER” displayed in plain legible letters as described in Sentence (3). (3) Lettering on warning signs shall be red or white letters 114 mm high with a 19 mm stroke on a contrasting background. Subsection 3.5.3. Revoked: O. Reg. 256/14, s. 76. SECTION 3.6, 3.7 Revoked: O. Reg. 256/14, s. 77. O. Reg. 213/07, Division B, Part 3; O. Reg. 256/14, ss. 48-77. PART 4   FLAMMABLE liquids AND COMBUSTIBLE LIQUIDS TABLE OF CONTENTS SECTION 4.1   GENERAL 

  Subsection 4.1.1.   Application and Compliance 

  Subsection 4.1.2.   Classification 

  Subsection 4.1.3.   Flash Point 

  Subsection 4.1.4.   Electrical Installations 

  Subsection 4.1.5.   Fire Prevention and Protection 

  Subsection 4.1.6.   Spill Control and Drainage Systems 

  Subsection 4.1.7.   Ventilation 

  Subsection 4.1.8.   Handling of Flammable and Combustible Liquids 

        

  SECTION 4.2   CONTAINER STORAGE AND HANDLING 

  Subsection 4.2.1.   Application 

  Subsection 4.2.2.   General 

  Subsection 4.2.3.   Containers and Portable Tanks 

  Subsection 4.2.4.   Assembly and Residential Occupancies 

  Subsection 4.2.5.   Mercantile Occupancies 

  Subsection 4.2.6.   Business and Personal Services, Detention, Educational, Care, and Care and Treatment Occupancies 

  Subsection 4.2.7.   Industrial Occupancies 

  Subsection 4.2.8.   Incidental Use 

  Subsection 4.2.9.   Rooms for Container Storage and Dispensing 

  Subsection 4.2.10.   Cabinets for Container Storage 

  Subsection 4.2.11.   Outdoor Container Storage 

        

  SECTION 4.3   STORAGE TANKS 

  Subsection 4.3.1.   Application and Storage Tank Design, Construction and Use 

  Subsection 4.3.2.   Installation of Outside Aboveground Storage Tanks 

  Subsection 4.3.3.   Supports, Foundations and Anchorage for Aboveground Storage Tanks 

  Subsection 4.3.4.   Normal and Emergency Venting for Aboveground Storage Tanks 

  Subsection 4.3.5.   Vent Piping for Aboveground Storage Tanks 

  Subsection 4.3.6.   Openings Other than Vents in Aboveground Storage Tanks 

  Subsection 4.3.7.   Secondary Containment for Aboveground Storage Tanks 

  Subsection 4.3.8.   Installation of Underground Storage Tanks 

  Subsection 4.3.9.   Corrosion Protection of Underground Steel Storage Tanks 

  Subsection 4.3.10.   Vents for Underground Storage Tanks 

  Subsection 4.3.11.   Openings Other than Vents in Underground Storage Tanks 

  Subsection 4.3.12.   Installation of Storage Tanks Inside Buildings 

  Subsection 4.3.13.   Rooms for Storage Tanks 

  Subsection 4.3.14.   Openings Other than Vents in Storage Tanks in Buildings 

  Subsection 4.3.15.   Leakage Testing of Storage Tanks 

  Subsection 4.3.16.   Leakage Detection of Storage Tanks 

  Subsection 4.3.17.   Out of Service 

        

  SECTION 4.4   PIPING AND TRANSFER SYSTEMS 

  Subsection 4.4.1.   Application 

  Subsection 4.4.2.   Materials for Piping, Valves and Fittings 

  Subsection 4.4.3.   Corrosion Protection of Piping Systems 

  Subsection 4.4.4.   Identification of Piping Systems 

  Subsection 4.4.5.   Joints in Piping Systems 

  Subsection 4.4.6.   Leakage Testing of Piping Systems 

  Subsection 4.4.7.   Location and Arrangement of Piping 

  Subsection 4.4.8.   Valves in Piping Systems 

  Subsection 4.4.9.   Heating of Piping Systems 

  Subsection 4.4.10.   Methods of Transfer in Piping Systems 

  Subsection 4.4.11.   Operating Procedures for Piping Systems 

        

  SECTION 4.5   FUEL DISPENSING STATIONS 

  Subsection 4.5.1.   Storage, handling and use of flammable liquids and combustible liquids 

        

  SECTION 4.6   BULK PLANTS 

  Subsection 4.6.1.   Application 

  Subsection 4.6.2.   Storage 

  Subsection 4.6.3.   Dispensing 

  Subsection 4.6.4.   Loading and Unloading Facilities 

  Subsection 4.6.5.   Fire Protection 

  Subsection 4.6.6.   Spill Control 

        

  SECTION 4.7   PIERS AND WHARVES 

  Subsection 4.7.1.   Application 

  Subsection 4.7.2.   General 

  Subsection 4.7.3.   Storage Tanks 

  Subsection 4.7.4.   Piping, Valves and Fittings 

  Subsection 4.7.5.   Bonding and Grounding 

  Subsection 4.7.6.   Fire Protection 

  Subsection 4.7.7.   Bulk Transfer Stations 

  Subsection 4.7.8.   Cargo Hose 

  Subsection 4.7.9.   Cargo Pumps 

  Subsection 4.7.10.   Pump Houses 

  Subsection 4.7.11.   Transfer Operations 

        

  SECTION 4.8   PROCESS PLANTS 

  Subsection 4.8.1.   Application 

  Subsection 4.8.2.   Outdoor Processing Equipment 

  Subsection 4.8.3.   Processing Buildings 

  Subsection 4.8.4.   Fire Prevention and Protection 

        

  SECTION 4.9   DISTILLERIES 

  Subsection 4.9.1.   Application 

  Subsection 4.9.2.   General 

  Subsection 4.9.3.   Storage Tanks and Containers 

  Subsection 4.9.4.   Storage 

  Subsection 4.9.5.   Piping and Pumping Systems 

  Subsection 4.9.6.   Ventilation 

  Subsection 4.9.7.   Spill Control 

  Subsection 4.9.8.   Fire Protection 

        

  SECTION 4.10   RESERVED 

        

  SECTION 4.11   TANK VEHICLES 

  Subsection 4.11.1.   Application 

  Subsection 4.11.2.   General 

  Subsection 4.11.3.   Loading, Unloading and Dispensing from Tank Vehicles 

        

  SECTION 4.12   LABORATORIES 

  Subsection 4.12.1.   Application 

  Subsection 4.12.2.   Separation 

  Subsection 4.12.3.   Maximum Quantities 

  Subsection 4.12.4.   Emergency Planning 

  Subsection 4.12.5.   Spill Control 

  Subsection 4.12.6.   Electrical Equipment 

  Subsection 4.12.7.   Inspection and Maintenance 

  Subsection 4.12.8.   Ventilation 

  Subsection 4.12.9.   Refrigerated Storage 

  Subsection 4.12.10   Existing Laboratories in Basements Section 4.1 General Subsection 4.1.1. Application and Compliance Application and interpretation