2.8.2.1. (1) A fire safety plan shall be prepared, approved and implemented in buildings and premises to which this Section applies. (2) A fire safety plan shall (a)  provide for the emergency procedures to be followed in case of fire, including (i)  sounding the fire alarm, (ii)  notifying the fire department, (iii)  instructing occupants on procedures to be followed when the fire alarm sounds, (iv)  evacuating occupants, including special provisions for persons requiring assistance, (v)  procedures for use of elevators, and (vi)  confining, controlling and extinguishing the fire, (b)  provide for the appointment and organization of supervisory staff to carry out fire safety duties, (c)  provide for the training of supervisory staff and the instruction of other occupants in their responsibilities for fire safety, (d)  include documents and diagrams showing the type, location and operation of the building
fire emergency systems, (e)  provide for the holding of fire drills and set out fire drill procedures, (f)  provide for the control of fire hazards in the building, (g)  provide for the maintenance of building facilities provided for the safety of occupants, and (h)  provide for alternative measures to be provided for the safety of occupants during a shutdown of any or all fire protection equipment or systems. (3) The fire safety plan shall be kept in the building or premises in an approved location. (4) The fire safety plan shall be reviewed as often as necessary, but at least every 12 months, and shall be revised as necessary so that it takes into account changes in the use or other characteristics of the building or premises. (5) Before demolition or construction, including hot surface applications, commences in or on the building or premises, the fire safety plan shall be revised to incorporate (a)  temporary alternative measures for the fire safety of the occupants during the demolition or construction, and (b)  temporary procedures to control fire hazards associated with the demolition or construction, including procedures to mitigate risks to adjacent buildings. (6) The revised fire safety plan prepared under Sentence (4) or (5) shall be implemented. (7) In the case of a care occupancy, care and treatment occupancy and retirement home, any training of supervisory staff carried out under a fire safety plan shall be recorded. (8) The original or a copy of at least the most recent and the immediately preceding record referred to in Sentence (7) shall be retained in the building for a period of at least two years after being prepared and shall be made available to the Chief Fire Official for examination on request. Supervisory staff 2.8.2.2. (1) There shall be sufficient supervisory staff available in care occupancies, care and treatment occupancies, detention occupancies
and retirement homes to carry out the duties required in the fire safety plan. (2) In
hotel establishments (a)  there shall be sufficient supervisory staff available to carry out the duties as required in the fire safety plan, and (b)  in buildings
greater than 3 storeys in building height or having a total area greater than 4000 m2, supervisory staff shall be on duty whenever the building is occupied. High buildings