GE Lighting 74475 GE260IS-MV-N-DIY LFL ProLine Electronic Multivolt Instant Start Ballast for 2 or 1-F96T12-F48T12
GE 74475 GE260IS-MV-N-DIY, LFL Multi-Volt ProLine Electronic Multivolt Instant Start BallastApplication: 2 or 1- F96T12-F48T12 Electronic Instant Start 120 to 277; DIY Pack, Category: Linear Fluorescent, Ballast Type: Electronic- Multivolt Instant Start. Starting Method: Instant start. Lamp Wiring: Parallel. Line Voltage Regulation (+/-): 10-percent. Case Temperature (MAX): 70 Degree C (158 Degree F). Ballast Factor: Normal. Power Factor Correction: Active. Sound Rating: A (20-24 decibels). Additional Info: Auto-restart, Thermally protected. ELECTRICAL CHARACTERISTICS. Supply Current Frequency: 60-Hz. Product Code: 74475. Description: GE260IS-MV-N-DIY. Mounting dimensions: Mount Length: (M) 8.9 in (225.80 mm) Mount Width (X or F) 1.1 in (28.70 mm) Mount Slots (MS) 0.3 in (7.92 mm) . Weight: 1.65-lbs Exit Type: Side . Remote Mounting Wire Gauge: 18 AWG Lead lengths Qty Exit Length (± 1 -Inch) White 1 Left 25.0 in (635 mm) Red 1 Right 59.0 in (1499 mm) Blue 2 Right 67.0 in (1702 mm) Black 1 Left 25.0 in (635 mm) Black 1 Left 25.0 in (635 mm).