Fantech DBF 4XLT Dryer Booster Kit w/FG 4XL Fan with wall mount indicator panel
The Fantech DBF4XLT Dryer Booster Fan Has Been Specially Designed To Solve The Problems Caused By Long Duct Runs On Clothes Dryers. According To Dryer Manufacturers And Some Local Building Codes, Booster Fans Should Be Added In The Dryer Duct Run When The Length Of The Duct Exceeds 24 Feet With No Bends, 20 Feet With One Bend Or 15 Feet With Two Bends. Feature and Specification Inline Dryer Booster Fan Featuring Self-Cleaning Backward Curved Impeller Capable Of Maintaining An Air Velocity Of 1200 Fpm In Duct Systems Up To 130 Feet. Galvanized Steel Housing With Powder-Coat Finish Integrated Pressure Sensing Switch Wall-Mount Indicator Panel Uses 4" Duct 5-1/2 Foot 120Vac Power Cord Mounting Bracket And Hardware Included Dryer Booster Fan Shall Be Capable Of Maintaining An Air Velocity Of 1200 fpm With An Equivalent Duct Length Of 130 Feet Of 4 Inch Rigid Steel Duct. The Dryer Booster Fan Shall Be Capable Of Exhausting Air Up To 75°C Motor Shall Be a Permanently Lubricated, Enclosed, External Rotor Design. The Blower Wheel Shall Be a Self Cleaning Backward Curved Impeller Design. A 50 Foot Cable Shall Be Provided To Connect The Remote Mount Indicator Panel To The Dryer Booster Fan. Dryer Booster Fan Is To Be Provided With Inlet And Outlet Flanges For Connection To 4" Duct. Quick Disconnect Duct Clamp To Be Provided. Unit Shall Be Provided With 18" Of Pressure Sensing Tubing With Mounting Grommet. Unit Shall Be CSA Listed For Use As A Dryer Booster Fan. Unit Shall Be Designed To Meet Csa T.I.L. No. G-48. Unit Shall Include Remote-Mount, Low Voltage Indicator Panel Capable Of Displaying: Normal Operation, No Power, Blocked Duct, Locked Motor Rotor And Low Speed Conditions. Electrical Specifications: 115 Volt, 0.73 Amp, 60 Hz, 83 Watt, 2800 RPM, 195 CFM