RadonAway Model GP301 3" Radon Fan
Click here for fan comparison guide CLICK HERE FOR RADON TEST KITSRadonAway Model GP301 3" Radon Fan.  This high pressure, powerful fan provides powerful suction for tough applications. 92 CFM at 1" WC Static Pressure  Stronger performance (suction) than GP201 but higher energy usage and slightly higher cost. Designed especially for radon mitigation, RadonAway's GP Series fans provide superb performance and are ultra-quiet and attractive. They are ideal for most active subslab radon mitigation systems Note: Choice of fan model is dependent on building characteristics and should be made by a radon professional. Features: High Suction (max pressure is 2.6" WC) for compacted subslab materials Quiet Operation Mounts on duct piope or with integral flange 3" Diameter duct collars Electrical box for hard wire or plug in (corded plug not included) ETL Listed - for indoor or outdoor use 5 Year Warranty Made in the USA Specifications: Power Consumption - 55-90 watts CFM at 0" W.C. - N/A CFM at 1" W.C. - 92 Weight - 12 lbs Inlet / Outlet - 3.5" OD for easy coupling to Schedule 40 PVC Size - 13" H x 12.5" x 11.5" Normal operating temperature range: -20 - 120 degrees F. Maximum inlet air temperature: 80 degrees F. Continuous Duty Class B Insulation 3000 RPM Thermally protected    RADON FAN COMPARISON TABLE:  Model Watts Max Pressure Duct Dia .5 1 1.5 2.0 2.5 3.0 3.5 4.0 Fantech HP2133 14-20 .84 4" 60 0 0 0 0 0 0 0 Fantech HP2190 60-95 1.93 4" 138 81 35 0 0 0 0 0 Fantech HP190 60-85 2.01 4.5" 123 89 45 0 0 0 0 0 Fantech HP220 85-152 2.46 6" 260 193 58 15 0 0 0 0 Fantech HP190SL 140 2.2 4" 133 103 76 27 0 0 0 0 RadonAway GP201 40-60 2.0 3" 0 82 58 5 0 0 0 0 RadonAway GP301 55-90  2.6 3" 0 92  77  45 10 0 0 0 RadonAway GP501 70-140 4.2