GE Security TX-6010-01-1 Supervised Wireless Smoke, Residential UL217 Transmitter
The GE TX-6010-01-1 Crystal smoke detector is a commercial-grade, photoelectric smoke detector. It is a wireless unit and allows flexibility in locating the unit on a wall or ceiling. Unlike units sold in retail stores (commonly ion detectors), these units are designed to work with your security system and to send a unique signal to the control panel enabling a fire response request to be sent to the Central Monitoring Station. The advantage is the signal is sent whether you are at the premise or not and the fire trucks will roll automatically on this signal. It has a self contained sounder, a low battery annunciator, and a status LED.SpecificationsThis model replaces the 60-848-02-95Voltage: 3VDCTypical average standby current: 35ATypical test current: 2mATypical alarm current: 70mABattery type: Duracell 3V lithium 123,Panasonic lithium CR123A, Sanyo lithium CR123ALow battery threshold: 2.70V causes low battery signalSounder: 85dBa at 10' temporal patternLow battery beep rate: 1 every 45 sec. 2 sec.Sensitivity: 2.2% 1.3%/ft.Operating temperature: 40-100F (4.4-37.8C)Operating humidity range: 0-95% non-condensing RFI Immunity: 20V/m minimum; 0-1000MHzColor: WhiteAlarm dimensions: 5.6" x 2.4" (14.2cm x 6.1cm)Base dimensions: 5.4" x 0.46" (13.7cm x 1.17cm)Drift compensation adjustment: 0.5%/ft. max.Heat detector specifications: Rate-of-rise 15F/min>105F (8.3C/min>40.6C) Fixed: 135F 5F (57.2C 2.8C) RF frequency: 319.5 MHzTransmitter ID: Pre-programmed, 1 Million codesModulation type: AMSignal format: PWMSignal output types: Alarm, tamper, test, low battery, trouble, supervisoryListings: UL217, C-UL US, CSFM, FCCAlternate Part #: CA-TX6010011