Hubbell HBL5269C Insulgrip Series
Hubbell HBL5269C Insulgrip SeriesHubbell's Wiring Devices division offers a wide array of electrical and electronic wiring devices, wire management systems, occupancy sensors, lighting controls and specialized wiring products for the marine and healthcare markets.2P3W, 15A 125V, 5-15R, Black and White Nylon.Hubbell HBL5269C Insulgrip Series Features: Product Type: connectors Body Style: Straight Standard: NEMA Amperage: 15A Voltage: 125V Poles and Wires: 2 Pole, 3 Wire Grounding Wiring Method: Back Wire Hospital Grade ?: No Plug/Connector Grade: Insulgrip NEMA No.: 5-15R Cord Dia.: .230"-.720" (5.8-18.3) Description: Straight Blade Connector Type: 2 Pole, 3 Wire, Grounding Rating: 15A, 125V Certification: UL Listed to UL498 File E1706, CSA Certified to C22.2 No. 42 File 280 IP Suitability: IP20 Housing Material: Nylon-Black Retainer Material: Polycarbonate-Clear Cord Clamp Material: Nylon-Natural Terminal Screw Material: #8-32 Brass, Multiple Drive Ground Screw Material: #8-32 Brass, Multiple Drive (Green) Wire Clamps Material: 0.062" (1.6) Steel - Ni Plated Body Holding Screws: Steel Multiple Drive Contact Holder Material: Nylon-Natural Power Contacts Material: .040" (1.0) Copper Alloy Dielectric Voltage: Withstands 2,000V minimum. Current Interrupting: Certified for current interrupting at full rated current. Temperature Rise: Max 30 DegreesC temperature rise at full rated current after 50 cycles of overload at 150% of rated current at a power factor of 75%.. Terminal Identification: Terminals identified in accordance with UL498 (Brass, White, Green). Terminal Accommodation: #18-#10 AWG copper stranded conductor Product Identification: Ratings are a permanent part of the device. Flammability: UL 94 HB or better. Operating Temperatures: Maximum continuous 75 DegreesC, minimum -40 DegreesC (w/o impact). Certified: UL2305 OEM and replacement use on convention center flat cable cord sets.