Improper maintaining of fire extinguisher at ECC and CRT areas, Number of fire extinguishers were found laid on the wet floor which is potential to rust and getting damaged. Action:- PIVOT to properly maintained the fire extinguishers and if empty must be shifted to the storage area.
Hazard category: Fire / explosion