The following observations have been observed from ANEL material storage area at GH # 37 MTB external area. 1- Poor housekeeping issues were observed in and around the storage area. 2- Inadequate cover protection for the combustible material. 3- Periodical inspection has not been done for the emergency firefighting equipment. 4- Lack of fire point in the whole material storage area.  Action - CMA addressed the concern to TCA JV to rectify all issues. TCA JV to replace fire extinguisher and ensure equipment's are periodically inspected and servicing of fire extinguisher should be done within the time period. TCA JV is requested to clean the area and keep good housekeeping always and also ensure to cover the combustible material with flame retardant sheet to prevent any potential fire hazard and provision of adequate fire point in and around the storage area.
Hazard category: Fire / explosion