Damaged sockets have been identified with DB at pier 3 level 2 area. Action: CMA addressed the issue to TCA JV HSE Person for immediate corrective action. TCA JV to maintain the periodical inspection and ensure the DB’s are in good condition.
Hazard category: Electrical equipment and connections