Depressurized and non-inspected fire extinguisher has been identified inside the temporary material storage area near GH no 18. Action: CMA notified the issue to L & T site supervisor for corrective action. L & T to ensure all fire extinguisher are inspected and in good working condition.
Hazard category: Fire / explosion