Following deficiencies were observed at the site office DG area: - The earthing for DG has not been provided. - Cable was not routed properly - The enclosure of DG was found open  Site safety personnel was advised to ensure that the all standard requirements have been provided.
Hazard category: Electrical equipment and connections