Poor housekeeping and FOD issues have been identified in between building and temporary storage area beside GSE road from gate house-2, 3, 4and5. process waste and refusal were left unattended and cluttered.Poor storage of surplus electrical cables.Risk of workplace fires due to combustible materials. ACTION: Addressed the finding to TCA JV HSE person for immediate action. Contractor was advised to conduct a general housekeeping and timely removal of construction waste.
Hazard category: Housekeeping