a.	Electrical safety:  •	During inspection conducted for the Sub contractor temporary stores at site the ELCB was not functioning in the main distribution board. •	Unsafe chemical storage. JV advised to fix it, conduct re-inspection for the above and submit the evidence. b.	Fire and Emergency: •	Few fire extinguisher tags were not updated or inspected. JV to ensure the fire marshals of logistics department performs the fire tag inspections. c.	Environment:  •	During the Lamination of GRP pipe the operatives are not protected the area with polythene /other to collect the excess adhesive which leaking to the ground.
Hazard category: Chemical