Fire protection measures were missing from the energized rooms at MTBC and pantry in site office. Portable fire extinguishers provided at the site were not been inspected for the current month and operational instruction/ PASS signs were missing from them and the periodical service and maintenance by a Civil defense approved agency was not carried out/ validated on few of them. L&T to confirm the status of automated fire suppression arrangements in energized rooms and regular inspection, service and maintenance should be carried out on all the fire extinguishers.
Hazard category: Fire / explosion