Poor cable management was identified at corridor 374, near GH-10 area; Live electrical cables are laid across the access way without required protection and it obstruct the access; some of the cables were rooted under the metal door which poses potential to cause damage and electrocution to the metal door. ACTION: CMA addressed the issue to TCA JV concern supervisor and HSE person to provide temporary protection for the live cables and provide stopper to the metal door. TCA JV to rearrange the cable roots with required protection and conduct awareness training to all the responsible personnel to avoid the recurrence at the site.
Hazard category: Electrical equipment and connections