Zone B - Shaft No.28 found generator without grounding, db and breaker, connection to the de-watering motor given straightly from the generator which is dangerous and poor cable connection observed hence there is highest possibility untoward incident. DB with breaker to be provided for the generator, grounding, fire fighting arrangements and appropriate insulation to be provided for the cable at the earliest.
Hazard category: Electrical equipment and connections