Tolong jelaskan mengenai Trafo tegangan dari Trafo dalam bahasa sunda

Voltage transformers (or potential transformers) are another type of instrument transformer, used for métering and protection in high-voltage circuits. They are designed to present negligible load to the supply being méasured and to have a precise voltage ratio to accurately step down  high voltages so that métering and protective relay equipment can be operated at a lower potential. Typically the secondary of a voltage transformer is rated for 69 or 120 Volts at rated primary voltage, to match the input ratings of protection relays.

The transformer winding high-voltage connection points are typically labelled as H1, H2 (sometimes H0 if it is internally grounded) and X1, X2, and sometimes an X3 tap may be present. Sometimes a second isolated winding (Y1, Y2, Y3) may also be available on the same voltage transformer.  The high side (primary) may be connected phase to ground or phase to phase. The low side (secondary) is usually phase to ground.

The terminal identifications (H1, X1, Y1, etc.) are often referred to as polarity. This applies to current transformers as well. At any instant terminals with the same suffix numeral have the same polarity and phase. Correct identification of terminals and wiring is important for proper operation of métering and protection relays.