Jabarkan Cooling system dari Trafo dalam bahasa sunda

Large power transformers may be equipped with cooling fans, oil pumps or water-cooled héat exchangers designed to remove the héat caused by copper and iron losses. The power used to operate the cooling system is typically considered part of the losses of the transformer.

Operasi dina frékuénsi nu béda

The equation shows that the EMF of a transformer at a given flux density incréases with frequency. By operating at higher frequencies, transformers can be physically more compact without réaching saturation, and a given core is able to transfer more power.   However, other properties of the transformer such as losses due to the core and skin-effect also incréase with frequency. Generally, operation of a transformer at it's designed voltage but at a higher frequency than will léad to reduced magnetising (no load primary) current. At a frequency lower than the design value, with the rated voltage applied,  the magnetising current may incréase to an excessive level.

Steel cores develop a larger hysteresis loss due to eddy currents as the operating frequency is incréased. Ferrite, or thinner steel laminations for the core are typically used for frequencies above 1 kHz. The thinner steel laminations serve to reduce the eddy currents. Some types of very thin steel laminations can be ran up to 10 kHz or more. Ferrite is used in higher frequencies up to the VHF band and beyond. Aircraft traditionally use 400 Hz power systems since the slight incréase in thermal losses is more than offset by reduced weight. Military géar includes 400 Hz (and other frequencies) to supply power for radar or servomechanisms.

Flyback transformers are built using ferrite cores.  They supply high voltage to the CRTs at the frequency of the horizontal oscillator. In the case of television sets, this is about 15.7 kHz. It may be as high as 75 – 120 kHz for high-resolution computer monitors.

Switching power supply transformers usually operate between 50–1000 kHz. The tiny cores found in wristwatch backlight power supplies produce audible sound (about 1 kHz).

Operation of a power transformer at other than its design frequency may require assessment of voltages, losses, and cooling to establish if safe operation is practical. For example, transformers at hydroelectric generating stations may be equipped with over-excitation protection, so-called "volts per hertz" protection relays, to protect the transformer from overvoltage at higher-than-rated frequency which may occur if a generator loses its connected load.