Search query: ed219rbk
Product: Elitech WJL-6000 HVAC Leak Detector Halogen Gas Tester HVAC Refrigerant AC Sniffer R22 R410A R134A
Brand: Elitech
Color: Halogen Sensor WJL-6000
Description: General descriptions:

Incorporated with advanced leak detect technology. Elitech WJL-6000 is our new product with the stable function and small appearance; It’s an ideal and economic halogen leak detector.

Under normal working circumstance, the detector will beep when it is turned on.

It is different with the rapid sound of warning alarm.

Applications:

The WJL-6000 may also be used to:

Detect leaks in other systems and storage/recovery containers. It will respond to all halogenated (contains Chlorine of Fluorine) refrigerants.

This includes, but is not limited to:

CFCs e.g. R12, R11, R500, R503 etc..
.
HCFCs e.g. R22, R123, R124, R502 etc...

HFCs e.g. R134a, R404s, R125 etc...

Blends such as AZ-50. HP62. MP39 etc...

Detect Ethylene Oxide gas leaks in hospital sterilizing equipment (it will detect the halogenated carrier gas).

Detect SF-6 in high voltage circuit breakers.

Detect most gases that contain chlorine, fluorine and bromine (halogen gases).

Detect cleaning agents used in dry cleaning applications such as per chloroethylene.

Detect halogen gases in fire-extinguishing system.

Technical parameters:

Operating temperature: 0~52℃ (30℉ to 125℉)

Maximum sensitivity: 6 gr/yr, for all halogenated refrigerants

Battery life: Approximately 50 hours normal use

Response time: Instantaneous

Work mode: continuous, no limitation

Fixed probe length: 20cm

Unit dimensions: 1.37 x 1.37 x 5.90 in

Warm-up time: approximately 6 seconds

Reset time: two to ten seconds

Power supply: 6V DC four cell 7# excellent batteries
Highlights: Freon leak detector triggers on R22, R134A, R404a, R410A and all halogenated refrigerants including HFCs, CFCs,HCFCs and blends.
Response within 3 seconds; Warm up in 6 seconds.
7 Adjustable Sensitivity; Maximum sensitivity is 0.21oz/yr.
Audible and visual gas leakage indicators and dual battery indicator.
A flexible probe around 7.9-inch allows detections in difficult and hard-to-reach areas. 24/7 US Technician Support via Email and Phone.
ESCI relevance label: I