TCVN3890:2023

Extinguishant Fire-fighting efficiency by fire class A B C D A1 A2 B1 B2 D1 D2 D3 Water ++ - - - Foam, water-based extinguishant Water-based extinguishant ++ + - - High expansion foam concentrate + - ++ + - - Low and medium expansion foam concentrate + + ++ + - - Gas CO 2 - + + - Nitrogen, HFC-227ea, Inergen, Argon, FK 5-1-12, etc. + + + - Powder BC powder - ++ ++ - ABC powder + - ABCD powder ++ - Aerosol + + + - NOTE: Fire is classified according to TCVN 4878 and TCVN 5760. “++” means Very effective. “+” means appropriate for fire extinguishing. “-” means inappropriate for fire extinguishing. BC powder is used to extinguish class B and C fires. ABC powder is used to extinguish class A, B and C fires. ABCD powder is used to extinguish class A, B, C and D fires. - Gaseous extinguishants are only used in areas where the extinguishing concentration is maintained for the specified hold time in accordance with TCVN 7161-1, TCVN 6101 and TCVN 13333. CO 2 extinguishant is only used in normally unoccupied areas. 4.5 When the renovation is carried for the purpose of scale increase or repurposing or the fire hazard and explosion class of the rooms, buildings and constructions are changed in a manner that increases the fire hazard of such rooms, buildings and constructions, this standard shall be applied accordingly. 4.6 The whole building should be equipment with an automatic fire extinguishing system if the total area of the building’s rooms subject to automatic fire extinguishing system equipment is 40% or more of the total floor area of that building. 4.7 If the building’s rooms belonging to functional fire hazard class F5 (excluding F5 rooms in the building belonging to other functional fire hazard category, the automatic fire extinguishing system have been equipped with an automatic fire extinguishing system inter-connected with the fire alarm control panel, automatic fire detectors are not required to be installed (other equipment of the automatic fire alarm system must be installed according to regulations). 4.8 Buildings and constructions must be equipped with fire protection equipment and systems by relying on the analysis of their functions, nature of fire hazards and other factors related to the protection of people and property. Buildings and constructions other than those specified in Annexes A, B, C, D, E, F and G are required to be equipped with fire protection equipment and systems which are the same as those intended for buildings and constructions of similar purposes. 4.9 Automatic fire alarm systems or devices intended for buildings must be connected to the fire database management system and incident reporting system of the fire police authority according to regulations [9], [10]. 4.10 When determining the equipment of an automatic fire extinguishing system and/or automatic fire alarm system, select an appropriate system for the entire building first (Table A.1), then for each item/area (Table A.2) and rooms in the building (Table A.3) as well as equipment located within a construction (Table A.4). 4.11 The buildings not divided or divided into rooms by frame structures: walls and floors with a fire-resistance rating less than REI 45, partitions with a fire-resistance rating less than REI 45 shall be equipped with an automatic fire alarm system and/or automatic fire extinguishing system corresponding to the room according to Table A.3. 4.12 In the buildings and constructions specified in Annex A must be equipped with an automatic fire extinguishing system and/or automatic fire alarm system, apart from the premises: ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 - Rooms of class D of fire hazard; - Single-loaded corridors; - Stairwells; - Pressurizes fire protection vestibules; - Areas in which there are no fire hazards. 4.13 Apartments of buildings belonging to F1.3 category with a height of no more than 75 m are only required to be equipped with sprinklers of the water automatic fire extinguishing system at the door of the apartments (installed inside the apartment). 4.14 Fire protection equipment and systems specified in this standard must be inspected and maintained on a periodic basis in compliance with regulations of law and related applicable technical regulations or instructions of the manufacturer. 4.15 In some specific cases, several requirements of this standard applicable to specific constructions may be replaced when there is a technical justification for complementary and alternative solutions and grounds of those solutions to ensure fire safety of the constructions. This justification must be approved by the ministerial fire authority. 5 Regulations on Equipment and installation of fire protection equipment and systems. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.1.1 Equipment and installation of portable and wheeled fire extinguishers. 5.1.1.1 All areas in buildings and constructions, including areas equipped with fire extinguishing systems, must be equipped with portable or wheeled fire extinguishers. 5.1.1.2 The selection, equipment and installation of fire extinguishers shall comply with the regulations laid down in Articles 6 and 7 of TCVN 7435-1. 5.1.1.3 For narrow and long areas or areas with different and adjacent floor levels, a fire extinguisher must be installed so that the travel distance from the position of a fire extinguisher to the farthest point to be protected does not exceed that specified in 5.1.1.2. 5.1.1.4 On the same floor or storey, if the premises is separated into different areas by walls, partitions or other obstacles without any passage-way, fire extinguishers must be installed separately in accordance with 5.1.1.2 and 5.1.1.3. 5.1.1.5 The number of fire extinguishers reserved must not be less than 10% of the total number of fire extinguishers intended for replacement where necessary (no more than 100 of each type). 5.1.1.6 Fire extinguishers must be placed in conspicuous and easily accessible locations and should be red. If it is difficult to identify them, signs that show their locations may be used and the regulations set out Article 5 of TCVN 7435-1 shall be complied with. Fire extinguishers must not be placed in a single location, except for the case where they are placed in a storage area in accordance with 5.1.1.5. Fire extinguishers should be always available for immediate use and located: a) where they will be readily seen by any person following an escape route; ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 c) in similar positions on each floor, where floors are of similar appearance. Fire extinguishers should not be located: a) where a potential fire might prevent access to them; b) close to heating appliances that might affect quality and efficiency of the extinguishers; c) in concealed positions behind doors, in cupboards or deep recesses; d) where they might cause obstruction to exit routes; e) in positions in rooms or corridors away from exit routes unless they are necessary to cover a particular hazard; f) where they might be damaged by daily activities. 5.1.1.7 Portable and wheeled fire extinguishers must have the functions and meet the specifications specified in TCVN 7026 and TCVN 7027. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.1.2.1 Hanging type automatic diffusion dry-powder fire extinguishers must conform to TCVN 12314-1. 5.1.2.2 Based on the actual conditions of buildings and constructions, they may be wall or ceiling mounted with an appropriate height to effectively cover the area to be protected as announced by the manufacturer. In any case, the distance from the temperature sensor to the ceiling should not exceed 40 cm. 5.1.2.3 Hanging type automatic diffusion dry-powder fire extinguishers may be installed in kitchen areas of restaurants, boiler rooms and laundry areas with an area not exceeding 100 m 2 . If installed in an area of more than 100 m 2 , it is recommended that such area be divided into the areas by a fire separating wall (with a fire-resistance rating at least REI 45) or a fire separating partition (with a fire-resistance rating at least EI 45), each of which must not exceed 100 m 2 . 5.1.3 Equipment and installation of automatic activated fire extinguishers - fire suppression cylinders 5.1.3.1 Automatic activated fire extinguishers - fire suppression cylinders must conform to TCVN 12314-2. 5.1.3.2 An automatic gas fire extinguishing system may be replaced with an automatic activated fire extinguisher - fire suppression cylinders (design it in such a way that the discharge monitoring function is added and discharge signals are transmitted to the fire alarm control panel) in normally unoccupied areas with an area not exceeding 100 m 2 . If installed in an area of more than 100 m2, it is recommended that such area be divided into the areas by a fire separating wall (with a fire-resistance rating at least REI 45) or a fire separating partition (with a fire-resistance rating at least EI 45), each of which must not exceed 100 m 2 . 5.2 Equipment and installation of automatic fire alarm systems and local fire alarms devices. 5.2.1 The list of buildings; items/areas; rooms and equipment to be protected by automatic fire alarm systems and local fire alarms devices is provided in Annex A. 5.2.2 The selection and equipment of local fire alarms devices shall be carried out as similar devices of an automatic fire alarm system. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.3 Equipment and installation of automatic fire extinguishing systems and equipment. 5.3.1 The list of buildings; items/areas; rooms and equipment subject to equipment and installation of automatic fire extinguishing systems and equipment is provided in Annex A. NOTE: Automatic activated fire extinguishing equipment includes automatic diffusion fire extinguishers - hanging type dry powder fire extinguishers and automatic activated fire extinguishers - fire suppression cylinders. 5.3.2 Extinguishants used in automatic fire extinguishing systems must have fire-fighting efficiency suitable for any type of fire of area to be protected as prescribed in Article 4.3 and in accordance with the requirements for protection. 5.3.3 Upon installation of an automatic fire extinguishing system that discharges an extinguishant which is dangerous to humans, it is required to determine the escape time to ensure the last person to escape the room or area to be protected before the automatic system releases the extinguishant. Other regulations on selection and installation of automatic fire extinguishing systems are enshrined in TCVN 5760, TCVN 6101, TCVN 6305, TCVN 7161, TCVN 7336, TCVN 13333 and other related Vietnam standards issued by the supervisory Ministry. 5.4 Equipment and installation of indoor hose reel systems and outdoor fire fighting water supply systems. 5.4.1 Equipment and installation of indoor hose reel systems. 5.4.1.1 Buildings must be equipped with indoor hose reel systems specified in Annex B. 5.4.1.2 Indoor hose reel systems of production buildings, warehouses with high fire hazard, buildings with a height of 25 m or more, markets, shopping malls, supermarkets, hotels, discotheques, karaoke businesses, bars, night clubs, railway stations, seaport service buildings, inland port service buildings, theaters and cinemas must regularly have water which is maintained at a pressure that facilitate automatic activation of such systems. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.4.1.4 The indoor hose reel system shall not be equipped in buildings, areas and rooms that use or store substances which, in contact with water, may cause fire, explosion or widespread flame. 5.4.2 Equipment and installation of outdoor fire fighting water supply systems. 5.4.2.1 Outdoor fire fighting water supply systems shall be equipped according to the regulations set out in Annex C. 5.4.2.2 Where the fire hydrants can cover any point of a building or construction along its width and cover radius of each hydrant which does not exceed 200 m along the path of travel of the fire hoses outside the building, from the fire hydrant or water intake area of ponds, lakes, rivers or public water tanks, if: - The flow rate and volume of fire fighting water are achieved according to regulations, the outdoor fire fighting water supply system is not required. - The flow rate and volume of fire fighting water are not achieved according to regulations, the outdoor fire fighting water supply system is required (when calculating the flow rate of the outdoor fire fighting water supply system, it is permissible to combine different water sources). 5.4.2.3 The combination of the outdoor fire fighting water supply systems and the domestic and production water supply system is permitted. 5.5 Installation and equipment of fire-fighting vehicles. 5.5.1 Warehouses, airports, seaports, key economic, political and social - cultural establishments, industrial parks, export-processing zones, hi-tech zones and industrial clusters shall, in addition to the fire extinguishing system, be equipped with fire-fighting vehicles according to TCVN 13316 Fire protection - Fire fighting vehicles (all parts), national standards, international and foreign standards permitted for application in Vietnam. The minimum number of fire-fighting vehicles to be equipped is prescribed in Annex D. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 a) have specifications and performance relevant the type of buildings and constructions to be protected; b) have extinguishants, attached instruments and equipment in accordance with regulations; c) Portable fire pumps must meet the technical specifications specified in TCVN 12110. 5.6 Equipment and installation of rudimentary demolition facilities and tools; filter masks and self-contained breathing apparatus 5.6.1 Equipment and installation of rudimentary demolition facilities and tools. 5.6.1.1 Buildings and constructions must be equipped with rudimentary demolition facilities and tools specified in Annex E. 5.6.1.2 Rudimentary demolition facilities and tools for buildings and constructions must be located in the area dedicated for storing fire-fighting equipment. 5.6.2 Equipment and installation of filter masks and self-contained breathing apparatus. 5.6.2.1 Buildings and constructions must be equipped with filter masks and self-contained breathing apparatus specified in Annex F. It is recommended that other buildings and constructions such as apartment buildings, hospitals, offices, theatres, cinemas, etc. be equipped with filter masks. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.6.2.3 Filter masks must have filters in accordance with applicable standards and technical regulations [19]. Self-contained breathing apparatus must have a full face mask that meets the requirements specified in TCVN 13332. 5.7 Equipment and installation of emergency and exit lighting equipment; public address and evacuation instruction systems. 5.7.1 Equipment and installation of emergency and exit lighting equipment. 5.7.1.1 Equipment and installation of emergency and exit lighting equipment shall be equipped in all buildings and constructions (except for single-family homes) 5.7.1.2 The selection and installation of emergency and exit lighting equipment are specified in TCVN 13456. 5.7.2 Equipment and installation of public address and evacuation instruction systems 5.7.2.1 Buildings and constructions must be equipped with public address and evacuation instruction systems specified in Annex G. 5.7.2.2 Public address and evacuation instruction systems shall be such that all occupants in buildings and constructions could clearly hear the alarm and instructions in case of emergency. 5.7.2.3 Audible signals of public address and evacuation instruction systems must have a total sound level (sound level of the continuous noise together with the sound from the warning signals generated) of at least 75 dBA at 3 m distance from the alarm signal, but no more than 120 dBA in any position. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.7.2.5 In a sleeping room, audible signals of public address and evacuation instruction systems shall produce a sound level at least 15 dBA above the sound level of the continuous noise in the room but the total sound level must be at least 70 dBA and no more than 120 dBA. The sound level shall be measured at the head pillow level. 5.7.2.6 Wall-mounted fire alert loudspeakers and evacuation alert control equipment must be arranged such that their upper part is at least 2.3 m from the floor and at least 0.15 m from the ceiling. 5.7.2.7 In areas where people are protected by noise cancellation devices and rooms where the noise exceeds 95 dBA, the public address and evacuation instruction systems must include light alarm. The use of flashing alarm equipment is permitted. 5.7.2.8 Voice alert loudspeakers and evacuation equipment must produce a sound with a frequency in the range from 200 Hz to 5 000 Hz. 5.7.2.9 The number of voice alert loudspeakers and evacuation equipment, their installation and capacity shall be such that the sound level in all areas conforms to the regulations enshrined in this standard. 5.8 Installation and equipment of initial fire fighting facilities. 5.8.1 Initial fire fighting facilities for warehouses, shops and production facilities are specified in Annex H. 5.8.2 Initial fire fighting facilities for petroleum and petroleum products terminals, filling stations, petroleum storages, terminals and pipelines, and LPG stations are specified in TCVN 5307, TCVN 4530, TCVN 5684, TCVN 6223 and other related Vietnam standards issued by the supervisory Ministry. 5.8.3 For other facilities, the equipment of initial fire fighting facilities shall depend on the conditions and requirements of each facility. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.8.5 Initial fire fighting facilities should be painted red. Annex A (normative) Equipment of automatic fire alarm systems, local fire alarms devices and automatic fire extinguishing system Table A.1 - For buildings No. Type of building Automatic fire extinguishing system (1) ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1. Single-family homes With height of 25 m or more 7 storeyed or more or 25 m or more high (equipment of local fire alarms devices is permitted) 2. Single-family homes not more than 30% of the area of which is used for trading and/or production of highly flammable goods and substances (2) With height of 25 m or more 3 storeyed or more or with volume of 1 500 m 3 or more (equipment of local fire alarms devices is permitted if the house has fewer than 5 storeys and a volume of less than 2 500 m 3 ) 3. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With height of 25 m or more or area of 5 000 m 2 or more 3 storeyed or more or with volume of 1 500 m 3 or more (equipment of local fire alarms devices is permitted if the building has fewer than 5 storeys and a volume of less than 1 500 m 3 ) 4. Apartment buildings, tenements; dorm With height of 25 m or more or area of 10 000 m 2 or more 5 storeyed or more or with volume of 2 500 m 3 or more (equipment of local fire alarms devices is permitted if the building has fewer than 5 storeys and a volume of less than 5 000 m 3 ) 5. Buildings for provision of accommodation services (inns); hotels, motels and accommodation establishments founded according to regulations [1] (except for camping sites) With height of 25 m or more or area of 5 000 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 6. Nursing homes, people with disabilities-care institutions Regardless of scale Regardless of scale (equipment of local fire alarms devices is permitted if the building has fewer than 3 storeys and a volume of less than 1 000 m 3 ) 7. Nurseries , kindergartens, preschools 4 storeyed or more (excluding the topmost technical floor) With 100 children or more or with volume of 1 000 m 3 or more (equipment of local fire alarms devices is permitted if the height is less than 15 m and the volume is less than 1 500 m 3 ) 8. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With height of 25 m or more 5 storeyed or more or with volume of 5 000 m 3 or more (equipment of local fire alarms devices is permitted if the volume is less than 2 000 m 3 ) 9. Air traffic control towers, airport terminals, railway terminals, gondola lift waiting lounges, seaport, inland port and inland waterway ports service buildings, bus stations, rest stops With height of 25 m or more or area of 10 000 m 2 or more Regardless of scale. (equipment of local fire alarms devices is permitted if the building has fewer than 3 storeys and the volume is less than 1 000 m 3 ) 10. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With height of 25 m or more or area of 5 000 m 2 or more 3 storeyed or more or with volume of 1 500 m 3 or more 11. Cultural centers, event centers With height of 25 m or more or area of 5 000 m 2 or more 3 storeyed or more or with volume of 1 500 m 3 or more 12. Book storage buildings; libraries With height of 25 m or more or area of 5 000 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 13. Food and beverage stores, beauty salons, massage service buildings; building blocks of amusement parks, aquariums With height of 25 m or more or area of 5 000 m 2 or more With volume of 1 000 m 3 or more (equipment of local fire alarms devices is permitted if the building has fewer than 3 storeys and volume of less than 1 500 m 3 ) 14. Sports stadiums, sports palaces With height of 25 m or more With volume of 1 500 m 3 or more or 200 seats or more (equipment of local fire alarms devices is permitted if the volume is less than 5 000 m 3 ) 15. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With height of 25 m or more or area of 2 000 m 2 or more 3 storeyed or more or with volume of 1 000 m 3 or more 16. Administrative buildings 3) With height of 25 m or more or area of 5 000 m 2 or more 5 storeyed or more or with a volume of 1 500 m 3 or more (equipment of local fire alarms devices is permitted if the building has fewer than 5 storeys and volume of less than 5 000 m 3 ) 17. Electronics stores, department stores, convenience stores and stores for sale of highly flammable goods and substances 4) 17.1. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 200 m 2 or more Regardless of scale 17.2. Situated on the ground With height of 25 m or more or area of 3 500 m 2 or more 3 storeyed or more or with a volume of 1 000 m 3 or more (equipment of local fire alarms devices is permitted if the building has fewer than 5 storeys and volume of less than 1 500 m 3 ) 18. Commercial buildings 5) (except for car showrooms), theatres, cinemas, circuses 18.1. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 200 m 2 or more Regardless of scale 18.2. Situated on the ground 18.2.1. One storeyed, two storeyed With area of 3 500 m 2 or more Regardless of scale 18.2.2. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of scale Regardless of scale 18.3. Buildings for sale of flammable and highly flammable liquids (except for goods contained in cans and bottles with a capacity of not more than 20 liters) Regardless of scale Regardless of scale 19. Buildings in section 3, sections 10 to 18 of this table at fire resistance level IV-V With area of 1 200 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 20. Karaoke, discotheque, bar and night club service buildings 20.1. Situated in basement or semibasement Regardless of scale Regardless of scale 20.2. Situated on the ground 20.2.1. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 500 m 2 or more Regardless of area 20.2.2. Three storeyed or more Regardless of area Regardless of area 21. Religious buildings With height of 25 m or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 22. Museums, exhibition buildings 22.1. Situated in basement or semibasement With area of 200 m 2 or more Regardless of scale 22.2. Situated on the ground 22.2.1. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 1 000 m 2 or more Regardless of scale 22.2.2. Three storeyed or more Regardless of scale Regardless of scale 23. Fire stations and brigades With height of 25 m or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 24. Car and moped garages and showrooms 6) 24.1. Of enclosed type 24.1.1. Situated in basement or semi-basement or on the ground, 02 storeyed or more Regardless of area Regardless of area 24.1.2. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 24.1.2.1. Fire resistance levels I, II and III of S0 grade structural fire hazard With area of 7 000 m 2 or more Regardless of area 24.1.2.2. Fire resistance levels I, II and III of S1 grade structural fire hazard With area of 3 600 m 2 or more Regardless of area 24.1.2.3. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 3 600 m 2 or more Regardless of area 24.1.2.4. Fire resistance level IV of S1 grade structural fire hazard With area of 2 000 m 2 or more Regardless of area 24.1.2.5. Fire resistance level IV of S2 and S3 grades structural fire hazard With area of 1 000 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 24.1.3. Automated parking garages Regardless of scale - 24.2. Of exposed type 7) 24.2.1. Distance from any point to the excluded side: no more than 12 m - ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 24.2.2. Distance from any point to the excluded side: more than 12 m With area of 4 000 m 2 or more or volume of 15 000 m 3 or more or 3 storeyed or more Regardless of area 25. Cattle and poultry farms 8) - With area of 10 000 m 2 or more 26. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 1 000 m 2 or more With area of 500 m 2 or more 27. Warehouses of fire hazard class C with goods on racks > 5.5 m high Regardless of scale Regardless of scale 28. Warehouses of fire hazard class B and C with 2 storeys or more Regardless of scale ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 NOTES: 1) A building having 2 or more functions is not required to be equipped with an automatic fire extinguishing system as specified in Table A.1 but any functional part of the building whose scale is required to be equipped with an automatic fire extinguishing system according to Table A.1 must be equipped with an automatic fire extinguishing system. When karaoke, discotheque, bar or night club business is conducted in a building of other purpose but the part intended for karaoke, discotheque, bar or night club business of the building whose scale is required to be equipped with an automatic fire extinguishing system according to Table A.1 or intended for karaoke, discotheque, bar or night club business is situated on the third storey or more, the whole building must be equipped with an automatic fire extinguishing system. 2) Only an automatic fire alarm systems or local fire alarms device may be equipped in the business and production area, however, on each storey of the building, there must be an audio warning device that is connected with the automatic fire alarm system or local fire alarm device. 3) Administrative buildings include premises of regulatory authorities at all levels, office buildings of enterprises and socio - political organizations. 4) Stores for sale of highly flammable goods and substances include stores for sale of furniture, clothing, bedding, books, votive papers and stores of a similar nature. 5) Commercial buildings include markets, supermarkets and shopping malls. An automatic fire extinguishing system is not required to be installed in storage and processing areas for the sale of meat, fish, fruits and vegetables (in non-flammable packaging), pots and pans, non-flammable equipment, goods and materials. 6) Automatic fire extinguishing is not mandatory in underground single-storey garages built on open ground and capable of up to 25 parking spots; ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Automatic fire extinguishing and fire alarm systems are not required to be equipped in buildings for moped storage and display which have no more than 02 storeys and an area of no more than 1 000 m 2 . 7) Exposed buildings mean those not covered externally by walls. A building is also considered to be exposed if two of its longest facing sides are excluded. A side is considered to be excluded if the total excluded area along it accounts for at least 50% of its external area on each level. 8) Automatic fire extinguishing and fire alarm systems are not required to be equipped in exposed buildings for cattle and poultry breeding and buildings for processing and storage of granular agricultural products. Table A.2 – For items/areas No. Items/areas Automatic fire extinguishing system Automatic fire alarm system 1. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of scale Regardless of scale 2. Cable structures 1) of electrical substations (exclusive of cables placed outside buildings and constructions) 2.1. With voltage of 500 kV or higher Regardless of scale Regardless of scale 2.2. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 - Regardless of scale 3. Cable structures 1) of electrical substations with voltage of 110-220kV (exclusive of cables placed outside buildings and constructions) having transformers with capacity: 3.1. 63 MVA or more Regardless of scale Regardless of scale 3.2. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 - Regardless of scale 4. Cable cellars of production buildings and civil buildings where cables or conductors with voltage of 220 V or more is laid: 4.1. Cellar volume more than 100 m 3 12 strands or more 5 strands or more 4.2. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 - 5 strands or more 5. Closed conveyors transporting highly flammable materials With height of 25 m or more With height of 25 m or more 6. The space above the false ceiling or under the raised floor of the areas 2) in rooms and buildings equipped with automatic fire extinguishing systems and/or automatic fire alarm systems 3) has: 6.1. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area and volume Regardless of area and volume 6.2. Cable trays (cable bundles) with voltage of 220V or more and total volume of flammable substances Ch2-Ch4 is 0.007 m 3 /meter in length or more Regardless of area and volume Regardless of area and volume 6.3. Cable trays (cable bundles) with voltage of 220V or more and total volume of flammable substances Ch2-Ch4 is 0.0015 m 3 /meter in length to less than 0.007 m 3 /meter in length - ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 NOTES: 1) Cable structures covered by this standard include cellars, tunnels, wells, raised floors, enclosed troughs and chambers for laying cables (including cooperation with other utilities). 2) Areas which satisfy the requirements set out in 6.1, 6.2 and 6.3 of this table include: - Escape corridors, halls, lobbies; - Rooms that have 50 persons or more; - Rooms of functional fire-hazard classes F1.1 and F4.1 and karaoke, discotheque, bar and night club services. Irrigators and fire detectors may be located in positions of technical pipelines and/or cable trays in the space above the suspended ceiling. 3) Cable structures located above the suspended ceiling and under the raised floor are not required to be equipped with automatic fire extinguishing and alarm systems (except for 1 to 3 of this table). To be specific: - Cables which are threaded onto conduits or sheathed with a non-flammable or flammable material Ch1; ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Table A.3- For rooms No. Protected objects Automatic fire extinguishing system Automatic fire alarm system 1. Storerooms 1.1. Belonging to class A and B fire hazards ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area 1.2. For rubber, resin beads; matches, alkali metals, pyrotechnic products; wool, fur; other flammable substances with small density (less than 3 kg/m 3 ) Regardless of area Regardless of area 1.3. Containing non-flammable goods but stored in flammable packaging (with fire load density 1 MJ/m 2 to 180 MJ/m 2 ) - With area of 300 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Belonging to class C fize hazard (excluding rooms mentioned in 1.2 and 1.3 of this table) when situated: 1.4.1. In basement or semibasement Regardless of area Regardless of area 1.4.2. On the ground With area of 300 m 2 or more With area of 300 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Cold stores - With area of 300 m 2 or more 2. Production rooms 2.1. Belonging to class A and B fire hazards With area of 300 m 2 or more Regardless of area ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Belonging to class C fize hazard (excluding rooms located in buildings and facilities for processing and storage of granola agricultural products) when situated: 2.2.1. In basement or semibasement Regardless of area Regardless of area 2.2.2. On the ground With area of 1 000 m 2 or more With area of 300 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Rooms for production of highly flammable liquids: solvents, paints, glues, mastics, impregnation compounds, synthetic rubber; rooms for production of aluminum powder suspension, rubber adhesives; rooms for paints, synthetic rubber, compressor rooms using gas turbines, petroleum and diesel heating rooms Regardless of area Regardless of area 3. Communication rooms 3.1. Ventilation rooms, transformer rooms, separating device rooms of broadcast stations with capacity of 150 kW or more, receiving stations with the number of at least 20, fixed stations of space communications with capacity of more than 1 kW, television relay stations with capacity of 25-50 kW, network nodes, inte-city and inter-provincial telephone exchanges, telegraph stations, terminal amplifying stations and regional communication centers ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area 3.2. Maintenance-free and maintained without the evening and night ships: technical workshops of terminal amplifying stations, intermediate relay stations, transmitting and receiving radio stations Regardless of area Regardless of area 3.3. Maintenance-free base stations of cellular mobile radio systems and maintenance-free relay stations of cellular mobile radio systems With area of 24 m 2 or more Regardless of area ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Digital switchboard rooms, telephone control centers; computation centers of post offices of provinces and cities with total volume of buildings: 3.4.1. 40 000 m 3 or more With area of 24 m 2 or more Regardless of area 3.4.2. Less than 40 000 m 3 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area 3.5. ATS sites where switching equipment of electronic or quasi-electronic type is installed together with ECM, used as a control complex, input-output devices; premises of electronic switching stations, networks, document electric communication centers with a capacity of: 3.5.1. 10 000 numbers, channels or connection points or more Regardless of area Regardless of area ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Fewer than 10 000 numbers, channels or connection points - Regardless of area 3.6. Dedicated rooms for dividing and connecting equipment using computers to control automatic telephone exchanges with station capacity: 3.6.1. 10 000 inter-provincial and inter-city channels or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area 3.6.2. Fewer than 10 000 inter-provincial and inter-city channels - Regardless of area 3.7. Rooms for processing, sorting, storage and delivery of dispatches, correspondence and printed media With area of 500 m 2 or more Regardless of area ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Transport rooms 4.1. Rooms and compartments for production, repair and fabrication of trains, electric trains, ships (electrical machines, equipment, repair and fabrication of wagons, wheels, engines, etc.) With area of 1 000 m 2 or more With area of 300 m 2 or more 4.2. Rooms and component constructions of the subway system (except for aisles and passenger lounges, subway tunnels, water pumping stations, heating equipment, ventilation chambers) ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area 4.3. Rooms for repair, maintenance and storage of automobiles 4.3.1. Chambers for repair, maintenance and storage of automobiles With area of 700 m 2 or more With area of 300 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Rooms for storage of automobiles in buildings of other purpose (except for homes) situated: 4.3.2.1. Above ground 3 automobiles or more Regardless of area 4.3.2.2. In basement or semi-basement (even under bridge) ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area 4.4. Rooms for disassembling and assembling aircraft engines, flying equipment, chassis and wheels for airplanes and helicopters; rooms for production and repair of aircraft engines Regardless of area Regardless of area 5. Rooms of public purposes 5.1. Storage rooms in libraries and archives with the number of documents and books: ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.1.1. 250 000 units or more Regardless of area Regardless of area 5.1.2. Fewer than 250 000 units - With area of 300 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Display and exhibition rooms 3) With area of 1 000 m 2 or more With area of 500 m 2 or more 5.3. Rooms for storage and display of museum values 3) Regardless of area Regardless of area 5.4. In cultural and entertaining buildings (theaters, clubs, concert and film and concert halls, event venues, cultural houses, circuses, studios, etc.) having stages and auditoriums: ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 5.4.1. With seating capacity of 700 seats or more 4) Regardless of area Regardless of area 5.4.2. With seating capacity of 400 seats or more and stage area of 100 m 2 or more 4) Regardless of area Regardless of area ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Warehouses for ornaments, utensils and props With area of 100 m 2 or more With area of 100 m 2 or more 5.5. Studios With area of 1 000 m 2 or more With area of 300 m 2 or more 5.6. Rooms for storage of cash in banks and treasuries ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of area 5.7. Rooms for storage of hand baggage, flammable materials in buildings stations (including air terminals) situated: 5.7.1. In basement or semibasement Regardless of area Regardless of area 5.7.2. On the ground ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 300 m 2 or more 5.8. Chambers and rooms for storage of flammable materials located: 5.8.1. Under tribunes of any capacity in the indoor sports facilities With area of 100 m 2 or more With area of 100 m 2 or more 5.8.2. In buildings of indoor sports facilities with a capacity of 800 spectators or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 100 m 2 or more 5.8.3. Under tribunes with capacity of 3 000 spectators or more in outdoor sport facilities With area of 100 m 2 or more With area of 100 m 2 or more 5.9. Dedicated server rooms With area of 24 m 2 or more With area of 24 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Trade rooms in buildings of other purposes: 5.10.1. In basement or semibasement With area of 200 m 2 or more Regardless of area 5.10.2. Above ground With area of 500 m 2 or more With area of 500 m 2 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Rooms for sale of flammable and highly flammable liquids (except for goods contained in cans and bottles with a capacity of not more than 20 liters) Regardless of scale Regardless of scale NOTES: 1) An automatic fire extinguishing system is not required to be installed in the entire room in case it has been equipped with an automatic fire alarm system and all electrical and electronic equipment (including equipment of the automatic process control system) are protected by automatic fire extinguishing installations according to national standards, international and foreign standards permitted for application in Vietnam. 2) In order to protect these rooms, the automatic fire extinguishing system must not cause damage or malfunction to the equipment even if it is accidentally activated. 3) This requirement does not apply to rooms used for temporary exhibitions. When placing cars in the exhibition and trade rooms, these premises must be equipped with an automatic fire extinguishing system in accordance with 5.3 and 5.11 of this table. The area of the rooms specified in this Table is understood as the area of a part of the building surrounded by fire barriers with fire-resistance rating: walls, floors and partitions - at least El 45. Where the rooms are separated by structures with fire-resistance rating less than El 45, the area of the rooms is the total area of these rooms and the functional part of the room to which the highest equipment requirements apply shall be taken into account in accordance with regulations of this Annex. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Table A.4. For equipment No. Protected objects Automatic fire extinguishing system Automatic fire alarm system 1. Paint shops with highly flammable or flammable liquids Regardless of type Regardless of type ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Drying chambers Regardless of type Regardless of type 3. Collectors (hoppers) for collection of combustible waste 1) Regardless of type Regardless of type 4. Oil power transformers: ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With voltage of 500 kV or more Regardless of power Regardless of power 4.2. With voltage of 220 kV 200 MVA or more Regardless of power 4.3. With voltage of 110 kV, installed in power plants ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 63 MVA or more 4.4. With voltage of 110 kV, installed in chambers of electrical substations 63 MVA or more Regardless of power 5. Transformers located in rooms of buildings of other purpose (exclusive of those in section 4 of this table) 63 MVA or more or 110 KV or more Regardless of power ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Test stations of mobile power stations and units with diesel and petrol-electric generating set assembled on trucks and trailers Regardless of area - 7. Tanks for highly flammable liquids located above ground 3 m 3 or more - NOTES: 1) Automatic fire extinguishing system may be replaced with automatic fire extinguishing system. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 "-" in the tables in Annex A indicates that it is not mandatory to be equipped with an automatic fire alarm/automatic fire extinguishing system (except for rooms, areas/items located buildings subject to protection by the automatic fire alarm/automatic fire extinguishing system according to Table A.1). Annex B (normative) Equipment of indoor hose reel systems Table B.1 - Equipment of indoor hose reel systems No. Type of building or construction Scale ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Homes and public constructions 1.1. Single-family homes 7 storeyed or more 1.2. Apartment buildings, tenements, dorms, hotels, guest houses, motels, inns and accommodation establishments founded according to regulations [1] (except for camping sites); multi-function buildings 1) 5 storeyed or more or 5 63 MVA or with volume of 5 000 m 3 or more 1.3. Premises of regulatory authorities at all levels, office buildings of enterprises, socio - political organizations, post offices, radio and television stations, telecommunications facilities, communication equipment installations, data management and storage centers ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1.4. Theaters, cinemas, circuses, halls 300 seats or more or with volume of 10 000 m 3 or more 1.5. - Amusement parks, zoos, aquariums. - Museums, exhibition buildings, art galleries, archive buildings, fair buildings, cultural buildings, religious buildings. - Stadiums, sports stadiums, indoor sports palaces, fitness and sports centers, race tracks, shooting ranges and other sports facilities established in accordance with applicable laws [6], [8], - Motor vehicle registries, stores for sale, repair and maintenance of automobiles, motorcycles and mopeds. 6 storeyed or more or with volume of 5 000 m 3 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Karaoke, discotheque, bar and night club service buildings 1.6.1. Situated in basement or semi-basement Regardless of scale 1.6.2. Situated above ground 1.6.2.1. One or two storeyed ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1.6.2 2. Three storeyed or more Regardless of area 1.7. Event centers, markets, supermarkets, shopping malls Regardless of scale 1.8. People with disabilities-care institutions Regardless of scale ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Air traffic control towers, airport terminals, railway terminals; gondola lift waiting lounges; seaport, inland port and inland waterway ports service buildings, bus stations, rest stops 6 storeyed or more or with volume of 5 000 m 3 or more 1.10 Schools and educational institutions (except for nurseries); buildings for medical examination and treatment and patient dormitories of hospitals, health stations, clinics, sanitariums, rehabilitation and orthopedic centers, centers for disease control and prevention, health centers, other health facilities according to applicable regulations [3] 3 storeyed or more or with volume of 2 000 m 3 or more 1.11 Nurseries, kindergartens, preschools 100 children or more or with volume of 3 000 m 3 or more or 03 storeyed or more 1.12 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With volume of 5 000 m 3 or more 1.13 Restaurants, food and beverage stores 5 storeyed or more or with volume of 5 000 m 3 or more 2. Production buildings, warehouses With area of 500 m 2 or with volume of 2 500 m 3 or more 3. Car and moped garages and showrooms, premises for car and moped maintenance ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Of enclosed type With volume of 500 m 3 or more 3.2. Of exposed type (except for automated parking garages) With volume of 3 000 m 3 or more NOTES: 1) A multi-function building is not subject to protection by an indoor hose reel system but any of its functional part whose scale is subject to protection by an indoor hose reel system according to Table B.1, such functional part must be equipped with the indoor hose reel system. If a multi-function building has a functional part used for provision of karaoke, discotheque, bar or night club service on the third floor or more, it is required to be equipped with an indoor hose reel system. Annex C ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Equipment of outdoor hose reel systems Table C.1 - Equipment of outdoor hose reel systems No. Type of building or construction Scale 1. Urban areas, economic zones, industrial parks, industrial clusters, export-processing zones, hi-tech zones and other dedicated areas in accordance with applicable regulations subject to approval by a district or higher-level authority [5] Regardless of scale 2. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of scale 3. Premises of regulatory authorities at all levels, office buildings of enterprises, socio - political organizations, cultural buildings, religious buildings 6 storeyed or more or with volume of 5 000 m 3 or more 4. Apartment buildings, tenements, dorms, multi-function buildings 6 storeyed or more or with volume of 5 000 m 3 or more 5. Nurseries, kindergartens, preschools ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 6. Schools and other educational institutions (except for nurseries) 3 storeyed or more or with volume of 5 000 m 3 or more 7. Buildings for medical examination and treatment and patient dormitories of hospitals, health stations, clinics, sanitariums, rehabilitation and orthopedic centers, centers for disease control and prevention, health centers, other health facilities according to applicable regulations [3] 3 storeyed or more or with volume of 3 000 m 3 or more 8. Theaters, cinemas, circuses Regardless of scale ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Convention and event centers Regardless of scale 10. Beauty salons, massage service buildings With volume of 1 500 m 3 or more 11. Clubs, amusement parks, zoos, aquariums 6 storeyed or more or with area of 10 000 m 2 or more 12. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 3 storeyed or more or with volume of 1 500 m 3 or more or situated in basement or semi-basement 13. Markets, shopping malls, supermarkets Regardless of scale 14. Electronics stores, department stores, convenience stores and stores for sale of highly flammable goods and substances With volume of 5 000 m 3 or more 15. Restaurants, food and beverage facilities ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 16. Guest houses, motels, inns and accommodation establishments founded according to prevailing regulations [1] 6 storeyed or more or with volume of 5 000 m 3 or more 17. Museums, libraries, art galleries, exhibition buildings, archive buildings, bookstores, fair buildings With volume of 5 000 m 3 or more 18. Post offices, radio and television stations, telecommunications facilities, communication equipment installations, data management and storage centers 6 storeyed or more or with volume of 5 000 m 3 or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Stadiums 6 storeyed or more or with volume of 5 000 m 3 or more 20. Sports stadiums, indoor sports palaces, fitness and sports centers, race tracks, shooting ranges and other sports facilities established in accordance with applicable laws [6], [8] 6 storeyed or more or with volume of 5 000 m 3 or more 21. Airports; air traffic control towers; seaports; inland ports; inland waterway ports Regardless of scale 22. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 6 storeyed or more or with volume of 5 000 m 3 or more 23. Component items of subway constructions; motor vehicle registries, stores for sale, repair and maintenance of automobiles, motorcycles and mopeds 6 storeyed or more or with volume of 5 000 m 3 or more 24. Car and moped garages and showrooms, premises for car and moped maintenance With volume of 3 000 m 3 or more 25. Nuclear facilities; facilities for production, trading, storage of industrial explosives and explosive precursors; warehouse of industrial explosives and explosive precursors; delivery ports for industrial explosives and explosive precursors; warehouses of weapons and support instruments; facilities for extraction, processing, production, transport, trading and storage of petroleum and petroleum products, and gas on land; petroleum and petroleum products terminals, gas terminals; delivery ports for petroleum and petroleum products, and gas; petrol and oil stores; petrol and oil filling stations; ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 26. Facilities for extraction, processing, production, transport, trading and storage of petroleum and petroleum products, and gas on land; petroleum and petroleum products terminals, gas terminals; delivery ports for petroleum and petroleum products, and gas; petrol and oil filling stations; highly flammable liquid filling stations; gas trading facilities Regardless of scale 27. Industrial facilities, production buildings, warehouses and constructions of similar purposes 27.1. Fire and explosion hazard classes A, B, C With area of 300 m 2 or with volume of 1 500 m 3 or more or 2 storeyed or more ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Fire and explosion hazard classes D, E With area of 500 m 2 or with volume of 2 500 m 3 or more 28. Electrical substations With voltage of 110 kV or more 29. Power plants Regardless of scale 30. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With volume of 1 000 m 3 or more 31. Warehouses of pyrophoric goods and objects or goods and objects whose packages are flammable With volume of 3 000 m 3 or more Annex D (normative) Equipment of fire-fighting vehicles Table D.1 - Equipment of fire-fighting vehicles ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Objects Scale Fire engines, pieces Fire ships, pieces Portable fire pumps, pieces 1 Warehouses 1.1 Storerooms ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 1.2 Storerooms At ministerial and sectoral levels 1 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Petroleum and petroleum products terminals With volume of more than 100 000 m 3 2 1.4 Petroleum and petroleum products terminals With volume of 50 000 to 100 000 m 3 1 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1.5 Petroleum and petroleum products terminals With volume of more than 50 000 m 3 1 2 Airports, seaports ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Airports International 3 2.2 Airports Domestic 2 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 2.3 Seaports Of special class, class I 2 1 2.4 Seaports ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 1 2.5 Seaports Class III 1 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Production facilities 3.1 Thermal power plants 1) 200 MW or more 1 3.2 Hydropower plants 1) ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 3.3 Thermal power plants and hydropower plants With capacity less than above capacity 1 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Nuclear power plants Regardless of capacity 2 3.6 Paper mills With capacity of more than 35 000 tonnes/year 1 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 3.7 Textile mills With capacity of more than 20 million square meters/year 1 3.8 Cement plants ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 3.9 Nitrogenous fertilizer plants With capacity of 180 000 tonnes or more /year 1 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Steel mills With capacity of 300 000 tonnes of billets or more/year 1 3.11 Paper mills, textile mills, cement plants, nitrogenous fertilizer plants, steel mills With capacity less than above capacity ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 3.12 Oil refineries, petrochemical and oil refineries, petrochemicals Regardless of capacity 2 3.13 Gas processing facilities ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 3.14 Mining facilities With capacity of 300 000 tonnes or more /year 1 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Gas processing facilities, mining facilities With capacity less than above capacity 1 4 Industrial parks, export-processing zones, hi-tech zones, industrial clusters 4.1 Industrial parks, export-processing zones, hi-tech zones ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 3 4.2 Industrial parks, export-processing zones, hi-tech zones With total area exceeding 150 ha but not exceeding 300 ha 2 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Industrial parks, export-processing zones, hi-tech zones, industrial clusters With total area exceeding 50 ha but not exceeding 150 ha 1 4.4 Industrial parks, export-processing zones, hi-tech zones, industrial clusters With total area of less than 50 ha ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 NOTES: 1) : For thermal power plants with capacity of 200 MW or more and power plants with capacity of 300 MW or more in the same area (or adjacent to each other) and under the same operator, only 01 fire engine is required. Annex E (normative) Equipment of rudimentary demolition tools Table E.1 - Equipment of rudimentary demolition tools No. Objects ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Quantity 1. Production buildings Regardless of scale 1 set of rudimentary demolition tools includes: + Rescue axe (2 kg in weight, 90 cm handle, high-carbon steel); + Crowbar (one sharp end, one flattened end; 100 cm in length); + Sledgehammer (high-carbon steel, 5 kg in weight, 50 cm handle); + Bolt cutter (60 cm in length, cutting load of 60 kg); ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Warehouses 3. Tenements, hotels, apartment buildings, food and beverage facilities 4. Administrative authorities, schools, hospitals 5. Railway stations, other public constructions 6. Theaters, cinemas, halls, karaoke, discotheque, bar and night club service buildings ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Permanent and semi-permanent markets, shopping malls Annex F (normative) Equipment of filter masks and self-contained breathing apparatus Table F.1 - Equipment of filter masks and self-contained breathing apparatus No. Objects Scale ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1. Hotels, guest houses, motels; inns and accommodation establishments founded according to regulations [1] (except for camping sites) 3 storeyed or more Regardless of scale Equip filter masks on all storeys with a required quantity of 1 piece/person (including guests and regular staff) 2. Facilities providing karaoke, discotheque, bar or night club services Regardless of scale Equip filter masks on all storeys. The quantity of masks on a storey depends on the number of persons present at the same time in a room with the largest area of that floor with a required quantity of 01 person/piece. 3. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of scale Equip at least 03 self-contained breathing apparatus 4. Airports, seaports. Regardless of scale 5. Petroleum and gas extraction and processing facilities Regardless of scale 6. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of scale 7. Weapon and explosive material production facilities and warehouses Regardless of scale 8. National stockpile; petroleum and petroleum products terminals With volume of more than 15 000 m 3 9. Hydropower plants ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 10. Thermal power plants 200 MW or more 11. Paper production facilities With capacity of 35 000 tonnes or more /year 12. Textile facilities With capacity of 25 million m 2 or more /year ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Nitrogenous fertilizer production facilities With capacity of 180 000 tonnes or more /year 14. Industrial parks, export-processing zones, hi-tech zones, industrial clusters With area of 50 ha or more 15. High-rise buildings With height of 75 m or more high or with 2 basements or more 16. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Regardless of scale Annex G (normative) Equipment of public address and evacuation instruction systems Table G.1 - Equipment of public address and evacuation instruction systems No. Objects Scale ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Homes and public constructions 10 storeyed or more or with 2 basements or more 2. Crowded public constructions: Theaters, cinemas, halls, karaoke, discotheque, bar and night club service buildings, hospitals, nursing homes and constructions of similar purposes 50 persons or more on 1 floor 3. Automobile and moped garages of enclosed type (including independent garages and garages in buildings of other purposes) With area of 18 000 m 2 or more 4. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 With area of 18 000 m 2 or more and 50 persons or more on 1 floor Annex H (normative) Equipment of initial fire fighting facilities Table H.1 - Equipment of initial fire fighting facilities No. Name of construction item Sand drum, m 3 ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Blanket 1x2(m), piece 1. Warehouses and stores containing liquid goods with an ignition temperature > 45°C 1 m 3 for every 350 m 2 of floor 2 pieces for every 350 m 2 of floor 1 piece for every 350 m 2 of floor 2. Production and processing workshops using mechanical equipment, drying ovens, welding machines ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 piece for every 200 m 2 of floor Bibliography [1]. Law on Tourism. [2]. Law on Education. [3]. Law on Medical Examination and Treatment [4]. Law on Fire Prevention and Fighting [5]. Law on Planning. [6]. Law on Physical Training and Sports. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 [8]. Law on Amendments to some Articles of the Law on Physical Training and Sports. [9]. Government’s Decree No. 136/2020/ND-CP dated November 24, 2020 providing guidelines for a number of Articles of Law on Fire Prevention and Fighting and Law on Amendments to Law on Fire Prevention and Fighting. [9]. Government’s Decree No. 149/2020/TT-BCA dated December 21, 2020 providing guidelines for Law on Fire Prevention and Fighting, Law on Amendments to Law on Fire Prevention and Fighting and the Government’s Decree No. 136/2020/ND-CP dated November 24, 2020 providing guidelines for a number of Articles of Law on Fire Prevention and Fighting and Law on Amendments to Law on Fire Prevention and Fighting. [11]. Circular No. 17/2022/TT-BCA dated February 05, 2022 on management, preservation, maintenance of fire prevention, firefighting and rescue equipment. [12]. Circular No. 147/2020/TT-BCA dated December 21, 2020 on fire safety and rescue measures for karaoke and nightclub establishments. [13]. Circular No. 150/TT-BCA dated December 31, 2020 on provision of fire prevention and fighting and rescue equipment to neighborhood watches, internal firefighting forces and specialized firefighting forces. [14]. Document No.20/VBHN dated May 09, 2014 consolidating Joint Circular joinly promulgated by Ministry of Trade and Ministry of Public Security No. 15/2001/TTLT-BTM-BCA dated May 10, 2021 on provision and management of fire-fighting facilities in petroleum and petroleum products terminals. [15]. Circular No. 04/2014/TT-BLDTBXH dated February 12, 2014 providing guidelines for implementation of regulations on personal protective equipment. [16]. QCVN 01:2020/BCT National technical regulation on design requirements for petrol filling stations; ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 [18]. QCVN 01:2019/BCT National technical regulation on safety in the process of producing, testing, performing check and acceptance, storage, transportation, use, disposal of industrial explosive materials and storage of explosive precursors. [19]. QCVN 10:2012/BLDTBXH National technical regulation on occupational safety with gas filters used in masks and respirators. [20]. QCVN 13:2018/BXD National technical regulation on Car Parking. [21]. TCXDVN 33:2006 Water Supply - Distribution System and Facilities. Design Standard. [22]. TCN 48:1996 Fire protection for trade and services enterprises - General provisions. [23]. TCN 58:1997 Fire protection for markets and shopping malls – Safety requirements for operation. [24]. TCVN 9310-3:2012 Fire protection - Vocabulary - Part 3: Fire detection and alarm. [25]. TCVN 9310-4:2012 Fire protection - Vocabulary - Part 4: Fire extinguishing equipment. [26]. TCVN 3254:1989. Fire safety - General requirements ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 [28]. TCVN 4245:1996 Amendment 1. Safety engineering requirements in production and utilization of oxygen, acetylene [29]. TCVN 4317:1986 Warehouses - Basic principles for design. [30]. TCVN 4879:1989 Group T - Fire protection - Safety signs. [31]. TCVN 5040:1990 Group T - Fire prevention and protection equipments - Graphical symbols used for protection schemes. [32]. TCXDVN 5065:1996 Hotels - Design standard. [33]. TCVN 5279:1990. Fire and explosion safely - Combustible dusts - General requirements. [34]. TCVN 13249:2020 (ISO 13943:2017) Fire safety - Vocabulary. [35]. TCVN 12823-4:2020 Mobile Offshore Units - Part 4: Safety Equipment and Fire Protection. [36]. TCVN 6160:1996 Fire protection - High-rise buildings - Design requirements. ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 [38]. TCVN 6174:1997 Amendment 2. Industrial explosion materials - Safety code for production, explosion test, check and acceptance. [39]. TCVN 6304:1997 Liquefied petroleum gas cylinders - Safety requirements in storage, handling and transportation. [40]. TCVN 6379:1998. Fire protection equipment - Fire hydrant - Technical requirements. [41]. Codes of Practice for minimum fire service installations and equipment and inspection and testing of installations and equipment. March, 1994. [42]. СП 486.1311500.2020 Перечень зданий, сооружений, помещений и оборудования, подлежащих защите автоматическими установками пожаротушения и системами пожарной сигнализации. (Fire protection systems. Fire alarm systems and automation of fire protection systems. Norms and rules of design. The list of buildings, structures, premises and equipment, subject to protection by automatic extinguishing and fire alarm systems. Russian Emergency Situations Ministry). [43]. СП 8.13130.2020 Требования пожарной безопасности. Наружное противопожарное водоснабжение. (The fire protection systems. Outdoor fire-fighting water supply. Fire safety requirements. Russian Emergency Situations Ministry). [44]. СП 10.13130.2020 Системы противопожарной защиты. Внутренний противопожарный водопровод. (Fire protection system. Installation of standpipe and hose systems. Designing and regulations rules. Russian Emergency Situations Ministry). [45]. KOFEIS 0106 (Korea). Index ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 1 Scope 2 Normative references 3 Terms and definitions 4 General provisions 5 Regulations on Equipment and installation of fire protection equipment and systems Annex A (normative) Equipment of automatic fire alarm systems, local fire alarms devices and automatic fire extinguishing system Annex B (normative) Equipment of indoor hose reel systems Annex C (normative) Equipment of outdoor hose reel systems Annex D (normative) Equipment of fire-fighting vehicles ... ... ... Bạn phải đăng nhập hoặc đăng ký Thành Viên TVPL Pro để sử dụng được đầy đủ các tiện ích gia tăng liên quan đến nội dung TCVN. Mọi chi tiết xin liên hệ: ĐT: (028) 3930 3279 DĐ: 0906 22 99 66 Annex F (normative) Equipment of filter masks and self-contained breathing apparatus Annex G (normative) Equipment of public address and evacuation instruction systems Annex H (normative) Equipment of initial fire fighting facilities Bibilography