Project: datamanagement
Issue DM-2376: revise and circulate data center requirements note
Reconvert the ~10 TBD's in the priori version of the note — I’ve kept the stipulation that end of service-lifee stuff will leave these spaces but added an appendix that “this is what the central space should provide” My understanding is there are now discussions on whether that central space will exist of not. The requirements can be promoted to center requirements no central space is evient. — The maximal average weight for a rack was computed from LDM-144 and is given. — There are more cu ft estimates for the need to dispose of dunnage and packing material. — TBD’s w.r.t overhead cabling are specificed. — The non- LSST requrements are in there, and have been as far as I am able to ascertain them from champaign urbana. Ron has been stating requirements as “rows” I have never fixed row length thinking that is for the designer to do. We’ve stated that rows are shareable, but racks are not. so what’s in the docs is definitive unless/until non LSST requirements can be stated in the same terms. "Shall support 16 racks for the NOAO tenant". is what I had. power requirements as per the common space, becasue we want a maximally flexible space.
Story points: 2