## 4 Reliability Analysis of Electric Power Network
### Results of Test Calculations  
Before the reliability indices have been calculated, the load \begin{table}
\begin{tabular}{c c c c} \hline \hline \multicolumn{4}{c}{**Variant: DNMG\_1**} \\ \hline
**Index** & **Case\_1** & **Case\_2** & **Case\_3** & **Case\_4** & **Case\_5** \\ \hline SAIFI [1/a] & 0.081363 & 0.080969 & 0.080475 & 0.080476 & 0.079877 \\ CAIFI [1/a] & 0.081363 & 0.080969 & 0.080475 & 0.080476 & 0.079877 \\ SAID [h] & 0.715 & 0.715 & 0.715 & 0.715 & 0.715 \\ CAID [h] & 8.788 & 8.831 & 8.885 & 8.885 \\ ASAI [-] & 0.9999183769 & 0.9999183769 & 0.9999183769 & 0.9999183769 \\ ASUI [-] & 0.000016231 & 0.000016231 & 0.000016231 & 0.00016231 \\ EENS [MWh/a] & 9.376 & 9.376 & 9.376 & 9.376 \\ \hline \multicolumn{4}{c}{Variant: AMDN\_3} \\ \hline Index & **Case\_1** & **Case\_2** & **Case\_4** & **Case\_5** \\ \hline SAIFI [1/a] & 0.073720 & 0.076901 & 0.080882 & 0.080871 & 0.080003 \\ CAIFI [1/a] & 0.213266 & 0.222469 & 0.233984 & 0.233954 & 0.231441 \\ SAID [h] & 0.700 & 0.700 & 0.700 & 0.700 & 0.700 \\ CAID [h] & 9.498 & 9.105 & 8.657 & 8.658 & 8.752 \\ ASAI [-] & 0.9999200708 & 0.999920708 & 0.9999200708 & 0.9999200708 & 0.9999200708 \\ ASUI [-] & 0.0000799292 & 0.0000799292 & 0.0000799292 & 0.0000799292 \\ EENS [MWh/a] & 9.283 & 9.283 & 9.283 & 9.283 & 9.283 \\ \hline \hline \end{tabular}
\end{table} 
Table 11: Reliability system indices for DNMG structure (Figure 11). \begin{table}
\begin{tabular}{c c c c c} \hline \hline \multicolumn{4}{c}{**Variant: AMDN\_1**} \\ \hline
**Index** & **Case\_1** & **Case\_2** & **Case\_3** & **Case\_4** & **Case\_5** \\ \hline SAIFI [1/a] & 0.087041 & 0.081571 & 0.074728 & 0.074746 & 0.076239 \\ CAIFI [1/a] & 0.087041 & 0.081571 & 0.074728 & 0.074746 & 0.076239 \\ SAID [h] & 0.661 & 0.661 & 0.661 & 0.661 \\ CAID [h] & 7.593 & 8.103 & 8.845 & 8.842 & 8.669 \\ ASAI [-] & 0.9999245511 & 0.9999245511 & 0.9999245511 & 0.9999245511 \\ ASUI [-] & 0.0000754489 & 0.0000754489 & 0.0000754489 & 0.0000754489 \\ EENS [MWh/a] & 9.037 & 9.037 & 9.037 & 9.037 & 9.037 \\ \hline \multicolumn{4}{c}{Variant: AMDN\_2} \\ \hline Index & **Case\_1** & **Case\_2** & **Case\_3** & **Case\_4** & **Case\_5** \\ \hline SAIFI [1/a] & 0.081363 & 0.080969 & 0.080475 & 0.080476 & 0.079877 \\ CAIFI [1/a] & 0.081363 & 0.080969 & 0.080475 & 0.080476 & 0.079877 \\ SAID [h] & 0.715 & 0.715 & 0.715 & 0.715 & 0.715 \\ CAID [h] & 8.788 & 8.831 & 8.885 & 8.885 & 8.952 \\ ASAI [-] & 0.9999183769 & 0.9999183769 & 0.9999183769 & 0.9999183769 \\ ASUI [-] & 0.000016231 & 0.000016231 & 0.000016231 & 0.000016231 & 0.000016231 \\ EENS [MWh/a] & 9.376 & 9.376 & 9.376 & 9.376 & 9.376 \\ \hline \multicolumn{4}{c}{Variant: AMDN\_3} \\ \hline Index & **Case\_1** & **Case\_2** & **Case\_3** & **Case\_4** & **Case\_5** \\ \hline SAIFI [1/a] & 0.073720 & 0.076901 & 0.080882 & 0.080871 & 0.080003 \\ CAIFI [1/a] & 0.213266 & 0.222469 & 0.233984 & 0.233954 & 0.231441 \\ SAID [h] & 0.700 & 0.700 & 0.700 & 0.700 & 0.700 \\ CAID [h] & 9.498 & 9.105 & 8.657 & 8.658 & 8.875 \\ ASAI [-] & 0.9999200708 & 0.999920708 & 0.999920708 & 0.9999200708 & 0.9999200708 \\ ASUI [-] & 0.0000799292 & 0.0000799292 & 0.0000799292 & 0.0000799292 \\ EENS [MWh/a] & 9.283 & 9.283 & 9.283 & 9.283 & 9.283 \\ \hline \hline \end{tabular}
\end{table} 
Table 12: Reliability system indices for AMDN structure (Figure 11). from no. 5 to no. 1 (UDN_2) and no. 8 (UDN_3). In each variant, three cases of different power generation levels of the considered PVPP and BES are analyzed, i.e., Case_1--51 kW, Case_2--100 kW and Case_3--510 kW. The other DG sources do not change the location in all variants and the power generation values in all cases. There are also three variants of DG unit location to be considered. Based on RDN_1 variant as a basic RDN structure (see Figure 10), a node the WTPP and BES are connected to changes from no. 72 to no. 43 (RDN_2) and no. 71 (RDN_3). In each variant, three cases of different power generation levels of the considered WTPP and BES are analyzed, i.e., Case_1--2.4 MW, Case_2--1.6 MW and Case_3--0.8 MW.