## 2 Case Study Location and Building Data
### Building Information: Outpatient Medical Center
In facilities for the care of patients, health, or other small-sized related matters, it has been verified that the energy consumption for air conditioning is around 60% [24]. \begin{table}
\begin{tabular}{c c c c c c c c c} \hline \hline \multirow{2}{*}{**Envelope**} & \multirow{2}{*}{\begin{tabular}{c} **U-Value** \\ **(W/(m2 K))** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Total Solar** \\ **Transmission** \\ **(\%)** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Light** \\ **Transmission** \\ **(\%)** \\ \end{tabular} } & \multirow{2}{*}{**Materials**} & \multirow{2}{*}{\begin{tabular}{c} **Width** \\ **(m)** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Thermal** \\ **Conductivity** \\ **(W/(m-K))** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Specific** \\ **Heat** \\ **(J/(kg-K))** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Density** \\ **(kg/m3)** \\ \end{tabular} } \\ \hline Windows & 5.894 & 79.3 & 88.1 & \begin{tabular}{c} Clear \\ simple glass \\ \end{tabular} & 0.003 & 0.96 & 800 & 2500 \\ \hline \multirow{2}{*}{\begin{tabular}{c} **Surface material** \\ **Surface material** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Solar reflectance (\%)** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Thermal** \\ **absorbance (\%)** \\ \end{tabular} } & \multirow{2}{*}{\
\begin{tabular}{c} **Solar absorbance (\%)** \\ \end{tabular} } & \multirow{2}{*}{
\begin{tabular}{c} **Solar absorbance (\%)** \\ \end{tabular} } \\ \hline gypsum plaster & 30 & & 90 & 70 & 70 \\ \hline \hline \end{tabular}
\end{table} 
Table 1: _Cont._ \begin{table}
\begin{tabular}{c c c c c c c c} \hline \hline \multirow{2}{*}{\begin{tabular}{c} **Zone** \\ **(m)** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Width** \\ **(m)** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Length** \\ **(m)** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **High** \\ **(m)** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Electric Devices** \\ **Lightning** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Air** \\ **Conditioning** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Medical** \\ **Equipment** \\ \end{tabular} } & \multirow{2}{*}{\begin{tabular}{c} **Office** \\ **Equipment** \\ \end{tabular} } \\ \hline \multirow{2}{*}{\begin{tabular}{c} Ophthalmological \\ office \\ \end{tabular} } & \multirow{2}{*}{3.38} & \multirow{2}{*}{6.69} & \multirow{2}{*}{4.60} & \multicolumn{2}{c}{11 plugs,} & \multirow{2}{*}{0.12} & \multirow{2}{*}{1.22} & \multirow{2}{*}{-} \\  & & & & \multicolumn{2}{c}{6 LED lamps 20 W,} & \multirow{2}{*}{0.12} & \multirow{2}{*}{1.22} & \multirow{2}{*}{-} \\  & & & & \multicolumn{2}{c}{4} & television, computer & & \\  & & & & and printer, & & & & \\ \hline \multirow{2}{*}{\begin{tabular}{c} Eye care \\ \end{tabular} } & \multirow{2}{*}{5.13} & \multirow{2}{*}{4.76} & \multirow{2}{*}{4.73} & \multirow{2}{*}{6 plugs, 7 LED lamps} & \multirow{2}{*}{0.14} & \multirow{2}{*}{1.28} & \multirow{2}{*}{-} \\  & & & & & \multicolumn{2}{c}{20 W, computer} & \multirow{2}{*}{0.12} & \multirow{2}{*}{-} & \multirow{2}{*}{-} \\  & & & & and printer, & & & \\ \hline \multirow{2}{*}{\
\begin{tabular}{c} Reception \\ \end{tabular} } & \multirow{2}{*}{2.62} & \multirow{2}{*}{4.76} & \multirow{2}{*}{4.73} & \multirow{2}{*}{
\begin{tabular}{c} 4 plugs, 6 LED lamps \\ 20 W \\ \end{tabular} } & \multirow{2}{*}{0.12} & \multirow{2}{*}{-} & \multirow{2}{*}{-} & \multirow{2}{*}{-} \\  & & & & & & \\ \end{tabular}
\end{table} 
Table 2: Installed loads and electrical energy consumption of the medical center based on the energy audit. For its part, Figure 3 illustrates the baseline of electricity consumption and the final use of energy measured throughout 2022 for the outpatient medical center. According to Figure 3a, the highest energy consumption occurs from May to October, exceeding 1.4 MWh per month.