# Study on the Influence of Dust Removal Fan Structure Parameters on Dust Removal Performance
###### Abstract  
In order to study the influence of various parts of the structure of a wet dust removal fan for mining (including the number of driving impeller blades, the airfoil of the driving impeller blades, the number of driven impeller blades, the rear guide vane, the swirl guide vane, and the length of the outlet section) on dust removal performance, a wet dust removal fan for mining was modeled according to different structural parameters. The internal flow field and dust removal of the fan were then numerically simulated using the Computational Fluid Dynamics (CFD) method. The results show that after the airflow passes through the swirl guide vane of the dust removal fan, there is an obvious swirl flow in the exit section of the dust removal fan. Under the action of centrifugal force, a large amount of dust is collected on the side wall of the exit section. With the increase in the number of driving impeller blades, the total pressure efficiency, static pressure efficiency, and dust removal efficiency of the dust removal fan decrease. When the driving impeller blade adopts the C-4 airfoil, the total pressure efficiency and static pressure efficiency of the dust removal fan are higher but the dust removal efficiency is lower than that of the same thickness circular plate airfoil. With the increase in the number of driven impeller blades, the power of the driving impeller shaft of the dust removal fan gradually increases; the total pressure and static pressure values first increase and then decrease; and the driven impeller speed, total pressure efficiency, static pressure efficiency, and dust removal efficiency gradually decrease. Adding the rear guide vane structure can improve the total pressure efficiency and static pressure efficiency of the dust removal fan but will reduce the dust removal efficiency of the dust removal fan. The increase in the swirl guide vane structure will reduce the total pressure efficiency and static pressure efficiency of the dust removal fan but the dust removal efficiency will be significantly improved. The extension of the outlet section of the dust removal fan will reduce the total pressure efficiency and static pressure efficiency of the dust removal fan, but the stun removal efficiency will increase. In this paper, by changing the structural parameters of the dust removal fan and establishing different models for numerical simulation and analysis, the influence law of the structural parameters of the dust removal fan on the dust removal performance is obtained, providing a way to improve the performance of the dust removal fan.  
dust removal fan; impeller; CFD simulation; moving grid method; dust removal efficiency Article  
[PERSON], [PERSON], [PERSON], X. Study on the Influence of Dust Removal Fan Structure Parameters on Dust Removal Performance  
1 College of Mechanical and Vehicle Engineering, Taiyuan University of Technology, Taiyuan 030024, China; [EMAIL_ADDRESS]  
2 Sharxi Provincial Engineering Laboratory for Mine Fluid Control, Taiyuan 030024, China  
3 School of Design, South China University of Technology, Guangzhou 510006, China; [EMAIL_ADDRESS]  
* Correspondence: [EMAIL_ADDRESS]