2003/629/EC: Commission Decision of 27 August 2003 amending Decision 2000/367/EC establishing a classification system for resistance-to-fire performance for construction products, as regards the inclusion of smoke and heat control products (Text with EEA relevance) (notified under document number C(2003) 2851)
Date: 2003-08-27
Institutions: European Commission
Subjects: approximation of laws, building, building materials, fire protection, product safety

30.8.2003

EN

Official Journal of the European Union

L 218/51

II

(Acts whose publication is not obligatory)

COMMISSION

COMMISSION DECISION

of 27 August 2003

amending Decision 2000/367/EC establishing a classification system for
resistance-to-fire
performance for construction products, as regards the inclusion of smoke and heat control
products

(notified under document number C(2003) 2851)

(Text with EEA relevance)

(2003/629/EC)

THE COMMISSION OF THE EUROPEAN COMMUNITIES,

Having regard to the Treaty establishing the European
Community,

Having regard to Council Directive 89/106/EEC of 21
December 1988 on the approximation of laws, regulations and
administrative provisions of
the Member States relating to
construction products (1), as amended by Directive 93/68/
EEC (2), and in particular Article 20(2) thereof,

Whereas:

(1)

Commission Decision 2000/367/EC of 3 May 2000
implementing Council Directive 89/106/EEC as regards
the classification of the resistance-to-fire performance of
construction products, construction works and parts
thereof (3) should, for the purposes of its adaptation to
technical progress, also cover smoke and heat control
products.

(2)

Decision 2000/367/EC should therefore be amended
accordingly.

(3)

The measures provided for in this Decision are in accor-
dance with the opinion of the Standing Committee on
Construction,

HAS ADOPTED THIS DECISION:

Article 1

The Annex to Decision 2000/367/EC is amended in accordance
with the Annex to this Decision.

This Decision is addressed to the Member States.

Article 2

Done at Brussels, 27 August 2003.

For the Commission

Erkki LIIKANEN

Member of the Commission

(1) OJ L 40, 11.2.1989, p. 12.
(2) OJ L 220, 30.8.1993, p. 1.
(3) OJ L 133, 6.6.2000, p. 26.

L 218/52

EN

Official Journal of the European Union

30.8.2003

ANNEX

The Annex to Decision 2000/367/EC is amended as follows.

1. The section entitled ‘SYMBOLS’ is amended as follows:

(a) in the table, the following rows are added:

‘D

DH

F

B

Stability duration under constant temperature

Stability duration under the standard time-temperature curve

Functionality of powered smoke and heat ventilators

Functionality of natural smoke and heat ventilators’

(b) in note 2, ‘EN 13501-4’ is inserted after ‘EN 13501-3’.

2. The section entitled ‘Classifications’ is amended as follows:

(a) point 2 is amended as follows:

(i) in the table applying to walls, classes RE360, REI360, REI-M360 and REW360 are added;
(ii) in the classification part of the table applying to floors and roofs:
— above row ‘RE’, a new row ‘R’ is inserted with class R30,
— classes RE360 and REI360 are added;

(b) in point 3 the words ‘fire protective coatings, claddings and screens’ are replaced by the words ‘fire protective

coatings, boards, renderings, claddings and screens’;

(c) point 4 is amended as follows:

(i) in the table applying to ‘partitions (including those incorporating uninsulated portions)’, classes EI-M180 and

EI-M240 are added;

(ii) in the table applying to ‘closures for conveyors and trackbound transportation systems’, the text relating to
‘Notes’ is replaced by the following: ‘The I classification is completed by the addition of the suffix “1” or “2”
to indicate which definition of insulation is used. An I classification shall be generated for those cases where
the test specimen is a pipe or duct configuration with no assessment of the closure for the conveyor system.
The addition of the symbol “C” indicates that the product also satisfies the “self-closing” criterion (pass/fail
test) (*).’;

(iii) the table applying to ‘wall and ceiling coverings’ is replaced by the following:

‘Applies to

Standard(s)

Classification:

K1

K2

10

10

Wall and ceiling coverings

EN 13501-2; EN 14135

30

60

Notes The suffixes “1” and “2” indicate which substrates, fire behaviour criteria and extension rules are used in this classifica-

tion.’

(d) the following point 7 is added:

‘7. Products to be used in smoke and heat control systems

The standards cited in this section are under preparation and may be due to revision or upgrade.

Applies to

Standard(s)

Classification: —

E300

E600

Single compartment smoke control ducts

EN 13501-4; EN 1363-1, 2, 3; EN 1366-9 EN 12101-7

30

30

60

60

90

90

120

120

Notes The classification is completed by the suffix “single” to indicate suitability for single compartment use only.

In addition, the symbols, “ve” and/or “ho” indicate the suitability for vertical and/or horizontal use.
“S” indicates a leakage rate of less than 5 m3/hr/m2 (All ducts without an “S” classification must have a leakage rate of
less than 10 m3/hr/m2)
“500”, “1 000”, “1 500” indicate the suitability for use up to these values of pressure, measured at ambient.

30.8.2003

EN

Official Journal of the European Union

L 218/53

Applies to

Standard(s)

Classification: —

Multi-compartment fire resistant smoke control ducts

EN 13501-4; EN 1363-1, 2, 3; EN 1366-8; EN 12101-7

EI

30

60

90

120

Notes The classification is completed by the suffix “multi” to indicate suitability for multi-compartment use.
In addition, the symbols “ve” and/or “ho” indicate the suitability for vertical and/or horizontal use.
“S” indicates a leakage rate of less than 5 m3/hr/m2 (All ducts without an “S” classification must have a leakage rate of
less than 10 m3/hr/m2)
“500”, “1 000”, “1 500” indicate the suitability for use up to these values of pressure, measured at ambient.

Applies to

Standard(s)

Classification: —

E300

E600

Single compartment smoke control dampers

EN 13501-4; EN 1363-1, 3; EN 1366- 9, 10; EN 12101-8

30

30

60

60

90

90

120

120

Notes The classification is completed by the suffix “single” to indicate suitability for single compartment use.

“HOT 400/30” (high operational temperature) indicates that the damper has the ability to be opened or closed during a
period of 30 minutes under temperature conditions below 400 °C (to be used only with E600 classification).
“ved”, “vew” “vedw” and/or “hod”, “how” “hodw” indicate the suitability for vertical and/or horizontal use, together with
mounting in a duct or in a wall or both respectively.
“S” indicates a leakage rate of less than 200 m3/hr/m2. All dampers without an “S” classification must have a leakage
rate of less than 360 m3/hr/m2. All damper less than 200 m3/hr/m2 take this value, all dampers between 200 m3/hr/m2
and 360 m3/hr/m2 take the 360 m3/hr/m2 value. Leakage rates are both at ambient and elevated temperatures.
“500”, “1 000”, “1 500” indicates the suitability for use up to at these values of under pressure, measured at ambient.
“AA” or “MA” indicates automatic activation or manual intervention
“i→o”, “i ←o”, “i (cid:3)o”, indicates the performance criteria are satisfied from inside to outside, outside to inside or both
respectively.
“C300”, “C10000”, “Cmod” indicates the suitability of the damper for use in smoke control only systems combined smoke
control and environmental systems, or modulating dampers used in combined smoke control and environmental
systems respectively.

Applies to

Standard(s)

Classification:

EI

E

Multi-compartment fire resistant smoke control dampers

EN 13501-4; EN 1363-1, 2, 3; EN 1366-2, 8, 10; EN 12101-8

30

30

60

60

90

90

120

120

Notes The classification is completed by the suffix “multi” to indicate suitability for multi-compartment use.

“HOT 400/30” (high operational temperature) indicates that the damper has the ability to be opened or closed during a
period of 30 minutes under temperature conditions below 400 °C.
“ved”, “vew” “vedw” and/or “hod”, “how” “hodw” indicate the suitability for vertical and/or horizontal use, together with
mounting in a duct or in a wall or both respectively.
“S” indicates a leakage rate of less than 200 m3/hr/m2. All dampers without an “S” classification must have a leakage
rate of less than 360 m3/hr/m2. All damper less than 200 m3/hr/m2 take this value, all dampers between 200 m3/hr/m2
and 360 m3/hr/m2 take the 360 m3/hr/m2 value. Leakage rates are both at ambient and elevated temperatures.
“500”, “1 000”, “1 500” indicates the suitability for use up to these values of pressure, measured at ambient.
“AA” or “MA” indicates automatic activation or manual intervention
“i→o”, “i ←o”, “i (cid:3)o”, indicates that the performance criteria are satisfied from inside to outside, outside to inside or
both, respectively.
“C300”, “C10000”, “Cmod” indicates the suitability of the damper for use in smoke control only systems, combined smoke
control and environmental systems, or modulating dampers used in combined smoke control and environmental
systems, respectively.

L 218/54

EN

Official Journal of the European Union

30.8.2003

Applies to

Standard(s)

Classification: D

D600

DH

Smoke barriers

EN 13501-4; EN 1363-1, 2; EN 12101-1

30

30

60

60

90

90

120

120

A

A

Notes ‘A’ can be any time over 120 minutes.

Applies to

Standard(s)

Classification: F

F200

F300

F400

F600

F842

Notes

Applies to

Standard(s)

Classification: B

B300

B600

Bθ

Powered smoke and heat exhaust ventilators (fans), connecting joints

EN13501-4; EN 1363-1; EN 12101-3; ISO 834-1

120

90

120

60

60

30

Natural smoke and heat exhaust ventilators

EN 13501-4; EN 1363-1; EN 12101-2

30

30

30

Notes Where θ indicates the exposure condition (temperature).’